Sample records for novovoronezh-3 reactor

1. Accident transient processes at NPPs with the WWER type reactors

International Nuclear Information System (INIS)

Bukrinskij, A.M.

1982-01-01

Thermal-physical and nuclear-physical transient processes at NPPs with the WWER type reactors during accidents with the main technological equipment failures and the accidents with loss of coolant in the primary and secondary coolant circuits are considered. Mathematical methods used for these processes modelling is described. Examples of concrete calculations for accidents with different failures are given. Comparative analysis of the results of dynamic tests at the Novo-Voronezh-3 reactor is presented. It is concluded that the modern NPP design is impossible without application of mathematical modelling methods. The mathematical modelling of transients is also necessary for proper and safe NPP operation. Mathematical modelling of accidents at NPPs is a comparatively new method of investigation. Its success and development are completely based on the progress in modern computer development. With their improvement the mathematical models will become more complicate and adequacy of real physical process representation by their means will increase

2. Reactor

International Nuclear Information System (INIS)

Toyama, Masahiro; Kasai, Shigeo.

1978-01-01

Purpose: To provide a lmfbr type reactor wherein effusion of coolants through a loop contact portion is reduced even when fuel assemblies float up, and misloading of reactor core constituting elements is prevented thereby improving the reactor safety. Constitution: The reactor core constituents are secured in the reactor by utilizing the differential pressure between the high-pressure cooling chamber and low-pressure cooling chamber. A resistance port is formed at the upper part of a connecting pipe, and which is connect the low-pressure cooling chamber and the lower surface of the reactor core constituent. This resistance part is formed such that the internal sectional area of the connecting pipe is made larger stepwise toward the upper part, and the cylinder is formed larger so that it profiles the inner surface of the connecting pipe. (Aizawa, K.)

3. Reactor

International Nuclear Information System (INIS)

Ikeda, Masaomi; Kashimura, Kazuo; Inoue, Kazuyuki; Nishioka, Kazuya.

1979-01-01

Purpose: To facilitate the construction of a reactor containment building, whereby the inspections of the outer wall of a reactor container after the completion of the construction of the reactor building can be easily carried out. Constitution: In a reactor accommodated in a container encircled by a building wall, a space is provided between the container and the building wall encircling the container, and a metal wall is provided in the space so that it is fitted in the building wall in an attachable or detatchable manner. (Aizawa, K.)

4. Reactors

DEFF Research Database (Denmark)

Shah, Vivek; Vaz Salles, Marcos António

2018-01-01

The requirements for OLTP database systems are becoming ever more demanding. Domains such as finance and computer games increasingly mandate that developers be able to encode complex application logic and control transaction latencies in in-memory databases. At the same time, infrastructure...... engineers in these domains need to experiment with and deploy OLTP database architectures that ensure application scalability and maximize resource utilization in modern machines. In this paper, we propose a relational actor programming model for in-memory databases as a novel, holistic approach towards......-level function calls. In contrast to classic transactional models, however, reactors allow developers to take advantage of intra-transaction parallelism and state encapsulation in their applications to reduce latency and improve locality. Moreover, reactors enable a new degree of flexibility in database...

5. Reactor

International Nuclear Information System (INIS)

Fujibayashi, Toru.

1976-01-01

Object: To provide a boiling water reactor which can enhance a quake resisting strength and flatten power distribution. Structure: At least more than four fuel bundles, in which a plurality of fuel rods are arranged in lattice fashion which upper and lower portions are supported by tie-plates, are bundled and then covered by a square channel box. The control rod is movably arranged within a space formed by adjoining channel boxes. A spacer of trapezoidal section is disposed in the central portion on the side of the channel box over substantially full length in height direction, and a neutron instrumented tube is disposed in the central portion inside the channel box. Thus, where a horizontal load is exerted due to earthquake or the like, the spacers come into contact with each other to support the channel box and prevent it from abnormal vibrations. (Furukawa, Y.)

6. Nuclear reactors

International Nuclear Information System (INIS)

Barre, Bertrand

2015-10-01

After some remarks on the nuclear fuel, on the chain reaction control, on fuel loading and unloading, this article proposes descriptions of the design, principles and operations of different types of nuclear reactors as well as comments on their presence and use in different countries: pressurized water reactors (design of the primary and secondary circuits, volume and chemistry control, backup injection circuits), boiling water reactors, heavy water reactors, graphite and boiling water reactors, graphite-gas reactors, fast breeder reactors, and fourth generation reactors (definition, fast breeding). For these last ones, six concepts are presented: sodium-cooled fast reactor, lead-cooled fast reactor, gas-cooled fast reactor, high temperature gas-cooled reactor, supercritical water-cooled reactor, and molten salt reactor

7. H Reactor

Data.gov (United States)

Federal Laboratory Consortium — The H Reactor was the first reactor to be built at Hanford after World War II.It became operational in October of 1949, and represented the fourth nuclear reactor on...

8. Reactor Physics

International Nuclear Information System (INIS)

Ait Abderrahim, A.

2002-01-01

SCK-CEN's Reactor Physics and MYRRHA Department offers expertise in various areas of reactor physics, in particular in neutron and gamma calculations, reactor dosimetry, reactor operation and control, reactor code benchmarking and reactor safety calculations. This expertise is applied in the Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 materials testing reactor dosimetry, and the preparation and interpretation of irradiation experiments by means of neutron and gamma calculations. The activities of the Fuzzy Logic and Intelligent Technologies in Nuclear Science programme cover several domains outside the department. Progress and achievements in these topical areas in 2001 are summarised

9. Reactor Physics

Energy Technology Data Exchange (ETDEWEB)

Ait Abderrahim, A

2001-04-01

The Reactor Physics and MYRRHA Department of SCK-CEN offers expertise in various areas of reactor physics, in particular in neutronics calculations, reactor dosimetry, reactor operation, reactor safety and control and non-destructive analysis of reactor fuel. This expertise is applied in the Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 reactor dosimetry, and the preparation and interpretation of irradiation experiments by means of neutron and gamma calculations. The activities of the Fuzzy Logic and Intelligent Technologies in Nuclear Science programme cover several domains outside the department. Progress and achievements in these topical areas in 2000 are summarised.

10. Reactor Physics

Energy Technology Data Exchange (ETDEWEB)

Ait Abderrahim, A

2002-04-01

SCK-CEN's Reactor Physics and MYRRHA Department offers expertise in various areas of reactor physics, in particular in neutron and gamma calculations, reactor dosimetry, reactor operation and control, reactor code benchmarking and reactor safety calculations. This expertise is applied in the Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 materials testing reactor dosimetry, and the preparation and interpretation of irradiation experiments by means of neutron and gamma calculations. The activities of the Fuzzy Logic and Intelligent Technologies in Nuclear Science programme cover several domains outside the department. Progress and achievements in these topical areas in 2001 are summarised.

11. Reactor Physics

International Nuclear Information System (INIS)

Ait Abderrahim, A.

2001-01-01

The Reactor Physics and MYRRHA Department of SCK-CEN offers expertise in various areas of reactor physics, in particular in neutronics calculations, reactor dosimetry, reactor operation, reactor safety and control and non-destructive analysis of reactor fuel. This expertise is applied in the Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 reactor dosimetry, and the preparation and interpretation of irradiation experiments by means of neutron and gamma calculations. The activities of the Fuzzy Logic and Intelligent Technologies in Nuclear Science programme cover several domains outside the department. Progress and achievements in these topical areas in 2000 are summarised

12. Reactor operation

CERN Document Server

Shaw, J

2013-01-01

Reactor Operation covers the theoretical aspects and design information of nuclear reactors. This book is composed of nine chapters that also consider their control, calibration, and experimentation.The opening chapters present the general problems of reactor operation and the principles of reactor control and operation. The succeeding chapters deal with the instrumentation, start-up, pre-commissioning, and physical experiments of nuclear reactors. The remaining chapters are devoted to the control rod calibrations and temperature coefficient measurements in the reactor. These chapters also exp

13. Reactor safeguards

CERN Document Server

Russell, Charles R

1962-01-01

Reactor Safeguards provides information for all who are interested in the subject of reactor safeguards. Much of the material is descriptive although some sections are written for the engineer or physicist directly concerned with hazards analysis or site selection problems. The book opens with an introductory chapter on radiation hazards, the construction of nuclear reactors, safety issues, and the operation of nuclear reactors. This is followed by separate chapters that discuss radioactive materials, reactor kinetics, control and safety systems, containment, safety features for water reactor

14. Nuclear reactors

International Nuclear Information System (INIS)

Middleton, J.E.

1977-01-01

Reference is made to water cooled reactors and in particular to the cooling system of steam generating heavy water reactors (SGHWR). A two-coolant circuit is described for the latter. Full constructural details are given. (U.K.)

15. Reactor decommissioning

International Nuclear Information System (INIS)

Lawton, H.

1984-01-01

A pioneering project on the decommissioning of the Windscale Advanced Gas-cooled Reactor, by the UKAEA, is described. Reactor data; policy; waste management; remote handling equipment; development; and recording and timescales, are all briefly discussed. (U.K.)

16. RA Reactor

International Nuclear Information System (INIS)

1978-02-01

In addition to basic characteristics of the RA reactor, organizational scheme and financial incentives, this document covers describes the state of the reactor components after 18 years of operation, problems concerned with obtaining the licence for operation with 80% fuel, problems of spent fuel storage in the storage pool of the reactor building and the need for renewal of reactor equipment, first of all instrumentation [sr

17. Multiregion reactors

International Nuclear Information System (INIS)

Moura Neto, C. de; Nair, R.P.K.

1979-08-01

The study of reflected reactors can be done employing the multigroup diffusion method. The neutron conservation equations, inside the intervals, can be written by fluxes and group constants. A reflected reactor (one and two groups) for a slab geometry is studied, aplying the continuity of flux and current in the interface. At the end, the appropriated solutions for a infinite cylindrical reactor and for a spherical reactor are presented. (Author) [pt

18. Nuclear reactor

International Nuclear Information System (INIS)

1994-01-01

Liquid metals such as liquid metal sodium are filled in a reactor container as primary coolants. A plurality of reactor core containers are disposed in a row in the circumferential direction along with the inner circumferential wall of the reactor container. One or a plurality of intermediate coolers are disposed at the inside of an annular row of the reactor core containers. A reactor core constituted with fuel rods and control rods (module reactor core) is contained at the inside of each of the reactor core containers. Each of the intermediate coolers comprises a cylindrical intermediate cooling vessels. The intermediate cooling vessel comprises an intermediate heat exchanger for heat exchange of primary coolants and secondary coolants and recycling pumps for compulsorily recycling primary coolants at the inside thereof. Since a plurality of reactor core containers are thus assembled, a great reactor power can be attained. Further, the module reactor core contained in one reactor core vessel may be small sized, to facilitate the control for the reactor core operation. (I.N.)

19. Nuclear power reactors

International Nuclear Information System (INIS)

1982-11-01

After an introduction and general explanation of nuclear power the following reactor types are described: magnox thermal reactor; advanced gas-cooled reactor (AGR); pressurised water reactor (PWR); fast reactors (sodium cooled); boiling water reactor (BWR); CANDU thermal reactor; steam generating heavy water reactor (SGHWR); high temperature reactor (HTR); Leningrad (RMBK) type water-cooled graphite moderated reactor. (U.K.)

20. Research reactors

International Nuclear Information System (INIS)

Merchie, Francois

2015-10-01

This article proposes an overview of research reactors, i.e. nuclear reactors of less than 100 MW. Generally, these reactors are used as neutron generators for basic research in matter sciences and for technological research as a support to power reactors. The author proposes an overview of the general design of research reactors in terms of core size, of number of fissions, of neutron flow, of neutron space distribution. He outlines that this design is a compromise between a compact enough core, a sufficient experiment volume, and high enough power densities without affecting neutron performance or its experimental use. The author evokes the safety framework (same regulations as for power reactors, more constraining measures after Fukushima, international bodies). He presents the main characteristics and operation of the two families which represent almost all research reactors; firstly, heavy water reactors (photos, drawings and figures illustrate different examples); and secondly light water moderated and cooled reactors with a distinction between open core pool reactors like Melusine and Triton, pool reactors with containment, experimental fast breeder reactors (Rapsodie, the Russian BOR 60, the Chinese CEFR). The author describes the main uses of research reactors: basic research, applied and technological research, safety tests, production of radio-isotopes for medicine and industry, analysis of elements present under the form of traces at very low concentrations, non destructive testing, doping of silicon mono-crystalline ingots. The author then discusses the relationship between research reactors and non proliferation, and finally evokes perspectives (decrease of the number of research reactors in the world, the Jules Horowitz project)

1. Reactor physics and reactor computations

International Nuclear Information System (INIS)

Ronen, Y.; Elias, E.

1994-01-01

Mathematical methods and computer calculations for nuclear and thermonuclear reactor kinetics, reactor physics, neutron transport theory, core lattice parameters, waste treatment by transmutation, breeding, nuclear and thermonuclear fuels are the main interests of the conference

2. Research reactors

International Nuclear Information System (INIS)

Kowarski, L.

1955-01-01

It brings together the techniques data which are involved in the discussion about the utility for a research institute to acquire an atomic reactor for research purposes. This type of decision are often taken by non-specialist people who can need a brief presentation of a research reactor and its possibilities in term of research before asking advises to experts. In a first part, it draws up a list of the different research programs which can be studied by getting a research reactor. First of all is the reactor behaviour and kinetics studies (reproducibility factor, exploration of neutron density, effect of reactor structure, effect of material irradiation...). Physical studies includes study of the behaviour of the control system, studies of neutron resonance phenomena and study of the fission process for example. Chemical studies involves the study of manipulation and control of hot material, characterisation of nuclear species produced in the reactor and chemical effects of irradiation on chemical properties and reactions. Biology and medicine research involves studies of irradiation on man and animals, genetics research, food or medical tools sterilization and neutron beams effect on tumour for example. A large number of other subjects can be studied in a reactor research as reactor construction material research, fabrication of radioactive sources for radiographic techniques or applied research as in agriculture or electronic. The second part discussed the technological considerations when choosing the reactor type. The technological factors, which are considered for its choice, are the power of the reactor, the nature of the fuel which is used, the type of moderator (water, heavy water, graphite or BeO) and the reflector, the type of coolants, the protection shield and the control systems. In the third part, it described the characteristics (place of installation, type of combustible and comments) and performance (power, neutron flux ) of already existing

3. Reactor container

International Nuclear Information System (INIS)

Naruse, Yoshihiro.

1990-01-01

The thickness of steel shell plates in a reactor container embedded in sand cussions is monitored to recognize the corrosion of the steel shell plates. That is, the reactor pressure vessel is contained in a reactor container shell and the sand cussions are disposed on the lower outside of the reactor container shell to elastically support the shell. A pit is disposed at a position opposing to the sand cussions for measuring the thickness of the reactor container shell plates. The pit is usually closed by a closing member. In the reactor container thus constituted, the closing member can be removed upon periodical inspection to measure the thickness of the shell plates. Accordingly, the corrosion of the steel shell plates can be recognized by the change of the plate thickness. (I.S.)

4. Hybrid reactors

International Nuclear Information System (INIS)

Moir, R.W.

1980-01-01

The rationale for hybrid fusion-fission reactors is the production of fissile fuel for fission reactors. A new class of reactor, the fission-suppressed hybrid promises unusually good safety features as well as the ability to support 25 light-water reactors of the same nuclear power rating, or even more high-conversion-ratio reactors such as the heavy-water type. One 4000-MW nuclear hybrid can produce 7200 kg of 233 U per year. To obtain good economics, injector efficiency times plasma gain (eta/sub i/Q) should be greater than 2, the wall load should be greater than 1 MW.m -2 , and the hybrid should cost less than 6 times the cost of a light-water reactor. Introduction rates for the fission-suppressed hybrid are usually rapid

5. Nuclear reactor

International Nuclear Information System (INIS)

Garabedian, G.

1988-01-01

A liquid reactor is described comprising: (a) a reactor vessel having a core; (b) one or more satellite tanks; (c) pump means in the satellite tank; (d) heat exchanger means in the satellite tank; (e) an upper liquid metal conduit extending between the reactor vessel and the satellite tank; (f) a lower liquid metal duct extending between the reactor vessel and satellite tanks the upper liquid metal conduit and the lower liquid metal duct being arranged to permit free circulation of liquid metal between the reactor vessel core and the satellite tank by convective flow of liquid metal; (g) a separate sealed common containment vessel around the reactor vessel, conduits and satellite tanks; (h) the satellite tank having space for a volume of liquid metal that is sufficient to dampen temperature transients resulting from abnormal operating conditions

6. Nuclear reactor

International Nuclear Information System (INIS)

Batheja, P.; Huber, R.; Rau, P.

1985-01-01

Particularly for nuclear reactors of small output, the reactor pressure vessel contains at least two heat exchangers, which have coolant flowing through them in a circuit through the reactor core. The circuit of at least one heat exchanger is controlled by a slide valve, so that even for low drive forces, particularly in natural circulation, the required even loading of the heat exchanger is possible. (orig./HP) [de

7. Heterogeneous reactors

International Nuclear Information System (INIS)

Moura Neto, C. de; Nair, R.P.K.

1979-08-01

The microscopic study of a cell is meant for the determination of the infinite multiplication factor of the cell, which is given by the four factor formula: K(infinite) = n(epsilon)pf. The analysis of an homogeneous reactor is similar to that of an heterogeneous reactor, but each factor of the four factor formula can not be calculated by the formulas developed in the case of an homogeneous reactor. A great number of methods was developed for the calculation of heterogeneous reactors and some of them are discussed. (Author) [pt

8. Slurry reactors

Energy Technology Data Exchange (ETDEWEB)

Kuerten, H; Zehner, P [BASF A.G., Ludwigshafen am Rhein (Germany, F.R.)

1979-08-01

Slurry reactors are designed on the basis of empirical data and model investigations. It is as yet not possible to calculate the flow behavior of such reactors. The swarm of gas bubbles and cluster formations of solid particles and their interaction in industrial reactors are not known. These effects control to a large extent the gas hold-up, the gas-liquid interface and, similarly as in bubble columns, the back-mixing of liquids and solids. These hydrodynamic problems are illustrated in slurry reactors which constructionally may be bubble columns, stirred tanks or jet loop reactors. The expected effects are predicted by means of tests with model systems modified to represent the conditions in industrial hydrogenation reactors. In his book 'Mass Transfer in Heterogeneous Catalysis' (1970) Satterfield complained of the lack of knowledge about the design of slurry reactors and hence of the impossible task of the engineer who has to design a plant according to accepted rules. There have been no fundamental changes since then. This paper presents the problems facing the engineer in designing slurry reactors, and shows new development trends.

9. Reactor safety

International Nuclear Information System (INIS)

Butz, H.P.; Heuser, F.W.; May, H.

1985-01-01

The paper comprises an introduction into nuclear physics bases, the safety concept generally speaking, safety devices of pwr type reactors, accident analysis, external influences, probabilistic safety assessment and risk studies. It further describes operational experience, licensing procedures under the Atomic Energy Law, research in reactor safety and the nuclear fuel cycle. (DG) [de

10. Nuclear reactor

International Nuclear Information System (INIS)

Mysels, K.J.; Shenoy, A.S.

1976-01-01

A nuclear reactor is described in which the core consists of a number of fuel regions through each of which regulated coolant flows. The coolant from neighbouring fuel regions is combined in a manner which results in an averaging of the coolant temperature at the outlet of the core. By this method the presence of hot streaks in the reactor is reduced. (UK)

11. Reactor container

International Nuclear Information System (INIS)

Kato, Masami; Nishio, Masahide.

1987-01-01

Purpose: To prevent the rupture of the dry well even when the melted reactor core drops into a reactor pedestal cavity. Constitution: In a reactor container in which a dry well disposed above the reactor pedestal cavity for containing the reactor pressure vessel and a torus type suppression chamber for containing pressure suppression water are connected with each other, the pedestal cavity and the suppression chamber are disposed such that the flow level of the pedestal cavity is lower than the level of the pressure suppression water. Further, a pressure suppression water introduction pipeway for introducing the pressure suppression water into the reactor pedestal cavity is disposed by way of an ON-OFF valve. In case if the melted reactor core should fall into the pedestal cavity, the ON-OFF valve for the pressure suppression water introduction pipeway is opened to introduce the pressure suppression water in the suppression chamber into the pedestal cavity to cool the melted reactor core. (Ikeda, J.)

12. RA Reactor

International Nuclear Information System (INIS)

1989-01-01

This chapter includes the following: General description of the RA reactor, organization of work, responsibilities of leadership and operators team, regulations concerning operation and behaviour in the reactor building, regulations for performing experiments, regulations and instructions for inserting samples into experimental channels [sr

13. Reactor physics

International Nuclear Information System (INIS)

Ait Abderrahim, H.

1998-01-01

Progress in research on reactor physics in 1997 at the Belgian Nuclear Research Centre SCK/CEN is described. Activities in the following four domains are discussed: core physics, ex-core neutron transport, experiments in Materials Testing Reactors, international benchmarks

14. Reactor core

International Nuclear Information System (INIS)

Azekura, Kazuo; Kurihara, Kunitoshi.

1992-01-01

In a BWR type reactor, a great number of pipes (spectral shift pipes) are disposed in the reactor core. Moderators having a small moderating cross section (heavy water) are circulated in the spectral shift pipes to suppress the excess reactivity while increasing the conversion ratio at an initial stage of the operation cycle. After the intermediate stage of the operation cycle in which the reactor core reactivity is lowered, reactivity is increased by circulating moderators having a great moderating cross section (light water) to extend the taken up burnup degree. Further, neutron absorbers such as boron are mixed to the moderator in the spectral shift pipe to control the concentration thereof. With such a constitution, control rods and driving mechanisms are no more necessary, to simplify the structure of the reactor core. This can increase the fuel conversion ratio and control great excess reactivity. Accordingly, a nuclear reactor core of high conversion and high burnup degree can be attained. (I.N.)

15. Reactor container

International Nuclear Information System (INIS)

Fukazawa, Masanori.

1991-01-01

A system for controlling combustible gases, it has been constituted at present such that the combustible gases are controlled by exhausting them to the wet well of a reactor container. In this system, however, there has been a problem, in a reactor container having plenums in addition to the wet well and the dry well, that the combustible gases in such plenums can not be controlled. In view of the above, in the present invention, suction ports or exhaust ports of the combustible gas control system are disposed to the wet well, the dry well and the plenums to control the combustible gases in the reactor container. Since this can control the combustible gases in the entire reactor container, the integrity of the reactor container can be ensured. (T.M.)

16. Reactor container

International Nuclear Information System (INIS)

Kojima, Yoshihiro; Hosomi, Kenji; Otonari, Jun-ichiro.

1997-01-01

In the present invention, a catalyst for oxidizing hydrogen to be disposed in a reactor container upon rupture of pipelines of a reactor primary coolant system is prevented from deposition of water droplets formed from a reactor container spray to suppress elevation of hydrogen concentration in the reactor container. Namely, a catalytic combustion gas concentration control system comprises a catalyst for oxidizing hydrogen and a support thereof. In addition, there is also disposed a water droplet deposition-preventing means for preventing deposition of water droplets in a reactor pressure vessel on the catalyst. Then, the effect of the catalyst upon catalytic oxidation reaction of hydrogen can be kept high. The local elevation of hydrogen concentration can be prevented even upon occurrence of such a phenomenon that various kinds of mobile forces in the container such as dry well cooling system are lost. (I.S.)

17. Nuclear reactor

International Nuclear Information System (INIS)

Tilliette, Z.

1975-01-01

A description is given of a nuclear reactor and especially a high-temperature reactor in which provision is made within a pressure vessel for a main cavity containing the reactor core and a series of vertical cylindrical pods arranged in spaced relation around the main cavity and each adapted to communicate with the cavity through two collector ducts or headers for the primary fluid which flows downwards through the reactor core. Each pod contains two superposed steam-generator and circulator sets disposed in substantially symmetrical relation on each side of the hot primary-fluid header which conveys the primary fluid from the reactor cavity to the pod, the circulators of both sets being mounted respectively at the bottom and top ends of the pod

18. Reactor building

International Nuclear Information System (INIS)

Maruyama, Toru; Murata, Ritsuko.

1996-01-01

In the present invention, a spent fuel storage pool of a BWR type reactor is formed at an upper portion and enlarged in the size to effectively utilize the space of the building. Namely, a reactor chamber enhouses reactor facilities including a reactor pressure vessel and a reactor container, and further, a spent fuel storage pool is formed thereabove. A second spent fuel storage pool is formed above the auxiliary reactor chamber at the periphery of the reactor chamber. The spent fuel storage pool and the second spent fuel storage pool are disposed in adjacent with each other. A wall between both of them is formed vertically movable. With such a constitution, the storage amount for spent fuels is increased thereby enabling to store the entire spent fuels generated during operation period of the plant. Further, since requirement of the storage for the spent fuels is increased stepwisely during periodical exchange operation, it can be used for other usage during the period when the enlarged portion is not used. (I.S.)

19. Reactor container

International Nuclear Information System (INIS)

Shibata, Satoru; Kawashima, Hiroaki

1984-01-01

Purpose: To optimize the temperature distribution of the reactor container so as to moderate the thermal stress distribution on the reactor wall of LMFBR type reactor. Constitution: A good heat conductor (made of Al or Cu) is appended on the outer side of the reactor container wall from below the liquid level to the lower face of a deck plate. Further, heat insulators are disposed to the outside of the good heat conductor. Furthermore, a gas-cooling duct is circumferentially disposed at the contact portion between the good heat conductor and the deck plate around the reactor container. This enables to flow the cold heat from the liquid metal rapidly through the good heat conductor to the cooling duct and allows to maintain the temperature distribution on the reactor wall substantially linear even with the abrupt temperature change in the liquid metal. Further, by appending the good heat conductor covered with inactive metals not only on the outer side but also on the inside of the reactor wall to introduce the heat near the liquid level to the upper portion and escape the same to the cooling layer below the roof slab, the effect can be improved further. (Ikeda, J.)

20. Nuclear reactor

International Nuclear Information System (INIS)

Rau, P.

1980-01-01

The reactor core of nuclear reactors usually is composed of individual elongated fuel elements that may be vertically arranged and through which coolant flows in axial direction, preferably from bottom to top. With their lower end the fuel elements gear in an opening of a lower support grid forming part of the core structure. According to the invention a locking is provided there, part of which is a control element that is movable along the fuel element axis. The corresponding locking element is engaged behind a lateral projection in the opening of the support grid. The invention is particularly suitable for breeder or converter reactors. (orig.) [de

1. Nuclear reactors

International Nuclear Information System (INIS)

Prescott, R.F.

1976-01-01

A nuclear reactor containment vessel faced internally with a metal liner is provided with thermal insulation for the liner, comprising one or more layers of compressible material such as ceramic fiber, such as would be conventional in an advanced gas-cooled reactor and also a superposed layer of ceramic bricks or tiles in combination with retention means therefor, the retention means (comprising studs projecting from the liner, and bolts or nuts in threaded engagement with the studs) being themselves insulated from the vessel interior so that the coolant temperatures achieved in a High-Temperature Reactor or a Fast Reactor can be tolerated with the vessel. The layer(s) of compressible material is held under a degree of compression either by the ceramic bricks or tiles themselves or by cover plates held on the studs, in which case the bricks or tiles are preferably bedded on a yielding layer (for example of carbon fibers) rather than directly on the cover plates

2. Nuclear reactor

International Nuclear Information System (INIS)

Miyashita, Akio.

1981-01-01

Purpose: To facilitate and accelerate a leakage test of valves of a main steam pipe by adding a leakage test partition valve thereto. Constitution: A leakage testing partition valve is provided between a pressure vessel for a nuclear reactor and the most upstream side valve of a plurality of valves to be tested for leakage, a testing branch pipe is communicated with the downstream side of the partition valve, and the testing water for preventing leakage is introduced thereto through the branch pipe. Since main steam pipe can be simply isolated by closing the partition valve in the leakage test, the leakage test can be conducted without raising or lowering the water level in the pressure vessel, and since interference with other work in the reactor can be eliminated, the leakage test can be readily conducted parallel with other work in the reactor in a short time. Clean water can be used without using reactor water as the test water. (Yoshihara, H.)

3. Reactor container

International Nuclear Information System (INIS)

Abe, Yoshihito; Sano, Tamotsu; Ueda, Sabuo; Tanaka, Kazuhisa.

1987-01-01

Purpose: To improve the liquid surface disturbance in LMFBR type reactors. Constitution: A horizontal flow suppressing mechanism mainly comprising vertical members is suspended near the free liquid surface of coolants in the upper plenum. The horizontal flow of coolants near the free liquid surface is reduced by the suppressing mechanism to effectively reduce the surface disturbance. The reduction in the liquid surface disturbance further prevails to the entire surface region with no particular vertical variations to the free liquid surface to remarkably improve the preventive performance for the liquid surface disturbance. Accordingly, it is also possible to attain the advantageous effects such as prevention for the thermal fatigue in reactor vessel walls, reactor upper mechanisms, etc. and prevention of burning damage to the reactor core due to the reduction of envolved Ar gas. (Kamimura, M.)

4. REACTOR SHIELD

Science.gov (United States)

Wigner, E.P.; Ohlinger, L.E.; Young, G.J.; Weinberg, A.M.

1959-02-17

Radiation shield construction is described for a nuclear reactor. The shield is comprised of a plurality of steel plates arranged in parallel spaced relationship within a peripheral shell. Reactor coolant inlet tubes extend at right angles through the plates and baffles are arranged between the plates at right angles thereto and extend between the tubes to create a series of zigzag channels between the plates for the circulation of coolant fluid through the shield. The shield may be divided into two main sections; an inner section adjacent the reactor container and an outer section spaced therefrom. Coolant through the first section may be circulated at a faster rate than coolant circulated through the outer section since the area closest to the reactor container is at a higher temperature and is more radioactive. The two sections may have separate cooling systems to prevent the coolant in the outer section from mixing with the more contaminated coolant in the inner section.

5. NUCLEAR REACTOR

Science.gov (United States)

Miller, H.I.; Smith, R.C.

1958-01-21

This patent relates to nuclear reactors of the type which use a liquid fuel, such as a solution of uranyl sulfate in ordinary water which acts as the moderator. The reactor is comprised of a spherical vessel having a diameter of about 12 inches substantially surrounded by a reflector of beryllium oxide. Conventionnl control rods and safety rods are operated in slots in the reflector outside the vessel to control the operation of the reactor. An additional means for increasing the safety factor of the reactor by raising the ratio of delayed neutrons to prompt neutrons, is provided and consists of a soluble sulfate salt of beryllium dissolved in the liquid fuel in the proper proportion to obtain the result desired.

6. Breeder reactors

International Nuclear Information System (INIS)

Gollion, H.

1977-01-01

The reasons for the development of fast reactors are briefly reviewed (a propitious neutron balance oriented towards a maximum uranium burnup) and its special requirements (cooling, fissile material density and reprocessing) discussed. The three stages in the French program of fast reactor development are outlined with Rapsodie at Cadarache, Phenix at Marcoule, and Super Phenix at Creys-Malville. The more specific features of the program of research and development are emphasized: kinetics and the core, the fuel and the components [fr

7. Nuclear reactor

International Nuclear Information System (INIS)

Schulze, I.; Gutscher, E.

1980-01-01

The core contains a critical mass of UN or U 2 N 3 in the form of a noncritical solution with melted Sn being kept below a N atmosphere. The lining of the reactor core consists of graphite. If fission progresses part of the melted metal solution is removed and cleaned from fission products. The reactor temperatures lie in the range of 300 to 2000 0 C. (Examples and tables). (RW) [de

8. Reactor technology

International Nuclear Information System (INIS)

Erdoes, P.

1977-01-01

This is one of a series of articles discussing aspects of nuclear engineering ranging from a survey of various reactor types for static and mobile use to mention of atomic thermo-electric batteries of atomic thermo-electric batteries for cardiac pacemakers. Various statistics are presented on power generation in Europe and U.S.A. and economics are discussed in some detail. Molten salt reactors and research machines are also described. (G.M.E.)

9. Reactor containment

International Nuclear Information System (INIS)

Kawabe, Ryuhei; Yamaki, Rika.

1990-01-01

A water vessel is disposed and the gas phase portion of the water vessel is connected to a reactor container by a pipeline having a valve disposed at the midway thereof. A pipe in communication with external air is extended upwardly from the liquid phase portion to a considerable height so as to resist against the back pressure by a waterhead in the pipeline. Accordingly, when the pressure in the container is reduced to a negative level, air passes through the pipeline and uprises through the liquid phase portion in the water vessel in the form of bubbles and then flows into the reactor container. When the pressure inside of the reactor goes higher, since the liquid surface in the water vessel is forced down, water is pushed up into the pipeline. Since the waterhead pressure of a column of water in the pipeline and the pressure of the reactor container are well-balanced, gases in the reactor container are not leaked to the outside. Further, in a case if a great positive pressure is formed in the reactor container, the inner pressure overcomes the waterhead of the column of water, so that the gases containing radioactive aerosol uprise in the pipeline. Since water and the gases flow being in contact with each other, this can provide the effect of removing aerosol. (T.M.)

10. Fast reactors

International Nuclear Information System (INIS)

Vasile, A.

2001-01-01

Fast reactors have capacities to spare uranium natural resources by their breeding property and to propose solutions to the management of radioactive wastes by limiting the inventory of heavy nuclei. This article highlights the role that fast reactors could play for reducing the radiotoxicity of wastes. The conversion of 238 U into 239 Pu by neutron capture is more efficient in fast reactors than in light water reactors. In fast reactors multi-recycling of U + Pu leads to fissioning up to 95% of the initial fuel ( 238 U + 235 U). 2 strategies have been studied to burn actinides: - the multi-recycling of heavy nuclei is made inside the fuel element (homogeneous option); - the unique recycling is made in special irradiation targets placed inside the core or at its surroundings (heterogeneous option). Simulations have shown that, for the same amount of energy produced (400 TWhe), the mass of transuranium elements (Pu + Np + Am + Cm) sent to waste disposal is 60,9 Kg in the homogeneous option and 204.4 Kg in the heterogeneous option. Experimental programs are carried out in Phenix and BOR60 reactors in order to study the feasibility of such strategies. (A.C.)

11. Generation IV reactors: reactor concepts

International Nuclear Information System (INIS)

Cardonnier, J.L.; Dumaz, P.; Antoni, O.; Arnoux, P.; Bergeron, A.; Renault, C.; Rimpault, G.; Delpech, M.; Garnier, J.C.; Anzieu, P.; Francois, G.; Lecomte, M.

2003-01-01

Liquid metal reactor concept looks promising because of its hard neutron spectrum. Sodium reactors benefit a large feedback experience in Japan and in France. Lead reactors have serious assets concerning safety but they require a great effort in technological research to overcome the corrosion issue and they lack a leader country to develop this innovative technology. In molten salt reactor concept, salt is both the nuclear fuel and the coolant fluid. The high exit temperature of the primary salt (700 Celsius degrees) allows a high energy efficiency (44%). Furthermore molten salts have interesting specificities concerning the transmutation of actinides: they are almost insensitive to irradiation damage, some salts can dissolve large quantities of actinides and they are compatible with most reprocessing processes based on pyro-chemistry. Supercritical water reactor concept is based on operating temperature and pressure conditions that infers water to be beyond its critical point. In this range water gets some useful characteristics: - boiling crisis is no more possible because liquid and vapour phase can not coexist, - a high heat transfer coefficient due to the low thermal conductivity of supercritical water, and - a high global energy efficiency due to the high temperature of water. Gas-cooled fast reactors combining hard neutron spectrum and closed fuel cycle open the way to a high valorization of natural uranium while minimizing ultimate radioactive wastes and proliferation risks. Very high temperature gas-cooled reactor concept is developed in the prospect of producing hydrogen from no-fossil fuels in large scale. This use implies a reactor producing helium over 1000 Celsius degrees. (A.C.)

12. Research reactors - an overview

International Nuclear Information System (INIS)

West, C.D.

1997-01-01

A broad overview of different types of research and type reactors is provided in this paper. Reactor designs and operating conditions are briefly described for four reactors. The reactor types described include swimming pool reactors, the High Flux Isotope Reactor, the Mark I TRIGA reactor, and the Advanced Neutron Source reactor. Emphasis in the descriptions is placed on safety-related features of the reactors. 7 refs., 7 figs., 2 tabs

13. Nuclear reactors

Energy Technology Data Exchange (ETDEWEB)

Prescott, R F; George, B V; Baglin, C J

1978-05-10

Reference is made to thermal insulation on the inner surfaces of containment vessels of fluid cooled nuclear reactors and particularly in situations where the thermal insulation must also serve a structural function and transmit substantial load forces to the surface which it covers. An arrangement is described that meets this requirement and also provides for core support means that favourably influences the flow of hot coolant from the lower end of the core into a plenum space in the hearth of the reactor. The arrangement comprises a course of thermally insulating bricks arranged as a mosaic covering a wall of the reactor and a course of thermally insulating tiles arranged as a mosaic covering the course of bricks. Full constructional details are given.

14. Nuclear reactors

International Nuclear Information System (INIS)

Prescott, R.F.; George, B.V.; Baglin, C.J.

1978-01-01

Reference is made to thermal insulation on the inner surfaces of containment vessels of fluid cooled nuclear reactors and particularly in situations where the thermal insulation must also serve a structural function and transmit substantial load forces to the surface which it covers. An arrangement is described that meets this requirement and also provides for core support means that favourably influences the flow of hot coolant from the lower end of the core into a plenum space in the hearth of the reactor. The arrangement comprises a course of thermally insulating bricks arranged as a mosaic covering a wall of the reactor and a course of thermally insulating tiles arranged as a mosaic covering the course of bricks. Full constructional details are given. (UK)

15. Bioconversion reactor

Science.gov (United States)

McCarty, Perry L.; Bachmann, Andre

1992-01-01

A bioconversion reactor for the anaerobic fermentation of organic material. The bioconversion reactor comprises a shell enclosing a predetermined volume, an inlet port through which a liquid stream containing organic materials enters the shell, and an outlet port through which the stream exits the shell. A series of vertical and spaced-apart baffles are positioned within the shell to force the stream to flow under and over them as it passes from the inlet to the outlet port. The baffles present a barrier to the microorganisms within the shell causing them to rise and fall within the reactor but to move horizontally at a very slow rate. Treatment detention times of one day or less are possible.

16. Nuclear reactor

International Nuclear Information System (INIS)

Scholz, M.

1976-01-01

An improvement of the accessibility of that part of a nuclear reactor serving for biological shield is proposed. It is intended to provide within the biological shield, distributed around the circumference of the reactor pressure vessel, several shielding chambers filled with shielding material, which are isolated gastight from the outside by means of glass panes with a given bursting strength. It is advantageous that, on the one hand, inspection and maintenance will be possible without great effort and, on the other, a large relief cross section will be at desposal if required. (UWI) [de

17. NEUTRONIC REACTOR

Science.gov (United States)

Wigner, E.P.; Weinberg, A.W.; Young, G.J.

1958-04-15

A nuclear reactor which uses uranium in the form of elongated tubes as fuel elements and liquid as a coolant is described. Elongated tubular uranium bodies are vertically disposed in an efficient neutron slowing agent, such as graphite, for example, to form a lattice structure which is disposed between upper and lower coolant tanks. Fluid coolant tubes extend through the uranium bodies and communicate with the upper and lower tanks and serve to convey the coolant through the uranium body. The reactor is also provided with means for circulating the cooling fluid through the coolant tanks and coolant tubes, suitable neutron and gnmma ray shields, and control means.

18. Neutronic reactor

International Nuclear Information System (INIS)

Wende, C.W.J.

1976-01-01

The method of operating a water-cooled neutronic reactor having a graphite moderator is described which comprises flowing a gaseous mixture of carbon dioxide and helium, in which the helium comprises 40--60 volume percent of the mixture, in contact with the graphite moderator. 2 claims, 4 figures

19. Neutronic reactor

International Nuclear Information System (INIS)

Wende, C.W.J.

1976-01-01

A safety rod for a nuclear reactor has an inner end portion having a gamma absorption coefficient and neutron capture cross section approximately equal to those of the adjacent shield, a central portion containing materials of high neutron capture cross section and an outer end portion having a gamma absorption coefficient at least equal to that of the adjacent shield

20. Reactor facility

International Nuclear Information System (INIS)

Suzuki, Hiroaki; Murase, Michio; Yokomizo, Osamu.

1997-01-01

The present invention provides a BWR type reactor facility capable of suppressing the amount of steams generated by the mutual effect of a failed reactor core and coolants upon occurrence of an imaginal accident, and not requiring spacial countermeasures for enhancing the pressure resistance of the container vessel. Namely, a means for supplying cooling water at a temperature not lower by 30degC than the saturated temperature corresponding to the inner pressure of the containing vessel upon occurrence of an accident is disposed to a lower dry well below the pressure vessel. As a result, upon occurrence of such an accident that the reactor core should be melted and flown downward of the pressure vessel, when cooling water at a temperature not lower than the saturated temperature, for example, cooling water at 100degC or higher is supplied to the lower dry well, abrupt generation of steams by the mutual effect of the failed reactor core and cooling water is scarcely caused compared with a case of supplying cooling water at a temperature lower than the saturation temperature by 30degC or more. Accordingly, the amount of steams to be generated can be suppressed, and special countermeasure is no more necessary for enhancing the pressure resistance of the container vessel is no more necessary. (I.S.)

1. Nuclear reactor

International Nuclear Information System (INIS)

Gilroy, J.E.

1980-01-01

An improved cover structure for liquid metal cooled fast breeder type reactors is described which it is claimed reduces the temperature differential across the intermediate grid plate of the core cover structure and thereby reduces its subjection to thermal stresses. (UK)

2. Reactor licensing

International Nuclear Information System (INIS)

Harvie, J.D.

2002-01-01

This presentation discusses reactor licensing and includes the legislative basis for licensing, other relevant legislation , the purpose of the Nuclear Safety and Control Act, important regulations, regulatory document, policies, and standards. It also discusses the role of the CNSC, its mandate and safety philosophy

3. Nuclear reactor

International Nuclear Information System (INIS)

1987-01-01

Purpose: To decrease the thickness of a reactor container and reduce the height and the height and plate thickness of a roof slab without using mechanical vibration stoppers. Constitution: Earthquake proofness is improved by filling fluids such as liquid metal between a reactor container and a secondary container and connecting the outer surface of the reactor container with the inner surface of the secondary container by means of bellows. That is, for the horizontal seismic vibrations, horizontal loads can be supported by the secondary container without providing mechanical vibration stoppers to the reactor container and the wall thickness can be reduced thereby enabling to simplify thermal insulation structure for the reduction of thermal stresses. Further, for the vertical seismic vibrations, verical loads can be transmitted to the secondary container thereby enabling to reduce the wall thickness in the same manner as for the horizontal load. By the effect of transferring the point of action of the container load applied to the roof slab to the outer circumferential portion, the intended purpose can be attained and, in addition, the radiation dose rate at the upper surface of the roof slab can be decreased. (Kamimura, M.)

4. Reactor system

International Nuclear Information System (INIS)

Miyano, Hiroshi; Narabayashi, Naoshi.

1990-01-01

The represent invention concerns a reactor system with improved water injection means to a pressure vessel of a BWR type reactor. A steam pump is connected to a heat removing system pipeline, a high pressure water injection system pipeline and a low pressure water injection system pipeline for injecting water into the pressure vessel. A pump actuation pipeline is disposed being branched from a main steam pump or a steam relieaf pipeline system, through which steams are supplied to actuate the steam pump and supply cooling water into the pressure vessel thereby cooling the reactor core. The steam pump converts the heat energy into the kinetic energy and elevates the pressure of water to a level higher than the pressure of the steams supplied by way of a pressure-elevating diffuser. Cooling water can be supplied to the pressure vessel by the pressure elevation. This can surely inject cooling water into the pressure vessel upon loss of coolant accident or in a case if reactor scram is necessary, without using an additional power source. (I.N.)

5. Reactor core

International Nuclear Information System (INIS)

Matsuura, Tetsuaki; Nomura, Teiji; Tokunaga, Kensuke; Okuda, Shin-ichi

1990-01-01

Fuel assemblies in the portions where the gradient of fast neutron fluxes between two opposing faces of a channel box is great are kept loaded at the outermost peripheral position of the reactor core also in the second operation cycle in the order to prevent interference between a control rod and the channel box due to bending deformation of the channel box. Further, the fuel assemblies in the second row from the outer most periphery in the first operation cycle are also kept loaded at the second row in the second operation cycle. Since the gradient of the fast neutrons in the reactor core is especially great at the outer circumference of the reactor core, the channel box at the outer circumference is bent such that the surface facing to the center of the reactor core is convexed and the channel box in the second row is also bent to the identical direction, the insertion of the control rod is not interfered. Further, if the positions for the fuels at the outermost periphery and the fuels in the second row are not altered in the second operation cycle, the gaps are not reduced to prevent the interference between the control rod and the channel box. (N.H.)

International Nuclear Information System (INIS)

Egorenkov, P.M.

2001-01-01

The multi-purpose research reactor MAPLE (Canada) and concept of new reactor MAPLE-CNF as will substitute the known Canadian research reactor NRU are described. New reactor will be used as contributor for investigations into materials, neutron beams and further developments for the CANDU type reactor. The Budapest research reactor (BRR) and its application after the last reconstruction are considered also [ru

7. Reactor core of nuclear reactor

International Nuclear Information System (INIS)

Sasagawa, Masaru; Masuda, Hiroyuki; Mogi, Toshihiko; Kanazawa, Nobuhiro.

1994-01-01

In a reactor core, a fuel inventory at an outer peripheral region is made smaller than that at a central region. Fuel assemblies comprising a small number of large-diameter fuel rods are used at the central region and fuel assemblies comprising a great number of smalldiameter fuel rods are used at the outer peripheral region. Since a burning degradation rate of the fuels at the outer peripheral region can be increased, the burning degradation rate at the infinite multiplication factor of fuels at the outer region can substantially be made identical with that of the fuels in the inner region. As a result, the power distribution in the direction of the reactor core can be flattened throughout the entire period of the burning cycle. Further, it is also possible to make the degradation rate of fuels at the outer region substantially identical with that of fuels at the inner side. A power peak formed at the outer circumferential portion of the reactor core of advanced burning can be lowered to improve the fuel integrity, and also improve the reactor safety and operation efficiency. (N.H.)

8. Nuclear reactor

International Nuclear Information System (INIS)

Gibbons, J.F.; McLaughlin, D.J.

1978-01-01

In the pressure vessel of the water-cooled nuclear reactor there is provided an internal flange on which the one- or two-part core barrel is hanging by means of an external flange. A cylinder is extending from the reactor vessel closure downwards to a seat on the core cupport structure and serves as compression element for the transmission of the clamping load from the closure head to the core barrel (upper guide structure). With the core barrel, subject to tensile stress, between the vessel internal flange and its seat on one hand and the compression of the cylinder resp. hold-down element between the closure head and the seat on the other a very strong, elastic sprung structure is obtained. (DG) [de

9. Nuclear reactor

International Nuclear Information System (INIS)

Sasaki, Tomozo.

1987-01-01

Purpose: To improve the nuclear reactor availability by enabling to continuously exchange fuels in the natural-slightly enriched uranium region during operation. Constitution: A control rod is withdrawn to the midway of a highly enriched uranium region by means of control rod drives and the highly enriched uranium region is burnt to maintain the nuclear reactor always at a critical state. At the same time, fresh uranium-slightly enriched uranium is continuously supplied gravitationally from a fresh fuel reservoir through fuel reservoir to each of fuel pipes in the natural-slightly enriched uranium region. Then, spent fuels reduced with the reactivity by the burn up are successively taken out from the bottom of each of the fuel pipes through an exit duct and a solenoid valve to the inside of a spent fuel reservoir and the burn up in the natural-slightly enriched uranium region is conducted continuously. (Kawakami, Y.)

10. Nuclear reactor

International Nuclear Information System (INIS)

Sakurai, Mikio; Yamauchi, Koki.

1983-01-01

Purpose: To improve the channel stability and the reactor core stability in a spontaneous circulation state of coolants. Constitution: A reactor core stabilizing device comprising a differential pressure automatic ON-OFF valve is disposed between each of a plurality of jet pumps arranged on a pump deck. The stabilizing device comprises a piston exerted with a pressure on the lower side of the pump deck by way of a pipeway and a valve for flowing coolants through the bypass opening disposed to the pump deck by the opening and closure of the valve ON-OFF. In a case where the jet pumps are stopped, since the differential pressure between the upper and the lower sides of the pump deck is removed, the valve lowers gravitationally into an opened state, whereby the coolants flow through the bypass opening to increase the spontaneous circulation amount thereby improve the stability. (Yoshino, Y.)

11. Nuclear reactor

International Nuclear Information System (INIS)

Aleite, W.; Bock, H.W.; Struensee, S.

1976-01-01

The invention concerns the use of burnable poisons in a nuclear reactor, especially in PWRs, in order to improve the controllability of the reactor. An unsymmetrical arrangement in the lattice is provided, if necessary also by insertion of special rods for these additions. It is proposed to arrange the burnable poisons in fuel elements taken over from a previous burn-up cycle and to distribute them, going out from the side facing the control rods, over not more than 20% of the lenth of the fuel elements. It seems sufficient, for the burnable poisons to bind an initial reactivity of only 0.1% and to become ineffective after normal operation of 3 to 4 months. (ORU) [de

12. Reactor container

International Nuclear Information System (INIS)

1979-01-01

Purpose: To improve the earthquake resistance as well as reduce the size of a container for a nuclear reactor with no adverse effects on the decrease of impact shock to the container and shortening of construction step. Constitution: Reinforcing profile steel materials are welded longitudinally and transversely to the inner surface of a container, and inner steel plates are secured to the above profile steel materials while keeping a gap between the materials and the container. Reactor shielding wall planted to the base concrete of the container is mounted to the pressure vessel, and main steam pipeways secured by the transverse beams and led to the outside of container is connected. This can improve the rigidity earthquake strength and the safetiness against the increase in the inside pressure upon failures of the container. (Yoshino, Y.)

13. Reactor container

International Nuclear Information System (INIS)

Oyamada, Osamu; Furukawa, Hideyasu; Uozumi, Hiroto.

1979-01-01

Purpose: To lower the position of an intermediate slab within a reactor container and fitting a heat insulating material to the inner wall of said intermediate slab, whereby a space for a control rod exchanging device and thermal stresses of the inner peripheral wall are lowered. Constitution: In the pedestal at the lower part of a reactor pressure vessel there is formed an intermediate slab at a position lower than diaphragm floor slab of the outer periphery of the pedestal thereby to secure a space for providing automatic exchanging device of a control rod driving device. Futhermore, a heat insulating material is fitted to the inner peripheral wall at the upper side of the intermediate slab part, and the temperature gradient in the wall thickness direction at the time of a piping rupture trouble is made gentle, and thermal stresses at the inner peripheral wall are lowered. (Sekiya, K.)

14. Neutronic reactor

International Nuclear Information System (INIS)

Lewis, W.R.

1978-01-01

Disclosed is a graphite-moderated, water-cooled nuclear reactor including a plurality of rectangular graphite blocks stacked in abutting relationship in layers, alternate layers having axes which are normal to one another, alternate rows of blocks in alternate layers being provided with a channel extending through the blocks, said channeled blocks being provided with concave sides and having smaller vertical dimensions than adjacent blocks in the same layer, there being nuclear fuel in the channels

15. Nuclear reactors

International Nuclear Information System (INIS)

Humphreys, P.; Davidson, D.F.; Thatcher, G.

1980-01-01

The cooling system of a liquid metal cooled fast breeder nuclear reactor of the pool kind is described. It has an intermediate heat exchange module comprising a tube-in-shell heat exchanger and an electromagnetic flow coupler in the base region of the module. Primary coolant is flowed through the heat exchanger being driven by electromagnetic interaction with secondary liquid metal coolant flow effected by a mechanical pump. (author)

16. Nuclear reactor

International Nuclear Information System (INIS)

Jungmann, A.

1975-01-01

Between a PWR's reactor pressure vessel made of steel and the biological shield made of concrete there is a gap. This gap is filled up with a heat insulation facting the reactor pressure vessel, for example with insulating concrete segments jacketed with sheet steel and with an additional layer. This layer serves for smooth absorption of compressive forces originating in radial direction from the reactor pressure vessel. It consists of cylinder-segment shaped bricks made of on situ concrete, for instance. The bricks have cooling agent ports in one or several rows which run parallel to the wall of the pressure vessel and in alignment with superposed bricks. Between the layer of bricks and the biological shield or rather the heat insulation, there are joints which are filled, however, with injected mortar. That guarantees a smooth series of connected components resistant tom compression. Besides, a slip foil can be set between the heat insulation and the joining joint filled with mortar for the reduction of the friction at thermal expansions. (TK) [de

17. Reactor building

International Nuclear Information System (INIS)

Ebata, Sakae.

1990-01-01

At least one valve rack is disposed in a reactor building, on which pipeways to a main closure valve, valves and bypasses of turbines are placed and contained. The valve rack is fixed to the main body of the building or to a base mat. Since the reactor building is designed as class A earthquake-proofness and for maintaining the S 1 function, the valve rack can be fixed to the building main body or to the base mat. With such a constitution, the portions for maintaining the S 1 function are concentrated to the reactor building. As a result, the dispersion of structures of earthquake-proof portion corresponding to the reference earthquake vibration S 1 can be prevented. Accordingly, the conditions for the earthquake-proof design of the turbine building and the turbine/electric generator supporting rack are defined as only the class B earthquake-proof design conditions. In view of the above, the amount of building materials can be saved and the time for construction can be shortened. (I.S.)

18. Nuclear reactors

International Nuclear Information System (INIS)

Yoshioka, Michiko.

1985-01-01

Purpose: To obtain an optimum structural arrangement of IRM having a satisfactory responsibility to the inoperable state of a nuclear reactor and capable of detecting the reactor power in an averaged manner. Constitution: As the structural arrangement of IRM, from 6 to 16 even number of IRM are bisected into equial number so as to belong two trip systems respectively, in which all of the detectors are arranged at an equal pitch along a circumference of a circle with a radius rl having the center at the position of the central control rod in one trip system, while one detector is disposed near the central control rod and other detectors are arranged substantially at an equal pitch along the circumference of a circle with a radius r2 having the center at the position for the central control rod in another trip system. Furthermore, the radius r1 and r2 are set such that r1 = 0.3 R, r2 = 0.5 R in the case where there are 6 IRM and r1 = 0.4 R and R2 = 0.8 R where there are eight IRM where R represents the radius of the reactor core. (Kawakami, Y.)

19. MLR reactor

International Nuclear Information System (INIS)

Ryazantsev, E.P.; Egorenkov, P.M.; Nasonov, V.A.; Smimov, A.M.; Taliev, A.V.; Gromov, B.F.; Kousin, V.V.; Lantsov, M.N.; Radchenko, V.P.; Sharapov, V.N.

1998-01-01

The Material Testing Loop Reactor (MLR) development was commenced in 1991 with the aim of updating and widening Russia's experimental base to validate the selected directions of further progress of the nuclear power industry in Russia and to enhance its reliability and safety. The MLR reactor is the pool-type one. As coolant it applies light water and as side reflector beryllium. The direction of water circulation in the core is upward. The core comprises 30 FA arranged as hexagonal lattice with the 90-95 mm pitch. The central materials channel and six loop channels are sited in the core. The reflector includes up to 11 loop channels. The reactor power is 100 MW. The average power density of the core is 0.4 MW/I (maximal value 1.0 MW/l). The maximum neutron flux density is 7.10 14 n/cm 2 s in the core (E>0.1 MeV), and 5.10 14 n/cm 2 s in the reflector (E<0.625 eV). In 1995 due to the lack of funding the MLR designing was suspended. (author)

20. Nuclear reactor

International Nuclear Information System (INIS)

Shirakawa, Toshihisa.

1979-01-01

Purpose: To prevent cladding tube injuries due to thermal expansion of each of the pellets by successively extracting each of the control rods loaded in the reactor core from those having less number of notches, as well as facilitate the handling work for the control rods. Constitution: A recycle flow control device is provided to a circulation pump for forcibly circulating coolants in the reactor container and an operational device is provided for receiving each of the signals concerning number of notches for each of the control rods and flow control depending on the xenon poisoning effect obtained from the signals derived from the in-core instrument system connected to the reactor core. The operational device is connected with a control rod drive for moving each of the control rods up and down and a recycle flow control device. The operational device is set with a pattern for the aimed control rod power and the sequence of extraction. Upon extraction of the control rods, they are extracted successively from those having less notch numbers. (Moriyama, K.)

1. Reactor container

International Nuclear Information System (INIS)

Hidaka, Masataka; Hatamiya, Shigeo; Kawasaki, Terufumi; Fukui, Toru; Suzuki, Hiroaki; Kataoka, Yoshiyuki; Kawabe, Ryuhei; Murase, Michio; Naito, Masanori.

1990-01-01

In order to suppress the pressure elevation in a reactor container due to high temperature and high pressure steams jetted out upon pipeway rupture accidents in the reactor container, the steams are introduced to a pressure suppression chamber for condensating them in stored coolants. However, the ability for suppressing the pressure elevation and steam coagulation are deteriorated due to the presence of inactive incondensible gases. Then, there are disposed a vent channel for introducing the steams in a dry well to a pressure suppression chamber in the reactor pressure vessel, a closed space disposed at the position lower than a usual liquid level, a first channel having an inlet in the pressure suppression chamber and an exit in the closed space and a second means connected by way of a backflow checking means for preventing the flow directing to the closed space. The first paths are present by plurality, a portion of which constitutes a syphon. The incondensible gases and the steams are discharged to the dry well at high pressure by using the difference of the water head for a long cooling time after the pipeway rupture accident. Then, safety can be improved without using dynamic equipments as driving source. (N.H.)

2. Reactor core in FBR type reactor

International Nuclear Information System (INIS)

Masumi, Ryoji; Kawashima, Katsuyuki; Kurihara, Kunitoshi.

1989-01-01

In a reactor core in FBR type reactors, a portion of homogenous fuels constituting the homogenous reactor core is replaced with multi-region fuels in which the enrichment degree of fissile materials is lower nearer to the axial center. This enables to condition the composition such that a reactor core having neutron flux distribution either of a homogenous reactor core or a heterogenous reactor core has substantially identical reactivity. Accordingly, in the transfer from the homogenous reactor core to the axially heterogenous reactor core, the average reactivity in the reactor core is substantially equal in each of the cycles. Further, by replacing a portion of the homogenous fuels with a multi-region fuels, thereby increasing the heat generation near the axial center, it is possiable to reduce the linear power output in the regions above and below thereof and, in addition, to improve the thermal margin in the reactor core. (T.M.)

3. Molten salt reactors: reactor cores

International Nuclear Information System (INIS)

1983-01-01

In this critical analysis of the MSBR I project are examined the problems concerning the reactor core. Advantages of breeding depend essentially upon solutions to technological problems like continuous reprocessing or graphite behavior under neutron irradiation. Graphite deformation, moderator unloading, control rods and core instrumentation require more studies. Neutronics of the core, influence of core geometry and salt composition, fuel evolution, and thermohydraulics are reviewed [fr

4. Increased SRP reactor power

International Nuclear Information System (INIS)

MacAfee, I.M.

1983-01-01

Major changes in the current reactor hydraulic systems could be made to achieve a total of about 1500 MW increase of reactor power for P, K, and C reactors. The changes would be to install new, larger heat exchangers in the reactor buildings to increase heat transfer area about 24%, to increase H 2 O flow about 30% per reactor, to increase D 2 O flow 15 to 18% per reactor, and increase reactor blanket gas pressure from 5 psig to 10 psig. The increased reactor power is possible because of reduced inlet temperature of reactor coolant, increased heat removal capacity, and increased operating pressure (larger margin from boiling). The 23% reactor power increase, after adjustment for increased off-line time for reactor reloading, will provide a 15% increase of production from P, K, and C reactors. Restart of L Reactor would increase SRP production 33%

5. Nuclear research reactors

International Nuclear Information System (INIS)

1985-01-01

It's presented data about nuclear research reactors in the world, retrieved from the Sien (Nuclear and Energetic Information System) data bank. The information are organized in table forms as follows: research reactors by countries; research reactors by type; research reactors by fuel and research reactors by purpose. (E.G.) [pt

6. Nuclear reactor physics course for reactor operators

International Nuclear Information System (INIS)

Baeten, P.

2006-01-01

The education and training of nuclear reactor operators is important to guarantee the safe operation of present and future nuclear reactors. Therefore, a course on basic 'Nuclear reactor physics' in the initial and continuous training of reactor operators has proven to be indispensable. In most countries, such training also results from the direct request from the safety authorities to assure the high level of competence of the staff in nuclear reactors. The aim of the basic course on 'Nuclear Reactor Physics for reactor operators' is to provide the reactor operators with a basic understanding of the main concepts relevant to nuclear reactors. Seen the education level of the participants, mathematical derivations are simplified and reduced to a minimum, but not completely eliminated

7. Nuclear reactor

International Nuclear Information System (INIS)

Jolly, R.

1979-01-01

The support grid for the fuel rods of a liquid metal cooled fast breeder reactor has a regular hexagonal contour and contains a large number of unit cells arranged honeycomb fashion. The totality of these cells make up a hexagonal shape. The grid contains a number of strips of material, and there is a window in each of three sidewalls staggered by one sidewall. The other sidewalls have embossed protrusions, thus generating a guide lining or guide bead. The windows reduce the rigidity of the areas in the middle between the ends of the cells. (DG) [de

8. Nuclear reactor

International Nuclear Information System (INIS)

Anthony, A.J.; Gruber, E.A.

1979-01-01

A nuclear reactor with control rods in channels between fuel assemblies wherein the fuel assemblies incorporate guide rods which protrude outwardly into the control rod channels to prevent the control rods from engaging the fuel elements. The guide rods also extend back into the fuel assembly such that they are relatively rigid members. The guide rods are tied to the fuel assembly end or support plates and serve as structural members which are supported independently of the fuel element. Fuel element spacing and support means may be attached to the guide rods. 9 claims

9. Nuclear reactors

International Nuclear Information System (INIS)

Prescott, R.F.; George, B.V.; Baglin, C.J.

1979-01-01

In a nuclear reactor (e.g. one having coolant down-flow through a core to a hearth below) thermal insulation (e.g. of a floor of the hearth) comprises a layer of bricks and a layer of tiles thereon, with smaller clearances between the tiles than between the bricks but with the bricks being of reduced cross-section immediately adjacent the tiles so as to be surrounded by interconnected passages, of relatively large dimensions, constituting a continuous chamber extending behind the layer of tiles. By this arrangement, lateral coolant flow in the inter-brick clearances is much reduced. The reactor core is preferably formed of hexagonal columns, supported on diamond-shaped plates each supported on a pillar resting on one of the hearth-floor tiles. Each plate has an internal duct, four upper channels connecting the duct with coolant ducts in four core columns supported by the plate, and lower channels connecting the duct to a downwardly-open recess common to three plates, grouped to form a hexagon, at their mutually-adjacent corners. This provides mixing, and temperature-averaging, of coolant from twelve columns

10. Reactor container

International Nuclear Information System (INIS)

Oikawa, Hirohide; Otonari, Jun-ichiro; Tozaki, Yuka.

1993-01-01

Partition walls are disposed between a reactor pressure vessel and a suppression chamber to separate a dry well to an upper portion and a lower portion. A communication pipe is disposed to the partition walls. One end of the communication pipe is opened in an upper portion of the dry well at a position higher than a hole disposed to a bent tube of the suppression chamber. When coolants overflow from a depressurization valve by an erroneous operation of an emergency reactor core cooling device, the coolants accumulate in the upper portion of the dry well. When the pipeline is ruptured at the upper portion of the pressure vessel, only the inside of the pressure vessel and the upper portion of the dry well are submerged in water. In this case, the water level of the coolants does not elevate to the opening of the commuication pipe but they flow into the suppression chamber from the hole disposed to the bent tube. Since the coolants do not flow out to the lower portion of the dry well, important equipments such as control rod drives disposed at the lower portion of the dry wall can be prevented from submerging in water. (I.N.)

11. Reactor monitor

International Nuclear Information System (INIS)

1992-01-01

The device of the present invention monitors a reactor so that each of the operations for the relocation of fuel assemblies and the withdrawal and the insertion of control rods upon exchange of fuel assemblies and control rods in the reactor. That is, when an operator conducts relocating operation by way of a fuel assembly operation section, the device of the present invention judges whether the operation indication is adequate or not, based on the information of control rod arrangement in a control rod memory section. When the operation indication is wrong, a stop signal is sent to a fuel assembly relocating device. Further, when the operator conducts control rod operation by way of a control rod operation section, the device of the present invention judges in the control rod withdrawal judging section, as to whether the operation indication given by the operator is adequate or not by comparing it with fuel assembly arrangement information. When the operation indication is wrong, a stop signal is sent to control rod drives. With such procedures, increase of nuclear heating upon occurrence of erroneous operation can be prevented. (I.S.)

12. Nuclear reactors

International Nuclear Information System (INIS)

Matheson, J.E.

1983-01-01

A nuclear reactor has an upper and a lower grid plate. Protrusions project from the upper grid plate. Fuel assemblies having end fittings fit between the grid plates. An arrangement is provided for accepting axial forces generated during the operation of the nuclear reactor by the flow of the cooling medium and thermal expansion and irradiation-induced growth of the fuel assembly, which comprises rods. Each fuel assembly rests on the lower grid plate and its upper end is elastically supported against the upper grid plate by the above-mentioned arrangement. The arrangement comprises four (for example) torsion springs each having a torsion tube and a torsion bar nested within the torsion tube and connected at one end thereto. The other end of the torsion bar is connected to an associated one of four lever arms. The torsion tube is rigidly connected to the other end fitting and the springs are disposed such that the lever arms are biassed against the protrusions. (author)

13. Reactor core fuel management

International Nuclear Information System (INIS)

Silvennoinen, P.

1976-01-01

The subject is covered in chapters, entitled: concepts of reactor physics; neutron diffusion; core heat transfer; reactivity; reactor operation; variables of core management; computer code modules; alternative reactor concepts; methods of optimization; general system aspects. (U.K.)

Science.gov (United States)

Tsotsis, Theodore T [Huntington Beach, CA; Sahimi, Muhammad [Altadena, CA; Fayyaz-Najafi, Babak [Richmond, CA; Harale, Aadesh [Los Angeles, CA; Park, Byoung-Gi [Yeosu, KR; Liu, Paul K. T. [Lafayette Hill, PA

2011-03-01

A hybrid adsorbent-membrane reactor in which the chemical reaction, membrane separation, and product adsorption are coupled. Also disclosed are a dual-reactor apparatus and a process using the reactor or the apparatus.

15. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-11-01

This single page document is the November 1, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the production reactor.

16. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-10-01

This single page document is the October 1, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the Production Reactor.

17. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-10-15

This single page document is the October 15, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the Production Reactor.

18. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-09-15

This single page document is the September 15, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the Production Reactor.

19. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-12-15

This single page document is the December 16, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the Production reactor.

20. Reactor outage schedule (tentative)

Energy Technology Data Exchange (ETDEWEB)

Walton, R.P.

1969-12-01

This single page document is the December 1, 1969 reactor refueling outage schedule for the Hanford Production Reactor. It also contains data on the amounts and types of fuels to be loaded and relocated in the Production reactor.

1. Reactor theory and power reactors. 1. Calculational methods for reactors. 2. Reactor kinetics

International Nuclear Information System (INIS)

Henry, A.F.

1980-01-01

Various methods for calculation of neutron flux in power reactors are discussed. Some mathematical models used to describe transients in nuclear reactors and techniques for the reactor kinetics' relevant equations solution are also presented

2. The CEA research reactors

International Nuclear Information System (INIS)

Schwartz, J.P.

1993-01-01

Two main research reactors, specifically designed, PEGASE reactor and Laue-Langevin high flux reactor, are presented. The PEGASE reactor was designed at the end of the 50s for the study of the gas cooled reactor fuel element behaviour under irradiation; the HFR reactor, was designed in the late 60s to serve as a high yield and high level neutron source. Historical backgrounds, core and fuel characteristics and design, flux characteristics, etc., are presented. 5 figs

3. Atomic reactor thermal engineering

International Nuclear Information System (INIS)

Kim, Gwang Ryong

1983-02-01

This book starts the introduction of atomic reactor thermal engineering including atomic reaction, chemical reaction, nuclear reaction neutron energy and soon. It explains heat transfer, heat production in the atomic reactor, heat transfer of fuel element in atomic reactor, heat transfer and flow of cooler, thermal design of atomic reactor, design of thermodynamics of atomic reactor and various. This deals with the basic knowledge of thermal engineering for atomic reactor.

4. Nuclear reactor types

International Nuclear Information System (INIS)

Jones, P.M.S.

1987-01-01

The characteristics of different reactor types designed to exploit controlled fission reactions are explained. Reactors vary from low power research devices to high power devices especially designed to produce heat, either for direct use or to produce steam to drive turbines to generate electricity or propel ships. A general outline of basic reactors (thermal and fast) is given and then the different designs considered. The first are gas cooled, including the Magnox reactors (a list of UK Magnox stations and reactor performance is given), advanced gas cooled reactors (a list of UK AGRs is given) and the high temperature reactor. Light water cooled reactors (pressurized water [PWR] and boiling water [BWR] reactors) are considered next. Heavy water reactors are explained and listed. The pressurized heavy water reactors (including CANDU type reactors), boiling light water, steam generating heavy water reactors and gas cooled heavy water reactors all come into this category. Fast reactors (liquid metal fast breeder reactors and gas cooled fast reactors) and then water-cooled graphite-moderated reactors (RBMK) (the type at Chernobyl-4) are discussed. (U.K.)

5. Reactor safety

International Nuclear Information System (INIS)

Meneley, D.A.

The people of Ontario have begun to receive the benefits of a low cost, assured supply of electrical energy from CANDU nuclear stations. This indigenous energy source also has excellent safety characteristics. Safety has been one of the central themes of the CANDU development program from its very beginning. A great deal of work has been done to establish that public risks are small. However, safety design criteria are now undergoing extensive review, with a real prospect of more stringent requirements being applied in the future. Considering the newness of the technology it is not surprising that a consensus does not yet exist; this makes it imperative to discuss the issues. It is time to examine the policies and practice of reactor safety management in Canada to decide whether or not further restrictions are justified in the light of current knowledge

6. Nuclear reactor

International Nuclear Information System (INIS)

Schabert, H.P.; Weber, R.; Bauer, A.

1975-01-01

7. Nuclear reactor

International Nuclear Information System (INIS)

Schweiger, F.; Glahe, E.

1976-01-01

In a nuclear reactor of the kind which is charged with spherical reaction elements and in which control rods are arranged to be thrust directly into the charge, each control rod has at least one screw thread on its external surface so that as the rod is thrust into the charge it is caused to rotate and thus make penetration easier. The length of each control rod may have two distinct portions, a latter portion which carries a screw thread and a lead-in portion which is shorter than the latter portion and which may carry a thread of greater pitch than that on the latter portion or may have a number of axially extending ribs instead of a thread

8. Reactor container

International Nuclear Information System (INIS)

Furukawa, Hideyasu; Oyamada, Osamu; Uozumi, Hiroto.

1976-01-01

Purpose: To provide a container for a reactor provided with a pressure suppressing chamber pool which can prevent bubble vibrating load, particularly negative pressure generated at the time of starting to release exhaust from a main steam escape-safety valve from being transmitted to a lower liner plate of the container. Constitution: This arrangement is characterized in that a safety valve exhaust pool for main steam escape, in which a pressure suppressing chamber pool is separated and intercepted from pool water in the pressure suppressing chamber pool, a safety valve exhaust pipe is open into said safety valve exhaust pool, and an isolator member, which isolates the bottom liner plate in the pressure suppressing chamber pool from the pool water, is disposed on the bottom of the safety valve exhaust pool. (Nakamura, S.)

9. Nuclear reactors

International Nuclear Information System (INIS)

Prescott, R.F.

1976-01-01

In the system described the fuel elements are arranged vertically in groups and are supported in such a manner as to tend to tilt them towards the center of the respective group, the fuel elements being urged laterally into abutment with one another. The elements have interlocking bearing pads, whereby lateral movement of adjacent elements is resisted; this improves the stability of the reactor core during refuelling operations. Fuel elements may comprise clusters of parallel fuel pins enclosed in a wrapper of hexagonal cross section, with bearing pads in the form of spline-like ribs located on each side of the wrapper and extending parallel to the longitudinal axis of the fuel element, being interlockable with ribs on pads of adjacent fuel elements. The arrangement is applicable to a reactor core in which fuel elements and control rod guide tubes are arranged in modules each of which comprises a cluster of at least three fuel elements, one of which is rigidly supported whilst the others are resiliently tilted towards the center of the cluster so as to lean on the rigidly supported element. It is also applicable to modules comprising a cluster of six fuel elements, each resiliently tilted towards a central void to form a circular arch. The modules may include additional fuel elements located outside the clusters and also resiliently tilted towards the central voids, the latter being used to accommodate control rod guide tubes. The need for separate structural members to act as leaning posts is thus avoided. Such structural members are liable to irradiation embrittlement, that could lead to core failure. (U.K.)

10. Nuclear reactor neutron shielding

Science.gov (United States)

Speaker, Daniel P; Neeley, Gary W; Inman, James B

2017-09-12

A nuclear reactor includes a reactor pressure vessel and a nuclear reactor core comprising fissile material disposed in a lower portion of the reactor pressure vessel. The lower portion of the reactor pressure vessel is disposed in a reactor cavity. An annular neutron stop is located at an elevation above the uppermost elevation of the nuclear reactor core. The annular neutron stop comprises neutron absorbing material filling an annular gap between the reactor pressure vessel and the wall of the reactor cavity. The annular neutron stop may comprise an outer neutron stop ring attached to the wall of the reactor cavity, and an inner neutron stop ring attached to the reactor pressure vessel. An excore instrument guide tube penetrates through the annular neutron stop, and a neutron plug comprising neutron absorbing material is disposed in the tube at the penetration through the neutron stop.

11. FBR type reactor

International Nuclear Information System (INIS)

Kimura, Kimitaka; Fukuie, Ken; Iijima, Tooru; Shimpo, Masakazu.

1994-01-01

In an FBR type reactor for exchanging fuels by pulling up reactor core upper mechanisms, a connection mechanism is disposed for connecting the top of the reactor core and the lower end of the reactor core upper mechanisms. In addition, a cylindrical body is disposed surrounding the reactor core upper mechanisms, and a support member is disposed to the cylindrical body for supporting an intermediate portion of the reactor core upper mechanisms. Then, the lower end of the reactor core upper mechanisms is connected to the top of the reactor core. Same displacements are caused to both of them upon occurrence of earthquakes and, as a result, it is possible to eliminate mutual horizontal displacement between a control rod guide hole of the reactor core upper mechanisms and a control rod insertion hole of the reactor core. In addition, since the intermediate portion of the reactor core upper mechanisms is supported by the support member disposed to the cylindrical body surrounding the reactor core upper mechanisms, deformation caused to the lower end of the reactor core upper mechanisms is reduced, so that the mutual horizontal displacement with respect to the control rod insertion hole of the reactor core can be reduced. As a result, performance of control rod insertion upon occurrence of the earthquakes is improved, so that reactor shutdown is conducted more reliably to improve reactor safety. (N.H.)

12. The prototype fast reactor

International Nuclear Information System (INIS)

Broomfield, A.M.

1985-01-01

The paper concerns the Prototype Fast Reactor (PFR), which is a liquid metal cooled fast reactor power station, situated at Dounreay, Scotland. The principal design features of a Fast Reactor and the PFR are given, along with key points of operating history, and health and safety features. The role of the PFR in the development programme for commercial reactors is discussed. (U.K.)

13. Department of reactor technology

International Nuclear Information System (INIS)

1980-01-01

The activities of the Department of Reactor Technology at Risoe during 1979 are described. The work is presented in five chapters: Reactor Engineering, Reactor Physics and Dynamics, Heat Transfer and Hydraulics, The DR 1 Reactor, and Non-Nuclear Activities. A list of the staff and of publications is included. (author)

14. NCSU Reactor Sharing Program

International Nuclear Information System (INIS)

Perez, P.B.

1993-01-01

The Nuclear Reactor Program at North Carolina State University provides the PULSTAR Research Reactor and associated facilities to eligible institutions with support, in part, from the Department of Energy Reactor Sharing Program. Participation in the NCSU Reactor Sharing Program continues to increase steadily with visitors ranging from advance high school physics and chemistry students to Ph.D. level research from neighboring universities

15. Reactor safety method

International Nuclear Information System (INIS)

Vachon, L.J.

1980-01-01

This invention relates to safety means for preventing a gas cooled nuclear reactor from attaining criticality prior to start up in the event the reactor core is immersed in hydrogenous liquid. This is accomplished by coating the inside surface of the reactor coolant channels with a neutral absorbing material that will vaporize at the reactor's operating temperature

16. Physics of nuclear reactors

International Nuclear Information System (INIS)

Baeten, Peter

2006-01-01

This course gives an introduction to Nuclear Reactor Physics. The first chapter explains the most important parameters and concepts in nuclear reactor physics such as fission, cross sections and the effective multiplication factor. Further on, in the second chapter, the flux distributions in a stationary reactor are derived from the diffusion equation. Reactor kinetics, reactor control and reactor dynamics (feedback effects) are described in the following three chapters. The course concludes with a short description of the different types of existing and future reactors. (author)

17. Reactor core and initially loaded reactor core of nuclear reactor

International Nuclear Information System (INIS)

Koyama, Jun-ichi; Aoyama, Motoo.

1989-01-01

In BWR type reactors, improvement for the reactor shutdown margin is an important characteristic condition togehter with power distribution flattening . However, in the reactor core at high burnup degree, the reactor shutdown margin is different depending on the radial position of the reactor core. That is , the reactor shutdown margin is smaller in the outer peripheral region than in the central region of the reactor core. In view of the above, the reactor core is divided radially into a central region and as outer region. The amount of fissionable material of first fuel assemblies newly loaded in the outer region is made less than the amount of the fissionable material of second fuel assemblies newly loaded in the central region, to thereby improve the reactor shutdown margin in the outer region. Further, the ratio between the amount of the fissionable material in the upper region and that of the fissionable material in the lower portion of the first fuel assemblies is made smaller than the ratio between the amount of the fissionable material in the upper region and that of the fissionable material in the lower region of the second fuel assemblies, to thereby obtain a sufficient thermal margin in the central region. (K.M.)

18. Nuclear reactors. Introduction

International Nuclear Information System (INIS)

Boiron, P.

1997-01-01

This paper is an introduction to the 'nuclear reactors' volume of the Engineers Techniques collection. It gives a general presentation of the different articles of the volume which deal with: the physical basis (neutron physics and ionizing radiations-matter interactions, neutron moderation and diffusion), the basic concepts and functioning of nuclear reactors (possible fuel-moderator-coolant-structure combinations, research and materials testing reactors, reactors theory and neutron characteristics, neutron calculations for reactor cores, thermo-hydraulics, fluid-structure interactions and thermomechanical behaviour of fuels in PWRs and fast breeder reactors, thermal and mechanical effects on reactors structure), the industrial reactors (light water, pressurized water, boiling water, graphite moderated, fast breeder, high temperature and heavy water reactors), and the technology of PWRs (conceiving and building rules, nuclear parks and safety, reactor components and site selection). (J.S.)

19. Thermonuclear reactor

International Nuclear Information System (INIS)

Yasutomi, Yoshiyuki; Nakagawa, Moroo; Sawai, Yuichi; Chiba, Akio; Suzuki, Yasutaka.

1997-01-01

Silicon composited with reinforcing metals is used for a divertor cooling substrate having an effect as a cooling tube to provide a silicon base composite material having increased electric resistance and toughness. The blending ratio of reinforcing materials in the form of granules, whiskers or long fibers is controlled in order to control heat conductivity, electric resistivity and mechanical performances. The divertor cooling substrate comprising the silicon base composite material is integrated with a plasma facing material. The production method therefor includes ordinary metal matrix composite forming methods such as powder metallurgy, melting penetration method, high pressure solidification casting method, centrifugal casting method and vacuum casting method. Since the cooling plate is constituted with the light metal and highly electric resistant metal base composite material, sharing force due to eddy current can be reduced, and radiation exposure can be minimized. Accordingly, a cooling structure for a thermonuclear reactor effective for the improvement of environmental problems caused by waste disposal can be attained. (N.H.)

20. Nuclear reactor

International Nuclear Information System (INIS)

Irion, L.; Tautz, J.; Ulrych, G.

1976-01-01

This additional patent complements the arrangement of non-return valves to prevent loss of cooling water on fracture of external tubes in the main coolant circuit (according to PS 24 24 427.7) by ensuring that the easily movable valves only operate in case of a fault, but do not flutter in operation, because the direction of flow is not the same at each location where they are installed. The remedy for this undesirable effect consists of allocating 1 non-return valve unit with 5 to 10 valves to each (of several) ducts for the cooling water intake. These units are installed in the annular space between the reactor vessel and the pressure vessel below the inlet of the ducts. Due to flow guidance surfaces in the same space, the incoming cooling water is deflected downwards and as the guiding surfaces are closed at the sides, must pass parallel to the valves of the non-return valve unit. On fracture of the external cooling water inlet pipe concerned, all valves of this unit close due to reversal of flow on the outlet side. (TK) [de

1. Nuclear reactors

International Nuclear Information System (INIS)

Pearson, K.G.

1977-01-01

Reference is made to auxiliary means of cooling the nuclear fuel clusters used in light or heavy water cooled nuclear reactors. One method is to provide one or more spray cooling tubes. From holes in the side walls of those tubes coolant water may be sprayed laterally into the cluster against the rods. The flow of main coolant may thus be supplemented or even replaced by the auxiliary coolant. A difficulty, however, is that only those fuel rods close to a spray cooling tube can readily be reached by the auxiliary coolant. In the arrangement described, where the fuel rods are spaced apart by transverse grids, at least one of the interspaces between the grids is provided with an axially extending auxiliary coolant conduit having lateral holes through which an auxiliary coolant is sprayed into the cluster. A deflector is provided that extends from a transverse grid into a position in front of the holes and deflects auxiliary coolant on to parts of the fuel rods otherwise inaccessible to the auxiliary coolant. The construction of the deflector is described. (U.K.)

2. Nuclear reactor coolant channels

International Nuclear Information System (INIS)

Macbeth, R.V.

1978-01-01

A nuclear reactor coolant channel is described that is suitable for sub-cooled reactors as in pressurised water reactors as well as for bulk boiling, as in boiling water reactors and steam generating nuclear reactors. The arrangement aims to improve heat transfer between the fuel elements and the coolant. Full constructional details are given. See also other similar patents by the author. (U.K.)

3. Fast breeder reactors

International Nuclear Information System (INIS)

Heinzel, V.

1975-01-01

The author gives a survey of 'fast breeder reactors'. In detail the process of breeding, the reasons for the development of fast breeders, the possible breeder reactors, the design criteria, fuels, cladding, coolant, and safety aspects are reported on. Design data of some experimental reactors already in operation are summarized in stabular form. 300 MWe Prototype-Reactors SNR-300 and PFR are explained in detail and data of KWU helium-cooled fast breeder reactors are given. (HR) [de

4. Reactor Physics Training

International Nuclear Information System (INIS)

Baeten, P.

2007-01-01

University courses in nuclear reactor physics at the universities consist of a theoretical description of the physics and technology of nuclear reactors. In order to demonstrate the basic concepts in reactor physics, training exercises in nuclear reactor installations are also desirable. Since the number of reactor facilities is however strongly decreasing in Europe, it becomes difficult to offer to students a means for demonstrating the basic concepts in reactor physics by performing training exercises in nuclear installations. Universities do not generally possess the capabilities for performing training exercises. Therefore, SCK-CEN offers universities the possibility to perform (on a commercial basis) training exercises at its infrastructure consisting of two research reactors (BR1 and VENUS). Besides the organisation of training exercises in the framework of university courses, SCK-CEN also organizes theoretical courses in reactor physics for the education and training of nuclear reactor operators. It is indeed a very important subject to guarantee the safe operation of present and future nuclear reactors. In this framework, an understanding of the fundamental principles of nuclear reactor physics is also necessary for reactor operators. Therefore, the organisation of a basic Nuclear reactor physics course at the level of reactor operators in the initial and continuous training of reactor operators has proven to be indispensable. In most countries, such training also results from the direct request from the safety authorities to assure the high level of competence of the staff in nuclear reactors. The objectives this activity are: (1) to provide training and education activities in reactor physics for university students and (2) to organise courses in nuclear reactor physics for reactor operators

5. The fast breeder reactor

International Nuclear Information System (INIS)

Collier, J.

1990-01-01

The arguments for and against the fast breeder reactor are debated. The case for the fast reactor is that the world energy demand will increase due to increasing population over the next forty years and that the damage to the global environment from burning fossil fuels which contribute to the greenhouse effect. Nuclear fission is the only large scale energy source which can achieve a cut in the use of carbon based fuels although energy conservation and renewable sources will also be important. Fast reactors produce more energy from uranium than other types of (thermal) reactors such as AGRs and PWRs. Fast reactors would be important from about 2020 onwards especially as by then many thermal reactors will need to be replaced. Fast reactors are also safer than normal reactors. The arguments against fast reactors are largely economic. The cost, especially the capital cost is very high. The viability of the technology is also questioned. (UK)

6. Nuclear reactor instrumentation at research reactor renewal

International Nuclear Information System (INIS)

Baers, B.; Pellionisz, P.

1981-10-01

The paper overviews the state-of-the-art of research reactor renewals. As a case study the instrumentation reconstruction of the Finnish 250 kW TRIGA reactor is described, with particular emphasis on the nuclear control instrumentation and equipment which has been developed and manufactured by the Central Research Institute for Physics, Budapest. Beside the presentation of the nuclear instrument family developed primarily for research reactor reconstructions, the quality assurance policy conducted during the manufacturing process is also discussed. (author)

7. Safeguarding research reactors

International Nuclear Information System (INIS)

Powers, J.A.

1983-03-01

The report is organized in four sections, including the introduction. The second section contains a discussion of the characteristics and attributes of research reactors important to safeguards. In this section, research reactors are described according to their power level, if greater than 25 thermal megawatts, or according to each fuel type. This descriptive discussion includes both reactor and reactor fuel information of a generic nature, according to the following categories. 1. Research reactors with more than 25 megawatts thermal power, 2. Plate fuelled reactors, 3. Assembly fuelled reactors. 4. Research reactors fuelled with individual rods. 5. Disk fuelled reactors, and 6. Research reactors fuelled with aqueous homogeneous fuel. The third section consists of a brief discussion of general IAEA safeguards as they apply to research reactors. This section is based on IAEA safeguards implementation documents and technical reports that are used to establish Agency-State agreements and facility attachments. The fourth and last section describes inspection activities at research reactors necessary to meet Agency objectives. The scope of the activities extends to both pre and post inspection as well as the on-site inspection and includes the examination of records and reports relative to reactor operation and to receipts, shipments and certain internal transfers, periodic verification of fresh fuel, spent fuel and core fuel, activities related to containment and surveillance, and other selected activities, depending on the reactor

8. Guide to power reactors

Energy Technology Data Exchange (ETDEWEB)

NONE

1959-07-15

The IAEA's major first scientific publication is the Directory of Power Reactors now in operation or under construction in various parts of the world. The purpose of the directory is to present important details of various power projects in such a way as to provide a source of easy reference for anyone interested in the development of the peaceful uses of atomic energy, either at the technical or management level. Six pages have been devoted to each reactor the first of which contains general information, reactor physics data and information about the core. The second and third contain sketches of the fuel element or of the fuel element assembly, and of the horizontal and vertical sections of the reactor. On the fourth page information is grouped under the following heads: fuel element, core heat transfer, control, reactor vessel and over-all dimensions, and fluid flow. The fifth page shows a simplified flow diagram, while the sixth provides information on reflector and shielding, containment and turbo generator. Some information has also been given, when available, on cost estimates and operating staff requirements. Remarks and a bibliography constitute the last part of the description of each reactor. Reactor projects included in this directory are pressurized light water cooled power reactors. Boiling light water cooled power reactors, heavy water cooled power reactors, gas cooled power reactors, organic cooled power reactors liquid metal cooled power reactors and liquid metal cooled power reactors

9. Reactor core of FBR type reactor

International Nuclear Information System (INIS)

Hayashi, Hideyuki; Ichimiya, Masakazu.

1994-01-01

A reactor core is a homogeneous reactor core divided into two regions of an inner reactor core region at the center and an outer reactor core region surrounding the outside of the inner reactor core region. In this case, the inner reactor core region has a lower plutonium enrichment degree and less amount of neutron leakage in the radial direction, and the outer reactor core region has higher plutonium enrichment degree and greater amount of neutron leakage in the radial direction. Moderator materials containing hydrogen are added only to the inner reactor core fuels in the inner reactor core region. Pins loaded with the fuels with addition of the moderator materials are inserted at a ratio of from 3 to 10% of the total number of the fuel pins. The moderator materials containing hydrogen comprise zirconium hydride, titanium hydride, or calcium hydride. With such a constitution, fluctuation of the power distribution in the radial direction along with burning is suppressed. In addition, an absolute value of the Doppler coefficient can be increased, and a temperature coefficient of coolants can be reduced. (I.N.)

10. Reactor core for LMFBR type reactors

International Nuclear Information System (INIS)

Masumi, Ryoji; Azekura, Kazuo; Kurihara, Kunitoshi; Bando, Masaru; Watari, Yoshio.

1987-01-01

Purpose: To reduce the power distribution fluctuations and obtain flat and stable power distribution throughout the operation period in an LMFBR type reactor. Constitution: In the inner reactor core region and the outer reactor core region surrounding the same, the thickness of the inner region is made smaller than the axial height of the reactor core region and the radial width thereof is made smaller than that of the reactor core region and the volume thereof is made to 30 - 50 % for the reactor core region. Further, the amount of the fuel material per unit volume in the inner region is made to 70 - 90 % of that in the outer region. The difference in the neutron infinite multiplication factor between the inner region and the outer region is substantially constant irrespective of the burnup degree and the power distribution fluctuation can be reduced to about 2/3, by which the effect of thermal striping to the reactor core upper mechanisms can be moderated. Further, the maximum linear power during operation can be reduced by 3 %, by which the thermal margin in the reactor core is increased and the reactor core fuels can be saved by 3 %. (Kamimura, M.)

11. Tokamak reactor studies

International Nuclear Information System (INIS)

Baker, C.C.

1981-01-01

This paper presents an overview of tokamak reactor studies with particular attention to commercial reactor concepts developed within the last three years. Emphasis is placed on DT fueled reactors for electricity production. A brief history of tokamak reactor studies is presented. The STARFIRE, NUWMAK, and HFCTR studies are highlighted. Recent developments that have increased the commercial attractiveness of tokamak reactor designs are discussed. These developments include smaller plant sizes, higher first wall loadings, improved maintenance concepts, steady-state operation, non-divertor particle control, and improved reactor safety features

12. Reactor Physics Programme

International Nuclear Information System (INIS)

De Raedt, C.

2000-01-01

The Reactor Physics and Department of SCK-CEN offers expertise in various areas of reactor physics, in particular in neutronics calculations, reactor dosimetry, reactor operation, reactor safety and control and non-destructive analysis on reactor fuel. This expertise is applied within the Reactor Physics and MYRRHA Research Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 reactor dosimetry, and the preparation and interpretation of irradiation experiments. Progress and achievements in 1999 in the following areas are reported on: (1) investigations on the use of military plutonium in commercial power reactors; (2) neutron and gamma calculations performed for BR-2 and for other reactors; (3) the updating of neutron and gamma cross-section libraries; (4) the implementation of reactor codes; (6) the management of the UNIX workstations; and (6) fuel cycle studies

13. Reactor Physics Programme

Energy Technology Data Exchange (ETDEWEB)

De Raedt, C

2000-07-01

The Reactor Physics and Department of SCK-CEN offers expertise in various areas of reactor physics, in particular in neutronics calculations, reactor dosimetry, reactor operation, reactor safety and control and non-destructive analysis on reactor fuel. This expertise is applied within the Reactor Physics and MYRRHA Research Department's own research projects in the VENUS critical facility, in the BR1 reactor and in the MYRRHA project (this project aims at designing a prototype Accelerator Driven System). Available expertise is also used in programmes external to the Department such as the reactor pressure steel vessel programme, the BR2 reactor dosimetry, and the preparation and interpretation of irradiation experiments. Progress and achievements in 1999 in the following areas are reported on: (1) investigations on the use of military plutonium in commercial power reactors; (2) neutron and gamma calculations performed for BR-2 and for other reactors; (3) the updating of neutron and gamma cross-section libraries; (4) the implementation of reactor codes; (6) the management of the UNIX workstations; and (6) fuel cycle studies.

International Nuclear Information System (INIS)

Edwards, R.M.; Power, M.A.; Bryan, M.

1992-01-01

A sequence of reactor and related experiments has been a central element of a senior-level laboratory course at Pennsylvania State University (Penn State) for more than 20 yr. A new experiment has been developed where the students program and operate a computer controller that manipulates the speed of a secondary control rod to regulate TRIGA reactor power. Elementary feedback control theory is introduced to explain the experiment, which emphasizes the nonlinear aspect of reactor control where power level changes are equivalent to a change in control loop gain. Digital control of nuclear reactors has become more visible at Penn State with the replacement of the original analog-based TRIGA reactor control console with a modern computer-based digital control console. Several TRIGA reactor dynamics experiments, which comprise half of the three-credit laboratory course, lead to the control experiment finale: (a) digital simulation, (b) control rod calibration, (c) reactor pulsing, (d) reactivity oscillator, and (e) reactor noise

15. Reactor System Design

International Nuclear Information System (INIS)

Chi, S. K.; Kim, G. K.; Yeo, J. W.

2006-08-01

SMART NPP(Nuclear Power Plant) has been developed for duel purpose, electricity generation and energy supply for seawater desalination. The objective of this project IS to design the reactor system of SMART pilot plant(SMART-P) which will be built and operated for the integrated technology verification of SMART. SMART-P is an integral reactor in which primary components of reactor coolant system are enclosed in single pressure vessel without connecting pipes. The major components installed within a vessel includes a core, twelve steam generator cassettes, a low-temperature self pressurizer, twelve control rod drives, and two main coolant pumps. SMART-P reactor system design was categorized to the reactor coe design, fluid system design, reactor mechanical design, major component design and MMIS design. Reactor safety -analysis and performance analysis were performed for developed SMART=P reactor system. Also, the preparation of safety analysis report, and the technical support for licensing acquisition are performed

16. Fusion reactor design studies

International Nuclear Information System (INIS)

Emmert, G.A.; Kulcinski, G.L.; Santarius, J.F.

1990-01-01

This report discusses the following topics on the ARIES tokamak: systems; plasma power balance; impurity control and fusion ash removal; fusion product ripple loss; energy conversion; reactor fueling; first wall design; shield design; reactor safety; and fuel cost and resources

17. Nuclear reactors; graphical symbols

International Nuclear Information System (INIS)

1987-11-01

This standard contains graphical symbols that reveal the type of nuclear reactor and is used to design graphical and technical presentations. Distinguishing features for nuclear reactors are laid down in graphical symbols. (orig.) [de

18. Control for nuclear reactor

International Nuclear Information System (INIS)

Ash, E.B.; Bernath, L.; Facha, J.V.

1980-01-01

A nuclear reactor is provided with several hydraulically-supported spherical bodies having a high neutron absorption cross section, which fall by gravity into the core region of the reactor when the flow of supporting fluid is shut off. (auth)

19. Hybrid plasmachemical reactor

Energy Technology Data Exchange (ETDEWEB)

Lelevkin, V. M., E-mail: lelevkin44@mail.ru; Smirnova, Yu. G.; Tokarev, A. V. [Kyrgyz-Russian Slavic University (Kyrgyzstan)

2015-04-15

A hybrid plasmachemical reactor on the basis of a dielectric barrier discharge in a transformer is developed. The characteristics of the reactor as functions of the dielectric barrier discharge parameters are determined.

20. Ship propulsion reactors technology

International Nuclear Information System (INIS)

Fribourg, Ch.

2002-01-01

This paper takes the state of the art on ship propulsion reactors technology. The french research programs with the corresponding technological stakes, the reactors specifications and advantages are detailed. (A.L.B.)

1. Guidebook to nuclear reactors

International Nuclear Information System (INIS)

Nero, A.V. Jr.

1976-05-01

A general introduction to reactor physics and theory is followed by descriptions of commercial nuclear reactor types. Future directions for nuclear power are also discussed. The technical level of the material is suitable for laymen

2. continuous stirred tank reactor (CSTR)

African Journals Online (AJOL)

AFRICAN JOURNALS ONLINE (AJOL) · Journals · Advanced Search ... stirred tank reactor (CSTR) and the small and large intestines as plug flow reactor (PFR) ... from the two equations are used for the reactor sizing of the modeled reactors.

3. Reactor physics aspects of CANDU reactors

International Nuclear Information System (INIS)

Critoph, E.

1980-01-01

These four lectures are being given at the Winter Course on Nuclear Physics at Trieste during 1978 February. They constitute part of the third week's lectures in Part II: Reactor Theory and Power Reactors. A physical description of CANDU reactors is given, followed by an overview of CANDU characteristics and some of the design options. Basic lattice physics is discussed in terms of zero energy lattice experiments, irradiation effects and analytical methods. Start-up and commissioning experiments in CANDU reactors are reviewed, and some of the more interesting aspects of operation discussed - fuel management, flux mapping and control of the power distribution. Finally, some of the characteristics of advanced fuel cycles that have been proposed for CANDU reactors are summarized. (author)

4. Molten salt breeder reactor

International Nuclear Information System (INIS)

1977-01-01

MSBR Study Group formed in October 1974 has studied molten salt breeder reactor and its various aspects. Usage of a molten salt fuel, extremely interesting as reactor chemistry, is a great feature to MSBR; there is no need for separate fuel making, reprocessing, waste storage facilities. The group studied the following, and these results are presented: molten salt technology, molten salt fuel chemistry and reprocessing, reactor characteristics, economy, reactor structural materials, etc. (Mori, K.)

5. Zero energy reactor 'RB'

Energy Technology Data Exchange (ETDEWEB)

Popovic, D; Takac, S; Markovic, H; Raisic, N; Zdravkovic, Z; Radanovic, Lj [Boris Kidric Institute of Nuclear Sciences, Vinca, Beograd (Yugoslavia)

1959-03-15

In 1958 the zero energy reactor RB was built with the purpose of enabling critical experiments with various reactor systems to be carried out. The first core assembly built in this reactor consists of heavy water as moderator and natural uranium metal as fuel. In order to be able to obtain very accurate results when measuring the main characteristics of the assembly the reactor was built as a completely bare system. (author)

6. Reactor utilization, Annex A

International Nuclear Information System (INIS)

Martinc, R.; Stanic, A.

1984-01-01

Reactor was operated until August 1984 due to prohibition issued by the Ministry since the reactor does not have the emergency cooling system nor special filters in the ventilation system yet. This means that the operation plan was fulfilled by 69%. This annex includes detailed tables containing data about utilization of reactor experimental channels, irradiated samples, as well as interruptions of operation. Detailed data about reactor power during this period are shown as well

7. PUSPATI TRIGA Reactor

International Nuclear Information System (INIS)

Masood, Z.

2016-01-01

The PUSPATI TRIGA Reactor is the only research reactor in Malaysia. This 1 MW TRIGA Mk II reactor first reached criticality on 28 June 1982 and is located at the Malaysian Nuclear Agency premise in Bangi, Malaysia. This reactor has been mainly utilised for research, training and education and isotope production. Over the years several systems have been refurbished or modernised to overcome ageing and obsolescence problems. Major achievements and milestones will also be elaborated in this paper. (author)

8. Nuclear reactor shutdown system

International Nuclear Information System (INIS)

Mangus, J.D.; Cooper, M.H.

1982-01-01

An improved nuclear reactor shutdown system is described comprising a temperature sensitive device connected to control the electric power supply to a magnetic latch holding a body of a neutron absorbing material. The temperature sensitive device is exposed to the reactor coolant so that when the reactor coolant temperature rises above a specific level, the temperature sensitive device will cause deenergization of the magnetic latch to allow the body of neutron absorbing material to enter the reactor core. (author)

9. The fast reactor

International Nuclear Information System (INIS)

1980-02-01

The subject is discussed as follows: brief description of fast reactors; advantage in conserving uranium resources; experience, in UK and elsewhere, in fast reactor design, construction and operation; safety; production of plutonium, security aspects; consideration of future UK fast reactor programme. (U.K.)

10. Mirror fusion reactor design

International Nuclear Information System (INIS)

Neef, W.S. Jr.; Carlson, G.A.

1979-01-01

Recent conceptual reactor designs based on mirror confinement are described. Four components of mirror reactors for which materials considerations and structural mechanics analysis must play an important role in successful design are discussed. The reactor components are: (a) first-wall and thermal conversion blanket, (b) superconducting magnets and their force restraining structure, (c) neutral beam injectors, and (d) plasma direct energy converters

11. Towards nuclear fusion reactors

International Nuclear Information System (INIS)

1993-11-01

The results of nuclear fusion researches in JAERI are summarized. In this report, following themes are collected: the concept of fusion reactor (including ITER), fusion reactor safety, plasma confinement, fusion reactor equipment, and so on. Includes glossary. (J.P.N.)

12. Rotating reactors : a review

NARCIS (Netherlands)

Visscher, F.; Schaaf, van der J.; Nijhuis, T.A.; Schouten, J.C.

2013-01-01

This review-perspective paper describes the current state-of-the-art in the field of rotating reactors. The paper has a focus on rotating reactor technology with applications at lab scale, pilot scale and industrial scale. Rotating reactors are classified and discussed according to their geometry:

13. Refuelling nuclear reactors

International Nuclear Information System (INIS)

Stacey, J.; Webb, J.; White, W.P.; McLaren, N.H.

1981-01-01

An improved nuclear reactor refuelling machine is described which can be left in the reactor vault to reduce the off-load refuelling time for the reactor. The system comprises a gripper device rangeable within a tubular chute, the gripper device being movable by a pantograph. (U.K.)

14. Reactor power measuring device

International Nuclear Information System (INIS)

Izumi, Mikio; Sano, Yuji; Seki, Eiji; Yoshida, Toshifumi; Ito, Toshiaki.

1993-01-01

The present invention provides a self-powered long detector having a sensitivity over the entire length of a reactor core as an entire control rod withdrawal range of a BWR type reactor, and a reactor power measuring device using a gamma ray thermometer which scarcely causes sensitivity degradation. That is, a hollow protection pipe is disposed passing through the reactor core from the outside of a reactor pressure vessel. The self-powered long detectors and the gamma ray thermometers are inserted and installed in the protection pipe. An average reactor power in an axial direction of the reactor relative to a certain position in the horizontal cross section of the reactor core is determined based on the power of the self-powered long detector over the entire length of the reactor core. Since the response of the self-powered detector relative to a local power change is rapid, the output is used as an input signal to a safety protection device of the reactor core. Further, a gamma ray thermometer secured in the reactor and having scarce sensitivity degradation is used instead of an incore travelling neutron monitor used for relative calibration of an existent neutron monitor secured in the reactor. (I.S.)

15. Ulysse, mentor reactor

International Nuclear Information System (INIS)

Bouquin, B.; Rio, I.; Safieh, J.

1997-01-01

On July 23, 1961, the ULYSSE reactor began its first power rise. Designed at that time to train nuclear engineering students and reactor operators, this reactor still remains an indispensable tool for nuclear teaching and a choice instrument for scientists. (author)

16. Mechanical spectral shift reactor

International Nuclear Information System (INIS)

Sherwood, D.G.; Wilson, J.F.; Salton, R.B.; Fensterer, H.F.

1981-01-01

A mechanical spectral shift reactor comprises apparatus for inserting and withdrawing water displacer elements from the reactor core for selectively changing the water-moderator volume in the core thereby changing the reactivity of the core. The apparatus includes drivemechanisms for moving the displacer elements relative to the core and guide mechanisms for guiding the displayer rods through the reactor vessel

17. Mechanical spectral shift reactor

International Nuclear Information System (INIS)

Sherwood, D.G.; Wilson, J.F.; Salton, R.B.; Fensterer, H.F.

1982-01-01

A mechanical spectral shift reactor comprises apparatus for inserting and withdrawing water displacer elements from the reactor core for selectively changing the water-moderator volume in the core thereby changing the reactivity of the core. The apparatus includes drive mechanisms for moving the displacer elements relative to the core and guide mechanisms for guiding the displacer rods through the reactor vessel. (author)

18. Neutron behavior, reactor control, and reactor heat transfer. Volume four

International Nuclear Information System (INIS)

Anon.

1986-01-01

Volume four covers neutron behavior (neutron absorption, how big are nuclei, neutron slowing down, neutron losses, the self-sustaining reactor), reactor control (what is controlled in a reactor, controlling neutron population, is it easy to control a reactor, range of reactor control, what happens when the fuel burns up, controlling a PWR, controlling a BWR, inherent safety of reactors), and reactor heat transfer (heat generation in a nuclear reactor, how is heat removed from a reactor core, heat transfer rate, heat transfer properties of the reactor coolant)

19. Reactor as furnace and reactor as lamp

International Nuclear Information System (INIS)

Goldanskii, V.I.

1992-01-01

There are presented general characteristics of the following ways of transforming of nuclear energy released in reactors into chemical : ordinary way (i.e. trough the heat, mechanical energy and electricity); chemonuclear synthesis ; use of high-temperature fuel elements (reactor as furnace); use of the mixed nγ-radiation of reactors; use of the radiation loops; radiation - photochemical synthesis (reactor as lamp). Advantage and disadvantages of all above variants are compared. The yield of the primary product of fixation of nitrogen (nitric oxide NO) in reactor with the high-temperature (above ca. 1900degC) fuel elements (reactor-furnace) can exceed W ∼ 200 kg per gram of burned uranium. For the latter variant (reactor-lamp) the yield of chemical products can reach W ∼ 60 kg. per gram of uranium. Such values of W are close to or even strongly exceed the yields of chemical products for other abovementioned variants and - what is particularly important - are not connected to the necessity of archscrupulous removal of radioactive contamination of products. (author)

20. Nuclear reactor physics

CERN Document Server

Stacey, Weston M

2010-01-01

Nuclear reactor physics is the core discipline of nuclear engineering. Nuclear reactors now account for a significant portion of the electrical power generated worldwide, and new power reactors with improved fuel cycles are being developed. At the same time, the past few decades have seen an ever-increasing number of industrial, medical, military, and research applications for nuclear reactors. The second edition of this successful comprehensive textbook and reference on basic and advanced nuclear reactor physics has been completely updated, revised and enlarged to include the latest developme

1. Light water reactor safety

CERN Document Server

Pershagen, B

2013-01-01

This book describes the principles and practices of reactor safety as applied to the design, regulation and operation of light water reactors, combining a historical approach with an up-to-date account of the safety, technology and operating experience of both pressurized water reactors and boiling water reactors. The introductory chapters set out the basic facts upon which the safety of light water reactors depend. The central section is devoted to the methods and results of safety analysis. The accidents at Three Mile Island and Chernobyl are reviewed and their implications for light wate

2. Fundamentals of reactor chemistry

International Nuclear Information System (INIS)

Akatsu, Eiko

1981-12-01

In the Nuclear Engineering School of JAERI, many courses are presented for the people working in and around the nuclear reactors. The curricula of the courses contain also the subject material of chemistry. With reference to the foreign curricula, a plan of educational subject material of chemistry in the Nuclear Engineering School of JAERI was considered, and the fundamental part of reactor chemistry was reviewed in this report. Since the students of the Nuclear Engineering School are not chemists, the knowledge necessary in and around the nuclear reactors was emphasized in order to familiarize the students with the reactor chemistry. The teaching experience of the fundamentals of reactor chemistry is also given. (author)

3. Generation III+ Reactor Portfolio

International Nuclear Information System (INIS)

2010-03-01

While the power generation needs of utilities are unique and diverse, they are all faced with the double challenge of meeting growing electricity needs while curbing CO 2 emissions. To answer these diverse needs and help tackle this challenge, AREVA has developed several reactor models which are briefly described in this document: The EPR TM Reactor: designed on the basis of the Konvoi (Germany) and N4 (France) reactors, the EPRTM reactor is an evolutionary model designed to achieve best-in-class safety and operational performance levels. The ATMEA1 TM reactor: jointly designed by Mitsubishi Heavy Industries and AREVA through ATMEA, their common company. This reactor design benefits from the competencies and expertise of the two mother companies, which have commissioned close to 130 reactor units. The KERENA TM reactor: Designed on the basis of the most recent German BWR reactors (Gundremmingen) the KERENA TM reactor relies on proven technology while also including innovative, yet thoroughly tested, features. The optimal combination of active and passive safety systems for a boiling water reactor achieves a very low probability of severe accident

4. The fast breeder reactor

International Nuclear Information System (INIS)

Davis, D.A.; Baker, M.A.W.; Hall, R.S.

1990-01-01

Following submission of written evidence, the Energy Committee members asked questions of three witnesses from the Central Electricity Generating Board and Nuclear Electric (which will be the government owned company running nuclear power stations after privatisation). Both questions and answers are reported verbatim. The points raised include where the responsibility for the future fast reactor programme should lie, with government only or with private enterprise or both and the viability of fast breeder reactors in the future. The case for the fast reactor was stated as essentially strategic not economic. This raised the issue of nuclear cost which has both a construction and a decommissioning element. There was considerable discussion as to the cost of building a European Fast reactor and the cost of the electricity it would generate compared with PWR type reactors. The likely demand for fast reactors will not arrive for 20-30 years and the need to build a fast reactor now is questioned. (UK)

5. One piece reactor removal

International Nuclear Information System (INIS)

Chia, Wei-Min; Wang, Song-Feng

1993-01-01

The strategy of Taiwan Research Reactor Renewal plan is to remove the old reactor block with One Piece Reactor Removal (OPRR) method for installing a new research reactor in original building. In this paper, the engineering design of each transportation works including the work method, the major equipments, the design policy and design criteria is described and discussed. In addition, to ensure the reactor block is safety transported for storage and to guarantee the integrity of reactor base mat is maintained for new reactor, operation safety is drawn special attention, particularly under seismic condition, to warrant safe operation of OPRR. ALARA principle and Below Regulatory Concern (BRC) practice were also incorporated in the planning to minimize the collective dose and the total amount of radioactive wastes. All these activities are introduced in this paper. (J.P.N.)

6. Reactor power control device

International Nuclear Information System (INIS)

Ishii, Yoshihiko; Arita, Setsuo; Miyamoto, Yoshiyuki; Fukazawa, Yukihisa; Ishii, Kazuhiko

1998-01-01

The present invention provides a reactor power control device capable of enhancing an operation efficiency while keeping high reliability and safety in a BWR type nuclear power plant. Namely, the device of the present invention comprises (1) a means for inputting a set value of a generator power and a set value of a reactor power, (2) a means for controlling the reactor power to either smaller one of the reactor power corresponding to the set value of the generator power and the set value of the reactor power. With such procedures, even if the nuclear power plant is set so as to operate it to make the reactor power 100%, when the generator power reaches the upper limit, the reactor power is controlled with a preference given to the upper limit value of the generator power. Accordingly, safety and reliability are not deteriorated. The operation efficiency of the plant can be improved. (I.S.)

7. Reactor power monitoring device

International Nuclear Information System (INIS)

Dogen, Ayumi; Ozawa, Michihiro.

1983-01-01

Purpose: To significantly improve the working efficiency of a nuclear reactor by reflecting the control rod history effect on thermal variants required for the monitoring of the reactor operation. Constitution: An incore power distribution calculation section reads the incore neutron fluxes detected by neutron detectors disposed in the reactor to calculate the incore power distribution. A burnup degree distribution calculation section calculates the burnup degree distribution in the reactor based on the thus calculated incore power distribution. A control rod history date store device supplied with the burnup degree distribution renews the stored control rod history data based on the present control rod pattern and the burnup degree distribution. Then, thermal variants of the nuclear reactor are calculated based on the thus renewed control rod history data. Since the control rod history effect is reflected on the thermal variants required for the monitoring of the reactor operation, the working efficiency of the nuclear reactor can be improved significantly. (Seki, T.)

8. The Maple reactor project

International Nuclear Information System (INIS)

Malkoske, G.R.; Labrie, J.-P.

2003-01-01

MDS Nordion supplies the majority of the world's reactor-produced medical isotopes. These isotopes are currently produced in the NRU reactor at AECL's Chalk River Laboratories (CRL). Medical isotopes and related technology are relied upon around the world to prevent, diagnose and treat disease. The NRU reactor, which has played a key role in supplying medical isotopes to date, has been in operation for over 40 years. Replacing this aging reactor has been a priority for MDS Nordion to assure the global nuclear medicine community that Canada will continue to be a dependable supplier of medical isotopes. MDS Nordion contracted AECL to construct two MAPLE reactors dedicated to the production of medical isotopes. The MDS Nordion Medical Isotope Reactor (MMIR) project started in September 1996. This paper describes the MAPLE reactors that AECL has built at its CRL site, and will operate for MDS Nordion. (author)

9. Fission reactors and materials

International Nuclear Information System (INIS)

Frost, B.R.T.

1981-12-01

The American-designed boiling water reactor and pressurized water reactor dominate the designs currently in use and under construction worldwide. As in all energy systems, materials problems have appeared during service; these include stress-corrosion of stainless steel pipes and heat exchangers and questions regarding crack behavior in pressure vessels. To obtain the maximum potential energy from our limited uranium supplies is is essential to develop the fast breeder reactor. The materials in these reactors are subjected to higher temperatures and neutron fluxes but lower pressures than in the water reactors. The performance required of the fuel elements is more arduous in the breeder than in water reactors. Extensive materials programs are in progress in test reactors and in large test rigs to ensure that materials will be available to meet these conditions

10. Reactor Vessel Surveillance Program for Advanced Reactor

Energy Technology Data Exchange (ETDEWEB)

Jeong, Kyeong-Hoon; Kim, Tae-Wan; Lee, Gyu-Mahn; Kim, Jong-Wook; Park, Keun-Bae; Kim, Keung-Koo

2008-10-15

This report provides the design requirements of an integral type reactor vessel surveillance program for an integral type reactor in accordance with the requirements of Korean MEST (Ministry of Education, Science and Technology Development) Notice 2008-18. This report covers the requirements for the design of surveillance capsule assemblies including their test specimens, test block materials, handling tools, and monitors of the surveillance capsule neutron fluence and temperature. In addition, this report provides design requirements for the program for irradiation surveillance of reactor vessel materials, a layout of specimens and monitors in the surveillance capsule, procedures of installation and retrieval of the surveillance capsule assemblies, and the layout of the surveillance capsule assemblies in the reactor.

11. Research reactors in Argentina

International Nuclear Information System (INIS)

Carlos Ruben Calabrese

1999-01-01

Argentine Nuclear Development started in early fifties. In 1957, it was decided to built the first a research reactor. RA-1 reactor (120 kw, today licensed to work at 40 kW) started operation in January 1958. Originally RA-1 was an Argonaut (American design) reactor. In early sixties, the RA-1 core was changed. Fuel rods (20% enrichment) was introduced instead the old Argonaut core design. For that reason, a critical facility named RA-0 was built. After that, the RA-3 project started, to build a multipurpose 5 MW nuclear reactor MTR pool type, to produce radioisotopes and research. For that reason and to define the characteristics of the RA-3 core, another critical facility was built, RA-2. Initially RA-3 was a 90 % enriched fuel reactor, and started operation in 1967. When Atucha I NPP project started, a German design Power Reactor, a small homogeneous reactor was donated by the German Government to Argentina (1969). This was RA-4 reactor (20% enrichment, 1W). In 1982, RA-6 pool reactor achieved criticality. This is a 500 kW reactor with 90% enriched MTR fuel elements. In 1990, RA-3 started to operate fueled by 20% enriched fuel. In 1997, the RA-8 (multipurpose critical facility located at Pilcaniyeu) started to operate. RA-3 reactor is the most important CNEA reactor for Argentine Research Reactors development. It is the first in a succession of Argentine MTR reactors built by CNEA (and INVAP SE ) in Argentina and other countries: RA-6 (500 kW, Bariloche-Argentina), RP-10 (10MW, Peru), NUR (500 kW, Algeria), MPR (22 MW, Egypt). The experience of Argentinian industry permits to compete with foreign developed countries as supplier of research reactors. Today, CNEA has six research reactors whose activities have a range from education and promotion of nuclear activity, to radioisotope production. For more than forty years, Argentine Research Reactors are working. The experience of Argentine is important, and argentine firms are able to compete in the design and

12. Siting of research reactors

International Nuclear Information System (INIS)

1987-01-01

The purpose of this document is to develop criteria for siting and the site-related design basis for research reactors. The concepts presented in this document are intended as recommendations for new reactors and are not suggested for backfitting purposes for facilities already in existence. In siting research reactors serious consideration is given to minimizing the effects of the site on the reactor and the reactor on the site and the potential impact of the reactor on the environment. In this document guidance is first provided on the evaluation of the radiological impact of the installation under normal reactor operation and accident conditions. A classification of research reactors in groups is then proposed, together with a different approach for each group, to take into account the relevant safety problems associated with facilities of different characteristics. Guidance is also provided for both extreme natural events and for man-induced external events which could affect the safe operation of the reactor. Extreme natural events include earthquakes, flooding for river or coastal sites and extreme meteorological phenomena. The feasibility of emergency planning is finally considered for each group of reactors

13. Reactor core for FBR type reactor

International Nuclear Information System (INIS)

Fujita, Tomoko; Watanabe, Hisao; Kasai, Shigeo; Yokoyama, Tsugio; Matsumoto, Hiroshi.

1996-01-01

In a gas-sealed assembly for a FBR type reactor, two or more kinds of assemblies having different eigen frequency and a structure for suppressing oscillation of liquid surface are disposed in a reactor core. Coolant introduction channels for introducing coolants from inside and outside are disposed in the inside of structural members of an upper shielding member to form a shielding member-cooling structure in the reactor core. A structure for promoting heat conduction between a sealed gas in the assembly and coolants at the inner side or the outside of the assembly is disposed in the reactor core. A material which generates heat by neutron irradiation is disposed in the assembly to heat the sealed gases positively by radiation heat from the heat generation member also upon occurrence of power elevation-type event to cause temperature expansion. Namely, the coolants flown out from or into the gas sealed-assemblies cause differential fluctuation on the liquid surface, and the change of the capacity of a gas region is also different on every gas-sealed assemblies thereby enabling to suppress fluctuation of the reactor power. Pressure loss is increased by a baffle plate or the like to lower the liquid surface of the sodium coolants or decrease the elevating speed thereof thereby suppressing fluctuation of the reactor power. (N.H.)

14. Thai research reactor

International Nuclear Information System (INIS)

Aramrattana, M.

1987-01-01

The Office of Atomic Energy for Peace (OAEP) was established in 1962, as a reactor center, by the virtue of the Atomic Energy for Peace Act, under operational policy and authority of the Thai Atomic Energy for Peace Commission (TAEPC); and under administration of Ministry of Science, Technology and Energy. It owns and operates the only Thai Research Reactor (TRR-1/M1). The TRR-1/M1 is a mixed reactor system constituting of the old MTR type swimming pool, irradiation facilities and cooling system; and TRIGA Mark III core and control instrumentation. The general performance of TRR-1/M1 is summarized in Table I. The safe operation of TRR-1/M1 is regulated by Reactor Safety Committee (RSC), established under TAEPC, and Health Physics Group of OAEP. The RCS has responsibility and duty to review of and make recommendations on Reactor Standing Orders, Reactor Operation Procedures, Reactor Core Loading and Requests for Reactor Experiments. In addition,there also exist of Emergency Procedures which is administered by OAEP. The Reactor Operation Procedures constitute of reactor operating procedures, system operating procedures and reactor maintenance procedures. At the level of reactor routine operating procedures, there is a set of Specifications on Safety and Operation Limits and Code of Practice from which reactor shift supervisor and operators must follow in order to assure the safe operation of TRR-1/M1. Table II is the summary of such specifications. The OAEP is now upgrading certain major components of the TRR-1/M1 such as the cooling system, the ventilation system and monitoring equipment to ensure their adequately safe and reliable performance under normal and emergency conditions. Furthermore, the International Atomic Energy Agency has been providing assistance in areas of operation and maintenance and safety analysis. (author)

15. Nuclear Reactor Physics

Science.gov (United States)

Stacey, Weston M.

2001-02-01

An authoritative textbook and up-to-date professional's guide to basic and advanced principles and practices Nuclear reactors now account for a significant portion of the electrical power generated worldwide. At the same time, the past few decades have seen an ever-increasing number of industrial, medical, military, and research applications for nuclear reactors. Nuclear reactor physics is the core discipline of nuclear engineering, and as the first comprehensive textbook and reference on basic and advanced nuclear reactor physics to appear in a quarter century, this book fills a large gap in the professional literature. Nuclear Reactor Physics is a textbook for students new to the subject, for others who need a basic understanding of how nuclear reactors work, as well as for those who are, or wish to become, specialists in nuclear reactor physics and reactor physics computations. It is also a valuable resource for engineers responsible for the operation of nuclear reactors. Dr. Weston Stacey begins with clear presentations of the basic physical principles, nuclear data, and computational methodology needed to understand both the static and dynamic behaviors of nuclear reactors. This is followed by in-depth discussions of advanced concepts, including extensive treatment of neutron transport computational methods. As an aid to comprehension and quick mastery of computational skills, he provides numerous examples illustrating step-by-step procedures for performing the calculations described and chapter-end problems. Nuclear Reactor Physics is a useful textbook and working reference. It is an excellent self-teaching guide for research scientists, engineers, and technicians involved in industrial, research, and military applications of nuclear reactors, as well as government regulators who wish to increase their understanding of nuclear reactors.

16. Reactor containment and reactor safety in the United States

International Nuclear Information System (INIS)

Kouts, H.

1986-01-01

The reactor safety systems of two reactors are studied aiming at the reactor containment integrity. The first is a BWR type reactor and is called Peachbottom 2, and the second is a PWR type reactor, and is called surry. (E.G.) [pt

17. Multipurpose research reactors

International Nuclear Information System (INIS)

1988-01-01

The international symposium on the utilization of multipurpose research reactors and related international co-operation was organized by the IAEA to provide for information exchange on current uses of research reactors and international co-operative projects. The symposium was attended by about 140 participants from 36 countries and two international organizations. There were 49 oral presentations of papers and 24 poster presentations. The presentations were divided into 7 sessions devoted to the following topics: neutron beam research and applications of neutron scattering (6 papers and 1 poster), reactor engineering (6 papers and 5 posters), irradiation testing of fuel and material for fission and fusion reactors (6 papers and 10 posters), research reactor utilization programmes (13 papers and 4 posters), neutron capture therapy (4 papers), neutron activation analysis (3 papers and 4 posters), application of small reactors in research and training (11 papers). A separate abstract was prepared for each of these papers. Refs, figs and tabs

18. TRIGA reactor main systems

International Nuclear Information System (INIS)

Boeck, H.; Villa, M.

2007-01-01

This module describes the main systems of low power (<2 MW) and higher power (≥2 MW) TRIGA reactors. The most significant difference between the two is that forced reactor cooling and an emergency core cooling system are generally required for the higher power TRIGA reactors. However, those TRIGA reactors that are designed to be operated above 3 MW also use a TRIGA fuel that is specifically designed for those higher power outputs (3 to 14 MW). Typical values are given for the respective systems although each TRIGA facility will have unique characteristics that may only be determined by the experienced facility operators. Due to the inherent wide scope of these research reactor facilities construction and missions, this training module covers those systems found at most operating TRIGA reactor facilities but may also discuss non-standard equipment that was found to be operationally useful although not necessarily required. (author)

19. Fast Spectrum Reactors

CERN Document Server

Todd, Donald; Tsvetkov, Pavel

2012-01-01

Fast Spectrum Reactors presents a detailed overview of world-wide technology contributing to the development of fast spectrum reactors. With a unique focus on the capabilities of fast spectrum reactors to address nuclear waste transmutation issues, in addition to the well-known capabilities of breeding new fuel, this volume describes how fast spectrum reactors contribute to the wide application of nuclear power systems to serve the global nuclear renaissance while minimizing nuclear proliferation concerns. Readers will find an introduction to the sustainable development of nuclear energy and the role of fast reactors, in addition to an economic analysis of nuclear reactors. A section devoted to neutronics offers the current trends in nuclear design, such as performance parameters and the optimization of advanced power systems. The latest findings on fuel management, partitioning and transmutation include the physics, efficiency and strategies of transmutation, homogeneous and heterogeneous recycling, in addit...

International Nuclear Information System (INIS)

Mammen, S.; Mukherjee, P.; Bhatnagar, A.; Sasidharan, K.; Raina, V.K.

2009-01-01

Apsara is a 1 MW swimming pool type research reactor using high enriched uranium as fuel with light water as coolant and moderator. The reactor is in operation for more than five decades and has been extensively used for basic research, radioisotope production, neutron radiography, detector testing, shielding experiments etc. In view of its long service period, it is planned to carry out refurbishment of the reactor to extend its useful life. During refurbishment, it is also planned to upgrade the reactor to a 2 MW reactor to improve its utilization and to upgrade the structure, system and components in line with the current safety standards. This paper gives a brief account of the design features and safety aspects of the upgraded Apsara reactor. (author)

1. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

1980-09-01

Research activities in the Division of Reactor Engineering in fiscal 1979 are described. The work of the Division is closely related to development of multi-purpose Very High Temperature Gas Cooled Reactor and fusion reactor, and development of Liquid Metal Fast Breeder Reactor carried out by Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are achievements in fields such as nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, reactor and nuclear instrumentation, reactor control and diagnosis, and fusion reactor technology, and activities of the Committees on Reactor Physics and on Decomissioning of Nuclear Facilities. (author)

2. Spectral shift reactor control method

International Nuclear Information System (INIS)

Impink, A.J. Jr.

1981-01-01

A method of operating a nuclear reactor having a core and coolant displacer elements arranged in the core wherein is established a reator coolant temperature set point at which it is desired to operate said reactor and first reactor coolant temperature band limits are provided within which said set point is located and it is desired to operate said reactor charactrized in that said reactor coolant displacer elements are moved relative to the reactor core for adjusting the volume of reactor coolant in said core as said reactor coolant temperature approaches said first band limits thereby to maintain said reactor coolant temperature near said set point and within said first band limits

3. Reactor Engineering Department annual report

International Nuclear Information System (INIS)

1985-08-01

Research and development activities in the Department of Reactor Engineering in fiscal 1984 are described. The work of the Department is closely related to development of multipurpose Very High Temperature Gas Cooled Reactor and Fusion Reactor, and development of Liquid Metal Fast Breeder Reactor carried out by Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are achievements in fields such as nuclear data and group constants, theoretical method and code development, reactor physics experiment and analysis, fusion neutronics, shielding, reactor and nuclear instrumentation, reactor control and diagnosis, safeguards technology, and activities of the Committee on Reactor Physics. (author)

4. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

Matsuura, Shojiro; Nakahara, Yasuaki; Takano, Hideki

1982-09-01

Research and development activities in the Division of Reactor Engineering in fiscal 1981 are described. The work of the Division is closely related to development of multipurpose Very High Temperature Gas Cooled Reactor and fusion reactor, and development of Liquid Metal Fast Breeder Reactor carried out by Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are achievements in fields such as nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, reactor and nuclear instrumentation, reactor control and diagnosis, and fusion reactor technology, and activities of the Committee on Reactor Physics. (author)

5. Power reactors operational diagnosis

International Nuclear Information System (INIS)

Dach, K.; Pecinka, L.

1976-01-01

The definition of reactor operational diagnostics is presented and the fundamental trends of research are determined. The possible sources of power reactor malfunctions, the methods of defect detection, the data evaluation and the analysis of the results are discussed in detail. In view of scarcity of a theoretical basis and of insufficient in-core instrumentation, operational diagnostics cannot be as yet incorporated in a computer-aided reactor control system. (author)

6. Fast reactors worldwide

International Nuclear Information System (INIS)

Hall, R.S.; Vignon, D.

1985-01-01

The paper concerns the evolution of fast reactors over the past 30 years, and their present status. Fast reactor development in different countries is described, and the present position, with emphasis on cost reduction and collaboration, is examined. The French development of the fast breeder type reactor is reviewed, and includes: the acquisition of technical skills, the search for competitive costs and the spx2 project, and more advanced designs. Future prospects are also discussed. (U.K.)

7. Pressurised water reactor operation

International Nuclear Information System (INIS)

Birnie, S.; Lamonby, J.K.

1987-01-01

The operation of a pressurized water reactor (PWR) is described with respect to the procedure for a unit start-up. The systems details and numerical data are for a four loop PWR station of the design proposed for Sizewell-'B', United Kingdom. A description is given of: the initial conditions, filling the reactor coolant system (RCS), heat-up and pressurisation of the RCS, secondary system preparations, reactor start-up, and reactivity control at power. (UK)

8. Reactor Safety Analysis

International Nuclear Information System (INIS)

Arien, B.

1998-01-01

The objective of SCK-CEN's programme on reactor safety is to develop expertise in probabilistic and deterministic reactor safety analysis. The research programme consists of four main activities, in particular the development of software for reliability analysis of large systems and participation in the international PHEBUS-FP programme for severe accidents, the development of an expert system for the aid to diagnosis; the development and application of a probabilistic reactor dynamics method. Main achievements in 1999 are reported

9. Seals in nuclear reactors

International Nuclear Information System (INIS)

1979-01-01

The aim of this invention is the provision of improved seals for reactor vessels in which fuel assemblies are located together with inlets and outlets for the circulation of a coolant. The object is to provide a seal arrangement for the rotatable plugs of nuclear reactor closure heads which has good sealing capacities over a wide gap during operation of the reactor but which also permits uninhibited rotation of the plugs for maintenance. (U.K.)

10. Reactor BR2

Energy Technology Data Exchange (ETDEWEB)

Gubel, P

2000-07-01

The BR2 reactor is still SCK-CEN's most important nuclear facility. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. Various aspects concerning the operation of the BR2 Reactor, the utilisation of the CALLISTO loop and the irradiation programme, the BR2 R and D programme and the production of isotopes and of NTD-silicon are discussed. Progress and achievements in 1999 are reported.

11. The Dragon reactor experiment

International Nuclear Information System (INIS)

Anon.

1976-01-01

The concept on which the Dragon Reactor Experiment was based was evolved at the Atomic Energy Research Establishment at Harwell in 1956, and in February of that year a High Temperature Gas- cooled Reactor Project Group was set up to study the feasibility of a helium-cooled reactor with a graphite or beryllium moderator, and with the emphasis on the thorium fuel cycle [af

12. The replacement research reactor

International Nuclear Information System (INIS)

Cameron, R.

1999-01-01

As a consequences of the government decision in September 1997. ANSTO established a replacement research reactor project to manage the procurement of the replacement reactor through the necessary approval, tendering and contract management stages This paper provides an update of the status of the project including the completion of the Environmental Impact Statement. Prequalification and Public Works Committee processes. The aims of the project, management organisation, reactor type and expected capabilities are also described

13. TRIGA reactor characteristics

International Nuclear Information System (INIS)

Boeck, H.; Villa, M.

2007-01-01

This module describes the general design, characteristics and parameters of TRIGA reactors and fuels. It is recommended that most of this information should be incorporated into any reactor operator training program and, in many cases, the facility Safety Analysis Report. It is oriented to teach the basics of the physics and mechanical design of the TRIGA fuel as well as its unique operational characteristics and the differences between TRIGA fuels and others more traditional reactor fuels. (nevyjel)

14. Integral fast reactor

International Nuclear Information System (INIS)

Chang, Y.I.

1989-01-01

The Integral Fast Reactor (IFR) is an innovative liquid metal reactor concept being developed at Argonne National Laboratory. It seeks to specifically exploit the inherent properties of liquid metal cooling and metallic fuel in a way that leads to substantial improvements in the characteristics of the complete reactor system. This paper describes the key features and potential advantages of the IFR concept, with emphasis on its safety characteristics

15. Reactor BR2

International Nuclear Information System (INIS)

Gubel, P.

2000-01-01

The BR2 reactor is still SCK-CEN's most important nuclear facility. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. Various aspects concerning the operation of the BR2 Reactor, the utilisation of the CALLISTO loop and the irradiation programme, the BR2 R and D programme and the production of isotopes and of NTD-silicon are discussed. Progress and achievements in 1999 are reported

16. The Integral Fast Reactor

International Nuclear Information System (INIS)

Chang, Y.I.

1988-01-01

The Integral Fast Reactor (IFR) is an innovative liquid metal reactor concept being developed at Argonne National Laboratory. It seeks to specifically exploit the inherent properties of liquid metal cooling and metallic fuel in a way that leads to substantial improvements in the characteristics of the complete reactor system. This paper describes the key features and potential advantages of the IFR concept, with emphasis on its safety characteristics. 3 refs., 4 figs., 1 tab

17. Mirror fusion reactors

International Nuclear Information System (INIS)

Anon.

1978-01-01

Conceptual design studies were made of fusion reactors based on the three current mirror-confinement concepts: the standard mirror, the tandem mirror, and the field-reversed mirror. Recent studies of the standard mirror have emphasized its potential as a fusion-fission hybrid reactor, designed to produce fuel for fission reactors. We have designed a large commercial hybrid and a small pilot-plant hybrid based on standard mirror confinement. Tandem mirror designs include a commercial 1000-MWe fusion power plant and a nearer term tandem mirror hybrid. Field-reversed mirror designs include a multicell commercial reactor producing 75 MWe and a single-cell pilot plant

18. HOMOGENEOUS NUCLEAR POWER REACTOR

Science.gov (United States)

King, L.D.P.

1959-09-01

A homogeneous nuclear power reactor utilizing forced circulation of the liquid fuel is described. The reactor does not require fuel handling outside of the reactor vessel during any normal operation including complete shutdown to room temperature, the reactor being selfregulating under extreme operating conditions and controlled by the thermal expansion of the liquid fuel. The liquid fuel utilized is a uranium, phosphoric acid, and water solution which requires no gus exhaust system or independent gas recombining system, thereby eliminating the handling of radioiytic gas.

19. Australian research reactor studies

International Nuclear Information System (INIS)

McCulloch, D.B.

1978-01-01

The Australian AEC has two research reactors at the Lucas Heights Research Establishment, a 10 HW DIDO class materials testing reactor, HIFAR, and a smaller 100kW reactor MOATA, which was recently upgraded from 10kW power level. Because of the HIFAR being some 20 years old, major renewal and repair programmes are necessary to keep it operational. To enable meeting projected increases in demand for radioisotopes, plans for a new reactor to replace the HIFAR have been made and the design criteria are described in the paper. (author)

20. Mirror fusion reactors

International Nuclear Information System (INIS)

Carlson, G.A.; Moir, R.W.

1978-01-01

We have carried out conceptual design studies of fusion reactors based on the three current mirror confinement concepts: the standard mirror, the tandem mirror, and the field-reversed mirror. Recent studies of the standard mirror have emphasized its potential as a fusion-fission hybrid reactor, designed to produce fission fuel for fission reactors. We have designed a large commercial hybrid based on standard mirror confinement, and also a small pilot plant hybrid. Tandem mirror designs include a commercial 1000 MWe fusion power plant and a nearer term tandem mirror hybrid. Field-reversed mirror designs include a multicell commercial reactor producing 75 MWe and a single cell pilot plant

1. Reactor feedwater system

International Nuclear Information System (INIS)

Hikabe, Katsumi.

1978-01-01

Purpose: In order to prevent thermal stresses of a core of PWR type reactor, described has been a method for feeding heated recirculating water to the core in the case of the reactor start-up or shut-down. Constitution: A recirculating water is degassed, cleaned up and heated in the steam condensers, and then feeds the water to the reactor, characterized in that heaters are provided in the bypasses of the turbine, so that heated water is constantly supplied to the reactor. (Nakamura, S.)

2. Remote Reactor Monitoring

Energy Technology Data Exchange (ETDEWEB)

Bernstein, Adam [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Dazeley, Steve [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Dobie, Doug [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Marleau, Peter [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States); Brennan, Jim [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States); Gerling, Mark [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States); Sumner, Matthew [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States); Sweany, Melinda [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States)

2014-10-21

The overall goal of the WATCHMAN project is to experimentally demonstrate the potential of water Cerenkov antineutrino detectors as a tool for remote monitoring of nuclear reactors. In particular, the project seeks to field a large prototype gadolinium-doped, water-based antineutrino detector to demonstrate sensitivity to a power reactor at ~10 kilometer standoff using a kiloton scale detector. The technology under development, when fully realized at large scale, could provide remote near-real-time information about reactor existence and operational status for small operating nuclear reactors out to distances of many hundreds of kilometers.

3. Fusion Reactor Materials

International Nuclear Information System (INIS)

Decreton, M.

2002-01-01

The objective of SCK-CEN's programme on fusion reactor materials is to contribute to the knowledge on the radiation-induced behaviour of fusion reactor materials and components as well as to help the international community in building the scientific and technical basis needed for the construction of the future reactor. Ongoing projects include: the study of the mechanical and chemical (corrosion) behaviour of structural materials under neutron irradiation and water coolant environment; the investigation of the characteristics of irradiated first wall material such as beryllium; investigations on the management of materials resulting from the dismantling of fusion reactors including waste disposal. Progress and achievements in these areas in 2001 are discussed

4. Trench reactor: an overview

International Nuclear Information System (INIS)

Spinrad, B.I.; Rohach, A.F.; Razzaque, M.M.; Sankoorikal, J.T.; Schmidt, R.S.; Lofshult, J.; Ramin, T.; Sokmen, N.; Lin, L.C.

1988-01-01

Recent fast, sodium-cooled reactor designs reflect new conditions. In nuclear energy these conditions are (a) emphasis on maintainability and operability, (b) design for more transparent safety, and (c) a surplus of uranium and enrichment availability that eases concerns about light water reactor fueling costs. In utility practice the demand is for less capital exposure, short construction time, smaller new unit sizes, and low capital cost. The PRISM, SAFR, and integral fast reactor (IFR) concepts are responses to these conditions. Fast reactors will not soon be deployed commercially, so more radical designs can be considered. The trench reactor is the product of such thinking. Its concepts are intended as contributions to the literature, which may be picked up by one of the existing programs or used in a new experimental project. The trench reactor is a thin-slab, pool-type reactor operated at very low power density and- for sodium-modest temperature. The thin slab is repeated in the sodium tank and the reactor core. The low power density permits a longer than conventional core height and a large-diameter fuel pin. Control is by borated steel slabs that can be lowered between the core and lateral sodium reflector. Shutdown is by semaphore slabs that can be swung into place just outside the control slabs. The paper presents major characteristics of the trench reactor that have been changed since the last report

5. New reactor concepts

International Nuclear Information System (INIS)

Meskens, G.; Govaerts, P.; Baugnet, J.-M.; Delbrassine, A.

1998-11-01

The document gives a summary of new nuclear reactor concepts from a technological point of view. Belgium supports the development of the European Pressurized-Water Reactor, which is an evolutionary concept based on the European experience in Pressurized-Water Reactors. A reorientation of the Belgian choice for this evolutionary concept may be required in case that a decision is taken to burn plutonium, when the need for flexible nuclear power plants arises or when new reactor concepts can demonstrate proved benefits in terms of safety and cost

International Nuclear Information System (INIS)

Dunn, J.T.; Finlay, R.B.; Olmstead, R.A.

1988-12-01

AECL has undertaken the design and development of a series of advanced CANDU reactors in the 700-1150 MW(e) size range. These advanced reactor designs are the product of ongoing generic research and development programs on CANDU technology and design studies for advanced CANDU reactors. The prime objective is to create a series of advanced CANDU reactors which are cost competitive with coal-fired plants in the market for large electricity generating stations. Specific plant designs in the advanced CANDU series will be ready for project commitment in the early 1990s and will be capable of further development to remain competitive well into the next century

7. Mechanical spectral shift reactor

International Nuclear Information System (INIS)

Doshi, P.K.; George, R.A.; Dollard, W.J.

1982-01-01

A mechanical spectral shift arrangement for controlling a nuclear reactor includes a plurality of reactor coolant displacer members which are inserted into a reactor core at the beginning of the core life to reduce the volume of reactor coolant-moderator in the core at start-up. However, as the reactivity of the core declines with fuel depletion, selected displacer members are withdrawn from the core at selected time intervals to increase core moderation at a time when fuel reactivity is declining. (author)

8. Nuclear reactor safety systems

International Nuclear Information System (INIS)

Ball, R.M.; Roberts, R.C.

1980-01-01

A safety system for shutting down a nuclear reactor under overload conditions is described. The system includes a series of parallel-connected computer memory type look-up tables each of which receives data on a particular reactor parameter and in each of which a precalculated functional value for that parameter is stored indicative of the percentage of maximum reactor load that the parameter contributes. The various functional values corresponding to the actual measured parameters are added together to provide a control signal used to shut down the reactor under overload conditions. (U.K.)

9. RA Reactor; Reaktor RA

Energy Technology Data Exchange (ETDEWEB)

NONE

1978-02-15

In addition to basic characteristics of the RA reactor, organizational scheme and financial incentives, this document covers describes the state of the reactor components after 18 years of operation, problems concerned with obtaining the licence for operation with 80% fuel, problems of spent fuel storage in the storage pool of the reactor building and the need for renewal of reactor equipment, first of all instrumentation. [Serbo-Croat] Pored osnovnih karakeristika reaktora RA, organizacije rada i finansijskih pokazatelja, razmatra se stanje opreme reaktora nakon 18 godina rada, pitanja dozvole za rad sa 80% obogacenim gorivom, problem skladistenja isluzenog goriva u bazenu zgrade reaktora i potreba za obnavljanjem komponenti opreme, pre svega elektronske.

10. Nuclear reactor internals arrangement

International Nuclear Information System (INIS)

Frisch, E.; Andrews, H.N.

1976-01-01

A nuclear reactor internals arrangement is disclosed which facilitates reactor refueling. A reactor vessel and a nuclear core is utilized in conjunction with an upper core support arrangement having means for storing withdrawn control rods therein. The upper core support is mounted to the underside of the reactor vessel closure head so that upon withdrawal of the control rods into the upper core support, the closure head, the upper core support and the control rods are removed as a single unit thereby directly exposing the core for purposes of refueling

11. Multi purpose research reactor

International Nuclear Information System (INIS)

Raina, V.K.; Sasidharan, K.; Sengupta, Samiran; Singh, Tej

2006-01-01

At present Dhruva and Cirus reactors provide the majority of research reactor based facilities to cater to the various needs of a vast pool of researchers in the field of material sciences, physics, chemistry, bio sciences, research and development work for nuclear power plants and production of radio isotopes. With a view to further consolidate and expand the scope of research and development in nuclear and allied sciences, a new 20 MWt multi purpose research reactor is being designed. This paper describes some of the design features and safety aspects of this reactor

12. FBR type reactors

International Nuclear Information System (INIS)

Suzuoki, Akira; Yamakawa, Masanori.

1985-01-01

Purpose: To enable safety and reliable after-heat removal from a reactor core. Constitution: During ordinary operation of a FBR type reactor, sodium coolants heated to a high temperature in a reactor core are exhausted therefrom, collide against the reactor core upper mechanisms to radially change the flowing direction and then enter between each of the guide vanes. In the case if a main recycling pump is failed and stopped during reactor operation and the recycling force is eliminated, the swirling stream of sodium that has been resulted by the flow guide mechanism during normal reactor operation is continuously maintained within a plenum at a high temperature. Accordingly, the sodium recycling force in the coolant flow channels within the reactor vessel can surely be maintained for a long period of time due to the centrifugal force of the sodium swirling stream. In this way, since the reactor core recycling flow rate can be secured even after the stopping of the main recycling pump, after-heat from the reactor core can safely and surely be removed. (Seki, T.)

13. FBR type reactor

International Nuclear Information System (INIS)

Hayase, Tamotsu.

1991-01-01

The present invention concerns an FBR type reactor in which transuranium elements are eliminated by nuclear conversion. There are loaded reactor core fuels being charged with mixed oxides of plutonium and uranium, and blanket fuels mainly comprising depleted uranium. Further, liquid sodium is used as coolants. As transuranium elements, isotope elements of neptunium, americium and curium contained in wastes taken out from light water reactors or the composition thereof are used. The reactor core comprises a region with a greater mixing ratio and a region with a less mixing ratio of the transuranium elements. The mixing ratio of the transuranium elements is made greater for the fuels in the reactor core region at the boundary with the blanket of great neutron leakage. With such a constitution, since the positive reactivity value at the reactor core central portion is small in the Na void reactivity distribution in the reactor core, the positive reactivity is small upon Na boiling in the reactor core central region upon occurrence of imaginable accident, to attain reactor safety. (I.N.)

14. Farewell to a reactor

International Nuclear Information System (INIS)

Skanborg, P.

1976-01-01

Denmark's second reactor, DR 2, whose first criticality took place the night of 18/19 December 1958 was shut down for the last time on 31 October 1975. It was a light-water moderrated and cooled reactor of swimming-pool type with a thermal power of 5 MW, using 90% enriched uranium. The operation is described. The reactor and auxiliary equipment are now being put 'in store' - all fuel elements sent for reprocessing, the reactor tank and cooling circuits emptied, and a lead shielding placed over the tank opening. The rest of the equipment will remain in place. (B.P.)

International Nuclear Information System (INIS)

Saha, D.; Sinha, R.K.

2005-01-01

For sustainable development of nuclear energy, a number of important issues like safety, waste management, economics etc. are to be addressed. To do this, a number of advanced reactor designs as well as fuel cycle technologies are being pursued worldwide. The advanced reactors being developed in India are the AHWR and the CHTR. Both the reactors use thorium based fuel and have many passive features. This paper describes the Indian advanced reactors and gives a brief account of the international initiatives for the sustainable development of nuclear energy. (author)

16. The research reactors their contribution to the reactors physics

International Nuclear Information System (INIS)

Barral, J.C.; Zaetta, A.; Johner, J.; Mathoniere, G.

2000-01-01

The 19 october 2000, the french society of nuclear energy organized a day on the research reactors. This associated report of the technical session, reactors physics, is presented in two parts. The first part deals with the annual meeting and groups general papers on the pressurized water reactors, the fast neutrons reactors and the fusion reactors industry. The second part presents more technical papers about the research programs, critical models, irradiation reactors (OSIRIS and Jules Horowitz) and computing tools. (A.L.B.)

17. RB Research nuclear reactor RB reactor, Annual report for 2000

International Nuclear Information System (INIS)

Milosevic, M.

2000-12-01

Report on RB reactor operation during 2000 contains 3 parts. Part one contains a brief description of reactor operation and reactor components, relevant dosimetry data and radiation protection issues, personnel and financial data. Part two is devoted to maintenance of the reactor components, namely, fuel, heavy water, reactor vessel, heavy water circulation system, absorption rods and heavy water level-meters, maintenance of electronic, mechanical, electrical and auxiliary equipment. Part three contains data concerned with reactor operation and utilization with a comprehensive list of publications resulting from experiments done at the RB reactor. It contains data about reactor operation during previous 14 years, i.e. from 1986 - 2000

18. FFTF reactor assembly system technology

International Nuclear Information System (INIS)

Mangelsdorf, T.A.

1975-01-01

An overview is presented of the FFTF reactor and plant together with descriptions of core components, core internals, core system, primary and secondary control rod system, reactor instrumentation, reactor vessel and closure head, and supporting test programs

19. Reactor building for a nuclear reactor

International Nuclear Information System (INIS)

Haidlen, F.

1976-01-01

The invention concerns the improvement of the design of a liner, supported by a latticed steel girder structure and destined for guaranteeing a gastight closure for the plant compartments in the reactor building of a pressurized water reactor. It is intended to provide the steel girder structure on their top side with grates, being suited for walking upon, and to hang on their lower side diaphragms in modular construction as a liner. At the edges they may be sealed with bellows in order to avoid thermal stresses. The steel girder structure may at the same time serve as supports for parts of the steam pipe. (RW) [de

20. Revitalization of reactor usage through reactor sharing

International Nuclear Information System (INIS)

Vernetson, W.G.

1986-01-01

The purpose of this work was to renew interest in using the University Florida Training Reactor (UFTR) for educational and training purposes outside the Nuclear Engineering Sciences (NES) and Environmental Engineering Sciences (EES) Departments at the University of Florida and for research by others outside the NES Department. The availability of the UFTR made possible through a US Department of Energy (DOE) Reactor Sharing Grant provided the mechanism to pursue generation of renewed interest at all levels both within the University of Florida and from other educational and corporate institutions

1. Reactor coolant pump for a nuclear reactor

International Nuclear Information System (INIS)

Burkhardt, W.; Richter, G.

1976-01-01

An improvement is proposed concerning the easier disengagement of the coupling at the reactor coolant pump for a nuclear reactor transporting a pressurized coolant. According to the invention the disengaging coupling consists of two parts separated by screws. At least one of the screws contains a propellent charge ananged within a bore and provided with a speed-dependent ignition device in such a way that by separation of the screws at overspeeds the coupling is disengaged. The sub-claims are concerned with the kind of ignition ot the propellent charge. (UWI) [de

2. The fusion reactor

International Nuclear Information System (INIS)

Brennan, M.H.

1974-01-01

Basic principles of the fusion reactor are outlined. Plasma heating and confinement schemes are described. These confinement systems include the linear Z pinch, magnetic mirrors and Tokamaks. A fusion reactor is described and a discussion is given of its environmental impact and its fuel situation. (R.L.)

3. Molten salt reactor concept

International Nuclear Information System (INIS)

Sood, D.D.

1980-01-01

Molten salt reactor is an advanced breeder concept which is suited for the utilization of thorium for nuclear power production. This reactor is based on the use of solutions of uranium or plutonium fluorides in LiF-BeF 2 -ThF 4 as fuel. Unlike the conventional reactors, no external coolant is used in the reactor core and the fuel salt itself is circulated through heat exchangers to transfer the fission produced heat to a secondary salt (NaF-NaBF 4 ) for steam generation. A part of the fuel stream is continuously processed to isolate 233 Pa, so that it can decay to fissile 233 U without getting converted to 234 Pa, and for the removal of neutron absorbing fission products. This on-line processing scheme makes this reactor concept to achieve a breeding ratio of 1.07 which is the highest for any thermal breeder reactor. Experimental studies at the Bhabha Atomic Research Centre, Bombay, have established the use of plutonium as fuel for this reactor. This molten salt reactor concept is described and the work conducted at the Bhabha Atomic Research Centre is summarised. (auth.)

4. The heavy water reactors

International Nuclear Information System (INIS)

Brudermueller, G.

1976-01-01

This is a survey of the development so far of this reactor line which is in operation all over the world in various types (e.g. BHWR, PHWR). MZFR and the CANDU-type reactors are discussed in more detail. (UA) [de

5. BWR type reactor

International Nuclear Information System (INIS)

Watanabe, Shoichi

1983-01-01

Purpose : To flatten the radial power distribution in the reactor core thereby improve the thermal performance of the reactor core by making the moderator-fuel ratio of fuel assemblies different depending on their position in the reactor core. Constitution : The volume of fuels disposed in the peripheral area of the reactor core is decreased by the increase of the volume of moderators in fuel assemblies disposed in the peripheral area of the reactor core to thereby make the moderator-fuel volume greater in the peripheral area than that in the central area. The moderator-fuel ratio adjustment is attained by making the number of water rods greater, decreasing the diameter of fuel pellets or decreasing the number of fuel pins in fuel assemblies disposed at the peripheral area of the reactor core as compared with fuel assemblies disposed at the central area of the reactor core. In this way, the infinite multiplication factors of fuels can be increased to thereby improve the reactor core performance. (Aizawa, K.)

6. Osiris reactor descriptive report

International Nuclear Information System (INIS)

1976-03-01

OSIRIS is a swimming pool reactor of 70 MW thermal power. Its main purpose is the irradiation of reactor materials in high neutron flux. A description is given of the air conditioning, ventilation, and radioactive gas removal system. (R.L.)

7. FBR type reactor core

International Nuclear Information System (INIS)

Tamiya, Tadashi; Kawashima, Katsuyuki; Fujimura, Koji; Murakami, Tomoko.

1995-01-01

Neutron reflectors are disposed at the periphery of a reactor core fuel region and a blanket region, and a neutron shielding region is disposed at the periphery of them. The neutron reflector has a hollow duct structure having a sealed upper portion, a lower portion opened to cooling water, in which a gas and coolants separately sealed in the inside thereof. A driving pressure of a primary recycling pump is lowered upon reduction of coolant flow rate, then the liquid level of coolants in the neutron reflector is lowered due to imbalance between the driving pressure and a gas pressure, so that coolants having an effect as a reflector are eliminated from the outer circumference of the reactor core. Therefore, the amount of neutrons leaking from the reactor core is increased, and negative reactivity is charged to the reactor core. The negative reactivity of the neutron reflector is made greater than a power compensation reactivity. Since this enables reactor scram by using an inherent performance of the reactor core, the reactor core safety of an LMFBR-type reactor can be improved. (I.N.)

8. Mirror hybrid reactor studies

International Nuclear Information System (INIS)

Bender, D.J.

1978-01-01

The hybrid reactor studies are reviewed. The optimization of the point design and work on a reference design are described. The status of the nuclear analysis of fast spectrum blankets, systems studies for fissile fuel producing hybrid reactor, and the mechanical design of the machine are reviewed

9. Reactor Safety Analysis

International Nuclear Information System (INIS)

Arien, B.

2000-01-01

The objective of SCK-CEN's programme on reactor safety is to develop expertise in probabilistic and deterministic reactor safety analysis. The research programme consists of two main activities, in particular the development of software for reliability analysis of large systems and participation in the international PHEBUS-FP programme for severe accidents. Main achievements in 1999 are reported

10. The Integral Fast Reactor

International Nuclear Information System (INIS)

Till, C.E.; Chang, Y.I.; Lineberry, M.J.

1990-01-01

Argonne National Laboratory, since 1984, has been developing the Integral Fast Reactor (IFR). This paper will describe the way in which this new reactor concept came about; the technical, public acceptance, and environmental issues that are addressed by the IFR; the technical progress that has been made; and our expectations for this program in the near term. 5 refs., 3 figs

11. Gas-cooled reactors

International Nuclear Information System (INIS)

Vakilian, M.

1977-05-01

The present study is the second part of a general survey of Gas Cooled Reactors (GCRs). In this part, the course of development, overall performance and present development status of High Temperature Gas Cooled Reactors (HTCRs) and advances of HTGR systems are reviewed. (author)

12. A nuclear power reactor

International Nuclear Information System (INIS)

Borrman, B.E.; Broden, P.; Lundin, N.

1979-12-01

The invention consists of shock absorbing support beams fastened to the underside of the reactor tank lid of a BWR type reactor, whose purpose is to provide support to the steam separator and dryer unit against accelerations due to earthquakes, without causing undue thermal stresses in the unit due to differential expansion. (J.I.W.)

13. International thermal reactor development

International Nuclear Information System (INIS)

Zebroski, E.L.

1977-01-01

The worldwide development of nuclear power plants is reviewed. Charts are presented which show the commitment to light-water reactor capacity construction with breakdown by region and country. Additional charts show the major nuclear research centers which have substantial scope in light water reactor development and extensive international activities

14. Thermal reactor strategy

International Nuclear Information System (INIS)

1981-01-01

This statement sets down briefly the CEGB's views on the requirement for nuclear power and outlines current progress in the implementation of the CEGB's thermal reactor strategy. The programme is traced historically, together with statements of Government policy. The place of Magnox, AGR, SGHWR, PWR and fast breeder reactors is discussed. Advantages and problems associated with the various types are outlined. (U.K.)

15. Supercritical Water Reactors

International Nuclear Information System (INIS)

Bouchter, J.C.; Dufour, P.; Guidez, J.; Latge, C.; Renault, C.; Rimpault, G.

2014-01-01

The supercritical water reactor (SCWR) is one of the 6 concepts selected for the 4. generation of nuclear reactors. SCWR is a new concept, it is an attempt to optimize boiling water reactors by using the main advantages of supercritical water: only liquid phase and a high calorific capacity. The SCWR requires very high temperatures (over 375 C degrees) and very high pressures (over 22.1 MPa) to operate which allows a high conversion yield (44% instead of 33% for a PWR). Low volumes of coolant are necessary which makes the neutron spectrum shift towards higher energies and it is then possible to consider fast reactors operating with supercritical water. The main drawbacks of supercritical water is the necessity to use very high pressures which has important constraints on the reactor design, its physical properties (density, calorific capacity) that vary strongly with temperatures and pressures and its very high corrosiveness. The feasibility of the concept is not yet assured in terms of adequate materials that resist to corrosion, reactor stability, reactor safety, and reactor behaviour in accidental situations. (A.C.)

16. Reactor Materials Research

International Nuclear Information System (INIS)

Van Walle, E.

2001-01-01

The activities of the Reactor Materials Research Department of the Belgian Nuclear Research Centre SCK-CEN in 2000 are summarised. The programmes within the department are focussed on studies concerning (1) fusion, in particular mechanical testing; (2) Irradiation Assisted Stress Corrosion Cracking (IASCC); (3) nuclear fuel; and (4) Reactor Pressure Vessel Steel (RPVS)

17. Fusion reactors - types - problems

International Nuclear Information System (INIS)

Schmitter, K.H.

1979-07-01

A short account is given of the principles of fusion reactions and of the expected advantages of fusion reactors. Descriptions are presented of various Tokamak experimental devices being developed in a number of countries and of some mirror machines. The technical obstacles to be overcome before a fusion reactor could be self-supporting are discussed. (U.K.)

18. Reactor cost driving items

International Nuclear Information System (INIS)

Spears, W.R.

1987-01-01

Assuming that the design solutions presently perceived for NET can be extrapolated for use in a power reactor, and using costing experience with present day fusion experiments and with fission power plants, the major components of the cost of a tokamak fusion power reactor are described. The analysis shows the emphasis worth placing on various areas of plant design to reduce costs

19. Tank type reactor

International Nuclear Information System (INIS)

Otsuka, Fumio.

1989-01-01

The present invention concerns a tank type reactor capable of securing reactor core integrity by preventing incorporation of gases to an intermediate heat exchanger, thgereby improving the reliability. In a conventional tank type reactor, since vortex flows are easily caused near the inlet of an intermediate heat exchanger, there is a fear that cover gases are involved into the coolant main streams to induce fetal accidents. In the present invention, a reactor core is suspended by way of a suspending body to the inside of a reactor vessel and an intermediate heat exchanger and a pump are disposed between the suspending body and the reactor vessel, in which a vortex current preventive plate is attached at the outside near the coolant inlet on the primary circuit of the intermediate heat exchanger. In this way vortex or turbulence near the inlet of the intermediate heata exchanger or near the surface of coolants can be prevented. Accordingly, the cover gases are no more involved, to insure the reactor core integrity and obtain a tank type nuclear reactor of high reliability. (I.S.)

20. Reactor Materials Research

Energy Technology Data Exchange (ETDEWEB)

Van Walle, E

2001-04-01

The activities of the Reactor Materials Research Department of the Belgian Nuclear Research Centre SCK-CEN in 2000 are summarised. The programmes within the department are focussed on studies concerning (1) fusion, in particular mechanical testing; (2) Irradiation Assisted Stress Corrosion Cracking (IASCC); (3) nuclear fuel; and (4) Reactor Pressure Vessel Steel (RPVS)

1. Space Nuclear Reactor Engineering

Energy Technology Data Exchange (ETDEWEB)

Poston, David Irvin [Los Alamos National Lab. (LANL), Los Alamos, NM (United States)

2017-03-06

We needed to find a space reactor concept that could be attractive to NASA for flight and proven with a rapid turnaround, low-cost nuclear test. Heat-pipe-cooled reactors coupled to Stirling engines long identified as the easiest path to near-term, low-cost concept.

2. Reactor dynamics calculations

International Nuclear Information System (INIS)

Devooght, J.; Lefvert, T.; Stankiewiez, J.

1981-01-01

This chapter deals with the work done in reactor dynamics within the Coordinated Research Program on Transport Theory and Advanced Reactor Calculations by three groups in Belgium, Poland, Sweden and Italy. Discretization methods in diffusion theory, collision probability methods in time-dependent neutron transport and singular perturbation method are represented in this paper

3. Status of French reactors

Energy Technology Data Exchange (ETDEWEB)

Ballagny, A. [Commissariat a l`Energie Atomique, Saclay (France)

1997-08-01

The status of French reactors is reviewed. The ORPHEE and RHF reactors can not be operated with a LEU fuel which would be limited to 4.8 g U/cm{sup 3}. The OSIRIS reactor has already been converted to LEU. It will use U{sub 3}Si{sub 2} as soon as its present stock of UO{sub 2} fuel is used up, at the end of 1994. The decision to close down the SILOE reactor in the near future is not propitious for the start of a conversion process. The REX 2000 reactor, which is expected to be commissioned in 2005, will use LEU (except if the fast neutrons core option is selected). Concerning the end of the HEU fuel cycle, the best option is reprocessing followed by conversion of the reprocessed uranium to LEU.

4. Compact torsatron reactors

International Nuclear Information System (INIS)

Lyon, J.F.; Carreras, B.A.; Lynch, V.E.; Tolliver, J.S.; Sviatoslavsky, I.N.

1988-05-01

Low-aspect-ratio torsatron configurations could lead to compact stellarator reactors with R 0 = 8--11m, roughly one-half to one-third the size of more conventional stellarator reactor designs. Minimum-size torsatron reactors are found using various assumptions. Their size is relatively insensitive to the choice of the conductor parameters and depends mostly on geometrical constraints. The smallest size is obtained by eliminating the tritium breeding blanket under the helical winding on the inboard side and by reducing the radial depth of the superconducting coil. Engineering design issues and reactor performance are examined for three examples to illustrate the feasibility of this approach for compact reactors and for a medium-size (R 0 ≅ 4 m,/bar a/ /approx lt/ 1 m) copper-coil ignition experiment. 26 refs., 11 figs., 7 tabs

5. Iris reactor conceptual design

International Nuclear Information System (INIS)

Carelli, M.D.; Conway, L.E.; Petrovic, B.; Paramonov, D.V.; Galvin, M.; Todreas, N.E.; Lombardi, C.V.; Maldari, F.; Ricotti, M.E.; Cinotti, L.

2001-01-01

IRIS (International Reactor Innovative and Secure) is a modular, integral, light water cooled, low-to-medium power (100-350 MWe) reactor which addresses the requirements defined by the US DOE for Generation IV reactors, i.e., proliferation resistance, enhanced safety, improved economics and fuel cycle sustainability. It relies on the proven technology of light water reactors and features innovative engineering, but it does not require new technology development. This paper discusses the current reference IRIS design, which features a 1000 MWt thermal core with proven 5%-enriched uranium oxide fuel and five-year long straight burn fuel cycle, integral reactor vessel housing helical tube steam generators and immersed spool pumps. Other major contributors to the high level of safety and economic attractiveness are the safety by design and optimized maintenance approaches, which allow elimination of some classes of accidents, lower capital cost, long operating cycle, and high capacity factors. (author)

6. The secure heating reactor

International Nuclear Information System (INIS)

Pind, C.

1987-01-01

The SECURE heating reactor was designed by ASEA-ATOM as a realistic alternative for district heating in urban areas and for supplying heat to process industries. SECURE has unique safety characteristics, that are based on fundamental laws of physics. The safety does not depend on active components or operator intervention for shutdown and cooling of the reactor. The inherent safety characteristics of the plant cannot be affected by operator errors. Due to its very low environment impact, it can be sited close to heat consumers. The SECURE heating reactor has been shown to be competitive in comparison with other alternatives for heating Helsinki and Seoul. The SECURE heating reactor forms a basis for the power-producing SECURE-P reactor known as PIUS (Process Inherent Ultimate Safety), which is based on the same inherent safety principles. The thermohydraulic function and transient response have been demonstrated in a large electrically heated loop at the ASEA-ATOM laboratories

7. Nuclear reactor design

CERN Document Server

2014-01-01

This book focuses on core design and methods for design and analysis. It is based on advances made in nuclear power utilization and computational methods over the past 40 years, covering core design of boiling water reactors and pressurized water reactors, as well as fast reactors and high-temperature gas-cooled reactors. The objectives of this book are to help graduate and advanced undergraduate students to understand core design and analysis, and to serve as a background reference for engineers actively working in light water reactors. Methodologies for core design and analysis, together with physical descriptions, are emphasized. The book also covers coupled thermal hydraulic core calculations, plant dynamics, and safety analysis, allowing readers to understand core design in relation to plant control and safety.

8. Mirror reactor surface study

Energy Technology Data Exchange (ETDEWEB)

Hunt, A. L.; Damm, C. C.; Futch, A. H.; Hiskes, J. R.; Meisenheimer, R. G.; Moir, R. W.; Simonen, T. C.; Stallard, B. W.; Taylor, C. E.

1976-09-01

A general survey is presented of surface-related phenomena associated with the following mirror reactor elements: plasma first wall, ion sources, neutral beams, director converters, vacuum systems, and plasma diagnostics. A discussion of surface phenomena in possible abnormal reactor operation is included. Several studies which appear to merit immediate attention and which are essential to the development of mirror reactors are abstracted from the list of recommended areas for surface work. The appendix contains a discussion of the fundamentals of particle/surface interactions. The interactions surveyed are backscattering, thermal desorption, sputtering, diffusion, particle ranges in solids, and surface spectroscopic methods. A bibliography lists references in a number of categories pertinent to mirror reactors. Several complete published and unpublished reports on surface aspects of current mirror plasma experiments and reactor developments are also included.

9. Reactor control device

International Nuclear Information System (INIS)

Fukami, Haruo; Morimoto, Yoshinori.

1981-01-01

Purpose: To operate a reactor always with safety operation while eliminating the danger of tripping. Constitution: In a reactor control device adapted to detect the process variants of a reactor, control a control rod drive controlling system based on the detected signal to thereby control the driving the control rods, control the reactor power and control the electric power generated from an electric generator by the output from the reactor, detection means is provided for the detection of the electric power from said electric generator, and a compensation device is provided for outputting control rod driving compensation signals to the control rod driving controlling system in accordance with the amount of variation in the detected value. (Seki, T.)

10. Reactor feedwater device

International Nuclear Information System (INIS)

Igarashi, Noboru.

1986-01-01

Purpose: To suppress soluble radioactive corrosion products in a feedwater device. Method: In a light water cooled nuclear reactor, an iron injection system is connected to feedwater pipeways and the iron concentration in the feedwater or reactor coolant is adjusted between twice and ten times of the nickel concentration. When the nickel/iron ratio in the reactor coolant or feedwater goes nearer to 1/2, iron ions are injected together with iron particles to the reactor coolant to suppress the leaching of stainless steels, decrease the nickel in water and increase the iron concentration. As a result, it is possible to suppress the intrusion of nickel as one of parent nuclide of radioactive nuclides. Further, since the iron particles intruded into the reactor constitute nuclei for capturing the radioactive nuclides to reduce the soluble radioactive corrosion products, the radioactive nuclides deposited uniformly to the inside of the pipeways in each of the coolant circuits can be reduced. (Kawakami, Y.)

11. Research reactor DHRUVA

International Nuclear Information System (INIS)

Veeraraghaven, N.

1990-01-01

DHRUVA, a 100 MWt research reactor located at the Bhabha Atomic Research Centre, Bombay, attained first criticality during August, 1985. The reactor is fuelled with natural uranium and is cooled, moderated and reflected by heavy water. Maximum thermal neutron flux obtained in the reactor is 1.8 X 10 14 n/cm 2 /sec. Some of the salient design features of the reactor are discussed in this paper. Some important features of the reactor coolant system, regulation and protection systems and experimental facilities are presented. A short account of the engineered safety features is provided. Some of the problems that were faced during commissioning and the initial phase of power operation are also dealt upon

12. Reactor power control device

International Nuclear Information System (INIS)

Kobayashi, Akira.

1980-01-01

Purpose: To prevent misoperation in a control system for the adjustment of core coolant flow rate, and the increase in the neutron flux density caused from the misoperation in BWR type reactors. Constitution: In a reactor power control system adapted to control the reactor power by the adjustment of core flow rate, average neutron flux signals of a reactor core, entire core flow rate signals and operation state signals for coolant recycling system are inputted to a microcomputer. The outputs from the computer are sent to a recycling MG set speed controller to control the reactor core flow rate. The computer calculates the change ratio with time in the average neutron flux signals, correlation between the average neutron flux signals and the entire core flow rate signals, change ratio with time in the operation state signals for the coolant recycling system and the like and judges the abnormality in the coolant recycling system based on the calculated results. (Ikeda, J.)

13. Fusion reactor pumped laser

International Nuclear Information System (INIS)

Jassby, D.L.

1988-01-01

A nuclear pumped laser is described comprising: a toroidal fusion reactor, the reactor generating energetic neutrons; an annular gas cell disposed around the outer periphery of the reactor, the cell including an annular reflecting mirror disposed at the bottom of the cell and an annular output window disposed at the top of the cell; a gas lasing medium disposed within the annular cell for generating output laser radiation; neutron reflector material means disposed around the annular cell for reflecting neutrons incident thereon back into the gas cell; neutron moderator material means disposed between the reactor and the gas cell and between the gas cell and the neutron reflector material for moderating the energy of energetic neutrons from the reactor; converting means for converting energy from the moderated neutrons to energy pumping means for pumping the gas lasing medium; and beam compactor means for receiving output laser radiation from the annular output window and generating a single output laser beam therefrom

14. Reactor core cooling device

International Nuclear Information System (INIS)

Kobayashi, Masahiro.

1986-01-01

Purpose: To safely and effectively cool down the reactor core after it has been shut down but is still hot due to after-heat. Constitution: Since the coolant extraction nozzle is situated at a location higher than the coolant injection nozzle, the coolant sprayed from the nozzle, is free from sucking immediately from the extraction nozzle and is therefore used effectively to cool the reactor core. As all the portions from the top to the bottom of the reactor are cooled simultaneously, the efficiency of the reactor cooling process is increased. Since the coolant extraction nozzle can be installed at a point considerably higher than the coolant injection nozzle, the distance from the coolant surface to the point of the coolant extraction nozzle can be made large, preventing cavitation near the coolant extraction nozzle. Therefore, without increasing the capacity of the heat exchanger, the reactor can be cooled down after a shutdown safely and efficiently. (Kawakami, Y.)

15. Mirror reactor surface study

International Nuclear Information System (INIS)

Hunt, A.L.; Damm, C.C.; Futch, A.H.; Hiskes, J.R.; Meisenheimer, R.G.; Moir, R.W.; Simonen, T.C.; Stallard, B.W.; Taylor, C.E.

1976-01-01

A general survey is presented of surface-related phenomena associated with the following mirror reactor elements: plasma first wall, ion sources, neutral beams, director converters, vacuum systems, and plasma diagnostics. A discussion of surface phenomena in possible abnormal reactor operation is included. Several studies which appear to merit immediate attention and which are essential to the development of mirror reactors are abstracted from the list of recommended areas for surface work. The appendix contains a discussion of the fundamentals of particle/surface interactions. The interactions surveyed are backscattering, thermal desorption, sputtering, diffusion, particle ranges in solids, and surface spectroscopic methods. A bibliography lists references in a number of categories pertinent to mirror reactors. Several complete published and unpublished reports on surface aspects of current mirror plasma experiments and reactor developments are also included

16. Status of French reactors

International Nuclear Information System (INIS)

Ballagny, A.

1997-01-01

The status of French reactors is reviewed. The ORPHEE and RHF reactors can not be operated with a LEU fuel which would be limited to 4.8 g U/cm 3 . The OSIRIS reactor has already been converted to LEU. It will use U 3 Si 2 as soon as its present stock of UO 2 fuel is used up, at the end of 1994. The decision to close down the SILOE reactor in the near future is not propitious for the start of a conversion process. The REX 2000 reactor, which is expected to be commissioned in 2005, will use LEU (except if the fast neutrons core option is selected). Concerning the end of the HEU fuel cycle, the best option is reprocessing followed by conversion of the reprocessed uranium to LEU

17. The CAREM reactor and present currents in reactor design

International Nuclear Information System (INIS)

Ordonez, J.P.

1990-01-01

INVAP has been working on the CAREM project since 1983. It concerns a very low power reactor for electrical energy generation. The design of the reactor and the basic criteria used were described in 1984. Since then, a series of designs have been presented for reactors which are similar to CAREM regarding the solutions presented to reduce the chance of major nuclear accidents. These designs have been grouped under different names: Advanced Reactors, Second Generation Reactors, Inherently Safe Reactors, or even, Revolutionary Reactors. Every reactor fabrication firm has, at least, one project which can be placed in this category. Presently, there are two main currents of Reactor Design; Evolutionary and Revolutionary. The present work discusses characteristics of these two types of reactors, some revolutionary designs and common criteria to both types. After, these criteria are compared with CAREM reactor design. (Author) [es

18. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

Hirota, Jitsuya; Asaoka, Takumi; Suzuki, Tomoo; Mitani, Hiroshi; Akino, Fujiyoshi

1977-09-01

Research activities in the Division of Reactor Engineering in fiscal 1976 are described. Works of the division concern mainly the development of multi-purpose Very High Temperature Gas Cooled Reactor, fusion reactor engineering, and the development of Liquid Metal Fast Breeder Reactor in Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, heat transfer and fluid dynamics, reactor and nuclear instrumentation, dynamics analysis and control method development, fusion reactor technology, and activities of the Committee on Reactor Physics. (auth.)

19. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

1978-10-01

Research activities in the Division of Reactor Engineering in fiscal 1977 are described. Works of the Division are development of multi-purpose Very High Temperature Gas Cooled Reactor, fusion reactor engineering, and development of Liquid Metal Fast Breeder Reactor for Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, heat transfer and fluid dynamics, reactor and nuclear instrumentation, dynamics analysis and control method development, fusion reactor technology, and Committee on Reactor Physics. (Author)

20. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

1976-09-01

Research activities conducted in Reactor Engineering Division in fiscal 1975 are summarized in this report. Works in the division are closely related to the development of multi-purpose High-temperature Gas Cooled Reactor, the development of Liquid Metal Fast Breeder Reactor by Power Reactor and Nuclear Fuel Development Corporation, and engineering research of thermonuclear fusion reactor. Many achievements are described concerning nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, heat transfer and fluid dynamics, reactor and nuclear instrumentation, dynamics analysis and control method development, fusion reactor technology and activities of the Committee on Reactor Physics. (auth.)

1. Reactor Engineering Department annual report

International Nuclear Information System (INIS)

1984-08-01

Research and development activities in the Department of Reactor Engineering in fiscal 1983 are described. The work of the Department is closely related to development of multipurpose Very High Temperature Gas Cooled Reactor and Fusion Reactor, and development of Liquid Metal Fast Breeder Reactor carried out by Power Reactor and Nuclear Fuel Development Corporation. Contents of the report are achievements in fields such as nuclear data and group constants, theoretical method and code development, integral experiment and analysis, fusion neutronics, shielding, reactor and nuclear instrumentation, reactor control and diagnosis, and safeguards technology, and activities of the Committee on Reactor Physics. (author)

2. Multi-purpose reactor

International Nuclear Information System (INIS)

1991-05-01

The Multi-Purpose-Reactor (MPR), is a pool-type reactor with an open water surface and variable core arrangement. Its main feature is plant safety and reliability. Its power is 22MW t h, cooled by light water and moderated by beryllium. It has platetype fuel elements (MTR type, approx. 20%. enriched uranium) clad in aluminium. Its cobalt (Co 60 ) production capacity is 50000 Ci/yr, 200 Ci/gr. The distribution of the reactor core and associated control and safety systems is essentially based on the following design criteria: - upwards cooling flow, to waive the need for cooling flow inversion in case the reactor is cooled by natural convection if confronted with a loss of pumping power, and in order to establish a superior heat transfer potential (a higher coolant saturation temperature); - easy access to the reactor core from top of pool level with the reactor operating at full power, in order to facilitate actual implementation of experiments. Consequently, mechanisms associated to control and safety rods s,re located underneath the reactor tank; - free access of reactor personnel to top of pool level with the reactor operating at full power. This aids in the training of personnel and the actual carrying out of experiments, hence: - a vast water column was placed over the core to act as radiation shielding; - the core's external area is cooled by a downwards flow which leads to a decay tank beyond the pool (for N 16 to decay); - a small downwards flow was directed to stream downwards from above the reactor core in order to drag along any possibly active element; and - a stagnant hot layer system was placed at top of pool level so as to minimize the upwards coolant flow rising towards pool level

3. Mirror reactor studies

International Nuclear Information System (INIS)

Moir, R.W.; Barr, W.L.; Bender, D.J.

1977-01-01

Design studies of a fusion mirror reactor, a fusion-fission mirror reactor, and two small mirror reactors are summarized. The fusion reactor uses 150-keV neutral-beam injectors based on the acceleration of negative ions. The injectors provide over 1 GW of continuous power at an efficiency greater than 80%. The fusion reactor has three-stage, modularized, Venetian blind, plasma direct converter with a predicted efficiency of 59% and a new concept for removal of the lune-shaped blanket: a crane is brought between the two halves of the Yin-Yang magnet, which are separated by a float. The design has desirable features such as steady-state operation, minimal impurity problems, and low first-wall thermal stress. The major disadvantage is low Q resulting in high re-circulating power and hence high cost of electrical power. However, the direct capital cost per unit of gross electrical power is reasonable [\$1000/kW(e)]. By contrast, the fusion-fission reactor design is not penalized by re-circulating power and uses relatively near-term fusion technology being developed for the fusion power program. New results are presented on the Th- 233 U and the U- 239 Pu fuel cycles. The purpose of this hybrid is fuel production, with projected costs at \$55/g of Pu or \$127/g of 233 U. Blanket and cooling system designs, including an emergency cooling system, by General Atomic Company, lead us to the opinion that the reactor can meet expected safety standards for licensing. The smallest mirror reactor having only a shield between the plasma and the coil is the 4.2-m long fusion engineering research facility (FERF) designed for material irradiation. The smallest mirror reactor having both a blanket and shield is the 7.5-m long experimental power reactor (EPR), which has both a fusion and a fusion-fission version. (author)

4. Reactor performance calculations for water reactors

International Nuclear Information System (INIS)

Hicks, D.

1970-04-01

The principles of nuclear, thermal and hydraulic performance calculations for water cooled reactors are discussed. The principles are illustrated by describing their implementation in the UKAEA PATRIARCH scheme of computer codes. This material was originally delivered as a course of lectures at the Technical University of Helsinki in Summer of 1969.

5. Reactor scram device for FBR type reactor

International Nuclear Information System (INIS)

Kumasaka, Katsuyuki; Arashida, Genji; Itooka, Satoshi.

1991-01-01

In a control rod attaching structure in a reactor scram device of an FBR type reactor, an anti-rising mechanism proposed so far against external upward force upon occurrence of earthquakes relies on the engagement of a mechanical structure but temperature condition is not taken into consideration. Then, in the present invention, a material having curie temperature characteristics and which exhibits ferromagnetism only under low temperature condition and a magnet device are disposed to one of a movable control rod and a portion secured to the reactor. Alternatively, a bimetal member or a shape memory alloy which actuates to fix to the mating member only under low temperature condition is secured. The fixing device is adapted to operate so as to secure the control rods when the low temperature state is caused depending on the temperature condition. With such a constitution, when the control rods are separated from a driving device, they are prevented from rising even if they undergo external upward force due to earthquakes and so on, which can improve the reactor safety. (N.H.)

6. Fourth Generation Reactor Concepts

International Nuclear Information System (INIS)

Furtek, A.

2008-01-01

Concerns over energy resources availability, climate changes and energy supply security suggest an important role for nuclear energy in future energy supplies. So far nuclear energy evolved through three generations and is still evolving into new generation that is now being extensively studied. Nuclear Power Plants are producing 16% of the world's electricity. Today the world is moving towards hydrogen economy. Nuclear technologies can provide energy to dissociate water into oxygen and hydrogen and to production of synthetic fuel from coal gasification. The introduction of breeder reactors would turn nuclear energy from depletable energy supply into an unlimited supply. From the early beginnings of nuclear energy in the 1940s to the present, three generations of nuclear power reactors have been developed: First generation reactors: introduced during the period 1950-1970. Second generation: includes commercial power reactors built during 1970-1990 (PWR, BWR, Candu, Russian RBMK and VVER). Third generation: started being deployed in the 1990s and is composed of Advanced LWR (ALWR), Advanced BWR (ABWR) and Passive AP600 to be deployed in 2010-2030. Future advances of the nuclear technology designs can broaden opportunities for use of nuclear energy. The fourth generation reactors are expected to be deployed by 2030 in time to replace ageing reactors built in the 1970s and 1980s. The new reactors are to be designed with a view of the following objectives: economic competitiveness, enhanced safety, minimal radioactive waste production, proliferation resistance. The Generation IV International Forum (GIF) was established in January 2000 to investigate innovative nuclear energy system concepts. GIF members include Argentina, Brazil, Canada, Euratom, France Japan, South Africa, South Korea, Switzerland, United Kingdom and United States with the IAEA and OECD's NEA as permanent observers. China and Russia are expected to join the GIF initiative. The following six systems

7. Reactor Engineering Department annual report

International Nuclear Information System (INIS)

1993-09-01

This report summarizes the research and development activities in the Department of Reactor Engineering during the fiscal year of 1992 (April 1, 1992-March 31, 1993). The major Department's programs promoted in the year are the assessment of the high conversion light water reactor, the design activities of advanced reactor system and development of a high energy proton linear accelerator for the engineering applications including TRU incineration. Other major tasks of the Department are various basic researches on the nuclear data and group constants, the developments of theoretical methods and codes, the reactor physics experiments and their analyses, fusion neutronics, radiation shielding, reactor instrumentation, reactor control/diagnosis, thermohydraulics and technology developments related to the reactor physics facilities. The cooperative works to JAERI's major projects such as the high temperature gas cooled reactor or the fusion reactor and to PNC's fast reactor project were also progressed. The activities of the Research Committee on Reactor Physics are also summarized. (author)

8. Reactor engineering department annual report

International Nuclear Information System (INIS)

1990-09-01

This report summarizes the research and development activities in the Department of Reactor Engineering during the fiscal year of 1989 (April 1, 1989 - March 31, 1990). One of major Department's programs is the assessment of the high conversion light water reactor and the design activities of advanced reactor system. Development of a high energy proton linear accelerator for the nuclear engineering including is also TRU incineration promoted. Other major tasks of the Department are various basic researches on nuclear data and group constants, theoretical methods and code development, on reactor physics experiments and analyses, fusion neutronics, radiation shielding, reactor instrumentation, reactor control/diagnosis, thermohydraulics, technology assessment of nuclear energy and technology developments related to the reactor physics facilities. The cooperative works to JAERI's major projects such as the high temperature gas cooled reactor or the fusion reactor and to PNC's fast reactor project also progressed. The activities of the Research Committee on Reactor Physics are also summarized. (author)

9. Reactor safety protection system

International Nuclear Information System (INIS)

Nishi, Hiroshi; Yokoyama, Tsuguo.

1989-01-01

A plurality of neutron detectors are disposed around a reactor core and detection signals from optional two neutron detectors are inputted into a ratio calculation device. If the ratio between both of the neutron flux level signals exceeds a predetermined value, a reactor trip signal is generated from an alarm setting device. Further, detection signals from all of the neutron detection devices are inputted into an average calculation device and the reactor trip signal is generated also in a case where the average value exceeds a predetermined set value. That is, when the reactor core power is increased locally, the detection signal from the neutron detector nearer to the point of power increase is greater than the increase rate for the entire reactor core power, while the detection signal from the neutron detector remote from the point of power increase is smaller. Thus, the local power increase ratio in the FBR reactor core can be detected efficiently by calculating the ratio for the neutron flux level signals from two neutron detectors, thereby enabling to exactly recognize the local power increase rate in the reactor core. (N.H.)

10. Nuclear reactor containing facility

International Nuclear Information System (INIS)

Hidaka, Masataka; Murase, Michio.

1994-01-01

In a reactor containing facility, a condensation means is disposed above the water level of a cooling water pool to condensate steams of the cooling water pool, and return the condensated water to the cooling water pool. Upon occurrence of a pipeline rupture accident, steams generated by after-heat of a reactor core are caused to flow into a bent tube, blown from the exit of the bent tube into a suppression pool and condensated in a suppression pool water, thereby suppressing the pressure in the reactor container. Cooling water in the cooling water pool is boiled by heat conduction due to the condensation of steams, then the steams are exhausted to the outside of the reactor container to remove the heat of the reactor container to the outside of the reactor. In addition, since cooling water is supplied to the cooling water pool quasi-permanently by gravity as a natural force, the reactor container can be cooled by the cooling water pool for a long period of time. Since the condensation means is constituted with a closed loop and interrupted from the outside, radioactive materials are never released to the outside. (N.H.)

11. Method of reactor operation

International Nuclear Information System (INIS)

Maeda, Katsuji.

1982-01-01

Purpose: To prevent stress corrosion cracks in stainless steels caused from hydrogen peroxide in reactor operation in which the density of hydrogen peroxide in the reactor water is controlled upon reactor start-up. Method: A heat exchanger equipped with a heat source for applying external heat is disposed into the recycling system for reactor coolants. Upon reactor start-up, the coolants are heated by the heat exchanger till arriving at a temperature at which the dissolving rate is faster than the forming rate of hydrogen peroxide in the coolants, and nuclear heating is started after reaching the above temperature. The temperature of the reactor water is increased in such a manner and, when it arrives at 140 0 C, extraction of control elements is started and the heat source for the heat exchanger is interrupted simultaneously. In this way spikes in the density of hydrogen peroxide are suppressed upon reactor start-up to thereby decrease the stress corrosion cracks in stainless steels. (Horiuchi, T.)

12. Nuclear reactor control column

International Nuclear Information System (INIS)

Bachovchin, D.M.

1982-01-01

The nuclear reactor control column comprises a column disposed within the nuclear reactor core having a variable cross-section hollow channel and containing balls whose vertical location is determined by the flow of the reactor coolant through the column. The control column is divided into three basic sections wherein each of the sections has a different cross-sectional area. The uppermost section of the control column has the greatest crosssectional area, the intermediate section of the control column has the smallest cross-sectional area, and the lowermost section of the control column has the intermediate cross-sectional area. In this manner, the area of the uppermost section can be established such that when the reactor coolant is flowing under normal conditions therethrough, the absorber balls will be lifted and suspended in a fluidized bed manner in the upper section. However, when the reactor coolant flow falls below a predetermined value, the absorber balls will fall through the intermediate section and into the lowermost section, thereby reducing the reactivity of the reactor core and shutting down the reactor

13. The integral fast reactor

International Nuclear Information System (INIS)

Till, C.E.

1987-01-01

On April 3rd, 1986, two dramatic demonstrations of the inherent capability of sodium-cooled fast reactors to survive unprotected loss of cooling accidents were carried out on the experimental sodium-cooled power reactor, EBR-II, on the Idaho site of Argonne National Laboratory. Transients potentially of the most serious kind, one an unprotected loss of flow, the other an unprotected loss of heat sink, both initiated from full power. In both cases the reactor quietly shut itself down, without damage of any kind. These tests were a part of the on-going development program at Argonne to develop an advanced reactor with significant new inherent safety characteristics. Called the Integral Fast Reactor, or IFR, the basic thrust is to develop everything that is needed for a complete nuclear power system - reactor, closed fuel cycle, and waste processing - as a single optimized entity, and, for simplicity in concept, as an integral part of a single plant. The particular selection of reactor materials emphasizes inherent safety characteristics and also makes possible a simplified closed fuel cycle and waste process improvements

14. The integral fast reactor

International Nuclear Information System (INIS)

Till, C.E.

1987-01-01

On April 3rd, 1986, two demonstrations of the inherent capability of sodium-cooled fast reactors to survive unprotected loss of cooling accidents were carried out on the experimental sodium-cooled power reactor, EBR-II, on the Idaho site of Argonne National Laboratory. Transients potentially of the most serious kind, one an unprotected loss of flow, the other an unprotected loss of heat sink, both initiated from full power. In both cases the reactor quietly shut itself down, without damage of any kind. These tests were a part of the on-going development program at Argonne to develop an advanced reactor with significant new inherent safety characteristics. Called the integral fast reactor, or IFR, the basic thrust is to develop everything that is needed for a complete nuclear power system - reactor, closed fuel cycle, and waste processing - as a single optimized entity, and, for simplicity in concept, as an integral part of a single plant. The particular selection of reactor materials emphasizes inherent safety characteristics also makes possible a simplified close fuel cycle and waste process improvements. The paper describes the IFR concept, the inherent safety, tests, and status of IFR development today

15. Reactor power control device

International Nuclear Information System (INIS)

Imaruoka, Hiromitsu.

1994-01-01

A high pressure water injection recycling system comprising injection pipelines of a high pressure water injection system and a flow rate control means in communication with a pool of a pressure control chamber is disposed to a feedwater system of a BWR type reactor. In addition, the flow rate control means is controlled by a power control device comprising a scram impossible transient event judging section, a required injection flow rate calculation section for high pressure water injection system and a control signal calculation section. Feed water flow rate to be supplied to the reactor is controlled upon occurrence of a scram impossible transient event of the reactor. The scram impossible transient event is judged based on reactor output signals and scram operation demand signals and injection flow rate is calculated based on a predetermined reactor water level, and condensate storage tank water or pressure control chamber pool water is injected to the reactor. With such procedures, water level can be ensured and power can be suppressed. Further, condensate storage tank water of low enthalpy is introduced to the pressure suppression chamber pool to directly control elevation of water temperature and ensure integrity of the pressure vessel and the reactor container. (N.H.)

16. Reactor water sampling device

International Nuclear Information System (INIS)

Sakamaki, Kazuo.

1992-01-01

The present invention concerns a reactor water sampling device for sampling reactor water in an in-core monitor (neutron measuring tube) housing in a BWR type reactor. The upper end portion of a drain pipe of the reactor water sampling device is attached detachably to an in-core monitor flange. A push-up rod is inserted in the drain pipe vertically movably. A sampling vessel and a vacuum pump are connected to the lower end of the drain pipe. A vacuum pump is operated to depressurize the inside of the device and move the push-up rod upwardly. Reactor water in the in-core monitor housing flows between the drain pipe and the push-up rod and flows into the sampling vessel. With such a constitution, reactor water in the in-core monitor housing can be sampled rapidly with neither opening the lid of the reactor pressure vessel nor being in contact with air. Accordingly, operator's exposure dose can be reduced. (I.N.)

17. Reactor container cooling device

Energy Technology Data Exchange (ETDEWEB)

Ando, Koji; Kinoshita, Shoichiro

1995-11-10

The device of the present invention efficiently lowers pressure and temperature in a reactor container upon occurrence of a severe accident in a BWR-type reactor and can cool the inside of the container for a long period of time. That is, (1) pipelines on the side of an exhaustion tower of a filter portion in a filter bent device of the reactor container are in communication with pipelines on the side of a steam inlet of a static container cooling device by way of horizontal pipelines, (2) a back flow check valve is disposed to horizontal pipelines, (3) a steam discharge valve for a pressure vessel is disposed closer to the reactor container than the joint portion between the pipelines on the side of the steam inlet and the horizontal pipelines. Upon occurrence of a severe accident, when the pressure vessel should be ruptured and steams containing aerosol in the reactor core should be filled in the reactor container, the inlet valve of the static container cooling device is closed. Steams are flown into the filter bent device of the reactor container, where the aerosols can be removed. (I.S.).

18. Reactor feedwater system

International Nuclear Information System (INIS)

Kagaya, Hiroyuki; Tominaga, Kenji.

1993-01-01

In a simplified water type reactor using a gravitationally dropping emergency core cooling system (ECCS), the present invention effectively prevents remaining high temperature water in feedwater pipelines from flowing into the reactor upon occurrence of abnormal events. That is, (1) upon LOCA, if a feedwater pipeline injection valve is closed, boiling under reduced pressure of the remaining high temperature water occurs in the feedwater pipelines, generated steams prevent the remaining high temperature water from flowing into the reactor. Accordingly, the reactor is depressurized rapidly. (2) The feedwater pipeline injection valve is closed and a bypassing valve is opened. Steams generated by boiling under reduced pressure of the remaining high temperature water in the feedwater pipelines are released to a condensator or a suppression pool passing through bypass pipelines. As a result, the remaining high temperature water is prevented from flowing into the reactor. Accordingly, the reactor is rapidly depressurized and cooled. It is possible to accelerate the depressurization of the reactor by the method described above. Further, load on the depressurization valve disposed to a main steam pipe can be reduced. (I.S.)

19. Reactor feedwater control device

International Nuclear Information System (INIS)

Koshi, Yuji.

1993-01-01

In the device of the present invention, an excess response is not caused in a reactor feed water system even when voids are fluctuated by using an actual water level signal as a reactor water level signal. That is, a standard water level signal and a reactor water level signal are inputted to a comparator. An adder adds water level difference signal outputted from the comparator and mismatch flow rate signal prepared by multiplying the difference between a main steam flow rate signal and a feed water flow rate signal by a mismatch gain. A feed water controller integrates the added signal and outputs flow rate demand signal. A feed water system receives the flow rate demand signal as input. A water level calculation means is disposed to such a device for calculating an actual water level based on the change of coolant possessing amount of the reactor, and the output thereof is defined as a reactor water level signal. With such procedures, excessive elevation of water level of the reactor can be prevented even upon occurrence of void fluctuation phenomenon or the like in the reactor such as upon sole scram operation. Accordingly, plant shut down caused thereby can be avoided safely. (I.S.)

20. Reactor safety device

International Nuclear Information System (INIS)

1987-01-01

Purpose: To scram control rods by processing signals from a plurality of temperature detectors and generating abnormal temperature warning upon occurrence of abnormal temperature in a nuclear reactor. Constitution: A temperature sensor comprising a plurality of reactors each having a magnetic body as the magnetic core having a curie point different from each other and corresponding to the abnormal temperature against which reactor core fuels have to be protected is disposed in an identical instrumentation well near the reactor core fuel outlet/inlet of a reactor. A temperature detection device actuated upon detection of an abnormal temperature by the abrupt reduction of the reactance of each of the reactors is disposed. An OR circuit and an AND circuit for conducting OR and AND operations for each of the abnormal temperature detection signals from the temperature detection device are disposed. The output from the OR circuit is used as the abnormal temperature warning signal, while the output from the AND circuit is utilized as a signal for actuating the scram operation of control rod drive mechanisms. Accordingly, it is possible to improve the reliability of the reactor scram system, particularly, improve the reliability under a high temperature atmosphere. (Kamimura, M.)

1. Heterogeneous gas core reactor

International Nuclear Information System (INIS)

Han, K.I.

1977-01-01

Preliminary investigations of a heterogeneous gas core reactor (HGCR) concept suggest that this potential power reactor offers distinct advantages over other existing or conceptual reactor power plants. One of the most favorable features of the HGCR is the flexibility of the power producing system which allows it to be efficiently designed to conform to a desired optimum condition without major conceptual changes. The arrangement of bundles of moderator/coolant channels in a fissionable gas or mixture of gases makes a truly heterogeneous nuclear reactor core. It is this full heterogeneity for a gas-fueled reactor core which accounts for the novelty of the heterogeneous gas core reactor concept and leads to noted significant advantages over previous gas core systems with respect to neutron and fuel economy, power density, and heat transfer characteristics. The purpose of this work is to provide an insight into the design, operating characteristics, and safety of a heterogeneous gas core reactor system. The studies consist mainly of neutronic, energetic and kinetic analyses of the power producing and conversion systems as a preliminary assessment of the heterogeneous gas core reactor concept and basic design. The results of the conducted research indicate a high potential for the heterogeneous gas core reactor system as an electrical power generating unit (either large or small), with an overall efficiency as high as 40 to 45%. The HGCR system is found to be stable and safe, under the conditions imposed upon the analyses conducted in this work, due to the inherent safety of ann expanding gaseous fuel and the intrinsic feedback effects of the gas and water coolant

2. Reactor Sharing Program

International Nuclear Information System (INIS)

Tehan, Terry

2002-01-01

Support utilization of the RINSC reactor for student and faculty instructions and research. The Department of Energy award has provided financial assistance during the period 9/29/1995 to 5/31/2001 to support the utilization of the Rhode Island Nuclear Science Center (RINSC) reactor for student and faculty instruction and research by non-reactor owning educational institutions within approximately 300 miles of Narragansett, Rhode Island. Through the reactor sharing program, the RINSC (including the reactor and analytical laboratories) provided reactor services and laboratory space that were not available to the other universities and colleges in the region. As an example of services provided to the users: Counting equipment, laboratory space, pneumatic and in-pool irradiations, demonstrations of sample counting and analysis, reactor tours and lectures. Funding from the Reactor Sharing Program has provided the RINSC to expand student tours and demonstration programs that emphasized our long history of providing these types of services to the universities and colleges in the area. The funding have also helped defray the cost of the technical assistance that the staff has routinely provided to schools, individuals and researchers who have called on the RINSC for resolution of problems relating to nuclear science. The reactor has been featured in a Public Broadcasting System documentary on Pollution in the Arctic and how a University of Rhode Island Professor used Neutron Activation Analysis conducted at the RINSC to discover the sources of the ''Arctic Haze''. The RINSC was also featured by local television on Earth Day for its role in environmental monitoring

3. Necessity of research reactors

International Nuclear Information System (INIS)

Ito, Tetsuo

2016-01-01

Currently, only three educational research reactors at two universities exist in Japan: KUR, KUCA of Kyoto University and UTR-KINKI of Kinki University. UTR-KINKI is a light-water moderated, graphite reflected, heterogeneous enriched uranium thermal reactor, which began operation as a private university No. 1 reactor in 1961. It is a low power nuclear reactor for education and research with a maximum heat output of 1 W. Using this nuclear reactor, researches, practical training, experiments for training nuclear human resources, and nuclear knowledge dissemination activities are carried out. As of October 2016, research and practical training accompanied by operation are not carried out because it is stopped. The following five items can be cited as challenges faced by research reactors: (1) response to new regulatory standards and stagnation of research and education, (2) strengthening of nuclear material protection and nuclear fuel concentration reduction, (3) countermeasures against aging and next research reactor, (4) outflow and shortage of nuclear human resources, and (5) expansion of research reactor maintenance cost. This paper would like to make the following recommendations so that we can make contribution to the world in the field of nuclear power. (1) Communication between regulatory authorities and business operators regarding new regulatory standards compliance. (2) Response to various problems including spent fuel measures for long-term stable utilization of research reactors. (3) Personal exchanges among nuclear experts. (4) Expansion of nuclear related departments at universities to train nuclear human resources. (5) Training of world-class nuclear human resources, and succession and development of research and technologies. (A.O.)

4. Development of Reactor Console Simulator for PUSPATI TRIGA Reactor

International Nuclear Information System (INIS)

Mohd Idris Taib; Izhar Abu Hussin; Mohd Khairulezwan Abdul Manan; Nufarhana Ayuni Joha; Mohd Sabri Minhat

2012-01-01

The Reactor Console Simulator will be an interactive tool for operator training and teaching of PUSPATI TRIGA Reactor. Behaviour and characteristic for reactor console and reactor itself can be evaluated and understand. This Simulator will be used as complement for actual present reactor console. Implementation of man-machine interface is using computer screens, keyboard and mouse. Multiple screens are used to match the physical of present reactor console. LabVIEW software are using for user interface and mathematical calculation. Polynomial equation based on control rods calibration data as well as operation parameters record was used to calculate the estimated reactor console parameters. (author)

5. Nuclear reactor safety system

International Nuclear Information System (INIS)

Ball, R.M.; Roberts, R.C.

1983-01-01

The invention provides a safety system for a nuclear reactor which uses a parallel combination of computer type look-up tables each of which receives data on a particular parameter (from transducers located in the reactor system) and each of which produces the functional counterpart of that particular parameter. The various functional counterparts are then added together to form a control signal for shutting down the reactor. The functional counterparts are developed by analysis of experimental thermal and hydraulic data, which are used to form expressions that define safe conditions

6. Fast breeder reactor

International Nuclear Information System (INIS)

Ito, Shin-ichi; Maki, Koichi.

1975-01-01

Object: To conserve loaded fuel, aquire controllable surplus reaction degree, increase the breeding index, flatten output and improve sealing of neutrons by inserting a decelerating substance in a blanket section. Structure: A decelerating substance such as beryllium or beryllium oxide is inserted in a blanket section between an outer reactor core and reflector. With this arrangement, neutrons are decelerated to increase the low energy components, which are partly subjected to reflection by the outer reactor core to thereby reduce leakage of neutrons from the reactor core. (Kamimura, M.)

7. Fast Breeder Reactor studies

International Nuclear Information System (INIS)

Till, C.E.; Chang, Y.I.; Kittel, J.H.; Fauske, H.K.; Lineberry, M.J.; Stevenson, M.G.; Amundson, P.I.; Dance, K.D.

1980-07-01

This report is a compilation of Fast Breeder Reactor (FBR) resource documents prepared to provide the technical basis for the US contribution to the International Nuclear Fuel Cycle Evaluation. The eight separate parts deal with the alternative fast breeder reactor fuel cycles in terms of energy demand, resource base, technical potential and current status, safety, proliferation resistance, deployment, and nuclear safeguards. An Annex compares the cost of decommissioning light-water and fast breeder reactors. Separate abstracts are included for each of the parts

8. Inherently safe reactors

International Nuclear Information System (INIS)

Maartensson, Anders

1992-01-01

A rethinking of nuclear reactor safety has created proposals for new designs based on inherent and passive safety principles. Diverging interpretations of these concepts can be found. This article reviews the key features of proposed advanced power reactors. An evaluation is made of the degree of inherent safety for four different designs: the AP-600, the PIUS, the MHTGR and the PRISM. The inherent hazards of today's most common reactor principles are used as reference for the evaluation. It is concluded that claims for the new designs being inherently, naturally or passively safe are not substantiated by experience. (author)

9. Reactor utilization, Part 1

International Nuclear Information System (INIS)

Martinc, R.; Stanic, A.

1981-01-01

The reactor operating plan for 1981 was subject to the needs of testing operation with the 80% enriched fuel and was fulfilled on the whole. This annex includes data about reactor operation, review of shorter interruptions due to demands of the experiments, data about safety shutdowns caused by power cuts. Period of operation at low power levels was used mostly for activation analyses, and the operation at higher power levels were used for testing and regular isotope production. Detailed data about samples activation are included as well as utilization of the reactor as neutron source and the operating plan for 1982 [sr

10. Reactor BR2: Introduction

International Nuclear Information System (INIS)

Gubel, P.

2000-01-01

The BR2 reactor is still SCK-CEN's most important nuclear facility. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. A safety audit was conduced by the IAEA, the conclusions of which demonstrated the excellent performance of the plant in terms of operational safety. In 1999, the CALLISTO facility was extensively used for various programmes involving LWR pressure vessel materials, IASCC of LWR structural materials, fusion reactor materials and martensic steels for use in ADS systems. In 1999, BR2's commercial programmes were further developed

11. Research reactor support

International Nuclear Information System (INIS)

2005-01-01

Research reactors (RRs) have been used in a wide range of applications including nuclear power development, basic physics research, education and training, medical isotope production, geology, industry and other fields. However, many research reactors are fuelled with High Enriched Uranium (HEU), are underutilized and aging, and have significant quantities of spent fuel. HEU inventories (fresh and spent) pose security risks Unavailability of a high-density-reprocessable fuel hinders conversion and limits back-end options and represents a survival dilemma for many RRs. Improvement of interim spent fuel storage is required at some RRs. Many RRs are under-utilized and/or inadequately funded and need to find users for their services, or permanently shut down and eventually decommission. Reluctance to decommission affect both cost and safety (loss of experienced staff ) and many shut down but not decommissioned RR with fresh and/or spent fuel at the sites invoke serious concern. The IAEA's research reactor support helps to ensure that research reactors can be operated efficiently with fuels and targets of lower proliferation and security concern and that operators have appropriate technology and options to manage RR fuel cycle issues, especially on long term interim storage of spent research reactor fuel. Availability of a high-density-reprocessable fuel would expand and improve back end options. The International Atomic Energy Agency provides assistance to Member States to convert research reactors from High Enriched Uranium fuel and targets (for medical isotope production) to qualified Low Enriched Uranium fuel and targets while maintaining reactor performance levels. The assistance includes provision of handbooks and training in the performance of core conversion studies, advice for the procurement of LEU fuel, and expert services for LEU fuel acceptance. The IAEA further provides technical and administrative support for countries considering repatriation of its

12. Nuclear reactor theory

International Nuclear Information System (INIS)

Sekimoto, Hiroshi

2007-09-01

This textbook is composed of two parts. Part 1 'Elements of Nuclear Reactor Theory' is composed of only elements but the main resource for the lecture of nuclear reactor theory, and should be studied as common knowledge. Much space is therefore devoted to the history of nuclear energy production and to nuclear physics, and the material focuses on the principles of energy production in nuclear reactors. However, considering the heavy workload of students, these subjects are presented concisely, allowing students to read quickly through this textbook. (J.P.N.)

13. Power reactor design trends

International Nuclear Information System (INIS)

Hogan, W.J.

1985-01-01

Cascade and Pulse Star represent new trends in ICF power reactor design that have emerged in the last few years. The most recent embodiments of these two concepts, and that of the HYLIFE design with which they will compare them, are shown. All three reactors depend upon protecting structural elements from neutrons, x rays and debris by injecting massive amounts of shielding material inside the reaction chamber. However, Cascade and Pulse Star introduce new ideas to improve the economics, safety, and environmental impact of ICF reactors. They also pose different development issues and thus represent technological alternatives to HYLIFE

14. Reactor power control system

International Nuclear Information System (INIS)

Tomisawa, Teruaki.

1981-01-01

Purpose: To restore reactor-power condition in a minimum time after a termination of turbine bypass by reducing the throttling of the reactor power at the time of load-failure as low as possible. Constitution: The transient change of the internal pressure of condenser is continuously monitored. When a turbine is bypassed, a speed-control-command signal for a coolant recirculating pump is generated according as the internal pressure of the condenser. When the signal relating to the internal pressure of the condenser indicates insufficient power, a reactor-control-rod-drive signal is generated. (J.P.N.)

15. Reactors of the world

International Nuclear Information System (INIS)

1971-01-01

Basic data relating to 127 power reactors in 15 countries which are expected to be in operation at the end of this year, with a total installed electrical generating capacity of 35 340.15 MW(e), and a listing of 361 research reactors in 46 countries are given in the 1971 edition of the IAEA handbook, Power and Research Reactors in Member States, which has just been published. This edition, the fourth, was prepared especially for the Fourth International Conference on the Peaceful Uses of Atomic Energy. (author)

16. Reactor Safety Assessment System

International Nuclear Information System (INIS)

Sebo, D.E.; Bray, M.A.; King, M.A.

1987-01-01

The Reactor Safety Assessment System (RSAS) is an expert system under development for the United States Nuclear Regulatory Commission (USNRC). RSAS is designed for use at the USNRC Operations Center in the event of a serious incident at a licensed nuclear power plant. RSAS is a situation assessment expert system which uses plant parametric data to generate conclusions for use by the NRC Reactor Safety Team. RSAS uses multiple rule bases and plant specific setpoint files to be applicable to all licensed nuclear power plants in the United States. RSAS currently covers several generic reactor categories and multiple plants within each category

17. Mirror machine reactors

International Nuclear Information System (INIS)

Carlson, G.A.; Moir, R.W.

1976-01-01

Recent mirror reactor conceptual design studies are described. Considered in detail is the design of ''standard'' Yin-Yang fusion power reactors with classical and enhanced confinement. It is shown that to be economically competitive with estimates for other future energy sources, mirror reactors require a considerable increase in Q, or major design simplifications, or preferably both. These improvements may require a departure from the ''standard'' configuration. Two attractive possibilities, both of which would use much of the same physics and technology as the ''standard'' mirror, are the field reversed mirror and the end-stoppered mirror

18. Corrosion of reactor materials

Energy Technology Data Exchange (ETDEWEB)

NONE

1963-01-15

Much operational experience and many experimental results have accumulated in recent years regarding corrosion of reactor materials, particularly since the 1958 Geneva Conference on the Peaceful Uses of Atomic Energy, where these problems were also discussed. It was, felt that a survey and critical appraisal of the results obtained during this period had become necessary and, in response to this need, IAEA organized a Conference on the Corrosion of Reactor Materials at Salzburg, Austria (4-9 June 1962). It covered many of the theoretical, experimental and engineering problems relating to the corrosion phenomena which occur in nuclear reactors as well as in the adjacent circuits

19. Reactor pressure tank

International Nuclear Information System (INIS)

Dorner, H.; Scholz, M.; Jungmann, A.

1975-01-01

In a reactor pressure tank for a nuclear reactor, self-locking hooks engage a steel ring disposed over the removable cover of the steel vessel. The hooks exert force upon the cover to maintain the cover in a closed position during operation of the reactor pressure tank. The force upon the removal cover is partly the result of the increasing temperature and thermal expansion of the steel vessel during operation. The steel vessel is surrounded by a reinforced-concrete tank. (U.S.)

20. Pool-type reactor

International Nuclear Information System (INIS)

Hopkins, S.R.

1977-01-01

This invention relates to a pool nuclear reactor fitted with a perfected system to raise the buckets into a vertical position at the bottom of a channel. This reactor has an inclined channel to guide a bucket containing a fuel assembly to introduce it into the reactor jacket or extract it therefrom and a damper at the bottom of the channel to stop the drop of the bucket. An upright vertically movable rod has a horizontally articulated arm with a hook. This can pivot to touch a radial lug on the bucket and pivot the bucket around its base in a vertical position, when the rod moves up [fr

1. Reactor safety assessment system

International Nuclear Information System (INIS)

Sebo, D.E.; Bray, M.A.; King, M.A.

1987-01-01

The Reactor Safety Assessment System (RSAS) is an expert system under development for the United States Nuclear Regulatory Commission (USNRC). RSA is designed for use at the USNRC Operations Center in the event of a serious incident at a licensed nuclear power plant. RSAS is a situation assessment expert system which uses plant parametric data to generate conclusions for use by the NRC Reactor Safety Team. RSAS uses multiple rule bases and plant specific setpoint files to be applicable to all licensed nuclear power plants in the United States. RSAS currently covers several generic reactor categories and multiple plants within each category

International Nuclear Information System (INIS)

1990-04-01

The Operating Units Status Report --- Licensed Operating Reactors provides data on the operation of nuclear units as timely and accurately as possible. This information is collected by the Office of Information Resources Management from the Headquarters staff on NRC's Office of Enforcement (OE), from NRC's Regional Offices, and from utilities. The three sections of the report are: monthly highlights and statistics for commercial operating units, and errata from previously reported data; a compilation of detailed information on each unit, provided by NRC's Regional Offices, OE Headquarters and the utilities; and an appendix for miscellaneous information such as spent fuel storage capability, reactor-years of experience and non- power reactors in the US

3. Fusion Reactor Materials

International Nuclear Information System (INIS)

Decreton, M.

2001-01-01

The objective of SCK-CEN's programme on fusion reactor materials is to contribute to the knowledge on the behaviour of fusion reactor materials and components during and after irradiation. Ongoing projects include: the study of the mechanical behaviour of structural materials under neutron irradiation; the investigation of the characteristics of irradiated first wall material such as beryllium; the detection of abrupt electrical degradation of insulating ceramics under high temperature and neutron irradiation; and the study of dismantling and waste disposal strategy for fusion reactors. Progress and achievements in these areas in 2000 are discussed

4. Sodium cooled fast reactor

Energy Technology Data Exchange (ETDEWEB)

Hokkyo, N; Inoue, K; Maeda, H

1968-11-21

In a sodium cooled fast neutron reactor, an ultrasonic generator is installed at a fuel assembly hold-down mechanism positioned above a blanket or fission gas reservoir located above the core. During operation of the reactor an ultrsonic wave of frequency 10/sup 3/ - 10/sup 4/ Hz is constantly transmitted to the core to resonantly inject the primary bubble with ultrasonic energy to thereby facilitate its growth. Hence, small bubbles grow gradually to prevent the sudden boiling of sodium if an accident occurs in the cooling system during operation of the reactor.

5. Elmo Bumpy Torus Reactor

International Nuclear Information System (INIS)

McAlees, D.G.; Uckan, N.A.; Lidsky, L.M.

1976-01-01

In the Elmo Bumpy Torus Reactor (EBTR) study the feasibility of achieving a fusion power plant based on the EBT confinement concept was evaluated. If the present understanding of the physics can be extrapolated to reactor scale devices the reactor could operate at high beta, high power density, and at steady state. The high aspect ratio of the device eases the accessibility, structural design and remote maintenance problems which are common to low aspect ratio machines. A version of the EBTR reference design described here could be constructed with only minor extrapolations in available technology

6. Fast Breeder Reactor studies

Energy Technology Data Exchange (ETDEWEB)

Till, C.E.; Chang, Y.I.; Kittel, J.H.; Fauske, H.K.; Lineberry, M.J.; Stevenson, M.G.; Amundson, P.I.; Dance, K.D.

1980-07-01

This report is a compilation of Fast Breeder Reactor (FBR) resource documents prepared to provide the technical basis for the US contribution to the International Nuclear Fuel Cycle Evaluation. The eight separate parts deal with the alternative fast breeder reactor fuel cycles in terms of energy demand, resource base, technical potential and current status, safety, proliferation resistance, deployment, and nuclear safeguards. An Annex compares the cost of decommissioning light-water and fast breeder reactors. Separate abstracts are included for each of the parts.

7. Fusion reactor radioactive waste management

International Nuclear Information System (INIS)

Kaser, J.D.; Postma, A.K.; Bradley, D.J.

1976-01-01

Quantities and compositions of non-tritium radioactive waste are estimated for some current conceptual fusion reactor designs, and disposal of large amounts of radioactive waste appears necessary. Although the initial radioactivity of fusion reactor and fission reactor wastes are comparable, the radionuclides in fusion reactor wastes are less hazardous and have shorter half-lives. Areas requiring further research are discussed

Energy Technology Data Exchange (ETDEWEB)

None

1960-12-15

Design information on the Canada-India Reactor is presented. Data are given on reactor physics, the core, fuel elements, core heat transfer, control, reactor vessel, fluid flow, reflector and shielding, containment, cost estimates, and research facilities. Drawings of vertical and horizontal sections of the reactor and fluid flow are included. (M.C.G.)

9. Nuclear reactor cavity streaming shield

International Nuclear Information System (INIS)

Klotz, R.J.; Stephen, D.W.

1978-01-01

The upper portion of a nuclear reactor vessel supported in a concrete reactor cavity has a structure mounted below the top of the vessel between the outer vessel wall and the reactor cavity wall which contains hydrogenous material which will attenuate radiation streaming upward between vessel and the reactor cavity wall while preventing pressure buildup during a loss of coolant accident

10. A multi-purpose reactor

International Nuclear Information System (INIS)

Changwen Ma

2000-01-01

An integrated natural circulation self pressurized reactor can be used for sea water desalination, electrogeneration, ship propulsion and district or process heating. The reactor can be used for ship propulsion because it has following advantages: it is a integrated reactor. Whole primary loop is included in a size limited pressure vessel. For a 200 MW reactor the diameter of the pressure vessel is about 5 m. It is convenient to arranged on a ship. Hydraulic driving facility of control rods is used on the reactor. It notably decreases the height of the reactor. For ship propulsion, smaller diameter and smaller height are important. Besides these, the operation reliability of the reactor is high enough, because there is no rotational machine (for example, circulating pump) in safety systems. Reactor systems are simple. There are no emergency water injection system and boron concentration regulating system. These features for ship propulsion reactor are valuable. Design of the reactor is based on existing demonstration district heating reactor design. The mechanic design principles are the same. But boiling is introduced in the reactor core. Several variants to use the reactor as a movable seawater desalination plant are presented in the paper. When the sea water desalination plant is working to produce fresh water, the reactor can supply electricity at the same time to the local electricity network. Some analyses for comprehensive application of the reactor have been done. Main features and parameters of the small (Thermopower 200 MW) reactor are given in the paper. (author)

11. Reactor Engineering Division annual report

International Nuclear Information System (INIS)

1975-11-01

Research activities in fiscal 1974 in Reactor Engineering Division of eight laboratories and computing center are described. Works in the division are closely related with the development of a multi-purpose High-temperature Gas Cooled Reactor, the development of a Liquid Metal Fast Breeder Reactor in Power Reactor and Nuclear Fuel Development Corporation, and engineering of thermonuclear fusion reactors. They cover nuclear data and group constants, theoretical method and code development, integral experiment and analysis, shielding, heat transfer and fluid dynamics, reactor and nuclear instrumentation, dynamics analysis and control method development, fusion reactor technology and aspects of the computing center. (auth.)

12. OKLO: fossil reactors

International Nuclear Information System (INIS)

Naudet, R.

Events leading up to the discovery during the summer of 1972 of the Oklo fossil reactor in Gabon and its subsequent exploration are reviewed. Results of studies are summarized; future investigations are outlined

13. Ageing of research reactors

International Nuclear Information System (INIS)

Ciocanescu, M.

2001-01-01

Historically, many of the research institutions were centred on a research reactor facility as main technological asset and major source of neutrons for research. Important achievements were made in time in these research institutions for development of nuclear materials technology and nuclear safety for nuclear energy. At present, ageing of nuclear research facilities among these research reactors and ageing of staff are considerable factors of reduction of competence in research centres. The safe way of mitigation of this trend deals with ageing management by so called, for power reactors, Plant Life Management and new investments in staff as investments in research, or in future resources of competence. A programmatic approach of ageing of research reactors in correlation with their actual and future utilisation, will be used as a basis for safety evaluation and future spending. (author)

14. Backfitting of research reactors

International Nuclear Information System (INIS)

Delrue, R.; Noesen, T.

1985-01-01

The backfitting of research reactors covers a variety of activities. 1. Instrumentation and control: Control systems have developed rapidly and many reactor operators wish to replace obsolete equipment by new systems. 2. Pool liners: Some pools are lined internally with ceramic tiles. These may become pervious with time necessitating replacement, e.g. by a new stainless steel liner. 3. Heat removal system: Deficiencies can occur in one or more of the cooling system components. Upgrading may require modifications of the system such as addition of primary loops, introduction of deactivation tanks, pump replacement. Recent experience in such work has shown that renewal, backfitting and upgrading of an existing reactor is economically attractive since the related costs and delivery times are substantially lower than those required to install a new research reactor

15. New reactor type proposed

CERN Multimedia

2003-01-01

"Russian scientists at the Research Institute of Nuclear Power Engineering in Moscow are hoping to develop a new reactor that will use lead and bismuth as fuel instead of uranium and plutonium" (1/2 page).

16. EPR (European Pressurized Reactor)

International Nuclear Information System (INIS)

2015-01-01

This document presents the EPR (European Pressurized Reactor), a modernised version of PWRs which uses nuclear fission. It indicates to which category it belongs (third generation). It briefly describes its operation: recalls on nuclear fission, electricity production in a nuclear reactor. It presents and comments its characteristics: power, thermal efficiency, redundant systems for safety control, double protective enclosure, expected lifetime, use of MOX fuel, modular design. It discusses economic stakes (expected higher nuclear electricity competitiveness, but high construction costs), and safety challenges (design characteristics, critics by nuclear safety authorities about the safety data processing system). It presents the main involved actors (Areva, EDF) and competitors in the field of advanced reactors (Rosatom with its VVER 1200, General Electric with its ABWR and its ESBWR, Mitsubishi with its APWR, Westinghouse with its AP100) while outlining the importance of certifications and delays to obtain them. After having evoked key data on EPR fuel consumption, it indicates reactors under construction, evokes potential markets and perspectives

17. Reactor power control device

International Nuclear Information System (INIS)

Doi, Kazuyori.

1981-01-01

Purpose: To automatically control the BWR type reactor power by simple and short-time searching the load pattern nearest to the required pattern at a nuclear power plant side. Constitution: The reactor power is automatically regulated by periodical modifying of coefficients fitting to a reactor core model, according as a required load pattern. When a load requirement pattern is given, a simulator estimates the total power change and the axial power distribution change from a xenon density change output calculated by a xenon dynamic characteristic estimating device, and a load pattern capable of being realized is searched. The amount to be recirculated is controlled on the basis of the load patteren thus searched, and the operation of the BWR type reactor is automatically controlled at the side of the nuclear power plant. (Kamimura, M.)

18. Inertial fusion reactor designs

International Nuclear Information System (INIS)

Meier, W.

1987-01-01

In this paper, a variety of reactor concepts are proposed. One of the prime concerns is dealing with the x-rays and debris that are emitted by the target. Internal neutron shielding can reduce radiation damage and activation, leading to longer life systems, reduced activation and fewer safety concerns. There is really no consensus on what the best reactor concept is at this point. There has been virtually no chamber technology development to date. This is the flip side of the coin of the separability of the target physics and the reactor design. Since reactor technology has not been required to do target experiments, it's not being developed. Economic analysis of conceptual designs indicates that ICF can be economically competitive with magnetic fusion, fission and fossil plants

19. Device for thermonuclear reactor

International Nuclear Information System (INIS)

Yanagisawa, Yutaro; Kawarazaki, Yuki; Sugiyama, Yu.

1996-01-01

A member comprising hydrogen occluding materials is introduced to a reactor incorporated with U-235 as fuels in order to moderate and breed fast neutrons and to control the reactor. Since the amount of light hydrogen or heavy hydrogen is substantially the same as that of metal, etc. of hydrogen occluding material, a moderating efficiency substantially equal with that of a moderator comprising H 2 O can be obtained. In addition, since the member acting as a moderator has an effect of multiplying neutrons, use of only natural uranium 0.72% as nuclear fuels causes chain reaction to provide a function as a nuclear reactor. Further, the hydrogen occluding material can be used also as a control rod for controlling the reactor. The hydrogen occluding material may be Ti, Zr, Pd, proton conductor, Ag, Pt, Rh or oxides thereof or alloys thereof. The member comprising hydrogen occluding materials is preferably coated with a material not permeating hydrogen. (N.H.)

20. The fast breeder reactor

International Nuclear Information System (INIS)

Patterson, W.

1990-01-01

The author criticises the United Kingdom Atomic Energy Authority's fast breeder reactor programme in his evidence to the House of Commons Select Committee on Energy in January 1990. He argues for power generation by renewable means and greater efficiency in the use rather than in the generation of electricity. He refutes the arguments for nuclear power on the basis of reduced global warming as he claims support technology produces significant amounts of carbon dioxide in any case. Serious doubts are raised about the costs of a fast breeder reactor programme compared to, say, generation by pressurised water reactors. The idea of a uranium scarcity in several decades is also refuted. The reliability of fast breeder reactor technology is called into question. He argues against reprocessing plutonium for economic, health and safety reasons. (UK)

1. Reactor vessel sealing plug

International Nuclear Information System (INIS)

Dooley, R.A.

1986-01-01

This invention relates to an apparatus and method for sealing the cold leg nozzles of a nuclear reactor pressure vessel from a remote location during maintenance and inspection of associated steam generators and pumps while the pressure vessel and refueling canal are filled with water. The apparatus includes a sealing plug for mechanically sealing the cold leg nozzle from the inside of a reactor pressure vessel. The sealing plugs include a primary and a secondary O-ring. An installation tool is suspended within the reactor vessel and carries the sealing plug. The tool telescopes to insert the sealing plug within the cold leg nozzle, and to subsequently remove the plug. Hydraulic means are used to activate the sealing plug, and support means serve to suspend the installation tool within the reactor vessel during installation and removal of the sealing plug

2. Gas cooled reactors

International Nuclear Information System (INIS)

Kojima, Masayuki.

1985-01-01

Purpose: To enable direct cooling of reactor cores thereby improving the cooling efficiency upon accidents. Constitution: A plurality sets of heat exchange pipe groups are disposed around the reactor core, which are connected by way of communication pipes with a feedwater recycling device comprising gas/liquid separation device, recycling pump, feedwater pump and emergency water tank. Upon occurrence of loss of primary coolants accidents, the heat exchange pipe groups directly absorb the heat from the reactor core through radiation and convection. Although the water in the heat exchange pipe groups are boiled to evaporate if the forcive circulation is interrupted by the loss of electric power source, water in the emergency tank is supplied due to the head to the heat exchange pipe groups to continue the cooling. Furthermore, since the heat exchange pipe groups surround the entire circumference of the reactor core, cooling is carried out uniformly without resulting deformation or stresses due to the thermal imbalance. (Sekiya, K.)

3. Reactor BR2. Introduction

International Nuclear Information System (INIS)

Gubel, P.

2002-01-01

The BR2 materials testing reactor is one of SCK-CEN's most important nuclear facilities. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. In 2001, the reactor was operated for a total of 123 days at a mean power of 59 MW in order to satisfy the irradiation conditions of the internal and external programmes using mainly the CALLISTO PWR loop. The mean consumption of fresh fuel elements was 5.26 per 1000 MWd. Main achievements in 2001 included the development of a three-dimensional full-scale model of the BR2 reactor for simulation and prediction of irradiation conditions for various experiments; the construction of the FUTURE-MT device designed for the irradiation of fuel plates under representative conditions of geometry, neutron spectrum, heat flux and thermal-hydraulic conditions and the development of in-pile instrumentation and a data acquisition system

4. Elements on reactor control

International Nuclear Information System (INIS)

Bruna, G.B.

1998-01-01

In order to achieve the two-fold goal of maximizing the energy obtained from reactor fuel and ensuring the large flexibility of plant operation in respect to safety regulations and keeping the reactor integrity the control of PWRs is generally based on real time monitoring and analysing of independent neutronic parameters: thermal power release, axial power distribution in the core and temperatures of the primary loop. Two control chains more or less coupled according to the control chosen mode are in charge of the control of these parameters. With the brief history of control in French power reactors the advanced X control mode adopted by Framatome for N4 plants is described in detail. A summary of N4 reactor control and protection system is included

5. FBR type reactor

International Nuclear Information System (INIS)

Yamaoka, Mitsuaki

1988-01-01

Purpose: To enable to increase the burning period by enabling to decrease the reduction of burning reactivity and unifying the irradiation amount of fast neutrons. Constitution: A cylindrical reactor core made of fissile material-enriched fuel is constituted so as to form a plurality of layer-like enriched regions in which the enrichment degree of the fissile material is increased from the center to the radial and axial directions. Then, the ratio between the average enrichment degree for all of the enrichment regions other than the region at the reactor core center with the lowest enrichment degree and the enrichment degree of the enriched region formed at the center of the reactor core is made greater by 5 % or 20 % than the ratio at the initial burning stage where the power distribution of the reactor core is most flattened. (Kawakami, Y.)

6. Nuclear reactor (1960)

International Nuclear Information System (INIS)

Maillard, M.L.

1960-01-01

The first French plutonium-making reactors G1, G2 and G3 built at Marcoule research center are linked to a power plant. The G1 electrical output does not offset the energy needed for operating this reactor. On the contrary, reactors G2 and G3 will each generate a net power of 25 to 30 MW, which will go into the EDF grid. This power is relatively small, but the information obtained from operation is great and will be helpful for starting up the power reactor EDF1, EDF2 and EDF3. The paper describes how, previous to any starting-up operation, the tests performed, especially those concerned with the power plant and the pressure vessel, have helped to bring the commissioning date closer. (author) [fr

7. Reactor BR2. Introduction

International Nuclear Information System (INIS)

Gubel, P.

2001-01-01

The BR2 is a materials testing reactor and is still one of SCK-CEN's important nuclear facilities. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. During the last three years, the availability of the installation was maintained at an average level of 97.6 percent. In the year 2000, the reactor was operated for a total of 104 days at a mean power of 56 MW. In 2000, most irradiation experiments were performed in the CALLISTO PWR loop. The report describes irradiations achieved or under preparation in 2000, including the development of advanced facilities and concept studies for new programmes. An overview of the scientific irradiation programmes as well as of the R and D programme of the BR2 reactor in 2000 is given

8. Reactor pressure vessel support

International Nuclear Information System (INIS)

Butti, J.P.

1977-01-01

A link and pin support system provides the primary vertical and lateral support for a nuclear reactor pressure vessel without restricting thermally induced radial and vertical expansion and contraction. (Auth.)

9. Method of reactor fueling

International Nuclear Information System (INIS)

Saito, Toshiro.

1983-01-01

Purpose: To decrease the cost and shorten the working time by saving fueling neutron detectors and their components. Method: Incore drive tubes for the neutron source range monitor (SRM) and intermediate range monitor (IRM) are disposed respectively within in a reactor core and a SRM detector assembly is inserted to the IRM incore drive tube which is most nearest to the neutron source upon reactor fueling. The reactor core reactivity is monitored by the SRM detector assembly. The SRM detector asesembly inserted into the IRM drive tube is extracted at the time of charging fuels up to the frame connecting the SRM and, thereafter, IRM detection assembly is inserted into the IRM drive tube and the SRM detector assembly is inserted into the SRM drive tube respectively for monitoring the reactor core. (Sekiya, K.)

10. Nuclear reactor fuel elements

International Nuclear Information System (INIS)

Hindle, E.D.

1981-01-01

An array of rods comprising zirconium alloy sheathed nuclear fuel pellets assembled to form a fuel element for a pressurised water reactor is claimed. The helium gas pressure within each rod differs substantially from that of its closest neighbours

11. Nuclear reactor fuel elements

International Nuclear Information System (INIS)

Hindle, E.D.

1984-01-01

The fuel elements for a pressurised water reactor comprise arrays of rods of zirconium alloy sheathed nuclear fuel pellets. The helium gas pressure within each rod differs substantially from that of its closest neighbours

12. Pressure tube type reactors

International Nuclear Information System (INIS)

1981-01-01

Purpose: To increase the safety of pressure tube type reactors by providing an additional ECCS system to an ordinary ECCS system and injecting heavy water in the reactor core tank into pressure tubes upon fractures of the tubes. Constitution: Upon fractures of pressure tubes, reduction of the pressure in the fractured tubes to the atmospheric pressure in confirmed and the electromagnetic valve is operated to completely isolate the pressure tubes from the fractured portion. Then, the heavy water in the reactor core tank flows into and spontaneously recycles through the pressure tubes to cool the fuels in the tube to prevent their meltdown. By additionally providing the separate ECCS system to the ordinary ECCS system, fuels can be cooled upon loss of coolant accidents to improve the safety of the reactors. (Moriyama, K.)

13. Fusion Reactor Materials

Energy Technology Data Exchange (ETDEWEB)

Decreton, M

2002-04-01

The objective of SCK-CEN's programme on fusion reactor materials is to contribute to the knowledge on the radiation-induced behaviour of fusion reactor materials and components as well as to help the international community in building the scientific and technical basis needed for the construction of the future reactor. Ongoing projects include: the study of the mechanical and chemical (corrosion) behaviour of structural materials under neutron irradiation and water coolant environment; the investigation of the characteristics of irradiated first wall material such as beryllium; investigations on the management of materials resulting from the dismantling of fusion reactors including waste disposal. Progress and achievements in these areas in 2001 are discussed.

14. Pulsed fusion reactors

International Nuclear Information System (INIS)

1975-01-01

This summer school specialized in examining specific fusion center systems. Papers on scientific feasibility are first presented: confinement of high-beta plasma, liners, plasma focus, compression and heating and the use of high power electron beams for thermonuclear reactors. As for technological feasibility, lectures were on the theta-pinch toroidal reactors, toroidal diffuse pinch, electrical engineering problems in pulsed magnetically confined reactors, neutral gas layer for heat removal, the conceptual design of a series of laser fusion power plants with ''Saturn'', implosion experiments and the problem of the targets, the high brightness lasers for plasma generation, and topping and bottoming cycles. Some problems common to pulsed reactors were examined: energy storage and transfer, thermomechanical and erosion effects in the first wall and blanket, the problems of tritium production, radiation damage and neutron activation in blankets, and the magnetic and inertial confinement

15. Reactor BR2. Introduction

Energy Technology Data Exchange (ETDEWEB)

Gubel, P

2002-04-01

The BR2 materials testing reactor is one of SCK-CEN's most important nuclear facilities. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. In 2001, the reactor was operated for a total of 123 days at a mean power of 59 MW in order to satisfy the irradiation conditions of the internal and external programmes using mainly the CALLISTO PWR loop. The mean consumption of fresh fuel elements was 5.26 per 1000 MWd. Main achievements in 2001 included the development of a three-dimensional full-scale model of the BR2 reactor for simulation and prediction of irradiation conditions for various experiments; the construction of the FUTURE-MT device designed for the irradiation of fuel plates under representative conditions of geometry, neutron spectrum, heat flux and thermal-hydraulic conditions and the development of in-pile instrumentation and a data acquisition system.

16. Reactor BR2. Introduction

Energy Technology Data Exchange (ETDEWEB)

Gubel, P

2001-04-01

The BR2 is a materials testing reactor and is still one of SCK-CEN's important nuclear facilities. After an extensive refurbishment to compensate for the ageing of the installation, the reactor was restarted in April 1997. During the last three years, the availability of the installation was maintained at an average level of 97.6 percent. In the year 2000, the reactor was operated for a total of 104 days at a mean power of 56 MW. In 2000, most irradiation experiments were performed in the CALLISTO PWR loop. The report describes irradiations achieved or under preparation in 2000, including the development of advanced facilities and concept studies for new programmes. An overview of the scientific irradiation programmes as well as of the R and D programme of the BR2 reactor in 2000 is given.

17. Nuclear reactor core catcher

International Nuclear Information System (INIS)

1977-01-01

A nuclear reactor core catcher is described for containing debris resulting from an accident causing core meltdown and which incorporates a method of cooling the debris by the circulation of a liquid coolant. (U.K.)

18. The Integral Fast Reactor

International Nuclear Information System (INIS)

Till, C.E.

1985-01-01

During the past two years, scientists from Argonne have developed an advanced breeder reactor with a closed self contained fuel cycle. The Integral Fast Reactor (IFR) is a new reactor concept, adaptable to a variety of designs, that is based on a fuel cycle radically different from the CRBR line of breeder development. The essential features of the IFR are metal fuel, pool layout, and pyro- and electro-reprocessing in a facility integral with the reactor plant. The IFR shows promise to provide an inexhaustible, safe, economic, environmentally acceptable, and diversion resistant source of nuclear power. It shows potential for major improvement in all of the areas that have led to concern about nuclear power

19. Pressurized water reactor systems

International Nuclear Information System (INIS)

Meyer, P.J.

1975-01-01

Design and mode of operation of the main PWR components are described: reactor core, pressure vessel and internals, cooling systems with pumps and steam generators, ancillary systems, and waste processing. (TK) [de

20. BWR type reactors

International Nuclear Information System (INIS)

Nakajima, Yoshitaka

1983-01-01

Purpose: To decrease the control rod exchanging frequency by increasing the working life of control rods for ordinary operation with large neutron irradiation dose, to thereby decrease the exposure dose for operators performing exchanging work, as well as decrease the amount of radioactive wastes resulted upon exchange of the control rods. Constitution: Hafnium solid metal is employed as the neutron absorber of control rods for usual operation inserted into and withdrawn from fuel assemblies for the reactor power control over the entire cycle of the ordinary reactor operation and boron carbide powder is employed as the neutron absorber for emergency control rods to be inserted between the fuel assemblies only upon reactor scram or shutdown, whereby the working life of the control rods for ordinary reactor operation with greater neutron irradiation dose can be improved. Accordingly, the control rod exchanging frequency can be reduced to decrease the exposure dose to the operator for conducting the exchanging work. (Yoshihara, H.)

1. Nuclear reactor assembly

International Nuclear Information System (INIS)

Dorner, H.; Scholz, M.; Jungmann, A.

1975-01-01

A nuclear reactor assembly includes a reactor pressure tank having a substantially cylindrical side wall surrounded by the wall of a cylindrical cavity formed by a biological shield. A rotative cylindrical wall is interposed between the walls and has means for rotating it from outside of the shield, and a probe is carried by the rotative wall for monitoring the pressure tank's wall. The probe is vertically movable relative to the rotative cylindrical wall, so that by the probe's vertical movement and rotation of the rotative cylinder, the reactor's wall can be very extensively monitored. If the reactor pressure tank's wall fails, it is contained by the rotative wall which is backed-up by the shield cavity wall. (Official Gazette)

2. Pressure tube reactor

International Nuclear Information System (INIS)

Matsumoto, Tomoyuki; Fujino, Michihira.

1980-01-01

Purpose: To equalize heavy water flow distribution by providing a nozzle for externally injecting heavy water from a vibration preventive plate to the upper portion to feed the heavy water in a pressure tube reactor and swallowing up heavy water in a calandria tank to supply the heavy water to the reactor core above the vibration preventive plate. Constitution: A moderator injection nozzle is mounted on the inner wall of a calandria tank. Heavy water is externally injected above the vibration preventive plate, and heavy water in the calandria tank is swallowed up to supply the heavy water to the core reactor above the vibration preventive plate. Therefore, the heavy water flow distribution can be equalized over the entire reactor core, and the distribution of neutron absorber dissolved in the heavy water is equalized. (Yoshihara, H.)

International Nuclear Information System (INIS)

Fowler, T.K.

1996-01-01

The spheromak has no toroidal magnetic field coils or other structure along its geometric axis, and is thus more attractive than the leading magnetic fusion reactor concept, the tokamak. As a consequence of this and other attributes, the spheromak reactor may be compact and produce a power density sufficiently high to warrant consideration of a liquid 'blanket' that breeds tritium, converts neutron kinetic energy to heat, and protects the reactor vessel from severe neutron damage. However, the physics is more complex, so that considerable research is required to learn how to achieve the reactor potential. Critical physics problems and possible ways of solving them are described. The opportunities and issues associated with a possible liquid wall are considered to direct future research

4. Reactor pressure boundary materials

International Nuclear Information System (INIS)

Hong, Jun Hwa; Chi, S. H.; Lee, B. S.

2002-04-01

With a long-term operation of nuclear power plants, the component materials are degraded under severe reactor conditions such as neutron irradiation, high temperature, high pressure and corrosive environment. It is necessary to establish the reliable and practical technologies for improving and developing the component materials and for evaluating the mechanical properties. Especially, it is very important to investigate the technologies for reactor pressure boundary materials such as reactor vessel and pipings in accordance with their critical roles. Therefore, this study was focused on developing and advancing the microstructural/micro-mechanical evaluation technologies, and on evaluating the neutron irradiation characteristics and radiation effects analysis technology of the reactor pressure boundary materials, and also on establishing a basis of nuclear material property database

5. Nuclear reactor fuel assembly

International Nuclear Information System (INIS)

Sakurai, Shungo; Ogiya, Shunsuke.

1990-01-01

In a fuel assembly, if the entire fuels comprise mixed oxide fuels, reactivity change in cold temperature-power operation is increased to worsen the reactor shutdown margin. The reactor shutdown margin has been improved by increasing the burnable poison concentration thereby reducing the reactivity of the fuel assembly. However, since unburnt poisons are present at the completion of the reactor operation, the reactivity can not be utilized effectively to bring about economical disadvantage. In view of the above, the reactivity change between lower temperature-power operations is reduced by providing a non-boiling range with more than 9.1% of cross sectional area at the inside of a channel at the central portion of the fuel assembly. As a result, the amount of the unburnt burnable poisons is decreased, the economy of fuel assembly is improved and the reactor shutdown margin can be increase. (N.H.)

6. Reactor shutdown device

International Nuclear Information System (INIS)

Inoue, Toyokazu.

1982-01-01

Purpose: To obtain a highly reliable reactor shutdown device capable of checking its function irrespective of the state whether shutdown or operation in a gas-cooled type reactor. Constitution: A hopper is disposed above a guide tube inserted into the reactor core and particulate neutron absorbers are contained in the hopper. An opening for falling particles is disposed to the bottom of the hopper in opposition to the upper end of the guide pipe and the opening is closed by a plug suspended by way of a weld line so as to be capable of dropping. A power source for supplying electrical current to the weld line is disposed. Accordingly, if the current is supplied to the weld line, the line is cut by welding to fall the plug so that the neutron-absorbing particles fall from the opening into the guide pipe to shutdown the reactor, whereby high reliability is obtained for the operation. (Seki, T.)

7. Small reactor operating mode

International Nuclear Information System (INIS)

Snell, V.G.

1997-01-01

There is a potential need for small reactors in the future for applications such as district heating, electricity production at remote sites, and desalination. Nuclear power can provide these at low cost and with insignificant pollution. The economies required by the small scale application, and/or the remote location, require a review of the size and location of the operating staff. Current concepts range all the way from reactors which are fully automatic, and need no local attention for days or weeks, to those with reduced local staff. In general the less dependent a reactor is on local human intervention, the greater its dependence on intrinsic safety features such as passive decay heat removal, low-stored energy and limited reactivity speed and depth in the control systems. A case study of the design and licensing of the SLOWPOKE Energy System heating reactor is presented. (author)

8. RA Reactor applications, Annex A

International Nuclear Information System (INIS)

2000-01-01

Full text: In 2000 Ra reactor was not operated. New instrumentation is not complete, without it, it is not possible to think about reactor start-up. Since 1985, when reactor operation was forbidden, there are 480 fuel elements left in 48 fuel channels in the reactor core. Heavy water was removed from the reactor core because of the repair of the heavy water pumps in 1986. The old instrumentation was removed. Eleven years after being left to its own destiny, it would be difficult to imagine that anybody would think of reactor restart without examining the state of reactor vessel and other vital reactor components. Maintaining the reactor under existing conditions without final decision about restart or permanent shutdown is destructive for this nuclear facility. The existing state that pertains for more than 10 years would have only one result, destruction of the RA reactor [sr

9. RA Reactor applications, Annex A

International Nuclear Information System (INIS)

1998-01-01

Full text: In 1998 Ra reactor was not operated. New instrumentation is not complete, without it, it is not possible to think about reactor start-up. Since 1985, when reactor operation was forbidden, there are 480 fuel elements left in 48 fuel channels in the reactor core. Heavy water was removed from the reactor core because of the repair of the heavy water pumps in 1986. The old instrumentation was removed. Eleven years after being left to its own destiny, it would be difficult to imagine that anybody would think of reactor restart without examining the state of reactor vessel and other vital reactor components. Maintaining the reactor under existing conditions without final decision about restart or permanent shutdown is destructive for this nuclear facility. The existing state that pertains for more than 10 years would have only one result, destruction of the RA reactor [sr

10. RA Reactor applications, Annex A

International Nuclear Information System (INIS)

1996-01-01

Full text: In 2000 Ra reactor was not operated. New instrumentation is not complete, without it, it is not possible to think about reactor start-up. Since 1985, when reactor operation was forbidden, there are 480 fuel elements left in 48 fuel channels in the reactor core. Heavy water was removed from the reactor core because of the repair of the heavy water pumps in 1986. The old instrumentation was removed. Eleven years after being left to its own destiny, it would be difficult to imagine that anybody would think of reactor restart without examining the state of reactor vessel and other vital reactor components. Maintaining the reactor under existing conditions without final decision about restart or permanent shutdown is destructive for this nuclear facility. The existing state that pertains for more than 10 years would have only one result, destruction of the RA reactor [sr

11. Alternative breeder reactor technologies

International Nuclear Information System (INIS)

1978-01-01

The significance of employing breeder reactors to stretch the world resources of nuclear fuels is briefly discussed, and the various types of breeder concepts are described. General descriptions, advantages, and disadvantages of the liquid metal cooled fast breeder, gas cooled fast breeder, molten salt breeder, thermal breeders, and spectral-shift control reactors are presented. Aspects of safeguarding fissile material connected with breeder operation are examined. 31 references

12. Nuclear reactor fuel elements

International Nuclear Information System (INIS)

Butterfield, C.E.; Waite, E.

1982-01-01

A nuclear reactor fuel element comprising a column of vibration compacted fuel which is retained in consolidated condition by a thimble shaped plug. The plug is wedged into gripping engagement with the wall of the sheath by a wedge. The wedge material has a lower coefficient of expansion than the sheath material so that at reactor operating temperature the retainer can relax sufficient to accommodate thermal expansion of the column of fuel. (author)

13. Possible fusion reactor

International Nuclear Information System (INIS)

Yoshikawa, S.

1976-05-01

A scheme to improve performance characteristics of a tokamak-type fusion reactor is proposed. Basically, the tokamak-type plasma could be moved around so that the plasma could be heated by compression, brought to the region where the blanket surrounds the plasma, and moved so as to keep wall loading below the acceptable limit. This idea should be able to help to economize a fusion reactor

14. Nuclear reactor monitoring system

International Nuclear Information System (INIS)

Drummond, C.N.; Bybee, R.T.; Mason, F.L.; Worsham, H.J.

1976-01-01

The invention pertains to an improved monitoring system for the neutron flux in a nuclear reactor. It is proposed to combine neutron flux detectors, a thermoelement, and a background radiation detector in one measuring unit. The spatial arrangement of these elements is fixed with great exactness; they are enclosed by an elastic cover and are brought into position in the reactor with the aid of a bent tube. The arrangement has a low failure rate and is easy to maintain. (HP) [de

15. Compact power reactor

International Nuclear Information System (INIS)

Wetch, J.R.; Dieckamp, H.M.; Wilson, L.A.

1978-01-01

There is disclosed a small compact nuclear reactor operating in the epithermal neutron energy range for supplying power at remote locations, as for a satellite. The core contains fuel moderator elements of Zr hydride with 7 w/o of 93% enriched uranium alloy. The core has a radial beryllium reflector and is cooled by liquid metal coolant such as NaK. The reactor is controlled and shut down by moving portions of the reflector

16. Reactor Neutron Sources

International Nuclear Information System (INIS)

Aksenov, V.L.

1994-01-01

The present status and the prospects for development of reactor neutron sources for neutron scattering research in the world are considered. The fields of application of neutron scattering relative to synchrotron radiation, the creation stages of reactors (steady state and pulsed) and their position in comparison with spallation neutron sources at present and in the foreseen future are discussed. (author). 15 refs.; 8 figs.; 3 tabs

17. Reactor pressure vessel design

International Nuclear Information System (INIS)

Foehl, J.

1998-01-01

As a result of the popularity of the Agencies report 'Neutron Irradiation Embrittlement of Reactor Pressure Vessel Steels' of 1975, it was decided that another report on this broad subject would be of use. In this report, background and contemporary views on specially identified areas of the subject are considered as self-contained chapters, written by experts. In chapter 2, the general principles of reactor pressure vessel design are elaborated. Crack and fracture initiation and propagation are treated in some detail

18. OECD Halden reactor project

International Nuclear Information System (INIS)

1978-01-01

This report summarizes the activities of the OECD Halden Reactor Project for the year 1976. The main items reported on are: a) the process supervision and control which have focused on core monitoring and control, and operator-process communication; b) the fuel performance and safety behavior which have provided data and analytical descriptions of the thermal, mechanical and chemical behavior of fuel under various operating conditions; c) the reactor operations and d) the administration and finance

19. Nuclear reactor container

International Nuclear Information System (INIS)

Hosaka, Seiichi.

1988-01-01

Cables coverd with non-halogen covering material are used as electric wire cables wired for supplying electric power to a reactor recycling pump. Silicone rubber having specified molecular formula is used for the non-halogen covering material. As a result, formation of chlorine in a nuclear reactor container can be eliminated and increase in the deposited salts to SUS pipeways, etc. can be prevented, to avoid the occurrence of stress corrosion cracks. (H.T.)

20. KS-150 reactor control

International Nuclear Information System (INIS)

Wagner, K.

1974-01-01

A thorough description is presented of the control and protection system of the Bohunice A-1 reactor. The system including auxiliary facilities was developed, manufactured and installed at the reactor by the SKODA Works, Plzen. The system parameters are listed and a brief account is also given of the development efforts and of the physical and power start-up of the A-1 nuclear power plant. (L.O.)

1. Department of Reactor Technology

DEFF Research Database (Denmark)

Risø National Laboratory, Roskilde

The general development of the Department of Reactor Technology at Risø during 1981 is presented, and the activities within the major subject fields are described in some detail. Lists of staff, publications, and computer programs are included.......The general development of the Department of Reactor Technology at Risø during 1981 is presented, and the activities within the major subject fields are described in some detail. Lists of staff, publications, and computer programs are included....

2. Generation IV reactors: economics

International Nuclear Information System (INIS)

Dupraz, B.; Bertel, E.

2003-01-01

The operating nuclear reactors were built over a short period: no more than 10 years and today their average age rounds 18 years. EDF (French electricity company) plans to renew its reactor park over a far longer period : 30 years from 2020 to 2050. According to EDF this objective implies 3 constraints: 1) a service life of 50 to 60 years for a significant part of the present operating reactors, 2) to be ready to built a generation 3+ unit in 2020 which infers the third constraint: 3) to launch the construction of an EPR (European pressurized reactor) prototype as soon as possible in order to have it operating in 2010. In this scheme, generation 4 reactor will benefit the feedback experience of generation 3 and will take over in 2030. Economic analysis is an important tool that has been used by the generation 4 international forum to select the likely future reactor systems. This analysis is based on 4 independent criteria: the basic construction cost, the construction time, the operation and maintenance costs and the fuel cycle cost. This analysis leads to the evaluation of the global cost of electricity generation and of the total investment required for each of the reactor system. The former defines the economic competitiveness in a de-regulated energy market while the latter is linked to the financial risk taken by the investor. It appears, within the limits of the assumptions and models used, that generation 4 reactors will be characterized by a better competitiveness and an equivalent financial risk when compared with the previous generation. (A.C.)

International Nuclear Information System (INIS)

Rice, P.D.

1991-01-01

This document describes some of the more significant accomplishments in the reactor restart program and details the magnitude and extent of the work completed to bring K-Reactor to a state of restart readiness. The discussion of restart achievements is organized into the three major categories of personnel, programs, and plant. Also presented is information on the scope and extent of internal and external oversight of the efforts, as well as some details on the startup plan

4. The replacement research reactor

International Nuclear Information System (INIS)

Cameron, R.; Horlock, K.

2001-01-01

The contract for the design, construction and commissioning of the Replacement Research Reactor was signed in July 2000. This was followed by the completion of the detailed design and an application for a construction licence was made in May 2001. This paper will describe the main elements of the design and their relation to the proposed applications of the reactor. The future stages in the project leading to full operation are also described

5. Fusion reactor materials

International Nuclear Information System (INIS)

Anon.

1977-01-01

The following topics are briefly discussed: (1) surface blistering studies on fusion reactor materials, (2) TFTR design support activities, (3) analysis of samples bombarded in-situ in PLT, (4) chemical sputtering effects, (5) modeling of surface behavior, (6) ion migration in glow discharge tube cathodes, (7) alloy development for irradiation performance, (8) dosimetry and damage analysis, and (9) development of tritium migration in fusion devices and reactors

6. OECD Halden reactor project

International Nuclear Information System (INIS)

1979-01-01

This is the nineteenth annual Report on the OECD Halden Reactor Project, describing activities at the Project during 1978, the last year of the 1976-1978 Halden Agreement. Work continued in two main fields: test fuel irradiation and fuel research, and computer-based process supervision and control. Project research on water reactor fuel focusses on various aspects of fuel behavior under normal, and off-normal transient conditions. In 1978, participating organisations continued to submit test fuel for irradiation in the Halden boiling heavy-water reactor, in instrumented test assemblies designed and manufactured by the Project. Work included analysis of the impact of fuel design and reactor operating conditions on fuel cladding behavior. Fuel performance modelling included characterization of thermal and mechanical behavior at high burn-up, of fuel failure modes, and improvement of data qualification procedures to reduce and quantify error bands on in-reactor measurements. Instrument development yielded new or improved designs for measuring rod temperature, internal pressure, axial neutron flux shape determination, and for detecting cladding defects. Work on computer-based methods of reactor supervision and control included continued development of a system for predictive core surveillance, and of special mathematical methods for core power distribution control

7. The reactor antineutrino anomalies

Energy Technology Data Exchange (ETDEWEB)

Haser, Julia; Buck, Christian; Lindner, Manfred [Max-Planck-Institut fuer Kernphysik, Heidelberg (Germany)

2016-07-01

Major discoveries were made in the past few years in the field of neutrino flavour oscillation. Nuclear reactors produce a clean and intense flux of electron antineutrinos and are thus an essential neutrino source for the determination of oscillation parameters. Most currently the reactor antineutrino experiments Double Chooz, Daya Bay and RENO have accomplished to measure θ{sub 13}, the smallest of the three-flavour mixing angles. In the course of these experiments two anomalies emerged: (1) the reanalysis of the reactor predictions revealed a deficit in experimentally observed antineutrino flux, known as the ''reactor antineutrino anomaly''. (2) The high precision of the latest generation of neutrino experiments resolved a spectral shape distortion relative to the expected energy spectra. Both puzzles are yet to be solved and triggered new experimental as well as theoretical studies, with the search for light sterile neutrinos as most popular explanation for the flux anomaly. This talk outlines the two reactor antineutrino anomalies. Discussing possible explanations for their occurrence, recent and upcoming efforts to solve the reactor puzzles are highlighted.

8. Fast breeder reactors

International Nuclear Information System (INIS)

Waltar, A.E.; Reynolds, A.B.

1981-01-01

This book describes the major design features of fast breeder reactors and the methods used for their design and analysis. The foremost objective of this book is to fulfill the need for a textbook on Fast Breeder Reactor (FBR) technology at the graduate level or the advanced undergraduate level. It is assumed that the reader has an introductory understanding of reactor theory, heat transfer, and fluid mechanics. The book is expected to be used most widely for a one-semester general course on fast breeder reactors, with the extent of material covered to vary according to the interest of the instructor. The book could also be used effectively for a two-quarter or a two-semester course. In addition, the book could serve as a text for a course on fast reactor safety since many topics other than those appearing in the safety chapters relate to FBR safety. Methodology in fast reactor design and analysis, together with physical descriptions of systems, is emphasized in this text more than numerical results. Analytical and design results continue to change with the ongoing evolution of FBR design whereas many design methods have remained fundamentally unchanged for a considerable time

9. Nuclear reactor buildings

International Nuclear Information System (INIS)

Nagashima, Shoji; Kato, Ryoichi.

1985-01-01

Purpose: To reduce the cost of reactor buildings and satisfy the severe seismic demands in tank type FBR type reactors. Constitution: In usual nuclear reactor buildings of a flat bottom embedding structure, the flat bottom is entirely embedded into the rock below the soils down to the deck level of the nuclear reactor. As a result, although the weight of the seismic structure can be decreased, the amount of excavating the cavity is significantly increased to inevitably increase the plant construction cost. Cross-like intersecting foundation mats are embedded to the building rock into a thickness capable withstanding to earthquakes while maintaining the arrangement of equipments around the reactor core in the nuclear buildings required by the system design, such as vertical relationship between the equipments, fuel exchange systems and sponteneous drainings. Since the rock is hard and less deformable, the rigidity of the walls and the support structures of the reactor buildings can be increased by the embedding into the rock substrate and floor responsivity can be reduced. This enables to reduce the cost and increasing the seismic proofness. (Kamimura, M.)

10. Molten salt reactors

International Nuclear Information System (INIS)

Bouchter, J.C.; Dufour, P.; Guidez, J.; Simon, N.; Renault, C.

2014-01-01

Molten salt reactors are one of the 6 concepts retained for the 4. generation of nuclear reactors. The principle of this reactor is very innovative: the nuclear fuel is dissolved in the coolant which allows the online reprocessing of the fuel and the online recovery of the fission products. A small prototype: the Molten Salt Reactor Experiment (MSRE - 8 MWt) was operating a few years in the sixties in the USA. The passage towards a fast reactor by the suppression of the graphite moderator leads to the concept of Molten Salt Fast Reactor (MSFR) which is presently studied through different European projects such as MOST, ALISIA and EVOL. Worldwide the main topics of research are: the adequate materials resisting to the high level of corrosiveness of the molten salts, fuel salt reprocessing, the 3-side coupling between neutron transport, thermohydraulics and thermo-chemistry, the management of the changing chemical composition of the salt, the enrichment of lithium with Li 7 in the case of the use of lithium fluoride salt and the use of MSFR using U 233 fuel (thorium cycle). The last part of the article presents a preliminary safety analysis of the MSFR. (A.C.)

11. Nuclear reactors to come

International Nuclear Information System (INIS)

Lung, M.

2002-01-01

The demand for nuclear energy will continue to grow at least till 2050 because of mainly 6 reasons: 1) the steady increase of the world population, 2) China, India and Indonesia will reach higher social standard and their energy consumption will consequently grow, 3) fossil energy resources are dwindling, 4) coal will be little by little banned because of its major contribution to the emission of green house effect gas, 5) renewable energies need important technological jumps to be really efficient and to take the lead, and 6) fusion energy is not yet ready to take over. All these reasons draw a promising future for nuclear energy. Today 450 nuclear reactors are operating throughout the world producing 17% of the total electrical power demand. In order to benefit fully of this future, nuclear industry has to improve some characteristics of reactors: 1) a more efficient use of uranium (it means higher burnups), 2) a simplification and automation of reprocessing-recycling chain of processes, 3) efficient measures against proliferation and against any misuse for terrorist purposes, and 4) an enhancement of safety for the next generation of reactors. The characteristics of fast reactors and of high-temperature reactors will likely make these kinds of reactors the best tools for energy production in the second half of this century. (A.C.)

12. Reactor operation method

International Nuclear Information System (INIS)

Osumi, Katsumi; Miki, Minoru.

1979-01-01

Purpose: To prevent stress corrosion cracks by decreasing the dissolved oxygen and hydrogen peroxide concentrations in the coolants within a reactor container upon transient operation such as at the start-up or shutdown of bwr type reactors. Method: After a condensate has been evacuated, deaeration operation is conducted while opening a main steam drain line, as well as a main steam separation valve and a by-pass valve in a turbine by-pass line connecting the main steam line and the condenser without by way of a turbine, and the reactor is started-up by the extraction of control rods after the concentration of dissolved oxygen in the cooling water within a pressure vessel has been decreased below a predetermined value. Nuclear heating is started after the reactor water has been increased to about 150 0 C by pump heating after the end of the deaeration operation for preventing the concentration of hydrogen peroxide and oxygen in the reactor water from temporarily increasing immediately after the start-up. The corrosive atmosphere in the reactor vessel can thus be moderated. (Horiuchi, T.)

13. LMFBR type reactor

International Nuclear Information System (INIS)

Masumi, Ryoji; Kawashima, Katsuyuki; Kurihara, Kunitoshi.

1988-01-01

Purpose: To flatten the power distribution while maintaining the flattening in the axial power distribution in LMFBR type reactors. Constitution: Main system control rods are divided into control rods used for the operation and starting rods used for the starting of the reactor, and the starting rods are disposed in the radial periphery of the reactor core, while the control rods are disposed to the inside of the starting rods. With such a constitution, adjusting rods can be disposed in the region where the radial power peaking is generated to facilitate the flattening of the power distribution even in such a design that the ratio of the number of control rods to that of fuel assemblies is relatively large. That is, in this reactor, the radial power peaking is reduced by about 10% as compared with the conventional reactor core. As a result, the maximum linear power density during operation is reduced by about 10% to increase the thermal margin of the reactor core. If the maximum linear power density is set identical, the number of the fuel assemblies can be decreased by about 10%, to thereby reduce the fuel production cost. (K.M.)

14. Operating US power reactors

International Nuclear Information System (INIS)

Silver, E.G.

1988-01-01

This update, which appears regularly in each issue of Nuclear Safety, surveys the operations of those power reactors in the US which have been issued operating licenses. Table 1 shows the number of such reactors and their net capacities as of September 30, 1987, the end of the three-month period covered in this report. Table 2 lists the unit capacity and forced outage rate for each licensed reactor for each of the three months (July, August, and September 1987) covered in this report and the cumulative values of these parameters since the beginning of commercial operation. In addition to the tabular data, this article discusses other significant occurrences and developments that affected licensed US power reactors during this reporting period. Status changes at Braidwood Unit 1, Nine Mile Point 2, and Beaver Valley 2 are discussed. Other occurrences discussed are: retraining of control-room operators at Peach Bottom; a request for 25% power for Shoreham, problems at Fermi 2 which delayed the request to go to 75% power; the results of a safety study of the N Reactor at Hanford; a proposed merger of Pacific Gas and Electric with Sacramento Municipal Utility District which would result in the decommissioning of Rancho Seco; the ordered shutdown of Oyster Creek; a minor radioactivity release caused by a steam generator tube rupture at North Anna 1; and 13 fines levied by the NRC on reactor licensees

15. Materials for fusion reactors

International Nuclear Information System (INIS)

Ehrlich, K.; Kaletta, D.

1978-03-01

The following report describes five papers which were given during the IMF seminar series summer 1977. The purpose of this series was to discuss especially the irradiation behaviour of materials intended for the first wall of future fusion reactors. The first paper deals with the basic understanding of plasma physics relating to the fusion reactor and presents the current state of art of fusion technology. The next two talks discuss the metals intended for the first wall and structural components of a fusion reactor. Since 14 MeV neutrons play an important part in the process of irradiation damage their role is discussed in detail. The question which machines are presently available to simulate irradiation damage under conditions similar to the ones found in a fusion reactor are investigated in the fourth talk which also presents the limitations of the different methods of simulation. In this context also discussed is the importance future intensive neutron sources and materials test reactors will have for this problem area. The closing paper has as a theme the review of the present status of research of metallic and non-metallic materials in view of the quite different requirements for different fusion systems; a closing topic is the world supply on rare materials required for fusion reactors. (orig) [de

16. Super critical water reactors

International Nuclear Information System (INIS)

Dumaz, P.; Antoni, O; Arnoux, P.; Bergeron, A; Renault, C.; Rimpault, G.

2005-01-01

Water is used as a calori-porter and moderator in the most major nuclear centers which are actually in function. In the pressurized water reactor (PWR) and boiling water reactor (BWR), water is maintained under critical point of water (21 bar, 374 Centigrade) which limits the efficiency of thermodynamic cycle of energy conversion (yield gain of about 33%) Crossing the critical point, one can then use s upercritical water , the obtained pressure and temperature allow a significant yield gains. In addition, the supercritical water offers important properties. Particularly there is no more possible coexistence between vapor and liquid. Therefore, we don't have more boiling problem, one of the phenomena which limits the specific power of PWR and BWR. Since 1950s, the reactor of supercritical water was the subject of studies more or less detailed but neglected. From the early 1990s, this type of conception benefits of some additional interests. Therefore, in the international term G eneration IV , the supercritical water reactors had been considered as one of the big options for study as Generation IV reactors. In the CEA, an active city has engaged from 1930 with the participation to a European program: The HPWR (High Performance Light Water Reactor). In this contest, the R and D studies are focused on the fields of neutrons, thermodynamic and materials. The CEA intends to pursue a limited effort of R and D in this field, in the framework of international cooperation, preferring the study of versions of rapid spectrum. (author)

17. LWR type reactor

International Nuclear Information System (INIS)

Kato, Kiyoshi.

1993-01-01

A water injection tank in an emergency reactor core cooling system is disposed at a position above a reactor pressure vessel. A liquid phase portion of the water injection tank and an inlet plenum portion in the reactor pressure vessel are connected by a water injection pipe. A gas phase portion of the water injection tank and an upper portion in the reactor pressure vessel are connected by a gas ventilation pipe. Hydraulic operation valves are disposed in the midway of the water injection pipe and the gas ventilation pipe respectively. A pressure conduit is disposed for connecting a discharge port of a main recycling pump and the hydraulic operation valve. In a case where primary coolants are not sent to the main recycling pump by lowering of a liquid level due to loss of coolants or in a case where the main recycling pump is stopped by electric power stoppage or occurrence of troubles, the discharge pressure of the main recycling pump is lowered. Then, the hydraulic operation valve is opened to release the flow channel, then, boric acid water in the water injection tank is sent into the reactor by a falling head, to lead the reactor to a scram state. (I.N.)

18. BWR type reactor

International Nuclear Information System (INIS)

Watanabe, Shoichi

1988-01-01

Purpose: To inhibit the lowering of the neutron moderation effect due to voids in the upper portion of the reactor core, thereby flatten the axial power distribution. Constitution: Although it has been proposed to enlarge the diameter at the upper portion of a water rod thereby increasing the moderator in the upper portion, since the water rod situates within the channel box, the increase in the capacity thereof is has certain limit. In the present invention, it is designed such that the volume of the region at the outside of the channel box for the fuel assembly to which non-boiling water in the non-boiling water region can enter is made greater in the upper portion than in the lower portion of the reactor core. Thus, if the moderator density in the upper portion of the reactor core should be decreased due to the generation of the voids, the neutron moderating effect in the upper portion of the reactor core is not lowered as compared with the lower portion of the reactor core and, accordingly, the axial power distribution can be flattening more as compared with that in the conventional nuclear reactors. (Takahashi, M.)

19. Reactor core structure

International Nuclear Information System (INIS)

Higashinakagawa, Emiko; Sato, Kanemitsu.

1992-01-01

Taking notice on the fact that Fe based alloys and Ni based alloys are corrosion resistant in a special atmosphere of a nuclear reactor, Fe or Ni based alloys are applied to reactor core structural components such as fuel cladding tubes, fuel channels, spacers, etc. On the other hand, the neutron absorption cross section of zirconium is 0.18 barn while that of iron is 2.52 barn and that of nickel is 4.6 barn, which amounts to 14 to 25 times compared with that of zirconium. Accordingly, if the reactor core structural components are constituted by the Fe or Ni based alloys, neutron economy is lowered. Since it is desirable that neutrons contribute to uranium fission with least absorption to the reactor core structural components, the reactor core structural components are constituted with the Fe or Ni based alloys of good corrosion resistance only at a portion in contact with reactor water, that is, at a surface portion, while the main body is constituted with zircalloy in the present invention. Accordingly, corrosion resistnace can be kept while keeping small neutron absorption cross section. (T.M.)

20. Nuclear reactor monitoring device

International Nuclear Information System (INIS)

Mihashi, Ishi; Honma, Hitoshi.

1993-01-01

The monitoring device of the present invention comprises a reactor core/reactor system data measuring and controlling device, a radioactivity concentration calculation device for activated coolants for calculating a radioactivity concentration of activated coolants in a main steam and reactor water by using an appropriate physical model, a radioactivity concentration correlation and comparison device for activated coolants for comparing correlationship with a radiation dose and an abnormality alarm device. Since radioactivity of activated primary coolants is monitored at each of positions in the reactor system and occurrence of leakage and the amount thereof from a primary circuit to a secondary circuit is monitored if the reactor has secondary circuit, integrity of the reactor system can be ensured and an abnormality can be detected rapidly. Further, radioactivity concentration of activated primary circuit coolants, represented by 16 N or 15 C, is always monitored at each of positions of PWR primary circuits. When a heat transfer pipe is ruptured in a steam generator, leakage of primary circuit coolants is detected rapidly, as well as the amount of the leakage can be informed. (N.H.)

1. Oklo natural reactor

International Nuclear Information System (INIS)

Fujii, Isao

1985-01-01

In 1954, Professor Kazuo, Kuroda of Arkansas University in USA published the possibility that spontaneously generated natural nuclear reactors existed in prehistoric age. In 1972, 18 years after that, Commissariat a l'Energie Atomique published that in the Oklo uranium deposit in Gabon, Africa, a natural nuclear reactor was found. This fact was immediately informed to the whole world, but in Japan, its details have not necessarily been well known. The chance of investigating into this fact and visiting the Oklo deposit by the favor of COMUF, the owner of the Oklo deposit, was given, therefore, the state of the natural reactors, which has been known so far, is reported. At present, 12 natural reactors have been found in the vicinity of the Oklo deposit. The natural reactors were generated spontaneously in uranium deposits about 1.7 billion years ago when the isotopic abundance of U-235 was 3 %, and the chain reaction started naturally. When the concentration of U-235 lowered, the reaction stopped naturally. The abnormality in the U-235 abundance in natural uranium was found, and the cause was pursued. The evidence of the existence of natural reactors was shown. (Kako, I.)

International Nuclear Information System (INIS)

Till, C.E.

1989-01-01

Consideration is given to what the aims of advanced reactor development have to be, if a new generation of nuclear power is really to play an important role in man's energy generation activities in a fragile environment. The background given briefly covers present atmospheric evidence, the current situation in nuclear power, how reactors work and what can go wrong with them, and the present magnitudes of world energy generation. The central part of the paper describes what is currently being done in advanced reactor development and what can be expected from various systems and various elements of it. A vigorous case is made that three elements must be present in any advanced reactor development: (1) breeding; (2) passive safety; and (3) shorter-live nuclear waste. All three are possible. In the right advanced reactor systems the ways of achieving them are known. But R and D is necessary. That is the central argument made in the paper. Not advanced reactor prototype construction at this point, but R and D itself. (author)

3. Licensing of nuclear reactor operators

International Nuclear Information System (INIS)

1979-09-01

Recommendations are presented for the licensing of nuclear reactor operators in units licensed according to the legislation in effect. They apply to all physical persons designated by the Operating Organization of the nuclear reactor or reactors to execute any of the following functional activities: a) to manipulate the controls of a definite reactor b) to direct the authorized activities of the reactor operators licesed according to the present recommendations. (F.E.) [pt

4. Reactor of the XXI century

International Nuclear Information System (INIS)

Zhotabaev, Zh.R.; Solov'ev, Yu.A.

2001-01-01

The advantages of both molten salt reactors (MSR) and homogenous molten salt reactors (HMSR) are illuminated. It is noted that the MSR possess accident probability A=10 -6 1/reactor.years and the HMSR with integral configuration has A=10 -7 1/reactor.years. The methods for these reactors technological problems solution - tritium removal, salt melt circulation and capacity pick up - are discussed

5. Regulations for RA reactor operation

International Nuclear Information System (INIS)

1980-09-01

Regulations for RA reactor operation are written in accordance with the legal regulations defined by the Law about radiation protection and related legal acts, as well as technical standards according to the IAEA recommendations. The contents of this book include: fundamental data about the reactor; legal regulations for reactor operation; organizational scheme for reactor operation; general and detailed instructions for operation, behaviour in the reactor building, performing experiments; operating rules for operation under steady state and accidental conditions [sr

6. Research reactor`s role in Korea

Energy Technology Data Exchange (ETDEWEB)

Choi, C-O [Korea Atomic Energy Research Inst., Taejon (Korea, Republic of)

1996-12-31

After a TRIGA MARK-II was constructed in 1962, new research activity of a general nature, utilizing neutrons, prevailed in Korea. Radioisotopes produced from the MARK-II played a good role in the 1960`s in educating people as to what could be achieved by a neutron source. Because the research reactor had implanted neutron science in the country, another TRIGA MARK-III had to be constructed within 10 years after importing the first reactor, due to increased neutron demand from the nuclear community. With the sudden growth of nuclear power, however, the emphasis of research changed. For a while research activities were almost all oriented to nuclear power plant technology. However, the specifics of nuclear power plant technology created a need for a more highly capable research reactor like HANARO 30MWt. HANARO will perform well with irradiation testing and other nuclear programs in the future, including: production of key radioisotopes, doping of silicon by transmutation, neutron activation analysis, neutron beam experiments, cold neutron source. 3 tabs., 2 figs.

7. Nuclear reactor construction with bottom supported reactor vessel

International Nuclear Information System (INIS)

Sharbaugh, J.E.

1987-01-01

This patent describes an improved liquid metal nuclear reactor construction comprising: (a) a nuclear reactor core having a bottom platform support structure; (b) a reactor vessel for holding a large pool of low pressure liquid metal coolant and housing the core; (c) a containment structure surrounding the reactor vessel and having a sidewall spaced outwardly from the reactor vessel side wall and having a base mat spaced below the reactor vessel bottom end wall; (d) a central small diameter post anchored to the containment structure base mat and extending upwardly to the reactor vessel to axially fix the bottom end wall of the reactor vessel and provide a center column support for the lower end of the reactor core; (e) annular support structure disposed in the reactor vessel on the bottom end wall and extending about the lower end of the core; (f) structural support means disposed between the containment structure base mat and bottom end of the reactor vessel wall and cooperating for supporting the reactor vessel at its bottom end wall on the containment structure base mat to allow the reactor vessel to expand radially but substantially prevent any lateral motions that might be imposed by the occurrence of a seismic event; (g) a bed of insulating material disposed between the containment structure base mat and the bottom end wall of the reactor vessel and uniformly supporting the reactor vessel at its bottom end wall; freely expand radially from the central post as it heats up while providing continuous support thereof; (h) a deck supported upon the wall of the containment vessel above the top open end of the reactor vessel; and (i) extendible and retractable coupling means extending between the deck and the top open end of the reactor vessel and flexibly and sealably interconnecting the reactor vessel at its top end to the deck

8. The reactor Cabri

International Nuclear Information System (INIS)

Ailloud, J.; Millot, J.P.

1964-01-01

It has become necessary to construct in France a reactor which would permit the investigation of the conditions of functioning of future installations, the choice, the testing and the development of safety devices to be adopted. A water reactor of a type corresponding to the latest CEA constructions in the field of laboratory or university reactors was decided upon: it appeared important to be able to evaluate the risks entailed and to study the possibilities of increasing the power, always demanded by the users; on the other hand, it is particularly interesting to clarify the phenomena of power oscillation and the risks of burn out. The work programme for CABRI will be associated with the work carried out on the American Sperts of the same type, during its construction, very useful contacts were made with the American specialists who designed the se reactors. A brief description of the reactor is given in the communication as well as the work programme for the first years with respect to the objectives up to now envisaged. Rough description of the reactor. CABRI is an open core swimming-pool reactor without any lateral protection, housed in a reinforced building with controlled leakage, in the Centre d'Etudes Nucleaires de Cadarache. It lies alone in the middle of an area whose radius is 300 meters long. Control and measurements equipment stand out on the edge of that zone. It consumes MTR fuel elements. The control-safety rods are propelled by compressed air. The maximum flow rate of cooling circuit is 1500 m 3 /h. Transient measurements are recorded in a RW330 unit. Aims and work programme. CABRI is meant for: - studies on the safety of water reactors - for the definition of the safety margins under working conditions: research of maximum power at which a swimming-pool reactor may operate with respect to a cooling accident, of local boiling effect on the nuclear behaviour of the reactor, performances of the control and safety instruments under exceptional

9. Materials for nuclear reactors

International Nuclear Information System (INIS)

Banerjee, S.; Kamath, H.S.

2005-01-01

10. REACTOR GROUT THERMAL PROPERTIES

Energy Technology Data Exchange (ETDEWEB)

Steimke, J.; Qureshi, Z.; Restivo, M.; Guerrero, H.

2011-01-28

Savannah River Site has five dormant nuclear production reactors. Long term disposition will require filling some reactor buildings with grout up to ground level. Portland cement based grout will be used to fill the buildings with the exception of some reactor tanks. Some reactor tanks contain significant quantities of aluminum which could react with Portland cement based grout to form hydrogen. Hydrogen production is a safety concern and gas generation could also compromise the structural integrity of the grout pour. Therefore, it was necessary to develop a non-Portland cement grout to fill reactors that contain significant quantities of aluminum. Grouts generate heat when they set, so the potential exists for large temperature increases in a large pour, which could compromise the integrity of the pour. The primary purpose of the testing reported here was to measure heat of hydration, specific heat, thermal conductivity and density of various reactor grouts under consideration so that these properties could be used to model transient heat transfer for different pouring strategies. A secondary purpose was to make qualitative judgments of grout pourability and hardened strength. Some reactor grout formulations were unacceptable because they generated too much heat, or started setting too fast, or required too long to harden or were too weak. The formulation called 102H had the best combination of characteristics. It is a Calcium Alumino-Sulfate grout that contains Ciment Fondu (calcium aluminate cement), Plaster of Paris (calcium sulfate hemihydrate), sand, Class F fly ash, boric acid and small quantities of additives. This composition afforded about ten hours of working time. Heat release began at 12 hours and was complete by 24 hours. The adiabatic temperature rise was 54 C which was within specification. The final product was hard and displayed no visible segregation. The density and maximum particle size were within specification.

11. Fast breeder reactor research

International Nuclear Information System (INIS)

1975-01-01

Full text: The meeting was attended by 15 participants from seven countries and two international organizations. The Eighth Annual Meeting of the International Working Group on Fast Reactors (IWGFR) was attended by representatives from France, Fed. Rep. Germany, Italy, Japan, United Kingdom, Union of Soviet Socialist Republics and the United States of America - countries that have made significant progress in developing the technology and physics of sodium cooled fast reactors and have extensive national programmes in this field - as well as by representatives of the Commission of the European Communities and the IAEA. The design of fast-reactor power plants is a more difficult task than developing facilities with thermal reactors. Different reactor kinetics and dynamics, a hard neutron spectrum, larger integral doses of fuel and structural material irradiation, higher core temperatures, the use of an essentially novel coolant, and, as a result of all these factors, the additional reliability and safety requirements that are imposed on the planning and operation of sodium cooled fast reactors - all these factors pose problems that can be solved comprehensively only by countries with a high level of scientific and technical development. The exchange of experience between these countries and their combined efforts in solving the fundamental problems that arise in planning, constructing and operating fast reactors are promoting technical progress and reducing the relative expenditure required for various studies on developing and introducing commercial fast reactors. For this reason, the meeting concentrated on reviewing and discussing national fast reactor programmes. The situation with regard to planning, constructing and operating fast experimental and demonstration reactors in the countries concerned, the experience accumulated in operating them, the difficulties arising during operation and ways of over-coming them, the search for optimal designs for the power

12. Method of operating a reactor

International Nuclear Information System (INIS)

Oosumi, Katsumi; Yamamoto, Michiyoshi.

1980-01-01

Purpose: To prevent stress corrosion cracking in the structural material of a reactor pressure vessel. Method: Prior to the starting of a reactor, the reactor pressure vessel is evacuated to carry out degassing of reactor water, and, at the same time, reactor water is heated. After reactor water is heated to a predetermined temperature, control rods are extracted to start nuclear heating. While the temperature of the reactor water is in a temperature range where elution of a metal which is a structural material of the reactor pressure vessel becomes vigorous and the sensitivity to the stress corrosion cracks increases, the reactor is operated at the maximum permissible temperature raising speed or maximum permissible cooling speed. (Aizawa, K.)

13. Spectral shift reactor control method

International Nuclear Information System (INIS)

Impink, A.J.

1982-01-01

A method of operating a nuclear reactor having a core and coolant displacer elements arranged in the core where there is established a reactor coolant temperature set point at which it is desired to operate the reactor and first reactor coolant temperature band limits within which the set point is characterized. The reactor coolant displacer elements are moved relative to the reactor core for adjusting the volume of reactor coolant in the core as the reactor coolant temperature approaches the first band limits to maintain the reactor coolant temperature near the set point and within the first band limits. The reactivity charges associated with movement of respective coolant displacer element clusters is calculated and compared with a calculated derived reactivity charge in order to select the cluster to be moved. (author)

14. BR2 Reactor: Introduction

International Nuclear Information System (INIS)

Moons, F.

2007-01-01

The irradiations in the BR2 reactor are in collaboration with or at the request of third parties such as the European Commission, the IAEA, research centres and utilities, reactor vendors or fuel manufacturers. The reactor also contributes significantly to the production of radioisotopes for medical and industrial applications, to neutron silicon doping for the semiconductor industry and to scientific irradiations for universities. Along the ongoing programmes on fuel and materials development, several new irradiation devices are in use or in design. Amongst others a loop providing enhanced cooling for novel materials testing reactor fuel, a device for high temperature gas cooled fuel as well as a rig for the irradiation of metallurgical samples in a Pb-Bi environment. A full scale 3-D heterogeneous model of BR2 is available. The model describes the real hyperbolic arrangement of the reactor and includes the detailed 3-D space dependent distribution of the isotopic fuel depletion in the fuel elements. The model is validated on the reactivity measurements of several tens of BR2 operation cycles. The accurate calculations of the axial and radial distributions of the poisoning of the beryllium matrix by 3 He, 6 Li and 3T are verified on the measured reactivity losses used to predict the reactivity behavior for the coming decades. The model calculates the main functionals in reactor physics like: conventional thermal and equivalent fission neutron fluxes, number of displacements per atom, fission rate, thermal power characteristics as heat flux and linear power density, neutron/gamma heating, determination of the fission energy deposited in fuel plates/rods, neutron multiplication factor and fuel burn-up. For each reactor irradiation project, a detailed geometry model of the experimental device and of its neighborhood is developed. Neutron fluxes are predicted within approximately 10 percent in comparison with the dosimetry measurements. Fission rate, heat flux and

15. Thermohydraulics of reactors

International Nuclear Information System (INIS)

Delhaye, J.M.

2008-01-01

This scientific and technical handbook about PWR reactors thermohydraulics is the result of many years of teaching in the framework of the CEA-INSTN's atomic engineering training courses, in engineering schools and during continuing training activities. Its main goal is to present in a rigorous and pedagogical way the basic knowledge necessary for the understanding and modeling of single phase and two-phase thermohydraulic phenomena encountered during the design and operation of nuclear reactors. In particular, heat transfers in two-phase flows are presented in a detailed way. Most chapters include some nuclear engineering examples of application of the studied concepts, and some exercises aiming at mastering these concepts. Each example or exercise is accompanied by its detailed solution. Content: - thermohydraulic characteristics of reactors; - design and thermal dimensioning of reactors; - thermal engineering of the fuel element; - two-phase flow configurations in ducts; - recalls about single-phase flow equations; - basic equations for two-phase flows; - modeling of two-phase flows inside ducts; - pressure drops in ducts; - boiling and vapor condensation heat transfers; - two-phase flow instabilities in ducts; - two-phase flow blocking; thermohydraulics of naval propulsion reactors

16. Pressure tube reactor

International Nuclear Information System (INIS)

Seki, Osamu; Kumasaka, Katsuyuki.

1988-01-01

Purpose: To remove the heat of reactor core using a great amount of moderators at the periphery of the reactor core as coolants. Constitution: Heat of a reactor core is removed by disposing a spontaneous recycling cooling device for cooling moderators in a moderator tank, without using additional power driven equipments. That is, a spontaneous recycling cooling device for cooling the moderators in the moderator tank is disposed. Further, the gap between the inner wall of a pressure tube guide pipe disposed through the vertical direction of a moderator tank and the outer wall of a pressure tube inserted through the guide pipe is made smaller than the rupture distortion caused by the thermal expansion upon overheating of the pressure tube and greater than the minimum gap required for heat shiels between the pressure tube and the pressure tube guide pipe during usual operation. In this way, even if such an accident as can not using a coolant cooling device comprising power driven equipment should occur in the pressure tube type reactor, the rise in the temperature of the reactor core can be retarded to obtain a margin with time. (Kamimura, M.)

17. BWR type reactors

International Nuclear Information System (INIS)

Hayashi, Katsuhisa; Watanabe, Shigeru.

1983-01-01

Purpose: To simplify the structure of control rod driving systems, as well as improve the safety and maintainability thereof. Constitution: Control-rod-guide tubes are disposed vertically above the reactor core and control-rod drives are disposed further thereabove, by which the control rods are moved upwardly and downwardly from above the reactor core through the guide tubes. Further, a partitioning cylinder is provided between the inner cirumferential wall at the upper portion of a pressure vessel and the control-rod-guide tubes and a gas-liquid separator is disposed to the space between the partitioning cylinder and the pressure vessel wall, to which steams generated in the reactor core are introduced. In such a structure of the reactor, since all of the control rods are inserted or extracted by the control rod drive system from above the reactor core, if the control rod drives or the likes should fail and accidentally drop the control rods, they exert in the direction of suppressing the nuclear reaction, whereby the safety can be improved. (Sekiya, K.)

18. Reactor core control device

International Nuclear Information System (INIS)

Sano, Hiroki

1998-01-01

The present invention provides a reactor core control device, in which switching from a manual operation to an automatic operation, and the control for the parameter of an automatic operation device are facilitated. Namely, the hysteresis of the control for the operation parameter by an manual operation input means is stored. The hysteresis of the control for the operation parameter is collected. The state of the reactor core simulated by an operation control to which the collected operation parameters are manually inputted is determined as an input of the reactor core state to the automatic input means. The record of operation upon manual operation is stored as a hysteresis of control for the operation parameter, but the hysteresis information is not only the result of manual operation of the operation parameter. This is results of operation conducted by a skilled operator who judge the state of the reactor core to be optimum. Accordingly, it involves information relevant to the reactor core state. Then, it is considered that the optimum automatic operation is not deviated greatly from the manual operation. (I.S.)

19. Fusion reactor fuel processing

International Nuclear Information System (INIS)

Johnson, E.F.

1972-06-01

For thermonuclear power reactors based on the continuous fusion of deuterium and tritium the principal fuel processing problems occur in maintaining desired compositions in the primary fuel cycled through the reactor, in the recovery of tritium bred in the blanket surrounding the reactor, and in the prevention of tritium loss to the environment. Since all fuel recycled through the reactor must be cooled to cryogenic conditions for reinjection into the reactor, cryogenic fractional distillation is a likely process for controlling the primary fuel stream composition. Another practical possibility is the permeation of the hydrogen isotopes through thin metal membranes. The removal of tritium from the ash discharged from the power system would be accomplished by chemical procedures to assure physiologically safe concentration levels. The recovery process for tritium from the breeder blanket depends on the nature of the blanket fluids. For molten lithium the only practicable possibility appears to be permeation from the liquid phase. For molten salts the process would involve stripping with inert gas followed by chemical recovery. In either case extremely low concentrations of tritium in the melts would be desirable to maintain low tritium inventories, and to minimize escape of tritium through unwanted permeation, and to avoid embrittlement of metal walls. 21 refs

20. Gas-cooled reactors

International Nuclear Information System (INIS)

Schulten, R.; Trauger, D.B.

1976-01-01

Experience to date with operation of high-temperature gas-cooled reactors has been quite favorable. Despite problems in completion of construction and startup, three high-temperature gas-cooled reactor (HTGR) units have operated well. The Windscale Advanced Gas-Cooled Reactor (AGR) in the United Kingdom has had an excellent operating history, and initial operation of commercial AGRs shows them to be satisfactory. The latter reactors provide direct experience in scale-up from the Windscale experiment to fullscale commercial units. The Colorado Fort St. Vrain 330-MWe prototype helium-cooled HTGR is now in the approach-to-power phase while the 300-MWe Pebble Bed THTR prototype in the Federal Republic of Germany is scheduled for completion of construction by late 1978. THTR will be the first nuclear power plant which uses a dry cooling tower. Fuel reprocessing and refabrication have been developed in the laboratory and are now entering a pilot-plant scale development. Several commercial HTGR power station orders were placed in the U.S. prior to 1975 with similar plans for stations in the FRG. However, the combined effects of inflation, reduced electric power demand, regulatory uncertainties, and pricing problems led to cancellation of the 12 reactors which were in various stages of planning, design, and licensing

1. International breeder reactor development

International Nuclear Information System (INIS)

Traube, K.

1976-01-01

For more than a decade, sodium cooled breeder reactors have now been in the focus of advanced nuclear power development in the major industrialized countries. In the sixties, a total of seven small experimental nuclear power stations were commissioned. Two of these have been shut down in the meantime, the others continue to work satisfactorily, their main purpose being the development of fuel elements. The years 1972-1974 saw the commissioning of the prototype power stations in the 300 MWe power category in France, the United Kingdom and the Soviet Union. Presently, other experimental reactors are under construction in the Federal Republic of Germany, Italy, Japan, the United States, plus another Soviet 600 MWe prototype reactor and the SNR 300 DeBeNeLux prototype at Kalkar. A comparison of the technological features either implemented or planned in the prototype and experimental power plants and of their fuel elements reveals a remarkable similarity in the basic concepts pursued in different countries. The two types of breeder reactors, viz. the loop and the pool types, show a closer resemblance to each other than do pressurized and boilling water reactors. The growing awareness of administrative problems emerging in the approaching phase of the introduction of large breeder power stations in a number of European countries has recently led to a streamlining effort in the structure of industries and to tentative steps towards international cooperation on a broad basis. (orig.) [de

International Nuclear Information System (INIS)

Balagi, V.

2005-01-01

Detection and measurement of radiation plays a vital role in nuclear reactors from the point of view of control and safety, personnel protection and process control applications. Various types of radiation are measured over a wide range of intensity. Consequently a variety of detectors find use in nuclear reactors. Some of these devices have been developed in Electronics Division. They include gas-filled detectors such as 10 B-lined proportional counters and chambers, fission detectors and BF 3 counters are used for the measurement of neutron flux both for reactor control and safety, process control as well as health physics instrumentation. In-core neutron flux instrumentation employs the use detectors such as miniature fission detectors and self-powered detectors. In this development effort, several indigenous materials, technologies and innovations have been employed to suit the specific requirement of nuclear reactor applications. This has particular significance in view of the fact that several new types of reactors such as P-4, PWR and AHWR critical facilities, FBTR, PFBR as well as the refurbishment of old units like CIRUS are being developed. The development work has sought to overcome some difficulties associated with the non-availability of isotopically enriched neutron-sensing materials, achieving all-welded construction etc. The present paper describes some of these innovations and performance results. (author)

3. PWR type reactor plant

International Nuclear Information System (INIS)

Matsuoka, Tsuyoshi.

1993-01-01

A water chamber of a horizontal U-shaped pipe type steam generator is partitioned to an upper high temperature water chamber portion and a lower low temperature water chamber portion. An exit nozzle of a reactor container containing a reactor core therein is connected to a suction port of a coolant pump by way of first high temperature pipelines. The exit port of the coolant pump is connected to the high temperature water chamber portion of the steam generator by way of second high temperature pipelines. The low temperature water chamber portion of the steam generator is connected to an inlet nozzle of the reactor container by way of the low temperature pipelines. The low temperature water chamber portion of the steam generator is positioned lower than the high temperature water chamber portion, but upper than the reactor core. Accordingly, all of the steam generator for a primary coolant system, coolant pumps as well as high temperature pipelines and low temperature pipelines connecting them are disposed above the reactor core. With such a constitution, there is no worry of interrupting core cooling even upon occurrence of an accident, to improve plant safety. (I.N.)

4. Power reactor noise

International Nuclear Information System (INIS)

Thie, J.A.

1981-01-01

This book concentrates on the different types of noise present in power reactors and how the analysis of this noise can be used as a tool for reactor monitoring and diagnostics. Noise analysis is a growing field that offers advantages such as simplicity, low cost, and natural multivariable interactions. A major advantage, continuous and undisturbed monitoring, supplies a means of obtaining early warnings of possible reactor malfunctions thus preventing further complications by alerting operators to a problem - and aiding in the diagnosis of that problem - before it demands major repairs. Following an introductory chapter, the theoretical basis for the various methods of noise analysis is explained, and full chapters are devoted to the fundamentals of statistics for time-domain analysis and Fourier series and related topics for frequency-domain analysis. General experimental techniques and associated theoretical considerations are reviewed, leading to discussion of practical applications in the latter half of the book. Besides chapters giving examples of neutron noise and acoustical noise, chapters are also devoted to extensive examples from pressurized water reactor and boiling water reactor power plants

International Nuclear Information System (INIS)

Jaouen, C.; Beroux, P.

2012-01-01

From Zoe, the first nuclear reactor, till the current EPR, the French nuclear industry has always advanced by profiting from the feedback from dozens of years of experience and operations, in particular by drawing lessons from the most significant events in its history, such as the Fukushima accident. The new generations of reactors must improve safety and economic performance so that the industry maintain its legitimacy and its share in the production of electricity. This article draws the history of nuclear power in France, gives a brief description of the pressurized water reactor design, lists the technical features of the different versions of PWR that operate in France and compares them with other types of reactors. The feedback experience concerning safety, learnt from the major nuclear accidents Three Miles Island (1979), Chernobyl (1986) and Fukushima (2011) is also detailed. Today there are 26 third generation reactors being built in the world: 4 EPR (1 in Finland, 1 in France and 2 in China); 2 VVER-1200 in Russia, 8 AP-1000 (4 in China and 4 in the Usa), 8 APR-1400 (4 in Korea and 4 in UAE), and 4 ABWR (2 in Japan and 2 in Taiwan)

6. Reactor protecting device

International Nuclear Information System (INIS)

Ono, Hiroshi; Kasuga, Hajime; Kasuga, Hiroshi.

1984-01-01

Purpose: To reduce the recycling flowrate thereby decrease the neutron flux level before the reactor shutdown upon generation of abnormality such as increase in the neutron flux, by setting the safety level lower than the value for generating the reaction scram signal. Constitution: A netron flux safety level setter and an instruction signal generator are disposed between a neutron flux detector and a recycling flowrate control device. A neutron flux safety level lower than the level for generating a reactor scram signal and higher that the level for the ordinary operation is set and, if the detection level for the neutron flux in the reactor core arrives at the safety level, a neutron flux decreasing instruction signal is outputted from the instruction signal generator to the recycling flowrate control device to thereby decrease the recycling flowrate and decrease the neutron flux without reaching the reactor shutdown, whereby the thermal safety of the fuel rod can be maintained and the reactor operation performance can be improved. (Moriyama, K.)

7. Nuclear reactor apparatus

International Nuclear Information System (INIS)

Braun, H.E.; Bonnet, H.P.

1978-01-01

The reactor and its containment, instead of being supported on a solid concrete pad, are supported on a truss formed of upper and lower reinforced horizontal plates and vertical walls integrated into a rigid structure. The plates and walls from chambers within which the auxiliary components of the reactor, such as valves, pumping equipment and various tanks, are disposed. Certain of the chambers are also access passages for personnel, pipe chases, valve chambers and the like. In particular the truss includes an annular chamber. This chamber is lined and sealed by a corrosion-resistant liner and contains coolant and serves as a refueling cooling storage tank. This tank is directly below the primary-coolant conductor loops which extend from the reactor above the upper plate. The upper plate includes a sump connected to the tank through which coolant flows into the tank in the event of the occurrence of a loss-of-coolant accident. The truss extends beyond the containment and has chambers in the extending annulus. Pumps for circulating the coolant between the refueling coolant storage tank and the reactor are provided in certain of these chambers. The pumps are connected to the reactor by relatively short coolant conductors. Access to these pumps is readily afforded through hatches in the extending annulus

8. Reactor container spray device

International Nuclear Information System (INIS)

Yanai, Ryoichi.

1980-01-01

Purpose: To enable decrease in the heat and the concentration of radioactive iodine released from the reactor vessel into the reactor container in the spray device of BWR type reactors. Constitution: A plurality of water receiving trays are disposed below the spray nozzle in the dry well and communicated to a pressure suppression chamber by way of drain pipeways passing through a diaphragm floor. When the recycling system is ruptured and coolants in the reactor vessel and radioactive iodine in the reactor core are released into the dry well, spray water is discharged from the spray nozzle to eliminate the heat and the radioactive iodine in the dry well. In this case, the receiving trays collect the portions of spray water whose absorption power for the heat and radioactive iodine is nearly saturated and falls them into the pool water of the pressure suppression chamber. Consequently, other portions of the spray water that still possess absorption power can be jetted with no hindrance, to increase the efficiency for the removal of the heat and iodine of the spray droplets. (Horiuchi, T.)

9. Reactor containing facility

International Nuclear Information System (INIS)

Akagawa, Katsuhiko.

1992-01-01

A cooling space having a predetermined capacity is formed between a reactor container and concrete walls. A circulation loop disposed to the outside of the concrete walls is connected to the top and the bottom of the cooling space. The circulation loop has a circulation pump and a heat exchanger, and a cooling water supply pipe is connected to the upstream of the circulation pump for introducing cooling water from the outside. Upon occurrence of loss of coolant accident, cooling water is introduced from the cooling water supply pipe to the cooling space between the reactor container and the concrete walls after shut-down of the reactor operation. Then, cooling water is circulated while being cooled by the heat exchanger, to cool the reactor container by cooling water flown in the cooling space. This can cool the reactor container in a short period of time upon occurrence of the loss of coolant accident. Accordingly, a repairing operation for a ruptured portion can be conducted rapidly. (I.N.)

10. Mirror reactor studies

International Nuclear Information System (INIS)

Moir, R.W.; Barr, W.L.; Bender, D.J.

1976-01-01

Design studies of a fusion mirror reactor, a fusion-fission mirror reactor, and two small mirror reactors are summarized. The fusion reactor uses 150-keV neutral-beam injectors based on the acceleration of negative ions. The injectors provide over 1 GW of continuous power at an efficiency greater than 80 percent. The fusion reactor has three-stage, modularized, Venetian blind, plasma direct converter with a predicted efficiency of 59 percent and a new concept for removal of the lune-shaped blanket: a crane is brought between the two halves of the Yin-Yang magnet, which are separated by a float. The design has desirable features such as steady-state operation, minimal impurity problems, and low first-wall thermal stress. The major disadvantage is low Q resulting in high recirculating power and hence high cost of electrical power. However, the direct capital cost per unit of gross electrical power is reasonable [\$1000/kW(e)

11. Reactor physics computations

International Nuclear Information System (INIS)

Shapiro, A.

1977-01-01

Those reactor-core calculations which provide the effective multiplication factor (or eigenvalue) and the stationary (or fundamental mode) neutron-flux distribution at selected times during the lifetime of the core are considered. The multiplication factor is required to establish the nuclear composition and configuration which satisfy criticality and control requirements. The steady-state flux distribution must be known to calculate reaction rates and power distributions which are needed for the thermal, mechanical and shielding design of the reactor, as well as for evaluating refueling requirements. The calculational methods and techniques used for evaluating the nuclear design information vary with the type of reactor and with the preferences and prejudices of the reactor-physics group responsible for the calculation. Additionally, new methods and techniques are continually being developed and made operational. This results in a rather large conglomeration of methods and computer codes which are available for reactor analysis. The author provides the basic calculational framework and discusses the more prominent techniques which have evolved. (Auth.)

12. Reactor shutdown device

International Nuclear Information System (INIS)

Matsumiya, Hirohito; Endo, Hiroshi; Tsuboi, Yasushi.

1993-01-01

The present invention concerns a reactor shutdown device capable of suppressing change of a core insertion amount relative to temperature change during normal operation and having a great extension amount due to thermal expansion and high mechanical strength. A control rod main body is contained vertically movably in a guide tube disposed in a reactor core. An extension member extends upward from the upper end of a control rod main body and suspends the control rod main body. A shrinkable member intervenes at a midway of the extension member and is made shrinkable. A temperature sensitive member contains coolants at the inside and surrounds the shrinkable member. Thus, if the temperature of external coolants rises abruptly, the shrinkable member is extended by thermal expansion of the coolants in the temperature sensitive member. Upon usual reactor startup, the coolants in the temperature sensitive member cause no substantial thermal expansion by temperature elevation from a cold shutdown temperature to a rated power operation temperature, and the shrinkable member maintains its original state, so that the control rod main body is not inserted into the reactor core. However, upon abrupt temperature elevation, the control rod main body is inserted into the reactor core. (I.S.)

13. FBR type reactors

International Nuclear Information System (INIS)

Maemoto, Junko.

1985-01-01

Purpose: To moderate abrupt temperature change near the inner walls of a suspended body thereby prevent thermal shocks and thermal deformations to structural materials. Constitution: High temperature coolants during ordinary operation of the nuclear reactor flow from the reactor core through the flow holes of the suspended body and from the upper plenum into an intermediate heat exchanger. The temperature of the coolants is lowered with heat exchanging effect with secondary coolants in the heat exchange and the coolants are then flow through the lower plenum into the reactor core and heated again. Upon generation of reactor scram, the temperature of the coolants at the exit of the reactor core is reduced abruptly and the flow rate is lowered due to the pump coast down. However, mixing of the coolants in the suspended body is accelerated by the coolants at high temperature flowing out of the flow holes and the coolants at the low temperature flowing from the flow hole group, to reduce the temperature difference and moderate the stratification flow forming an abrupt temperature slope. (Yoshihara, H.)

14. BWR type nuclear reactors

International Nuclear Information System (INIS)

Yamamoto, Toru.

1987-01-01

Purpose: To obtain reactor core characteristics with less changes in the excess reactivity due to fuel burnup even when the operation period varies. Constitution: In a BWR type reactor where fuel assemblies containing fuel rods incorporated with burnable poisons are arranged, the fuel assemblies are grouped into first fuel assemblies and second fuel assemblies. Then, the number of fuel rods incorporated with burnable poisons within the first fuel assemblies is made greater than that of the second fuel rods, while the concentration of the burnable poisons in the fuel rods incorporated with the burnable poisons in the first fuel assemblies is made lower than that of the fuel rods incorporated with the burnable poisons in the second fuel assemblies. In the BWR type reactor constituted in this way, the reactor core characteristics can be improved by changing the ratio between the first fuel assemblies and the second fuel assemblies charged to the reactor core, thereby decreasing the changes in the burnup of the excess reactivity. (Kamimura, M.)

15. Reactor Structural Materials: Reactor Pressure Vessel Steels

International Nuclear Information System (INIS)

2000-01-01

The objectives of SCK-CEN's R and D programme on Rector Pressure Vessel (RPV) Steels are:(1) to complete the fracture toughness data bank of various reactor pressure vessel steels by using precracked Charpy specimens that were tested statically as well as dynamically; (2) to implement the enhanced surveillance approach in a user-friendly software; (3) to improve the existing reconstitution technology by reducing the input energy (short cycle welding) and modifying the stud geometry. Progress and achievements in 1999 are reported

16. Research and materials irradiation reactors

International Nuclear Information System (INIS)

Ballagny, A.; Guigon, B.

2004-01-01

Devoted to the fundamental and applied research on materials irradiation, research reactors are nuclear installations where high neutrons flux are maintained. After a general presentation of the research reactors in the world and more specifically in France, this document presents the heavy water cooled reactors and the water cooled reactors. The third part explains the technical characteristics, thermal power, neutron flux, operating and details the Osiris, the RHF (high flux reactor), the Orphee and the Jules Horowitz reactors. The last part deals with the possible utilizations. (A.L.B.)

17. RB research reactor Safety Report

International Nuclear Information System (INIS)

Sotic, O.; Pesic, M.; Vranic, S.

1979-04-01

This RB reactor safety report is a revised and improved version of the Safety report written in 1962. It contains descriptions of: reactor building, reactor hall, control room, laboratories, reactor components, reactor control system, heavy water loop, neutron source, safety system, dosimetry system, alarm system, neutron converter, experimental channels. Safety aspects of the reactor operation include analyses of accident causes, errors during operation, measures for preventing uncontrolled activity changes, analysis of the maximum possible accident in case of different core configurations with natural uranium, slightly and highly enriched fuel; influence of possible seismic events

18. Mimic of OSU research reactor

International Nuclear Information System (INIS)

Lu, Hong; Miller, D.W.

1991-01-01

The Ohio State University research reactor (OSURR) is undergoing improvements in its research and educational capabilities. A computer-based digital data acquisition system, including a reactor system mimic, will be installed as part of these improvements. The system will monitor the reactor system parameters available to the reactor operator either in digital parameters available to the reactor operator either in digital or analog form. The system includes two computers. All the signals are sent to computer 1, which processes the data and sends the data through a serial port to computer 2 with a video graphics array VGA monitor, which is utilized to display the mimic system of the reactor

19. Nuclear reactor containment device

International Nuclear Information System (INIS)

1980-01-01

Purpose: To reduce the volume of a containment shell and decrease the size of a containment equipment for BWR type reactors by connecting the containment shell and a suppression pool with slanted vent tubes to thereby shorten the vent tubes. Constitution: A pressure vessel containing a reactor core is installed at the center of a building and a containment vessel for the nuclear reactor that contains the pressure vessel forms a cabin. To a building situated below the containment shell, is provided a suppression chamber in which cooling water is charged to form a suppression pool. The suppression pool is communicated with vent tubes that pass through the partition wall of the containment vessel. The vent tubes are slanted and their lower openings are immersed in coolants. Therefore, if accident is resulted and fluid at high temperature and high pressure is jetted from the pressure vessel, the jetting fluid is injected and condensated in the cooling water. (Moriyama, K.)

20. Nuclear reactor container

International Nuclear Information System (INIS)

Ishiyama, Takenori.

1989-01-01

This invention concerns a nuclear reactor container in which heat is removed from a container by external water injection. Heat is removed from the container by immersing the lower portion of the container into water and scattering spary water from above. Thus, the container can be cooled by the spray water falling down along the outer wall of the container to condensate and cool vapors filled in the container upon occurrence of accidents. Further, since the inside of the container can be cooled also during usual operation, it can also serve as a dry well cooler. Accordingly, heat is removed from the reactor container upon occurrence of accidents by the automatic operation of a spray device corresponding to the change of the internal temperature and the pressure in the reactor container. Further, since all of these devices are disposed out of container, maintenance is also facilitated. (I.S.)

1. Evaluation of reactor safety

Energy Technology Data Exchange (ETDEWEB)

NONE

1960-04-15

Although the operation of nuclear reactors has a remarkably good record of safety, the prevention of possible reactor accidents is one of the major factors that atomic planners have to contend with. At the same time, excessive caution may breed an attitude that hampers progress, either by resisting new development or by demanding unnecessarily elaborate and expensive precautions out of proportion to the actual hazards involved. The best course obviously is to determine the possible dangers and adopt adequate measures for their prevention, providing of course, for a reasonable margin of error in judging the hazards and the effectiveness of the measures. The greater the expert understanding and thoroughness with which this is done, the narrower need the margin be. This is the basic idea behind the evaluation of reactor safety

2. International Thermonuclear Experimental Reactor

International Nuclear Information System (INIS)

1989-09-01

An international design team comprised of members from Canada, Europe, Japan, the Soviet Union, and the United States of America, are designing an experimental fusion test reactor. The engineering and testing objectives of this International Thermonuclear Experimental Reactor (ITER) are to validate the design and to demonstrate controlled ignition, extended burn of a deuterium and tritium plasma, and achieve steady state using technology expected to be available by 1990. The concept maximizes flexibility while allowing for a variety of plasma configurations and operating scenarios. During physics phase operation, the machine produces a 22 MA plasma current. In the technology phase, the machine can be reconfigured with a thicker shield and a breeding blanket to operate with an 18 MA plasma current at a major radius of 5.5 meters. Canada's involvement in the areas of safety, facility design, reactor configuration and maintenance builds on our internationally recognized design and operational expertise in developing tritium processes and CANDU related technologies

3. Fusion reactor problems

International Nuclear Information System (INIS)

Carruthers, R.

It is pointed out that plasma parameters for a fusion reactor have been fairly accurately defined for many years, and the real plasma physics objective must be to find the means of achieving and maintaining these specifiable parameters. There is good understanding of the generic technological problems: breading blankets and shields, radiation damage, heat transfer and methods of magnet design. The required plasma parameters for fusion self-heated reactors are established at ntausub(E) approximately 2.10 14 cm -3 sec, plasma radius 1.5 to 3 m, wall loading 5 to 10 MW cm -2 , temperature 15 keV. Within this model plasma control by quasi-steady burn as a key problem is studied. It is emphasized that the future programme must interact more closely with engineering studies and should concentrate upon research which is relevant to reactor plasmas. (V.P.)

4. The nuclear reactor systems

International Nuclear Information System (INIS)

Bacher, P.

2008-01-01

This paper describes the various nuclear reactor systems, starting with the Generation II, then the present development of the Generation III and the stakes and challenges of the future Generation IV. Some have found appropriate to oppose reactor systems or generations one to another, especially by minimizing the enhancements of generation III compared to generation II or by expecting the earth from generation IV (meaning that generation III is already obsolete). In the first part of the document (chapter 2), some keys are given to the reader to develop its proper opinion. Chapter 3 describes more precisely the various reactor systems and generations. Chapter 4 discusses the large industrial manoeuvres around the generation III, and the last chapter gives some economical references, taking into account, for the various means of power generation, the impediments linked to climate protection

5. Nuclear Rocket Engine Reactor

CERN Document Server

Lanin, Anatoly

2013-01-01

The development of a nuclear rocket engine reactor (NRER ) is presented in this book. The working capacity of an active zone NRER under mechanical and thermal load, intensive neutron fluxes, high energy generation (up to 30 MBT/l) in a working medium (hydrogen) at temperatures up to 3100 K is displayed. Design principles and bearing capacity of reactors area discussed on the basis of simulation experiments and test data of a prototype reactor. Property data of dense constructional, porous thermal insulating and fuel materials like carbide and uranium carbide compounds in the temperatures interval 300 - 3000 K are presented. Technological aspects of strength and thermal strength resistance of materials are considered. The design procedure of possible emergency processes in the NRER is developed and risks for their origination are evaluated. Prospects of the NRER development for pilotless space devices and piloted interplanetary ships are viewed.

International Nuclear Information System (INIS)

1989-08-01

THE OPERATING UNITS STATUS REPORT - LICENSED OPERATING REACTORS provides data on the operation of nuclear units as timely and accurately as possible. This information is collected by the Office of Information Resources Management from the Headquarters staff of NRC's Office of Enforcement (OE), from NRC's Regional Offices, and from utilities. The three sections of the report are: monthly highlights and statistics for commercial operating units, and errata from previously reported data; a compilation of detailed information on each unit, provided by NRC's Regional Offices, OE Headquarters and the utilities; and an appendix for miscellaneous information such as spent fuel storage capability, reactor-years of experience and non-power reactors in the US

7. Reactor lattice codes

International Nuclear Information System (INIS)

Kulikowska, T.

1999-01-01

The present lecture has a main goal to show how the transport lattice calculations are realised in a standard computer code. This is illustrated on the example of the WIMSD code, belonging to the most popular tools for reactor calculations. Most of the approaches discussed here can be easily modified to any other lattice code. The description of the code assumes the basic knowledge of reactor lattice, on the level given in the lecture on 'Reactor lattice transport calculations'. For more advanced explanation of the WIMSD code the reader is directed to the detailed descriptions of the code cited in References. The discussion of the methods and models included in the code is followed by the generally used homogenisation procedure and several numerical examples of discrepancies in calculated multiplication factors based on different sources of library data. (author)

8. Breazeale Reactor Modernization Program

International Nuclear Information System (INIS)

Davison, C. C.

2003-01-01

The Penn State Breazeale Nuclear Reactor is the longest operating licensed research reactor in the nation. The facility has played a key role in educating scientists, engineers and in providing facilities and services to researchers in many different disciplines. In order to remain a viable and effective research and educational institution, a multi-phase modernization project was proposed. Phase I was the replacement of the 25-year old reactor control and safety system along with associated wiring and hardware. This phase was fully funded by non-federal funds. Tasks identified in Phases II-V expand upon and complement the work done in Phase I to strategically implement state-of-the-art technologies focusing on identified national needs and priorities of the future

9. Reactor for exothermic reactions

Science.gov (United States)

Smith, L.A. Jr.; Hearn, D.; Jones, E.M. Jr.

1993-03-02

A liquid phase process is described for oligomerization of C[sub 4] and C[sub 5] isoolefins or the etherification thereof with C[sub 1] to C[sub 6] alcohols wherein the reactants are contacted in a reactor with a fixed bed acid cation exchange resin catalyst at an LHSV of 5 to 20, pressure of 0 to 400 psig and temperature of 120 to 300 F. Wherein the improvement is the operation of the reactor at a pressure to maintain the reaction mixture at its boiling point whereby at least a portion but less than all of the reaction mixture is vaporized. By operating at the boiling point and allowing a portion of the reaction mixture to vaporize, the exothermic heat of reaction is dissipated by the formation of more boil up and the temperature in the reactor is controlled.

10. FBR type reactor

International Nuclear Information System (INIS)

Inoue, Kotaro; Kawashima, Katsuyuki; Zuketen, Atsushi.

1982-01-01

Purpose: To flatten the power distribution of a reactor core and shorten the breeding time. Constitution: The reactor core comprises a core region having fission products, an outer blanket region surrounding the outer side of the core region and having fertile material and an inner blanket region disposed within the core region and having fertile material. The axial thickness of the inner blanket region is made greater at the central portion and smaller at the peripheral portion of the inner blanket region, and the outermost peripheral end at the peripheral portion of the inner blanket region is opposed by way of the core region to the outer blanket region. In such an arrangement, the power decrease in the peripheral portion of the core region can be suppressed to thereby flatten the power distribution in the reactor core and shorten the breeding time. (Moriyama, K.)

11. Reactor control device

International Nuclear Information System (INIS)

Araki, Takao; Inoue, Toyokazu.

1981-01-01

Purpose: To protect the reactor floor by alleviating the shock imparted to the reactor floor by a dropped control rod when a wire rope accidentally breaks. Constitution: A control rod is hung by wire rope from a control rod drive, and shock absorbers are mounted at the upper and lower portions of the control rod. The outer diameter of the upper shock absorber is made larger than the inner diameter of a control rod inserting hole formed in the reactor core. If the control rod drops, the upper absorber is stopped at the upper tapered portion of the inserting hole. Thus, the dropping energy of the control rod can be sufficiently absorbed by the upper and lower shock absorbers. (Kamimura, M.)

12. Reactor container facility

International Nuclear Information System (INIS)

Saito, Takashi; Nagasaka, Hideo.

1990-01-01

A dry-well pool for spontaneously circulating stored pool water and a suppression pool for flooding a pressure vessel by feeding water, when required, to a flooding gap by means of spontaneous falling upto the flooding position, thereby flooding the pressure vessel are contained at the inside of a reactor container. Thus, when loss of coolant accidents such as caused by main pipe rupture accidents should happen, pool water in the suppression pool is supplied to the flooding gap by spontaneously falling. Further, if the flooding water uprises exceeding a predetermined level, the flooding gap is in communication with the dry-well pool at the upper and the lower portions respectively. Accordingly, flooding water at high temperature heated by the after-heat of the reactor core is returned again into the flooding gap to cool the reactor core repeatedly. (T.M.)

13. Compact stellarators as reactors

International Nuclear Information System (INIS)

Lyon, J.F.; Valanju, P.; Zarnstorff, M.C.; Hirshman, S.; Spong, D.A.; Strickler, D.; Williamson, D.E.; Ware, A.

2001-01-01

Two types of compact stellarators are examined as reactors: two- and three-field-period (M=2 and 3) quasi-axisymmetric devices with volume-average =4-5% and M=2 and 3 quasi-poloidal devices with =10-15%. These low-aspect-ratio stellarator-tokamak hybrids differ from conventional stellarators in their use of the plasma-generated bootstrap current to supplement the poloidal field from external coils. Using the ARIES-AT model with B max =12T on the coils gives Compact Stellarator reactors with R=7.3-8.2m, a factor of 2-3 smaller R than other stellarator reactors for the same assumptions, and neutron wall loadings up to 3.7MWm -2 . (author)

14. Utilization of research reactors

International Nuclear Information System (INIS)

1962-01-01

About 200 research reactors are now in operation in different parts of the world, and at least 70 such facilities, which are in advanced stages of planning and construction, should be critical within the next two or three years. In the process of this development a multitude of problems are being encountered in formulating and carrying out programs for the proper utilization of these facilities, especially in countries which have just begun or are starting their atomic energy work. An opportunity for scientific personnel from different Member States to discuss research reactor problems was given at an international symposium on the Programing and Utilization of Research Reactors organized by the Agency almost immediately after the General Conference session. Two hundred scientists from 35 countries, as well as from the European Nuclear Energy Agency and EURATOM, attended the meeting which was held in Vienna from 16 to 21 October 1961

15. Emergency reactor shutdown device

International Nuclear Information System (INIS)

Ikehara, Morihiko.

1982-01-01

Purpose: To smoothen the emergency operation of the control rod in a BWR type reactor and to eliminate the external discharge of radioactively contaminated water. Constitution: A drain receiving tank is connected through a scram valve to the top of a cylinder which is containing a hydraulic piston connected to a trombone-shaped control rod and an accumulator is connected through another scram valve to the bottom of the cylinder. The respective scram valves are constructed to be opened by the reactor emergency shutdown signal from a reactor control system in such a manner that drain valve and a vent valve of the tank normally opened at the standby time are closed after approx. 10 seconds from the opening of the scram valves. In this manner, back pressure is not applied to the hydraulic piston at the emergency time, thereby smoothly operating the control rod. (Sikiya, K.)

16. Reactor utilization; Eksploatacija reaktora

Energy Technology Data Exchange (ETDEWEB)

Zecevic, V [Institute of Nuclear Sciences Boris Kidric, Reaktor RA, Vinca, Beograd (Serbia and Montenegro)

1963-02-15

In 1962, the RA reactor was operated almost three times more than in 1961, producing total of 25 555 MWh. Diagram containing comparative data about reactor operation for 1960, 1961, and 1962, percent of fuel used and U-235 burnup shows increase in reactor operation. Number of samples irradiated was 659, number of experiments done was 16. mean powered level was 5.93 MW. Fuel was added into the core twice during the reporting year. In fact the core was increased from 56 to 68 fuel channels and later to 84 fuel channels. Fuel was added to the core when the reactivity worth decreased to the minimum operation level due to burnup. In addition to this 5 central fuel channels were exchanged with fresh fuel in february for the purpose of irradiation in the VISA-2 channel.

International Nuclear Information System (INIS)

1990-01-01

The US Nuclear Regulatory Commission's monthly LICENSED OPERATING REACTORS Status Summary Report provides data on the operation of nuclear units as timely and accurately as possible. This information is collected by the Office of Information Resources Management, from the Headquarters Staff of NRC's Office of Inspection and Enforcement, from NRC's Regional Offices, and from utilities. This report is divided into three sections: the first contains monthly highlights and statistics for commercial operating units, and errata from previously reported data; the second is a compilation of detailed information on each unit, provided by NRC Regional Offices, IE Headquarters and the Utilities; and the third section is an appendix for miscellaneous information such as spent fuel storage capability, reactor years of experience and non-power reactors in the United States

18. Reactor safety analysis

International Nuclear Information System (INIS)

Arien, B.

1998-01-01

Risk assessments of nuclear installations require accurate safety and reliability analyses to estimate the consequences of accidental events and their probability of occurrence. The objective of the work performed in this field at the Belgian Nuclear Research Centre SCK-CEN is to develop expertise in probabilistic and deterministic reactor safety analysis. The four main activities of the research project on reactor safety analysis are: (1) the development of software for the reliable analysis of large systems; (2) the development of an expert system for the aid to diagnosis; (3) the development and the application of a probabilistic reactor-dynamics method, and (4) to participate in the international PHEBUS-FP programme for severe accidents. Progress in research during 1997 is described

19. Reactor protection system

International Nuclear Information System (INIS)

Fairbrother, D.B.; Lesniak, L.M.; Orgera, E.G.

1977-10-01

The report describes the reactor protection system (RPS-II) designed for use on Babcock and Wilcox 145-, later 177-, and 205-fuel assembly pressurized water reactors. In this system, relays in the trip logic have been replaced by solid state devices. A calculating module for the low DNBR, pump status, and offset trip functions has replaced the overpower trip (based on flow and imbalance), the power/RC pump trip, and the variable low-pressure trip. Included is a description of the changes from the present Oconee-type reactor protection system (RPS-I), a functional and hardware description of the calculating module, a description of the software programmed in the calculating module, and a discussion of the qualification program conducted to ensure that the degree of protection provided by RPS-II is not less than that provided by previously licensed systems supplied by B and W

20. Nuclear reactor refueling system

International Nuclear Information System (INIS)

1978-01-01

A system for transferring fuel assemblies between a nuclear reactor core and a fuel storage area while the fuel assembies remain completely submerged in a continuous body of coolant is described. The system comprises an in-vessel fuel transfer machine located inside the reactor vessel and an ex-vessel fuel transfer machine located in a fuel storage tank. The in-vessel fuel transfer machine comprises two independently rotatable frames with a pivotable fuel transfer apparatus disposed on the lower rotatable frame. The ex-vessel fuel transfer machine comprises one frame with a pivotable fuel transfer apparatus disposed thereon. The pivotable apparatuses are capable of being aligned with each other to transfer a fuel assembly between the reactor vessel and fuel storage tank while the fuel assembly remains completely submerged in a continuous body of coolant. 9 claims, 7 figures

1. Heat dissipating nuclear reactor

Science.gov (United States)

Hunsbedt, A.; Lazarus, J.D.

1985-11-21

Disclosed is a nuclear reactor containment adapted to retain and cool core debris in the unlikely event of a core meltdown and subsequent breach in the reactor vessel. The reactor vessel is seated in a cavity which has a thick metal sidewall that is integral with a thick metal basemat at the bottom of the cavity. The basemat extends beyond the perimeter of the cavity sidewall. Underneath the basemat is a porous bed with water pipes and steam pipes running into it. Water is introduced into the bed and converted into steam which is vented to the atmosphere. A plurality of metal pilings in the form of H-beams extend from the metal base plate downwardly and outwardly into the earth.

International Nuclear Information System (INIS)

Hartfield, R.A.

1990-03-01

The US Nuclear Regulatory Commission's monthly Licensed Operating Reactors Status Summary Report provides data on the operation of nuclear units as timely and accurately as possible. This information is collected by the Office of Information Resources Management, from the Headquarters Staff of NRC's Office of Inspection and Enforcement, from NRC's Regional Offices, and from utilities. This report is divided into three sections: the first contains monthly highlights and statistics for commercial operating units, and errata from previously reported data; the second is a compilation of detailed information on each unit, provided by NRC Regional Offices, IE Headquarters and the Utilities; and the third section is an appendix for miscellaneous information such as spent fuel storage capability, reactor years of experience and non-power reactors in the United States

3. Reactor control device

International Nuclear Information System (INIS)

Kameda, Akiyuki.

1979-01-01

Purpose: To enable three types of controls, that is, level control, scram control and excess reactivity control required for a reactor by a same mechanism by feeding neutron absorber liquid and pressure control gas to several blind pipes provided in the reactor core. Constitution: A plurality of blind pipes are disposed spaced apart in a reactor core and connected by way of injection pipes to a neutron absorber liquid tank. A pressure regulator is connected to the blind pipes, to which pressure control gas is supplied. The neutron absorber liquid used herein consists of sodium, potassium or their alloy, or mercury as a basic substance incorporated with one or more selected from boron, tantalum, rhenium, europium or their compounds. The level control, scram control and excess reactivity control can be attained by moderating the pressure changes in the pressure control gas or by regulating the fluctuation in the liquid level. (Horiughi, T.)

4. Fusion reactor materials

International Nuclear Information System (INIS)

Rowcliffe, A.F.; Burn, G.L.; Knee', S.S.; Dowker, C.L.

1994-02-01

This is the fifteenth in a series of semiannual technical progress reports on fusion reactor materials. This report combines research and development activities which were previously reported separately in the following progress reports: Alloy Development for Irradiation Performance; Damage Analysis and Fundamental Studies; Special purpose Materials. These activities are concerned principally with the effects of the neutronic and chemical environment on the properties and performance of reactor materials; together they form one element of the overall materials programs being conducted in support of the Magnetic Fusion Energy Program of the U.S. Department of Energy. The Fusion Reactor Materials Program is a national effort involving several national laboratories, universities, and industries. The purpose of this series of reports is to provide a working technical record for the use of the program participants, and to provide a means of communicating the efforts of materials scientists to the rest of the fusion community, both nationally and worldwide

5. BWR type reactor system

International Nuclear Information System (INIS)

Morooka, Shin-ichi.

1980-01-01

Purpose: To reduce the internal structure in a reactor by rapidly and efficiently transferring heat generated in a reactor core out of the reactor and eliminating the danger of radiation exposure. Constitution: Steam generated in a pressure vessel is introduced into heat pipe group by inserting the heat pipe group into the steam dome of the pressure vessel. The introduced steam is condensed in the heat pipes to transfer the heat of the steam to the heat pipe group. The transferred heat is transmitted to a heat exchanger provided out of a containment vessel to generate steam to operate a turbine. Thus, it is not necessary to introduce the steam including radioactive substance externally and can remove only the heat so as to carry out the desired purpose. (Kamimura, M.)

6. Reactor coolant cleanup device

International Nuclear Information System (INIS)

Igarashi, Noboru.

1986-01-01

Purpose: To enable to introduce reactor water at high temperature and high pressure as it is, as well as effectively adsorb to eliminate cobalt in reactor water. Constitution: The coolant cleanup device comprises a vessel main body inserted to coolant pipeway circuits in a water cooled reactor power plant and filters contained within the vessel main body. The filters are prepared by coating and baking powder of metal oxides such as manganese ferrite having a function capable of adsorbing cobalt in the coolants onto the surface of supports made of metals or ceramics resistant to strong acids and alkalies in the form of three-dimensional network structure, for example, zircaloy-2, SUS 303 and the zirconia (baking) to form a basic filter elements. The basic filter elements are charged in plurality to the vessel main body. (Kawaiami, Y.)

7. The fast breeder reactor

International Nuclear Information System (INIS)

Keck, O.

1984-01-01

Nowadays the fast-breeder reactor is a negative symbol of advanced technology which is getting out of control and, due to its complexity, is incomprehensible for politicians and therefore by-passes the established order. The author lists the most important decisions over state aid to the fast-breeder-reactors up until the mid-seventies and uses documents from the appropriate advisory bodies as reference. He was also aided by interviews with those directly involved with the project. The empirical facts forces us to discard our traditional view of the relationship between state and industry with regard to advanced technology. The author explains that it is impossible to find any economic value in the fast-breeder reactor. The insight gained through this project allows him to draw conclusions which apply to all aspects of state aid to advanced technology. (orig.) [de

8. Backfitting swimming pool reactors

International Nuclear Information System (INIS)

Roebert, G.A.

1978-01-01

Calculations based on measurements in a critical assembly, and experiments to disclose fuel element surface temperatures in case of accidents like stopping of primary coolant flow during full power operation, have shown that the power of the swimming pool type research reactor FRG-2 (15 MW, operating since 1967) might be raised to 21 MW within the present rules of science and technology, without major alterations of the pool buildings and the cooling systems. A backfitting program is carried through to adjust the reactor control systems of FRG-2 and FRG-1 (5 MW, housed in the same reactor hall) to the present safety rules and recommendations, to ensure FRG-2 operation at 21 MW for the next decade. (author)

International Nuclear Information System (INIS)

1989-08-01

The US Nuclear Regulatory Commission's monthly LICENSED OPERATING REACTORS Status Summary Report provides data on the operation of nuclear units as timely and accurately as possible. This information is collected by the Office of Information Resources Management, from the Headquarters Staff of NRC's Office of Inspection and Enforcement, from NRC's Regional Offices, and from utilities. This report is divided into three sections: the first contains monthly highlights and statistics for commercial operating units, and errata from previously reported data; the second is a compilation of detailed information on each unit, provided by NRC Regional Offices, IE Headquarters and the utilities; and the third section is an appendix for miscellaneous information such as spent fuel storage capability, reactor years of experience and non-power reactors in the United States

10. Plasma core reactor applications

International Nuclear Information System (INIS)

Latham, T.S.; Rodgers, R.J.

1976-01-01

Analytical and experimental investigations are being conducted to demonstrate the feasibility of fissioning uranium plasma core reactors and to characterize space and terrestrial applications for such reactors. Uranium hexafluoride (UF 6 ) fuel is injected into core cavities and confined away from the surface by argon buffer gas injected tangentially from the peripheral walls. Power, in the form of thermal radiation emitted from the high-temperature nuclear fuel, is transmitted through fused-silica transparent walls to working fluids which flow in axial channels embedded in segments of the cavity walls. Radiant heat transfer calculations were performed for a six-cavity reactor configuration; each cavity is approximately 1 m in diameter by 4.35 m in length. Axial working fluid channels are located along a fraction of each cavity peripheral wall

11. Natural convection type reactor

International Nuclear Information System (INIS)

Nakayama, Takafumi; Horiuchi, Tetsuo; Moriya, Kimiaki; Matsumoto, Masayoshi; Akita, Minoru.

1988-01-01

Purpose: To improve the reliability by decreasing the number of dynamic equipments and safely shutdown the reactor core upon occurrence of accidents. Constitution: A pressure relief valve and a pressurizing tank or gravitational water falling tank disposed to the main steam pipe of a reactor are installed in combination. Upon loss-of-coolant accident, the pressure relief valve is opened to reduce the pressure in the reactor pressure vessel to the operation pressure for each of the tanks, thereby enabling to inject water in the pressurizing tank at first and, thereafter, water in the gravitational water falling tank successively to the inside of the pressure vessel. By utilizing the natural force in this way, the reliability can be improved as compared with the case of pumped water injection. Further, by injecting an aqueous boric acid to a portion of a plurality of tanks, if the control rod insertion becomes impossible, aqueous boric acid can be injected. (Takahashi, M.)

12. Reactor fuel charging equipment

International Nuclear Information System (INIS)

1977-01-01

In many types of reactor fuel charging equipment, tongs or a grab, attached to a trolley, housed in a guide duct, can be used for withdrawing from the core a selected spent fuel assembly or to place a new fuel assembly in the core. In these facilities, the trolley may have wheels that roll on rails in the guide duct. This ensures the correct alignment of the grab, the trolley and fuel assembly when this fuel assembly is being moved. By raising or lowering such a fuel assembly, the trolley can be immerged in the coolant bath of the reactor, whereas at other times it can be at a certain level above the upper surface of the coolant bath. The main object of the invention is to create a fuel handling apparatus for a sodium cooled reactor with bearings lubricated by the sodium coolant and in which the contamination of these bearings is prevented [fr

13. Chernobyl reactor accident

International Nuclear Information System (INIS)

Malinauskas, A.P.; Buchanan, J.R.; Lorenz, R.A.; Yamashita, T.

1986-01-01

On April 26, 1986, an explosion occurred at the newest of four operating nuclear reactors at the Chernobyl site in the USSR. The accident initiated an international technical exchange of almost unprecedented magnitude; this exchange was climaxed with a meeting at the International Atomic Energy Agency in Vienna during the week of August 25, 1986. The meeting was attended by more than 540 official representatives from 51 countries and 20 international organizations. Information gleaned from that technical exchange is presented in this report. A description of the Chernobyl reactor, which differs significantly from commercial US reactors, is presented, the accident scenario advanced by the Russian delegation is discussed, and observations that have been made concerning fission product release are described

14. Reactor power distribution monitor

International Nuclear Information System (INIS)

Hoizumi, Atsushi.

1986-01-01

Purpose: To grasp the margin for the limit value of the power distribution peaking factor inside the reactor under operation by using the reactor power distribution monitor. Constitution: The monitor is composed of the 'constant' file, (to store in-reactor power distributions obtained from analysis), TIP and thermocouple, lateral output distribution calibrating apparatus, axial output distribution synthesizer and peaking factor synthesizer. The lateral output distribution calibrating apparatus is used to make calibration by comparing the power distribution obtained from the thermocouples to the power distribution obtained from the TIP, and then to provide the power distribution lateral peaking factors. The axial output distribution synthesizer provides the power distribution axial peaking factors in accordance with the signals from the out-pile neutron flux detector. These axial and lateral power peaking factors are synthesized with high precision in the three-dimensional format and can be monitored at any time. (Kamimura, M.)

15. Reactor lattice codes

International Nuclear Information System (INIS)

Kulikowska, T.

2001-01-01

The description of reactor lattice codes is carried out on the example of the WIMSD-5B code. The WIMS code in its various version is the most recognised lattice code. It is used in all parts of the world for calculations of research and power reactors. The version WIMSD-5B is distributed free of charge by NEA Data Bank. The description of its main features given in the present lecture follows the aspects defined previously for lattice calculations in the lecture on Reactor Lattice Transport Calculations. The spatial models are described, and the approach to the energy treatment is given. Finally the specific algorithm applied in fuel depletion calculations is outlined. (author)

16. Technology of nuclear reactors

International Nuclear Information System (INIS)

Ravelet, F.

2016-01-01

This academic report for graduation in engineering first presents operation principles of a nuclear reactor core. It presents core components, atomic nuclei, the notions of transmutation and radioactivity, quantities used to characterize ionizing radiations, the nuclear fission, statistical aspects of fission and differences between fast and slow neutrons, a comparison between various heat transfer fluids, the uranium enrichment process, and different types of reactor (boiling water, natural uranium and heavy water, pressurized water, and fourth generation). Then, after having recalled the French installed power, the author proposes an analysis of a typical 900 MWe nuclear power plant: primary circuit, reactor, fuel, spent fuel, pressurizer and primary pump, secondary circuit, aspects related to control-command, regulation, safety and exploitation. The last part proposes a modelling of the thermodynamic cycle of a pressurized water plant by using an equivalent Carnot cycle, a Rankine cycle, and a two-phase expansion cycle with drying-overheating

17. AREVA's nuclear reactors portfolio

International Nuclear Information System (INIS)

Marincic, A.

2009-01-01

A reasonable assumption for the estimated new build market for the next 25 years is over 340 GWe net. The number of prospect countries is growing almost each day. To address this new build market, AREVA is developing a comprehensive portfolio of reactors intended to meet a wide range of power requirements and of technology choices. The EPR reactor is the flagship of the fleet. Intended for large power requirements, the four first EPRs are being built in Finland, France and China. Other countries and customers are in view, citing just two examples: the Usa where the U.S. EPR has been selected as the technology of choice by several U.S utilities; and the United Kingdom where the Generic Design Acceptance process of the EPR design submitted by AREVA and EDF is well under way, and where there is a strong will to have a plant on line in 2017. For medium power ranges, the AREVA portfolio includes a boiling water reactor and a pressurized water reactor which both offer all of the advantages of an advanced plant design, with excellent safety performance and competitive power generation cost: -) KERENA (1250+ MWe), developed in collaboration with several European utilities, and in particular with Eon; -) ATMEA 1 (1100+ MWe), a 3-loop evolutionary PWR which is being developed by AREVA and Mitsubishi. AREVA is also preparing the future and is deeply involved into Gen IV concepts. It has developed the ANTARES modular HTR reactor (pre-conceptual design completed) and is building upon its vast Sodium Fast Reactor experience to take part into the development of the next prototype. (author)

18. Oscillatory flow chemical reactors

Directory of Open Access Journals (Sweden)

Slavnić Danijela S.

2014-01-01

Full Text Available Global market competition, increase in energy and other production costs, demands for high quality products and reduction of waste are forcing pharmaceutical, fine chemicals and biochemical industries, to search for radical solutions. One of the most effective ways to improve the overall production (cost reduction and better control of reactions is a transition from batch to continuous processes. However, the reactions of interests for the mentioned industry sectors are often slow, thus continuous tubular reactors would be impractically long for flow regimes which provide sufficient heat and mass transfer and narrow residence time distribution. The oscillatory flow reactors (OFR are newer type of tube reactors which can offer solution by providing continuous operation with approximately plug flow pattern, low shear stress rates and enhanced mass and heat transfer. These benefits are the result of very good mixing in OFR achieved by vortex generation. OFR consists of cylindrical tube containing equally spaced orifice baffles. Fluid oscillations are superimposed on a net (laminar flow. Eddies are generated when oscillating fluid collides with baffles and passes through orifices. Generation and propagation of vortices create uniform mixing in each reactor cavity (between baffles, providing an overall flow pattern which is close to plug flow. Oscillations can be created by direct action of a piston or a diaphragm on fluid (or alternatively on baffles. This article provides an overview of oscillatory flow reactor technology, its operating principles and basic design and scale - up characteristics. Further, the article reviews the key research findings in heat and mass transfer, shear stress, residence time distribution in OFR, presenting their advantages over the conventional reactors. Finally, relevant process intensification examples from pharmaceutical, polymer and biofuels industries are presented.

19. Study of future reactors

International Nuclear Information System (INIS)

Bouchard, J.

1992-01-01

Today, more than 420 large reactors with a gross output of close to 350 GWe supply 20 percent of world electricity needs, accounting for less than 5 percent of primary energy consumption. These figures are not expected to change in the near future, due to suspended reactor construction in many countries. Nevertheless, world energy needs continue to grow: the planet's population already exceeds five billion and is forecast to reach ten billion by the middle of the next century. Most less developed countries have a very low rate of energy consumption and, even though some savings can be made in industrialized countries, it will become increasingly difficult to satisfy needs using fossil fuels only. Furthermore, there has been no recent breakthrough in the energy landscape. The physical feasibility of the other great hope of nuclear energy, fusion, has yet to be proved; once this has been done, it will be necessary to solve technological problems and to assess economic viability. Although it is more ever necessary to pursue fusion programs, there is little likelihood of industrial applications being achieved in the coming decades. Coal and fission are the only ways to produce massive amounts of energy for the next century. Coal must overcome the pollution problems inherent in its use; fission nuclear power has to gain better public acceptance, which is obviously colored by safety and waste concerns. Most existing reactors were commissioned in the 1970s; reactor lifetime is a parameter that has not been clearly established. It will certainly be possible to refurbish some to extend their operation beyond the initial target of 30 or 40 years. But normal advances in technology and safety requirements will make the operation of the oldest reactors increasingly difficult. It becomes necessary to develop new generations of nuclear reactors, both to replace older ones and to revive plant construction in their countries that are not yet equipped or that have halted their

20. Fusion-fission hybrid reactors

International Nuclear Information System (INIS)

Greenspan, E.

1984-01-01

This chapter discusses the range of characteristics attainable from hybrid reactor blankets; blanket design considerations; hybrid reactor designs; alternative fuel hybrid reactors; multi-purpose hybrid reactors; and hybrid reactors and the energy economy. Hybrid reactors are driven by a fusion neutron source and include fertile and/or fissile material. The fusion component provides a copious source of fusion neutrons which interact with a subcritical fission component located adjacent to the plasma or pellet chamber. Fissile fuel and/or energy are the main products of hybrid reactors. Topics include high F/M blankets, the fissile (and tritium) breeding ratio, effects of composition on blanket properties, geometrical considerations, power density and first wall loading, variations of blanket properties with irradiation, thermal-hydraulic and mechanical design considerations, safety considerations, tokamak hybrid reactors, tandem-mirror hybrid reactors, inertial confinement hybrid reactors, fusion neutron sources, fissile-fuel and energy production ability, simultaneous production of combustible and fissile fuels, fusion reactors for waste transmutation and fissile breeding, nuclear pumped laser hybrid reactors, Hybrid Fuel Factories (HFFs), and scenarios for hybrid contribution. The appendix offers hybrid reactor fundamentals. Numerous references are provided

1. Space-time reactor kinetics for heterogeneous reactor structure

Energy Technology Data Exchange (ETDEWEB)

Raisic, N [Boris Kidric Institute of nuclear sciences Vinca, Belgrade (Yugoslavia)

1969-11-15

An attempt is made to formulate time dependent diffusion equation based on Feinberg-Galanin theory in the from analogue to the classical reactor kinetic equation. Parameters of these equations could be calculated using the existing codes for static reactor calculation based on the heterogeneous reactor theory. The obtained kinetic equation could be analogues in form to the nodal kinetic equation. Space-time distribution of neutron flux in the reactor can be obtained by solving these equations using standard methods.

International Nuclear Information System (INIS)

Starr, C.

1989-01-01

The objectives for nuclear power have always emphasized competitive costs, reliability, and public safety. During its initial two decades, the nuclear reactor program was enthusiastically and generously supported by the public, government, and industry. In the subsequent decades this external support was substantially eroded by the growing public fears of catastrophic accidents, poor economic performance of many nuclear plants, regulatory constraints, and a plethora of engineering issues disclosed by plant operations. The technical and institutional histories are discussed with particular relevance to their influence on the framework for future development of the several proposed advance reactors

3. Netherlands Interuniversity Reactor Institut

International Nuclear Information System (INIS)

1978-01-01

This is the annual report of the Interuniversity Reactor Institute in the Netherlands for the Academic Year 1977-78. Activities of the general committee, the daily committee and the scientific advice board are presented. Detailed reports of the scientific studies performed are given under five subjects - radiation physics, reactor physics, radiation chemistry, radiochemistry and radiation hygiene and dosimetry. Summarised reports of the various industrial groups are also presented. Training and education, publications and reports, courses, visits and cooperation with other institutes in the area of scientific research are mentioned. (C.F.)

4. Fusion Reactor Materials

International Nuclear Information System (INIS)

Decreton, M.

2000-01-01

SCK-CEN's research and development programme on fusion reactor materials includes: (1) the study of the mechanical behaviour of structural materials under neutron irradiation (including steels, inconel, molybdenum, chromium); (2) the determination and modelling of the characteristics of irradiated first wall materials such as beryllium; (3) the detection of abrupt electrical degradation of insulating ceramics under high temperature and neutron irradiation; (4) the study of the dismantling and waste disposal strategy for fusion reactors.; (5) a feasibility study for the testing of blanket modules under neutron radiation. Main achievements in these topical areas in the year 1999 are summarised

5. RA Reactor; Reaktor RA

Energy Technology Data Exchange (ETDEWEB)

NONE

1989-07-01

This chapter includes the following: General description of the RA reactor, organization of work, responsibilities of leadership and operators team, regulations concerning operation and behaviour in the reactor building, regulations for performing experiments, regulations and instructions for inserting samples into experimental channels. [Serbo-Croat] Ovo (prvo) poglavlje sadrzi sledece: Opis reaktora RA; semu organizacije rada i rukovodjenja; prava i duznosti direktora i rukovodioca pogona reaktora, propise o rezimu rada i kretanja u zgradi reaktora, propise o izvodjenju eksperimenata, propise o unosenju uzoraka u eksperimentalne kanale reaktora.

6. Nuclear reactor constructions

International Nuclear Information System (INIS)

Aspden, G.J.

1980-01-01

A nuclear reactor construction comprising a reactor core submerged in a pool of liquid metal coolant in a primary vessel which is suspended from the roof structure of a containment vault. Control rods supported from the roof structure are insertable in the core which is carried on a support structure from the wall of the primary vessel. To prevent excessive relaxation of the support structure whereby the control rods would be displaced relative to the core, the support structure incorporates a normally inactive secondary structure designed to become effective in bracing the primary structure against further relaxation beyond a predetermined limit. (author)

7. Small mirror fusion reactors

International Nuclear Information System (INIS)

Carlson, G.A.; Schultz, K.R.; Smith, A.C. Jr.

1978-01-01

Basic requirements for the pilot plants are that they produce a net product and that they have a potential for commercial upgrade. We have investigated a small standard mirror fusion-fission hybrid, a two-component tandem mirror hybrid, and two versions of a field-reversed mirror fusion reactor--one a steady state, single cell reactor with a neutral beam-sustained plasma, the other a moving ring field-reversed mirror where the plasma passes through a reaction chamber with no energy addition

8. Nuclear reactor installation

International Nuclear Information System (INIS)

Keller, W.

1976-01-01

A nuclear reactor installation includes a pressurized-water coolant reactor vessel and a concrete biological shield surrounding this vessel. The shield forms a space between it and the vessel large enough to permit rapid escape of the pressurized-water coolant therefrom in the event the vessel ruptures. Struts extend radially between the vessel and shield for a distance permitting normal radial thermal movement of the vessel, while containing the vessel in the event it ruptures, the struts being interspaced from each other to permit rapid escape of the pressurized-water coolant from the space between the shield and the vessel

9. Australia's new nuclear reactor

International Nuclear Information System (INIS)

Kemeny, L.

2007-01-01

On 19 and 20 April 2007, the Australian Nuclear Science and Technology Organisation (ANSTO) celebrated the recent commissioning of its new, world-class, OPAL (Open Pool Australian Lightwater) research reactor at the Lucas Heights. On the 19th, scientists, business leaders and academics were introduced to the reactor and its technical capacity for the manufacture of radiopharmaceuticals, its material science applications, its environmental services and its neutron scattering facilities for business applications. The formal OPAL opening function took place that evening and, on the 20th, Prime Minister John Howard visited ANSTO to be briefed about OPAL and to be shown the work being carried out at Lucas Heights

10. Nuclear reactor core assembly

International Nuclear Information System (INIS)

Baxi, C.B.

1978-01-01

The object of the present invention is to provide a fast reactor core assembly design for use with a fluid coolant such as liquid sodium or carbon monoxide incorporating a method of increasing the percentage of coolant flow though the blanket elements relative to the total coolant flow through the blanket and fuel elements during shutdown conditions without using moving parts. It is claimed that deterioration due to reactor radiation or temperature conditions is avoided and ready modification or replacement is possible. (U.K.)

11. Reactor PIK construction

International Nuclear Information System (INIS)

Konoplev, Kir

2003-01-01

The construction work at the 100 MW researches reactor PIK in year 2002 was in progress. The main activity was concentrated on mechanical, ventilation and electrical equipment. Some systems and subsystems are under adjustment. Hydraulic driving gear for beam shutters are finished in installation, rinsing, and adjusting. Regulating rods test assembling was done. On the critical assembly the first reactor fueling was tested to evaluate the starting neutron source intensity and a sufficiency of existing control and instrument board. Mainline of the PIK facility design and neutron parameters are presented. (author)

12. Reactor Materials Research

Energy Technology Data Exchange (ETDEWEB)

Van Walle, E

2002-04-01

The activities of SCK-CEN's Reactor Materials Research Department for 2001 are summarised. The objectives of the department are: (1) to evaluate the integrity and behaviour of structural materials used in nuclear power industry; (2) to conduct research to unravel and understand the parameters that determine the material behaviour under or after irradiation; (3) to contribute to the interpretation, the modelling of the material behaviour and to develop and assess strategies for optimum life management of nuclear power plant components. The programmes within the department are focussed on studies concerning (1) Irradiation Assisted Stress Corrosion Cracking (IASCC); (2) nuclear fuel; and (3) Reactor Pressure Vessel Steel.

13. Nuclear reactor simulator

International Nuclear Information System (INIS)

Baptista, Vinicius Damas

1996-01-01

The Nuclear Reactor Simulator was projected to help the basic training in the formation of the Nuclear Power Plants operators. It gives the trainee the opportunity to see the nuclear reactor dynamics. It's specially indicated to be used as the support tool to NPPT (Nuclear Power Preparatory Training) from NUS Corporation. The software was developed to Intel platform (80 x 86, Pentium and compatible ones) working under the Windows operational system from Microsoft. The program language used in development was Object Pascal and the compiler used was Delphi from Borland. During the development, computer algorithms were used, based in numeric methods, to the resolution of the differential equations involved in the process. (author)

14. Reactor Materials Research

International Nuclear Information System (INIS)

Van Walle, E.

2002-01-01

The activities of SCK-CEN's Reactor Materials Research Department for 2001 are summarised. The objectives of the department are: (1) to evaluate the integrity and behaviour of structural materials used in nuclear power industry; (2) to conduct research to unravel and understand the parameters that determine the material behaviour under or after irradiation; (3) to contribute to the interpretation, the modelling of the material behaviour and to develop and assess strategies for optimum life management of nuclear power plant components. The programmes within the department are focussed on studies concerning (1) Irradiation Assisted Stress Corrosion Cracking (IASCC); (2) nuclear fuel; and (3) Reactor Pressure Vessel Steel

15. Reactor neutron dosimetry

International Nuclear Information System (INIS)

Najzer, M.; Pauko, M.; Glumac, B.; Acquah, I.N.; Moskon, F.

1977-01-01

An analysis of requirements and possibilities for experimental neutron spectrum determination during the reactor pressure vessel surveil lance programme is given. Fast neutron spectrum and neutron dose rate were measured in the Fast neutron irradiation facility of our TRIGA reactor. It was shown that the facility can be used for calibration of neutron dosimeters and for irradiation of samples sensitive to neutron radiation. The investigation of the unfolding algorithm ITER was continued. Based on this investigations are two specialized unfolding program packages ITERAD and ITERGS written this year. They are able to unfold data from activation detectors and NaI(T1) gamma spectrometer respectively

16. Refueling of nuclear reactor

International Nuclear Information System (INIS)

Kaufmann, J.W.; Swidwa, K.J.; Hornak, L.P.

1989-01-01

This patent describes an apparatus for refueling a nuclear reactor, the reactor being disposed for refueling under water in a pit in a containment, the apparatus including a bridge to be mounted moveably over the pit on the containment, first means connected to the bridge, for moving the bridge forward and backward on the containment over the pit along a first path, a first pulse generator, connected to the moving means, responsive to the movement of the bridge, for producing pulses, means, connected to the generator,for counting the pulses, the count of the pulses being dependent on the distance of the movement of the bridge

17. Space nuclear reactor safety

International Nuclear Information System (INIS)

Damon, D.; Temme, M.; Brown, N.

1990-01-01

Definition of safety requirements and design features of the SP-100 space reactor power system has been guided by a mission risk analysis. The analysis quantifies risk from accidental radiological consequences for a reference mission. Results show that the radiological risk from a space reactor can be made very low. The total mission risk from radiological consequences for a shuttle-launched, earth orbit SP-100 mission is estimated to be 0.05 Person-REM (expected values) based on a 1 mREM/yr de Minimus dose. Results are given for each mission phase. The safety benefits of specific design features are evaluated through risk sensitivity analyses

18. Netherlands Reactor Centre

International Nuclear Information System (INIS)

Anon.

1976-01-01

Briefly reviews the last year's work of the twenty year old Netherlands Reactor Centre (RCN) in the fields of reactor safety, fissile material, nuclear fission, non-nuclear energy systems and overseas co-operation. The annual report thus summarised is the last one to appear under the name of RCN. The terms of reference of the organisation having been broadened to include research into energy supply in general, it is to be known in future as the Netherlands Energy Research Centre (ECN). (D.J.B.)

19. Fusion Reactor Materials

Energy Technology Data Exchange (ETDEWEB)

Decreton, M

2000-07-01

SCK-CEN's research and development programme on fusion reactor materials includes: (1) the study of the mechanical behaviour of structural materials under neutron irradiation (including steels, inconel, molybdenum, chromium); (2) the determination and modelling of the characteristics of irradiated first wall materials such as beryllium; (3) the detection of abrupt electrical degradation of insulating ceramics under high temperature and neutron irradiation; (4) the study of the dismantling and waste disposal strategy for fusion reactors.; (5) a feasibility study for the testing of blanket modules under neutron radiation. Main achievements in these topical areas in the year 1999 are summarised.

20. ARIES tokamak reactor study

International Nuclear Information System (INIS)

Steiner, D.; Embrechts, M.

1990-07-01

This is a status report on technical progress relative to the tasks identified for the fifth year of Grant No. FG02-85-ER52118. The ARIES tokamak reactor study is a multi-institutional effort to develop several visions of the tokamak as an attractive fusion reactor with enhanced economic, safety, and environmental features. The ARIES study is being coordinated by UCLA and involves a number of institutions, including RPI. The RPI group has been pursuing the following areas of research in the context of the ARIES-I design effort: MHD equilibrium and stability analyses; plasma-edge modeling and blanket materials issues. Progress in these areas is summarized herein

1. Particle bed reactor modeling

Science.gov (United States)

Sapyta, Joe; Reid, Hank; Walton, Lew

The topics are presented in viewgraph form and include the following: particle bed reactor (PBR) core cross section; PBR bleed cycle; fuel and moderator flow paths; PBR modeling requirements; characteristics of PBR and nuclear thermal propulsion (NTP) modeling; challenges for PBR and NTP modeling; thermal hydraulic computer codes; capabilities for PBR/reactor application; thermal/hydralic codes; limitations; physical correlations; comparison of predicted friction factor and experimental data; frit pressure drop testing; cold frit mask factor; decay heat flow rate; startup transient simulation; and philosophy of systems modeling.

2. Nuclear reactors theory

International Nuclear Information System (INIS)

Naudan, G.; Nigon, J.L.

1993-01-01

After principles of chain reaction and criticality notion, a descriptive model of neutrons behaviour is exposed from a local point of view (this model is called four factors model). One justifies the use of middle values for the calculation of the distribution in space of reactor, quantities representing heterogeneous middle from a local point of view (fuel, moderator, can or clad, and so on ...) by substitution of an equivalent homogeneous middle. Time dependence, dynamical behaviour of reactor are studied. Long term effects of evolution of constituents elements of heart under irradiation, and ways to balance this evolution are in the last paragraph. 18 refs., 26 figs

3. Reactor gamma spectrometry: status

International Nuclear Information System (INIS)

Gold, R.; Kaiser, B.J.

1979-01-01

Current work is described for Compton Recoil Gamma-Ray Spectrometry including developments in experimental technique as well as recent reactor spectrometry measurements. The current status of the method is described concerning gamma spectromoetry probe design and response characteristics. Emphasis is given to gamma spectrometry work in US LWR and BR programs. Gamma spectrometry in BR environments are outlined by focussing on start-up plans for the Fast Test Reactor (FTR). Gamma spectrometry results are presented for a LWR pressure vessel mockup in the Poolside Critical Assembly (PCA) at Oak Ridge National Laboratory

4. Perspectives on reactor safety

Energy Technology Data Exchange (ETDEWEB)

Haskin, F.E. [New Mexico Univ., Albuquerque, NM (United States). Dept. of Chemical and Nuclear Engineering; Camp, A.L. [Sandia National Labs., Albuquerque, NM (United States)

1994-03-01

The US Nuclear Regulatory Commission (NRC) maintains a technical training center at Chattanooga, Tennessee to provide appropriate training to both new and experienced NRC employees. This document describes a one-week course in reactor, safety concepts. The course consists of five modules: (1) historical perspective; (2) accident sequences; (3) accident progression in the reactor vessel; (4) containment characteristics and design bases; and (5) source terms and offsite consequences. The course text is accompanied by slides and videos during the actual presentation of the course.

5. Perspectives on reactor safety

International Nuclear Information System (INIS)

1994-03-01

The US Nuclear Regulatory Commission (NRC) maintains a technical training center at Chattanooga, Tennessee to provide appropriate training to both new and experienced NRC employees. This document describes a one-week course in reactor, safety concepts. The course consists of five modules: (1) historical perspective; (2) accident sequences; (3) accident progression in the reactor vessel; (4) containment characteristics and design bases; and (5) source terms and offsite consequences. The course text is accompanied by slides and videos during the actual presentation of the course

6. Reactor transients tests for SNR fuel elements in HFR reactor

International Nuclear Information System (INIS)

Plitz, H.

1989-01-01

In HFR reactor, fuel pins of LMFBR reactors are putted in irradiation specimen capsules cooled with sodium for reactor transients tests. These irradiation capsules are instrumented and the experiences realized until this day give results on: - Fuel pins subjected at a continual variation of power - melting fuel - axial differential elongation of fuel pins

7. Computerized reactor monitor and control for research reactors

International Nuclear Information System (INIS)

Buerger, L.; Vegh, E.

1981-09-01

The computerized process control system developed in the Central Research Institute for Physics, Budapest, Hungary, is described together with its special applications at research reactors. The nuclear power of the Hungarian research reactor is controlled by this computerized system, too, while in Lybia many interesting reactor-hpysical calculations are built into the computerized monitor system. (author)

8. Reactor science and technology: operation and control of reactors

International Nuclear Information System (INIS)

Qiu Junlong

1994-01-01

This article is a collection of short reports on reactor operation and research in China in 1991. The operation of and research activities linked with the Heavy Water Research Reactor, Swimming Pool Reactor and Miniature Neutron Source Reactor are briefly surveyed. A number of papers then follow on the developing strategies in Chinese fast breeder reactor technology including the conceptual design of an experimental fast reactor (FFR), theoretical studies of FFR thermo-hydraulics and a design for an immersed sodium flowmeter. Reactor physics studies cover a range of topics including several related to work on zero power reactors. The section on reactor safety analysis is concerned largely with the assessment of established, and the presentation of new, computer codes for use in PWR safety calculations. Experimental and theoretical studies of fuels and reactor materials for FBRs, PWRs, BWRs and fusion reactors are described. A final miscellaneous section covers Mo-Tc isotope production in the swimming pool reactor, convective heat transfer in tubes and diffusion of tritium through plastic/aluminium composite films and Li 2 SiO 3 . (UK)

9. Reactor operation environmental information document

Energy Technology Data Exchange (ETDEWEB)

Haselow, J.S.; Price, V.; Stephenson, D.E.; Bledsoe, H.W.; Looney, B.B.

1989-12-01

The Savannah River Site (SRS) produces nuclear materials, primarily plutonium and tritium, to meet the requirements of the Department of Defense. These products have been formed in nuclear reactors that were built during 1950--1955 at the SRS. K, L, and P reactors are three of five reactors that have been used in the past to produce the nuclear materials. All three of these reactors discontinued operation in 1988. Currently, intense efforts are being extended to prepare these three reactors for restart in a manner that protects human health and the environment. To document that restarting the reactors will have minimal impacts to human health and the environment, a three-volume Reactor Operations Environmental Impact Document has been prepared. The document focuses on the impacts of restarting the K, L, and P reactors on both the SRS and surrounding areas. This volume discusses the geology, seismology, and subsurface hydrology. 195 refs., 101 figs., 16 tabs.

10. Radiation shielding for fission reactors

Energy Technology Data Exchange (ETDEWEB)

Oka, Yoshiaki [Tokyo Univ., Nuclear Engineering Research Laboratory, Tokyo (Japan)

2000-03-01

Radiation shielding aspects relating fission reactors have been reviewed. Domestic activities in the past five years have been mainly described concerning nuclear data, calculation methods, shielding and skyshine experiments, Advanced Boiling Water Reactor (ABWR), Advanced Pressurized Water Reactor (APWR), High Temperature Engineering Test Reactor (HTTR), Experimental and Prototype Fast Reactors (JOYO, MONJU), Demonstration FBR, core shroud replacement of BWR, and spent fuel transportation cask and vessel. These studies have valuable information in safety and cost reduction issues of fission reactor design for not only existing reactors but also new reactor concepts in the next century. It has been concluded that we should maintain existing shielding technologies and improve these data and methods for coming generations in the next millennium. (author)

11. Reactor Engineering Department annual report

International Nuclear Information System (INIS)

Matsuura, S.; Nakahara, Y.; Takano, H.

1983-09-01

Research and development activities in the Department of Reactor Engineering in fiscal 1982 are described. The work of the Department is closely related to development of multipurpose Very High Temperature Gas Cooled Reactor and Fusion Reactor, and development of Liquid Metal Fast Breeder Reactor carried out by Power Reactor and Nuclear Fuel Development Corporation. Since fiscal 1982, Systematic research and development work on safeguards technology has been added to the activities of the Department. Contents of the report are achievements in fields such as nuclear data and group constants, theoretical method and code development, integral experiment and analysis, fusion neutronics, shielding, reactor and nuclear instrumentation, reactor control and diagnosis, and safeguards technology, and activities of the Committee on Reactor Physics. (author)

12. Operating reactors licensing actions summary

International Nuclear Information System (INIS)

1981-08-01

The Operating Reactors Licensing Actions Summary is designed to provide the management of the Nuclear Regulatory Commission (NRC) with an overview of licensing actions dealing with operating power and nonpower reactors

13. The market for research reactors

International Nuclear Information System (INIS)

Roegler, H.J.

1986-01-01

The assay deals with some basic questions if there is an international market for research reactors at all, which influencing factors affect this market, and if research reactors have any effects on the future market for nuclear engineering. (UA) [de

14. High Flux Isotope Reactor (HFIR)

Data.gov (United States)

Federal Laboratory Consortium — The HFIR at Oak Ridge National Laboratory is a light-water cooled and moderated reactor that is the United States’ highest flux reactor-based neutron source. HFIR...

15. Engineering reactors for catalytic reactions

126, No. 2, March 2014, pp. 341–351. c Indian Academy of Sciences. ... enhancement was realized by catalyst design, appropriate choice of reactor, better injection and .... Gas–liquid and liquid–solid transport processes in catalytic reactors.5.

16. Spiral-shaped disinfection reactors

KAUST Repository

Ghaffour, NorEddine; Ait-Djoudi, Fariza; Naceur, Wahib Mohamed; Soukane, Sofiane

2015-01-01

This disclosure includes disinfection reactors and processes for the disinfection of water. Some disinfection reactors include a body that defines an inlet, an outlet, and a spiral flow path between the inlet and the outlet, in which the body

17. RA Reactor applications, Annex A

International Nuclear Information System (INIS)

Martinc, R.; Cupac, S.; Stanic, A.

1990-01-01

RA reactor was not operated during the past five years due to the renewal and reconstruction of the reactor systems, which in underway. In the period from 1986-1990, reactor was operated only 144 MWh in 1986, for the need of testing the reactor systems and possibility of irradiating 125 I. Reactor will not be operated in 1991 because of the exchange of complete instrumentation which is planned to be finished by the end of 1991. It is expected to start operation in May 1992. That is why this annex includes the plan of reactor operation for period of nine months starting from from the moment of start-up. It is planned to operate the reactor at 0.02 MW power first three months, to increase the power gradually and reach 3.5 MW after 8 months of operation. It is foreseen to operate the reactor at 4.7 MW from the tenth month on [sr

18. Reactor operation safety information document

Energy Technology Data Exchange (ETDEWEB)

1990-01-01

The report contains a reactor facility description which includes K, P, and L reactor sites, structures, operating systems, engineered safety systems, support systems, and process and effluent monitoring systems; an accident analysis section which includes cooling system anomalies, radioactive materials releases, and anticipated transients without scram; a summary of onsite doses from design basis accidents; severe accident analysis (reactor core disruption); a description of operating contractor organization and emergency planning; and a summary of reactor safety evolution. (MB)

19. Research reactors and materials testing

International Nuclear Information System (INIS)

Vidal, H.

1986-01-01

Research reactors can be classified in three main groups according to the moderator which is used. Their technical characteristics are given and the three most recent research and materials testing reactors are described: OSIRIS, ORPHEE and the high-flux reactor of Grenoble. The utilization of research reactors is reviewed in four fields of activity: training, fundamental or applied research and production (eg. radioisotopes) [fr

20. Reactor safety in Eastern Europe

International Nuclear Information System (INIS)

1995-02-01

The papers presented to the GRS colloquium refer to the cooperative activities for reactor accident analysis and modification of the GRS computer codes for their application to reactors of the Russian design types of WWER or RBMK. Another topic is the safety of RBMK reactors in particular, and the current status of investigations and studies addressing the containment of unit 4 of the Chernobyl reactor station. All papers are indexed separately in report GRS--117. (HP)