Maximum permissible voltage of YBCO coated conductors
Energy Technology Data Exchange (ETDEWEB)
Wen, J.; Lin, B.; Sheng, J.; Xu, J.; Jin, Z. [Department of Electrical Engineering, Shanghai Jiao Tong University, Shanghai (China); Hong, Z., E-mail: zhiyong.hong@sjtu.edu.cn [Department of Electrical Engineering, Shanghai Jiao Tong University, Shanghai (China); Wang, D.; Zhou, H.; Shen, X.; Shen, C. [Qingpu Power Supply Company, State Grid Shanghai Municipal Electric Power Company, Shanghai (China)
2014-06-15
Highlights: • We examine three kinds of tapes’ maximum permissible voltage. • We examine the relationship between quenching duration and maximum permissible voltage. • Continuous I{sub c} degradations under repetitive quenching where tapes reaching maximum permissible voltage. • The relationship between maximum permissible voltage and resistance, temperature. - Abstract: Superconducting fault current limiter (SFCL) could reduce short circuit currents in electrical power system. One of the most important thing in developing SFCL is to find out the maximum permissible voltage of each limiting element. The maximum permissible voltage is defined as the maximum voltage per unit length at which the YBCO coated conductors (CC) do not suffer from critical current (I{sub c}) degradation or burnout. In this research, the time of quenching process is changed and voltage is raised until the I{sub c} degradation or burnout happens. YBCO coated conductors test in the experiment are from American superconductor (AMSC) and Shanghai Jiao Tong University (SJTU). Along with the quenching duration increasing, the maximum permissible voltage of CC decreases. When quenching duration is 100 ms, the maximum permissible of SJTU CC, 12 mm AMSC CC and 4 mm AMSC CC are 0.72 V/cm, 0.52 V/cm and 1.2 V/cm respectively. Based on the results of samples, the whole length of CCs used in the design of a SFCL can be determined.
Energy Technology Data Exchange (ETDEWEB)
Djukanovic, M [Inst. ' Nikola Tesla' , Belgrade (Yugoslavia); Sobajic, D J; Pao, Yohhan [Case Western Reserve Univ., Cleveland, OH (United States). Dept. of Electrical Engineering and Applied Physics Case Western Reserve Univ., Cleveland, OH (United States). Dept. of Computer Engineering and Science AI WARE inc., Cleveland, OH (United States)
1992-10-01
In heavily stressed power systems, post-fault transient voltage dips can lead to undesired tripping of industrial drives and large induction motors. The lowest transient voltage dips occur when fault clearing times are less than critical ones. In this paper, we propose a new iterative analytical methodology to obtain more accurate estimates of voltage dips at maximum angular swing in direct transient stability analysis. We also propose and demonstrate the possibility of storing the results of these computations in the associative memory (AM) system, which exhibits remarkable generalization capabilities. Feature-based models stored in the AM can be utilized for fast and accurate prediction of the location, duration and the amount of the worst voltage dips, thereby avoiding the need and cost for lengthy time-domain simulations. Numerical results obtained using the example of the New England power system are presented to illustrate our approach. (Author)
Bhatara, Sevty Satria; Iskandar, Reza Fauzi; Kirom, M. Ramdlan
2016-02-01
Solar energy is one of renewable energy resource where needs a photovoltaic module to convert it into electrical energy. One of the problems on solar energy conversion is the process of battery charging. To improve efficiency of energy conversion, PV system needs another control method on battery charging called maximum power point tracking (MPPT). This paper report the study on charging optimation using constant voltage (CV) method. This method has a function of determining output voltage of the PV system on maximal condition, so PV system will always produce a maximal energy. A model represented a PV system with and without MPPT was developed using Simulink. PV system simulation showed a different outcome energy when different solar radiation and numbers of solar module were applied in the model. On the simulation of solar radiation 1000 W/m2, PV system with MPPT produces 252.66 Watt energy and PV system without MPPT produces 252.66 Watt energy. The larger the solar radiation, the greater the energy of PV modules was produced.
Maximum penetration level of distributed generation without violating voltage limits
Morren, J.; Haan, de S.W.H.
2009-01-01
Connection of Distributed Generation (DG) units to a distribution network will result in a local voltage increase. As there will be a maximum on the allowable voltage increase, this will limit the maximum allowable penetration level of DG. By reactive power compensation (by the DG unit itself) a
Computer controlled high voltage system
Energy Technology Data Exchange (ETDEWEB)
Kunov, B; Georgiev, G; Dimitrov, L [and others
1996-12-31
A multichannel computer controlled high-voltage power supply system is developed. The basic technical parameters of the system are: output voltage -100-3000 V, output current - 0-3 mA, maximum number of channels in one crate - 78. 3 refs.
International Nuclear Information System (INIS)
Martin, M.
1991-01-01
Industrial processes usually require electrical power. This power is used to drive motors, to heat materials, or in electrochemical processes. Often the power requirements of a plant require the electric power to be delivered at high voltage. In this paper high voltage is considered any voltage over 600 V. This voltage could be as high as 138,000 V for some very large facilities. The characteristics of this voltage and the enormous amounts of power being transmitted necessitate special safety considerations. Safety must be considered during the four activities associated with a high voltage electrical system. These activities are: Design; Installation; Operation; and Maintenance
30 CFR 77.902-1 - Fail safe ground check circuits; maximum voltage.
2010-07-01
... voltage. 77.902-1 Section 77.902-1 Mineral Resources MINE SAFETY AND HEALTH ADMINISTRATION, DEPARTMENT OF... OF UNDERGROUND COAL MINES Low- and Medium-Voltage Alternating Current Circuits § 77.902-1 Fail safe ground check circuits; maximum voltage. The maximum voltage used for ground check circuits under § 77.902...
30 CFR 77.803-1 - Fail safe ground check circuits; maximum voltage.
2010-07-01
... voltage. 77.803-1 Section 77.803-1 Mineral Resources MINE SAFETY AND HEALTH ADMINISTRATION, DEPARTMENT OF... OF UNDERGROUND COAL MINES Surface High-Voltage Distribution § 77.803-1 Fail safe ground check circuits; maximum voltage. The maximum voltage used for ground check circuits under § 77.803 shall not...
Best voltage bias-flipping strategy towards maximum piezoelectric power generation
International Nuclear Information System (INIS)
Liang, Junrui; Chung, Henry Shu-Hung
2013-01-01
In piezoelectric energy harvesting (PEH) systems, energy extracted from piezoelectric structure can be increased by making piezoelectric voltage in phase with vibration velocity and raising the voltage amplitude. Such voltage manipulations can be realized by synchronously flipping the piezoelectric voltage with respect to a bias dc source at every displacement extremum. Given that net harvested energy is obtained by deducting dissipated energy from total extracted energy, a sophisticated voltage bias-flipping scheme, which can maximize extracted energy at low dissipative cost, is required towards harvested energy optimization. This paper extends the state of the art by proposing the best bias-flip strategy, which is delivered on conceptual synchronized multiple bias-flip (SMBF) interface circuits. The proposed strategy coordinates both requirements on larger voltage change in synchronized instant for more extracted energy and smaller voltage change in each bias-flip action for less dissipated energy. It not only leads to further enhancement of harvesting capability beyond existing solutions, but also provides an unprecedented physical insight on maximum achievable harvesting capability of PEH interface circuit
System for memorizing maximum values
Bozeman, Richard J., Jr.
1992-08-01
The invention discloses a system capable of memorizing maximum sensed values. The system includes conditioning circuitry which receives the analog output signal from a sensor transducer. The conditioning circuitry rectifies and filters the analog signal and provides an input signal to a digital driver, which may be either linear or logarithmic. The driver converts the analog signal to discrete digital values, which in turn triggers an output signal on one of a plurality of driver output lines n. The particular output lines selected is dependent on the converted digital value. A microfuse memory device connects across the driver output lines, with n segments. Each segment is associated with one driver output line, and includes a microfuse that is blown when a signal appears on the associated driver output line.
A maximum power point tracking for photovoltaic-SPE system using a maximum current controller
Energy Technology Data Exchange (ETDEWEB)
Muhida, Riza [Osaka Univ., Dept. of Physical Science, Toyonaka, Osaka (Japan); Osaka Univ., Dept. of Electrical Engineering, Suita, Osaka (Japan); Park, Minwon; Dakkak, Mohammed; Matsuura, Kenji [Osaka Univ., Dept. of Electrical Engineering, Suita, Osaka (Japan); Tsuyoshi, Akira; Michira, Masakazu [Kobe City College of Technology, Nishi-ku, Kobe (Japan)
2003-02-01
Processes to produce hydrogen from solar photovoltaic (PV)-powered water electrolysis using solid polymer electrolysis (SPE) are reported. An alternative control of maximum power point tracking (MPPT) in the PV-SPE system based on the maximum current searching methods has been designed and implemented. Based on the characteristics of voltage-current and theoretical analysis of SPE, it can be shown that the tracking of the maximum current output of DC-DC converter in SPE side will track the MPPT of photovoltaic panel simultaneously. This method uses a proportional integrator controller to control the duty factor of DC-DC converter with pulse-width modulator (PWM). The MPPT performance and hydrogen production performance of this method have been evaluated and discussed based on the results of the experiment. (Author)
Maximum Safety Regenerative Power Tracking for DC Traction Power Systems
Directory of Open Access Journals (Sweden)
Guifu Du
2017-02-01
Full Text Available Direct current (DC traction power systems are widely used in metro transport systems, with running rails usually being used as return conductors. When traction current flows through the running rails, a potential voltage known as “rail potential” is generated between the rails and ground. Currently, abnormal rises of rail potential exist in many railway lines during the operation of railway systems. Excessively high rail potentials pose a threat to human life and to devices connected to the rails. In this paper, the effect of regenerative power distribution on rail potential is analyzed. Maximum safety regenerative power tracking is proposed for the control of maximum absolute rail potential and energy consumption during the operation of DC traction power systems. The dwell time of multiple trains at each station and the trigger voltage of the regenerative energy absorbing device (READ are optimized based on an improved particle swarm optimization (PSO algorithm to manage the distribution of regenerative power. In this way, the maximum absolute rail potential and energy consumption of DC traction power systems can be reduced. The operation data of Guangzhou Metro Line 2 are used in the simulations, and the results show that the scheme can reduce the maximum absolute rail potential and energy consumption effectively and guarantee the safety in energy saving of DC traction power systems.
Mitigation of voltage sags in the distribution system with dynamic voltage restorer
International Nuclear Information System (INIS)
Viglas, D.; Belan, A.
2012-01-01
Dynamic voltage restorer is a custom power device that is used to improve voltage sags or swells in electrical distribution system. The components of the Dynamic Voltage Restorer consist of injection transformers, voltage source inverter, passive filters and energy storage. The main function of the Dynamic voltage restorer is used to inject three phase voltage in series and in synchronism with the grid voltages in order to compensate voltage disturbances. This article deals with mitigation of voltage sags caused by three-phase short circuit. Dynamic voltage restorer is modelled in MATLAB/Simulink. (Authors)
Frequency-Domain Maximum-Likelihood Estimation of High-Voltage Pulse Transformer Model Parameters
Aguglia, D; Martins, C.D.A.
2014-01-01
This paper presents an offline frequency-domain nonlinear and stochastic identification method for equivalent model parameter estimation of high-voltage pulse transformers. Such kinds of transformers are widely used in the pulsed-power domain, and the difficulty in deriving pulsed-power converter optimal control strategies is directly linked to the accuracy of the equivalent circuit parameters. These components require models which take into account electric fields energies represented by stray capacitance in the equivalent circuit. These capacitive elements must be accurately identified, since they greatly influence the general converter performances. A nonlinear frequency-based identification method, based on maximum-likelihood estimation, is presented, and a sensitivity analysis of the best experimental test to be considered is carried out. The procedure takes into account magnetic saturation and skin effects occurring in the windings during the frequency tests. The presented method is validated by experim...
The LMF triaxial MITL voltage adder system
International Nuclear Information System (INIS)
Mazarakis, M.G.; Smith, D.L.; Bennett, L.F.; Lockner, T.R.; Olson, R.E.; Poukey, J.W.
1992-01-01
The light-ion microfusion driver design consists of multiple accelerating modules fired in coincidence and sequentially in order to provide the desired ion energy, power pulse shape and energy deposition uniformity on an Inertial Confinement Fusion (ICF) target. The basic energy source is a number of Marx generators which, through the appropriate pulse power conditioning, provide the necessary voltage pulse wave form to the accelerating gaps or feeds of each module. The cavity gaps are inductively isolated, and the voltage addition occurs in the center conductor of the voltage adder which is the positive electrode while the electrons of the sheath flow closer to the outer cylinder which is the magnetically insulated cathode electrode. Each module powers a separate two-stage extraction diode which provides a low divergence ion beam. In order to provide the two separate voltage pulses required by the diode, a triaxial adder system is designed for each module. The voltage addition occurs in two separate MITLs. The center hollow cylinder (anode) of the second MITL also serves as the outer cathode electrode for the extension of the first voltage adder MITL. The voltage of the second stage is about twice that of the first stage. The cavities are connected in series to form the outer cylinder of each module. The accelerating modules are positioned radially in a symmetrical way around the fusion chamber. A preliminary conceptual design of the LMF modules with emphasis on the voltage adders and extension MITLs will be presented and discussed
Fiber-optic voltage measuring system
Ye, Miaoyuan; Nie, De-Xin; Li, Yan; Peng, Yu; Lin, Qi-Qing; Wang, Jing-Gang
1993-09-01
A new fibre optic voltage measuring system has been developed based on the electrooptic effect of bismuth germanium oxide (Bi4Ge3O12)crystal. It uses the LED as the light source. The light beam emitted from the light source is transmitted to the sensor through the optic fibre and the intensity of the output beam is changed by the applied voltage. This optic signal is transmitted to the PIN detector and converted to an electric signal which is processed by the electronic circuit and 8098 single chip microcomputer the output voltage signal obtained is directly proportional to the applied voltage. This paper describes the principle the configuration and the performance parameters of the system. Test results are evaluated and discussed.
Multiagent voltage and reactive power control system
Directory of Open Access Journals (Sweden)
I. Arkhipov
2014-12-01
Full Text Available This paper is devoted to the research of multiagent voltage and reactive power control system development. The prototype of the system has been developed by R&D Center at FGC UES (Russia. The control system architecture is based on the innovative multiagent system theory application that leads to the achievement of several significant advantages (in comparison to traditional control systems implementation such as control system efficiency enhancement, control system survivability and cyber security.
Maximum Temperature Detection System for Integrated Circuits
Frankiewicz, Maciej; Kos, Andrzej
2015-03-01
The paper describes structure and measurement results of the system detecting present maximum temperature on the surface of an integrated circuit. The system consists of the set of proportional to absolute temperature sensors, temperature processing path and a digital part designed in VHDL. Analogue parts of the circuit where designed with full-custom technique. The system is a part of temperature-controlled oscillator circuit - a power management system based on dynamic frequency scaling method. The oscillator cooperates with microprocessor dedicated for thermal experiments. The whole system is implemented in UMC CMOS 0.18 μm (1.8 V) technology.
Inductive voltage compensation in superconducting magnet systems
International Nuclear Information System (INIS)
Yeh, H.T.; Goddard, J.S.; Shen, S.S.
1979-01-01
This paper details several techniques of inductive voltage compensation developed for quench detection in superconducting magnet systems with multiple coils and power supplies, with particular application for the Large Coil Test Facility (LCTF). Sources of noise, their magnitudes, and the sensitivity required for normal zone detection to avoid damage to the magnets are discussed. Two passive compensation schemes (second difference and central difference) are introduced and illustrated by parameters of LCTF; these take advantage of coil symmetries and other system characteristics. An active compensation scheme based on current rate input fom pickup coils and utilizing theory on ac loss voltage for calibration was tested, and the experimental setup and test results are discussed
Individual Module Maximum Power Point Tracking for a Thermoelectric Generator Systems
DEFF Research Database (Denmark)
Vadstrup, Casper; Chen, Min; Schaltz, Erik
Thermo Electric Generator (TEG) modules are often connected in a series and/or parallel system in order to match the TEG system voltage with the load voltage. However, in order to be able to control the power production of the TEG system a DC/DC converter is inserted between the TEG system...... and the load. The DC/DC converter is under the control of a Maximum Power Point Tracker (MPPT) which insures that the TEG system produces the maximum possible power to the load. However, if the conditions, e.g. temperature, health, etc., of the TEG modules are different each TEG module will not produce its...
DEFF Research Database (Denmark)
Wang, Dong; Lu, Kaiyuan; Rasmussen, Peter Omand
2015-01-01
The conventional high frequency signal injection method is to superimpose a high frequency voltage signal to the commanded stator voltage before space vector modulation. Therefore, the magnitude of the voltage used for machine torque production is limited. In this paper, a new high frequency...... amplitude. This may be utilized to develop new position estimation algorithm without involving the inductance in the medium to high speed range. As an application example, a developed inductance independent position estimation algorithm using the proposed high frequency injection method is applied to drive...... injection method, in which high frequency signal is generated by shifting the duty cycle between two neighboring switching periods, is proposed. This method allows injecting a high frequency signal at half of the switching frequency without the necessity to sacrifice the machine fundamental voltage...
Development of an Intelligent Maximum Power Point Tracker Using an Advanced PV System Test Platform
DEFF Research Database (Denmark)
Spataru, Sergiu; Amoiridis, Anastasios; Beres, Remus Narcis
2013-01-01
The performance of photovoltaic systems is often reduced by the presence of partial shadows. The system efficiency and availability can be improved by a maximum power point tracking algorithm that is able to detect partial shadow conditions and to optimize the power output. This work proposes...... an intelligent maximum power point tracking method that monitors the maximum power point voltage and triggers a current-voltage sweep only when a partial shadow is detected, therefore minimizing power loss due to repeated current-voltage sweeps. The proposed system is validated on an advanced, flexible...... photovoltaic inverter system test platform that is able to reproduce realistic partial shadow conditions, both in simulation and on hardware test system....
Voltage control on a train system
Gordon, Susanna P.; Evans, John A.
2004-01-20
The present invention provides methods for preventing low train voltages and managing interference, thereby improving the efficiency, reliability, and passenger comfort associated with commuter trains. An algorithm implementing neural network technology is used to predict low voltages before they occur. Once voltages are predicted, then multiple trains can be controlled to prevent low voltage events. Further, algorithms for managing inference are presented in the present invention. Different types of interference problems are addressed in the present invention such as "Interference During Acceleration", "Interference Near Station Stops", and "Interference During Delay Recovery." Managing such interference avoids unnecessary brake/acceleration cycles during acceleration, immediately before station stops, and after substantial delays. Algorithms are demonstrated to avoid oscillatory brake/acceleration cycles due to interference and to smooth the trajectories of closely following trains. This is achieved by maintaining sufficient following distances to avoid unnecessary braking/accelerating. These methods generate smooth train trajectories, making for a more comfortable ride, and improve train motor reliability by avoiding unnecessary mode-changes between propulsion and braking. These algorithms can also have a favorable impact on traction power system requirements and energy consumption.
Modeling of Maximum Power Point Tracking Controller for Solar Power System
Directory of Open Access Journals (Sweden)
Aryuanto Soetedjo
2012-09-01
Full Text Available In this paper, a Maximum Power Point Tracking (MPPT controller for solar power system is modeled using MATLAB Simulink. The model consists of PV module, buck converter, and MPPT controller. The contribution of the work is in the modeling of buck converter that allowing the input voltage of the converter, i.e. output voltage of PV is changed by varying the duty cycle, so that the maximum power point could be tracked when the environmental changes. The simulation results show that the developed model performs well in tracking the maximum power point (MPP of the PV module using Perturb and Observe (P&O Algorithm.
On-site voltage measurement with capacitive sensors on high voltage systems
Wu, L.; Wouters, P.A.A.F.; Heesch, van E.J.M.; Steennis, E.F.
2011-01-01
In Extra/High-Voltage (EHV/HV) power systems, over-voltages occur e.g. due to transients or resonances. At places where no conventional voltage measurement devices can be installed, on-site measurement of these occurrences requires preferably non intrusive sensors, which can be installed with little
International Nuclear Information System (INIS)
Arab, M.N.; Ayaz, M.
2004-01-01
The performance of transmission line insulator is greatly affected by dust, fumes from industrial areas and saline deposit near the coast. Such pollutants in the presence of moisture form a coating on the surface of the insulator, which in turn allows the passage of leakage current. This leakage builds up to a point where flashover develops. The flashover is often followed by permanent failure of insulation resulting in prolong outages. With the increase in system voltage owing to the greater demand of electrical energy over the past few decades, the importance of flashover due to pollution has received special attention. The objective of the present work was to study the performance of overhead line insulators in the presence of contaminants such as induced salts. A detailed review of the literature and the mechanisms of insulator flashover due to the pollution are presented. Experimental investigations on the behavior of overhead line insulators under industrial salt contamination are carried out. A special fog chamber was designed in which the contamination testing of insulators was carried out. Flashover behavior under various degrees of contamination of insulators with the most common industrial fume components such as Nitrate and Sulphate compounds was studied. Substituting the normal distribution parameter in the probability distribution function based on maximum likelihood develops a statistical method. The method gives a high accuracy in the estimation of the 50% flashover voltage, which is then used to evaluate the critical flashover index at various contamination levels. The critical flashover index is a valuable parameter in insulation design for numerous applications. (author)
Lightning-induced overvoltages in low-voltage systems
Energy Technology Data Exchange (ETDEWEB)
Hoeidalen, Hans Kristian
1997-12-31
Lightning-induced overvoltages (LIOs) are a main source of failures in low-voltage overhead line systems. This thesis deals mainly with calculations of LIOs aiming to enable the design of a proper voltage protection. Models for calculation of LIOs are adapted from the literature or developed based on measurements. The models used are believed to be fairly accurate for the first few microseconds, which is usually sufficient for predicting the maximum induced voltage in the system. The lightning channel is modelled by the Modified Transmission Line (MTL) model with the Transmission Line (TL) model as a special case. The coupling between the electrical fields from a lightning channel and an overhead line is modelled by Agrawal`s model. The attenuation of electrical fields over a lossy ground is modelled by Norton`s- or the Surface Impedance methods. The validity of all the applied models is analysed. In addition, measurements have been performed in order to develop models of distribution transformers and low-voltage power installation (LVPI) networks. Simple models of typical transformers and LVPIs are developed for calculations when specific data are unavailable. The practical range of values and its influence on the LIOs in a system is investigated. The main frequency range of interest related to LIOs is 10 kHz - 1 MHz in which all the models are accurate. The adapted or developed models are used to calculate LIOs in low-voltage systems. The influence of various key parameters in the system is investigated. Most important are the return stroke amplitude and rise time, the overhead line height and location, the termination of overhead line segments, neutral grounding, and the ground conductivity. 135 refs., 136 figs., 12 tabs.
Zero voltage mass spectrometry probes and systems
Cooks, Robert Graham; Wleklinski, Michael Stanley; Bag, Soumabha; Li, Yafeng
2017-10-10
The invention generally relates to zero volt mass spectrometry probes and systems. In certain embodiments, the invention provides a system including a mass spectrometry probe including a porous material, and a mass spectrometer (bench-top or miniature mass spectrometer). The system operates without an application of voltage to the probe. In certain embodiments, the probe is oriented such that a distal end faces an inlet of the mass spectrometer. In other embodiments, the distal end of the probe is 5 mm or less from an inlet of the mass spectrometer.
Electrical system architecture having high voltage bus
Hoff, Brian Douglas [East Peoria, IL; Akasam, Sivaprasad [Peoria, IL
2011-03-22
An electrical system architecture is disclosed. The architecture has a power source configured to generate a first power, and a first bus configured to receive the first power from the power source. The architecture also has a converter configured to receive the first power from the first bus and convert the first power to a second power, wherein a voltage of the second power is greater than a voltage of the first power, and a second bus configured to receive the second power from the converter. The architecture further has a power storage device configured to receive the second power from the second bus and deliver the second power to the second bus, a propulsion motor configured to receive the second power from the second bus, and an accessory motor configured to receive the second power from the second bus.
Accelerator System Development at High Voltage Engineering
International Nuclear Information System (INIS)
Klein, M. G.; Gottdang, A.; Haitsma, R. G.; Mous, D. J. W.
2009-01-01
Throughout the years, HVE has continuously extended the capabilities of its accelerator systems to meet the rising demands from a diverse field of applications, among which are deep level ion implantation, micro-machining, neutron production for biomedical research, isotope production or accelerator mass spectrometry. Characteristic for HVE accelerators is the coaxial construction of the all solid state power supply around the acceleration tubes. With the use of solid state technology, the accelerators feature high stability and very low ripple. Terminal voltages range from 1 to 6 MV for HVE Singletrons and Tandetrons. The high-current versions of these accelerators can provide ion beams with powers of several kW. In the last years, several systems have been built with terminal voltages of 1.25 MV, 2 MV and 5 MV. Recently, the first system based on a 6 MV Tandetron has passed the factory tests. In this paper we describe the characteristics of the HVE accelerator systems and present as example recent systems.
Advanced Control of the Dynamic Voltage Restorer for Mitigating Voltage Sags in Power Systems
Directory of Open Access Journals (Sweden)
Dung Vo Tien
2018-01-01
Full Text Available The paper presents a vector control with two cascaded loops to improve the properties of Dynamic Voltage Restorer (DVR to minimize Voltage Sags on the grid. Thereby, a vector controlled structure was built on the rotating dq-coordinate system with the combination of voltage control and the current control. The proposed DVR control method is modelled using MATLAB-Simulink. It is tested using balanced/unbalanced voltage sags as well as fluctuant and distorted voltages. As a result, by using this controlling method, the dynamic characteristics of the system have been improved significantly. The system performed with higher accuracy, faster response and lower distortion in the voltage sags compensation. The paper presents real time experimental results to verify the performance of the proposed method in real environments.
High voltage bus and auxiliary heater control system for an electric or hybrid vehicle
Murty, Balarama Vempaty
2000-01-01
A control system for an electric or hybrid electric vehicle includes a vehicle system controller and a control circuit having an electric immersion heater. The heater is electrically connected to the vehicle's high voltage bus and is thermally coupled to a coolant loop containing a heater core for the vehicle's climate control system. The system controller responds to cabin heat requests from the climate control system by generating a pulse width modulated signal that is used by the control circuit to operate the heater at a duty cycle appropriate for the amount of cabin heating requested. The control system also uses the heater to dissipate excess energy produced by an auxiliary power unit and to provide electric braking when regenerative braking is not desirable and manual braking is not necessary. The control system further utilizes the heater to provide a safe discharge of a bank of energy storage capacitors following disconnection of the battery or one of the high voltage connectors used to transmit high voltage operating power to the various vehicle systems. The control circuit includes a high voltage clamping circuit that monitors the voltage on the bus and operates the heater to clamp down the bus voltage when it exceeds a pre-selected maximum voltage. The control system can also be used to phase in operation of the heater when the bus voltage exceeds a lower threshold voltage and can be used to phase out the auxiliary power unit charging and regenerative braking when the battery becomes fully charged.
Complete low power controller for high voltage power systems
International Nuclear Information System (INIS)
Sumner, R.; Blanar, G.
1997-01-01
The MHV100 is a custom CMOS integrated circuit, developed for the AMS experiment. It provides complete control for a single channel high voltage (HV) generator and integrates all the required digital communications, D to A and A to D converters, the analog feedback loop and output drivers. This chip has been designed for use in both distributed high voltage systems or for low cost single channel high voltage systems. The output voltage and current range is determined by the external components
Development of Multi-Functional Voltage Restore System
Suzuki, Satoshi; Ueda, Yoshinobu; Koganezawa, Takehisa; Ogihara, Yoshinori; Mori, Kenjiro; Fukazu, Naoaki
Recently, with the dawn of the electric deregulation, the installation of distributed generation with power electronics device has grown. This current causes a greater concern of power quality, primarily voltage disturbance for power companies, and their interest in power quality is peaking. Utilities are also interested in keeping their customers satisfied, as well as keeping them on-line and creating more revenue for the utility. As a countermeasure against the above surroundings, a variety type of devices based on power electronics has been developed to protect customers' load from power line voltage disturbance. One of them is the series type voltage restore. The series device is an active device, designed to provide a pure sinusoidal load voltage at all times, correcting voltage disturbance. Series type device compensates for voltage anomalies by inserting the ‘missing’ voltage onto the line through insertion transformer and inverter. This paper shows the setting guideline of target level to compensate voltage disturbance, that is, voltage dip, voltage harmonics, voltage imbalance and voltage flicker, and the design approach of the prototype of series voltage restores to accomplish the required compensation level. The prototype system gives satisfactory compensation performance through evaluation tests, which confirm the validity and effectiveness of the system.
A fast high-voltage current-peak detection system for the ALICE transition radiation detector
Energy Technology Data Exchange (ETDEWEB)
Verclas, Robert [Physikalisches Institut, Ruprecht-Karls-Universitaet Heidelberg (Germany); Collaboration: ALICE-Collaboration
2016-07-01
During LHC operation in run 1, the gaseous detectors of ALICE occasionally experienced simultaneous trips in their high voltage which affected the majority of the high voltage channels. These trips are caused by large anode currents in the detector and are potentially related to LHC machine operations. We developed and installed a fast current-peak detection system for the ALICE Transition Radiation Detector. This system is based on FPGA technology and monitors 144 out 522 high voltage channels minimally invasively at a maximum readout rate of 2 MHz. It is an integral part of the LHC beam monitoring system. We report on the latest status.
Maximum Power Point Tracking of Photovoltaic System for Traffic Light Application
Directory of Open Access Journals (Sweden)
Riza Muhida
2013-07-01
Full Text Available Photovoltaic traffic light system is a significant application of renewable energy source. The development of the system is an alternative effort of local authority to reduce expenditure for paying fees to power supplier which the power comes from conventional energy source. Since photovoltaic (PV modules still have relatively low conversion efficiency, an alternative control of maximum power point tracking (MPPT method is applied to the traffic light system. MPPT is intended to catch up the maximum power at daytime in order to charge the battery at the maximum rate in which the power from the battery is intended to be used at night time or cloudy day. MPPT is actually a DC-DC converter that can step up or down voltage in order to achieve the maximum power using Pulse Width Modulation (PWM control. From experiment, we obtained the voltage of operation using MPPT is at 16.454 V, this value has error of 2.6%, if we compared with maximum power point voltage of PV module that is 16.9 V. Based on this result it can be said that this MPPT control works successfully to deliver the power from PV module to battery maximally.
Directory of Open Access Journals (Sweden)
Yong Chen
2016-01-01
Full Text Available The Modular Multilevel Converters (MMC have been a spotlight for the high voltage and high power transmission systems. In the VSC-HVDC (High Voltage Direct Current based on Voltage Source Converter transmission system, the energy of DC link is stored in the distributed capacitors, and the difference of capacitors in parameters and charge rates causes capacitor voltage balance which affects the safety and stability of HVDC system. A method of MMC based on the expert system for reducing the frequency of the submodules (SMs of the IGBT switching frequency is proposed. Firstly, MMC with 51 levels for HVDC is designed. Secondly, the nearest level control (NLC for 51-level MMC is introduced. Thirdly, a modified capacitor voltage balancing method based on expert system for MMC-based HVDC transmission system is proposed. Finally, a simulation platform for 51-level Modular Multilevel Converter is constructed by using MATLAB/SIMULINK. The results indicate that the strategy proposed reduces the switching frequency on the premise of keeping submodule voltage basically identical, which greatly reduces the power losses for MMC-HVDC system.
LED-Based High-Voltage Lines Warning System
Directory of Open Access Journals (Sweden)
Eldar MUSA
2013-04-01
Full Text Available LED-based system, running with the current of high-voltage lines and converting the current flowing through the line into the light by using a toroid transformer, has been developed. The transformer’s primary winding is constituted by the high voltage power line. Toroidal core consists of two equal parts and the secondary windings are evenly placed on these two parts. The system is mounted on the high-voltage lines as a clamp. The secondary winding ends are connected in series by the connector on the clamp. LEDs are supplied by the voltage at the ends of secondary. Current flowing through highvoltage transmission lines is converted to voltage by the toroidal transformer and the light emitting LEDs are supplied with this voltage. The theory of the conversion of the current flowing through the line into the light is given. The system, running with the current of the line and converting the current into the light, has been developed. System has many application areas such as warning high voltage lines (warning winches to not hinder the high-voltage lines when working under the lines, warning planes to not touch the high-voltage lines, remote measurement of high-voltage line currents, and local illumination of the line area
Modeling and simulation of dynamic voltage restorer in power system
International Nuclear Information System (INIS)
Abdel Aziz, M.A.A.M.
2012-01-01
There are many loads subjected to several Power Quality Problems such as voltage sags/swells, unbalance, harmonics distortion, and short interruption. These loads encompass a wide range of equipment which are very sensitive to voltage disturbances. The Dynamic Voltage Restorer (DVR) has recently been introduced to protect sensitive loads from voltage sags and other voltage disturbances in addition to this, it mitigates current harmonics distortion. It is a series connected power electronic based device. It is considered as one of the most efficient and effective solutions. Its appeal includes smaller size and fast dynamic response to disturbances. This work describes a proposal of the DVR to improve power quality distribution (medium voltage) system. The control of the compensation voltage and harmonics cancellation in the DVR is based on Adaptive Noise Canceling (ANC) technique. Simulation results carried out by PSCAD/EMTDC to investigate the performance of the proposed method.
Energy Storage System with Voltage Equalization Strategy for Wind Energy Conversion
Directory of Open Access Journals (Sweden)
Cheng-Tao Tsai
2012-07-01
Full Text Available In this paper, an energy storage system with voltage equalization strategy for wind energy conversion is presented. The proposed energy storage system provides a voltage equalization strategy for series-connected lead-acid batteries to increase their total storage capacity and lifecycle. In order to draw the maximum power from the wind energy, a perturbation-and-observation method and digital signal processor (DSP are incorporated to implement maximum power point tracking (MPPT algorithm and power regulating scheme. In the proposed energy storage system, all power switches have zero-voltage-switching (ZVS feature at turn-on transition. Therefore, the conversion efficiency can be increased. Finally, a prototype energy storage system for wind energy conversion is built and implemented. Experimental results have verified the performance and feasibility of the proposed energy storage system for wind energy conversion.
Methods of computing steady-state voltage stability margins of power systems
Chow, Joe Hong; Ghiocel, Scott Gordon
2018-03-20
In steady-state voltage stability analysis, as load increases toward a maximum, conventional Newton-Raphson power flow Jacobian matrix becomes increasingly ill-conditioned so power flow fails to converge before reaching maximum loading. A method to directly eliminate this singularity reformulates the power flow problem by introducing an AQ bus with specified bus angle and reactive power consumption of a load bus. For steady-state voltage stability analysis, the angle separation between the swing bus and AQ bus can be varied to control power transfer to the load, rather than specifying the load power itself. For an AQ bus, the power flow formulation is only made up of a reactive power equation, thus reducing the size of the Jacobian matrix by one. This reduced Jacobian matrix is nonsingular at the critical voltage point, eliminating a major difficulty in voltage stability analysis for power system operations.
Impact of the Voltage Dips in Shipboard Microgrid Power Systems
DEFF Research Database (Denmark)
Liu, Wenzhao; Guerrero, Josep M.; Savaghebi, Mehdi
2017-01-01
Voltage and frequency transient variations are the most common power quality issues in a ship microgrid system. In this paper, the impacts of the voltage dips induced by the sudden-load of ballast pump are analyzed in detail for the ship power systems. Several relevant ship power quality standards...
Development of a terminal voltage stabilization system for the FOTIA ...
Indian Academy of Sciences (India)
Abstract. A terminal voltage stabilization system for the folded tandem ion accelerator (FOTIA) was developed and is in continuous use. The system achieves good voltage stabilization, eliminates ground loops and noise interference. It incorporates a correcting circuit for compensating the mains frequency variations in the ...
Robust Fallback Scheme for the Danish Automatic Voltage Control System
DEFF Research Database (Denmark)
Qin, Nan; Dmitrova, Evgenia; Lund, Torsten
2015-01-01
This paper proposes a fallback scheme for the Danish automatic voltage control system. It will be activated in case of the local station loses telecommunication to the control center and/or the local station voltage violates the acceptable operational limits. It cuts in/out switchable and tap...... power system....
Automatic Voltage Control (AVC) System under Uncertainty from Wind Power
DEFF Research Database (Denmark)
Qin, Nan; Abildgaard, Hans; Flynn, Damian
2016-01-01
An automatic voltage control (AVC) system maintains the voltage profile of a power system in an acceptable range and minimizes the operational cost by coordinating the regulation of controllable components. Typically, all of the parameters in the optimization problem are assumed to be certain...... and constant in the decision making process. However, for high shares of wind power, uncertainty in the decision process due to wind power variability may result in an infeasible AVC solution. This paper proposes a voltage control approach which considers the voltage uncertainty from wind power productions....... The proposed method improves the performance and the robustness of a scenario based approach by estimating the potential voltage variations due to fluctuating wind power production, and introduces a voltage margin to protect the decision against uncertainty for each scenario. The effectiveness of the proposed...
Construction of test-bed system of voltage management system to ...
African Journals Online (AJOL)
Construction of test-bed system of voltage management system to apply physical power system. ... Journal of Fundamental and Applied Sciences ... system of voltage management system (VMS) in order to apply physical power system.
Directory of Open Access Journals (Sweden)
Jaw-Kuen Shiau
2015-04-01
Full Text Available This paper presents the design of a fuzzy-logic-based voltage-regulated solar power maximum power point tracking (MPPT system for applications involving hybrid power systems. The system contains a solar power system and battery as the primary and secondary power sources, respectively. The solar system alone supplies power to the electric motor and maintains the output voltage at a predetermined level when it has sufficient power. When the solar power is insufficient, the solar system is operated at its maximum power point (MPP and the battery is engaged to compensate for the insufficiency. First, a variant of the incremental conductance MPP condition was established. Under the MPP condition, the voltage-regulated MPPT system was formulated as a feedback control system, where the MPP condition and voltage regulation requirements were used as the system inputs. Next, a fuzzy controller was developed to perform the voltage-regulated MPPT function for the hybrid power system. A simulation model based on Matrix laboratory (MATLAB/SIMULINK (a block diagram environment for multi-domain simulation and model-based design and a piecewise linear electric circuit simulation (PLECS tool for controlling the dc motor velocity was developed to verify the voltage-regulated solar power MPPT system.
Voltage Quench Dynamics of a Kondo System.
Antipov, Andrey E; Dong, Qiaoyuan; Gull, Emanuel
2016-01-22
We examine the dynamics of a correlated quantum dot in the mixed valence regime. We perform numerically exact calculations of the current after a quantum quench from equilibrium by rapidly applying a bias voltage in a wide range of initial temperatures. The current exhibits short equilibration times and saturates upon the decrease of temperature at all times, indicating Kondo behavior both in the transient regime and in the steady state. The time-dependent current saturation temperature connects the equilibrium Kondo temperature to a substantially increased value at voltages outside of the linear response. These signatures are directly observable by experiments in the time domain.
DEFF Research Database (Denmark)
Ding, Tao; Kou, Yu; Yang, Yongheng
2017-01-01
. However, the intermittency of solar PV energy (e.g., due to passing clouds) may affect the PV generation in the district distribution network. To address this issue, the voltage magnitude constraints under the cloud shading conditions should be taken into account in the optimization model, which can......As photovoltaic (PV) integration increases in distribution systems, to investigate the maximum allowable PV integration capacity for a district distribution system becomes necessary in the planning phase, an optimization model is thus proposed to evaluate the maximum PV integration capacity while...
Local Dynamic Reactive Power for Correction of System Voltage Problems
Energy Technology Data Exchange (ETDEWEB)
Kueck, John D [ORNL; Rizy, D Tom [ORNL; Li, Fangxing [ORNL; Xu, Yan [ORNL; Li, Huijuan [University of Tennessee, Knoxville (UTK); Adhikari, Sarina [ORNL; Irminger, Philip [ORNL
2008-12-01
Distribution systems are experiencing outages due to a phenomenon known as local voltage collapse. Local voltage collapse is occurring in part because modern air conditioner compressor motors are much more susceptible to stalling during a voltage dip than older motors. These motors can stall in less than 3 cycles (.05s) when a fault, such as on the sub-transmission system, causes voltage to sag to 70 to 60%. The reasons for this susceptibility are discussed in the report. During the local voltage collapse, voltages are depressed for a period of perhaps one or two minutes. There is a concern that these local events are interacting together over larger areas and may present a challenge to system reliability. An effective method of preventing local voltage collapse is the use of voltage regulation from Distributed Energy Resources (DER) that can supply or absorb reactive power. DER, when properly controlled, can provide a rapid correction to voltage dips and prevent motor stall. This report discusses the phenomenon and causes of local voltage collapse as well as the control methodology we have developed to counter voltage sag. The problem is growing because of the use of low inertia, high efficiency air conditioner (A/C) compressor motors and because the use of electric A/C is growing in use and becoming a larger percentage of system load. A method for local dynamic voltage regulation is discussed which uses reactive power injection or absorption from local DER. This method is independent, rapid, and will not interfere with conventional utility system voltage control. The results of simulations of this method are provided. The method has also been tested at the ORNL s Distributed Energy Communications and Control (DECC) Laboratory using our research inverter and synchronous condenser. These systems at the DECC Lab are interconnected to an actual distribution system, the ORNL distribution system, which is fed from TVA s 161kV sub-transmission backbone. The test results
International Nuclear Information System (INIS)
Park, Jae-Do; Lee, Hohyun; Bond, Matthew
2014-01-01
Highlights: • Feedforward MPPT scheme for uninterrupted TEG energy harvesting is suggested. • Temperature sensors are used to avoid current measurement or source disconnection. • MPP voltage reference is generated based on OCV vs. temperature differential model. • Optimal operating condition is maintained using hysteresis controller. • Any type of power converter can be used in the proposed scheme. - Abstract: In this paper, a thermoelectric generator (TEG) energy harvesting system with a temperature-sensor-based maximum power point tracking (MPPT) method is presented. Conventional MPPT algorithms for photovoltaic cells may not be suitable for thermoelectric power generation because a significant amount of time is required for TEG systems to reach a steady state. Moreover, complexity and additional power consumption in conventional circuits and periodic disconnection of power source are not desirable for low-power energy harvesting applications. The proposed system can track the varying maximum power point (MPP) with a simple and inexpensive temperature-sensor-based circuit without instantaneous power measurement or TEG disconnection. This system uses TEG’s open circuit voltage (OCV) characteristic with respect to temperature gradient to generate a proper reference voltage signal, i.e., half of the TEG’s OCV. The power converter controller maintains the TEG output voltage at the reference level so that the maximum power can be extracted for the given temperature condition. This feedforward MPPT scheme is inherently stable and can be implemented without any complex microcontroller circuit. The proposed system has been validated analytically and experimentally, and shows a maximum power tracking error of 1.15%
Zou, Yunlong; Holmes, Russell
2013-03-01
Transition metal oxides including molybdenum oxide (MoOx) are characterized by large work functions and deep energy levels relative to the organic semiconductors used in photovoltaic cells (OPVs). These materials have been used in OPVs as interlayers between the indium-tin-oxide anode and the active layers to increase the open-circuit voltage (VOC) and power conversion efficiency. We examine the role of MoOx in determining the maximum achievable VOC in planar heterojunction OPVs based on the donor-acceptor pairing of boron subphthalocyanine chloride (SubPc) and C60. While causing minor changes in VOC at room temperature, the inclusion of MoOx significantly changes the temperature dependence of VOC. Devices containing no interlayer show a maximum VOC\\ of 1.2 V, while devices containing MoOx show no saturation in VOC, reaching a value of >1.4 V at 110 K. We propose that the MoOx-SubPc interface forms a dissociating Schottky junction that provides an additional contribution to VOC at low temperature. Separate measurements of photoluminescence confirm that excitons in SubPc can be quenched by MoOx. Charge transfer at this interface is by hole extraction from SubPc to MoOx, and this mechanism favors donors with a deep highest occupied molecular orbital (HOMO) energy level. Consistent with this expectation, the temperature dependence of VOC for devices constructed using a donor with a shallower HOMO level, e.g. copper phthalocyanine, is independent of the presence of MoOx.
Development of anode high voltage power supply system for ECRH of HL-2A tokamak
International Nuclear Information System (INIS)
Chen Wenguang
2009-01-01
The anode high voltage power supply system consist of DC high-voltage power supply (HVPS) and pulse modulator. SCR is used to vary AC input voltage of the step-up transformer by controlling the trigger phase in the HVPS, and regulate the DC output voltage linearly at the potential of low-end via BJT, Dual closed-loop control technology is applied in the controller, and its maximum output is at 30kV and 130mA. Tetrode is the core component of the modulator. The circuit design is optimized by using the simulation software. Test and HL-2A discharge experimental results show that the power supply system is designed with some characteristics of output scale widely, low ripple and modulate quickly. (authors)
Maximum power point tracking for PV systems under partial shading conditions using current sweeping
International Nuclear Information System (INIS)
Tsang, K.M.; Chan, W.L.
2015-01-01
Highlights: • A novel approach for tracking the maximum power point of photovoltaic systems. • Able to handle both the uniform insolation and partial shading conditions. • Maximum power point tracking based on current sweeping. - Abstract: Partial shading on photovoltaic (PV) arrays causes multiple peaks on the output power–voltage characteristic curve and local searching technique such as perturb and observe (P&O) method could easily fail in searching for the global maximum. Moreover, existing global searching techniques are still not very satisfactory in terms of speed and implementation complexity. In this paper, a fast global maximum power point (MPPT) tracking method which is using current sweeping for photovoltaic arrays under partial shading conditions is proposed. Unlike conventional approach, the proposed method is current based rather than voltage based. The initial maximum power point will be derived based on a current sweeping test and the maximum power point can be enhanced by a finer local search. The speed of the global search is mainly governed by the apparent time constant of the PV array and the generation of a fast current sweeping test. The fast current sweeping test can easily be realized by a DC/DC boost converter with a very fast current control loop. Experimental results are included to demonstrate the effectiveness of the proposed global searching scheme
Erbay, Celal; Carreon-Bautista, Salvador; Sanchez-Sinencio, Edgar; Han, Arum
2014-12-02
Microbial fuel cell (MFC) that can directly generate electricity from organic waste or biomass is a promising renewable and clean technology. However, low power and low voltage output of MFCs typically do not allow directly operating most electrical applications, whether it is supplementing electricity to wastewater treatment plants or for powering autonomous wireless sensor networks. Power management systems (PMSs) can overcome this limitation by boosting the MFC output voltage and managing the power for maximum efficiency. We present a monolithic low-power-consuming PMS integrated circuit (IC) chip capable of dynamic maximum power point tracking (MPPT) to maximize the extracted power from MFCs, regardless of the power and voltage fluctuations from MFCs over time. The proposed PMS continuously detects the maximum power point (MPP) of the MFC and matches the load impedance of the PMS for maximum efficiency. The system also operates autonomously by directly drawing power from the MFC itself without any external power. The overall system efficiency, defined as the ratio between input energy from the MFC and output energy stored into the supercapacitor of the PMS, was 30%. As a demonstration, the PMS connected to a 240 mL two-chamber MFC (generating 0.4 V and 512 μW at MPP) successfully powered a wireless temperature sensor that requires a voltage of 2.5 V and consumes power of 85 mW each time it transmit the sensor data, and successfully transmitted a sensor reading every 7.5 min. The PMS also efficiently managed the power output of a lower-power producing MFC, demonstrating that the PMS works efficiently at various MFC power output level.
International Nuclear Information System (INIS)
Awan, M.M.A.; Awan, F.G.
2017-01-01
Extraction of maximum power from PV (Photovoltaic) cell is necessary to make the PV system efficient. Maximum power can be achieved by operating the system at MPP (Maximum Power Point) (taking the operating point of PV panel to MPP) and for this purpose MPPT (Maximum Power Point Trackers) are used. There are many tracking algorithms/methods used by these trackers which includes incremental conductance, constant voltage method, constant current method, short circuit current method, PAO (Perturb and Observe) method, and open circuit voltage method but PAO is the mostly used algorithm because it is simple and easy to implement. PAO algorithm has some drawbacks, one is low tracking speed under rapid changing weather conditions and second is oscillations of PV systems operating point around MPP. Little improvement is achieved in past papers regarding these issues. In this paper, a new method named 'Decrease and Fix' method is successfully introduced as improvement in PAO algorithm to overcome these issues of tracking speed and oscillations. Decrease and fix method is the first successful attempt with PAO algorithm for stability achievement and speeding up of tracking process in photovoltaic system. Complete standalone photovoltaic system's model with improved perturb and observe algorithm is simulated in MATLAB Simulink. (author)
Directory of Open Access Journals (Sweden)
Arnautović Dušan
2014-01-01
Full Text Available The paper, discusses the possibility to use coordinated Q-V controller (CQVC to perform secondary voltage control at the power plant level. The CQVC performs the coordination of the synchronous generators' (SG reactive power outputs in order to maintain the same total reactive power delivered by the steam power plant (SPP, while at the same time maintaining a constant voltage with programmed reactive droop characteristic at the SPP HV busbar. This busbar is the natural pilot node for secondary voltage control at HV level as the node with maximum power production and maximum power consumption. In addition to voltage control, the CQVC maintains the uniform allocation of reactive power reserves at all SGs in the power plant. This is accomplished by setting the reactive power of each SG at given operating point in accordance to the available reactive power of the same SG at that point. Different limitations imposed by unit's and plant equipment are superimposed on original SG operating chart (provided by the manufacturer in order to establish realistic limits of SG operation at given operating point. The CQVC facilitates: i practical implementation of secondary voltage control in power system, as it is capable of ensuring delivery of reactive power as requested by regional/voltage control while maintaining voltage at system pilot node, ii the full deployment of available reactive power of SGs which in turn contributes to system stability, iii assessment of the reactive power impact/contribution of each generator in providing voltage control as ancillary service. Furthermore, it is also possible to use CQVC to pricing reactive power production cost at each SG involved and to design reactive power bidding structure for transmission network devices by using recorded data. Practical exploitation experience acquired during CQVC continuous operation for over two years enabled implementation of the optimal setting of reference voltage and droop on daily
Low cost photomultiplier high-voltage readout system
International Nuclear Information System (INIS)
Oxoby, G.J.; Kunz, P.F.
1976-10-01
The Large Aperture Solenoid Spectrometer (LASS) at Stanford Linear Accelerator Center (SLAC) requires monitoring over 300 voltages. This data is recorded on magnetic tapes along with the event data. It must also be displayed so that operators can easily monitor and adjust the voltages. A low-cost high-voltage readout system has been implemented to offer stand-alone digital readout capability as well as fast data transfer to a host computer. The system is flexible enough to permit use of a DVM or ADC and commercially available analogue multiplexers
Maximum power point tracking: a cost saving necessity in solar energy systems
Energy Technology Data Exchange (ETDEWEB)
Enslin, J H.R. [Stellenbosch Univ. (South Africa). Dept. of Electrical and Electronic Engineering
1992-12-01
A well engineered renewable remote energy system, utilizing the principal of Maximum Power Point Tracking (MPPT) can improve cost effectiveness, has a higher reliability and can improve the quality of life in remote areas. A high-efficient power electronic converter, for converting the output voltage of a solar panel, or wind generator, to the required DC battery bus voltage has been realized. The converter is controlled to track the maximum power point of the input source under varying input and output parameters. Maximum power point tracking for relative small systems is achieved by maximization of the output current in a battery charging regulator, using an optimized hill-climbing, inexpensive microprocessor based algorithm. Through practical field measurements it is shown that a minimum input source saving of between 15 and 25% on 3-5 kWh/day systems can easily be achieved. A total cost saving of at least 10-15% on the capital cost of these systems are achievable for relative small rating Remote Area Power Supply (RAPS) systems. The advantages at large temperature variations and high power rated systems are much higher. Other advantages include optimal sizing and system monitor and control. (author).
Voltage Control System of A DC Generator Using PLC
Subrata CHATTOPADHYAY; Sagarika PAL
2008-01-01
The voltage control system of a DC generator may suffer from high frequency oscillations without offset or low frequency oscillation with offset. A PID controller can eliminate both these errors. In the present paper, the voltage control system of a DC generator using a PLC based PID controller has been designed. Operation of PLC as a continuous controller has been described and the load characteristic of DC generator with and without controller have been determined experimentally and reporte...
A Transformerless Medium Voltage Multiphase Motor Drive System
Directory of Open Access Journals (Sweden)
Dan Wang
2016-04-01
Full Text Available A multiphase motor has several major advantages, such as high reliability, fault tolerance, and high power density. It is a critical issue to develop a reliable and efficient multiphase motor drive system. In this paper, a transformerless voltage source converter-based drive system for a medium-voltage (MV multiphase motor is proposed. This drive converter employs cascaded H-bridge rectifiers loaded by H-bridge inverters as the interface between the grid and multiphase motor. The cascaded H-bridge rectifier technique makes the drive system able to be directly connected to the MV grid without the phase-shifting transformer because it can offset the voltage level gap between the MV grid and the semiconductor devices, provide near-sinusoidal AC terminal voltages without filters, and draw sinusoidal line current from the grid. Based on a digital signal processor (DSP, a complete improved Phase Disposition Pulse Width Modulation (PD-PWM method is developed to ensure the individual DC-link capacitor voltage balancing for enhancing the controllability and limiting the voltage and power stress on the H-bridge cells. A downscaled prototype is designed and developed based on a nine-phase motor. The experimental results verify the excellent performances of the proposed drive system and control strategy in steady-state and variant-frequency startup operations.
Optical control system for high-voltage terminals
International Nuclear Information System (INIS)
Bicek, J.J.
1978-01-01
An optical control system for the control of devices in the terminal of an electrostatic accelerator includes a laser that is modulated by a series of preselected codes produced by an encoder. A photodiode receiver is placed in the laser beam at the high-voltage terminal of an electrostatic accelerator. A decoder connected to the photodiode decodes the signals to provide control impulses for a plurality of devices at the high voltage of the terminal
Microprocessor-controlled step-down maximum-power-point tracker for photovoltaic systems
Mazmuder, R. K.; Haidar, S.
1992-12-01
An efficient maximum power point tracker (MPPT) has been developed and can be used with a photovoltaic (PV) array and a load which requires lower voltage than the PV array voltage to be operated. The MPPT makes the PV array to operate at maximum power point (MPP) under all insolation and temperature, which ensures the maximum amount of available PV power to be delivered to the load. The performance of the MPPT has been studied under different insolation levels.
Grid Integration of Single Stage Solar PV System using Three-level Voltage Source Converter
Hussain, Ikhlaq; Kandpal, Maulik; Singh, Bhim
2016-08-01
This paper presents a single stage solar PV (photovoltaic) grid integrated power generating system using a three level voltage source converter (VSC) operating at low switching frequency of 900 Hz with robust synchronizing phase locked loop (RS-PLL) based control algorithm. To track the maximum power from solar PV array, an incremental conductance algorithm is used and this maximum power is fed to the grid via three-level VSC. The use of single stage system with three level VSC offers the advantage of low switching losses and the operation at high voltages and high power which results in enhancement of power quality in the proposed system. Simulated results validate the design and control algorithm under steady state and dynamic conditions.
Lightning Overvoltage on Low-Voltage Distribution System
Michishita, Koji
The portion of the faults of a medium-voltage line, cause by lightning, tends to increase with often reaching beyond 30%. However, due to the recent progress of the lightning protection design, the number of faults has decreased to 1/3 of that at 30 years ago. As for the low-voltage distribution line, the fault rate has been estimated primarily, although the details of the overvoltages have not been studied yet. For the further development of highly information-oriented society, improvement of reliability of electric power supply to the appliance in a low-voltage customer will be socially expected. Therefore, it is important to establish effective lightning protection design of the low-voltage distribution system, defined to be composed of lines having mutual interaction on the customers' electric circuits, such as a low-voltage distribution line, an antenna line and a telecommunication line. In this report, the author interprets the recent research on the lightning overvoltage on a low-voltage distribution system.
Computer applications: Automatic control system for high-voltage accelerator
International Nuclear Information System (INIS)
Bryukhanov, A.N.; Komissarov, P.Yu.; Lapin, V.V.; Latushkin, S.T.. Fomenko, D.E.; Yudin, L.I.
1992-01-01
An automatic control system for a high-voltage electrostatic accelerator with an accelerating potential of up to 500 kV is described. The electronic apparatus on the high-voltage platform is controlled and monitored by means of a fiber-optic data-exchange system. The system is based on CAMAC modules that are controlled by a microprocessor crate controller. Data on accelerator operation are represented and control instructions are issued by means of an alphanumeric terminal. 8 refs., 6 figs
Novel TPPO Based Maximum Power Point Method for Photovoltaic System
Directory of Open Access Journals (Sweden)
ABBASI, M. A.
2017-08-01
Full Text Available Photovoltaic (PV system has a great potential and it is installed more when compared with other renewable energy sources nowadays. However, the PV system cannot perform optimally due to its solid reliance on climate conditions. Due to this dependency, PV system does not operate at its maximum power point (MPP. Many MPP tracking methods have been proposed for this purpose. One of these is the Perturb and Observe Method (P&O which is the most famous due to its simplicity, less cost and fast track. But it deviates from MPP in continuously changing weather conditions, especially in rapidly changing irradiance conditions. A new Maximum Power Point Tracking (MPPT method, Tetra Point Perturb and Observe (TPPO, has been proposed to improve PV system performance in changing irradiance conditions and the effects on characteristic curves of PV array module due to varying irradiance are delineated. The Proposed MPPT method has shown better results in increasing the efficiency of a PV system.
Voltage Quality Improvement Using Solar Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Denisa Galzina
2015-06-01
This paper briefly shows the methods of power quality improvement, and then the results of on-site power quality measurements in the grid before and after the connection of the solar photovoltaic system.
Stator insulation systems for medium voltage PWM drives fed motors
International Nuclear Information System (INIS)
Gao, G.; Chen, W.
2005-01-01
This paper presents the partial results of a research project that studied the impact of medium voltage PWM ASD (adjustable speed drives) on motor stator insulation system. The findings from this study/ investigation have aided designers to improve the robustness of the insulation system used for ASD-fed motors, based on accelerated laboratory tests. (author)
Harmonics and voltage stability analysis in power systems including ...
Indian Academy of Sciences (India)
R. Narasimhan (Krishtel eMaging) 1461 1996 Oct 15 13:05:22
two parameters affecting power quality – harmonics and voltage stability. ... is necessary to pay attention to energy system stability in the planning, management, and ... where k ∈ {m, m + 1,... ,n} and n is total number of the buses in the system.
Energy Technology Data Exchange (ETDEWEB)
Shen, Tengming [Fermilab; Ye, Liyang [NCSU, Raleigh; Turrioni, Daniele [Fermilab; Li, Pei [Fermilab
2015-01-01
Small insert coils have been built using a multifilamentary Bi2Sr2CaCu2Ox round wire, and characterized in background fields to explore the quench behaviors and limits of Bi2Sr2CaCu2Ox superconducting magnets, with an emphasis on assessing the impact of slow normal zone propagation on quench detection. Using heaters of various lengths to initiate a small normal zone, a coil was quenched safely more than 70 times without degradation, with the maximum coil temperature reaching 280 K. Coils withstood a resistive voltage of tens of mV for seconds without quenching, showing the high stability of these coils and suggesting that the quench detection voltage shall be greater than 50 mV to not to falsely trigger protection. The hot spot temperature for the resistive voltage of the normal zone to reach 100 mV increases from ~40 K to ~80 K with increasing the operating wire current density Jo from 89 A/mm2 to 354 A/mm2 whereas for the voltage to reach 1 V, it increases from ~60 K to ~140 K, showing the increasing negative impact of slow normal zone propagation on quench detection with increasing Jo and the need to limit the quench detection voltage to < 1 V. These measurements, coupled with an analytical quench model, were used to access the impact of the maximum allowable voltage and temperature upon quench detection on the quench protection, assuming to limit the hot spot temperature to <300 K.
Voltage Control System of A DC Generator Using PLC
Directory of Open Access Journals (Sweden)
Subrata CHATTOPADHYAY
2008-06-01
Full Text Available The voltage control system of a DC generator may suffer from high frequency oscillations without offset or low frequency oscillation with offset. A PID controller can eliminate both these errors. In the present paper, the voltage control system of a DC generator using a PLC based PID controller has been designed. Operation of PLC as a continuous controller has been described and the load characteristic of DC generator with and without controller have been determined experimentally and reported in this paper.
Stability of DC Voltage Droop Controllers in VSC HVDC Systems
DEFF Research Database (Denmark)
Thams, Florian; Suul, Jon Are; D’Arco, Salvatore
2015-01-01
Future multi-terminal HVDC systems are expected to utilize dc voltage droop controllers and several control implementations have been proposed in literature. This paper first classifies possible dc droop implementations in a simple framework. Then, the small-signal stability of a VSC-based conver......Future multi-terminal HVDC systems are expected to utilize dc voltage droop controllers and several control implementations have been proposed in literature. This paper first classifies possible dc droop implementations in a simple framework. Then, the small-signal stability of a VSC...
Voltage control in the future power transmission systems
DEFF Research Database (Denmark)
Qin, Nan
Wind energy in Denmark covers 42% of the total power consumption in 2015, and will share up to 50% by 2020. Consequently, the conventional power plants are decommissioning. Under the progress of the green transition, the national decision leads to underground many overhead lines in the future...... stages. The voltage uncertainty caused by the wind power forecasting errors is estimated, which is applied as a voltage security margin to further constrain the voltage magnitude in the optimization problem. The problem under the uncertainty is therefore converted to a deterministic problem, which...... to ensure a highly reliable transmission, e.g. balancing the generation and the consumption in large geographic regions, the exchange capacities will be enlarged by upgrading the interconnections. The Danish power system, the electricity transportation hub between the Nordic and continental European systems...
Directory of Open Access Journals (Sweden)
Yongchun Yang
2018-04-01
Full Text Available The modular multilevel converter (MMC, as a new type of voltage source converter, is increasingly used because it is a distributed storage system. There are many advantages of using the topological structure of the MMC on a unified power quality controller (UPQC, and voltage sag mitigation is an important use of the MMC energy storage system for the power quality compensation process. In this paper, based on the analysis of the topology of the MMC, the essence of energy conversion in a UPQC of voltage sag compensation is analyzed; then, the energy storage characteristics are calculated and analyzed to determine the performance index of voltage sag compensation; in addition, the simulation method is used to verify the voltage sag compensation characteristics of the UPQC; finally, an industrial prototype of the UPQC based on an MMC for 10 kV of medium voltage distribution network has been developed, and the basic functions of UPQC have been tested.
International Nuclear Information System (INIS)
Kareim, Ameer A; Mansor, Muhamad Bin
2013-01-01
The aim of this paper is to improve efficiency of maximum power point tracking (MPPT) for PV systems. The Support Vector Machine (SVM) was proposed to achieve the MPPT controller. The theoretical, the perturbation and observation (P and O), and incremental conductance (IC) algorithms were used to compare with proposed SVM algorithm. MATLAB models for PV module, theoretical, SVM, P and O, and IC algorithms are implemented. The improved MPPT uses the SVM method to predict the optimum voltage of the PV system in order to extract the maximum power point (MPP). The SVM technique used two inputs which are solar radiation and ambient temperature of the modeled PV module. The results show that the proposed SVM technique has less Root Mean Square Error (RMSE) and higher efficiency than P and O and IC methods.
Intelligent distributed voltage control system for smart grid application
Energy Technology Data Exchange (ETDEWEB)
Sajadi, Amirhossein [Warsaw Univ. of Technology (Poland); Ariatabar, Mitra [RWTH Aachen Univ. (Germany)
2012-07-01
Increasing penetration of the renewable energy source (RES) units in distribution networks particularly due to nonlinear and unpredictable nature of renewable units brings up new challenges in different aspects of electricity network, which leads to more complex power systems. Multi-agent system is consisting of agents which are capable to perceive environment that they are located in and to reacts with each other by communication infrastructure in order to achieve overall goals. In this paper an approach to control the voltage based on in the power distribution system is proposed and discussed. Therefore, a multi-agent system has been integrated with artificial intelligence to come up with fuzzy multi-agent based system. The proposed control scheme is deployed to a smart distribution system consisting distribution generation units, modelled in MATLAB/Simulink, to evaluate its effectiveness. The simulation results show how proposed system can regulate voltage in smart distribution feeders. (orig.)
Energy Technology Data Exchange (ETDEWEB)
Syafaruddin; Hiyama, Takashi [Department of Computer Science and Electrical Engineering of Kumamoto University, 2-39-1 Kurokami, Kumamoto 860-8555 (Japan); Karatepe, Engin [Department of Electrical and Electronics Engineering of Ege University, 35100 Bornova-Izmir (Turkey)
2009-12-15
It is crucial to improve the photovoltaic (PV) system efficiency and to develop the reliability of PV generation control systems. There are two ways to increase the efficiency of PV power generation system. The first is to develop materials offering high conversion efficiency at low cost. The second is to operate PV systems optimally. However, the PV system can be optimally operated only at a specific output voltage and its output power fluctuates under intermittent weather conditions. Moreover, it is very difficult to test the performance of a maximum-power point tracking (MPPT) controller under the same weather condition during the development process and also the field testing is costly and time consuming. This paper presents a novel real-time simulation technique of PV generation system by using dSPACE real-time interface system. The proposed system includes Artificial Neural Network (ANN) and fuzzy logic controller scheme using polar information. This type of fuzzy logic rules is implemented for the first time to operate the PV module at optimum operating point. ANN is utilized to determine the optimum operating voltage for monocrystalline silicon, thin-film cadmium telluride and triple junction amorphous silicon solar cells. The verification of availability and stability of the proposed system through the real-time simulator shows that the proposed system can respond accurately for different scenarios and different solar cell technologies. (author)
Congestion management considering voltage security of power systems
International Nuclear Information System (INIS)
Esmaili, Masoud; Shayanfar, Heidar Ali; Amjady, Nima
2009-01-01
Congestion in a power network is turned up due to system operating limits. To relieve congestion in a deregulated power market, the system operator pays to market participants, GENCOs and DISCOs, to alter their active powers considering their bids. After performing congestion management, the network may be operated with a low security level because of hitting some flows their upper limit and some voltages their lower limit. In this paper, a novel congestion management method based on the voltage stability margin sensitivities is introduced. Using the proposed method, the system operator so alleviates the congestion that the network can more retain its security. The proposed method not only makes the system more secure after congestion management than other methods already presented for this purpose but also its cost of providing security is lower than the earlier methods. Test results of the proposed method along with the earlier ones on the New-England test system elaborate the efficiency of the proposed method from the viewpoint of providing a better voltage stability margin and voltage profile as well as a lower security cost. (author)
Comparative Study of Maximum Power Point Tracking Techniques for Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Fernando Lessa Tofoli
2015-01-01
Full Text Available The generation of electricity from photovoltaic (PV arrays has been increasingly considered as a prominent alternative to fossil fuels. However, the conversion efficiency is typically low and the initial cost is still appreciable. A required feature of a PV system is the ability to track the maximum power point (MPP of the PV array. Besides, MPP tracking (MPPT is desirable in both grid-connected and stand-alone photovoltaic systems because the solar irradiance and temperature change throughout the day, as well as along seasons and geographical conditions, also leading to the modification of the I×V (current versus voltage and P×V (power versus voltage curves of the PV module. MPPT is also justified by the relatively high cost of the energy generated by PV systems if compared with other sources. Since there are various MPPT approaches available in the literature, this work presents a comparative study among four popular techniques, which are the fixed duty cycle method, constant voltage (CV, perturb and observe (P&O, and incremental conductance (IC. It considers different operational climatic conditions (i.e., irradiance and temperature, since the MPP is nonlinear with the environment status. PSIM software is used to validate the assumptions, while relevant results are discussed in detail.
Symmetric low-voltage powering system for relativistic electronic devices
International Nuclear Information System (INIS)
Agafonov, A.V.; Lebedev, A.N.; Krastelev, E.G.
2005-01-01
A special driver for double-sided powering of relativistic magnetrons and several methods of localized electron flow forming in the interaction region of relativistic magnetrons are proposed and discussed. Two experimental installations are presented and discussed. One of them is designed for laboratory research and demonstration experiments at a rather low voltage. The other one is a prototype of a full-scale installation for an experimental research at relativistic levels of voltages on the microwave generation in the new integrated system consisting of a relativistic magnetron and symmetrical induction driver
Harmonics and voltage stability analysis in power systems including
Indian Academy of Sciences (India)
In this study, non-sinusoidal quantities and voltage stability, both known as power quality criteria, are examined together in detail. The widespread use of power electronics elements cause the existence of signiﬁcant non-sinusoidal quantities in the system. These non-sinusoidal quantities can create serious harmonic ...
Global voltage control for the LEP RF system
International Nuclear Information System (INIS)
Ciapala, E.; Butterworth, A.; Peschardt, E.
1993-01-01
The LEG RF system is installed as independent 16 cavity units. In addition to the eight copper cavity units originally installed 12 units with super-conducting cavities are being added for the LEP200 energy upgrade. The total RF voltage determines the synchrotron tune (Qs) and must be controlled precisely during energy ramping. Local function generators in each of the RF units are pre-loaded such that when triggered simultaneously by ramp timing events transmitted over the general timing system the total voltage varies to give the Qs function required. A disadvantage is that loss of RF in a unit at any time after the loading process cannot be corrected. As the number of RF units increases automatic control of the total RF voltage and its distribution around LEP becomes desirable. A global voltage control system, based on a central VME controller, has recently been installed. It has direct and rapid access to the RF units over the LEP time division multiplexing system. Initial tests on operation and performance at fixed energy and during energy ramping are described, as well as the implementation of a Qs loop in which Qs can be set directly using on-line synchrotron frequency measurements
Digital measurement system for the LHC klystron high voltage modulator.
Mikkelsen, Anders
Accelerating voltage in the Large Hadron Collider (LHC) is created by a means of 16 superconducting standing wave RF cavities, each fed by a 400MHz/300kW continuous wave klystron amplifier. Part of the upgrade program for the LHC long shutdown one is to replace the obsolete analogue current and voltage measurement circuitry located in the high voltage bunkers by a new, digital system, using ADCs and optical fibres. A digital measurement card is implemented and integrated into the current HV modulator oil tank (floating at -58kV) and interfaced to the existing digital VME boards collecting the data for several klystrons at the ground potential. Measured signals are stored for the logging, diagnostics and post-mortem analysis purposes.
Design and realization of high voltage disconnector condition monitoring system
Shi, Jinrui; Xu, Tianyang; Yang, Shuixian; Li, Buoyang
2017-08-01
The operation status of the high voltage disconnector directly affects the safe and stable operation of the power system. This article uses the wireless frequency hopping communication technology of the communication module to achieve the temperature acquisition of the switch contacts and high voltage bus, to introduce the current value of the loop in ECS, and judge the operation status of the disconnector by considering the ambient temperature, calculating the temperature rise; And through the acquisition of the current of drive motor in the process of switch closing and opening, and fault diagnosis of the disconnector by analyzing the change rule of the drive motor current, the condition monitoring of the high voltage disconnector is realized.
Design and implementation of the wireless high voltage control system
International Nuclear Information System (INIS)
Srivastava, Saurabh; Misra, A.; Pandey, H.K.; Thakur, S.K.; Pandit, V.S.
2011-01-01
In this paper we will describe the implementation of the wireless link for controlling and monitoring the serial data between control PC and the interface card (general DAQ card), by replacing existing RS232 based remote control system for controlling and monitoring High Voltage Power Supply (120kV/50mA). The enhancement in the reliability is achieved by replacing old RS232 based control system with wireless system by isolating ground loop. (author)
DEFF Research Database (Denmark)
Douglass, Philip James; Garcia-Valle, Rodrigo; Østergaard, Jacob
2014-01-01
This paper presents a novel controller design for controlling appliances based on local measurements of voltage. The controller finds the normalized voltage deviation accounting for the sensitivity of voltage measurements to appliance state. The controller produces a signal indicating desired pow...
DEFF Research Database (Denmark)
Zhu, Jiebei; Guerrero, Josep M.; Hung, William
2014-01-01
A generic Inertia Emulation Controller (INEC) scheme for Multi-Terminal Voltage-Source-Converter based HVDC (VSC-MTDC) systems is proposed and presented in this paper. The proposed INEC can be incorporated in any Grid-side Voltage-Source-Converter (GVSC) station, allowing the MTDC terminal...
Directory of Open Access Journals (Sweden)
Lee Gyu-sub
2016-01-01
Full Text Available The exhaustion of fossil fuel and the greenhouse gas emission are one of the most significant energy and environmental issues, respectively. Photovoltaic (PV generators and battery energy storage systems (BESSs have been significantly increased for recent years. The BESSs are mainly used for smoothing active power fluctuation of the PV. In this paper, PV–BESSs integration of two DC/DC converters and one AC/DC converter is investigated and DC-link voltage control to compensate the AC voltage deviation is proposed for the PV‒BESS system in low-voltage (LV networks.
She, Xu; Chokhawala, Rahul Shantilal; Zhou, Rui; Zhang, Di; Sommerer, Timothy John; Bray, James William
2016-12-13
A voltage source converter based high-voltage direct-current (HVDC) transmission system includes a voltage source converter (VSC)-based power converter channel. The VSC-based power converter channel includes an AC-DC converter and a DC-AC inverter electrically coupled to the AC-DC converter. The AC-DC converter and a DC-AC inverter include at least one gas tube switching device coupled in electrical anti-parallel with a respective gas tube diode. The VSC-based power converter channel includes a commutating circuit communicatively coupled to one or more of the at least one gas tube switching devices. The commutating circuit is configured to "switch on" a respective one of the one or more gas tube switching devices during a first portion of an operational cycle and "switch off" the respective one of the one or more gas tube switching devices during a second portion of the operational cycle.
Roselyn, J. Preetha; Devaraj, D.; Dash, Subhransu Sekhar
2013-11-01
Voltage stability is an important issue in the planning and operation of deregulated power systems. The voltage stability problems is a most challenging one for the system operators in deregulated power systems because of the intense use of transmission line capabilities and poor regulation in market environment. This article addresses the congestion management problem avoiding offline transmission capacity limits related to voltage stability by considering Voltage Security Constrained Optimal Power Flow (VSCOPF) problem in deregulated environment. This article presents the application of Multi Objective Differential Evolution (MODE) algorithm to solve the VSCOPF problem in new competitive power systems. The maximum of L-index of the load buses is taken as the indicator of voltage stability and is incorporated in the Optimal Power Flow (OPF) problem. The proposed method in hybrid power market which also gives solutions to voltage stability problems by considering the generation rescheduling cost and load shedding cost which relieves the congestion problem in deregulated environment. The buses for load shedding are selected based on the minimum eigen value of Jacobian with respect to the load shed. In the proposed approach, real power settings of generators in base case and contingency cases, generator bus voltage magnitudes, real and reactive power demands of selected load buses using sensitivity analysis are taken as the control variables and are represented as the combination of floating point numbers and integers. DE/randSF/1/bin strategy scheme of differential evolution with self-tuned parameter which employs binomial crossover and difference vector based mutation is used for the VSCOPF problem. A fuzzy based mechanism is employed to get the best compromise solution from the pareto front to aid the decision maker. The proposed VSCOPF planning model is implemented on IEEE 30-bus system, IEEE 57 bus practical system and IEEE 118 bus system. The pareto optimal
MAXIMUM POWEWR POINT TRACKING SYSTEM FOR PHOTOVOLTAIC STATION: A REVIEW
Directory of Open Access Journals (Sweden)
I. Elzein
2015-01-01
Full Text Available In recent years there has been a growing attention towards the use of renewable energy sources. Among them solar energy is one of the most promising green energy resources due to its environment sustainability and inexhaustibility. However photovoltaic systems (PhV suffer from big cost of equipment and low efficiency. Moreover, the solar cell V-I characteristic is nonlinear and varies with irradiation and temperature. In general, there is a unique point of PhV operation, called the Maximum Power Point (MPP, in which the PV system operates with maximum efficiency and produces its maximum output power. The location of the MPP is not known in advance, but can be located, either through calculation models or by search algorithms. Therefore MPPT techniques are important to maintain the PV array’s high efficiency. Many different techniques for MPPT are discussed. This review paper hopefully will serve as a convenient tool for future work in PhV power conversion.
A Self-Biased Active Voltage Doubler for Energy Harvesting Systems
Tayyab, Umais
2017-12-03
An active voltage doubler utilizing a single supply op-amp for energy harvesting system is presented. The proposed doubler is used for rectification process to achieve both acceptably high power conversion efficiency (PCE) and large rectified DC voltage. The incorporated op-amp is self-biased, meaning no external supply is needed but rather it uses part of the harvested energy for its biasing. The proposed active doubler achieves maximum power conversion efficiency (PCE) of 61.7% for a 200 Hz sinusoidal input of 0.8 V for a 20 K load resistor. This efficiency is 2 times more when compared with the passive voltage doubler. The rectified DC voltage is almost 2 times more than conventional passive doubler. The relation between PCE and the load resistor is also presented. The proposed active voltage doubler is designed and simulated in LF 0.15 μm CMOS process technology using Cadence virtuoso tool.
International Nuclear Information System (INIS)
Fathabadi, Hassan
2016-01-01
Highlights: • Novel sensorless MPPT technique without drawbacks of other sensor/sensorless methods. • Tracking the actual MPP of WECSs, no tracking the MPP of their wind turbines. • Actually extracting the highest output power from WECSs. • Novel MPPT technique having the MPPT efficiency more than 98.5% for WECSs. • Novel MPPT technique having short convergence time for WECSs. - Abstract: In this study, a novel high accurate sensorless maximum power point tracking (MPPT) method is proposed. The technique tracks the actual maximum power point of a wind energy conversion system (WECS) at which maximum output power is extracted from the system, not the maximum power point of its wind turbine at which maximum mechanical power is obtained from the turbine, so it actually extracts the highest output power from the system. The technique only uses input voltage and current of the converter used in the system, and neither needs any speed sensors (anemometer and tachometer) nor has the drawbacks of other sensor/sensorless based MPPT methods. The technique has been implemented as a MPPT controller by constructing a WECS. Theoretical results, the technique performance, and its advantages are validated by presenting real experimental results. The real static-dynamic response of the MPPT controller is experimentally obtained that verifies the proposed MPPT technique high accurately extracts the highest instant power from wind energy conversion systems with the MPPT efficiency of more than 98.5% and a short convergence time that is only 25 s for the constructed system having a total inertia and friction coefficient of 3.93 kg m 2 and 0.014 N m s, respectively.
High-Voltage Power Supply System for Laser Isotope Separation
Energy Technology Data Exchange (ETDEWEB)
Ketaily, E.C.; Buckner, R.P.; Uhrik, R.L.
1979-06-26
This report presents several concepts for Laser High-Voltage Power Supply (HVPS) Systems for a Laser Isotope Separation facility. Selection of equipments and their arrangement into operational systems is based on proven designs and on application concepts now being developed. This report has identified a number of alternative system arrangements and has provided preliminary cost estimates for each. The report includes a recommendation for follow-on studies that will further define the optimum Laser HVPS Systems. Brief descriptions are given of Modulator/Regulator circuit trade-offs, system control interfaces, and their impact on costs.
High-Voltage Power Supply System for Laser Isotope Separation
International Nuclear Information System (INIS)
Ketaily, E.C.; Buckner, R.P.; Uhrik, R.L.
1979-01-01
This report presents several concepts for Laser High-Voltage Power Supply (HVPS) Systems for a Laser Isotope Separation facility. Selection of equipments and their arrangement into operational systems is based on proven designs and on application concepts now being developed. This report has identified a number of alternative system arrangements and has provided preliminary cost estimates for each. The report includes a recommendation for follow-on studies that will further define the optimum Laser HVPS Systems. Brief descriptions are given of Modulator/Regulator circuit trade-offs, system control interfaces, and their impact on costs
Automatic Voltage Control (AVC) of Danish Transmission System - Concept design
DEFF Research Database (Denmark)
Qin, Nan; Abildgaard, Hans; Lund, P.
2014-01-01
For more than 20 years it has been a consistent plan by all Danish governments to turn the Danish power production away from fossil fuels towards renewable energy. The result today is that 37% of the total Danish power consumption was covered by mainly wind energy in 2013 aiming at 50% by 2020......, objectives, constraints, algorithms for optimal power flow and some special functions in particular systems, which inspires the concept design of a Danish AVC system to address the future challenges of voltage control. In the concept, the Danish AVC design is based on a centralized control scheme. All...... the substation loses the telecommunications to the control center. RPCs will be integrated to the AVC system as normative regulators in the later stage. Distributed generation units can be organized as virtual power plants and participate in voltage control at transmission level. Energinet.dk as the Danish TSO...
Maximum-power-point tracking control of solar heating system
Huang, Bin-Juine
2012-11-01
The present study developed a maximum-power point tracking control (MPPT) technology for solar heating system to minimize the pumping power consumption at an optimal heat collection. The net solar energy gain Q net (=Q s-W p/η e) was experimentally found to be the cost function for MPPT with maximum point. The feedback tracking control system was developed to track the optimal Q net (denoted Q max). A tracking filter which was derived from the thermal analytical model of the solar heating system was used to determine the instantaneous tracking target Q max(t). The system transfer-function model of solar heating system was also derived experimentally using a step response test and used in the design of tracking feedback control system. The PI controller was designed for a tracking target Q max(t) with a quadratic time function. The MPPT control system was implemented using a microprocessor-based controller and the test results show good tracking performance with small tracking errors. It is seen that the average mass flow rate for the specific test periods in five different days is between 18.1 and 22.9kg/min with average pumping power between 77 and 140W, which is greatly reduced as compared to the standard flow rate at 31kg/min and pumping power 450W which is based on the flow rate 0.02kg/sm 2 defined in the ANSI/ASHRAE 93-1986 Standard and the total collector area 25.9m 2. The average net solar heat collected Q net is between 8.62 and 14.1kW depending on weather condition. The MPPT control of solar heating system has been verified to be able to minimize the pumping energy consumption with optimal solar heat collection. © 2012 Elsevier Ltd.
A High-Voltage SOI CMOS Exciter Chip for a Programmable Fluidic Processor System.
Current, K W; Yuk, K; McConaghy, C; Gascoyne, P R C; Schwartz, J A; Vykoukal, J V; Andrews, C
2007-06-01
A high-voltage (HV) integrated circuit has been demonstrated to transport fluidic droplet samples on programmable paths across the array of driving electrodes on its hydrophobically coated surface. This exciter chip is the engine for dielectrophoresis (DEP)-based micro-fluidic lab-on-a-chip systems, creating field excitations that inject and move fluidic droplets onto and about the manipulation surface. The architecture of this chip is expandable to arrays of N X N identical HV electrode driver circuits and electrodes. The exciter chip is programmable in several senses. The routes of multiple droplets may be set arbitrarily within the bounds of the electrode array. The electrode excitation waveform voltage amplitude, phase, and frequency may be adjusted based on the system configuration and the signal required to manipulate a particular fluid droplet composition. The voltage amplitude of the electrode excitation waveform can be set from the minimum logic level up to the maximum limit of the breakdown voltage of the fabrication technology. The frequency of the electrode excitation waveform can also be set independently of its voltage, up to a maximum depending upon the type of droplets that must be driven. The exciter chip can be coated and its oxide surface used as the droplet manipulation surface or it can be used with a top-mounted, enclosed fluidic chamber consisting of a variety of materials. The HV capability of the exciter chip allows the generated DEP forces to penetrate into the enclosed chamber region and an adjustable voltage amplitude can accommodate a variety of chamber floor thicknesses. This demonstration exciter chip has a 32 x 32 array of nominally 100 V electrode drivers that are individually programmable at each time point in the procedure to either of two phases: 0deg and 180deg with respect to the reference clock. For this demonstration chip, while operating the electrodes with a 100-V peak-to-peak periodic waveform, the maximum HV electrode
Solar maximum mission panel jettison analysis remote manipulator system
Bauer, R. B.
1980-01-01
A study is presented of the development of the Remote Manipulator System (RMS) configurations for jettison of the solar panels on the Solar Maximum Mission/Multimission Satellite. A valid RMS maneuver between jettison configurations was developed. Arm and longeron loads and effector excursions due to the solar panel jettison were determined to see if they were within acceptable limits. These loads and end effector excursions were analyzed under two RMS modes, servos active in position hold submode, and in the brakes on mode.
Application of the maximum entropy production principle to electrical systems
International Nuclear Information System (INIS)
Christen, Thomas
2006-01-01
For a simple class of electrical systems, the principle of the maximum entropy production rate (MaxEP) is discussed. First, we compare the MaxEP principle and the principle of the minimum entropy production rate and illustrate the superiority of the MaxEP principle for the example of two parallel constant resistors. Secondly, we show that the Steenbeck principle for the electric arc as well as the ohmic contact behaviour of space-charge limited conductors follow from the MaxEP principle. In line with work by Dewar, the investigations seem to suggest that the MaxEP principle can also be applied to systems far from equilibrium, provided appropriate information is available that enters the constraints of the optimization problem. Finally, we apply the MaxEP principle to a mesoscopic system and show that the universal conductance quantum, e 2 /h, of a one-dimensional ballistic conductor can be estimated
DEFF Research Database (Denmark)
Yang, Yongheng; Sangwongwanich, Ariya; Liu, Hongpeng
2017-01-01
In this paper, a cost-effective control scheme for two-stage grid-connected PhotoVoltaic (PV) systems in Low Voltage Ride-Through (LVRT) operation is proposed. In the case of LVRT, the active power injection by PV panels should be limited to prevent from inverter over-current and also energy...... aggregation at the dc-link, which will challenge the dc-link capacitor lifetime if remains uncontrolled. At the same time, reactive currents should be injected upon any demand imposed by the system operators. In the proposed scheme, the two objectives can be feasibly achieved. The active power is regulated...... point tracking controller without significant hardware or software modifications. In this way, the PV system will not operate at the maximum power point, whereas the inverter will not face any over-current challenge but can provide reactive power support in response to the grid voltage fault...
International Nuclear Information System (INIS)
2013-01-01
The project on the requirements for the retrofitting an extension of the maximum voltage power grid from the point of view of environmental protection and cultivated landscape work includes contributions on the following topics: the development of the European transmission grid, the grid extension law, restrictions for the power grid and their infrastructure, requirements for the regulations concerning the realization of the transnational grid extension, inclusion of the public - public acceptance - communication, requirements concerning the environmental compensation law, overhead line - underground cable - health hazards, ecological effects of overhead lines and underground cables, infrastructural projects, power supply in the future, structural relief by photovoltaics.
DEFF Research Database (Denmark)
Yang, Zilong; Wang, Zhe; Zhang, Ying
2017-01-01
-up structure, instead of applying line-frequency step-up transformer, is proposed to connect PV directly to the 10 kV medium voltage grid. This series-connected step-up PV system integrates with multiple functions, including separated maximum power point tracking (MPPT), centralized energy storage, power...
Parametric characteristics of a solar thermophotovoltaic system at the maximum efficiency
International Nuclear Information System (INIS)
Liao, Tianjun; Chen, Xiaohang; Yang, Zhimin; Lin, Bihong; Chen, Jincan
2016-01-01
Graphical abstract: A model of the far-field TPVC driven by solar energy, which consists of an optical concentrator, an absorber, an emitter, and a PV cell and is simply referred as to the far-field STPVS. - Highlights: • A model of the far-field solar thermophotovoltaic system (STPVS) is established. • External and internal irreversible losses are considered. • The maximum efficiency of the STPVS is calculated. • Optimal values of key parameters at the maximum efficiency are determined. • Effects of the concentrator factor on the performance of the system are discussed. - Abstract: A model of the solar thermophotovoltaic system (STPVS) consisting of an optical concentrator, a thermal absorber, an emitter, and a photovoltaic (PV) cell is proposed, where the far-field thermal emission between the emitter and the PV cell, the radiation losses from the absorber and emitter to the environment, the reflected loss from the absorber, and the finite-rate heat exchange between the PV cell and the environment are taken into account. Analytical expressions for the power output of and overall efficiency of the STPVS are derived. By solving thermal equilibrium equations, the operating temperatures of the emitter and PV cell are determined and the maximum efficiency of the system is calculated numerically for given values of the output voltage of the PV cell and the ratio of the front surface area of the absorber to that of the emitter. For different bandgaps, the maximum efficiencies of the system are calculated and the corresponding optimum values of several operating parameters are obtained. The effects of the concentrator factor on the optimum performance of the system are also discussed.
The frequency characteristics of medium voltage distribution system impedances
Directory of Open Access Journals (Sweden)
Liviu Emil Petrean
2009-10-01
Full Text Available In this paper we present the frequency characteristics of impedances involved in the electrical equivalent circuit of a large medium voltage distribution system. These impedances influence harmonics distortions propagation occurring due to the nonsinusoidal loads. We analyse the case of a 10 kV large urban distribution system which supplies industrial, commercial and residential customers. The influence of various parameters of the distribution network on the frequency characteristics are presented, in order to assess the interaction of harmonic distortion and distribution system network.
International Nuclear Information System (INIS)
Guan, Mingjie; Wang, Kunpeng; Xu, Dazheng; Liao, Wei-Hsin
2017-01-01
Highlights: • A thermoelectric energy harvesting system for wireless sensor nodes is designed. • An ultra-low voltage self-startup is implemented. • Maximum power point tracking and low power designs are applied for high efficiency. • Efficiency of 44.2–75.4% is obtained with open-circuit voltage of 84–400 mV. • System efficiency is higher than the commercial BQ25504 converter. - Abstract: A thermoelectric energy harvesting system designed to harvest tens of microwatts to several milliwatts from low-voltage thermoelectric generators is presented in this paper. The proposed system is based-on a two-stage boost scheme with self-startup ability. A maximum power point tracking technique based on the open-circuit voltage is adopted in the boost converter for high efficiency. Experimental results indicate that the proposed system can harvest thermoelectric energy and run a microcontroller unit and a wireless sensor node under low input voltage and power with high efficiency. The harvest system and wireless sensor node can be self-powered with minimum thermoelectric open-circuit voltage as 62 mV and input power of 84 μW. With a self-startup scheme, the proposed system can self-start with a 20 mV input voltage. Low power designs are applied in the system to reduce the quiescent dissipation power. It results in better performance considering the conversion efficiency and self-startup ability compared to commercial boost systems used for thermal energy harvesting.
Different types of maximum power point tracking techniques for renewable energy systems: A survey
Khan, Mohammad Junaid; Shukla, Praveen; Mustafa, Rashid; Chatterji, S.; Mathew, Lini
2016-03-01
Global demand for electricity is increasing while production of energy from fossil fuels is declining and therefore the obvious choice of the clean energy source that is abundant and could provide security for development future is energy from the sun. In this paper, the characteristic of the supply voltage of the photovoltaic generator is nonlinear and exhibits multiple peaks, including many local peaks and a global peak in non-uniform irradiance. To keep global peak, MPPT is the important component of photovoltaic systems. Although many review articles discussed conventional techniques such as P & O, incremental conductance, the correlation ripple control and very few attempts have been made with intelligent MPPT techniques. This document also discusses different algorithms based on fuzzy logic, Ant Colony Optimization, Genetic Algorithm, artificial neural networks, Particle Swarm Optimization Algorithm Firefly, Extremum seeking control method and hybrid methods applied to the monitoring of maximum value of power at point in systems of photovoltaic under changing conditions of irradiance.
Design philosophy and use of high voltage power systems for multi-megawatt ion beam accelerators
International Nuclear Information System (INIS)
Barber, G.C.; Broverman, A.Y.; Hill, R.E.; Loring, C.M.; Ponte, N.S.
1977-01-01
The requirements for a neutral beam high voltage power system are derived from the characteristics of the ion source. High voltage system component characteristic requirements and choices are described
High voltage power supplies for INDUS-2 RF system
International Nuclear Information System (INIS)
Badapanda, M.K.; Hannurkar, P.R.
2003-01-01
The RF system of Indus-2 employs klystron amplifiers operating at 505.812 MHz. A precession controlled high voltage DC supply of appropriate rating is needed for each klystron amplifier, as its bias supply. Since internal flashover and arcing are common with the operation of these klystrons and stored energies beyond particular limit inside its bias power supply is detrimental to this device, a properly designed crowbar is incorporated between each klystron and its power supply. This crowbar bypass these stored energies and helps protecting klystron under any of these unfavorable conditions. In either case, power supply sees a near short circuit across its load. So, its power circuit is designed to reduce the fault current level and its various components are also designed to withstand these fault currents, as and when it appears. Finally, operation of these high voltage power supplies (HVPS) generates lot of harmonics on the source side, which distort the input waveform substantially and reduces the input power factor also. Source multiplication between two power supplies are planned to improve upon above parameters and suitable detuned line filters are incorporated to keep the input voltage total harmonics distortion (THD) below 5 % and input power factor (IFF) near unity. (author)
Accelerated maximum likelihood parameter estimation for stochastic biochemical systems
Directory of Open Access Journals (Sweden)
Daigle Bernie J
2012-05-01
Full Text Available Abstract Background A prerequisite for the mechanistic simulation of a biochemical system is detailed knowledge of its kinetic parameters. Despite recent experimental advances, the estimation of unknown parameter values from observed data is still a bottleneck for obtaining accurate simulation results. Many methods exist for parameter estimation in deterministic biochemical systems; methods for discrete stochastic systems are less well developed. Given the probabilistic nature of stochastic biochemical models, a natural approach is to choose parameter values that maximize the probability of the observed data with respect to the unknown parameters, a.k.a. the maximum likelihood parameter estimates (MLEs. MLE computation for all but the simplest models requires the simulation of many system trajectories that are consistent with experimental data. For models with unknown parameters, this presents a computational challenge, as the generation of consistent trajectories can be an extremely rare occurrence. Results We have developed Monte Carlo Expectation-Maximization with Modified Cross-Entropy Method (MCEM2: an accelerated method for calculating MLEs that combines advances in rare event simulation with a computationally efficient version of the Monte Carlo expectation-maximization (MCEM algorithm. Our method requires no prior knowledge regarding parameter values, and it automatically provides a multivariate parameter uncertainty estimate. We applied the method to five stochastic systems of increasing complexity, progressing from an analytically tractable pure-birth model to a computationally demanding model of yeast-polarization. Our results demonstrate that MCEM2 substantially accelerates MLE computation on all tested models when compared to a stand-alone version of MCEM. Additionally, we show how our method identifies parameter values for certain classes of models more accurately than two recently proposed computationally efficient methods
The mechanics of granitoid systems and maximum entropy production rates.
Hobbs, Bruce E; Ord, Alison
2010-01-13
A model for the formation of granitoid systems is developed involving melt production spatially below a rising isotherm that defines melt initiation. Production of the melt volumes necessary to form granitoid complexes within 10(4)-10(7) years demands control of the isotherm velocity by melt advection. This velocity is one control on the melt flux generated spatially just above the melt isotherm, which is the control valve for the behaviour of the complete granitoid system. Melt transport occurs in conduits initiated as sheets or tubes comprising melt inclusions arising from Gurson-Tvergaard constitutive behaviour. Such conduits appear as leucosomes parallel to lineations and foliations, and ductile and brittle dykes. The melt flux generated at the melt isotherm controls the position of the melt solidus isotherm and hence the physical height of the Transport/Emplacement Zone. A conduit width-selection process, driven by changes in melt viscosity and constitutive behaviour, operates within the Transport Zone to progressively increase the width of apertures upwards. Melt can also be driven horizontally by gradients in topography; these horizontal fluxes can be similar in magnitude to vertical fluxes. Fluxes induced by deformation can compete with both buoyancy and topographic-driven flow over all length scales and results locally in transient 'ponds' of melt. Pluton emplacement is controlled by the transition in constitutive behaviour of the melt/magma from elastic-viscous at high temperatures to elastic-plastic-viscous approaching the melt solidus enabling finite thickness plutons to develop. The system involves coupled feedback processes that grow at the expense of heat supplied to the system and compete with melt advection. The result is that limits are placed on the size and time scale of the system. Optimal characteristics of the system coincide with a state of maximum entropy production rate. This journal is © 2010 The Royal Society
Integration Test of the High Voltage Hall Accelerator System Components
Kamhawi, Hani; Haag, Thomas; Huang, Wensheng; Pinero, Luis; Peterson, Todd; Dankanich, John
2013-01-01
NASA Glenn Research Center is developing a 4 kilowatt-class Hall propulsion system for implementation in NASA science missions. NASA science mission performance analysis was completed using the latest high voltage Hall accelerator (HiVHAc) and Aerojet-Rocketdyne's state-of-the-art BPT-4000 Hall thruster performance curves. Mission analysis results indicated that the HiVHAc thruster out performs the BPT-4000 thruster for all but one of the missions studied. Tests of the HiVHAc system major components were performed. Performance evaluation of the HiVHAc thruster at NASA Glenn's vacuum facility 5 indicated that thruster performance was lower than performance levels attained during tests in vacuum facility 12 due to the lower background pressures attained during vacuum facility 5 tests when compared to vacuum facility 12. Voltage-Current characterization of the HiVHAc thruster in vacuum facility 5 showed that the HiVHAc thruster can operate stably for a wide range of anode flow rates for discharge voltages between 250 and 600 volts. A Colorado Power Electronics enhanced brassboard power processing unit was tested in vacuum for 1,500 hours and the unit demonstrated discharge module efficiency of 96.3% at 3.9 kilowatts and 650 volts. Stand-alone open and closed loop tests of a VACCO TRL 6 xenon flow control module were also performed. An integrated test of the HiVHAc thruster, brassboard power processing unit, and xenon flow control module was performed and confirmed that integrated operation of the HiVHAc system major components. Future plans include continuing the maturation of the HiVHAc system major components and the performance of a single-string integration test.
Decentralized Adaptive Overcurrent Protection for Medium Voltage Maritime Power Systems
DEFF Research Database (Denmark)
Ciontea, Catalin-Iosif; Bak, Claus Leth; Blaabjerg, Frede
2016-01-01
the entire electrical network and changes the relay settings accordingly, but this approach is not adequate for the maritime power systems. This paper propose a decentralized adaptive protection method, where each protection relay is able to identify by itself the network status without the need of a central...... control unit. The new adaptive protection method is based on communication between the overcurrent relays and the equipment that could affect the protection system, such as circuit breakers and generators. Using PSCAD, the proposed method is implemented in a test medium voltage maritime power system......More and more maritime applications as marine vessels and offshore platforms need an adaptive protection power system. However, the adaptive protection is yet to be implemented in the maritime sector. Usually, the adaptive protection implies the existence of a central control unit that monitors...
Soreng, Bineeta; Behera, Pradyumna; Pradhan, Raseswari
2017-08-01
This paper presents model of a grid-integrated photovoltaic array with Maximum Power Point Tracker (MPPT) and voltage oriented controller. The MPPT of the PV array is usually an essential part of PV system as MPPT helps the operating point of the solar array to align its maximum power point. In this model, the MPPT along with a DC-DC converter lets a PV generator to produce continuous power, despite of the measurement conditions. The neutral-point-clamped converter (NPC) with a boost converter raises the voltage from the panels to the DC-link. An LCL-filter smoothens the current ripple caused by the PWM modulation of the grid-side inverter. In addition to the MPPT, the system has two more two controllers, such as voltage controller and a current controller. The voltage control has a PI controller to regulate the PV voltage to optimal level by controlling the amount of current injected into the boost stage. Here, the grid-side converter transfers the power from the DC-link into the grid and maintains the DC-link voltage. Three-phase PV inverters are used for off-grid or designed to create utility frequency AC. The PV system can be connected in series or parallel to get the desired output power. To justify the working of this model, the grid-integrated PV system has been designed in MATLAB/PLECS. The simulation shows the P-V curve of implemented PV Array consisting 4 X 20 modules, reactive, real power, grid voltage and current.
Improved voltage gradient control system for electrostatic accelerators
International Nuclear Information System (INIS)
Jones, N.L.; Dittner, P.F.
1993-01-01
An improved voltage gradient control system has been designed and installed in the EN tandem at the Oak Ridge National Laboratory. An improved design was sought due to high failure rates, increasing replacement parts and labor costs, and decreasing availability of the original carbon film resistor systems supplied for the EN-12 at ORNL. The resulting system utilizes two inexpensive, readily available, metal oxide resistors in series between each plane. They are protected by coaxial stainless steel shielding tubes, and spark gaps across individual resistors and adjacent pairs. The new resistors mount atop the column bridge in a compact configuration. This permits easy access both to the resistors and to the interior column components such as the belt. Well controlled gradients now provide improved machine performance. Both initial capital outlay and future maintenance result in reduced costs. Design, installation, performance, and cost details are reported. (orig.)
Bi-directional power control system for voltage converter
Garrigan, Neil Richard; King, Robert Dean; Schwartz, James Edward
1999-01-01
A control system for a voltage converter includes: a power comparator for comparing a power signal on input terminals of the converter with a commanded power signal and producing a power comparison signal; a power regulator for transforming the power comparison signal to a commanded current signal; a current comparator for comparing the commanded current signal with a measured current signal on output terminals of the converter and producing a current comparison signal; a current regulator for transforming the current comparison signal to a pulse width modulator (PWM) duty cycle command signal; and a PWM for using the PWM duty cycle command signal to control electrical switches of the converter. The control system may further include: a command multiplier for converting a voltage signal across the output terminals of the converter to a gain signal having a value between zero (0) and unity (1), and a power multiplier for multiplying the commanded power signal by the gain signal to provide a limited commanded power signal, wherein power comparator compares the limited commanded power signal with the power signal on the input terminals.
Energy Technology Data Exchange (ETDEWEB)
Kuo, J.-L.; Hong, P.-J. [National Kaohsiung First Univ. of Science and Technology, Nantze, Kaohsiung, Taiwan (China). Dept. of Mechanical and Automation Engineering; Chao, K.-L. [National Kaohsiung Univ. of Applied Sciences, Nantze, Kaohsiung, Taiwan (China). Dept. of Electrical Engineering; Wang, T.-Y. [Chang-Gung Univ., Kwei-Shan, Tao-Yuan, Taiwan (China). Dept. of Electrical Engineering
2007-07-01
Solar energy is a popular renewable energy source for the future because it does not produce any pollution. In addition, it is unlimited and a clean source of energy. This paper discussed a photovoltaic solar fan system that could be used inside the house with the potential of cooling the indoor temperature. The solar cell module is located at the eaves of the house and could block the sunlight directly into the house, and convert solar power into electric power through the battery. The paper described software implementation and hardware circuit design in detail. The paper also illustrated a different algorithm to calculate the maximum power point regulation. The conventional algorithm calculates the solar cell module output power by multiplying the input voltage and input current for the solar cell module directly. By changing the input voltage variable into duty variable, the voltage sensor is not required under the proposed scheme. Only the duty and current variables are needed to calculate the maximum power. The microchip dsPIC microcontroller was used to implement the algorithm. Different DC link levels were verified and implemented for comparison. It was concluded that the characteristics of the solar cell module could be measured automatically, and the maximum power point could be guaranteed by the proposed algorithm. 9 refs., 6 tabs., 14 figs.
Adaptive double-integral-sliding-mode-maximum-power-point tracker for a photovoltaic system
Directory of Open Access Journals (Sweden)
Bidyadhar Subudhi
2015-10-01
Full Text Available This study proposed an adaptive double-integral-sliding-mode-controller-maximum-power-point tracker (DISMC-MPPT for maximum-power-point (MPP tracking of a photovoltaic (PV system. The objective of this study is to design a DISMC-MPPT with a new adaptive double-integral-sliding surface in order that MPP tracking is achieved with reduced chattering and steady-state error in the output voltage or current. The proposed adaptive DISMC-MPPT possesses a very simple and efficient PWM-based control structure that keeps switching frequency constant. The controller is designed considering the reaching and stability conditions to provide robustness and stability. The performance of the proposed adaptive DISMC-MPPT is verified through both MATLAB/Simulink simulation and experiment using a 0.2 kW prototype PV system. From the obtained results, it is found out that this DISMC-MPPT is found to be more efficient compared with that of Tan's and Jiao's DISMC-MPPTs.
Directory of Open Access Journals (Sweden)
Ho-Yong Jeong
2015-08-01
Full Text Available Voltage is an important variable that reflects system conditions in DC distribution systems and affects many characteristics of a system. In a DC distribution system, there is a close relationship between the real power and the voltage magnitude, and this is one of major differences from the characteristics of AC distribution systems. One such relationship is expressed as the voltage sensitivity, and an understanding of voltage sensitivity is very useful to describe DC distribution systems. In this paper, a formulation for a novel approximate expression for the voltage sensitivity in a radial DC distribution system is presented. The approximate expression is derived from the power flow equation with some additional assumptions. The results of approximate expression is compared with an exact calculation, and relations between the voltage sensitivity and electrical quantities are analyzed analytically using both the exact form and the approximate voltage sensitivity equation.
Commercialization of Medium Voltage HTS Triax TM Cable Systems
Energy Technology Data Exchange (ETDEWEB)
Knoll, David
2012-12-31
The original project scope that was established in 2007 aimed to install a 1,700 meter (1.1 mile) medium voltage HTS Triax{TM} cable system into the utility grid in New Orleans, LA. In 2010, however, the utility partner withdrew from the project, so the 1,700 meter cable installation was cancelled and the scope of work was reduced. The work then concentrated on the specific barriers to commercialization of HTS cable technology. The modified scope included long-length HTS cable design and testing, high voltage factory test development, optimized cooling system development, and HTS cable life-cycle analysis. In 2012, Southwire again analyzed the market for HTS cables and deemed the near term market acceptance to be low. The scope of work was further reduced to the completion of tasks already started and to testing of the existing HTS cable system in Columbus, OH. The work completed under the project included: • Long-length cable modeling and analysis • HTS wire evaluation and testing • Cable testing for AC losses • Optimized cooling system design • Life cycle testing of the HTS cable in Columbus, OH • Project management. The 200 meter long HTS Triax{TM} cable in Columbus, OH was incorporated into the project under the initial scope changes as a test bed for life cycle testing as well as the site for an optimized HTS cable cooling system. The Columbus cable utilizes the HTS TriaxTM design, so it provided an economical tool for these of the project tasks.
Optimum voltage of auxiliary systems for thermal and nuclear power plants
International Nuclear Information System (INIS)
Tokumitsu, Iwao; Segawa, Motomichi
1979-01-01
In the power plants in Japan, their unit power output has been greatly enhanced since the introduction of new powerful thermal power plants from 1950's to 1960's. In both thermal and nuclear power plants, 1,000 MW machines have been already in operation. The increase of unit power output results in the increase of in-plant load capacity. Of these the voltage adopted for in-plant low voltage systems is now mainly 440 V at load terminals, and the voltage for in-plant high voltage systems has been changing to 6 kV level via 3 kV and 4 kV levels. As plant capacity increases, the load of low voltage systems significantly increases, and it is required to raise the voltage of 400 V level. By the way, the low voltage in AC is specified to be not higher than 600 V. This makes the change within the above range comparatively easy. Considering these conditions, it is recommended to change the voltage for low voltage systems to 575 V at power source terminals and 550 V at load terminals. Some merits in constructing power systems and in economy by raising the voltage were examined. Though demerits are also found, they are only about 15% of total merits. The most advantageous point in raising the voltage is to be capable of increasing the supplying range to low voltage system loads. (Wakatsuki, Y.)
Directory of Open Access Journals (Sweden)
Subiyanto
2013-01-01
Full Text Available Photovoltaic (PV system is one of the promising renewable energy technologies. Although the energy conversion efficiency of the system is still low, but it has the advantage that the operating cost is free, very low maintenance and pollution-free. Maximum power point tracking (MPPT is a significant part of PV systems. This paper presents a novel intelligent MPPT controller for PV systems. For the MPPT algorithm, an optimized fuzzy logic controller (FLC using the Hopfield neural network is proposed. It utilizes an automatically tuned FLC membership function instead of the trial-and-error approach. The MPPT algorithm is implemented in a new variant of coupled inductor soft switching boost converter with high voltage gain to increase the converter output from the PV panel. The applied switching technique, which includes passive and active regenerative snubber circuits, reduces the insulated gate bipolar transistor switching losses. The proposed MPPT algorithm is implemented using the dSPACE DS1104 platform software on a DS1104 board controller. The prototype MPPT controller is tested using an agilent solar array simulator together with a 3 kW real PV panel. Experimental test results show that the proposed boost converter produces higher output voltages and gives better efficiency (90% than the conventional boost converter with an RCD snubber, which gives 81% efficiency. The prototype MPPT controller is also found to be capable of tracking power from the 3 kW PV array about 2.4 times more than that without using the MPPT controller.
Dinzi, R.; Hamonangan, TS; Fahmi, F.
2018-02-01
In the current distribution system, a large-capacity distribution transformer supplies loads to remote locations. The use of 220/380 V network is nowadays less common compared to 20 kV network. This results in losses due to the non-optimal distribution transformer, which neglected the load location, poor consumer profile, and large power losses along the carrier. This paper discusses how high voltage distribution systems (HVDS) can be a better system used in distribution networks than the currently used distribution system (Low Voltage Distribution System, LVDS). The proposed change of the system into the new configuration is done by replacing a large-capacity distribution transformer with some smaller-capacity distribution transformers and installed them in positions that closest to the load. The use of high voltage distribution systems will result in better voltage profiles and fewer power losses. From the non-technical side, the annual savings and payback periods on high voltage distribution systems will also be the advantage.
El-Zoghby, Helmy M.; Bendary, Ahmed F.
2016-10-01
Maximum Power Point Tracking (MPPT) is now widely used method in increasing the photovoltaic (PV) efficiency. The conventional MPPT methods have many problems concerning the accuracy, flexibility and efficiency. The MPP depends on the PV temperature and solar irradiation that randomly varied. In this paper an artificial intelligence based controller is presented through implementing of an Adaptive Neuro-Fuzzy Inference System (ANFIS) to obtain maximum power from PV. The ANFIS inputs are the temperature and cell current, and the output is optimal voltage at maximum power. During operation the trained ANFIS senses the PV current using suitable sensor and also senses the temperature to determine the optimal operating voltage that corresponds to the current at MPP. This voltage is used to control the boost converter duty cycle. The MATLAB simulation results shows the effectiveness of the ANFIS with sensing the PV current in obtaining the MPPT from the PV.
DEFF Research Database (Denmark)
Petersen, Lennart; Iov, Florin; Hansen, Anca Daniela
2016-01-01
This paper focusses on voltage control support and coordination between renewable generation plants in medium voltage distribution systems. An exemplary benchmark grid in Denmark, including a number of flexible ReGen plants providing voltage control functionality, is used as a base case. First......, voltage sensitivity analysis is performed to quantify node voltage variations due to injections of reactive power for given operational points of the network. The results are then used to develop an adaptive voltage droop control method, where various droop settings are allocated to each ReGen plant...... according to the sensitivity indices of corresponding node voltages and the location of respective ReGen plants in the distribution system. Case studies are performed in time-domain to analyze the impact of voltage fluctuations due to active power variations of ReGen plants in order to verify...
DEFF Research Database (Denmark)
Petersen, Lennart; Iov, Florin; Hansen, Anca Daniela
2016-01-01
This paper focusses on voltage control support and coordination between renewable generation plants in medium voltage distribution systems. An exemplary benchmark grid in Denmark, including a number of flexible ReGen plants providing voltage control functionality, is used as a base case. First...
Near-maximum-power-point-operation (nMPPO) design of photovoltaic power generation system
Energy Technology Data Exchange (ETDEWEB)
Huang, B.J.; Sun, F.S.; Ho, R.W. [Department of Mechanical Engineering, National Taiwan University, Taipei 106, Taiwan (China)
2006-08-15
The present study proposes a PV system design, called 'near-maximum power-point-operation' (nMPPO) that can maintain the performance very close to PV system with MPPT (maximum-power-point tracking) but eliminate hardware of the MPPT. The concept of nMPPO is to match the design of battery bank voltage V{sub set} with the MPP (maximum-power point) of the PV module based on an analysis using meteorological data. Three design methods are used in the present study to determine the optimal V{sub set}. The analytical results show that nMPPO is feasible and the optimal V{sub set} falls in the range 13.2-15.0V for MSX60 PV module. The long-term performance simulation shows that the overall nMPPO efficiency {eta}{sub nMPPO} is higher than 94%. Two outdoor field tests were carried out in the present study to verify the design of nMPPO. The test results for a single PV module (60Wp) indicate that the nMPPO efficiency {eta}{sub nMPPO} is mostly higher than 93% at various PV temperature T{sub pv}. Another long-term field test of 1kWp PV array using nMPPO shows that the power generation using nMPPO is almost identical with MPPT at various weather conditions and T{sub pv} variation from 24{sup o}C to 70{sup o}C. (author)
Accurate Maximum Power Tracking in Photovoltaic Systems Affected by Partial Shading
Directory of Open Access Journals (Sweden)
Pierluigi Guerriero
2015-01-01
Full Text Available A maximum power tracking algorithm exploiting operating point information gained on individual solar panels is presented. The proposed algorithm recognizes the presence of multiple local maxima in the power voltage curve of a shaded solar field and evaluates the coordinated of the absolute maximum. The effectiveness of the proposed approach is evidenced by means of circuit level simulation and experimental results. Experiments evidenced that, in comparison with a standard perturb and observe algorithm, we achieve faster convergence in normal operating conditions (when the solar field is uniformly illuminated and we accurately locate the absolute maximum power point in partial shading conditions, thus avoiding the convergence on local maxima.
Systems and methods for switched-inductor integrated voltage regulators
Shepard, Kenneth L.; Sturcken, Noah Andrew
2017-12-12
Power controller includes an output terminal having an output voltage, at least one clock generator to generate a plurality of clock signals and a plurality of hardware phases. Each hardware phase is coupled to the at least one clock generator and the output terminal and includes a comparator. Each hardware phase is configured to receive a corresponding one of the plurality of clock signals and a reference voltage, combine the corresponding clock signal and the reference voltage to produce a reference input, generate a feedback voltage based on the output voltage, compare the reference input and the feedback voltage using the comparator and provide a comparator output to the output terminal, whereby the comparator output determines a duty cycle of the power controller. An integrated circuit including the power controller is also provided.
Alemadi, Nasser Ahmed
Deregulation has brought opportunities for increasing efficiency of production and delivery and reduced costs to customers. Deregulation has also bought great challenges to provide the reliability and security customers have come to expect and demand from the electrical delivery system. One of the challenges in the deregulated power system is voltage instability. Voltage instability has become the principal constraint on power system operation for many utilities. Voltage instability is a unique problem because it can produce an uncontrollable, cascading instability that results in blackout for a large region or an entire country. In this work we define a system of advanced analytical methods and tools for secure and efficient operation of the power system in the deregulated environment. The work consists of two modules; (a) contingency selection module and (b) a Security Constrained Optimization module. The contingency selection module to be used for voltage instability is the Voltage Stability Security Assessment and Diagnosis (VSSAD). VSSAD shows that each voltage control area and its reactive reserve basin describe a subsystem or agent that has a unique voltage instability problem. VSSAD identifies each such agent. VS SAD is to assess proximity to voltage instability for each agent and rank voltage instability agents for each contingency simulated. Contingency selection and ranking for each agent is also performed. Diagnosis of where, why, when, and what can be done to cure voltage instability for each equipment outage and transaction change combination that has no load flow solution is also performed. A security constrained optimization module developed solves a minimum control solvability problem. A minimum control solvability problem obtains the reactive reserves through action of voltage control devices that VSSAD determines are needed in each agent to obtain solution of the load flow. VSSAD makes a physically impossible recommendation of adding reactive
A detailed comparison of system topologies for dynamic voltage restorers
DEFF Research Database (Denmark)
Nielsen, J.G.; Blaabjerg, Frede
2005-01-01
of energy storage, with energy taken from the grid during the voltage sag, and two topologies that take energy from stored energy devices during the voltage sag. Experimental tests using a 10-kVA DVR show that the no-energy storage concept is feasible, but an improved performance can be achieved for certain...... voltage sags using stored energy topologies. The results of this comparison rank the no-storage topology with a passive shunt converter on the load side first, followed by the stored energy topology with a constant dc-link voltage....
Directory of Open Access Journals (Sweden)
Ru-Min Chao
2016-01-01
Full Text Available This paper identifies the partial shading problem of a PV module using the one-diode model and simulating the characteristics exhibiting multiple-peak power output condition that is similar to a PV array. A modified particle swarm optimization (PSO algorithm based on the suggested search-agent deployment, retracking condition, and multicore operation is proposed in order to continuously locate the global maximum power point for the PV system. Partial shading simulation results for up to 16 modules in series/parallel formats are presented. A distributed PV system consisting of up to 8 a-silicon thin film PV panels and also having a dedicated DC/DC buck converter on each of the modules is tested. The converter reaches its steady state voltage output in 10 ms. However for MPPT operation, voltage, and current measurement interval is set to 20 ms to avoid unnecessary noise from the entire electric circuit. Based on the simulation and experiment results, each core of the proposed PSO operation should control no more than 4 PV modules in order to have the maximum tracking accuracy and minimum overall tracking time. Tracking for the global maximum power point of a distributed PV system under various partial shading conditions can be done within 1.3 seconds.
Directory of Open Access Journals (Sweden)
Tofael Ahmed
2014-06-01
Full Text Available In this paper, a single phase doubly grounded semi-Z-source inverter with maximum power point tracking (MPPT is proposed for photovoltaic (PV systems. This proposed system utilizes a single-ended primary inductor (SEPIC converter as DC-DC converter to implement the MPPT algorithm for tracking the maximum power from a PV array and a single phase semi-Z-source inverter for integrating the PV with AC power utilities. The MPPT controller utilizes a fast-converging algorithm to track the maximum power point (MPP and the semi-Z-source inverter utilizes a nonlinear SPWM to produce sinusoidal voltage at the output. The proposed system is able to track the MPP of PV arrays and produce an AC voltage at its output by utilizing only three switches. Experimental results show that the fast-converging MPPT algorithm has fast tracking response with appreciable MPP efficiency. In addition, the inverter shows the minimization of common mode leakage current with its ground sharing feature and reduction of the THD as well as DC current components at the output during DC-AC conversion.
Maximum likelihood convolutional decoding (MCD) performance due to system losses
Webster, L.
1976-01-01
A model for predicting the computational performance of a maximum likelihood convolutional decoder (MCD) operating in a noisy carrier reference environment is described. This model is used to develop a subroutine that will be utilized by the Telemetry Analysis Program to compute the MCD bit error rate. When this computational model is averaged over noisy reference phase errors using a high-rate interpolation scheme, the results are found to agree quite favorably with experimental measurements.
International Nuclear Information System (INIS)
Shokri, Abdollah; Shareef, Hussain; Mohamed, Azah; Farhoodnea, Masoud; Zayandehroodi, Hadi
2014-01-01
Highlights: • A new phase space based voltage mode controller for D-STATCOM was proposed. • The proposed compensator was tested to mitigate voltage disturbances in distribution systems. • Voltage fluctuation, voltage sag and voltage swell are considered to evaluate the performance of the proposed compensator. - Abstract: Distribution static synchronous compensator (D-STATCOM) has been developed and attained a great interest to compensate the power quality disturbances of distribution systems. In this paper, a novel single-phase control scheme for D-STATCOM is proposed to improve voltage profile at the Point of Common Coupling (PCC). The proposed voltage mode (VM) controller is based on the phase space algorithm, which is able to rapidly detect and mitigate any voltage deviations from reference voltage including voltage sags and voltage swells. To investigate the efficiency and accuracy of the proposed compensator, a system is modeled using Matlab/Simulink. The simulation results approve the capability of the proposed VM controller to provide a regulated and disturbance-free voltage for the connected loads at the PCC
High Voltage Homemade Capacitor Charger for Plasma Focus System
International Nuclear Information System (INIS)
Abdul Halim Baijan; Azaman Ahmad; Rokiah Mohd Sabri; Siti Aiasah Hashim; Mohd Rizal Md Chulan; Wah, L.K.; Azhar Ahmad; Rosli Che Ros; Mohd Faiz Mohd Zin
2015-01-01
A high voltage capacitor charger has been designed and built to replace a high voltage charger type General Atomics CCDs Power Supply which was damaged. The fabrication design was using materials which were easily available in the local market. Among the main components of the high-voltage charger is a transformer for neon lights, variable transformer rated 0 - 240 V 1 KVA, and 240 V transformer isolator. The results of experiments that have been conducted shows that a homemade capacitor charger was able to charge high voltage capacitors up to the required voltage of which was 12 kV. However the time taken for charging is quite long, up to more than 6 minutes. (author)
Isolated data acquisition system for high voltage applications
International Nuclear Information System (INIS)
Waitz, A.; Donaldson, A.
1985-06-01
This report describes the design and operation of a microcomputer controlled system for acquisition of both analog and binary data within the high voltage stages of a linac modulator. The system is comprised of a microprocessor Controller which communicates with the remote data Acquisition circuits via an optical bus. The bus, which uses a 1 MHz Manchester II format, is configured as a loop, starting at the Controller, daisy-chaining the remote cards and terminating back at the Controller. Upon receiving a linac timing pulse, the Controller sends addressed commands to the individual remote cards and receives data back. It then passes this data to the linac control system through a Multibus connection. Each remote circuit can return 16 binary sense and 7 (12 bit) analog parameters within 270 us. This speed is possible because of a pipelined design where one word is transmitted while another is being converted. A data conversion cycle is initiated when a remote data acquisition card receives the proper command and address from the controller
Quality Control of Mega Voltage Portal Imaging System
International Nuclear Information System (INIS)
Diklic, A.; Dundara Debeljuh, D.; Jurkovic, S.; Smilovic Radojcic, D.; Svabic Kolacio; Kasabasic, M.; Faj, D.
2013-01-01
The Electronic Portal Imaging Device (EPID) is a system used to verify either the correct positioning of the patient during radiotherapy treatment or the linear accelerator beam parameters. The correct position of the patient corresponds to the position at which the patient was scanned at the CT simulator and according to which the therapy plan was made and optimized. Regarding this, besides the advanced treatment planning system and optimized treatment planning techniques, the day-to-day reproduction of simulated conditions is of great importance for the treatment outcome. Therefore, to verify the patient set-up portal imaging should be applied prior to the first treatment session and repeated according to treatment prescriptions during the treatment. In order to achieve full functionality and precision of the EPID, it must be included in radiotherapy Quality Control (QC) programme. The QC of the Mega Voltage portal imaging system was separated in two parts. In the first, the QC of the detector parameters should be performed. For this purpose, the FC2 and QC3 phantoms should be used, along with the Portal Image Processing System program (PIPSpro) package for data analysis. The second part of the QC of the linear accelerator's portal imaging system should include the QC of the CBCT. In this part a set of predefined manufacturer's tests using two different phantoms, one for the geometry calibration and the other for the image quality evaluation, should be performed. Also, the treatment conditions should be simulated using anthropomorphic phantoms and dose distributions for particular EPID protocols should be measured. Procedures for quality control of the portal imaging system developed and implemented at University Hospital Rijeka are presented in this paper.(author)
A comparative study of voltage stability indices in a power system
Energy Technology Data Exchange (ETDEWEB)
Sinha, A.K. [I.I.T., Kharagpur (India). Dept. of Electrical Engineering; Hazarika, D. [Assam Engineering College (India)
2000-11-01
The paper compares the effectiveness of voltage stability indices in providing information about the proximity of voltage instability of a power system. Three simple voltage stability indices are proposed and their effectiveness is compared with some of the recently proposed indices. The comparison is carried out over a wide range of system operating conditions by changing the load power factor and feeder X/R ratios. Test results for the IEEE 57 bus and IEEE 118 bus system are presented. (author)
A Half-Bridge Voltage Balancer with New Controller for Bipolar DC Distribution Systems
Directory of Open Access Journals (Sweden)
Byung-Moon Han
2016-03-01
Full Text Available This paper proposes a half-bridge voltage balancer with a new controller for bipolar DC distribution systems. The proposed control scheme consists of two cascaded Proportional Integral (PI controls rather than one PI control for balancing the pole voltage. In order to confirm the excellence of voltage balancing performance, a typical bipolar DC distribution system including a half-bridge voltage balancer with proposed controller was analyzed by computer simulations. Experiments with a scaled prototype were also carried out to confirm the simulation results. The half-bridge voltage balancer with proposed controller shows better performance than the half-bridge voltage balancer with one PI control for balancing the pole voltage.
Short-Term State Forecasting-Based Optimal Voltage Regulation in Distribution Systems: Preprint
Energy Technology Data Exchange (ETDEWEB)
Yang, Rui; Jiang, Huaiguang; Zhang, Yingchen
2017-05-17
A novel short-term state forecasting-based optimal power flow (OPF) approach for distribution system voltage regulation is proposed in this paper. An extreme learning machine (ELM) based state forecaster is developed to accurately predict system states (voltage magnitudes and angles) in the near future. Based on the forecast system states, a dynamically weighted three-phase AC OPF problem is formulated to minimize the voltage violations with higher penalization on buses which are forecast to have higher voltage violations in the near future. By solving the proposed OPF problem, the controllable resources in the system are optimally coordinated to alleviate the potential severe voltage violations and improve the overall voltage profile. The proposed approach has been tested in a 12-bus distribution system and simulation results are presented to demonstrate the performance of the proposed approach.
Operation voltage of the counting system of nuclear traces in solids
International Nuclear Information System (INIS)
Garcia, M.L.; Quirino, L.L.; Mireles, F.; Davila, J.I.; Pinedo, J.L.; Lugo, J.F.; Vadillo, V.E.
2002-01-01
The semi-automatic counting system based on electric spark and used for traces reading in solid state detectors is evaluated for obtaining its counting voltage and also the breaking voltage of material. In the treatment of the solid state detectors it is continued the NTD methodology for concluding with the individual counting of the films, whose graphics offer the existing relationship among the applied voltage and the traces number. From each film a counting and breaking voltages are obtained. Finally, an average voltage of all them is estimated. (Author)
Corsi, Sandro
2015-01-01
Based on the author’s twenty years of experience, this book shows the practicality of modern, conceptually new, wide area voltage control in transmission and distribution smart grids, in detail. Evidence is given of the great advantages of this approach, as well as what can be gained by new control functionalities which modern technologies now available can provide. The distinction between solutions of wide area voltage regulation (V-WAR) and wide area voltage protection (V-WAP) are presented, demonstrating the proper synergy between them when they operate on the same power system as well as the simplicity and effectiveness of the protection solution in this case. The author provides an overview and detailed descriptions of voltage controls, distinguishing between generalities of underdeveloped, on-field operating applications and modern and available automatic control solutions, which are as yet not sufficiently known or perceived for what they are: practical, high-performance and reliable solutions. At th...
Using Expert Systems in Evaluation of the State of High Voltage Machine Insulation Systems
Directory of Open Access Journals (Sweden)
K. Záliš
2000-01-01
Full Text Available Expert systems are used for evaluating the actual state and future behavior of insulating systems of high voltage electrical machines and equipment. Several rule-based expert systems have been developed in cooperation with top diagnostic workplaces in the Czech Republic for this purpose. The IZOLEX expert system evaluates diagnostic measurement data from commonly used offline diagnostic methods for the diagnostic of high voltage insulation of rotating machines, non-rotating machines and insulating oils. The CVEX expert system evaluates the discharge activity on high voltage electrical machines and equipment by means of an off-line measurement. The CVEXON expert system is for evaluating the discharge activity by on-line measurement, and the ALTONEX expert system is the expert system for on-line monitoring of rotating machines. These developed expert systems are also used for educating students (in bachelor, master and post-graduate studies and in courses which are organized for practicing engineers and technicians and for specialists in the electrical power engineering branch. A complex project has recently been set up to evaluate the measurement of partial discharges. Two parallel expert systems for evaluating partial dischatge activity on high voltage electrical machines will work at the same time in this complex evaluating system.
Energy Technology Data Exchange (ETDEWEB)
Lin, Whei-Min; Hong, Chih-Ming [Department of Electrical Engineering, National Sun Yat-Sen University, Kaohsiung 80424 (China)
2010-06-15
To achieve maximum power point tracking (MPPT) for wind power generation systems, the rotational speed of wind turbines should be adjusted in real time according to wind speed. In this paper, a Wilcoxon radial basis function network (WRBFN) with hill-climb searching (HCS) MPPT strategy is proposed for a permanent magnet synchronous generator (PMSG) with a variable-speed wind turbine. A high-performance online training WRBFN using a back-propagation learning algorithm with modified particle swarm optimization (MPSO) regulating controller is designed for a PMSG. The MPSO is adopted in this study to adapt to the learning rates in the back-propagation process of the WRBFN to improve the learning capability. The MPPT strategy locates the system operation points along the maximum power curves based on the dc-link voltage of the inverter, thus avoiding the generator speed detection. (author)
Directory of Open Access Journals (Sweden)
Ramji Tiwari
2018-02-01
Full Text Available This paper proposes an artificial neural network (ANN based maximum power point tracking (MPPT control strategy for wind energy conversion system (WECS implemented with a DC/DC converter. The proposed topology utilizes a radial basis function network (RBFN based neural network control strategy to extract the maximum available power from the wind velocity. The results are compared with a classical Perturb and Observe (P&O method and Back propagation network (BPN method. In order to achieve a high voltage rating, the system is implemented with a quadratic boost converter and the performance of the converter is validated with a boost and single ended primary inductance converter (SEPIC. The performance of the MPPT technique along with a DC/DC converter is demonstrated using MATLAB/Simulink.
A Stochastic Maximum Principle for General Mean-Field Systems
International Nuclear Information System (INIS)
Buckdahn, Rainer; Li, Juan; Ma, Jin
2016-01-01
In this paper we study the optimal control problem for a class of general mean-field stochastic differential equations, in which the coefficients depend, nonlinearly, on both the state process as well as of its law. In particular, we assume that the control set is a general open set that is not necessary convex, and the coefficients are only continuous on the control variable without any further regularity or convexity. We validate the approach of Peng (SIAM J Control Optim 2(4):966–979, 1990) by considering the second order variational equations and the corresponding second order adjoint process in this setting, and we extend the Stochastic Maximum Principle of Buckdahn et al. (Appl Math Optim 64(2):197–216, 2011) to this general case.
A Stochastic Maximum Principle for General Mean-Field Systems
Energy Technology Data Exchange (ETDEWEB)
Buckdahn, Rainer, E-mail: Rainer.Buckdahn@univ-brest.fr [Université de Bretagne-Occidentale, Département de Mathématiques (France); Li, Juan, E-mail: juanli@sdu.edu.cn [Shandong University, Weihai, School of Mathematics and Statistics (China); Ma, Jin, E-mail: jinma@usc.edu [University of Southern California, Department of Mathematics (United States)
2016-12-15
In this paper we study the optimal control problem for a class of general mean-field stochastic differential equations, in which the coefficients depend, nonlinearly, on both the state process as well as of its law. In particular, we assume that the control set is a general open set that is not necessary convex, and the coefficients are only continuous on the control variable without any further regularity or convexity. We validate the approach of Peng (SIAM J Control Optim 2(4):966–979, 1990) by considering the second order variational equations and the corresponding second order adjoint process in this setting, and we extend the Stochastic Maximum Principle of Buckdahn et al. (Appl Math Optim 64(2):197–216, 2011) to this general case.
Transient voltage sharing in series-coupled high voltage switches
Directory of Open Access Journals (Sweden)
Editorial Office
1992-07-01
Full Text Available For switching voltages in excess of the maximum blocking voltage of a switching element (for example, thyristor, MOSFET or bipolar transistor such elements are often coupled in series - and additional circuitry has to be provided to ensure equal voltage sharing. Between each such series element and system ground there is a certain parasitic capacitance that may draw a significant current during high-speed voltage transients. The "open" switch is modelled as a ladder network. Analysis reveals an exponential progression in the distribution of the applied voltage across the elements. Overstressing thus occurs in some of the elements at levels of the total voltage that are significantly below the design value. This difficulty is overcome by grading the voltage sharing circuitry, coupled in parallel with each element, in a prescribed manner, as set out here.
Maximum-power-point tracking control of solar heating system
Huang, Bin-Juine; Ton, Wei-Zhe; Wu, Chen-Chun; Ko, Hua-Wei; Chang, Hsien-Shun; Yen, Rue-Her; Wang, Jiunn-Cherng
2012-01-01
was used to determine the instantaneous tracking target Q max(t). The system transfer-function model of solar heating system was also derived experimentally using a step response test and used in the design of tracking feedback control system. The PI
DiSC: A Simulation Framework for Distribution System Voltage Control
DEFF Research Database (Denmark)
Pedersen, Rasmus; Sloth, Christoffer Eg; Andresen, Gorm
2015-01-01
This paper presents the MATLAB simulation framework, DiSC, for verifying voltage control approaches in power distribution systems. It consists of real consumption data, stochastic models of renewable resources, flexible assets, electrical grid, and models of the underlying communication channels....... The simulation framework makes it possible to validate control approaches, and thus advance realistic and robust control algorithms for distribution system voltage control. Two examples demonstrate the potential voltage issues from penetration of renewables in the distribution grid, along with simple control...
A Case Study Of Turkish Transmission System For VoltageDips
DEFF Research Database (Denmark)
Inan, E.; Alboyaci, B.; Bak, Claus Leth
2009-01-01
Power quality problems usually appear in the form of voltage sags, transients and harmonics. From these three broad categories of power quality problems, voltage dips account the most disturbances experienced by industrial customers. Voltage dips generally refer to instantaneous short-duration vo......Power quality problems usually appear in the form of voltage sags, transients and harmonics. From these three broad categories of power quality problems, voltage dips account the most disturbances experienced by industrial customers. Voltage dips generally refer to instantaneous short...... analysis of voltage dip performance of the whole transmission system, is used to compare with results constructed fault statics from SIMPOW DIPS analysis program real data. SIMPOW DIPS software enables to calculate dip frequency for all busses and lines....
Common-mode Voltage Reduction in a Motor Drive System with a Power Factor Correction
DEFF Research Database (Denmark)
Adabi, J.; Boora, A.A.; Zare, F.
2012-01-01
Common-mode voltage generated by a power converter in combination with parasitic capacitive couplings is a potential source of shaft voltage in an AC motor drive system. In this study, a three-phase motor drive system supplied with a single-phase AC-DC diode rectifier is investigated in order...... to reduce shaft voltage in a three-phase AC motor drive system. In this topology, the AC-DC diode rectifier influences the common-mode voltage generated by the inverter because the placement of the neutral point is changing in different rectifier circuit states. A pulse width modulation technique...
Directory of Open Access Journals (Sweden)
Rozana Alik
2016-03-01
Full Text Available This paper presents a simple checking algorithm for maximum power point tracking (MPPT technique for Photovoltaic (PV system using Perturb and Observe (P&O algorithm. The main benefit of this checking algorithm is the simplicity and efficiency of the system whose duty cycle produced by the MPPT is smoother and changes faster according to maximum power point (MPP. This checking algorithm can determine the maximum power first before the P&O algorithm takes place to identify the voltage at MPP (VMPP, which is needed to calculate the duty cycle for the boost converter. To test the effectiveness of the algorithm, a simulation model of PV system has been carried out using MATLAB/Simulink under different level of irradiation; or in other words partially shaded condition of PV array. The results from the system using the proposed approach prove to have faster response and low ripple. Besides, the results are close to the desired outputs and exhibit an approximately 98.25% of the system efficiency. On the other hand, the system with conventional P&O MPPT seems to be unstable and has higher percentage of error. In summary, the proposed method is useful under varying level of irradiation with higher efficiency of the system.
Directory of Open Access Journals (Sweden)
Dariusz Kołodziej
2012-06-01
Full Text Available This paper presents examples of coordination between automatic voltage and reactive power control systems (ARST covering adjacent and strongly related extra high voltage substations. Included are conclusions resulting from the use of these solutions. The Institute of Power Engineering, Gdańsk Division has developed and deployed ARST systems in the national power system for a dozen or so years.
High voltage system design for the IUCF 300 KV electron cooling system
International Nuclear Information System (INIS)
Bertuccio, T.; Brown, B.; Donica, G.; Ellison, T.; Friesel, D.L.
1985-01-01
A summary of the electron beam high voltage system design for the IUCF Cooler now under construction, is presented. There are extremely stringent regulation requirements (about 10ppm) on the main high voltage power supply (-300 kVDC, 15 mA), and less stringent requirements on the gun anode power supply, in order to achieve the regulation needed to store beams in the IUCF Cooler with very low momentum spreads (Δp/p approx. = 2 x 10 -5 ). An overview of the main high voltage power supply (HVPS) specifications and design, as well as provisions and plans to improve the regulation are discussed. The electron collection system, modeled after the FNAL collector which was able to collect between 99.9% and 99.99% of the electron beam, is discussed along with the requirements of the associated power supplies. The designs of the high voltage acceleration structures and high voltage platform are discussed, as well as practical design considerations based upon experience with the Fermilab 120 keV electron cooling system
A Low-Cost Maximum Power Point Tracking System Based on Neural Network Inverse Model Controller
Directory of Open Access Journals (Sweden)
Carlos Robles Algarín
2018-01-01
Full Text Available This work presents the design, modeling, and implementation of a neural network inverse model controller for tracking the maximum power point of a photovoltaic (PV module. A nonlinear autoregressive network with exogenous inputs (NARX was implemented in a serial-parallel architecture. The PV module mathematical modeling was developed, a buck converter was designed to operate in the continuous conduction mode with a switching frequency of 20 KHz, and the dynamic neural controller was designed using the Neural Network Toolbox from Matlab/Simulink (MathWorks, Natick, MA, USA, and it was implemented on an open-hardware Arduino Mega board. To obtain the reference signals for the NARX and determine the 65 W PV module behavior, a system made of a 0.8 W PV cell, a temperature sensor, a voltage sensor and a static neural network, was used. To evaluate performance a comparison with the P&O traditional algorithm was done in terms of response time and oscillations around the operating point. Simulation results demonstrated the superiority of neural controller over the P&O. Implementation results showed that approximately the same power is obtained with both controllers, but the P&O controller presents oscillations between 7 W and 10 W, in contrast to the inverse controller, which had oscillations between 1 W and 2 W.
Control of total voltage in the large distributed RF system of LEP
Ciapala, Edmond
1995-01-01
The LEP RF system is made up of a large number of independent RF units situated around the ring near the interaction points. These have different available RF voltages depending on their type and they may be inactive or unable to provide full voltage for certain periods. The original RF voltage control system was based on local RF unit voltage function generators pre-loaded with individual tables for energy ramping. This was replaced this year by a more flexible global RF voltage control system. A central controller in the main control room has direct access to the units over the LEP TDM system via multiplexers and local serial links. It continuously checks the state of all the units and adjusts their voltages to maintain the desired total voltage under all conditions. This voltage is distributed among the individual units to reduce the adverse effects of RF voltage asymmetry around the machine as far as possible. The central controller is a VME system with 68040 CPU and real time multitasking operating syste...
Kobayashi, Kenji; Takano, Ichiro; Sawada, Yoshio
A photovoltaic array shows relatively low output power density, and has a greatly drooping Current-Voltage (I-V) characteristic. Therefore, Maximum Power Point Tracking (MPPT) control is used to maximize the output power of the array. Many papers have been reported in relation to MPPT. However, the Current-Power (I-P) curve sometimes shows multi-local maximum points mode under non-uniform insolation conditions. The operating point of the PV system tends to converge to a local maximum output point which is not the real maximal output point on the I-P curve. Some papers have been also reported, trying to avoid this difficulty. However most of those control systems become rather complicated. Then, the two stage MPPT control method is proposed in this paper to realize a relatively simple control system which can track the real maximum power point even under non-uniform insolation conditions. The feasibility of this control concept is confirmed for steady insolation as well as for rapidly changing insolation by simulation study using software PSIM and LabVIEW. In addition, simulated experiment confirms fundament al operation of the two stage MPPT control.
Energy Technology Data Exchange (ETDEWEB)
Kobayashi, Kenji; Takano, Ichiro; Sawada, Yoshio [Kogakuin University, Tokyo 163-8677 (Japan)
2006-11-23
A photovoltaic (PV) array shows relatively low output power density, and has a greatly drooping current-voltage (I-V) characteristic. Therefore, maximum power point tracking (MPPT) control is used to maximize the output power of the PV array. Many papers have been reported in relation to MPPT. However, the current-power (I-P) curve sometimes shows multi-local maximum point mode under non-uniform insolation conditions. The operating point of the PV system tends to converge to a local maximum output point which is not the real maximal output point on the I-P curve. Some papers have been also reported, trying to avoid this difficulty. However, most of those control systems become rather complicated. Then, the two stage MPPT control method is proposed in this paper to realize a relatively simple control system which can track the real maximum power point even under non-uniform insolation conditions. The feasibility of this control concept is confirmed for steady insolation as well as for rapidly changing insolation by simulation study using software PSIM and LabVIEW. (author)
BEHAVIOUR OF BACKFILL MATERIALS FOR ELECTRICAL GROUNDING SYSTEMS UNDER HIGH VOLTAGE CONDITIONS
Directory of Open Access Journals (Sweden)
S. C. LIM
2015-06-01
Full Text Available Backfill materials like Bentonite and cement are effective in lowering grounding resistance of electrodes for a considerable period. During lightning, switching impulses and earth fault occurrences in medium and high voltage networks, the grounding system needs to handle extremely high currents either for a short duration or prolonged period respectively. This paper investigates the behaviour of bentonite, cement and sand under impulse and alternating high voltage (50Hz conditions. Fulguritic-formation was observed in all materials under alternating high voltage. The findings reveal that performance of grounding systems under high voltage conditions may significantly change from the outcomes anticipated at design stage.
Design of auto-control high-voltage control system of pulsed neutron generator
International Nuclear Information System (INIS)
Lv Juntao
2008-01-01
It is difficult to produce multiple anode controlling time sequences under different logging mode for the high-voltage control system of the conventional pulsed neutron generator. It is also difficult realize sequential control among anode high-voltage, filament power supply and target voltage to make neutron yield stable. To these problems, an auto-control high-voltage system of neutron pulsed generator was designed. It not only can achieve anode high-voltage double blast time sequences, which can measure multiple neutron blast time sequences such as Σ, activated spectrum, etc. under inelastic scattering mode, but also can realize neutron generator real-time measurement of multi-state parameters and auto-control such as target voltage pulse width modulation (PWM), filament current, anode current, etc., there by it can produce stable neutron yield and realize stable and accurate measurement of the pulsed neutron full spectral loging tool. (authors)
30 CFR 75.803 - Fail safe ground check circuits on high-voltage resistance grounded systems.
2010-07-01
... High-Voltage Distribution § 75.803 Fail safe ground check circuits on high-voltage resistance grounded systems. [Statutory Provisions] On and after September 30, 1970, high-voltage, resistance grounded systems... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Fail safe ground check circuits on high-voltage...
Voltage-Ratio Calibration System up to 50 kHz
Trigo, Leonardo; Slomovitz, Daniel; Faverio, Carlos; Kyriazis, Gregory
2018-03-01
This paper describes a voltage-ratio measuring system that can be used up to 50 kHz with high accuracy. It is based on two Keysight 3458A digital multimeters, working in DCV sampling mode. An external trigger based on a rubidium clock, drives both digital multimeters. It is applied to the calibration of a set of voltage dividers with primary voltages from 4 V to 1024 V.
PV Power-Generation System with a Phase-Shift PWM Technique for High Step-Up Voltage Applications
Directory of Open Access Journals (Sweden)
Cheng-Tao Tsai
2012-01-01
Full Text Available A PV power-generation system with a phase-shift pulse-width modulation (PWM technique for high step-up voltage applications is proposed. The proposed power-generation system consists of two stages. In the input stage, all power switches of the full-bridge converter with phase-shift technique can be operated with zero-current switching (ZCS at turn-on or turn-off transition. Hence, the switching losses of the power switches can be reduced. Then, in the DC output stage, a voltage-doubler circuit is used to boost a high dc-link bus voltage. To supply a utility power, a dc/ac inverter is connected to induce a sinusoidal source. In order to draw a maximum power from PV arrays source, a microcontroller is incorporated with the perturbation and observation method to implement maximum power point tracking (MPPT algorithm and power regulating scheme. In this study, a full load power of 300 W prototype has been built. Experimental results are presented to verify the performance and feasibility of the proposed PV power-generation system.
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2013-01-01
The progressively growing of single-phase photovoltaic (PV) systems makes the Distribution System Operators (DSO) to update or revise the existing grid codes in order to guarantee the availability, quality and reliability of the electrical system. It is expected that the future PV systems connected...... to the low-voltage grid will be more active with functionalities of low voltage ride-through (LVRT) and the grid support capability, which is not the case today. In this paper, the operation principle is demonstrated for a single-phase grid-connected PV system in low voltage ride through operation in order...... to map future challenges. The system is verified by simulations and experiments. Test results show that the proposed power control method is effective and the single-phase PV inverters connected to low-voltage networks are ready to provide grid support and ride-through voltage fault capability...
Perisic, Milun; Kinoshita, Michael H; Ranson, Ray M; Gallegos-Lopez, Gabriel
2014-06-03
Methods, system and apparatus are provided for controlling third harmonic voltages when operating a multi-phase machine in an overmodulation region. The multi-phase machine can be, for example, a five-phase machine in a vector controlled motor drive system that includes a five-phase PWM controlled inverter module that drives the five-phase machine. Techniques for overmodulating a reference voltage vector are provided. For example, when the reference voltage vector is determined to be within the overmodulation region, an angle of the reference voltage vector can be modified to generate a reference voltage overmodulation control angle, and a magnitude of the reference voltage vector can be modified, based on the reference voltage overmodulation control angle, to generate a modified magnitude of the reference voltage vector. By modifying the reference voltage vector, voltage command signals that control a five-phase inverter module can be optimized to increase output voltages generated by the five-phase inverter module.
Directory of Open Access Journals (Sweden)
ABYANEH, H. A.
2010-11-01
Full Text Available Development of distribution network and power consumption growth, increase voltage drop on the line impedance and therefore voltage drop in system buses. In some cases consumption is so high that voltage in some buses exceed from standard. In this paper, effect of the fuel cell and photovoltaic hybrid system on distribution network for solving expressed problem is studied. For determining the capacity of each distributed generation source, voltage limitation on the bus voltages under different conditions is considered. Simulation is done by using DIgSILENT software on the part of the 20 kV real life Sirjan distribution system. In this article, optimum location with regard to system and environmental conditions are studied in two different viewpoints.
Voltage regulator placement in radial distribution system using plant ...
African Journals Online (AJOL)
user
location and number along with tap setting of the voltage regulators that ... can be fixed or switched type; they are considered integer multiple of a capacitor unit ..... By simulating the growth process of plant phototropism, a probability model ..... He is referee for IEE Proceedings - Generation Transmission and Distribution and ...
Restoration of Low-Voltage Distribution Systems with Inverter-Interfaced DG Units
DEFF Research Database (Denmark)
Dietmannsberger, Markus; Wang, Xiongfei; Blaabjerg, Frede
2018-01-01
-area voltage collapse. This paper proposes a restoration strategy from zero voltage conditions for inverter-interfaced DG under islanded conditions. In the approach, a flexible and scalable Master DG inverter concept is introduced for distributed generations, where no communication is needed and an outage......The increasing share of distributed generation (DG) offers new chances in grid restoration of low-voltage distribution grids. Instead of relying on the transmission or high- and medium-voltage levels, establishing islanding operation in low-voltage grids might be a good option after a wide...... of the Master can be balanced by other DG inverters. The control strategy ensures the tracking of nominal values of the system voltage and frequency without zero steady-state error. The influences of non-controllable DG are also taken into account in the strategy with an effective countermeasure developed...
An analog RF gap voltage regulation system for the Advanced Photon Source storage ring
International Nuclear Information System (INIS)
Horan, D.
1999-01-01
An analog rf gap voltage regulation system has been designed and built at Argonne National Laboratory to maintain constant total storage ring rf gap voltage, independent of beam loading and cavity tuning effects. The design uses feedback control of the klystron mod-anode voltage to vary the amount of rf power fed to the storage ring cavities. The system consists of two independent feedback loops, each regulating the combined rf gap voltages of eight storage ring cavities by varying the output power of either one or two rf stations, depending on the mode of operation. It provides full operator control and permissive logic to permit feedback control of the rf system output power only if proper conditions are met. The feedback system uses envelope-detected cavity field probe outputs as the feedback signal. Two different methods of combining the individual field probe signals were used to generate a relative DC level representing one-half of the total storage ring rf voltage, an envelope-detected vector sum of the field probe rf signals, and the DC sum of individual field probe envelope detector outputs. The merits of both methods are discussed. The klystron high-voltage power supply (HVPS) units are fitted with an analog interface for external control of the mod-anode voltage level, using a four-quadrant analog multiplier to modulate the HVPS mod-anode voltage regulator set-point in response to feedback system commands
International Nuclear Information System (INIS)
Ferreira, Andreza C.; Blasques, Luis C. M.; Galhardo, Marcos A. B.; Pinho, João T.
2017-01-01
This paper describes the modeling of the electrical equipment and control mechanisms used in the power conditioning system of a grid-connected photovoltaic system (GCPVS), such as the photovoltaic generator, the DC/DC converter, the voltage inverter with PWM control, its output filter, as well as the converter controls and their functionalities, and the interconnection of the system with the distribution grid and load. In addition to the modeling of the grid-tie inverter, the main equipment of the power conditioning system, this paper describes the synchronization form of the photovoltaic (PV) generation with the electricity distribution grid, considering the power injection control method, the maximum power point tracking technique for maximizing the energy supplied by the photovoltaic generator, and the complete topology of the proposed PV system. The main objective is to provide a computational model capable of simulating the behavior of the GCPVS elements, varying the climatic conditions and the power demand on the AC side, presenting consistent results for different operating conditions, such as variations of climatic parameters (solar irradiance, wind speed, and ambient temperature) and load. In these cases, it is possible to evaluate the behavior of the system, sometimes supplying both the active and reactive power of the load, according to the need. (author)
A pragmatic approach to voltage stability analysis of large power systems
Energy Technology Data Exchange (ETDEWEB)
Sarmiento, H.G.; Pampin, G. [Inst. de Investigaciones Electricas, Morelos (Mexico); Diaz de Leon, J.A. [American Superconductor, Middleton, WI (United States)
2008-07-01
A methodology for performing voltage stability analyses for large power systems was presented. Modal and time-domain analyses were used for selection and siting solutions for potential voltage instability and collapse. Steady state systems were used to compute the smallest eigenvalues and associated eigenvalues of a reduced Jacobean matrix. The eigenvalues were used to provide a relative measure of proximity to voltage instability. The analysis was applied to provide an indication of a network's proximity to voltage collapse. Negative eigenvalues were representative of voltage instability conditions, while small positive values indicated proximity to voltage instability. The analysis technique was used to identify buses, lines, and generators prone to voltage instabilities for a 10-node network. A comparative analysis of results obtained from modal and time domain analyses were used to identify areas vulnerable to voltage instability conditions. Pre-fault, fault, and post-fault conditions were analyzed statically and dynamically. Results of the study showed that the combined method can be used to identify and place reactive power compensation solutions for voltage collapses in electric networks. 20 refs., 5 tabs., 7 figs.
Bias-Voltage Stabilizer for HVHF Amplifiers in VHF Pulse-Echo Measurement Systems.
Choi, Hojong; Park, Chulwoo; Kim, Jungsuk; Jung, Hayong
2017-10-23
The impact of high-voltage-high-frequency (HVHF) amplifiers on echo-signal quality is greater with very-high-frequency (VHF, ≥100 MHz) ultrasound transducers than with low-frequency (LF, ≤15 MHz) ultrasound transducers. Hence, the bias voltage of an HVHF amplifier must be stabilized to ensure stable echo-signal amplitudes. We propose a bias-voltage stabilizer circuit to maintain stable DC voltages over a wide input range, thus reducing the harmonic-distortion components of the echo signals in VHF pulse-echo measurement systems. To confirm the feasibility of the bias-voltage stabilizer, we measured and compared the deviations in the gain of the HVHF amplifier with and without a bias-voltage stabilizer. Between -13 and 26 dBm, the measured gain deviations of a HVHF amplifier with a bias-voltage stabilizer are less than that of an amplifier without a bias-voltage stabilizer. In order to confirm the feasibility of the bias-voltage stabilizer, we compared the pulse-echo responses of the amplifiers, which are typically used for the evaluation of transducers or electronic components used in pulse-echo measurement systems. From the responses, we observed that the amplitudes of the echo signals of a VHF transducer triggered by the HVHF amplifier with a bias-voltage stabilizer were higher than those of the transducer triggered by the HVHF amplifier alone. The second, third, and fourth harmonic-distortion components of the HVHF amplifier with the bias-voltage stabilizer were also lower than those of the HVHF amplifier alone. Hence, the proposed scheme is a promising method for stabilizing the bias voltage of an HVHF amplifier, and improving the echo-signal quality of VHF transducers.
DEFF Research Database (Denmark)
Choi, Ui-Min; Blaabjerg, Frede; Lee, Kyo-Beum
2015-01-01
The centralized topology with three-level inverters are widely used in photovoltaic (PV) systems due to their less installation costs and complexity. However, the common maximum power point tracking (MPPT) is a disadvantage of the centralized topology particularly under the partial shading...... and panel mismatch conditions. In this system, if PV modules are separately connected to the split capacitor voltage, the MPPT efficiency can be improved by the proposed control strategy. By the proposed method, the two capacitor voltages can be controlled asymmetrically to perform the separate MPPTs...... of each PV module connected to separate capacitors. The outputs can be generated without distortion even if two capacitors are asymmetrically regulated. Simulation and experimental results verify the validity and feasibility of the proposed methods....
Chalise, Santosh
Although solar photovoltaic (PV) systems have remained the fastest growing renewable power generating technology, variability as well as uncertainty in the output of PV plants is a significant issue. This rapid increase in PV grid-connected generation presents not only progress in clean energy but also challenges in integration with traditional electric power grids which were designed for transmission and distribution of power from central stations. Unlike conventional electric generators, PV panels do not have rotating parts and thus have no inertia. This potentially causes a problem when the solar irradiance incident upon a PV plant changes suddenly, for example, when scattered clouds pass quickly overhead. The output power of the PV plant may fluctuate nearly as rapidly as the incident irradiance. These rapid power output fluctuations may then cause voltage fluctuations, frequency fluctuations, and power quality issues. These power quality issues are more severe with increasing PV plant power output. This limits the maximum power output allowed from interconnected PV plants. Voltage regulation of a distribution system, a focus of this research, is a prime limiting factor in PV penetration levels. The IEEE 13-node test feeder, modeled and tested in the MATLAB/Simulink environment, was used as an example distribution feeder to analyze the maximum acceptable penetration of a PV plant. The effect of the PV plant's location was investigated, along with the addition of a VAR compensating device (a D-STATCOM in this case). The results were used to develop simple guidelines for determining an initial estimate of the maximum PV penetration level on a distribution feeder. For example, when no compensating devices are added to the system, a higher level of PV penetration is generally achieved by installing the PV plant close to the substation. The opposite is true when a VAR compensator is installed with the PV plant. In these cases, PV penetration levels over 50% may be
Directory of Open Access Journals (Sweden)
Qiang Jiaxi
2013-01-01
Full Text Available Batteries, as the main or assistant power source of EV (Electric Vehicle, are usually connected in series with high voltage to improve the drivability and energy efficiency. Today, more and more batteries are connected in series with high voltage, if there is any fault in high voltage system (HVS, the consequence is serious and dangerous. Therefore, it is necessary to monitor the electric parameters of HVS to ensure the high voltage safety and protect personal safety. In this study, a high voltage safety monitor system is developed to solve this critical issue. Four key electric parameters including precharge, contact resistance, insulation resistance, and remaining capacity are monitored and analyzed based on the equivalent models presented in this study. The high voltage safety controller which integrates the equivalent models and control strategy is developed. By the help of hardware-in-loop system, the equivalent models integrated in the high voltage safety controller are validated, and the online electric parameters monitor strategy is analyzed and discussed. The test results indicate that the high voltage safety monitor system designed in this paper is suitable for EV application.
Transient Voltage Stability Analysis and Improvement of A Network with different HVDC Systems
DEFF Research Database (Denmark)
Liu, Yan; Chen, Zhe
2011-01-01
This paper presents transient voltage stability analysis of an AC system with multi-infeed HVDC links including a traditional LCC HVDC link and a VSC HVDC link. It is found that the voltage supporting capability of the VSC-HVDC link is significantly influenced by the tie-line distance between the...
Dynamics of voltage source converter in a grid connected solar photovoltaic system
DEFF Research Database (Denmark)
Haribabu, Divyanagalakshmi; Vangari, Adithya; Sakamuri, Jayachandra N.
2015-01-01
This paper emphasises the modelling and control of a voltage source converter (VSC) for three phase grid connected PV system. The transfer functions for inner current control and outer DC link voltage control for VSC are derived. The controllers for VSC are designed based on PI and K factor contr...
Multi-Period Optimization for Voltage Control System in Transmission Grids
DEFF Research Database (Denmark)
Qin, Nan; Chen, Si; Liu, Chengxi
2015-01-01
Automatic Voltage Control (AVC) systems maintain the voltage in an acceptable range and minimize the power loss of the grid by coordinately regulating the controllable components. Switchable shunts and tap-able transformers are expected to be operated as few times as possible. This paper proposes...
Computation of Steady State Nodal Voltages for Fast Security Assessment in Power Systems
DEFF Research Database (Denmark)
Møller, Jakob Glarbo; Jóhannsson, Hjörtur; Østergaard, Jacob
2014-01-01
Development of a method for real-time assess-ment of post-contingency nodal voltages is introduced. Linear network theory is applied in an algorithm that utilizes Thevenin equivalent representation of power systems as seen from every voltage-controlled node in a network. The method is evaluated b...
Jiaxi, Qiang; Lin, Yang; Jianhui, He; Qisheng, Zhou
2013-01-01
Batteries, as the main or assistant power source of EV (Electric Vehicle), are usually connected in series with high voltage to improve the drivability and energy efficiency. Today, more and more batteries are connected in series with high voltage, if there is any fault in high voltage system (HVS), the consequence is serious and dangerous. Therefore, it is necessary to monitor the electric parameters of HVS to ensure the high voltage safety and protect personal safety. In this study, a high voltage safety monitor system is developed to solve this critical issue. Four key electric parameters including precharge, contact resistance, insulation resistance, and remaining capacity are monitored and analyzed based on the equivalent models presented in this study. The high voltage safety controller which integrates the equivalent models and control strategy is developed. By the help of hardware-in-loop system, the equivalent models integrated in the high voltage safety controller are validated, and the online electric parameters monitor strategy is analyzed and discussed. The test results indicate that the high voltage safety monitor system designed in this paper is suitable for EV application.
A nanosecond high voltage pulse device for accelerator time analytical system
International Nuclear Information System (INIS)
Lou Binqiao; Ding Furong; Xue Zhihua; Wang Xuemei; Shen Dingyu
2002-01-01
A nanosecond high voltage pulse device has been designed. The pulse rise time is 10 ns. The pulse voltage reached 16000 V. This device has been used to accelerator time analytical system, its resolution time is less than 0.8%
DC-link Voltage Coordinative-Proportional Control in Cascaded Converter Systems
DEFF Research Database (Denmark)
Tian, Yanjun; Loh, Poh Chiang; Deng, Fujin
2015-01-01
PI controllers are frequently implemented in cascaded converter system to control the DC-link voltage, because they can achieve zero steady state error. However the PI controller adds a pole at the origin point and a zero on the left half plane, and it increases the control system type number......, and then the system is more difficult to control. This paper proposed a DC-link control method for the two stages cascaded converter, and it uses proportional controller for the DC-link voltage control. This control method can achieve zero steady state error on the DC-link voltage; reduce the control system type...
International Nuclear Information System (INIS)
Enslin, J.H.R.
1990-01-01
A well engineered renewable remote energy system, utilizing the principal of Maximum Power Point Tracking can be m ore cost effective, has a higher reliability and can improve the quality of life in remote areas. This paper reports that a high-efficient power electronic converter, for converting the output voltage of a solar panel, or wind generator, to the required DC battery bus voltage has been realized. The converter is controlled to track the maximum power point of the input source under varying input and output parameters. Maximum power point tracking for relative small systems is achieved by maximization of the output current in a battery charging regulator, using an optimized hill-climbing, inexpensive microprocessor based algorithm. Through practical field measurements it is shown that a minimum input source saving of 15% on 3-5 kWh/day systems can easily be achieved. A total cost saving of at least 10-15% on the capital cost of these systems are achievable for relative small rating Remote Area Power Supply systems. The advantages at larger temperature variations and larger power rated systems are much higher. Other advantages include optimal sizing and system monitor and control
2017-07-31
integrated into unique power system architectures that employ energy generation and storage capable of working together to supply the intermittent ...unidirectional and bidirectional TVS diodes is seen in Figure 3. TVS diodes are known for having fast switch on times but their switch off times are...switch in the circuit, simulating the fast changes in current in the profile of interest. The simulation is run for 50 ms and the initial condition of
Identification of voltage stability condition of a power system using measurements of bus variables
Directory of Open Access Journals (Sweden)
Durlav Hazarika
2014-12-01
Full Text Available Several online methods were proposed for investigating the voltage stability condition of an interconnected power system using the measurements of voltage and current phasors at a bus. For this purpose, phasor measurement units (PMUs are used. A PMU is a device which measures the electrical waves on an electrical network, using a common time source (reference bus for synchronisation. This study proposes a method for online monitoring of voltage stability condition of a power system using measurements of bus variables namely – (i real power, (ii reactive power and (iii bus voltage magnitude at a bus. The measurements of real power, reactive power and bus voltage magnitude could be extracted/captured from a smart energy meter. The financial involvement for implementation of the proposed method would significantly lower compared with the PMU-based method.
Optimized Controller Design for a 12-Pulse Voltage Source Converter Based HVDC System
Agarwal, Ruchi; Singh, Sanjeev
2017-12-01
The paper proposes an optimized controller design scheme for power quality improvement in 12-pulse voltage source converter based high voltage direct current system. The proposed scheme is hybrid combination of golden section search and successive linear search method. The paper aims at reduction of current sensor and optimization of controller. The voltage and current controller parameters are selected for optimization due to its impact on power quality. The proposed algorithm for controller optimizes the objective function which is composed of current harmonic distortion, power factor, and DC voltage ripples. The detailed designs and modeling of the complete system are discussed and its simulation is carried out in MATLAB-Simulink environment. The obtained results are presented to demonstrate the effectiveness of the proposed scheme under different transient conditions such as load perturbation, non-linear load condition, voltage sag condition, and tapped load fault under one phase open condition at both points-of-common coupling.
A portable storage maximum thermometer
International Nuclear Information System (INIS)
Fayart, Gerard.
1976-01-01
A clinical thermometer storing the voltage corresponding to the maximum temperature in an analog memory is described. End of the measurement is shown by a lamp switch out. The measurement time is shortened by means of a low thermal inertia platinum probe. This portable thermometer is fitted with cell test and calibration system [fr
Marzocchi, Badder
2017-01-01
The CMS Electromagnetic Calorimeter is made of scintillating lead tungstate crystals, using avalanche photodiodes (APD) as photo-detectors in the barrel part. The high voltage system, consisting of 1224 channels, biases groups of 50 APD pairs, each at a voltage of about 380 V. The APD gain dependence on the voltage is 3pct/V. A stability of better than 60 mV is needed to have negligible impact on the calorimeter energy resolution. Until 2015 manual calibrations were performed yearly. A new calibration system was deployed recently, which satisfies the requirement of low disturbance and high precision. The system is discussed in detail and first operational experience is presented.
The Possibility of Functioning at Maximum Power for Solar Photovoltaic - Electric Battery Systems
Directory of Open Access Journals (Sweden)
Chioncel Cristian Paul
2013-01-01
Full Text Available The paper presents the functioning of a solar photovoltaic module(PVM that debits direct to on electric battery (EB. By a good adaptingof PVM to EB, so that the no load voltage of the two components (PVMand EB are well suited, during a day the energy value can be reachednear to the maximum possible value, when the PVM functions in themaximum power point (MPP. The proposed solution is much moreeconomic than the classical: PVM + DC – DC + EB because the directcurrent - direct current power converter, is not necessary (DC - DC.
The system of high-voltage power PMT for experiments at the JINR Nuclotron
International Nuclear Information System (INIS)
Piyadin, S.M.; Ladygin, V.P.; Pilyar, A.V.; Reznikov, S.G.; Janek, M.
2015-01-01
An 8-channel high-voltage power system based on the use of the module «Wenzel Elektronik N1130» is described. Specifications of control modules 8DAC-12 and 8ADC-14 designed for the high-voltage systems in CAMAC standard are presented. This system is designed to provide the power for the detectors used in physics experiments at the JINR Nuclotron.
Charging system of ECRH high-voltage power supply and its control system
International Nuclear Information System (INIS)
Hu Guofu; Ding Tonghai; Liu Baohua; Jiang Shufang
2003-01-01
High-voltage power supply (HVPS) of Electron Cyclotron Resonance Heating (ECRH) for HT-7 and HT-7U is presently being constructed. The high voltage (100 kV) energy of HVPS is stored in the capacitor banks, and they can power one or two gyrotrons. All the operation of the charging system will be done by the control system, where the field signals are interfaced to programmable logic controller (PLC). The use of PLC not only simplifies the control system, but also enhances the reliability. The software written by using configuration software installed in the master computer allows for remote and multiple operator control, and the status and data information is also remotely available
Altin, Necmi
2018-05-01
An interval type-2 fuzzy logic controller-based maximum power point tracking algorithm and direct current-direct current (DC-DC) converter topology are proposed for photovoltaic (PV) systems. The proposed maximum power point tracking algorithm is designed based on an interval type-2 fuzzy logic controller that has an ability to handle uncertainties. The change in PV power and the change in PV voltage are determined as inputs of the proposed controller, while the change in duty cycle is determined as the output of the controller. Seven interval type-2 fuzzy sets are determined and used as membership functions for input and output variables. The quadratic boost converter provides high voltage step-up ability without any reduction in performance and stability of the system. The performance of the proposed system is validated through MATLAB/Simulink simulations. It is seen that the proposed system provides high maximum power point tracking speed and accuracy even for fast changing atmospheric conditions and high voltage step-up requirements.
On the Pontryagin maximum principle for systems with delays. Economic applications
Kim, A. V.; Kormyshev, V. M.; Kwon, O. B.; Mukhametshin, E. R.
2017-11-01
The Pontryagin maximum principle [6] is the key stone of finite-dimensional optimal control theory [1, 2, 5]. So beginning with opening the maximum principle it was important to extend the maximum principle on various classes of dynamical systems. In t he paper we consider some aspects of application of i-smooth analysis [3, 4] in the theory of the Pontryagin maximum principle [6] for systems with delays, obtained results can be applied by elaborating optimal program controls in economic models with delays.
Directory of Open Access Journals (Sweden)
Rui Li
2016-12-01
Full Text Available The AC voltage control of a DC/DC converter based on the modular multilevel converter (MMC is considered under normal operation and during a local DC fault. By actively setting the AC voltage according to the two DC voltages of the DC/DC converter, the modulation index can be near unity, and the DC voltage is effectively utilized to output higher AC voltage. This significantly decreases submodule (SM capacitance and conduction losses of the DC/DC converter, yielding reduced capital cost, volume, and higher efficiency. Additionally, the AC voltage is limited in the controllable range of both the MMCs in the DC/DC converter; thus, over-modulation and uncontrolled currents are actively avoided. The AC voltage control of the DC/DC converter during local DC faults, i.e., standby operation, is also proposed, where only the MMC connected on the faulty cable is blocked, while the other MMC remains operational with zero AC voltage output. Thus, the capacitor voltages can be regulated at the rated value and the decrease of the SM capacitor voltages after the blocking of the DC/DC converter is avoided. Moreover, the fault can still be isolated as quickly as the conventional approach, where both MMCs are blocked and the DC/DC converter is not exposed to the risk of overcurrent. The proposed AC voltage control strategy is assessed in a three-terminal high-voltage direct current (HVDC system incorporating a DC/DC converter, and the simulation results confirm its feasibility.
Directory of Open Access Journals (Sweden)
Mustafa Inci
2018-01-01
Full Text Available Voltage harmonics, sag, and swell are the most harmful disturbances in distribution systems. This paper introduces a novel effective controller method for simultaneous compensation of both voltage sag/swell and voltage harmonics by using multifunctional dynamic voltage restorer. In proposed controller method called FFT with integrated ISRF, ISRF detects the magnitudes of voltage sag/swell quickly and precisely, and FFT extracts the selective components of voltage harmonics very effectively. The proposed method integrates the superior properties of ISRF and FFT methods. FFT integrated ISRF is applied for the first time to provide the compensation of both sag/swell and selective harmonics together. The proposed system has ability to compensate symmetrical/asymmetrical sag/swell and symmetrical/asymmetrical selective harmonics which are 5th, 7th, 11th and 13th. The controlled system is modelled in PSCAD/EMDTC and compared with conventional methods. The performance results verify that the proposed method compensates voltage disturbances effectively in the system.
International Nuclear Information System (INIS)
Daili, Yacine; Gaubert, Jean-Paul; Rahmani, Lazhar
2015-01-01
Highlights: • A new maximum power point tracking algorithm for small wind turbines is proposed. • This algorithm resolves the problems of the classical perturb and observe method. • The proposed method has been tested under several wind speed profiles. • The validity of the new algorithm has been confirmed by the experimental results. - Abstract: This paper proposes a modified perturbation and observation maximum power point tracking algorithm for small wind energy conversion systems to overcome the problems of the conventional perturbation and observation technique, namely rapidity/efficiency trade-off and the divergence from peak power under a fast variation of the wind speed. Two modes of operation are used by this algorithm, the normal perturbation and observation mode and the predictive mode. The normal perturbation and observation mode with small step-size is switched under a slow wind speed variation to track the true maximum power point with fewer fluctuations in steady state. When a rapid change of wind speed is detected, the algorithm tracks the new maximum power point in two phases: in the first stage, the algorithm switches to the predictive mode in which the step-size is auto-adjusted according to the distance between the operating point and the estimated optimum point to move the operating point near to the maximum power point rapidly, and then the normal perturbation and observation mode is used to track the true peak power in the second stage. The dc-link voltage variation is used to detect rapid wind changes. The proposed algorithm does not require either knowledge of system parameters or of mechanical sensors. The experimental results confirm that the proposed algorithm has a better performance in terms of dynamic response and efficiency compared with the conventional perturbation and observation algorithm
A new VME-based high voltage power supply for large photomultiplier systems
International Nuclear Information System (INIS)
Neumaier, S.; Hubbeling, T.; Kolb, B.W.; Purschke, M.L.; Ippolitov, M.; Blume, C.; Bohne, E.M.; Bucher, D.; Claussen, A.; Peitzmann, T.; Schepers, G.; Schlagheck, H.
1995-01-01
We describe a new high voltage power supply, developed for the leadglass calorimeter of the WA98 experiment at CERN. The high voltage is produced for each of the 10,080 photomultiplier tubes of the detector individually, by the same number of active bases with on-board Greinacher voltage multipliers. The full VME-based HV controller system, which addresses each base via bus cables once per second, is miniaturized and fits into a single VME crate. The main advantages of this approach are the low heat dissipation, the considerably reduced amount of cabling and cost, as well as the high stability and low noise of the system. (orig.)
Design Comparison of Autonomous High Voltage Driving System for DEAP Actuator
DEFF Research Database (Denmark)
Huang, Lina; Pittini, Riccardo; Zhang, Zhe
2014-01-01
As a new type of smart material, the Dielectric Electro Active Polymer (DEAP) is introduced in terms of configuration, working principle and potential applications. The design of an autonomous high voltage driving system for DEAP actuator is investigated. The system configuration and the design...... methodology of a high voltage converter are discussed in detail. Based on the heating valve application, three different high voltage converter solutions have been proposed. The different proposals have been compared in terms of energy loss, volume and cost. Finally, the design selection suggestions...
Application of Multipoint DC Voltage Control in VSC-MTDC System
Directory of Open Access Journals (Sweden)
Yang Xi
2013-01-01
Full Text Available The voltage-source-converter- (VSC- based multiterminal VSC-HVDC power transmission system (VSC-MTDC is an ideal approach to connect wind farm with power grid. Analyzing the characteristics of doubly fed induction generators as well as the basic principle and the control strategy of VSC-MTDC, a multiterminal DC voltage control strategy suitable for wind farm connected with VSC-MTDC is proposed. By use of PSCAD/EMTDC, the proposed control strategy is simulated, and simulation results show that using the proposed control strategy the conversion between constant power control mode and constant DC voltage control mode can be automatically implemented; thus the DC voltage stability control and reliable power output of wind farm can be ensured after the fault-caused outage of converter station controlled by constant DC voltage and under other faults. The simulation result shows that the model can fulfill multiterminal power transmission and fast response control.
A Self-Biased Active Voltage Doubler for Energy Harvesting Systems
Tayyab, Umais; Alzaher, Hussain A.
2017-01-01
An active voltage doubler utilizing a single supply op-amp for energy harvesting system is presented. The proposed doubler is used for rectification process to achieve both acceptably high power conversion efficiency (PCE) and large rectified DC
A Grid Voltage Measurement Method for Wind Power Systems during Grid Fault Conditions
Directory of Open Access Journals (Sweden)
Cheol-Hee Yoo
2014-11-01
Full Text Available Grid codes in many countries require low-voltage ride-through (LVRT capability to maintain power system stability and reliability during grid fault conditions. To meet the LVRT requirement, wind power systems must stay connected to the grid and also supply reactive currents to the grid to support the recovery from fault voltages. This paper presents a new fault detection method and inverter control scheme to improve the LVRT capability for full-scale permanent magnet synchronous generator (PMSG wind power systems. Fast fault detection can help the wind power systems maintain the DC-link voltage in a safe region. The proposed fault detection method is based on on-line adaptive parameter estimation. The performance of the proposed method is verified in comparison to the conventional voltage measurement method defined in the IEC 61400-21 standard.
Control of hybrid fuel cell/energy storage distributed generation system against voltage sag
Energy Technology Data Exchange (ETDEWEB)
Hajizadeh, Amin; Golkar, Masoud Aliakbar [Electrical Engineering Department, K.N. Toosi University of Technology, Seyedkhandan, Dr. Shariati Ave, P.O. Box 16315-1355, Tehran (Iran)
2010-06-15
Fuel cell (FC) and energy storage (ES) based hybrid distributed power generation systems appear to be very promising for satisfying high energy and high power requirements of power quality problems in distributed generation (DG) systems. In this study, design of control strategy for hybrid fuel cell/energy storage distributed power generation system during voltage sag has been presented. The proposed control strategy allows hybrid distributed generation system works properly when a voltage disturbance occurs in distribution system and hybrid system stays connected to the main grid. Hence, modeling, controller design, and simulation study of a hybrid distributed generation system are investigated. The physical model of the fuel cell stack, energy storage and the models of power conditioning units are described. Then the control design methodology for each component of the hybrid system is proposed. Simulation results are given to show the overall system performance including active power control and voltage sag ride-through capability of the hybrid distributed generation system. (author)
Variable speed wind turbine generator system with current controlled voltage source inverter
International Nuclear Information System (INIS)
Muyeen, S.M.; Al-Durra, Ahmed; Tamura, J.
2011-01-01
highlights: → Current controlled voltage source inverter scheme for wind power application. → Low voltage ride through of wind farm. → Variable speed wind turbine driven permanent magnet synchronous generator-operation and control. -- Abstract: The present popular trend of wind power generation is to use variable speed wind turbine (VSWT) driving a doubly fed induction generator (DFIG), wound field synchronous generator (WFSG) or permanent magnet synchronous generator (PMSG). Among them, stability analyses of DFIG type of VSWT have already been reported in many literatures. However, transient stability and low voltage ride through (LVRT) characteristics analyses for synchronous generator type of VSWT is not sufficient enough. This paper focuses on detailed LVRT characteristic analysis of variable speed wind turbine driving a PMSG (VSWT-PMSG) with current controlled voltage source inverter (CC-VSI). Modeling and suitable control strategies for overall system are developed to augment the low voltage ride through capability of variable speed wind generator, considering recent wind farm grid code. Both symmetrical and unsymmetrical faults are analyzed as network disturbances in this paper. The permanent fault due to unsuccessful reclosing of circuit breakers is taken into consideration, which is a salient feature of this study. Moreover, the dynamic characteristic is analyzed using real wind speed data measured in Hokkaido Island, Japan. The proposed control scheme is simulated by using the standard power system simulation package PSCAD/EMTDC and results are verified by comparing that of voltage controlled voltage source inverter scheme available in power system literature.
Variable speed wind turbine generator system with current controlled voltage source inverter
Energy Technology Data Exchange (ETDEWEB)
Muyeen, S.M., E-mail: muyeen0809@yahoo.co [Dept. of Electrical Engineering, Petroleum Institute, P.O. Box 2533, Abu Dhabi (United Arab Emirates); Al-Durra, Ahmed [Dept. of Electrical Engineering, The Petroleum Institute, P.O. Box 2533, Abu Dhabi (United Arab Emirates); Tamura, J. [Dept. of EEE, Kitami Institute of Technology, 165 Koen-cho, Kitami 090-8507 (Japan)
2011-07-15
highlights: {yields} Current controlled voltage source inverter scheme for wind power application. {yields} Low voltage ride through of wind farm. {yields} Variable speed wind turbine driven permanent magnet synchronous generator-operation and control. -- Abstract: The present popular trend of wind power generation is to use variable speed wind turbine (VSWT) driving a doubly fed induction generator (DFIG), wound field synchronous generator (WFSG) or permanent magnet synchronous generator (PMSG). Among them, stability analyses of DFIG type of VSWT have already been reported in many literatures. However, transient stability and low voltage ride through (LVRT) characteristics analyses for synchronous generator type of VSWT is not sufficient enough. This paper focuses on detailed LVRT characteristic analysis of variable speed wind turbine driving a PMSG (VSWT-PMSG) with current controlled voltage source inverter (CC-VSI). Modeling and suitable control strategies for overall system are developed to augment the low voltage ride through capability of variable speed wind generator, considering recent wind farm grid code. Both symmetrical and unsymmetrical faults are analyzed as network disturbances in this paper. The permanent fault due to unsuccessful reclosing of circuit breakers is taken into consideration, which is a salient feature of this study. Moreover, the dynamic characteristic is analyzed using real wind speed data measured in Hokkaido Island, Japan. The proposed control scheme is simulated by using the standard power system simulation package PSCAD/EMTDC and results are verified by comparing that of voltage controlled voltage source inverter scheme available in power system literature.
A voltage regulator system with dynamic bandwidth boosting for passive UHF RFID transponders
International Nuclear Information System (INIS)
Shen Jinpeng; Wang Xin'an; Liu Shan; Li Shoucheng; Ruan Zhengkun
2013-01-01
This paper presents a voltage regulator system for passive UHF RFID transponders, which contains a rectifier, a limiter, and a regulator. The rectifier achieves power by rectifying the incoming RF energy. Due to the huge variation of the rectified voltage, a limiter at the rectifier output is used to clamp the rectified voltage. In this paper, the design of a limiter circuit is discussed in detail, which can provide a stable limiting voltage with low sensitivity to temperature variation and process dispersion. The key aspect of the voltage regulator system is the dynamic bandwidth boosting in the regulator. By sensing the excess current that is bypassed in the limiter during periods of excess energy, the bias current as well as the bandwidth of the regulator are increased, the output supply voltage can recover quickly from line transients during the periods of no RF energy to a full blast of RF energy. This voltage regulator system is implemented in a 0.18 μm CMOS process. (semiconductor integrated circuits)
A Grid Voltage Measurement Method for Wind Power Systems during Grid Fault Conditions
Yoo, Cheol-Hee; Chung, Il-Yop; Yoo, Hyun-Jae; Hong, Sung-Soo
2014-01-01
Grid codes in many countries require low-voltage ride-through (LVRT) capability to maintain power system stability and reliability during grid fault conditions. To meet the LVRT requirement, wind power systems must stay connected to the grid and also supply reactive currents to the grid to support the recovery from fault voltages. This paper presents a new fault detection method and inverter control scheme to improve the LVRT capability for full-scale permanent magnet synchronous generator (P...
POWER STABILITY MONITORING BASED ON VOLTAGE INSTABILITY PREDICTION APPROACH THROUGH WIDE AREA SYSTEM
H. H. Goh; Q. S. Chua; S. W. Lee; B. C. Kok; K. C. Goh; K. T.K. Teo
2014-01-01
Nowadays, power systems are being forced to operate closer to its security limit due to current economic growth and the difficulties to upgrade the existing grid infrastructure. With the sudden increment of power demand, voltage instability problem has become a main concern to the power system operator because voltage instability has led or crucially contributed to some major blackouts throughout the world. Hence, methods for early warning and early prevention are required to prevent the powe...
DEFF Research Database (Denmark)
Zecchino, Antonio; Marinelli, Mattia; Træholt, Chresten
2017-01-01
The increasing success of electric vehicles is bringing new technical challenges to power system operators. This work intends to provide guidelines for distribution system operators in terms of reactive power requirements when evaluating and authorizing electric vehicles supply equipment with fast...... the amount of reactive power that an individual electric vehicle is expected to provide when connected to a low voltage feeder, in order to benefit of the desired voltage rise effect in comparison to the case of unitary power factor....
DEFF Research Database (Denmark)
Choi, Uimin; Blaabjerg, Frede; Lee, Kyo-Beum
2014-01-01
To improve the efficiency of the photovoltaic (PV) system, the centralized topology using three-level inverters are widely used. In this system, PV modules are separately connected to the split DC-links. This causes a decrease of maximum power point tracking (MPPT) efficiency under the partial...... shading condition. This paper proposes an independent control of two DC-link voltages for separate MPPT of each PV module in three-level inverters. The proposed method is simply implemented by adding or subtracting the time-offset to the three-phase turn-on times and modifying the reference voltages...
Xiao, Ning-Cong; Li, Yan-Feng; Wang, Zhonglai; Peng, Weiwen; Huang, Hong-Zhong
2013-01-01
In this paper the combinations of maximum entropy method and Bayesian inference for reliability assessment of deteriorating system is proposed. Due to various uncertainties, less data and incomplete information, system parameters usually cannot be determined precisely. These uncertainty parameters can be modeled by fuzzy sets theory and the Bayesian inference which have been proved to be useful for deteriorating systems under small sample sizes. The maximum entropy approach can be used to cal...
Nakachi, Yoshiki; Ueda, Fukashi; Kajikawa, Takuya; Amau, Tooru; Kameyama, Hirokazu; Ito, Hisanori
This paper verifies the mechanism of occurring over voltage phenomena in the distributed power system on energizing the transformer. This over-voltage, which is observed at the actual distributed power system, with heavy inrush current is found to occur at about 0.1-0.2sec after the energizing and continue for a duration of more than 0.1[sec]. There is a concern that this over-voltage may operate the protection relay and deteriorate the insulation of apparatus. It is basically caused by the resonance between the shunt capacitors and saturated/unsaturated magnetizing inductance of transformer, system inductance. By using analytical formulation of a simple equivalent circuit, its mechanism has been verified through simulations carried out by using EMTP. Moreover, the sympathetic interaction between transformers is prolonged the duration of the over-voltage by the field test data is discussed in this paper.
High voltage pulse system for the streamer chamber supply of the GIBS spectrometer
International Nuclear Information System (INIS)
Aksinenko, V.D.; Glagoleva, N.S.; Dement'ev, E.A.; Kaminskij, N.I.; Matyushin, A.T.; Matyushin, V.T.; Rozhnyatovskaya, S.A.; Ryakhovskij, V.N.; Nurgozhin, N.N.; Khusainov, E.K.
1987-01-01
Results of development and testing of high voltage pulse system HVPS for the streamer chamber supply of the GIBS spectrometer are presented. HVPS consists of the following basic blocks: nanosecond pulse high voltage generator, high voltage charging supply, trigger generator, chamber parameter control devices, gas-oil vacuuming supply systems, auxiliary and fire-prevention devices. The system blocks are described. Experimental results of HVPC testing are presented. HVPC provides a reliable (10 5 operations) of streamer chamber supply with high voltage pulse parameters: amplitude - 500 kV, amplitude instability (0.5-1.5)%, pulse duration - 12 ns, delay time - 500 ns, delay instability (2.5-5)%, mean frequency of output a signals - 0.1 Hz
HF-voltage testing of accelerating system functional model
International Nuclear Information System (INIS)
Gladkov, A.V.; Stepanov, V.B.
1989-01-01
Owing to ambiguity in interpreting the notion of the electron strength of the operating HF device in an acceleator a technique of measurements and result processing, based on statistical analysis of the data is suggested. Experimental testing on electric strength of structures with HF focusing was carried out using a bench in the form of a cylindrical vacuum container inside which a double H-resonator with HF quadrupole electrodes without surface modulation was installed. The dependences obtained permit to evaluate the bahaviour of the HF device from the viewpoint of electric strength and radiation hazard for the whole range of possible values of voltage on the basis of data on the frequency of breakdowns and radiation situation only in one experimental point. 12 refs.; 8 figs
International Nuclear Information System (INIS)
Zhang Jian; Huang Yiyun; Liu Baohua; Guo Wenjun; Shen Xiaoling; Wei Wei
2011-01-01
A high voltage power supply system has been developed for the diagnostic neutral beam on the HT-7 experimental Tokamak, and the over-voltage phenomenon of storage capacitor was founded in the experiment. In order to analyse and resolve this problem, the structure and principle of high voltage power supply is described and the primary high voltage charging power supply system is introduced in detail. The phenomenon of over-voltage on the capacitors is also studied with circuit model, and the conclusion is obtained that the leakage inductance is the mA in reason which causes the over-voltage on the capacitors. (authors)
DEFF Research Database (Denmark)
Liu, Wenzhao; Tarasiuk, Tomasz; Gorniak, Mariusz
2018-01-01
were proposed and carried out in a real ship under sea-going conditions to address this problem. The ship experimental results were presented and discussed considering non-linear bow thruster load and high power ballast pump loads under unbalanced and harmonic voltage conditions. In addition......, the analysis of voltage transient dips during ballast pump starting up is presented. Further, the voltage/current distortions of working generator, bow thruster and pump loads are analyzed. The paper provides a valuable analysis for coping with PQ issues in the real ship power system....
Lizcano, Maricela
2017-01-01
High voltage hybrid electric propulsion systems are now pushing new technology development efforts for air transportation. A key challenge in hybrid electric aircraft is safe high voltage distribution and transmission of megawatts of power (>20 MW). For the past two years, a multidisciplinary materials research team at NASA Glenn Research Center has investigated the feasibility of distributing high voltage power on future hybrid electric aircraft. This presentation describes the team's approach to addressing this challenge, significant technical findings, and next steps in GRC's materials research effort for MW power distribution on aircraft.
Insulation co-ordination in high-voltage electric power systems
Diesendorf, W
2015-01-01
Insulation Co-ordination in High-Voltage Electric Power Systems deals with the methods of insulation needed in different circumstances. The book covers topics such as overvoltages and lightning surges; disruptive discharge and withstand voltages; self-restoring and non-self-restoring insulation; lightning overvoltages on transmission lines; and the attenuation and distortion of lightning surges. Also covered in the book are topics such as the switching surge designs of transmission lines, as well as the insulation coordination of high-voltage stations. The text is recommended for electrical en
A Low-Voltage Ride-Through Control Strategy for Three-Phase Grid-Connected PV Systems
DEFF Research Database (Denmark)
Afshari, Ehsan; Farhangi, Babak; Yang, Yongheng
2017-01-01
similar variations in the dc-link voltage of conventional two-stage PV inverters. In such systems with an electrolytic capacitor in the dc-link, the oscillations of the dc-link voltage with DGF can deteriorate the capacitor lifetime, and thus the entire system. The proposed Low-Voltage Ride-Through (LVRT...
30 CFR 77.803 - Fail safe ground check circuits on high-voltage resistance grounded systems.
2010-07-01
... circuits on high-voltage resistance grounded systems. On and after September 30, 1971, all high-voltage... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Fail safe ground check circuits on high-voltage resistance grounded systems. 77.803 Section 77.803 Mineral Resources MINE SAFETY AND HEALTH ADMINISTRATION...
An Estimation Method of System Voltage Sag Profile using Recorded Sag Data
Tanaka, Kazuyuki; Sakashita, Tadashi
The influence of voltage sag to electric equipment has become big issues because of wider utilization of voltage sensitive devices. In order to reduce the influence of voltage sag appearing at each customer side, it is necessary to recognize the level of receiving voltage drop due to lightning faults for transmission line. However it is hard to measure directly those sag level at every load node. In this report, a new method of efficiently estimating system voltage sag profile is proposed based on symmetrical coordinate. In the proposed method, limited recorded sag data is used as the estimation condition which is recorded at each substation in power systems. From the point of view that the number of the recorded node is generally far less than those of the transmission route, a fast solution method is developed to calculate only recorder faulted voltage by applying reciprocity theorem for Y matrix. Furthermore, effective screening process is incorporated, in which the limited candidate of faulted transmission line can be chosen. Demonstrative results are presented using the IEEJ East10 standard system and actual 1700 bus system. The results show that estimation accuracy is sufficiently acceptable under less computation labor.
Voltage Unbalance Compensation with Smart Three-phase Loads
DEFF Research Database (Denmark)
Douglass, Philip; Trintis, Ionut; Munk-Nielsen, Stig
2016-01-01
unbalance originating in the power supply network. Two variants of the algorithm are tested: first, using phase-neutral voltage as input, second, using phase-phase voltage. The control algorithm is described, and evaluated in simulations and laboratory tests. Two metrics for quantifying voltage unbalance...... are evaluated: one metric based on the maximum deviation of RMS phaseneutral voltage from the average voltage and one metric based on negative sequence voltage. The tests show that controller that uses phase-neutral voltage as input can in most cases eliminate the deviations of phase voltage from the average...... is caused by asymmetrical loads. These results suggest that the optimal algorithm to reduce system unbalance depends on which system parameter is most important: phase-neutral voltage unbalance, phase-phase voltage unbalance, or current unbalance....
A novel maximum power point tracking method for PV systems using fuzzy cognitive networks (FCN)
Energy Technology Data Exchange (ETDEWEB)
Karlis, A.D. [Electrical Machines Laboratory, Department of Electrical & amp; Computer Engineering, Democritus University of Thrace, V. Sofias 12, 67100 Xanthi (Greece); Kottas, T.L.; Boutalis, Y.S. [Automatic Control Systems Laboratory, Department of Electrical & amp; Computer Engineering, Democritus University of Thrace, V. Sofias 12, 67100 Xanthi (Greece)
2007-03-15
Maximum power point trackers (MPPTs) play an important role in photovoltaic (PV) power systems because they maximize the power output from a PV system for a given set of conditions, and therefore maximize the array efficiency. This paper presents a novel MPPT method based on fuzzy cognitive networks (FCN). The new method gives a good maximum power operation of any PV array under different conditions such as changing insolation and temperature. The numerical results show the effectiveness of the proposed algorithm. (author)
Automatic Voltage Control System with Market Price Employing Large Wind Farms
DEFF Research Database (Denmark)
Qin, Nan; Bak, Claus Leth; Abildgaard, Hans
2018-01-01
of the voltage control service provided by the power plant owners. The benefit of employing the large offshore wind farms in this AVC system is investigated. The simulation based on the measurement data from the Danish electricity control center demonstrates the superiority of the proposed approach in terms...... of the cost minimization. The gained profit by employing the wind farms can be an argument to purchase the voltage control service provided by these wind farms....
Directory of Open Access Journals (Sweden)
Guido Ala
2018-03-01
Full Text Available This paper presents the results of a first investigation on the effects of lightning stroke on medium voltage installations’ grounding systems, interconnected with the metal shields of the Medium Voltage (MV distribution grid cables or with bare buried copper ropes. The study enables us to evaluate the distribution of the lightning current among interconnected ground electrodes in order to estimate if the interconnection, usually created to reduce ground potential rise during a single-line-to-ground fault, can give place to dangerous situations far from the installation hit by the lightning stroke. Four different case studies of direct lightning stroke are presented and discussed: (1 two secondary substations interconnected by the cables’ shields; (2 two secondary substations interconnected by a bare buried conductor; (3 a high voltage/medium voltage station connected with a secondary substation by the medium voltage cables’ shields; (4 a high voltage/medium voltage station connected with a secondary substation by a bare buried conductor. The results of the simulations show that a higher peak-lowering action on the lighting-stroke current occurs due to the use of bare conductors as interconnection elements in comparison to the cables’ shields.
Influence of Wind Plant Ancillary Voltage Control on System Small Signal Stability
DEFF Research Database (Denmark)
Su, Chi; Chen, Zhe
2012-01-01
As a common tendency, large-scale wind farms are increasingly connected to the transmission system of modern power grids. This introduces some new challenges to the connected power systems, and the transmission system operators (TSOs) have to put some new requirements as part of the grid codes...... on the integration of wind farms. One common requirement to wind farms is the function of system voltage control which can be implemented in the grid-side convertor controller of a variable speed wind turbine. This ancillary voltage control provided by wind farms could have some influence on the system small signal...... stability. This paper implements an ancillary voltage control strategy on a direct-drive-full-convertor-based wind farm and studies its influence on the damping ratio values of the dominant oscillation mode within the connected power system. All the calculations and simulations are conducted in DIg...
DEFF Research Database (Denmark)
Sun, Xiaofeng; Zeng, Jian; Chen, Zhe
2013-01-01
, and analyze the harmonic voltage propagation caused by the background harmonic voltage in power systems. Then, a new strategy is proposed for the site selection of resistive active power filter to damp the background harmonic voltage in power systems. Experiments have been performed to verify the theoretical......Series resonance between capacitance and line inductance may magnify background harmonic voltage and worsen the harmonic voltage distortion in power systems. To solve this problem, in this paper, the transmission line theory is used to set up the distributed parameter model of power system feeders...
Directory of Open Access Journals (Sweden)
Muhamad Zalani Daud
2014-01-01
Full Text Available This paper presents an evaluation of an optimal DC bus voltage regulation strategy for grid-connected photovoltaic (PV system with battery energy storage (BES. The BES is connected to the PV system DC bus using a DC/DC buck-boost converter. The converter facilitates the BES power charge/discharge to compensate for the DC bus voltage deviation during severe disturbance conditions. In this way, the regulation of DC bus voltage of the PV/BES system can be enhanced as compared to the conventional regulation that is solely based on the voltage-sourced converter (VSC. For the grid side VSC (G-VSC, two control methods, namely, the voltage-mode and current-mode controls, are applied. For control parameter optimization, the simplex optimization technique is applied for the G-VSC voltage- and current-mode controls, including the BES DC/DC buck-boost converter controllers. A new set of optimized parameters are obtained for each of the power converters for comparison purposes. The PSCAD/EMTDC-based simulation case studies are presented to evaluate the performance of the proposed optimized control scheme in comparison to the conventional methods.
Daud, Muhamad Zalani; Mohamed, Azah; Hannan, M A
2014-01-01
This paper presents an evaluation of an optimal DC bus voltage regulation strategy for grid-connected photovoltaic (PV) system with battery energy storage (BES). The BES is connected to the PV system DC bus using a DC/DC buck-boost converter. The converter facilitates the BES power charge/discharge to compensate for the DC bus voltage deviation during severe disturbance conditions. In this way, the regulation of DC bus voltage of the PV/BES system can be enhanced as compared to the conventional regulation that is solely based on the voltage-sourced converter (VSC). For the grid side VSC (G-VSC), two control methods, namely, the voltage-mode and current-mode controls, are applied. For control parameter optimization, the simplex optimization technique is applied for the G-VSC voltage- and current-mode controls, including the BES DC/DC buck-boost converter controllers. A new set of optimized parameters are obtained for each of the power converters for comparison purposes. The PSCAD/EMTDC-based simulation case studies are presented to evaluate the performance of the proposed optimized control scheme in comparison to the conventional methods.
Simulation model of ANN based maximum power point tracking controller for solar PV system
Energy Technology Data Exchange (ETDEWEB)
Rai, Anil K.; Singh, Bhupal [Department of Electrical and Electronics Engineering, Ajay Kumar Garg Engineering College, Ghaziabad 201009 (India); Kaushika, N.D.; Agarwal, Niti [School of Research and Development, Bharati Vidyapeeth College of Engineering, A-4 Paschim Vihar, New Delhi 110063 (India)
2011-02-15
In this paper the simulation model of an artificial neural network (ANN) based maximum power point tracking controller has been developed. The controller consists of an ANN tracker and the optimal control unit. The ANN tracker estimates the voltages and currents corresponding to a maximum power delivered by solar PV (photovoltaic) array for variable cell temperature and solar radiation. The cell temperature is considered as a function of ambient air temperature, wind speed and solar radiation. The tracker is trained employing a set of 124 patterns using the back propagation algorithm. The mean square error of tracker output and target values is set to be of the order of 10{sup -5} and the successful convergent of learning process takes 1281 epochs. The accuracy of the ANN tracker has been validated by employing different test data sets. The control unit uses the estimates of the ANN tracker to adjust the duty cycle of the chopper to optimum value needed for maximum power transfer to the specified load. (author)
High voltage power supply systems for electron beam and plasma technologies. Its new element base
International Nuclear Information System (INIS)
Dermengi, P.G.; Kureghan, A.S.; Pokrovsky, S.V.; Tchvanov, V.A.
1994-01-01
Transforming technique and high voltage technique supplementing each other more and more unite in indivisible constructions of modern apparatuses and systems and applicated in modern technologies providing its high efficiency. Specially worked out, ecologically clean, inertial, inflammable perfluororganic liquid is used in elements and electronic apparatuses simultaneously as insulating and cooling media. This liquid is highly fluid, fills tiny cavities in construction elements and in the places of high concentration of losses, where maximum local overheating of active parts or apparatus constructions takes place, it transforms to boiling state with highly intensive taking off of heat energy from cooled surface point. For instance, being cooled by mentioned perfluororganic liquid, copper wire can conduct current to 50 A/mm 2 density, but in ordinary conditions of transformers, reactors and busses, current density can reach only few Amperes. Possibility of considerable increasing of current density, that is reached by means of intensive cooling, provided by worked out liquid, and taking into account its incredibly high insulating features (liquid has electric strength to 50 KV/mm) allows to provide optimum heat regime of active parts of transformers. reactors, condenser, semiconductor devices, resistors, construction elements and electrotechnical apparatus in general. Particularly high effect of decreasing of weight and dimensions characteristics of elements and electrotechnical apparatus in general can be reached under working out of special constructions of each element and apparatus details, adapted to use of mentioned liquid as insulating and cooling media
The High-Voltage System of Calet Apparatus
Directory of Open Access Journals (Sweden)
Petroni Francesco
2017-01-01
This paper presents the experience gained in the implementation of the CALET HV system: the system design requirements and the technical solutions adopted, the two system sections block schemes and the main characteristics of the DC/DC converters that guarantee the CALET HV system technical performance.
DEFF Research Database (Denmark)
Qin, Nan; Bak, Claus Leth; Abildgaard, Hans
2017-01-01
This paper proposes an automatic voltage control (AVC) system for power systems with limited continuous voltage control capability. The objective is to minimize the operational cost over a period, which consists of the power loss in the grid, the shunt switching cost, the transformer tap change...... electricity control center, where study cases based on the western Danish power system demonstrate the superiority of the proposed AVC system in term of the cost minimization. Monte Carlo simulations are carried out to verify the proposed method on the robustness improvements....
The control system based on PXI technology for high voltage power supply
International Nuclear Information System (INIS)
Chen Dehong; Zhang Ming; Ma Shaoxiang; Xia Linglong; Zeng Zhen; Zhang Xueliang; Wang Chuliang; Yu Kexun
2014-01-01
A 100 kV/60 A high voltage power supply (HVPS) is being developed to carry some auxiliary heating research on J-TEXT and supply the auxiliary heating system. The power supply which consists of 144 switch modules is based on PSM technology. For the requirement of isolation, control and protection, a control system based on the PCI extensions for instrumentation (PXI) which meets up with the CODAC standards is designed with developed PSM technology for the high voltage power supply. The compact structure of hardware in the control system is presented too. And the control strategy which is based on shift phase pulse width modulation is discussed Some tests are performed on the control system to validate the control strategy, the experimental results show that the system has a good control performance and fast response, which meets the control requirement of 100 kV/60 A high voltage power supply. (authors)
49 CFR 192.621 - Maximum allowable operating pressure: High-pressure distribution systems.
2010-10-01
... STANDARDS Operations § 192.621 Maximum allowable operating pressure: High-pressure distribution systems. (a) No person may operate a segment of a high pressure distribution system at a pressure that exceeds the... segment of a distribution system otherwise designed to operate at over 60 p.s.i. (414 kPa) gage, unless...
2010-10-01
... distribution systems. (a) No person may operate a low-pressure distribution system at a pressure high enough to...) No person may operate a low pressure distribution system at a pressure lower than the minimum... 49 Transportation 3 2010-10-01 2010-10-01 false Maximum and minimum allowable operating pressure...
DEFF Research Database (Denmark)
Bjørk, Rasmus; Nielsen, Kaspar Kirstein
2017-01-01
The maximum efficiency for photovoltaic (PV) and thermoelectric generator (TEG) systems without concentration is investigated. Both a combined system where the TEG is mounted directly on the back of the PV and a tandem system where the incoming sunlight is split, and the short wavelength radiation...
Monitoring operating temperature and supply voltage in achieving high system dependability
Khan, M.A.; Kerkhoff, Hans G.
2013-01-01
System dependability being a set of number of attributes, of which the important reliability, heavily depends on operating temperature and supply voltage. Any change beyond the designed specifications may change the system performance and could result in system reliability and hence dependability
Study of the tomographic image quality provided by a conical beam system kilo voltage
International Nuclear Information System (INIS)
Garayoa Roca, J.; Castro Tejero, P.
2011-01-01
Imaging systems play an increasingly important role in radiotherapy, and to ensure the quality of the process, you must know the characteristics and limitations of available imaging systems. In this study we sought to evaluate the image quality of an IGRT system based on a kilo voltage cone beam.
Quamruzzaman, M.; Mohammad, Nur; Matin, M. A.; Alam, M. R.
2016-10-01
Solar photovoltaics (PVs) have nonlinear voltage-current characteristics, with a distinct maximum power point (MPP) depending on factors such as solar irradiance and operating temperature. To extract maximum power from the PV array at any environmental condition, DC-DC converters are usually used as MPP trackers. This paper presents the performance analysis of a coupled inductor single-ended primary inductance converter for maximum power point tracking (MPPT) in a PV system. A detailed model of the system has been designed and developed in MATLAB/Simulink. The performance evaluation has been conducted on the basis of stability, current ripple reduction and efficiency at different operating conditions. Simulation results show considerable ripple reduction in the input and output currents of the converter. Both the MPPT and converter efficiencies are significantly improved. The obtained simulation results validate the effectiveness and suitability of the converter model in MPPT and show reasonable agreement with the theoretical analysis.
A New Study of Maximum Power Point Tracker Techniques and Comparison for PV Systems
Directory of Open Access Journals (Sweden)
Ahmed M. Atallah
2016-07-01
Full Text Available The maximum power point tracker techniques vary in many aspects as simplicity, digital or analogical implementation, sensor required, convergence speed, range of effectiveness, implementation hardware,popularity, cost and in other aspects. This paper presents in details comparative study between two most popular algorithm technique which is incremental conductance algorithm and perturb and observe algorithm. Two different converters buck and cuk converter use for comparative in this study. Few comparisons such as efficiency, voltage, current and power output for each different combination have been recorded. Multi changes in irradiance, temperature by keeping voltage and current as main sensed parameter been done in the simulation. Matlab simulink tools have been used for performance evaluation on energy point. Simulation will consider different solar irradiance and temperature variations.
Maximum power point tracking for photovoltaic solar pump based on ANFIS tuning system
Directory of Open Access Journals (Sweden)
S. Shabaan
2018-05-01
Full Text Available Solar photovoltaic (PV systems are a clean and naturally replenished energy source. PV panels have a unique point which represents the maximum available power and this point depend on the environmental conditions such as temperature and irradiance. A maximum power point tracking (MPPT is therefore necessary for maximum efficiency. In this paper, a study of MPPT for PV water pumping system based on adaptive neuro-fuzzy inference system (ANFIS is discussed. A comparison between the performance of the system with and without MPPT is carried out under varying irradiation and temperature conditions. ANFIS based controller shows fast response with high efficiency at all irradiance and temperature levels making it a powerful technique for non-linear systems as PV modules. Keywords: MPPT, ANFIS, Boost converter, PMDC pump
A maximum principle for time dependent transport in systems with voids
International Nuclear Information System (INIS)
Schofield, S.L.; Ackroyd, R.T.
1996-01-01
A maximum principle is developed for the first-order time dependent Boltzmann equation. The maximum principle is a generalization of Schofield's κ(θ) principle for the first-order steady state Boltzmann equation, and provides a treatment of time dependent transport in systems with void regions. The formulation comprises a direct least-squares minimization allied with a suitable choice of bilinear functional, and gives rise to a maximum principle whose functional is free of terms that have previously led to difficulties in treating void regions. (Author)
Voltage control on TEG-inverter system with pulse width modulation
International Nuclear Information System (INIS)
Kimura, N.; Kinoshita, H.; Matsuura, K.
1984-01-01
An ocean thermoelectric generating system can be expected to supply cheap electric power in future. And it can be used as base power supply or isolated power source in developing areas. The authors propose to apply forced-commutation inverter to thermoelectric energy conversion system and construct an electric power station which can be operated without any other synchronous generator (S-G) and can control ac system as stable as S-G. This paper shows that inverters can control voltage constant, though within a range of 10% load change, by using pulse width modulation (PWM). It also describes the design of the voltage control system covering from 50% to 100% load with combination of PWM and output voltage tap changing of TEG
Energy Technology Data Exchange (ETDEWEB)
Cardozo Sanchez, Freddy [Mirant Americas (United States); Fernandez Krekeler, Ubaldo [Administracion Nacional de Electricidad (ANDE), Asuncion (Paraguay)
2001-07-01
This document presents analyses of permanent status of the ANDE transmission system, seeking to evaluate the voltage stability and impact that would have possible reinforcements in 500 kV. The transmission under this new voltage level, besides to be a reinforcement to the system for satisfying the national demand, will permit the increase of energy exportation to Brazil, depending on the adopted reinforcement. The system current status and its evolution according to the planning of short and medium period are analysed. In the voltage stability evolution, static analysis techniques to draw the Q-V and P-V curves were used, as well as for determination of the system self-values and stability margins.
Verification of a Novel Method of Detecting Faults in Medium-Voltage Systems with Covered Conductors
Directory of Open Access Journals (Sweden)
Mišák Stanislav
2017-06-01
Full Text Available This paper describes the use of new methods of detecting faults in medium-voltage overhead lines built of covered conductors. The methods mainly address such faults as falling of a conductor, contacting a conductor with a tree branch, or falling a tree branch across three phases of a medium-voltage conductor. These faults cannot be detected by current digital relay protection systems. Therefore, a new system that can detect the above mentioned faults was developed. After having tested its operation, the system has already been implemented to protect mediumvoltage overhead lines built of covered conductors.
Energy Technology Data Exchange (ETDEWEB)
Sainz, Luis; Pedra, Joaquin [Department of Electrical Engineering, ETSEIB-UPC, Av. Diagonal 647, 08028 Barcelona (Spain); Caro, Manuel [IDOM Ingenieria y Arquitectura, C. Barcas 2, 46002 Valencia (Spain)
2009-01-15
In traction systems, it is usual to connect reactances in delta configuration with single-phase loads to reduce voltage unbalances and avoid electric system operation problems. This set is known as Steinmetz circuit. Parallel and series resonances can occur due to the capacitive reactance of the Steinmetz circuit and affect power quality. In this paper, the series resonance ''observed'' from the supply system is numerically located. The study of this resonance is important to avoid problems due to background voltage distortion. Experimental measurements are also presented to validate the obtained numerical results. (author)
A new reconfiguration scheme for voltage stability enhancement of radial distribution systems
International Nuclear Information System (INIS)
Arun, M.; Aravindhababu, P.
2009-01-01
Network reconfiguration is an operation problem, which entails altering the topological structure of the distribution feeders by rearranging the status of switches in order to obtain an optimal configuration in order to minimise the system losses. This paper presents a new reconfiguration algorithm that enhances voltage stability and improves the voltage profile besides minimising losses without incurring any additional cost for installation of capacitors, tap changing transformers and related switching equipment in the distribution system. Test results on a 69 node distribution system reveal the superiority of this algorithm.
Wong, Jianhui; Lim, Yun Seng; Morris, Stella; Morris, Ezra; Chua, Kein Huat
2017-04-01
The amount of small-scaled renewable energy sources is anticipated to increase on the low-voltage distribution networks for the improvement of energy efficiency and reduction of greenhouse gas emission. The growth of the PV systems on the low-voltage distribution networks can create voltage unbalance, voltage rise, and reverse-power flow. Usually these issues happen with little fluctuation. However, it tends to fluctuate severely as Malaysia is a region with low clear sky index. A large amount of clouds often passes over the country, hence making the solar irradiance to be highly scattered. Therefore, the PV power output fluctuates substantially. These issues can lead to the malfunction of the electronic based equipment, reduction in the network efficiency and improper operation of the power protection system. At the current practice, the amount of PV system installed on the distribution network is constraint by the utility company. As a result, this can limit the reduction of carbon footprint. Therefore, energy storage system is proposed as a solution for these power quality issues. To ensure an effective operation of the distribution network with PV system, a fuzzy control system is developed and implemented to govern the operation of an energy storage system. The fuzzy driven energy storage system is able to mitigate the fluctuating voltage rise and voltage unbalance on the electrical grid by actively manipulates the flow of real power between the grid and the batteries. To verify the effectiveness of the proposed fuzzy driven energy storage system, an experimental network integrated with 7.2kWp PV system was setup. Several case studies are performed to evaluate the response of the proposed solution to mitigate voltage rises, voltage unbalance and reduce the amount of reverse power flow under highly intermittent PV power output.
Evaluation of maximum power point tracking in hydrokinetic energy conversion systems
Directory of Open Access Journals (Sweden)
Jahangir Khan
2015-11-01
Full Text Available Maximum power point tracking is a mature control issue for wind, solar and other systems. On the other hand, being a relatively new technology, detailed discussion on power tracking of hydrokinetic energy conversion systems are generally not available. Prior to developing sophisticated control schemes for use in hydrokinetic systems, existing know-how in wind or solar technologies can be explored. In this study, a comparative evaluation of three generic classes of maximum power point scheme is carried out. These schemes are (a tip speed ratio control, (b power signal feedback control, and (c hill climbing search control. In addition, a novel concept for maximum power point tracking: namely, extremum seeking control is introduced. Detailed and validated system models are used in a simulation environment. Potential advantages and drawbacks of each of these schemes are summarised.
Directory of Open Access Journals (Sweden)
Ning-Cong Xiao
2013-12-01
Full Text Available In this paper the combinations of maximum entropy method and Bayesian inference for reliability assessment of deteriorating system is proposed. Due to various uncertainties, less data and incomplete information, system parameters usually cannot be determined precisely. These uncertainty parameters can be modeled by fuzzy sets theory and the Bayesian inference which have been proved to be useful for deteriorating systems under small sample sizes. The maximum entropy approach can be used to calculate the maximum entropy density function of uncertainty parameters more accurately for it does not need any additional information and assumptions. Finally, two optimization models are presented which can be used to determine the lower and upper bounds of systems probability of failure under vague environment conditions. Two numerical examples are investigated to demonstrate the proposed method.
Low-voltage grid-connection of photovoltaic power systems
Energy Technology Data Exchange (ETDEWEB)
Collinson, A.; Thornycroft, J.
1999-07-01
This report summarises the results of a project aimed at developing technical guidelines concerning grid connected photovoltaic (PV) inverter generators which are to be published in draft form as the {sup U}K Technical Guidelines for Inverter Connected Single Phase Photovoltaic (PV) Generators up to 5kVA{sup .} The background to the use of PV in the UK is traced, and the technical criteria for electrical integration of PV systems, and UK guidelines for grid connected PV systems are examined. The findings of the working group of the International Energy Agency (IEA) Implementing Agreement on Photovoltaic Power Systems are also presented in this report. Appendices discuss the UK technical guidelines, the IEA Task V activities,, utility aspects of grid-connected PV systems, and demonstration tests on grid-connected PV systems, and lists Task V reports.
Possibility of persistent voltage observation in a system of asymmetric superconducting rings
International Nuclear Information System (INIS)
Burlakov, A.A.; Gurtovoi, V.L.; Ilin, A.I.; Nikulov, A.V.; Tulin, V.A.
2012-01-01
The possibility of observing persistent voltage in superconducting rings of different arm widths is experimentally investigated. It was previously found that switching of the arms between superconducting and normal states by an AC current induces DC voltage oscillation in the magnetic field with a period corresponding to the flux quantum inside the ring. We used systems with a large number of asymmetric rings connected in series to investigate the possibility of observing this quantum phenomenon near the superconducting transition, where thermal fluctuations lead to switching of ring segments without an external influence and the persistent current is much smaller than in the superconducting state. -- Highlights: ► A possibility to observe the persistent voltage is investigated experimentally. ► The persistent voltage is a DC voltage observed at thermodynamic equilibrium. ► It oscillates in magnetic field like the persistent current in superconducting ring. ► The period of the oscillations corresponds to the flux quantum inside the ring. ► The quantum oscillations of the DC voltage were observed on asymmetric rings.
Directory of Open Access Journals (Sweden)
Yu-En Wu
2016-09-01
Full Text Available In this study, a novel, non-isolated, cascade-type, single-switch, high step-up DC/DC converter was developed for green energy systems. An integrated coupled inductor and voltage lift circuit were applied to simplify the converter structure and satisfy the requirements of high efficiency and high voltage gain ratios. In addition, the proposed structure is controllable with a single switch, which effectively reduces the circuit cost and simplifies the control circuit. With the leakage inductor energy recovery function and active voltage clamp characteristics being present, the circuit yields optimizable conversion efficiency and low component voltage stress. After the operating principles of the proposed structure and characteristics of a steady-state circuit were analyzed, a converter prototype with 450 W, 40 V of input voltage, 400 V of output voltage, and 95% operating efficiency was fabricated. The Renesas MCU RX62T was employed to control the circuits. Experimental results were analyzed to validate the feasibility and effectiveness of the proposed system.
Maximum Principle for General Controlled Systems Driven by Fractional Brownian Motions
International Nuclear Information System (INIS)
Han Yuecai; Hu Yaozhong; Song Jian
2013-01-01
We obtain a maximum principle for stochastic control problem of general controlled stochastic differential systems driven by fractional Brownian motions (of Hurst parameter H>1/2). This maximum principle specifies a system of equations that the optimal control must satisfy (necessary condition for the optimal control). This system of equations consists of a backward stochastic differential equation driven by both fractional Brownian motions and the corresponding underlying standard Brownian motions. In addition to this backward equation, the maximum principle also involves the Malliavin derivatives. Our approach is to use conditioning and Malliavin calculus. To arrive at our maximum principle we need to develop some new results of stochastic analysis of the controlled systems driven by fractional Brownian motions via fractional calculus. Our approach of conditioning and Malliavin calculus is also applied to classical system driven by standard Brownian motions while the controller has only partial information. As a straightforward consequence, the classical maximum principle is also deduced in this more natural and simpler way.
Interconnected High-Voltage Pulsed-Power Converters System Design for H− Ion Sources
Aguglia, D
2014-01-01
This paper presents the design and experimental validations of a system of three new high-voltage (HV) pulsedpower converters for the H− sources. The system requires three pulsed voltages (50, 40, and 25 kV to ground) at 2-Hz repetition rate, for 700 μs of usable flat-top. The solution presents ripplefree output voltages and minimal stored energy to protect the ion source from the consequences of arc events. Experimental results on the final full-scale prototype are presented. In case of short-circuit events, the maximal energy delivered to the source is in the Joule range. HV flat-top stability of 1% is experimentally achieved with a simple Proportional-Integral- Derivative regulation and preliminary tuned H− source (e.g., radio frequency control, gas injection, and so forth). The system is running since more than a year with no power converter failures and damage to the source.
Comparison of the converter systems for a high-voltage variable-frequency AC drive
Directory of Open Access Journals (Sweden)
G.G. Zhemerov
2013-12-01
Full Text Available Matlab-models of two converter systems of an 8 MW AC drive are developed, one based on a self-contained current inverter with cut-off diodes, the other based on a multilevel cascade voltage inverter. By applying virtual simulation, qualitative characteristics of these systems are compared.
The high-voltage monitor system for the calorimeter of the OBELIX experiment
International Nuclear Information System (INIS)
Bertin, A.; Bruschi, M.; Capponi, M.; Cereda, B.; D'Antone, I.; De Castro, S.; Galli, D.; Giacobbe, B.; Marconi, U.; Massa, I.; Piccinini, M.; Poli, M.; Semprini-Cesari, N.; Spighi, R.; Vecchi, S.; Vezzani, A.; Villa, M.; Vitale, A.; Zoccoli, A.
1993-01-01
We describe the monitor system developed to manage the high voltage power supply for the electromagnetic calorimeter of the OBELIX experiment, installed on the LEAR facility at CERN. The hardware and software characteristics of the system are discussed, as well as the performance of the same. (orig.)
Active and reactive power control schemes for distributed generation systems under voltage dips
Wang, F.; Duarte, J.L.; Hendrix, M.A.M.
2009-01-01
During voltage dips continuous power delivery from distributed generation systems to the grid is desirable for the purpose of grid support. In order to facilitate the control of distributed generation systems adapted to the expected change of grid requirements, generalized power control schemes
Service quality in low-voltage systems. General principles. [EDF, France
Energy Technology Data Exchange (ETDEWEB)
Heisch, J. (Electricite de France, 75 - Paris)
1984-01-01
Voltage quality and service continuity are two components of service quality, as limited to the technical aspect of the concept. After reviewing the current situation, the actions undertaken to improve said situation are enumerated, actions essentially directed towards MV systems, taking into account system structures. With service quality still of an industrial character, certain users might be led to install additional equipment.
Wang, F.; Duarte, J.L.; Hendrix, M.A.M.
2011-01-01
Grid-interfacing converter systems with enhanced voltage quality are proposed for microgrid application in this paper. By adapting the conventional series-parallel structure, a group of grid-interfacing system topologies are proposed for the purpose of interfacing local generation/microgrid to the
Voltage and Frequency Control for Future Power Systems: the ELECTRA IRP Proposal
DEFF Research Database (Denmark)
D’hulst, R.; Merino Fernandez, J.; Rikos, E.
2015-01-01
In this paper a high level functional architecture for frequency and voltage control for the future (2030+) power system is presented. The proposal suggests a decomposition of the present organization of power system operation into a ”web of cells”. Each cell in this web is managed by a single...
Concept of voltage monitoring for a nuclear power plant emergency power supply system (PWR 1300 MWe)
International Nuclear Information System (INIS)
Andrade, R.B. de
1988-01-01
Voltage monitoring concept for a Nuclear Power Plant Emergency Power Supply Systems (PWR 1300 MWe) is described based on the phylosophy adopted for Angra 2 and 3 NPP's. Some suggested setpoints are only guidance values and can be modified during plant commissioning for a better performance of the whole protection system. (author) [pt
Neba, Yasuhiko
This paper deals with a maximum power point tracking (MPPT) control of the photovoltaic generation with the single-phase utility interactive inverter. The photovoltaic arrays are connected by employing the PWM current source inverter to the utility. The use of the pulsating dc current and voltage allows the maximum power point to be searched. The inverter can regulate the array voltage and keep the arrays to the maximum power. This paper gives the control method and the experimental results.
International Nuclear Information System (INIS)
Cruz E, P.
2001-01-01
The work developed for the Laguna Verde Nuclear Power Central allows to obtain the voltage plateau, graphic of sensitivity and operation voltage of three types of ionization chambers which are used in their monitoring systems of process radiation. The automated system is based in a personal computer (Pc) for controlling and acquiring data from the different instruments used, its programming was realized with virtual instruments (LabVIEW, National Instruments software). The system also realizes a diagnosis of the ionization chamber and determine whether the parameters obtained are inside of the manufacturer specifications, that is to say, it determines when the ionization chamber must be replaced. (Author)
Comparison of fuzzy logic and neural network in maximum power point tracker for PV systems
Energy Technology Data Exchange (ETDEWEB)
Ben Salah, Chokri; Ouali, Mohamed [Research Unit on Intelligent Control, Optimization, Design and Optimization of Complex Systems (ICOS), Department of Electrical Engineering, National School of Engineers of Sfax, BP. W, 3038, Sfax (Tunisia)
2011-01-15
This paper proposes two methods of maximum power point tracking using a fuzzy logic and a neural network controllers for photovoltaic systems. The two maximum power point tracking controllers receive solar radiation and photovoltaic cell temperature as inputs, and estimated the optimum duty cycle corresponding to maximum power as output. The approach is validated on a 100 Wp PVP (two parallels SM50-H panel) connected to a 24 V dc load. The new method gives a good maximum power operation of any photovoltaic array under different conditions such as changing solar radiation and PV cell temperature. From the simulation and experimental results, the fuzzy logic controller can deliver more power than the neural network controller and can give more power than other different methods in literature. (author)
Overview of Maximum Power Point Tracking Techniques for Photovoltaic Energy Production Systems
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2015-01-01
A substantial growth of the installed photovoltaic systems capacity has occurred around the world during the last decade, thus enhancing the availability of electric energy in an environmentally friendly way. The maximum power point tracking technique enables maximization of the energy production...... of photovoltaic sources during stochastically varying solar irradiation and ambient temperature conditions. Thus, the overall efficiency of the photovoltaic energy production system is increased. Numerous techniques have been presented during the last decade for implementing the maximum power point tracking...... process in a photovoltaic system. This article provides an overview of the operating principles of these techniques, which are suited for either uniform or non-uniform solar irradiation conditions. The operational characteristics and implementation requirements of these maximum power point tracking...
Power supply and stabilization of the supply system on board using decentralized voltage rectifiers
Energy Technology Data Exchange (ETDEWEB)
Grueb, W; Wegerer, K
1987-04-01
The functionally redundant power supply system of the Transrapid 06 II maglev train is described; it comprises four independent, battery-buffered networks and 30 linear generators per train section. Voltage rectifiers adapt the velocity- and load-dependent linear generator voltage to the 440 V d.c. networks and assure dynamic stabilisation as well as buffer battery loading. The result is a high-reliability power supply system on board with optimum utilisation of the power supplied by the linear generators while the train is running.
Fasanella, Giuseppe
2017-01-01
The CMS Electromagnetic Calorimeter utilizes scintillating lead tungstate crystals, with avalanche photodiodes (APD) as photo-detectors in the barrel part. 1224 HV channels bias groups of 50 APD pairs, each at a voltage of about 380 V. The APD gain dependence on the voltage is 3pct/V. A stability of better than 60 mV is needed to have negligible impact on the calorimeter energy resolution. Until 2015 manual calibrations were performed yearly. A new calibration system was deployed recently, which satisfies the requirement of low disturbance and high precision. The system is discussed in detail and first operational experience is presented.
Fasanella, Giuseppe
2016-01-01
The CMS Electromagnetic Calorimeter utilizes scintillating lead tungstate crystals, with avalanche photodiodes (APD) as photo-detectors in the barrel part. 1224 HV channels bias groups of 50 APD pairs, each at a voltage of about 380 V. The APD gain dependence on the voltage is 3pct/V. A stability of better than 60 mV is needed to have negligible impact on the calorimeter energy resolution. Until 2015 manual calibrations were performed yearly. A new calibration system was deployed recently, which satisfies the requirement of low disturbance and high precision. The system is discussed in detail and first operational experience is presented.
Wind Power Impact to Transient and Voltage Stability of the Power System in Eastern Denmark
DEFF Research Database (Denmark)
Rasmussen, Joana; Jørgensen, Preben; Palsson, Magni Thor
2005-01-01
Voltage stability, transient stability and reactive power compensation are extremely important issues for largescale integration of wind power in areas distant from the main transmission system in Eastern Denmark. This paper describes the application of a dynamic wind farm model in simulation...... studies for assessments of a large wind power penetration. The simulation results reveal problems with voltage stability due to the characteristic of wind turbine generation as well as the inability of the power system to meet the reactive power demand. Furthermore, the established model is applied...
ANALYSIS OF GRID-CONNECTED PHOTOVOLTAIC SYSTEM INTEGRATON ON LOW-VOLTAGE DISTRIBUTION NETWORK
Directory of Open Access Journals (Sweden)
NEMES C.
2016-03-01
Full Text Available The introduction of new local sources on the distribution network will impact the quality of power in different ways. The low-voltage customers are strongly affected by the level of power quality, especially by harmonic distortions. In present paper, the impact on the power quality of a low-voltage utility network with an integrated PV system has been assessed at the point of common coupling of the PV system. In this order, the most representative power quality indices concerning the harmonic distortion have been monitored and compared with the limits set by the corresponding standards.
Energy Technology Data Exchange (ETDEWEB)
NONE
2013-06-15
The project on the requirements for the retrofitting an extension of the maximum voltage power grid from the point of view of environmental protection and cultivated landscape work includes contributions on the following topics: the development of the European transmission grid, the grid extension law, restrictions for the power grid and their infrastructure, requirements for the regulations concerning the realization of the transnational grid extension, inclusion of the public - public acceptance - communication, requirements concerning the environmental compensation law, overhead line - underground cable - health hazards, ecological effects of overhead lines and underground cables, infrastructural projects, power supply in the future, structural relief by photovoltaics.
Energy Systems Integration: Demonstrating Distribution Feeder Voltage Control
Energy Technology Data Exchange (ETDEWEB)
2017-01-01
Overview fact sheet about the Smarter Grid Solutions Integrated Network Testbed for Energy Grid Research and Technology Experimentation (INTEGRATE) project at the Energy Systems Integration Facility. INTEGRATE is part of the U.S. Department of Energy's Grid Modernization Initiative.
Directory of Open Access Journals (Sweden)
Zetty Adibah Kamaruzzaman
2016-06-01
Full Text Available This paper presents the impact of grid-connected photovoltaic (PV generator on dynamic voltage stability of a power distribution system by considering solar intermittency, PV penetration level, and contingencies such as line outage and load increase. The IEEE 13 node test feeder is used as a test system, and a solar PV of 0.48 kV/0.5 MVA is integrated into the test system. Test results show that system voltage is stable at high PV penetration levels. Increase in load causes voltage instability, in which voltage drops below its allowable operating limit. Thus, increase in PV penetration level does not improve system voltage stability because the system experiences voltage collapse during line outage.
An approach for high voltage power supply system for HCAL of LHCb experiment
International Nuclear Information System (INIS)
Cimpean, A.; Dumitru, D.; Kluger, A.; Magureanu, C.; Tarta, D.; Coca, C.; Orlandea, M.; Popescu, S.
2003-01-01
The main aim of the calorimeter system of the LHCb (Large Hadron Collider Beauty) experiment dedicated to precision measurements of CP violation and rare phenomena is to provide identification of the electrons, hadrons and photons, for the level-0 trigger and offline analysis with measurements of position and energy. The system consists in a scintillator pad/preshower (SPD/PS) detector, an electromagnetic calorimeter (ECAL) and a hadron calorimeter (HCAL), all the sub-detectors having a similar technology with scintillating tiles as active material and being read out via wavelength-shifting fibers and with an identical readout electronics for ECAL and HCAL and similar electronics for the PS. During 1997-1999 a computer controlled High Voltage (HV) distribution scheme was developed by Horia Hulubei National Institute for Physics and Nuclear Engineering (IFIN-HH) group and used to supply the PMTs of half HCAL prototype during the beam tests (1998-2000). This scheme consisted of three parts: 1) a control box which includes low voltage power supply, the RS232 interface to a PC and three modules of high voltage power supply; 2) two types of multichannel HV distributors with an individual voltage setting; 3) a software package to control all settings and refresh them periodically. Based on the acquired experience, a new design for a High Voltage Power Supply (HVPS) which satisfies the LHCb requirements has been developed for PMTs of the hadron calorimeter. The demands of this system are simplicity and low cost. This HVPS with multiple outputs (HV for photocathode and D1 - D4 dynodes) is destined to supply, with the same high voltage, groups of PMTs sorted by similar characteristics as gain and sensitivity. Because of the high rates (∼ 40 MHz) supported by PMTs, booster voltage sources are necessary to supply current for the last 4 dynodes. The box has 5 HV power supplies for photocathodes and the last 4 dynodes, each HV power supply being followed by a 4 channel
Directory of Open Access Journals (Sweden)
Emerson Charles M. Silva
2013-09-01
Full Text Available This paper presents a proposal for a voltage inverter topology based on push-pull converters, switched at high frequency to inject energy into the grid from a source of DC power. A system using two reverse voltage static converters provides the power grid; energy in the form of alternating current, that can work in conjunction with the provision of utility power. Aiming at the possible use of renewable energy sources, that can be stored in the form of voltage continuous, such as wind, solar, hydroelectric and others. The functioning of topology is presented, such as the power and control circuits, as well as sizing components, theoretical and practical results achieved with the assembly of a prototype 100W of power and switching in 40khz, which after filtering provides the frequency of 60Hz, which is compatible with the Brazilian electrical system.
System for high-voltage control detectors with large number photomultipliers
International Nuclear Information System (INIS)
Donskov, S.V.; Kachanov, V.A.; Mikhajlov, Yu.V.
1985-01-01
A simple and inexpensive on-line system for hihg-voltage control which is designed for detectors with a large number of photomultipliers is developed and manufactured. It has been developed for the GAMC type hodoscopic electromagnetic calorimeters, comprising up to 4 thousand photomultipliers. High voltage variation is performed by a high-speed potentiometer which is rotated by a microengine. Block-diagrams of computer control electronics are presented. The high-voltage control system has been used for five years in the IHEP and CERN accelerator experiments. The operation experience has shown that it is quite simple and convenient in operation. In case of about 6 thousand controlled channels in both experiments no potentiometer and microengines failures were observed
Design of Simplified Maximum-Likelihood Receivers for Multiuser CPM Systems
Directory of Open Access Journals (Sweden)
Li Bing
2014-01-01
Full Text Available A class of simplified maximum-likelihood receivers designed for continuous phase modulation based multiuser systems is proposed. The presented receiver is built upon a front end employing mismatched filters and a maximum-likelihood detector defined in a low-dimensional signal space. The performance of the proposed receivers is analyzed and compared to some existing receivers. Some schemes are designed to implement the proposed receivers and to reveal the roles of different system parameters. Analysis and numerical results show that the proposed receivers can approach the optimum multiuser receivers with significantly (even exponentially in some cases reduced complexity and marginal performance degradation.
Design of simplified maximum-likelihood receivers for multiuser CPM systems.
Bing, Li; Bai, Baoming
2014-01-01
A class of simplified maximum-likelihood receivers designed for continuous phase modulation based multiuser systems is proposed. The presented receiver is built upon a front end employing mismatched filters and a maximum-likelihood detector defined in a low-dimensional signal space. The performance of the proposed receivers is analyzed and compared to some existing receivers. Some schemes are designed to implement the proposed receivers and to reveal the roles of different system parameters. Analysis and numerical results show that the proposed receivers can approach the optimum multiuser receivers with significantly (even exponentially in some cases) reduced complexity and marginal performance degradation.
High Voltage AC underground cable systems for power transmission
DEFF Research Database (Denmark)
Bak, Claus Leth; Silva, Filipe Miguel Faria da
2016-01-01
researching electrical engineering topics related to using underground cables for power transmission at EHV level and including the 420 kV level. The research topics were laid down by ET/AAU and Energinet.dk in the DANPAC (DANish Power systems with AC Cables) research project. The main topics are discussed...... on the basis of 39 references published by ET/AAU and Energinet.dk. Part I of the paper explains the events that lead to the research project, reactive power compensation, modelling for transient studies, including field measurements and improvements to the existing models, and temporary overvoltages due...... to resonances. Part II covers transient phenomena, harmonics in cables, system modelling for different phenomena, main and backup protections in cable-based networks, online fault detection and future trends....
High Voltage AC underground cable systems for power transmission
DEFF Research Database (Denmark)
Bak, Claus Leth; Silva, Filipe Miguel Faria da
2016-01-01
researching electrical engineering topics related to using underground cables for power transmission at EHV level and including the 420 kV level. The research topics were laid down by ET/AAU and Energinet.dk in the DANPAC (DANish Power systems with Ac Cables) research project. The main topics are discussed...... on the basis of 39 references published by ET/AAU and Energinet.dk. Part I of the paper explains the events that lead to the research project, reactive power compensation, modelling for transient studies, including field measurements and improvements to the existing models, and temporary overvoltages due...... to resonances. Part II covers transient phenomena, harmonics in cables, system modelling for different phenomena, main and backup protections in cable-based networks, online fault detection and future trends....
International Nuclear Information System (INIS)
Gilai, D.
1976-01-01
The Maximum Principle deals with optimization problems of systems, which are governed by ordinary differential equations, and which include constraints on the state and control variables. The development of nuclear engineering confronted the designers of reactors, shielding and other nuclear devices with many requests of optimization and savings and it was straight forward to use the Maximum Principle for solving optimization problems in nuclear engineering, in fact, it was widely used both structural concept design and dynamic control of nuclear systems. The main disadvantage of the Maximum Principle is that it is suitable only for systems which may be described by ordinary differential equations, e.g. one dimensional systems. In the present work, starting from the variational approach, the original Maximum Principle is extended to multidimensional systems, and the principle which has been derived, is of a more general form and is applicable to any system which can be defined by linear partial differential equations of any order. To check out the applicability of the extended principle, two examples are solved: the first in nuclear shield design, where the goal is to construct a shield around a neutron emitting source, using given materials, so that the total dose outside of the shielding boundaries is minimized, the second in material distribution design in the core of a power reactor, so that the power peak is minimised. For the second problem, an iterative method was developed. (B.G.)
Mnati, Mohannad Jabbar; Van den Bossche, Alex; Chisab, Raad Farhood
2017-04-15
In this paper, a new smart voltage and current monitoring system (SVCMS) technique is proposed. It monitors a three phase electrical system using an Arduino platform as a microcontroller to read the voltage and current from sensors and then wirelessly send the measured data to monitor the results using a new Android application. The integrated SVCMS design uses an Arduino Nano V3.0 as the microcontroller to measure the results from three voltage and three current sensors and then send this data, after calculation, to the Android smartphone device of an end user using Bluetooth HC-05. The Arduino Nano V3.0 controller and Bluetooth HC-05 are a cheap microcontroller and wireless device, respectively. The new Android smartphone application that monitors the voltage and current measurements uses the open source MIT App Inventor 2 software. It allows for monitoring some elementary fundamental voltage power quality properties. An effort has been made to investigate what is possible using available off-the-shelf components and open source software.
Nonlinear control of voltage source converters in AC-DC power system.
Dash, P K; Nayak, N
2014-07-01
This paper presents the design of a robust nonlinear controller for a parallel AC-DC power system using a Lyapunov function-based sliding mode control (LYPSMC) strategy. The inputs for the proposed control scheme are the DC voltage and reactive power errors at the converter station and the active and reactive power errors at the inverter station of the voltage-source converter-based high voltage direct current transmission (VSC-HVDC) link. The stability and robust tracking of the system parameters are ensured by applying the Lyapunov direct method. Also the gains of the sliding mode control (SMC) are made adaptive using the stability conditions of the Lyapunov function. The proposed control strategy offers invariant stability to a class of systems having modeling uncertainties due to parameter changes and exogenous inputs. Comprehensive computer simulations are carried out to verify the proposed control scheme under several system disturbances like changes in short-circuit ratio, converter parametric changes, and faults on the converter and inverter buses for single generating system connected to the power grid in a single machine infinite-bus AC-DC network and also for a 3-machine two-area power system. Furthermore, a second order super twisting sliding mode control scheme has been presented in this paper that provides a higher degree of nonlinearity than the LYPSMC and damps faster the converter and inverter voltage and power oscillations. Copyright © 2014 ISA. Published by Elsevier Ltd. All rights reserved.
Power System Decomposition for Practical Implementation of Bulk-Grid Voltage Control Methods
Energy Technology Data Exchange (ETDEWEB)
Vallem, Mallikarjuna R.; Vyakaranam, Bharat GNVSR; Holzer, Jesse T.; Elizondo, Marcelo A.; Samaan, Nader A.
2017-10-19
Power system algorithms such as AC optimal power flow and coordinated volt/var control of the bulk power system are computationally intensive and become difficult to solve in operational time frames. The computational time required to run these algorithms increases exponentially as the size of the power system increases. The solution time for multiple subsystems is less than that for solving the entire system simultaneously, and the local nature of the voltage problem lends itself to such decomposition. This paper describes an algorithm that can be used to perform power system decomposition from the point of view of the voltage control problem. Our approach takes advantage of the dominant localized effect of voltage control and is based on clustering buses according to the electrical distances between them. One of the contributions of the paper is to use multidimensional scaling to compute n-dimensional Euclidean coordinates for each bus based on electrical distance to perform algorithms like K-means clustering. A simple coordinated reactive power control of photovoltaic inverters for voltage regulation is used to demonstrate the effectiveness of the proposed decomposition algorithm and its components. The proposed decomposition method is demonstrated on the IEEE 118-bus system.
Performance improvement of a slip energy recovery drive system by a voltage-controlled technique
Energy Technology Data Exchange (ETDEWEB)
Tunyasrirut, Satean [Department of Instrumentation Engineering, Faculty of Engineering, Pathumwan Institute of Technology, 833 Rama1 Road, Pathumwan, Bangkok 10330 (Thailand); Kinnares, Vijit [Department of Electrical Engineering, Faculty of Engineering, King Mongkut' s Institute of Technology Ladkrabang, Bangkok 10520 (Thailand); Ngamwiwit, Jongkol [Department of Control Engineering, Faculty of Engineering, King Mongkut' s Institute of Technology Ladkrabang, Bangkok 10520 (Thailand)
2010-10-15
This paper introduces the performance improvement of a slip energy recovery drive system for the speed control of a wound rotor induction motor by a voltage-controlled technique. The slip energy occurred in the rotor circuit is transferred back to ac mains supply through a reactor instead of a step up transformer. The objective of the voltage-controlled technique is to increase power factor of the system and to reduce low order harmonics of the input line current. The drive system is designed and implemented using a voltage source inverter in conjunction with a boost chopper for DC link voltage, instead of a conventional drive using a 6 pulse converter or a Scherbius system. The slip power is recovered by the help of a voltage source inverter (VSI) based on a space vector pulse width modulation (SVPWM) technique. In order to keep the speed of the wound rotor induction motor constant over a certain range of operating conditions, the servo state feedback controller designed by a linear quadratic regulator (LQR) is also introduced in this paper. The overall control system is implemented on DSP, DS1104'TMS320F240 controller board. The performance improvement of the proposed system is tested in comparison with the conventional Scherbius system and the modified conventional Scherbius system by a 12 pulse converter in conjunction with a chopper at steady state and at dynamic conditions. A 220 W wound motor is employed for testing. It is found that the motor speed can be controlled to be constant in the operating range of 450-1200 rpm at no load and full load. It is also found that the efficiency of the proposed system is remarkably increased since the harmonics of the input ac line current is reduced while the ac line input power factor is increased. (author)
Stochastic behavior of a cold standby system with maximum repair time
Directory of Open Access Journals (Sweden)
Ashish Kumar
2015-09-01
Full Text Available The main aim of the present paper is to analyze the stochastic behavior of a cold standby system with concept of preventive maintenance, priority and maximum repair time. For this purpose, a stochastic model is developed in which initially one unit is operative and other is kept as cold standby. There is a single server who visits the system immediately as and when required. The server takes the unit under preventive maintenance after a maximum operation time at normal mode if one standby unit is available for operation. If the repair of the failed unit is not possible up to a maximum repair time, failed unit is replaced by new one. The failure time, maximum operation time and maximum repair time distributions of the unit are considered as exponentially distributed while repair and maintenance time distributions are considered as arbitrary. All random variables are statistically independent and repairs are perfect. Various measures of system effectiveness are obtained by using the technique of semi-Markov process and RPT. To highlight the importance of the study numerical results are also obtained for MTSF, availability and profit function.
2016-09-01
Khaligh, “Optimization of sizing and battery cycle life in battery/ultracapacitor hybrid energy storage systems for electric vehicle applications...depth cycling operation in photovoltaic system ,” in 22nd International Conference “Mixed Design of Integrated Circuits and Systems ,” Toruń, Poland...CURRENT LINK HARMONIC RIPPLE IN SINGLE-PHASE VOLTAGE SOURCE INVERTER SYSTEMS USING SUPERCAPACITORS by Gabriel D. Hernandez September 2016
Directory of Open Access Journals (Sweden)
V. M. Zolotaryov
2018-04-01
Full Text Available Aim. The article is devoted to the analysis of the electromechanical transient processes in a system of three frequency-controlled electric drives based on asynchronous motors that control current-carrying core motion, as well as to the study of the effect of such processes on the modes applying three-layer polymer insulation to the current-carrying core. Technique. The study was conducted based on the concepts of electromechanics, electromagnetic field theory, mathematical physics, mathematical modeling. Results. A mathematical model has been developed to analyze transients in an electromechanical system consisting of three frequency-controlled electric drives providing current-carrying core motion of ultra-high voltage cables in an inclined extrusion line. The coordination of the electromechanical parameters of the system drives has been carried out and the permissible changes in the supply voltage at the limiting mass while moving current-carrying core of ultra-high voltage cables with applied polymer insulation have been estimated. Scientific novelty. For the first time it is determined that with the limiting mass of the current-carrying core, the electromechanical system allows to stabilize the current-carrying core speed with the required accuracy at short-term decreases in the supply voltage by no more than 27 % of its amplitude value. It is also shown that this system is resistant to short-term increases in voltage by 32 % for 0.2 s. Practical significance. Using the developed model, it is possible to calculate the change in the configuration and speed of the slack current-carrying core when applying polymer insulation, depending on the specific mass of the current-carrying core per unit length, its tension at the bottom, the torque of the traction motor and the supply voltage to achieve stable operation of the system and accurate working of the set parameters.
International Nuclear Information System (INIS)
Zhao Huidong; Hei Yong; Qiao Shushan; Ye Tianchun
2012-01-01
An optimized channel estimation algorithm based on a time-spread structure in OFDM low-voltage power line communication (PLC) systems is proposed to achieve a lower bit error rate (BER). This paper optimizes the best maximum multi-path delay of the linear minimum mean square error (LMMSE) algorithm in time-domain spread OFDM systems. Simulation results indicate that the BER of the improved method is lower than that of conventional LMMSE algorithm, especially when the signal-to-noise ratio (SNR) is lower than 0 dB. Both the LMMSE algorithm and the proposed algorithm are implemented and fabricated in CSMC 0.18 μm technology. This paper analyzes and compares the hardware complexity and performance of the two algorithms. Measurements indicate that the proposed channel estimator has better performance than the conventional estimator.
Maximum Power Point Tracking of Photovoltaic System for Traffic Light Application
Muhida, Riza; Mohamad, Nor Hilmi; Legowo, Ari; Irawan, Rudi; Astuti, Winda
2013-01-01
Photovoltaic traffic light system is a significant application of renewable energy source. The development of the system is an alternative effort of local authority to reduce expenditure for paying fees to power supplier which the power comes from conventional energy source. Since photovoltaic (PV) modules still have relatively low conversion efficiency, an alternative control of maximum power point tracking (MPPT) method is applied to the traffic light system. MPPT is intended to catch up th...
Impact of marine reserve on maximum sustainable yield in a traditional prey-predator system
Paul, Prosenjit; Kar, T. K.; Ghorai, Abhijit
2018-01-01
Multispecies fisheries management requires managers to consider the impact of fishing activities on several species as fishing impacts both targeted and non-targeted species directly or indirectly in several ways. The intended goal of traditional fisheries management is to achieve maximum sustainable yield (MSY) from the targeted species, which on many occasions affect the targeted species as well as the entire ecosystem. Marine reserves are often acclaimed as the marine ecosystem management tool. Few attempts have been made to generalize the ecological effects of marine reserve on MSY policy. We examine here how MSY and population level in a prey-predator system are affected by the low, medium and high reserve size under different possible scenarios. Our simulation works shows that low reserve area, the value of MSY for prey exploitation is maximum when both prey and predator species have fast movement rate. For medium reserve size, our analysis revealed that the maximum value of MSY for prey exploitation is obtained when prey population has fast movement rate and predator population has slow movement rate. For high reserve area, the maximum value of MSY for prey's exploitation is very low compared to the maximum value of MSY for prey's exploitation in case of low and medium reserve. On the other hand, for low and medium reserve area, MSY for predator exploitation is maximum when both the species have fast movement rate.
Dynamic Voltage Stability Studies using a Modified IEEE 30-Bus System
Directory of Open Access Journals (Sweden)
Oluwafemi Emmanuel Oni
2016-09-01
Full Text Available Power System stability is an essential study in the planning and operation of an efficient, economic, reliable and secure electric power system because it encompasses all the facet of power systems operations, from planning, to conceptual design stages of the project as well as during the systems operating life span. This paper presents different scenario of power system stability studies on a modified IEEE 30-bus system which is subjected to different faults conditions. A scenario whereby the longest high voltage alternating current (HVAC line is replaced with a high voltage direct current (HVDC line was implemented. The results obtained show that the HVDC line enhances system stability more compared to the contemporary HVAC line. Dynamic analysis using RMS simulation tool was used on DigSILENT PowerFactory.
Concept design of the high voltage transmission system for the collider tunnel
International Nuclear Information System (INIS)
Norman, L.S.
1992-03-01
In order to provide electrical service to the Superconducting Super Collider Laboratory (SSCL) 54-mile-circumference collider of 125 MVA at 69 kV or 155 MVA at 138 kV of distributed power, it must be demonstrated that the concept design for a high-voltage transmission system can meet the distribution requirements of the collider electrical system with its cryogenic system's large motor loads and its pulsed power technical systems. It is a practical design, safe for operating personnel and cost-effective. The normal high-voltage transmission techniques of overhead and underground around the 54-mile collider tunnel could not be applied because of technical and physical constraints, or was environmentally unacceptable. The approach taken to solve these problems is the installation of 69-kV or 138-kV exposed solid dielectric transmission cable inside the collider tunnel with the superconducting magnets, cryogenic piping, electrical medium, and low-voltage distribution systems, and electronic/instrumentation wiring systems. This mixed-use approach has never been attempted in a collider tunnel. Research into all aspects of the engineering and installation problems and consultation with transmission cable manufacturers, electrical utilities, and European entities with similar installations -- such as the Channel Tunnel -- demonstrate that the concept design is feasible and practical. This paper presents a history of the evolution of the concept design. Design studies are underway to determine the system configuration and voltages. Included in this report are tunnel transmission cable system considerations and evaluation of solid dielectric high-voltage cable design
Concept design of the high-voltage transmission system for the collider tunnel
International Nuclear Information System (INIS)
Norman, L.S.
1992-01-01
In order to provide electrical service to the Superconducting Super Collider Laboratory (SSCL) 54-mile-circumference collider of 125 MVA at 69 kV or 155 MVA at 138 kV of distributed power, it must be demonstrated that the concept design for a high-voltage transmission system can meet the distribution requirements of the collider electrical system with its cryogenic system's large motor loads and its pulsed power technical systems. It is a practical design, safe for operating personnel and cost-effective. The normal high-voltage transmission techniques of overhead and underground around the 54-mile collider tunnel could not be applied because of technical and physical constraints, or was environmentally unacceptable. The approach taken to solve these problems is the installation of 69-kV or 138-kV exposed solid dielectric transmission cable inside the collider tunnel with the superconducting magnets, cryogenic piping, electrical medium, and low-voltage distribution systems, and electronic/instrumentation wiring systems. This mixed-use approach has never been attempted in a collider tunnel. Research into all aspects of the engineering and installation problems and consultation with transmission cable manufacturers, electrical utilities, and European entities with similar installations-such as the Channel Tunnel-demonstrate that the concept design is feasible and practical. This paper presents a history of the evolution of the concept design. Design studies are underway to determine the system configuration and voltages. Included in this report are tunnel transmission cable system considerations and evaluation of solid dielectric high-voltage cable design
Directory of Open Access Journals (Sweden)
I Made Ginarsa
2013-11-01
Full Text Available Chaos and voltage collapse occurred in critical power systems due to disturbing of energy. PID-SVC layered reccurrent neural network-based (LRN-based PID-SVC was proposed to solve this problem. A PID was used to control chaos and voltage collapse. Then, an SVC LRN-based to maintan the load voltage. By using the proposed controller, chaos and voltage collapse were able to suppress and maintain the load voltage around the setting value. Furthemore, the proposed controller gives better response than PI-SVC controller.
Maximum Likelihood Blind Channel Estimation for Space-Time Coding Systems
Directory of Open Access Journals (Sweden)
Hakan A. Çırpan
2002-05-01
Full Text Available Sophisticated signal processing techniques have to be developed for capacity enhancement of future wireless communication systems. In recent years, space-time coding is proposed to provide significant capacity gains over the traditional communication systems in fading wireless channels. Space-time codes are obtained by combining channel coding, modulation, transmit diversity, and optional receive diversity in order to provide diversity at the receiver and coding gain without sacrificing the bandwidth. In this paper, we consider the problem of blind estimation of space-time coded signals along with the channel parameters. Both conditional and unconditional maximum likelihood approaches are developed and iterative solutions are proposed. The conditional maximum likelihood algorithm is based on iterative least squares with projection whereas the unconditional maximum likelihood approach is developed by means of finite state Markov process modelling. The performance analysis issues of the proposed methods are studied. Finally, some simulation results are presented.
Conditions for maximum isolation of stable condensate during separation in gas-condensate systems
Energy Technology Data Exchange (ETDEWEB)
Trivus, N.A.; Belkina, N.A.
1969-02-01
A thermodynamic analysis is made of the gas-liquid separation process in order to determine the relationship between conditions of maximum stable condensate separation and physico-chemical nature and composition of condensate. The analysis was made by considering the multicomponent gas-condensate fluid produced from Zyrya field as a ternary system, composed of methane, an intermediate component (propane and butane) and a heavy residue, C/sub 6+/. Composition of 5 ternary systems was calculated for a wide variation in separator conditions. At each separator pressure there is maximum condensate production at a certain temperature. This occurs because solubility of condensate components changes with temperature. Results of all calculations are shown graphically. The graphs show conditions of maximum stable condensate separation.
Directory of Open Access Journals (Sweden)
Arbutina Bojan
2011-01-01
Full Text Available AM CVn-type stars and ultra-compact X-ray binaries are extremely interesting semi-detached close binary systems in which the Roche lobe filling component is a white dwarf transferring mass to another white dwarf, neutron star or a black hole. Earlier theoretical considerations show that there is a maximum mass ratio of AM CVn-type binary systems (qmax ≈ 2/3 below which the mass transfer is stable. In this paper we derive slightly different value for qmax and more interestingly, by applying the same procedure, we find the maximum expected white dwarf mass in ultra-compact X-ray binaries.
High voltage interactions of a sounding rocket with the ambient and system-generated environments
International Nuclear Information System (INIS)
Kuharski, R.A.; Jongeward, G.A.; Wilcox, K.G.; Rankin, T.V.; Roche, J.C.
1990-01-01
The high-power space systems will interact with their environment far more severely than the low-voltage, low-power space systems flown to date. As a minimum, these interactions will include ionization and bulk breakdown, plasma-induced surface flashover, oxygen erosion, meteor and debris damage, and radiation effects. The SPEAR program is addressing some of these issues through the development and testing of high-powered systems for the space environment. SPEAR III, the latest in the SPEAR program, is scheduled to fly in early 1991. It will test high-voltage designs in both ambient and system-generated environments. Two of the key questions that the experiment hopes to address are whether or not the Earth's magnetic field can cause the current that a high-voltage object draws from the plasma to be far less then the current that would be drawn in the absence of the magnetic field and under what neutral environment conditions a discharge from the high-voltage object to the plasma will occur. In this paper, the authors use EPSAT (the environment power system analysis tool) to baseline the design of SPEAR III. The authors' calculations indicate that the experiment will produce the conditions necessary to address these questions
Li-Ion Electrolytes with Improved Safety and Tolerance to High-Voltage Systems
Smart, Marshall C.; Bugga, Ratnakumar V.; Prakash, Surya; Krause, Frederick C.
2013-01-01
Given that lithium-ion (Li-ion) technology is the most viable rechargeable energy storage device for near-term applications, effort has been devoted to improving the safety characteristics of this system. Therefore, extensive effort has been devoted to developing nonflammable electrolytes to reduce the flammability of the cells/battery. A number of promising electrolytes have been developed incorporating flame-retardant additives, and have been shown to have good performance in a number of systems. However, these electrolyte formulations did not perform well when utilizing carbonaceous anodes with the high-voltage materials. Thus, further development was required to improve the compatibility. A number of Li-ion battery electrolyte formulations containing a flame-retardant additive [i.e., triphenyl phosphate (TPP)] were developed and demonstrated in high-voltage systems. These electrolytes include: (1) formulations that incorporate varying concentrations of the flame-retardant additive (from 5 to 15%), (2) the use of mono-fluoroethylene carbonate (FEC) as a co-solvent, and (3) the use of LiBOB as an electrolyte additive intended to improve the compatibility with high-voltage systems. Thus, improved safety has been provided without loss of performance in the high-voltage, high-energy system.
High voltage direct current transmission converters, systems and DC grids
Jovcic, Dragan
2015-01-01
This comprehensive reference guides the reader through all HVDC technologies, including LCC (Line Commutated Converter), 2-level VSC and VSC HVDC based on modular multilevel converters (MMC) for an in-depth understanding of converters, system level design, operating principles and modeling. Written in a tutorial style, the book also describes the key principles of design, control, protection and operation of DC transmission grids, which will be substantially different from the practice with AC transmission grids. The first dedicated reference to the latest HVDC technologies and DC grid developments; this is an essential resource for graduate students and researchers as well as engineers and professionals working on the design, modeling and operation of DC grids and HVDC.
Realworld maximum power point tracking simulation of PV system based on Fuzzy Logic control
Othman, Ahmed M.; El-arini, Mahdi M. M.; Ghitas, Ahmed; Fathy, Ahmed
2012-12-01
In the recent years, the solar energy becomes one of the most important alternative sources of electric energy, so it is important to improve the efficiency and reliability of the photovoltaic (PV) systems. Maximum power point tracking (MPPT) plays an important role in photovoltaic power systems because it maximize the power output from a PV system for a given set of conditions, and therefore maximize their array efficiency. This paper presents a maximum power point tracker (MPPT) using Fuzzy Logic theory for a PV system. The work is focused on the well known Perturb and Observe (P&O) algorithm and is compared to a designed fuzzy logic controller (FLC). The simulation work dealing with MPPT controller; a DC/DC Ćuk converter feeding a load is achieved. The results showed that the proposed Fuzzy Logic MPPT in the PV system is valid.
Realworld maximum power point tracking simulation of PV system based on Fuzzy Logic control
Directory of Open Access Journals (Sweden)
Ahmed M. Othman
2012-12-01
Full Text Available In the recent years, the solar energy becomes one of the most important alternative sources of electric energy, so it is important to improve the efficiency and reliability of the photovoltaic (PV systems. Maximum power point tracking (MPPT plays an important role in photovoltaic power systems because it maximize the power output from a PV system for a given set of conditions, and therefore maximize their array efficiency. This paper presents a maximum power point tracker (MPPT using Fuzzy Logic theory for a PV system. The work is focused on the well known Perturb and Observe (P&O algorithm and is compared to a designed fuzzy logic controller (FLC. The simulation work dealing with MPPT controller; a DC/DC Ćuk converter feeding a load is achieved. The results showed that the proposed Fuzzy Logic MPPT in the PV system is valid.
MODEL PREDICTIVE CONTROL FOR PHOTOVOLTAIC STATION MAXIMUM POWER POINT TRACKING SYSTEM
Directory of Open Access Journals (Sweden)
I. Elzein
2015-01-01
Full Text Available The purpose of this paper is to present an alternative maximum power point tracking, MPPT, algorithm for a photovoltaic module, PVM, to produce the maximum power, Pmax, using the optimal duty ratio, D, for different types of converters and load matching.We present a state-based approach to the design of the maximum power point tracker for a stand-alone photovoltaic power generation system. The system under consideration consists of a solar array with nonlinear time-varying characteristics, a step-up converter with appropriate filter.The proposed algorithm has the advantages of maximizing the efficiency of the power utilization, can be integrated to other MPPT algorithms without affecting the PVM performance, is excellent for Real-Time applications and is a robust analytical method, different from the traditional MPPT algorithms which are more based on trial and error, or comparisons between present and past states. The procedure to calculate the optimal duty ratio for a buck, boost and buck-boost converters, to transfer the maximum power from a PVM to a load, is presented in the paper. Additionally, the existence and uniqueness of optimal internal impedance, to transfer the maximum power from a photovoltaic module using load matching, is proved.
The high voltage system for the novel MPGD-based photon detectors of COMPASS RICH-1
Dalla Torre, S.; Birsa, R.; Bradamante, F.; Bressan, A.; Chatterjee, C.; Ciliberti, P.; Dasgupta, S.; Gobbo, B.; Gregori, M.; Hamar, G.; Levorato, S.; Martin, A.; Menon, G.; Tessarotto, F.; Zhao, Y.
2018-01-01
The architecture of the novel MPGD-based photon detectors of COMPASS RICH-1 consists in a large-size hybrid MPGD multilayer layout combining two layers of Thick-GEMs and a bulk resistive MICROMEGAS. Concerning biasing voltage, the Thick-GEMs are segmented in order to reduce the energy released in case of occasional discharges, while the MICROMEGAS anode is segmented in pads individually biased at positive voltage, while the micromesh is grounded. In total, there are ten different electrode types and more than 20000 electrodes supplied by more than 100 HV channels. Commercial power supply units are used. The original elements of the power supply system are the architecture of the voltage distribution net, the compensation, by voltage adjustment, of the effects of pressure and temperature variation affecting the detector gain and a sophisticated control software, which allows to protect the detectors against errors by the operator, to monitor and log voltages and current at 1 Hz rate and to automatically react ...
Application to the system of insulated of diagnosis in high-voltage motors by partial discharge
International Nuclear Information System (INIS)
Mikami, M.
2005-01-01
In order to detect electric insulators degradation of high-voltage electric motors at an early stage, measurements of partial discharge of operating high-voltage electric motors (about 150 units) in the nuclear power plants were conducted from 2001 to 2004 by the use of on-line monitoring systems that could measure partial discharge of electric insulators. Influencing factors for measured values were identified from measured data and evaluation criteria of electric insulators integrity were established based on variations of partial discharge values. (T. Tanaka)
Space vector modulation strategy for neutral-point voltage balancing in three-level inverter systems
DEFF Research Database (Denmark)
Choi, Uimin; Lee, Kyo Beum
2013-01-01
This study proposes a space vector modulation (SVM) strategy to balance the neutral-point voltage of three-level inverter systems. The proposed method is implemented by combining conventional symmetric SVM with nearest three-vector (NTV) modulation. The conventional SVM is converted to NTV...... modulation by properly adding or subtracting a minimum gate-on time. In addition, using this method, the switching frequency is reduced and a decrease of switching loss would be yielded. The neutral-point voltage is balanced by the proposed SVM strategy without additional hardware or complex calculations....... Simulation and experimental results are shown to verify the validity and feasibility of the proposed SVM strategy....
Negative-feedback control system of the high voltage power supply for ECRH
International Nuclear Information System (INIS)
Ding Tonghai; Liu Baohua; Jiang Shufang
2001-01-01
A kind of high accuracy negative high voltage power supply (HVPS) was introduced. The serial feedback was regulated according to the character of the high power tetrode and a new kind of integrator with preset value, which solved the key technological problem of the HVPS that the ECRH system required a voltage of -80 kV, a pulse width of 10 - 100 ms and a precision of 99.7%. The result using a PSPICE code simulation has shown that the method is practical
Control and protection system for an electron injector installed in a high-voltage terminal
International Nuclear Information System (INIS)
Martin, D.; Radu, A.; Baciu, G.; Grigore, D.
1979-01-01
The basic principles of operation of the control and protection system for an electron accelerator gun are described. The electron gun parameters are independently controlled by using four special secondary windings of the high-voltage transformer providing the accelerating voltage. Four groups of thyristor ac regulators employing phase control are connected so as to provide independent adjustment of each parameter of the gun. The power controller of modular construction has a single-phase supply from the 50 Hz 220 V mains. (orig.)
Control of a battery energy storage system connected to a low voltage grid
van Dun, J.J.C.M.; de Groot, Robert; Morren, Johan; Slootweg, Han
2015-01-01
This paper describes the development of a control algorithm for a battery energy storage system, which is connected to a residential low voltage grid. By predicting future load demand and photovoltaic production within the neighbourhood concerned, flattening of the aggregated neighbourhood
Wu, H.; Zhou, L.; Xu, T.; Fang, W. L.; He, W. G.; Liu, H. M.
2017-11-01
In order to improve the situation of voltage violation caused by the grid-connection of photovoltaic (PV) system in a distribution network, a bi-level programming model is proposed for battery energy storage system (BESS) deployment. The objective function of inner level programming is to minimize voltage violation, with the power of PV and BESS as the variables. The objective function of outer level programming is to minimize the comprehensive function originated from inner layer programming and all the BESS operating parameters, with the capacity and rated power of BESS as the variables. The differential evolution (DE) algorithm is applied to solve the model. Based on distribution network operation scenarios with photovoltaic generation under multiple alternative output modes, the simulation results of IEEE 33-bus system prove that the deployment strategy of BESS proposed in this paper is well adapted to voltage violation regulation invariable distribution network operation scenarios. It contributes to regulating voltage violation in distribution network, as well as to improve the utilization of PV systems.
Low voltage electroosmotic pump for high density integration into microfabricated fluidic systems
Heuck, F.C.A.; Staufer, U.
2011-01-01
A low voltage electroosmotic (eo) pump suitable for high density integration into microfabricated fluidic systems has been developed. The high density integration of the eo pump required a small footprint as well as a specific on-chip design to ventilate the electrolyzed gases emerging at the
Chen, Y.; Wang, J.; Wang, H. H.; Yang, L.; Chen, W.; Xu, Y. T.
2016-08-01
Double-fed induction generator (DFIG) is sensitive to the disturbances of grid, so the security and stability of the grid and the DFIG itself are under threat with the rapid increase of DFIG. Therefore, it is important to study dynamic response of the DFIG when voltage drop failure is happened in power system. In this paper, firstly, mathematical models and the control strategy about mechanical and electrical response processes is respectively introduced. Then through the analysis of response process, it is concluded that the dynamic response characteristics are related to voltage drop level, operating status of DFIG and control strategy adapted to rotor side. Last, the correctness of conclusion is validated by the simulation about mechanical and electrical response processes in different voltage levels drop and different DFIG output levels under DIgSILENT/PowerFactory software platform.
Impact of Wind Power Plants on Voltage Control of Power System
DEFF Research Database (Denmark)
Sarkar, Moumita; Altin, Müfit; Hansen, Anca Daniela
High penetration of renewable energy sources poses numerous challenges on stability and security of power systems. Wind power plants (WPPs) of considerable size when connected to a weak grid by long transmission line results in low short circuit ratio at the point of connection. This may result...... control, during transient voltage dips. Steady-state analysis is performed for stressed system conditions. Results are validated through simulation in a detailed power system model....
Directory of Open Access Journals (Sweden)
Amiri RABIE
2009-12-01
Full Text Available Voltage Source Converter (VSC based HVDC transmission technology hasbeen selected as the basis for several recent projects due to its controllability,compact modular design, ease of system interface, and low environmentalimpact. This paper investigates the dynamic performance of a 200MW,±100kV VSC-HVDC transmission system under some faulted conditionsusing MATLAB/Simulink. Simulation results confirm the satisfactoryperformance of the proposed system under active and reactive powervariations and fault conditions.
Fiber Optic Telemetry System for LLL High-Voltage Test Stand
International Nuclear Information System (INIS)
Richter, J.P.
1977-01-01
This paper describes the Fiber Optic Telemetry System designed to operate in the hostile particle and electromagnetic radiation environment of the High Voltage Test Stand. It discusses system criteria, components, packaging, and performance. In all tests to date, the system exceeds its design goals with very comfortable margins. It is well advanced into the fabrication stages with all crucial components tested and only straightforward TTL (Transistor Transistor Logic) circuitry to be completed
Robust Controller to Extract the Maximum Power of a Photovoltaic System
Directory of Open Access Journals (Sweden)
OULD CHERCHALI Noureddine
2014-05-01
Full Text Available This paper proposes a technique of intelligent control to track the maximum power point (MPPT of a photovoltaic system . The PV system is non-linear and it is exposed to external perturbations like temperature and solar irradiation. Fuzzy logic control is known for its stability and robustness. FLC is adopted in this work for the improvement and optimization of control performance of a photovoltaic system. Another technique called perturb and observe (P & O is studied and compared with the FLC technique. The PV system is constituted of a photovoltaic panel (PV, a DC-DC converter (Boost and a battery like a load. The simulation results are developed in MATLAB / Simulink software. The results show that the controller based on fuzzy logic is better and faster than the conventional controller perturb and observe (P & O and gives a good maximum power of a photovoltaic generator under different changes of weather conditions.
Recent Developments in Maximum Power Point Tracking Technologies for Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Nevzat Onat
2010-01-01
Full Text Available In photovoltaic (PV system applications, it is very important to design a system for operating of the solar cells (SCs under best conditions and highest efficiency. Maximum power point (MPP varies depending on the angle of sunlight on the surface of the panel and cell temperature. Hence, the operating point of the load is not always MPP of PV system. Therefore, in order to supply reliable energy to the load, PV systems are designed to include more than the required number of modules. The solution to this problem is that switching power converters are used, that is called maximum power point tracker (MPPT. In this study, the various aspects of these algorithms have been analyzed in detail. Classifications, definitions, and basic equations of the most widely used MPPT technologies are given. Moreover, a comparison was made in the conclusion.
Energy Technology Data Exchange (ETDEWEB)
Barboza, Luciano Vitoria [Sul-riograndense Federal Institute for Education, Science and Technology (IFSul), Pelotas, RS (Brazil)], E-mail: luciano@pelotas.ifsul.edu.br
2009-07-01
This paper presents an overview about the maximum load ability problem and aims to study the main factors that limit this load ability. Specifically this study focuses its attention on determining which electric system buses influence directly on the power demand supply. The proposed approach uses the conventional maximum load ability method modelled by an optimization problem. The solution of this model is performed using the Interior Point methodology. As consequence of this solution method, the Lagrange multipliers are used as parameters that identify the probable 'bottlenecks' in the electric power system. The study also shows the relationship between the Lagrange multipliers and the cost function in the Interior Point optimization interpreted like sensitivity parameters. In order to illustrate the proposed methodology, the approach was applied to an IEEE test system and to assess its performance, a real equivalent electric system from the South- Southeast region of Brazil was simulated. (author)
Zero-voltage DC/DC converter with asymmetric pulse-width modulation for DC micro-grid system
Lin, Bor-Ren
2018-04-01
This paper presents a zero-voltage switching DC/DC converter for DC micro-grid system applications. The proposed circuit includes three half-bridge circuit cells connected in primary-series and secondary-parallel in order to lessen the voltage rating of power switches and current rating of rectifier diodes. Thus, low voltage stress of power MOSFETs can be adopted for high-voltage input applications with high switching frequency operation. In order to achieve low switching losses and high circuit efficiency, asymmetric pulse-width modulation is used to turn on power switches at zero voltage. Flying capacitors are used between each circuit cell to automatically balance input split voltages. Therefore, the voltage stress of each power switch is limited at Vin/3. Finally, a prototype is constructed and experiments are provided to demonstrate the circuit performance.
Anderson, Karl F. (Inventor); Parker, Allen R., Jr. (Inventor)
1993-01-01
A constant current loop measuring system measures a property including the temperature of a sensor responsive to an external condition being measured. The measuring system includes thermocouple conductors connected to the sensor, sensing first and second induced voltages responsive to the external condition. In addition, the measuring system includes a current generator and reverser generating a constant current, and supplying the constant current to the thermocouple conductors in forward and reverse directions generating first and second measured voltages, and a determining unit receiving the first and second measured voltages from the current generator and reverser, and determining the temperature of the sensor responsive to the first and second measured voltages.
High voltage power supplies for ITER RF heating and current drive systems
International Nuclear Information System (INIS)
Gassmann, T.; Arambhadiya, B.; Beaumont, B.; Baruah, U.K.; Bonicelli, T.; Darbos, C.; Purohit, D.; Decamps, H.; Albajar, F.; Gandini, F.; Henderson, M.; Kazarian, F.; Lamalle, P.U.; Omori, T.; Parmar, D.; Patel, A.; Rathi, D.; Singh, N.P.
2011-01-01
The RF heating and current drive (H and CD) systems to be installed for the ITER fusion machine are the electron cyclotron (EC), ion cyclotron (IC) and, although not in the first phase of the project, lower hybrid (LH). These systems require high voltage, high current power supplies (HVPS) in CW operation. These HVPS should deliver around 50 MW electrical power to each of the RF H and CD systems with stringent requirements in terms of accuracy, voltage ripple, response time, turn off time and fault energy. The PSM (Pulse Step Modulation) technology has demonstrated over the past 20 years its ability to fulfill these requirements in many industrial facilities and other fusion reactors and has therefore been chosen as reference design for the IC and EC HVPS systems. This paper describes the technical specifications, including interfaces, the resulting constraints on the design, the conceptual design proposed for ITER EC and IC HVPS systems and the current status.
Zero-voltage ride-through capability of single-phase grid-connected photovoltaic systems
DEFF Research Database (Denmark)
Zhang, Zhen; Yang, Yongheng; Ma, Ruiqing
2017-01-01
Distributed renewable energy systems play an increasing role in today’s energy paradigm. Thus, intensive research activities have been centered on improving the performance of renewable energy systems, including photovoltaic (PV) systems, which should be of multiple-functionality. That is, the PV...... systems should be more intelligent in the consideration of grid stability, reliability, and fault protection. Therefore, in this paper, the performance of single-phase grid-connected PV systems under an extreme grid fault (i.e., when the grid voltage dips to zero) is explored. It has been revealed...... that combining a fast and accurate synchronization mechanism with appropriate control strategies for the zero-voltage ride-through (ZVRT) operation is mandatory. Accordingly, the representative synchronization techniques (i.e., the phase-locked loop (PLL) methods) in the ZVRT operation are compared in terms...
High Voltage Solar Array Arc Testing for a Direct Drive Hall Effect Thruster System
Schneider, Todd; Carruth, M. R., Jr.; Vaughn, J. A.; Jongeward, G. A.; Mikellides, I. G.; Ferguson, D.; Kerslake, T. W.; Peterson, T.; Snyder, D.; Hoskins, A.
2004-01-01
The deleterious effects of spacecraft charging are well known, particularly when the charging leads to arc events. The damage that results from arcing can severely reduce system lifetime and even cause critical system failures. On a primary spacecraft system such as a solar array, there is very little tolerance for arcing. Motivated by these concerns, an experimental investigation was undertaken to determine arc thresholds for a high voltage (200-500 V) solar array in a plasma environment. The investigation was in support of a NASA program to develop a Direct Drive Hall-Effect Thruster (D2HET) system. By directly coupling the solar array to a Hall-effect thruster, the D2HET program seeks to reduce mass, cost and complexity commonly associated with the power processing in conventional power systems. In the investigation, multiple solar array technologies and configurations were tested. The cell samples were biased to a negative voltage, with an applied potential difference between them, to imitate possible scenarios in solar array strings that could lead to damaging arcs. The samples were tested in an environment that emulated a low-energy, HET-induced plasma. Short duration trigger arcs as well as long duration sustained arcs were generated. Typical current and voltage waveforms associated with the arc events are presented. Arc thresholds are also defined in terms of voltage, current and power. The data will be used to propose a new, high-voltage (greater than 300 V) solar array design for which the likelihood of damage from arcing is minimal.
Directory of Open Access Journals (Sweden)
Chen-Han Wu
2011-12-01
Full Text Available Due to Japan’s recent nuclear crisis and petroleum price hikes, the search for renewable energy sources has become an issue of immediate concern. A promising candidate attracting much global attention is solar energy, as it is green and also inexhaustible. A maximum power point tracking (MPPT controller is employed in such a way that the output power provided by a photovoltaic (PV system is boosted to its maximum level. However, in the context of abrupt changes in irradiance, conventional MPPT controller approaches suffer from insufficient robustness against ambient variation, inferior transient response and a loss of output power as a consequence of the long duration required of tracking procedures. Accordingly, in this work the maximum power point tracking is carried out successfully using a sliding mode extremum-seeking control (SMESC method, and the tracking performances of three controllers are compared by simulations, that is, an extremum-seeking controller, a sinusoidal extremum-seeking controller and a sliding mode extremum-seeking controller. Being able to track the maximum power point promptly in the case of an abrupt change in irradiance, the SMESC approach is proven by simulations to be superior in terms of system dynamic and steady state responses, and an excellent robustness along with system stability is demonstrated as well.
Energy Technology Data Exchange (ETDEWEB)
Sahoo, N.C. [Faculty of Engineering and Technology, Multimedia University, Jalan Ayer Keroh Lama, Bukit Beruang, 75450 Melaka (Malaysia); Prasad, K. [Faculty of Information Science and Technology, Multimedia University, Jalan Ayer Keroh Lama, Bukit Beruang, 75450 Melaka (Malaysia)
2006-11-15
This paper presents a fuzzy genetic approach for reconfiguration of radial distribution systems (RDS) so as to maximize the voltage stability of the network for a specific set of loads. The network reconfiguration involves a mechanism for selection of the best set of branches to be opened, one from each loop, such that the reconfigured RDS possesses desired performance characteristics. This discrete solution space is better handled by the proposed scheme, which maximizes a suitable optimizing function (computed using two different approaches). In the first approach, this function is chosen as the average of a voltage stability index of all the buses in the RDS, while in the second approach, the complete RDS is reduced to a two bus equivalent system and the optimizing function is the voltage stability index of this reduced two bus system. The fuzzy genetic algorithm uses a suitable coding and decoding scheme for maintaining the radial nature of the network at every stage of genetic evolution, and it also uses a fuzzy rule based mutation controller for efficient search of the solution space. This method, tested on 69 bus and 33 bus RDSs, shows promising results for the both approaches. It is also observed that the network losses are reduced when the voltage stability is enhanced by the network reconfiguration. (author)
International Nuclear Information System (INIS)
Sahoo, N.C.; Prasad, K.
2006-01-01
This paper presents a fuzzy genetic approach for reconfiguration of radial distribution systems (RDS) so as to maximize the voltage stability of the network for a specific set of loads. The network reconfiguration involves a mechanism for selection of the best set of branches to be opened, one from each loop, such that the reconfigured RDS possesses desired performance characteristics. This discrete solution space is better handled by the proposed scheme, which maximizes a suitable optimizing function (computed using two different approaches). In the first approach, this function is chosen as the average of a voltage stability index of all the buses in the RDS, while in the second approach, the complete RDS is reduced to a two bus equivalent system and the optimizing function is the voltage stability index of this reduced two bus system. The fuzzy genetic algorithm uses a suitable coding and decoding scheme for maintaining the radial nature of the network at every stage of genetic evolution, and it also uses a fuzzy rule based mutation controller for efficient search of the solution space. This method, tested on 69 bus and 33 bus RDSs, shows promising results for the both approaches. It is also observed that the network losses are reduced when the voltage stability is enhanced by the network reconfiguration
Energy Technology Data Exchange (ETDEWEB)
Gu, Z.; Rizy, D.T.
1996-02-01
A neural network for controlling shunt capacitor banks and feeder voltage regulators in electric distribution systems is presented. The objective of the neural controller is to minimize total I{sup 2}R losses and maintain all bus voltages within standard limits. The performance of the neural network for different input selections and training data is discussed and compared. Two different input selections are tried, one using the previous control states of the capacitors and regulator along with measured line flows and voltage which is equivalent to having feedback and the other with measured line flows and voltage without previous control settings. The results indicate that the neural net controller with feedback can outperform the one without. Also, proper selection of a training data set that adequately covers the operating space of the distribution system is important for achieving satisfactory performance with the neural controller. The neural controller is tested on a radially configured distribution system with 30 buses, 5 switchable capacitor banks an d one nine tap line regulator to demonstrate the performance characteristics associated with these principles. Monte Carlo simulations show that a carefully designed and relatively compact neural network with a small but carefully developed training set can perform quite well under slight and extreme variation of loading conditions.
Huang, Yu
Solar energy becomes one of the major alternative renewable energy options for its huge abundance and accessibility. Due to the intermittent nature, the high demand of Maximum Power Point Tracking (MPPT) techniques exists when a Photovoltaic (PV) system is used to extract energy from the sunlight. This thesis proposed an advanced Perturbation and Observation (P&O) algorithm aiming for relatively practical circumstances. Firstly, a practical PV system model is studied with determining the series and shunt resistances which are neglected in some research. Moreover, in this proposed algorithm, the duty ratio of a boost DC-DC converter is the object of the perturbation deploying input impedance conversion to achieve working voltage adjustment. Based on the control strategy, the adaptive duty ratio step size P&O algorithm is proposed with major modifications made for sharp insolation change as well as low insolation scenarios. Matlab/Simulink simulation for PV model, boost converter control strategy and various MPPT process is conducted step by step. The proposed adaptive P&O algorithm is validated by the simulation results and detail analysis of sharp insolation changes, low insolation condition and continuous insolation variation.
Zero-Voltage Ride-Through Capability of Single-Phase Grid-Connected Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Zhen Zhang
2017-03-01
Full Text Available Distributed renewable energy systems play an increasing role in today’s energy paradigm. Thus, intensive research activities have been centered on improving the performance of renewable energy systems, including photovoltaic (PV systems, which should be of multiple-functionality. That is, the PV systems should be more intelligent in the consideration of grid stability, reliability, and fault protection. Therefore, in this paper, the performance of single-phase grid-connected PV systems under an extreme grid fault (i.e., when the grid voltage dips to zero is explored. It has been revealed that combining a fast and accurate synchronization mechanism with appropriate control strategies for the zero-voltage ride-through (ZVRT operation is mandatory. Accordingly, the representative synchronization techniques (i.e., the phase-locked loop (PLL methods in the ZVRT operation are compared in terms of detection precision and dynamic response. It shows that the second-order generalized integrator (SOGI-PLL is a promising solution for single-phase systems in the case of fault ride-through. A control strategy by modifying the SOGI-PLL scheme is then introduced to single-phase grid-connected PV systems for ZVRT operation. Simulations are performed to verify the discussions. The results have demonstrated that the proposed method can help single-phase PV systems to temporarily ride through zero-voltage faults with good dynamics.
Directory of Open Access Journals (Sweden)
Rafael Cisneros-Magaña
2018-06-01
Full Text Available This paper proposes a time-domain methodology based on the unscented Kalman filter to estimate voltage sags and their characteristics, such as magnitude and duration in power systems represented by nonlinear models. Partial and noisy measurements from the electrical network with nonlinear loads, used as data, are assumed. The characteristics of voltage sags can be calculated in a discrete form with the unscented Kalman filter to estimate all the busbar voltages; being possible to determine the rms voltage magnitude and the voltage sag starting and ending time, respectively. Voltage sag state estimation results can be used to obtain the power quality indices for monitored and unmonitored busbars in the power grid and to design adequate mitigating techniques. The proposed methodology is successfully validated against the results obtained with the time-domain system simulation for the power system with nonlinear components, being the normalized root mean square error less than 3%.
Directory of Open Access Journals (Sweden)
Chih-Lung Shen
2015-09-01
Full Text Available In this paper, an integrated three-voltage-booster DC-DC (direct current to direct current converter is proposed to achieve high voltage gain for renewable-energy generation systems. The proposed converter integrates three voltage-boosters into one power stage, which is composed of an active switch, a coupled-inductor, five diodes, and five capacitors. As compared with conventional high step-up converters, it has a lower component count. In addition, the features of leakage-energy recycling and switching loss reduction can be accomplished for conversion efficiency improvement. While the active switch is turned off, the converter can inherently clamp the voltage across power switch and suppress voltage spikes. Moreover, the reverse-recovery currents of all diodes can be alleviated by leakage inductance. A 200 W prototype operating at 100 kHz switching frequency with 36 V input and 400 V output is implemented to verify the theoretical analysis and to demonstrate the feasibility of the proposed high step-up DC-DC converter.
Yang, G.; Stark, B. H.; Burrow, S. G.; Hollis, S. J.
2014-11-01
This paper demonstrates the use of passive voltage multipliers for rapid start-up of sub-milliwatt electromagnetic energy harvesting systems. The work describes circuit optimization to make as short as possible the transition from completely depleted energy storage to the first powering-up of an actively controlled switched-mode converter. The dependency of the start-up time on component parameters and topologies is derived by simulation and experimentation. The resulting optimized multiplier design reduces the start-up time from several minutes to 1 second. An additional improvement uses the inherent cascade structure of the voltage multiplier to power sub-systems at different voltages. This multi-rail start-up is shown to reduce the circuit losses of the active converter by 72% with respect to the optimized single-rail system. The experimental results provide insight into the multiplier's transient behaviour, including circuit interactions, in a complete harvesting system, and offer important information to optimize voltage multipliers for rapid start-up.
International Nuclear Information System (INIS)
Yang, G; Stark, B H; Burrow, S G; Hollis, S J
2014-01-01
This paper demonstrates the use of passive voltage multipliers for rapid start-up of sub-milliwatt electromagnetic energy harvesting systems. The work describes circuit optimization to make as short as possible the transition from completely depleted energy storage to the first powering-up of an actively controlled switched-mode converter. The dependency of the start-up time on component parameters and topologies is derived by simulation and experimentation. The resulting optimized multiplier design reduces the start-up time from several minutes to 1 second. An additional improvement uses the inherent cascade structure of the voltage multiplier to power sub-systems at different voltages. This multi-rail start-up is shown to reduce the circuit losses of the active converter by 72% with respect to the optimized single-rail system. The experimental results provide insight into the multiplier's transient behaviour, including circuit interactions, in a complete harvesting system, and offer important information to optimize voltage multipliers for rapid start-up
Directory of Open Access Journals (Sweden)
Margo P
2009-11-01
Full Text Available Dynamic Voltage Restorer (DVR is a power electronics device to protect sensitive load when voltage sag occurs. Commonly, sensitive loads are electronic-based devices which generate harmonics. The magnitude and phase of compensated voltage in DVR depend on grounding system and type of fault. If the system is floating, the zero sequence components do not appear on the load side. Meanwhile, in a neutral grounded system, voltage sag is extremely affected by zero sequence components. A blocking transformer is commonly installed in series with DVR to reduce the effect of zero sequence components. This paper proposes a new DVR control scheme that is capable of eliminating the blocking transformer and reducing harmonic distortion. The system uses fuzzy polar controller to replace the conventional PI or FL controller that is commonly used. By taking into account the zero sequence components in the controller design, the effects of zero sequence components can be compensated. Simulated results show the effectiveness of the proposed DVR controller
An automotive thermoelectric-photovoltaic hybrid energy system using maximum power point tracking
International Nuclear Information System (INIS)
Zhang Xiaodong; Chau, K.T.
2011-01-01
In recent years, there has been active research on exhaust gas waste heat energy recovery for automobiles. Meanwhile, the use of solar energy is also proposed to promote on-board renewable energy and hence to improve their fuel economy. In this paper, a new thermoelectric-photovoltaic (TE-PV) hybrid energy system is proposed and implemented for automobiles. The key is to newly develop the power conditioning circuit using maximum power point tracking so that the output power of the proposed TE-PV hybrid energy system can be maximized. An experimental system is prototyped and tested to verify the validity of the proposed system.
Power electronics and control techniques for maximum energy harvesting in photovoltaic systems
Femia, Nicola
2012-01-01
Incentives provided by European governments have resulted in the rapid growth of the photovoltaic (PV) market. Many PV modules are now commercially available, and there are a number of power electronic systems for processing the electrical power produced by PV systems, especially for grid-connected applications. Filling a gap in the literature, Power Electronics and Control Techniques for Maximum Energy Harvesting in Photovoltaic Systems brings together research on control circuits, systems, and techniques dedicated to the maximization of the electrical power produced by a photovoltaic (PV) so
Chaos control of ferroresonance system based on RBF-maximum entropy clustering algorithm
International Nuclear Information System (INIS)
Liu Fan; Sun Caixin; Sima Wenxia; Liao Ruijin; Guo Fei
2006-01-01
With regards to the ferroresonance overvoltage of neutral grounded power system, a maximum-entropy learning algorithm based on radial basis function neural networks is used to control the chaotic system. The algorithm optimizes the object function to derive learning rule of central vectors, and uses the clustering function of network hidden layers. It improves the regression and learning ability of neural networks. The numerical experiment of ferroresonance system testifies the effectiveness and feasibility of using the algorithm to control chaos in neutral grounded system
Voltage Stability Bifurcation Analysis for AC/DC Systems with VSC-HVDC
Directory of Open Access Journals (Sweden)
Yanfang Wei
2013-01-01
Full Text Available A voltage stability bifurcation analysis approach for modeling AC/DC systems with VSC-HVDC is presented. The steady power model and control modes of VSC-HVDC are briefly presented firstly. Based on the steady model of VSC-HVDC, a new improved sequential iterative power flow algorithm is proposed. Then, by use of continuation power flow algorithm with the new sequential method, the voltage stability bifurcation of the system is discussed. The trace of the P-V curves and the computation of the saddle node bifurcation point of the system can be obtained. At last, the modified IEEE test systems are adopted to illustrate the effectiveness of the proposed method.
System for Relay Protection Command Transmission by High-Voltage Lines
Directory of Open Access Journals (Sweden)
D. A. Yenkov
2009-01-01
Full Text Available Development of a system for relay protection command transmission by high-voltage lines is shown in the paper. The paper describes an architecture of the system, main principles of its operation, engineering aspects of the development that is accomplishment of technical requirements, solution of trades-off. Justification of the selected design and an algorithm of the reliable detection of relay protection signals are given in the paper.
The prediction and prevention of voltage collapse in the Finnish power system
Energy Technology Data Exchange (ETDEWEB)
Bastman, J; Lakervi, E [Tampere Univ. of Tech. (Finland); Hirvonen, R; Kuronen, P; Hagman, E [IVO Group (Finland)
1994-12-31
The Finnish power system is a part of the Nordic power system (NORDEL), which includes Finland, Sweden, Norway and the eastern part of Denmark. In NORDEL the transmission distances are long, which implies that the power transmission capacities are determined by stability criteria . The methods to prevent and predict the voltage collapse during severe disturbances are studied using advances simulation program. Results are presented. (author) 10 figs., 1 tab.
DEFF Research Database (Denmark)
Yao, Jun; Li, Qing; Chen, Zhe
2013-01-01
in the multiple synchronous rotating reference frames. In order to counteract the adverse effects of the voltage harmonics upon the DFIG, the SGSC generates series compensation control voltages to keep the stator voltage sinusoidal and symmetrical, which allows the use of the conventional vector control strategy......This paper presents a coordinated control method for a doubly-fed induction generator (DFIG)-based wind-power generation system with a series grid-side converter (SGSC) under distorted grid voltage conditions. The detailed mathematical models of the DFIG system with SGSC are developed...
International Nuclear Information System (INIS)
Amjady, Nima; Ansari, Mohammad Reza
2008-01-01
The introduction of liberalized electricity markets in many countries has resulted in more highly stressed power systems. On the other hand, operating points of a power system are acceptable in the feasible region, which is surrounded by the borders of different stabilities. Power system instability is critical for all participants of the electricity market. Determination of different stability margins can result in the optimum utilization of power system with minimum risk. This paper focuses on the small disturbance voltage stability, which is an important subset of the power system global stability. This kind of voltage stability is usually evaluated by static analysis tools such as continuation power flow, while it essentially has dynamic nature. Besides, a combination of linear and nonlinear analysis tools is required to correctly analyze it. In this paper, a hybrid evaluation method composed of static, dynamic, linear, and nonlinear analysis tools is proposed for this purpose. Effect of load scenario, generation pattern, branch and generator contingency on the small disturbance voltage stability are evaluated by the hybrid method. The test results are given for New England and IEEE68 bus test systems. (author)
International Nuclear Information System (INIS)
Elnaggar, M.; Abdel Fattah, H.A.; Elshafei, A.L.
2014-01-01
This paper presents a complete design of a two-level control system to capture maximum power in wind energy conversion systems. The upper level of the proposed control system adopts a modified line search optimization algorithm to determine a setpoint for the wind turbine speed. The calculated speed setpoint corresponds to the maximum power point at given operating conditions. The speed setpoint is fed to a generalized predictive controller at the lower level of the control system. A different formulation, that treats the aerodynamic torque as a disturbance, is postulated to derive the control law. The objective is to accurately track the setpoint while keeping the control action free from unacceptably fast or frequent variations. Simulation results based on a realistic model of a 1.5 MW wind turbine confirm the superiority of the proposed control scheme to the conventional ones. - Highlights: • The structure of a MPPT (maximum power point tracking) scheme is presented. • The scheme is divided into the optimization algorithm and the tracking controller. • The optimization algorithm is based on an online line search numerical algorithm. • The tracking controller is treating the aerodynamics torque as a loop disturbance. • The control technique is simulated with stochastic wind speed by Simulink and FAST
Khoshkbar Sadigh, Arash
Part I: Dynamic Voltage Restorer In the present power grids, voltage sags are recognized as a serious threat and a frequently occurring power-quality problem and have costly consequence such as sensitive loads tripping and production loss. Consequently, the demand for high power quality and voltage stability becomes a pressing issue. Dynamic voltage restorer (DVR), as a custom power device, is more effective and direct solutions for "restoring" the quality of voltage at its load-side terminals when the quality of voltage at its source-side terminals is disturbed. In the first part of this thesis, a DVR configuration with no need of bulky dc link capacitor or energy storage is proposed. This fact causes to reduce the size of the DVR and increase the reliability of the circuit. In addition, the proposed DVR topology is based on high-frequency isolation transformer resulting in the size reduction of transformer. The proposed DVR circuit, which is suitable for both low- and medium-voltage applications, is based on dc-ac converters connected in series to split the main dc link between the inputs of dc-ac converters. This feature makes it possible to use modular dc-ac converters and utilize low-voltage components in these converters whenever it is required to use DVR in medium-voltage application. The proposed configuration is tested under different conditions of load power factor and grid voltage harmonic. It has been shown that proposed DVR can compensate the voltage sag effectively and protect the sensitive loads. Following the proposition of the DVR topology, a fundamental voltage amplitude detection method which is applicable in both single/three-phase systems for DVR applications is proposed. The advantages of proposed method include application in distorted power grid with no need of any low-pass filter, precise and reliable detection, simple computation and implementation without using a phased locked loop and lookup table. The proposed method has been verified
The project of autocontrol for CAEN high voltage systems in high energy physics experiments
International Nuclear Information System (INIS)
Qian Sen; Wang Zhimin; Chinese Academy of Sciences, Beijing; Cai Xiao; Wang Yifang; Zhang Jiawen; Yang Changgen
2008-01-01
Based on TCP/IP network communication techniques, CAMAC Bus Technology, PCI Bus Technology and RS232 Serial Communication Technique, we developed and established a serial of software in Linux or Win32 system to auto control these high voltage systems made by CAEN Company, which are always used in high energy physics experiments. The operator can use this software to control and monitor the system independently, or encapsulate it into the DAQ system to control the test system and acquire data synchronously and high-efficaciously. (authors)
Liu, Chuncheng; Qu, Da; Wang, Chongyang; Lv, Chunlei; Li, Guoqiang
2017-12-01
With the rapid development of technology and society, all walks of life in China are becoming more and more dependent on power systems. When earthquake occurs, the electrical equipment of substation is prone to damage because of its own structural features, top-heavy, and brittleness of main body. At the same time, due to the complex coupling of the soft electrical connection of substation electrical equipment, the negative impact can not be estimated. In this paper, the finite element model of the coupling system of the single unit of high voltage electrical equipment with the connecting soft bus is established and the seismic response is analysed. The results showed that there is a significant difference between the simple analysis for the seismic response of electrical equipment monomer and the analytical results of electrical equipment systems, and the impact on different electrical equipment is different. It lays a foundation for the future development of seismic performance analysis of extra high voltage electrical equipment.
Hopf bifurcation and chaos from torus breakdown in voltage-mode controlled DC drive systems
International Nuclear Information System (INIS)
Dai Dong; Ma Xikui; Zhang Bo; Tse, Chi K.
2009-01-01
Period-doubling bifurcation and its route to chaos have been thoroughly investigated in voltage-mode and current-mode controlled DC motor drives under simple proportional control. In this paper, the phenomena of Hopf bifurcation and chaos from torus breakdown in a voltage-mode controlled DC drive system is reported. It has been shown that Hopf bifurcation may occur when the DC drive system adopts a more practical proportional-integral control. The phenomena of period-adding and phase-locking are also observed after the Hopf bifurcation. Furthermore, it is shown that the stable torus can breakdown and chaos emerges afterwards. The work presented in this paper provides more complete information about the dynamical behaviors of DC drive systems.
Maximum sustainable yield and species extinction in a prey-predator system: some new results.
Ghosh, Bapan; Kar, T K
2013-06-01
Though the maximum sustainable yield (MSY) approach has been legally adopted for the management of world fisheries, it does not provide any guarantee against from species extinction in multispecies communities. In the present article, we describe the appropriateness of the MSY policy in a Holling-Tanner prey-predator system with different types of functional responses. It is observed that for both type I and type II functional responses, harvesting of either prey or predator species at the MSY level is a sustainable fishing policy. In the case of combined harvesting, both the species coexist at the maximum sustainable total yield (MSTY) level if the biotic potential of the prey species is greater than a threshold value. Further, increase of the biotic potential beyond the threshold value affects the persistence of the system.
Directory of Open Access Journals (Sweden)
R. Ramaprabha
2015-06-01
Full Text Available Mismatching effects due to partial shaded conditions are the major drawbacks existing in today’s photovoltaic (PV systems. These mismatch effects are greatly reduced in distributed PV system architecture where each panel is effectively decoupled from its neighboring panel. To obtain the optimal operation of the PV panels, maximum power point tracking (MPPT techniques are used. In partial shaded conditions, detecting the maximum operating point is difficult as the characteristic curves are complex with multiple peaks. In this paper, a neural network control technique is employed for MPPT. Detailed analyses were carried out on MPPT controllers in centralized and distributed architecture under partial shaded environments. The efficiency of the MPPT controllers and the effectiveness of the proposed control technique under partial shaded environments was examined using MATLAB software. The results were validated through experimentation.
Fuzzy sliding mode control for maximum power point tracking of a photovoltaic pumping system
Directory of Open Access Journals (Sweden)
Sabah Miqoi
2017-03-01
Full Text Available In this paper a new maximum power point tracking method based on fuzzy sliding mode control is proposed, and employed in a PV water pumping system based on a DC-DC boost converter, to produce maximum power from the solar panel hence more speed in the DC motor and more water quantity. This method combines two different tracking techniques sliding mode control and fuzzy logic; our controller is based on sliding mode control, then to give better stability and enhance the power production a fuzzy logic technique was added. System modeling, sliding method definition and the new control method presentation are represented in this paper. The results of the simulation that are compared to both sliding mode controller and perturbation and observation method demonstrate effectiveness and robustness of the proposed controller.
Maximum principles and sharp constants for solutions of elliptic and parabolic systems
Kresin, Gershon
2012-01-01
The main goal of this book is to present results pertaining to various versions of the maximum principle for elliptic and parabolic systems of arbitrary order. In particular, the authors present necessary and sufficient conditions for validity of the classical maximum modulus principles for systems of second order and obtain sharp constants in inequalities of Miranda-Agmon type and in many other inequalities of a similar nature. Somewhat related to this topic are explicit formulas for the norms and the essential norms of boundary integral operators. The proofs are based on a unified approach using, on one hand, representations of the norms of matrix-valued integral operators whose target spaces are linear and finite dimensional, and, on the other hand, on solving certain finite dimensional optimization problems. This book reflects results obtained by the authors, and can be useful to research mathematicians and graduate students interested in partial differential equations.
Kleidon, Axel
2009-06-01
The Earth system is maintained in a unique state far from thermodynamic equilibrium, as, for instance, reflected in the high concentration of reactive oxygen in the atmosphere. The myriad of processes that transform energy, that result in the motion of mass in the atmosphere, in oceans, and on land, processes that drive the global water, carbon, and other biogeochemical cycles, all have in common that they are irreversible in their nature. Entropy production is a general consequence of these processes and measures their degree of irreversibility. The proposed principle of maximum entropy production (MEP) states that systems are driven to steady states in which they produce entropy at the maximum possible rate given the prevailing constraints. In this review, the basics of nonequilibrium thermodynamics are described, as well as how these apply to Earth system processes. Applications of the MEP principle are discussed, ranging from the strength of the atmospheric circulation, the hydrological cycle, and biogeochemical cycles to the role that life plays in these processes. Nonequilibrium thermodynamics and the MEP principle have potentially wide-ranging implications for our understanding of Earth system functioning, how it has evolved in the past, and why it is habitable. Entropy production allows us to quantify an objective direction of Earth system change (closer to vs further away from thermodynamic equilibrium, or, equivalently, towards a state of MEP). When a maximum in entropy production is reached, MEP implies that the Earth system reacts to perturbations primarily with negative feedbacks. In conclusion, this nonequilibrium thermodynamic view of the Earth system shows great promise to establish a holistic description of the Earth as one system. This perspective is likely to allow us to better understand and predict its function as one entity, how it has evolved in the past, and how it is modified by human activities in the future.
Preliminary application of maximum likelihood method in HL-2A Thomson scattering system
International Nuclear Information System (INIS)
Yao Ke; Huang Yuan; Feng Zhen; Liu Chunhua; Li Enping; Nie Lin
2010-01-01
Maximum likelihood method to process the data of HL-2A Thomson scattering system is presented. Using mathematical statistics, this method maximizes the possibility of the likeness between the theoretical data and the observed data, so that we could get more accurate result. It has been proved to be applicable in comparison with that of the ratios method, and some of the drawbacks in ratios method do not exist in this new one. (authors)
Determination of Maximum Follow-up Speed of Electrode System of Resistance Projection Welders
DEFF Research Database (Denmark)
Wu, Pei; Zhang, Wenqi; Bay, Niels
2004-01-01
the weld process settings for the stable production and high quality of products. In this paper, the maximum follow-up speed of electrode system was tested by using a special designed device which can be mounted to all types of machine and easily to be applied in industry, the corresponding mathematical...... expression was derived based on a mathematical model. Good accordance was found between test and model....
Directory of Open Access Journals (Sweden)
EMIROGLU, S.
2017-11-01
Full Text Available This paper proposes a distributed reactive power control based approach to deploy Volt/VAr optimization (VVO / Conservation Voltage Reduction (CVR algorithm in a distribution network with distributed generations (DG units and distribution static synchronous compensators (D-STATCOM. A three-phase VVO/CVR problem is formulated and the reactive power references of D-STATCOMs and DGs are determined in a distributed way by decomposing the VVO/CVR problem into voltage and reactive power control. The main purpose is to determine the coordination between voltage regulator (VR and reactive power sources (Capacitors, D-STATCOMs and DGs based on VVO/CVR. The study shows that the reactive power injection capability of DG units may play an important role in VVO/CVR. In addition, it is shown that the coordination of VR and reactive power sources does not only save more energy and power but also reduces the power losses. Moreover, the proposed VVO/CVR algorithm reduces the computational burden and finds fast solutions. To illustrate the effectiveness of the proposed method, the VVO/CVR is performed on the IEEE 13-node test system feeder considering unbalanced loading and line configurations. The tests are performed taking the practical voltage-dependent load modeling and different customer types into consideration to improve accuracy.
International Nuclear Information System (INIS)
Shigeru Aoki
2005-01-01
The secondary system such as pipings, tanks and other mechanical equipment is installed in the primary system such as building. The important secondary systems should be designed to maintain their function even if they are subjected to destructive earthquake excitations. The secondary system has many nonlinear characteristics. Impact and friction characteristic, which are observed in mechanical supports and joints, are common nonlinear characteristics. As impact damper and friction damper, impact and friction characteristic are used for reduction of seismic response. In this paper, analytical methods of the first excursion probability of the secondary system with impact and friction, subjected to earthquake excitation are proposed. By using the methods, the effects of impact force, gap size and friction force on the first excursion probability are examined. When the tolerance level is normalized by the maximum response of the secondary system without impact or friction characteristics, variation of the first excursion probability is very small for various values of the natural period. In order to examine the effectiveness of the proposed method, the obtained results are compared with those obtained by the simulation method. Some estimation methods for the maximum response of the secondary system with nonlinear characteristics have been developed. (author)
Directory of Open Access Journals (Sweden)
Md Shafiul Alam
2017-11-01
Full Text Available This paper proposes the use of bridge type fault current limiters (BFCLs as a potential solution to reduce the impact of fault disturbance on voltage source converter-based high voltage DC (VSC-HVDC systems. Since VSC-HVDC systems are vulnerable to faults, it is essential to enhance the fault ride-through (FRT capability with auxiliary control devices like BFCLs. BFCL controllers have been developed to limit the fault current during the inception of system disturbances. Real and reactive power controllers for the VSC-HVDC have been developed based on current control mode. DC link voltage control has been achieved by a feedback mechanism such that net power exchange with DC link capacitor is zero. A grid-connected VSC-HVDC system and a wind farm integrated VSC-HVDC system along with the proposed BFCL and associated controllers have been implemented in a real time digital simulator (RTDS. Symmetrical three phase as well as different types of unsymmetrical faults have been applied in the systems in order to show the effectiveness of the proposed BFCL solution. DC link voltage fluctuation, machine speed and active power oscillation have been greatly suppressed with the proposed BFCL. Another significant feature of this work is that the performance of the proposed BFCL in VSC-HVDC systems is compared to that of series dynamic braking resistor (SDBR. Comparative results show that the proposed BFCL is superior over SDBR in limiting fault current as well as improving system fault ride through (FRT capability.
Voltage regulator for generator
Energy Technology Data Exchange (ETDEWEB)
Naoi, K
1989-01-17
It is an object of this invention to provide a voltage regulator for a generator charging a battery, wherein even if the ambient temperature at the voltage regulator rises abnormally high, possible thermal breakage of the semiconductor elements constituting the voltage regulator can be avoided. A feature of this invention is that the semiconductor elements can be protected from thermal breakage, even at an abnormal ambient temperature rise at the voltage regulator for the battery charging generator, by controlling a maximum conduction ratio of a power transistor in the voltage regulator in accordance with the temperature at the voltage regulator. This is achieved through a switching device connected in series to the field coil of the generator and adapted to be controlled in accordance with an output voltage of the generator and the ambient temperature at the voltage regulator. 6 figs.
CAMAC system for data acquisition on output of digital panel meter for DC voltage measurement
International Nuclear Information System (INIS)
Noda, Nobuaki.
1979-03-01
An interface between the digital panel meter (DPM) for DC voltage measurement and the CAMAC system for T-2 experiment in JIPP (Japan Institute of Plasma Physics) was designed and produced. This panel meter is used for the purpose of monitoring the deflected electrode voltage of a 6 channel, neutral particle, energy analyzer (parallel plate electrodes, electro static type). The method of connecting the DPM to the CAMAC system is that of taking the gate pulses with the width proportional to the voltage to be measured out of the output of the DPM and counting the clock pulses. This system uses each one channel of output register, interrupting register, scaler and clock generator, and the binary digital data is obtained in the scaler, and sent to the main memory of the computer HITAC 10-2 through the CAMAC crate controller. At this time, the interface gives the output of the gate pulses with the width proportional to the DPM input voltage from the DPM BUSY output and PRINT COMMAND output, depending on the sampling pulses from the output register. The interface also gives the end pulse communicating the completion of the output of gate pulses to the interrupting register. The software is summarized in the flow chart of the program and in the program list used for the test on this data acquisition system. The features of this system are to be able to obtain the binary data directly, and to be capable of saving the number of transmission lines required for data transfer. (Wakatsuki, Y.)
Dynamics and Collapse in a Power System Model with Voltage Variation: The Damping Effect.
Ma, Jinpeng; Sun, Yong; Yuan, Xiaoming; Kurths, Jürgen; Zhan, Meng
2016-01-01
Complex nonlinear phenomena are investigated in a basic power system model of the single-machine-infinite-bus (SMIB) with a synchronous generator modeled by a classical third-order differential equation including both angle dynamics and voltage dynamics, the so-called flux decay equation. In contrast, for the second-order differential equation considering the angle dynamics only, it is the classical swing equation. Similarities and differences of the dynamics generated between the third-order model and the second-order one are studied. We mainly find that, for positive damping, these two models show quite similar behavior, namely, stable fixed point, stable limit cycle, and their coexistence for different parameters. However, for negative damping, the second-order system can only collapse, whereas for the third-order model, more complicated behavior may happen, such as stable fixed point, limit cycle, quasi-periodicity, and chaos. Interesting partial collapse phenomena for angle instability only and not for voltage instability are also found here, including collapse from quasi-periodicity and from chaos etc. These findings not only provide a basic physical picture for power system dynamics in the third-order model incorporating voltage dynamics, but also enable us a deeper understanding of the complex dynamical behavior and even leading to a design of oscillation damping in electric power systems.
Coordinated Control Strategies of VSC-HVDC-Based Wind Power Systems for Low Voltage Ride Through
Directory of Open Access Journals (Sweden)
Xinyin Zhang
2015-07-01
Full Text Available The Voltage Source Converter-HVDC (VSC-HVDC system applied to wind power generation can solve large scale wind farm grid-connection and long distance transmission problems. However, the low voltage ride through (LVRT of the VSC-HVDC connected wind farm is a key technology issue that must be solved, and it is currently lacking an economic and effective solution. In this paper, a LVRT coordinated control strategy is proposed for the VSC-HVDC-based wind power system. In this strategy, the operation and control of VSC-HVDC and wind farm during the grid fault period is improved. The VSC-HVDC system not only provides reactive power support to the grid, but also effectively maintains the power balance and DC voltage stability by reducing wind-farm power output, without increasing the equipment investment. Correspondingly, to eliminate the influence on permanent magnet synchronous generator (PMSG-based wind turbine (WT systems, a hierarchical control strategy is designed. The speed and validity of the proposed LVRT coordinated control strategy and hierarchical control strategy were verified by MATLAB/Simulink simulations.
Power converter with maximum power point tracking MPPT for small wind-electric pumping systems
International Nuclear Information System (INIS)
Lara, David; Merino, Gabriel; Salazar, Lautaro
2015-01-01
Highlights: • We implement a wind electric pumping system of small power. • The power converter allowed to change the operating point of the electro pump. • Two control techniques were implemented in the power converter. • The control V/f variable allowed to increase the power generated by the permanent magnet generator. - Abstract: In this work, an AC–DC–AC direct-drive power converter was implemented for a wind electric pumping system consisting of a permanent magnet generator (PMG) of 1.3 kW and a peripheral single phase pump of 0.74 kW. In addition, the inverter linear V/f control scheme and the maximum power point tracking (MPPT) algorithm with variable V/f were developed. MPPT algorithm seeks to extract water in a wide range of power input using the maximum amount of wind power available. Experimental trials at different pump pressures were conducted. With a MPPT tracking system with variable V/f, a power value of 1.3 kW was obtained at a speed of 350 rpm and a maximum operating hydraulic head of 50 m. At lower operating heads pressures (between 10 and 40 m), variable V/f control increases the power generated by the PMG compared to the linear V/f control. This increase ranged between 4% and 23% depending on the operating pressure, with an average of 13%, getting close to the maximum electrical power curve of the PMG. The pump was driven at variable frequency reaching a minimum speed of 0.5 times the rated speed. Efficiency of the power converter ranges between 70% and 95% with a power factor between 0.4 and 0.85, depending on the operating pressure
The high-voltage system for the LHCb RICH hybrid photon detectors
International Nuclear Information System (INIS)
Arnaboldi, C.; Bellunato, T.; De Lucia, A.; Fanchini, E.; Perego, D.L.; Pessina, G.
2009-01-01
We describe the characterization of the high-voltage (HV) distribution system designed and produced for the pixel hybrid photon detectors of the ring imaging Cherenkov counters of the LHCb experiment. The HV system consists of a series of printed circuit boards with a specific layout designed to prevent any discharge arising from high electric fields. The system has dedicated monitoring and control features to supervise HV set-up during data taking. The full production of the HV system has been now completed and all the boards have been fully characterized and installed in the detector, which is currently being commissioned.
Maximum power point tracking controller for PV systems using neural networks
Energy Technology Data Exchange (ETDEWEB)
Bahgat, A.B.G. [Cairo Univ. (Egypt). Faculty of Engineering; Helwa, N.H.; Ahmad, G.E.; El Shenawy, E.T. [National Research Center, Dokki, Cairo (Egypt). Solar Energy Dept.
2005-07-01
This paper presents a development and implementation of a PC-based maximum power point tracker (MPPT) for PV system using neural networks (NN). The system consists of a PV module via a MPPT supplying a dc motor that drives an air fan. The control algorithm is developed to use the artificial NN for detecting the optimal operating point under different operating conditions, then the control action gives the driving signals to the MPPT. A PC is used for data acquisition, running the control algorithm, data storage, as well as data display and analysis. The system has been implemented and tested under various operating conditions. The experimental results showed that the PV system with MPPT always tracks the peak power point of the PV module under various operating conditions. The MPPT transmits about 97% of the actual maximum power generated by the PV module. The MPPT not only increases the power from the PV module to the load, but also maintains longer operating periods for the PV system. The air velocity and the air mass flow rate of the mechanical load are increased considerably, due to the increase of the PV system power. It is also found that the increase in the output energy due to using the MPPT is about 45.2% for a clear sunny day. (Author)
International Nuclear Information System (INIS)
Arfaoui, S.
2011-10-01
The main goals of the ATLAS scientific programme are the observation or exclusion of physics beyond the Standard Model (SM), as well as the measurement of production cross-sections of SM processes. In order to do so, it is important to measure the luminosity at the interaction point with great precision. The ATLAS luminosity is extracted using several detectors with varying efficiencies and acceptances. Different methods, such as inclusive - or coincidence - event counting and calorimeter integrated current measurements, are calibrated and cross-compared to provide the most accurate luminosity determination. In order to provide more cross-checks and a better control on the systematic uncertainties, an independent measurement using the liquid argon (LAr) forward calorimeter (FCal), based on the readout current of its high-voltage system, has been developed. This document describes how the LAr calorimeter high-voltage system has been installed and commissioned, as well as its application to a relative luminosity determination. (author)
The Architecture Design of Detection and Calibration System for High-voltage Electrical Equipment
Ma, Y.; Lin, Y.; Yang, Y.; Gu, Ch; Yang, F.; Zou, L. D.
2018-01-01
With the construction of Material Quality Inspection Center of Shandong electric power company, Electric Power Research Institute takes on more jobs on quality analysis and laboratory calibration for high-voltage electrical equipment, and informationization construction becomes urgent. In the paper we design a consolidated system, which implements the electronic management and online automation process for material sampling, test apparatus detection and field test. In the three jobs we use QR code scanning, online Word editing and electronic signature. These techniques simplify the complex process of warehouse management and testing report transferring, and largely reduce the manual procedure. The construction of the standardized detection information platform realizes the integrated management of high-voltage electrical equipment from their networking, running to periodic detection. According to system operation evaluation, the speed of transferring report is doubled, and querying data is also easier and faster.
Arfaoui, Samir; Monnier, E
2011-01-01
The main goals of the ATLAS scientific programme are the observation or exclusion of physics beyond the Standard Model (SM), as well as the measurement of production cross-sections of SM processes. In oder to do so,it is important to measure the luminosity at the interaction point with great precision. The ATLAS luminosity is extracted using several detectors with varying efficiencies and acceptances. Different methods, such as inclusive - or coincidence - event counting and calorimeter integrated current measurements, are calibrated and cross-compared to provide the most accurate luminosity determination. In order to provide more cross-checks and a better control on the systematic uncertainties, an independent measurement using the liquid argon (LAr) forward calorimeter (FCal), based on the readout current of its high-voltage system, has been developed. This document describes how the LAr calorimeter high-voltage system has been installed and commissioned, as well as its application to a relative luminosity ...
Distribution and function of voltage-gated sodium channels in the nervous system.
Wang, Jun; Ou, Shao-Wu; Wang, Yun-Jie
2017-11-02
Voltage-gated sodium channels (VGSCs) are the basic ion channels for neuronal excitability, which are crucial for the resting potential and the generation and propagation of action potentials in neurons. To date, at least nine distinct sodium channel isoforms have been detected in the nervous system. Recent studies have identified that voltage-gated sodium channels not only play an essential role in the normal electrophysiological activities of neurons but also have a close relationship with neurological diseases. In this study, the latest research findings regarding the structure, type, distribution, and function of VGSCs in the nervous system and their relationship to neurological diseases, such as epilepsy, neuropathic pain, brain tumors, neural trauma, and multiple sclerosis, are reviewed in detail.
Power-supply system for high-voltage electron guns with grid control
International Nuclear Information System (INIS)
Grigorev, Y.V.
1985-01-01
A power-supply system for electron guns with grid control is described which consists of a source of accelerating voltage between 20 and 180 kV with a current of 100 mA and a control circuit for an electron gun that contains a pulse generator having an output voltage of up to 5 kV for pulse durations of 2, 10, 50 and 90 microseconds. The output pulses of the generator are synchronized with a certain phase of the cathode heater current of the gun, and they can be repeated at a frequency between 100 and 0.4 Hz. The system is reliable and resistant to the overloads associated with breakdowns in the gun
Energy Technology Data Exchange (ETDEWEB)
Thiery, Matthias; Schwarz, Stefan [Siemens AG, Mannheim (Germany); Wingerter, Dieter [BASF SE, Ludwigshafen (Germany); Doering, Holger [B. Goebel und Sohn GmbH, Asschaffenburg (Germany). Fahrzeugbau
2011-02-28
BASF SE Ludwigshafen operates more than 100 medium-voltage switching stations for power supply to its plants. The complexity of the production plants and production method make it necessary to have immediate standby power supply in case of interruption of a medium-voltage switching station. For this purpose, a transportable emergency container was acquired that contains a medium-voltage switching system. Power can be supplied at very short notice, simply by plugging the necessary cable connections. No cranes or other tools are required for installation. The emergency container is designed for use at varying voltage levels and can be transported by road to other BASF sites in Europe. The switching station is a gas-insulated medium-voltage switching station 8DA10 by Siemens, designed for operating voltages of 6, 10, 20, and 35 kW.
Directory of Open Access Journals (Sweden)
Axel Kleidon
2010-03-01
Full Text Available The Maximum Entropy Production (MEP principle has been remarkably successful in producing accurate predictions for non-equilibrium states. We argue that this is because the MEP principle is an effective inference procedure that produces the best predictions from the available information. Since all Earth system processes are subject to the conservation of energy, mass and momentum, we argue that in practical terms the MEP principle should be applied to Earth system processes in terms of the already established framework of non-equilibrium thermodynamics, with the assumption of local thermodynamic equilibrium at the appropriate scales.
Maximum power point tracking techniques for wind energy systems using three levels boost converter
Tran, Cuong Hung; Nollet, Frédéric; Essounbouli, Najib; Hamzaoui, Abdelaziz
2018-05-01
This paper presents modeling and simulation of three level Boost DC-DC converter in Wind Energy Conversion System (WECS). Three-level Boost converter has significant advantage compared to conventional Boost. A maximum power point tracking (MPPT) method for a variable speed wind turbine using permanent magnet synchronous generator (PMSG) is also presented. Simulation of three-level Boost converter topology with Perturb and Observe algorithm and Fuzzy Logic Control is implemented in MATLAB/SIMULINK. Results of this simulation show that the system with MPPT using fuzzy logic controller has better performance to the Perturb and Observe algorithm: fast response under changing conditions and small oscillation.
Appelbaum, J.; Singer, S.
1989-01-01
A calculation of the starting torque ratio of permanent magnet, series, and shunt-excited dc motors powered by solar cell arrays is presented for two cases, i.e., with and without a maximum-power-point tracker (MPPT). Defining motor torque magnification by the ratio of the motor torque with an MPPT to the motor torque without an MPPT, a magnification of 3 for the permanent magnet motor and a magnification of 7 for both the series and shunt motors are obtained. The study also shows that all motor types are less sensitive to solar insolation variation in systems including MPPTs as compared to systems without MPPTs.
Maximum principle for a stochastic delayed system involving terminal state constraints.
Wen, Jiaqiang; Shi, Yufeng
2017-01-01
We investigate a stochastic optimal control problem where the controlled system is depicted as a stochastic differential delayed equation; however, at the terminal time, the state is constrained in a convex set. We firstly introduce an equivalent backward delayed system depicted as a time-delayed backward stochastic differential equation. Then a stochastic maximum principle is obtained by virtue of Ekeland's variational principle. Finally, applications to a state constrained stochastic delayed linear-quadratic control model and a production-consumption choice problem are studied to illustrate the main obtained result.
Lu, Dong-dong; Gu, Jin-liang; Luo, Hong-e.; Xia, Yan
2017-10-01
According to specific requirements of the X-ray machine system for measuring velocity of outfield projectile, a DC high voltage power supply system is designed for the high voltage or the smaller current. The system comprises: a series resonant circuit is selected as a full-bridge inverter circuit; a high-frequency zero-current soft switching of a high-voltage power supply is realized by PWM output by STM32; a nanocrystalline alloy transformer is chosen as a high-frequency booster transformer; and the related parameters of an LCC series-parallel resonant are determined according to the preset parameters of the transformer. The concrete method includes: a LCC series parallel resonant circuit and a voltage doubling circuit are stimulated by using MULTISM and MATLAB; selecting an optimal solution and an optimal parameter of all parts after stimulation analysis; and finally verifying the correctness of the parameter by stimulation of the whole system. Through stimulation analysis, the output voltage of the series-parallel resonant circuit gets to 10KV in 28s: then passing through the voltage doubling circuit, the output voltage gets to 120KV in one hour. According to the system, the wave range of the output voltage is so small as to provide the stable X-ray supply for the X-ray machine for measuring velocity of outfield projectile. It is fast in charging and high in efficiency.
Voltage controlled nano-injection system for single-cell surgery
Seger, R. Adam; Actis, Paolo; Penfold, Catherine; Maalouf, Michelle; Vilozny, Boaz; Pourmand, Nader
2015-01-01
Manipulation and analysis of single cells is the next frontier in understanding processes that control the function and fate of cells. Herein we describe a single-cell injection platform based on nanopipettes. The system uses scanning microscopy techniques to detect cell surfaces, and voltage pulses to deliver molecules into individual cells. As a proof of concept, we injected adherent mammalian cells with fluorescent dyes. PMID:22899383
Electron beam producing system for very high acceleration voltages and beam powers
International Nuclear Information System (INIS)
Andelfinger, C.; Dommaschk, W.; Ott, W.; Ulrich, M.; Weber, G.
1975-01-01
An electron beam producing system for acceleration voltages on the order of megavolts and beam powers on the order of gigawatts is described. A tubular housing of insulating material is used, and adjacent to its one closed end, a field emission cathode with a large surface area is arranged, while at its other end, from which the electron beam emerges, an annular anode is arranged. The device for collimating the electron beam consists of annular electrodes. (auth)
Determination of the wind power systems load to achieve operation in the maximum energy area
Chioncel, C. P.; Tirian, G. O.; Spunei, E.; Gillich, N.
2018-01-01
This paper analyses the operation of the wind turbine, WT, in the maximum power point, MPP, by linking the load of the Permanent Magnet Synchronous Generator, PMSG, with the wind speed value. The load control methods at wind power systems aiming an optimum performance in terms of energy are based on the fact that the energy captured by the wind turbine significantly depends on the mechanical angular speed of the wind turbine. The presented control method consists in determining the optimal mechanical angular speed, ωOPTIM, using an auxiliary low power wind turbine, WTAUX, operating without load, at maximum angular velocity, ωMAX. The method relies on the fact that the ratio ωOPTIM/ωMAX has a constant value for a given wind turbine and does not depend on the time variation of the wind speed values.
An improved maximum power point tracking method for a photovoltaic system
Ouoba, David; Fakkar, Abderrahim; El Kouari, Youssef; Dkhichi, Fayrouz; Oukarfi, Benyounes
2016-06-01
In this paper, an improved auto-scaling variable step-size Maximum Power Point Tracking (MPPT) method for photovoltaic (PV) system was proposed. To achieve simultaneously a fast dynamic response and stable steady-state power, a first improvement was made on the step-size scaling function of the duty cycle that controls the converter. An algorithm was secondly proposed to address wrong decision that may be made at an abrupt change of the irradiation. The proposed auto-scaling variable step-size approach was compared to some various other approaches from the literature such as: classical fixed step-size, variable step-size and a recent auto-scaling variable step-size maximum power point tracking approaches. The simulation results obtained by MATLAB/SIMULINK were given and discussed for validation.
Sliding-Mode Controller for Maximum Power Point Tracking in Grid-Connected Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Paula Andrea Ortiz Valencia
2015-11-01
Full Text Available The maximum power point tracking (MPPT of photovoltaic systems must be as fast and accurate as possible to increase the power production, which eventually increases the PV system profitability. This paper proposes and mathematically analyses a sliding-mode controller to provide a fast and accurate maximum power point tracking in grid-connected photovoltaic systems using a single control stage. This approach avoids the circular dependency in the design of classical cascade controllers used to optimize the photovoltaic system operation, and at the same time, it reduces the number of controllers and avoids the use of linearized models to provide global stability in all the operation range. Such a compact solution also reduces the system cost and implementation complexity. To ensure the stability of the proposed solution, detailed mathematical analyses are performed to demonstrate the fulfillment of the transversality, reachability and equivalent control conditions. Finally, the performance of the proposed solution is validated using detailed simulations, executed in the power electronics simulator PSIM, accounting for both environmental and load perturbations.
Thurner, Stefan; Corominas-Murtra, Bernat; Hanel, Rudolf
2017-09-01
There are at least three distinct ways to conceptualize entropy: entropy as an extensive thermodynamic quantity of physical systems (Clausius, Boltzmann, Gibbs), entropy as a measure for information production of ergodic sources (Shannon), and entropy as a means for statistical inference on multinomial processes (Jaynes maximum entropy principle). Even though these notions represent fundamentally different concepts, the functional form of the entropy for thermodynamic systems in equilibrium, for ergodic sources in information theory, and for independent sampling processes in statistical systems, is degenerate, H (p ) =-∑ipilogpi . For many complex systems, which are typically history-dependent, nonergodic, and nonmultinomial, this is no longer the case. Here we show that for such processes, the three entropy concepts lead to different functional forms of entropy, which we will refer to as SEXT for extensive entropy, SIT for the source information rate in information theory, and SMEP for the entropy functional that appears in the so-called maximum entropy principle, which characterizes the most likely observable distribution functions of a system. We explicitly compute these three entropy functionals for three concrete examples: for Pólya urn processes, which are simple self-reinforcing processes, for sample-space-reducing (SSR) processes, which are simple history dependent processes that are associated with power-law statistics, and finally for multinomial mixture processes.
Directory of Open Access Journals (Sweden)
Liran Li
2016-06-01
Full Text Available Due to its fast charge and discharge rate, a supercapacitor-based energy storage system is especially suitable for power smoothing in renewable energy generation applications. Voltage equalization is essential for series-connected supercapacitors in an energy storage system, because it supports the system’s sustainability and maximizes the available cell energy. In this paper, we present a high-efficiency voltage equalization scheme for supercapacitor energy storage systems in renewable generation applications. We propose an improved isolated converter topology that uses a multi-winding transformer. An improved push-pull forward circuit is applied on the primary side of the transformer. A coupling inductor is added on the primary side to allow the switches to operate under the zero-voltage switching (ZVS condition, which reduces switching losses. The diodes in the rectifier are replaced with metal-oxide-semiconductor field-effect transistors (MOSFETs to reduce the power dissipation of the secondary side. In order to simplify the control, we designed a controllable rectifying circuit to achieve synchronous rectifying on the secondary side of the transformer. The experimental results verified the effectiveness of the proposed design.
The Simulation Study of a Restructured Residential Low-Voltage Distribution System Microgrid
Directory of Open Access Journals (Sweden)
L. Ramesh
2016-12-01
Full Text Available A primary and necessary focus in creating a greener environment is the conversion of existing power-generation sources to renewable power sources in the near future. Another important focus is to develop sustainable household power generation to a low-voltage electricity grid with a power purchase and selling facility. To help with achieving the above vision, the objective of this work is to critically analyze the existing low-voltage distribution system and make suggestions for restructuring it to the low-voltage interconnected microgrid (MG. The test was carried out in the Tamil Nadu Electricity Board (TNEB 100kVA transformer feeder which was connected to supply around 100 houses with electricity. The performance analysis of the proposed system was examined through different case studies, represented as a normal operating condition of the existing distribution system and a reconstructed and interconnected MG to the TNEB grid. The project was designed and analyzed using PSCAD software. The results discussed in the project are helpful in examining the effects of multiple distributed energy resources on distributed generation. In future, knowledge of these effects may be helpful for rural area electrification.
DEFF Research Database (Denmark)
Blank, Tobias; Thomas, Stephan; Roggendorf, Christoph
2010-01-01
system efficiency. High voltage batteries may be advantageous for future medium voltage DC-grids as well. In all cases, high availability and reliability is indispensable. Investigations on the operating behavior of such systems are needed. For this purpose, a test bench for high voltage storage systems...... was built to analyze these processes for different battery technologies. A special safety infrastructure for the test bench was developed due to the high voltage and the storable energy of approximately 120 kWh. This paper presents the layout of the test bench for analyzing high voltage batteries with about...... 4,300 volts including all components, the safety requirements with the resultant safety circuit and the aim of the investigations to be performed with the test bench....
Directory of Open Access Journals (Sweden)
N.A. Kostin
2015-03-01
Full Text Available The paper proposes the non-canonical spectral decomposition of random functions of the traction voltages and currents. This decomposition is adapted for the electric transportation systems. The numerical representation is carried out for the random function of voltage on the pantograph of electric locomotives VL8 and DE1.
Energy storage and alternatives to improve train voltage on a mass transit system
Gordon, S. P.; Rorke, W. S.
1995-04-01
The wide separation of substations in the Bay Area Rapid Transit system's transbay tunnel contributes to voltage sag when power demand is high. In the future, expansions to the system will exacerbate this problem by increasing traffic density. Typically, this situation is remedied through the installation of additional substations to increase the system's power capacity. We have evaluated the efficacy of several alternatives to this approach - specifically, installation of an 8 megajoule energy storage system, modification of the existing substations, or reduction of the resistance of the running rails or the third rail. To support this analysis, we have developed a simple model of the traction power system in the tunnel. We have concluded that the storage system does not have sufficient capacity to deal with the expected voltage sags; in this application, the alternatives present more effective solutions. We have also investigated the potential impact of these system upgrades on expected future capital outlays by BART for traction power infrastructure additions. We have found that rail or substation upgrades may reduce the need for additional substations. These upgrades may also be effective on other parts of the BART system and on other traction power systems.
Radiation Damage Observations in the ATLAS Pixel Detector Using the High Voltage Delivery System
Toms, K
2011-01-01
We describe the implementation of radiation damage monitoring using leakage current measurement of the silicon pixel sensors provided by the circuits of the ATLAS Pixel Detector high voltage delivery (HVPP4) system. The dependence of the leakage current upon the integrated luminosity for several temperature scenarios is presented. Based on the analysis we have determined the sensitivity specifications for a Current Measurement System. The status of the system and the first measurement of the radiation damage corresponding to 2--4 fb$^{-1}$ of integrated luminosity are presented, as well as the comparison with the theoretical model.
Grid Voltage Synchronization for Distributed Generation Systems under Grid Fault Conditions
DEFF Research Database (Denmark)
Luna, Alvaro; Rocabert, J.; Candela, I.
2015-01-01
on the installation of STATCOMs and DVRs, as well as on advanced control functionalities for the existing power converters of distributed generation plants, have contributed to enhance their response under faulty and distorted scenarios and, hence, to fulfill these requirements. In order to achieve satisfactory......The actual grid code requirements for the grid connection of distributed generation systems, mainly wind and PV systems, are becoming very demanding. The Transmission System Operators (TSOs) are especially concerned about the Low Voltage Ride Through requirements. Solutions based...
Hanel, Rudolf; Thurner, Stefan; Gell-Mann, Murray
2014-05-13
The maximum entropy principle (MEP) is a method for obtaining the most likely distribution functions of observables from statistical systems by maximizing entropy under constraints. The MEP has found hundreds of applications in ergodic and Markovian systems in statistical mechanics, information theory, and statistics. For several decades there has been an ongoing controversy over whether the notion of the maximum entropy principle can be extended in a meaningful way to nonextensive, nonergodic, and complex statistical systems and processes. In this paper we start by reviewing how Boltzmann-Gibbs-Shannon entropy is related to multiplicities of independent random processes. We then show how the relaxation of independence naturally leads to the most general entropies that are compatible with the first three Shannon-Khinchin axioms, the (c,d)-entropies. We demonstrate that the MEP is a perfectly consistent concept for nonergodic and complex statistical systems if their relative entropy can be factored into a generalized multiplicity and a constraint term. The problem of finding such a factorization reduces to finding an appropriate representation of relative entropy in a linear basis. In a particular example we show that path-dependent random processes with memory naturally require specific generalized entropies. The example is to our knowledge the first exact derivation of a generalized entropy from the microscopic properties of a path-dependent random process.
Power system voltage stability and agent based distribution automation in smart grid
Nguyen, Cuong Phuc
2011-12-01
Our interconnected electric power system is presently facing many challenges that it was not originally designed and engineered to handle. The increased inter-area power transfers, aging infrastructure, and old technologies, have caused many problems including voltage instability, widespread blackouts, slow control response, among others. These problems have created an urgent need to transform the present electric power system to a highly stable, reliable, efficient, and self-healing electric power system of the future, which has been termed "smart grid". This dissertation begins with an investigation of voltage stability in bulk transmission networks. A new continuation power flow tool for studying the impacts of generator merit order based dispatch on inter-area transfer capability and static voltage stability is presented. The load demands are represented by lumped load models on the transmission system. While this representation is acceptable in traditional power system analysis, it may not be valid in the future smart grid where the distribution system will be integrated with intelligent and quick control capabilities to mitigate voltage problems before they propagate into the entire system. Therefore, before analyzing the operation of the whole smart grid, it is important to understand the distribution system first. The second part of this dissertation presents a new platform for studying and testing emerging technologies in advanced Distribution Automation (DA) within smart grids. Due to the key benefits over the traditional centralized approach, namely flexible deployment, scalability, and avoidance of single-point-of-failure, a new distributed approach is employed to design and develop all elements of the platform. A multi-agent system (MAS), which has the three key characteristics of autonomy, local view, and decentralization, is selected to implement the advanced DA functions. The intelligent agents utilize a communication network for cooperation and
Performance of the TJ-II ECRH system with the new -80 kV 50 A high voltage power supply
International Nuclear Information System (INIS)
Fernandez, A.; de la Fuente, J.M.; Ganuza, D.; Kirpitchev, I.; Alonso, J.; Garcia, F.; Ascasibar, E.; del Rio, J.M.; Garcia, I.; Ros, A.; Alvarez, P.; Tolkachev, A.; Catalan, G.
2009-01-01
The ECRH system of the TJ-II stellarator consists of two triode - 53.2 GHz - gyrotrons, which can deliver a maximum power of 300 kW each, during 1 s. Both gyrotrons are fed by a common high voltage power supply (HVPS). During the last experimental campaigns the performance of the gyrotrons were limited by the HVPS, whose maximum output current was limited to 30 A and the ripple level of the output voltage was around 7%. In order to guarantee the reliability of the ECRH system and to improve its performance, a new HVPS has been developed and manufactured by the company JEMA and was commissioned at CIEMAT during 2007. The design is based on solid-state technology and high frequency commutation techniques. The new unit reaches -80 kV and 50 A during a maximum pulse length of 1 s. The complete design, testing and commissioning of the HVPS are presented, as well as the routine operation of the ECRH system during the TJ-II experimental campaign.
Performance of the TJ-II ECRH system with the new -80 kV 50 A high voltage power supply
Energy Technology Data Exchange (ETDEWEB)
Fernandez, A. [Laboratorio Nacional de Fusion, EURATOM-CIEMAT Association, Avda. Complutense 22, 28040 Madrid (Spain)], E-mail: angela.curto@ciemat.es; de la Fuente, J.M.; Ganuza, D. [Grupo JEMA, Paseo del Circuito 10, 20160 Lasarte-Oria (Spain); Kirpitchev, I.; Alonso, J. [Laboratorio Nacional de Fusion, EURATOM-CIEMAT Association, Avda. Complutense 22, 28040 Madrid (Spain); Garcia, F. [Grupo JEMA, Paseo del Circuito 10, 20160 Lasarte-Oria (Spain); Ascasibar, E. [Laboratorio Nacional de Fusion, EURATOM-CIEMAT Association, Avda. Complutense 22, 28040 Madrid (Spain); del Rio, J.M.; Garcia, I. [Grupo JEMA, Paseo del Circuito 10, 20160 Lasarte-Oria (Spain); Ros, A.; Alvarez, P.; Tolkachev, A.; Catalan, G. [Laboratorio Nacional de Fusion, EURATOM-CIEMAT Association, Avda. Complutense 22, 28040 Madrid (Spain)
2009-06-15
The ECRH system of the TJ-II stellarator consists of two triode - 53.2 GHz - gyrotrons, which can deliver a maximum power of 300 kW each, during 1 s. Both gyrotrons are fed by a common high voltage power supply (HVPS). During the last experimental campaigns the performance of the gyrotrons were limited by the HVPS, whose maximum output current was limited to 30 A and the ripple level of the output voltage was around 7%. In order to guarantee the reliability of the ECRH system and to improve its performance, a new HVPS has been developed and manufactured by the company JEMA and was commissioned at CIEMAT during 2007. The design is based on solid-state technology and high frequency commutation techniques. The new unit reaches -80 kV and 50 A during a maximum pulse length of 1 s. The complete design, testing and commissioning of the HVPS are presented, as well as the routine operation of the ECRH system during the TJ-II experimental campaign.
Voltage Based Detection Method for High Impedance Fault in a Distribution System
Thomas, Mini Shaji; Bhaskar, Namrata; Prakash, Anupama
2016-09-01
High-impedance faults (HIFs) on distribution feeders cannot be detected by conventional protection schemes, as HIFs are characterized by their low fault current level and waveform distortion due to the nonlinearity of the ground return path. This paper proposes a method to identify the HIFs in distribution system and isolate the faulty section, to reduce downtime. This method is based on voltage measurements along the distribution feeder and utilizes the sequence components of the voltages. Three models of high impedance faults have been considered and source side and load side breaking of the conductor have been studied in this work to capture a wide range of scenarios. The effect of neutral grounding of the source side transformer is also accounted in this study. The results show that the algorithm detects the HIFs accurately and rapidly. Thus, the faulty section can be isolated and service can be restored to the rest of the consumers.
Energy Technology Data Exchange (ETDEWEB)
Barros, Paulo R.G.M. de; Oliveira Aires, Joao C. de; Nascimento, Anselmo R; Almeida, Antonio J.B. de [Light Servicos de Eletricidade SA, Rio de Janeiro, RJ (Brazil); Souza Pedroso, Alquindar de [Centro de Pesquisas de Energia Eletrica, Rio de Janeiro, RJ (Brazil)
1988-12-31
This paper presents the studies and solutions adopted by Light to mitigate the problems relative to the lack of power and voltage oscillation damping in the Rio de Janeiro area (Southeast Brazil) for the contingencies of South/Southeast interconnection loss and 500 kV transmission line loss. The characteristics of Light generating system, comprised of the Fontes Velha, Fontes Nova, Ilha dos Pombos, Nilo Pecanha, and Pereira Passos hydroelectric plants are shown. Excitation/Voltage regulation alternatives are also presented. The performance of proposed equipment is discussed based on some simulation analysis. Finally, some alternatives for improvement of Rio de Janeiro area dynamic performance are suggested. 4 refs., 3 tabs., 5 figs.
Pulok, Md Kamrul Hasan
Intelligent and effective monitoring of power system stability in control centers is one of the key issues in smart grid technology to prevent unwanted power system blackouts. Voltage stability analysis is one of the most important requirements for control center operation in smart grid era. With the advent of Phasor Measurement Unit (PMU) or Synchrophasor technology, real time monitoring of voltage stability of power system is now a reality. This work utilizes real-time PMU data to derive a voltage stability index to monitor the voltage stability related contingency situation in power systems. The developed tool uses PMU data to calculate voltage stability index that indicates relative closeness of the instability by producing numerical indices. The IEEE 39 bus, New England power system was modeled and run on a Real-time Digital Simulator that stream PMU data over the Internet using IEEE C37.118 protocol. A Phasor data concentrator (PDC) is setup that receives streaming PMU data and stores them in Microsoft SQL database server. Then the developed voltage stability monitoring (VSM) tool retrieves phasor measurement data from SQL server, performs real-time state estimation of the whole network, calculate voltage stability index, perform real-time ranking of most vulnerable transmission lines, and finally shows all the results in a graphical user interface. All these actions are done in near real-time. Control centers can easily monitor the systems condition by using this tool and can take precautionary actions if needed.
Dynamic characteristics of motor-gear system under load saltations and voltage transients
Bai, Wenyu; Qin, Datong; Wang, Yawen; Lim, Teik C.
2018-02-01
In this paper, a dynamic model of a motor-gear system is proposed. The model combines a nonlinear permeance network model (PNM) of a squirrel-cage induction motor and a coupled lateral-torsional dynamic model of a planetary geared rotor system. The external excitations including voltage transients and load saltations, as well as the internal excitations such as spatial effects, magnetic circuits topology and material nonlinearity in the motor, and time-varying mesh stiffness and damping in the planetary gear system are considered in the proposed model. Then, the simulation results are compared with those predicted by the electromechanical model containing a dynamic motor model with constant inductances. The comparison showed that the electromechanical system model with the PNM motor model yields more reasonable results than the electromechanical system model with the lumped-parameter electric machine. It is observed that electromechanical coupling effect can induce additional and severe gear vibrations. In addition, the external conditions, especially the voltage transients, will dramatically affect the dynamic characteristics of the electromechanical system. Finally, some suggestions are offered based on this analysis for improving the performance and reliability of the electromechanical system.
Energy Technology Data Exchange (ETDEWEB)
Larbes, C.; Ait Cheikh, S.M.; Obeidi, T.; Zerguerras, A. [Laboratoire des Dispositifs de Communication et de Conversion Photovoltaique, Departement d' Electronique, Ecole Nationale Polytechnique, 10, Avenue Hassen Badi, El Harrach, Alger 16200 (Algeria)
2009-10-15
This paper presents an intelligent control method for the maximum power point tracking (MPPT) of a photovoltaic system under variable temperature and irradiance conditions. First, for the purpose of comparison and because of its proven and good performances, the perturbation and observation (P and O) technique is briefly introduced. A fuzzy logic controller based MPPT (FLC) is then proposed which has shown better performances compared to the P and O MPPT based approach. The proposed FLC has been also improved using genetic algorithms (GA) for optimisation. Different development stages are presented and the optimized fuzzy logic MPPT controller (OFLC) is then simulated and evaluated, which has shown better performances. (author)
Maximum power point tracker for portable photovoltaic systems with resistive-like load
Energy Technology Data Exchange (ETDEWEB)
De Cesare, G.; Caputo, D.; Nascetti, A. [Department of Electronic Engineering, University of Rome La Sapienza via Eudossiana, 18 00184 Rome (Italy)
2006-08-15
In this work we report on the design and realization of a maximum power point tracking (MPPT) circuit suitable for low power, portable applications with resistive load. The design rules included cost, size and power efficiency considerations. A novel scheme for the implementation of the control loop of the MPPT circuit is proposed, combining good performance with compact design. The operation and performances were simulated at circuit schematic level with simulation program with integrated circuit emphasis (SPICE). The improved operation of a PV system using our MPPT circuit was demonstrated using a purely resistive load. (author)
Directory of Open Access Journals (Sweden)
Ssennoga Twaha
2017-12-01
Full Text Available This study proposes and implements maximum power Point Tracking (MPPT control on thermoelectric generation system using an extremum seeking control (ESC algorithm. The MPPT is applied to guarantee maximum power extraction from the TEG system. The work has been carried out through modelling of thermoelectric generator/dc-dc converter system using Matlab/Simulink. The effectiveness of ESC technique has been assessed by comparing the results with those of the Perturb and Observe (P&O MPPT method under the same operating conditions. Results indicate that ESC MPPT method extracts more power than the P&O technique, where the output power of ESC technique is higher than that of P&O by 0.47 W or 6.1% at a hot side temperature of 200 °C. It is also noted that the ESC MPPT based model is almost fourfold faster than the P&O method. This is attributed to smaller MPPT circuit of ESC compared to that of P&O, hence we conclude that the ESC MPPT method outperforms the P&O technique.
Photovoltaic System Modeling with Fuzzy Logic Based Maximum Power Point Tracking Algorithm
Directory of Open Access Journals (Sweden)
Hasan Mahamudul
2013-01-01
Full Text Available This paper represents a novel modeling technique of PV module with a fuzzy logic based MPPT algorithm and boost converter in Simulink environment. The prime contributions of this work are simplification of PV modeling technique and implementation of fuzzy based MPPT system to track maximum power efficiently. The main highlighted points of this paper are to demonstrate the precise control of the duty cycle with respect to various atmospheric conditions, illustration of PV characteristic curves, and operation analysis of the converter. The proposed system has been applied for three different PV modules SOLKAR 36 W, BP MSX 60 W, and KC85T 87 W. Finally the resultant data has been compared with the theoretical prediction and company specified value to ensure the validity of the system.
Overview of Maximum Power Point Tracking Techniques for Photovoltaic Energy Production Systems
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2017-01-01
production of PV sources, despite the stochastically varying solar irradiation and ambient temperature conditions. Thereby, the overall efficiency of the PV energy production system is increased. Numerous techniques have been presented during the last decades for implementing the MPPT process in a PV system......A substantial growth of the installed photovoltaic (PV) systems capacity has occurred around the world during the last decade, thus enhancing the availability of electric energy in an environmentally friendly way. The maximum power point tracking (MPPT) technique enables to maximize the energy....... This chapter provides an overview of the operating principles of these techniques, which are suited for either uniform or nonuniform solar irradiation conditions. The operational characteristics and implementation requirements of these MPPT methods are also analyzed in order to demonstrate their performance...
Solar Panel System for Street Light Using Maximum Power Point Tracking (MPPT Technique
Directory of Open Access Journals (Sweden)
Wiedjaja A.
2014-03-01
Full Text Available Solar energy is one form of the renewable energy which is very abundant in regions close to the equator. One application of solar energy is for street light. This research focuses on using the maximum power point tracking technique (MPPT, particularly the perturb and observe (P&O algorithm, to charge battery for street light system. The proposed charger circuit can achieve 20.73% higher power efficiency compared to that of non-MPPT charger. We also develop the LED driver circuit for the system which can achieve power efficiency up to 91.9% at a current of 1.06 A. The proposed street lightning system can be implemented with a relatively low cost for public areas.
Entropy-Based Voltage Fault Diagnosis of Battery Systems for Electric Vehicles
Directory of Open Access Journals (Sweden)
Peng Liu
2018-01-01
Full Text Available The battery is a key component and the major fault source in electric vehicles (EVs. Ensuring power battery safety is of great significance to make the diagnosis more effective and predict the occurrence of faults, for the power battery is one of the core technologies of EVs. This paper proposes a voltage fault diagnosis detection mechanism using entropy theory which is demonstrated in an EV with a multiple-cell battery system during an actual operation situation. The preliminary analysis, after collecting and preprocessing the typical data periods from Operation Service and Management Center for Electric Vehicle (OSMC-EV in Beijing, shows that overvoltage fault for Li-ion batteries cell can be observed from the voltage curves. To further locate abnormal cells and predict faults, an entropy weight method is established to calculate the objective weight, which reduces the subjectivity and improves the reliability. The result clearly identifies the abnormity of cell voltage. The proposed diagnostic model can be used for EV real-time diagnosis without laboratory testing methods. It is more effective than traditional methods based on contrastive analysis.
Directory of Open Access Journals (Sweden)
Andrés Peña Asensio
2018-02-01
Full Text Available This paper addresses the design and analysis of a voltage and frequency control (VFC strategy for full converter (FC-based wind energy conversion systems (WECSs and its applicability for the supply of an isolated load. When supplying an isolated load, the role of the back-to-back converters in the FC must change with respect to a grid-connected application. Voltage and frequency are established by the FC line side converter (LSC, while the generator side converter (GSC is responsible for maintaining constant voltage in the DC link. Thus, the roles of the converters in the WECS are inverted. Under such control strategies, the LSC will automatically supply the load power and hence, in order to maintain a stable operation of the WECS, the wind turbine (WT power must also be controlled in a load-following strategy. The proposed VFC is fully modelled and a stability analysis is performed. Then, the operation of the WECS under the proposed VFC is simulated and tested on a real-time test bench, demonstrating the performance of the VFC for the isolated operation of the WECS.
A Fiber-Optic Sensor for Acoustic Emission Detection in a High Voltage Cable System
Zhang, Tongzhi; Pang, Fufei; Liu, Huanhuan; Cheng, Jiajing; Lv, Longbao; Zhang, Xiaobei; Chen, Na; Wang, Tingyun
2016-01-01
We have proposed and demonstrated a Michelson interferometer-based fiber sensor for detecting acoustic emission generated from the partial discharge (PD) of the accessories of a high-voltage cable system. The developed sensor head is integrated with a compact and relatively high sensitivity cylindrical elastomer. Such a sensor has a broadband frequency response and a relatively high sensitivity in a harsh environment under a high-voltage electric field. The design and fabrication of the sensor head integrated with the cylindrical elastomer is described, and a series of experiments was conducted to evaluate the sensing performance. The experimental results demonstrate that the sensitivity of our developed sensor for acoustic detection of partial discharges is 1.7 rad/(m⋅Pa). A high frequency response up to 150 kHz is achieved. Moreover, the relatively high sensitivity for the detection of PD is verified in both the laboratory environment and gas insulated switchgear. The obtained results show the great potential application of a Michelson interferometer-based fiber sensor integrated with a cylindrical elastomer for in-situ monitoring high-voltage cable accessories for safety work. PMID:27916900
A Fiber-Optic Sensor for Acoustic Emission Detection in a High Voltage Cable System
Directory of Open Access Journals (Sweden)
Tongzhi Zhang
2016-11-01
Full Text Available We have proposed and demonstrated a Michelson interferometer-based fiber sensor for detecting acoustic emission generated from the partial discharge (PD of the accessories of a high-voltage cable system. The developed sensor head is integrated with a compact and relatively high sensitivity cylindrical elastomer. Such a sensor has a broadband frequency response and a relatively high sensitivity in a harsh environment under a high-voltage electric field. The design and fabrication of the sensor head integrated with the cylindrical elastomer is described, and a series of experiments was conducted to evaluate the sensing performance. The experimental results demonstrate that the sensitivity of our developed sensor for acoustic detection of partial discharges is 1.7 rad / ( m ⋅ Pa . A high frequency response up to 150 kHz is achieved. Moreover, the relatively high sensitivity for the detection of PD is verified in both the laboratory environment and gas insulated switchgear. The obtained results show the great potential application of a Michelson interferometer-based fiber sensor integrated with a cylindrical elastomer for in-situ monitoring high-voltage cable accessories for safety work.
The Design of Operational Amplifier for Low Voltage and Low Current Sound Energy Harvesting System
Fang, Liew Hui; Rahim, Rosemizi Bin Abd; Isa, Muzamir; Idris Syed Hassan, Syed; Ismail, Baharuddin Bin
2018-03-01
The objective of this paper is to design a combination of an operational amplifier (op-amp) with a rectifier used in an alternate current (ac) to direct current (dc) power conversion. The op-amp was designed to specifically work at low voltage and low current for a sound energy harvesting system. The goal of the op-amp design with adjustable gain was to control output voltage based on the objectives of the experiment conducted. The op-amp was designed for minimum power dissipation performance, with the means of increasing the output current when receiving a large amount of load. The harvesting circuits which designed further improved the power output efficiency by shortening the fully charged time needed by a supercapacitor bank. It can fulfil the long-time power demands for low power device. Typically, a small amount of energy sources were converted to electricity and stored in the supercapacitor bank, which was built by 10 pieces of capacitors with 0.22 F each, arranged in parallel connection. The highest capacitance was chosen based on the characteristic that have the longest discharging time to support the applications of a supercapacitor bank. Testing results show that the op-amp can boost the low input ac voltage (∼3.89 V) to high output dc voltage (5.0 V) with output current of 30 mA and stored the electrical energy in a big supercapacitor bank having a total of 2.2 F, effectively. The measured results agree well with the calculated results.
Principle of maximum Fisher information from Hardy's axioms applied to statistical systems.
Frieden, B Roy; Gatenby, Robert A
2013-10-01
Consider a finite-sized, multidimensional system in parameter state a. The system is either at statistical equilibrium or general nonequilibrium, and may obey either classical or quantum physics. L. Hardy's mathematical axioms provide a basis for the physics obeyed by any such system. One axiom is that the number N of distinguishable states a in the system obeys N=max. This assumes that N is known as deterministic prior knowledge. However, most observed systems suffer statistical fluctuations, for which N is therefore only known approximately. Then what happens if the scope of the axiom N=max is extended to include such observed systems? It is found that the state a of the system must obey a principle of maximum Fisher information, I=I(max). This is important because many physical laws have been derived, assuming as a working hypothesis that I=I(max). These derivations include uses of the principle of extreme physical information (EPI). Examples of such derivations were of the De Broglie wave hypothesis, quantum wave equations, Maxwell's equations, new laws of biology (e.g., of Coulomb force-directed cell development and of in situ cancer growth), and new laws of economic fluctuation and investment. That the principle I=I(max) itself derives from suitably extended Hardy axioms thereby eliminates its need to be assumed in these derivations. Thus, uses of I=I(max) and EPI express physics at its most fundamental level, its axiomatic basis in math.
International Nuclear Information System (INIS)
Hong, Chih-Ming; Chen, Chiung-Hsing; Tu, Chia-Sheng
2013-01-01
Highlights: ► This paper presents MPPT based control for optimal wind energy capture using RBFN. ► MPSO is adopted to adjust the learning rates to improve the learning capability. ► This technique can maintain the system stability and reach the desired performance. ► The EMF in the rotating reference frame is utilized in order to estimate speed. - Abstract: This paper presents maximum-power-point-tracking (MPPT) based control algorithms for optimal wind energy capture using radial basis function network (RBFN) and a proposed torque observer MPPT algorithm. The design of a high-performance on-line training RBFN using back-propagation learning algorithm with modified particle swarm optimization (MPSO) regulating controller for the sensorless control of a permanent magnet synchronous generator (PMSG). The MPSO is adopted in this study to adapt the learning rates in the back-propagation process of the RBFN to improve the learning capability. The PMSG is controlled by the loss-minimization control with MPPT below the base speed, which corresponds to low and high wind speed, and the maximum energy can be captured from the wind. Then the observed disturbance torque is feed-forward to increase the robustness of the PMSG system
A comparative study of the maximum power point tracking methods for PV systems
International Nuclear Information System (INIS)
Liu, Yali; Li, Ming; Ji, Xu; Luo, Xi; Wang, Meidi; Zhang, Ying
2014-01-01
Highlights: • An improved maximum power point tracking method for PV system was proposed. • Theoretical derivation procedure of the proposed method was provided. • Simulation models of MPPT trackers were established based on MATLAB/Simulink. • Experiments were conducted to verify the effectiveness of the proposed MPPT method. - Abstract: Maximum power point tracking (MPPT) algorithms play an important role in the optimization of the power and efficiency of a photovoltaic (PV) generation system. According to the contradiction of the classical Perturb and Observe (P and Oa) method between the corresponding speed and the tracking accuracy on steady-state, an improved P and O (P and Ob) method has been put forward in this paper by using the Atken interpolation algorithm. To validate the correctness and performance of the proposed method, simulation and experimental study have been implemented. Simulation models of classical P and Oa method and improved P and Ob method have been established by MATLAB/Simulink to analyze each technique under varying solar irradiation and temperature. The experimental results show that the tracking efficiency of P and Ob method is an average of 93% compared to 72% for P and Oa method, this conclusion basically agree with the simulation study. Finally, we proposed the applicable conditions and scope of these MPPT methods in the practical application
Directory of Open Access Journals (Sweden)
Hassibi Babak
2002-01-01
Full Text Available Multiple antenna systems are capable of providing high data rate transmissions over wireless channels. When the channels are dispersive, the signal at each receive antenna is a combination of both the current and past symbols sent from all transmit antennas corrupted by noise. The optimal receiver is a maximum-likelihood sequence detector and is often considered to be practically infeasible due to high computational complexity (exponential in number of antennas and channel memory. Therefore, in practice, one often settles for a less complex suboptimal receiver structure, typically with an equalizer meant to suppress both the intersymbol and interuser interference, followed by the decoder. We propose a sphere decoding for the sequence detection in multiple antenna communication systems over dispersive channels. The sphere decoding provides the maximum-likelihood estimate with computational complexity comparable to the standard space-time decision-feedback equalizing (DFE algorithms. The performance and complexity of the sphere decoding are compared with the DFE algorithm by means of simulations.
Hu, Chen; Chen, Mian-zhou; Li, Hong-bin; Zhang, Zhu; Jiao, Yang; Shao, Haiming
2018-05-01
Ordinarily electronic voltage transformers (EVTs) are calibrated off-line and the calibration procedure requires complex switching operations, which will influence the reliability of the power grid and induce large economic losses. To overcome this problem, this paper investigates a 110 kV on-site calibration system for EVTs, including a standard channel, a calibrated channel and a PC equipped with the LabView environment. The standard channel employs a standard capacitor and an analogue integrating circuit to reconstruct the primary voltage signal. Moreover, an adaptive full-phase discrete Fourier transform (DFT) algorithm is proposed to extract electrical parameters. The algorithm involves the process of extracting the frequency of the grid, adjusting the operation points, and calculating the results using DFT. In addition, an insulated automatic lifting device is designed to realize the live connection of the standard capacitor, which is driven by a wireless remote controller. A performance test of the capacitor verifies the accurateness of the standard capacitor. A system calibration test shows that the system ratio error is less than 0.04% and the phase error is below 2‧, which meets the requirement of the 0.2 accuracy class. Finally, the developed calibration system was used in a substation, and the field test data validates the availability of the system.
Okou, Francis A.; Akhrif, Ouassima; Dessaint, Louis A.; Bouchard, Derrick
2013-05-01
This papter introduces a decentralized multivariable robust adaptive voltage and frequency regulator to ensure the stability of large-scale interconnnected generators. Interconnection parameters (i.e. load, line and transormer parameters) are assumed to be unknown. The proposed design approach requires the reformulation of conventiaonal power system models into a multivariable model with generator terminal voltages as state variables, and excitation and turbine valve inputs as control signals. This model, while suitable for the application of modern control methods, introduces problems with regards to current design techniques for large-scale systems. Interconnection terms, which are treated as perturbations, do not meet the common matching condition assumption. A new adaptive method for a certain class of large-scale systems is therefore introduces that does not require the matching condition. The proposed controller consists of nonlinear inputs that cancel some nonlinearities of the model. Auxiliary controls with linear and nonlinear components are used to stabilize the system. They compensate unknown parametes of the model by updating both the nonlinear component gains and excitation parameters. The adaptation algorithms involve the sigma-modification approach for auxiliary control gains, and the projection approach for excitation parameters to prevent estimation drift. The computation of the matrix-gain of the controller linear component requires the resolution of an algebraic Riccati equation and helps to solve the perturbation-mismatching problem. A realistic power system is used to assess the proposed controller performance. The results show that both stability and transient performance are considerably improved following a severe contingency.
Energy Technology Data Exchange (ETDEWEB)
Pazos, Francisco Jose; Amantegui, Javier; Ferrandis, Francisco; Barona, Amaya [Iberdrola, Madrid (Spain)
2008-04-15
The voltage interruption due to mean voltage maneuverers normal operation produces a transient type which is converted in a overvoltage on the low voltage circuit. Nevertheless to be considered a normal phenomena those over voltages have been pointed out as cause for damage in electric home appliances. What are the reasons? Inadequate protection or lack of immunity of the equipment?.
DEFF Research Database (Denmark)
Wickramasinghe, Harith R.; Konstantinou, Georgios; Pou, Josep
2018-01-01
Estimation-based indirect dc-voltage control in MMCs interacts with circulating current control methods. This paper proposes an estimation-based indirect dc-voltage control method for MMC-HVDC systems and analyzes its performance compared to alternative estimations. The interactions between......-state and transient performance is demonstrated using a benchmark MMC-HVDC transmission system, implemented in a real-time digital simulator. The results verify the theoretical evaluations and illustrate the operation and performance of the proposed indirect dc-voltage control method....
National Research Council Canada - National Science Library
Swaminathan, Vishnu; Chakrabarty, Krishnendu
2005-01-01
We investigate the effect of voltage-switching on task execution times and energy consumption for dual-speed hard real-time systems, and present a new approach for scheduling workloads containing periodic tasks...
Directory of Open Access Journals (Sweden)
Hsueh-Hsien Chang
2017-04-01
Full Text Available This paper proposes statistical feature extraction methods combined with artificial intelligence (AI approaches for fault locations in non-intrusive single-line-to-ground fault (SLGF detection of low voltage distribution systems. The input features of the AI algorithms are extracted using statistical moment transformation for reducing the dimensions of the power signature inputs measured by using non-intrusive fault monitoring (NIFM techniques. The data required to develop the network are generated by simulating SLGF using the Electromagnetic Transient Program (EMTP in a test system. To enhance the identification accuracy, these features after normalization are given to AI algorithms for presenting and evaluating in this paper. Different AI techniques are then utilized to compare which identification algorithms are suitable to diagnose the SLGF for various power signatures in a NIFM system. The simulation results show that the proposed method is effective and can identify the fault locations by using non-intrusive monitoring techniques for low voltage distribution systems.
Directory of Open Access Journals (Sweden)
Neeraj Priyadarshi
2018-04-01
Full Text Available In this research paper, a hybrid Artificial Neural Network (ANN-Fuzzy Logic Control (FLC tuned Flower Pollination Algorithm (FPA as a Maximum Power Point Tracker (MPPT is employed to amend root mean square error (RMSE of photovoltaic (PV modeling. Moreover, Gaussian membership functions have been considered for fuzzy controller design. This paper interprets the Luo converter occupied brushless DC motor (BLDC-directed PV water pump application. Experimental responses certify the effectiveness of the suggested motor-pump system supporting diverse operating states. The Luo converter, a newly developed DC-DC converter, has high power density, better voltage gain transfer and superior output waveform and can track optimal power from PV modules. For BLDC speed control there is no extra circuitry, and phase current sensors are enforced for this scheme. The most recent attempt using adaptive neuro-fuzzy inference system (ANFIS-FPA-operated BLDC directed PV pump with advanced Luo converter, has not been formerly conferred.
Appelbaum, Joseph; Singer, S.
1989-01-01
Direct current (dc) motors are used in terrestrial photovoltaic (PV) systems such as in water-pumping systems for irrigation and water supply. Direct current motors may also be used for space applications. Simple and low weight systems including dc motors may be of special interest in space where the motors are directly coupled to the solar cell array (with no storage). The system will operate only during times when sufficient insolation is available. An important performance characteristic of electric motors is the starting to rated torque ratio. Different types of dc motors have different starting torque ratios. These ratios are dictated by the size of solar cell array, and the developed motor torque may not be sufficient to overcome the load starting torque. By including a maximum power point tracker (MPPT) in the PV system, the starting to rated torque ratio will increase, the amount of which depends on the motor type. The starting torque ratio is calculated for the permanent magnet, series and shunt excited dc motors when powered by solar cell arrays for two cases: with and without MPPT's. Defining a motor torque magnification by the ratio of the motor torque with an MPPT to the motor torque without an MPPT, a magnification of 3 was obtained for the permanent magnet motor and a magnification of 7 for both the series and shunt motors. The effect of the variation of solar insolation on the motor starting torque was covered. All motor types are less sensitive to insolation variation in systems including MPPT's as compared to systems with MPPT's. The analysis of this paper will assist the PV system designed to determine whether or not to include an MPPT in the system for a specific motor type.
Non-equilibrium thermodynamics, maximum entropy production and Earth-system evolution.
Kleidon, Axel
2010-01-13
The present-day atmosphere is in a unique state far from thermodynamic equilibrium. This uniqueness is for instance reflected in the high concentration of molecular oxygen and the low relative humidity in the atmosphere. Given that the concentration of atmospheric oxygen has likely increased throughout Earth-system history, we can ask whether this trend can be generalized to a trend of Earth-system evolution that is directed away from thermodynamic equilibrium, why we would expect such a trend to take place and what it would imply for Earth-system evolution as a whole. The justification for such a trend could be found in the proposed general principle of maximum entropy production (MEP), which states that non-equilibrium thermodynamic systems maintain steady states at which entropy production is maximized. Here, I justify and demonstrate this application of MEP to the Earth at the planetary scale. I first describe the non-equilibrium thermodynamic nature of Earth-system processes and distinguish processes that drive the system's state away from equilibrium from those that are directed towards equilibrium. I formulate the interactions among these processes from a thermodynamic perspective and then connect them to a holistic view of the planetary thermodynamic state of the Earth system. In conclusion, non-equilibrium thermodynamics and MEP have the potential to provide a simple and holistic theory of Earth-system functioning. This theory can be used to derive overall evolutionary trends of the Earth's past, identify the role that life plays in driving thermodynamic states far from equilibrium, identify habitability in other planetary environments and evaluate human impacts on Earth-system functioning. This journal is © 2010 The Royal Society
International Nuclear Information System (INIS)
Drevet, F.; Chadelas, R.; Montarou, G.
1996-01-01
We present here after a preliminary study on field buses for the control system of the high voltage of the photomultipliers of the TILECAL calorimeter. After some generalities, different commercial buses are reviewed (CAN, ARCET, WorldFIP, Profibus and LonWorks). The Profibus and LonWorks solution are more extensively studies as a possible solution for the high voltage system of the TILE hadronic calorimeter. (authors)
Efficient Photovoltaic System Maximum Power Point Tracking Using a New Technique
Directory of Open Access Journals (Sweden)
Mehdi Seyedmahmoudian
2016-03-01
Full Text Available Partial shading is an unavoidable condition which significantly reduces the efficiency and stability of a photovoltaic (PV system. When partial shading occurs the system has multiple-peak output power characteristics. In order to track the global maximum power point (GMPP within an appropriate period a reliable technique is required. Conventional techniques such as hill climbing and perturbation and observation (P&O are inadequate in tracking the GMPP subject to this condition resulting in a dramatic reduction in the efficiency of the PV system. Recent artificial intelligence methods have been proposed, however they have a higher computational cost, slower processing time and increased oscillations which results in further instability at the output of the PV system. This paper proposes a fast and efficient technique based on Radial Movement Optimization (RMO for detecting the GMPP under partial shading conditions. The paper begins with a brief description of the behavior of PV systems under partial shading conditions followed by the introduction of the new RMO-based technique for GMPP tracking. Finally, results are presented to demonstration the performance of the proposed technique under different partial shading conditions. The results are compared with those of the PSO method, one of the most widely used methods in the literature. Four factors, namely convergence speed, efficiency (power loss reduction, stability (oscillation reduction and computational cost, are considered in the comparison with the PSO technique.
Energy Technology Data Exchange (ETDEWEB)
Guzman, Eusebio; Mendoza, Victor X; Carrillo, Jose J . A; Galarza, Cristian [Universidad Autonoma Metropolitana, Mexico, D.F. (Mexico)
2000-07-01
A maximum power point tracker MPPT for photovoltaic systems is presented. The equipment can output up to 600 W and its control signals are generated by a PIC microcontroller. The principle of control is based on current and voltage sampling at the output terminals of the photovoltaic generator. From power comparison of two consecutive samples, it is possible to know how far from the optimal point the system is working. Output voltage control is used to force the system to work within the optimal area of operation. The microcontroller program sequence, the DC/DC converter structure and the most relevant results are shown. [Spanish] En este trabajo se presenta el desarrollo de un controlador de potencia maxima para su aplicacion en sistemas fotovoltaicos (SFVs). El diseno alcanza una potencia de 600 W y sus senales de control son generadas con un controlador PIC. El principio de control se basa en el muestreo de la corriente y la tension en las terminadas del generador fotovoltaico GFV. De dos muestreos consecutivos, y por comparacion de las potencias, se determina que tan alejado del punto optimo opera el sistema. La operacion del sistema dentro de la zona de funcionamiento optimo se asegura mediante un control por tension. Se muestra la secuencia de programacion del microcontrolador, la estructura del convertidor CD/CD empleado y algunos resultados relevantes.
Man, E. A.; Sera, D.; Mathe, L.; Schaltz, E.; Rosendahl, L.
2016-03-01
Characterization of thermoelectric generators (TEG) is widely discussed and equipment has been built that can perform such analysis. One method is often used to perform such characterization: constant temperature with variable thermal power input. Maximum power point tracking (MPPT) methods for TEG systems are mostly tested under steady-state conditions for different constant input temperatures. However, for most TEG applications, the input temperature gradient changes, exposing the MPPT to variable tracking conditions. An example is the exhaust pipe on hybrid vehicles, for which, because of the intermittent operation of the internal combustion engine, the TEG and its MPPT controller are exposed to a cyclic temperature profile. Furthermore, there are no guidelines on how fast the MPPT must be under such dynamic conditions. In the work discussed in this paper, temperature gradients for TEG integrated in several applications were evaluated; the results showed temperature variation up to 5°C/s for TEG systems. Electrical characterization of a calcium-manganese oxide TEG was performed at steady-state for different input temperatures and a maximum temperature of 401°C. By using electrical data from characterization of the oxide module, a solar array simulator was emulated to perform as a TEG. A trapezoidal temperature profile with different gradients was used on the TEG simulator to evaluate the dynamic MPPT efficiency. It is known that the perturb and observe (P&O) algorithm may have difficulty accurately tracking under rapidly changing conditions. To solve this problem, a compromise must be found between the magnitude of the increment and the sampling frequency of the control algorithm. The standard P&O performance was evaluated experimentally by using different temperature gradients for different MPPT sampling frequencies, and efficiency values are provided for all cases. The results showed that a tracking speed of 2.5 Hz can be successfully implemented on a TEG
Improving maximum power point tracking of partially shaded photovoltaic system by using IPSO-BELBIC
International Nuclear Information System (INIS)
El-Garhy, M. Abd Al-Alim; Mubarak, R.I.; El-Bably, M.
2017-01-01
Solar photovoltaic (PV) arrays in remote applications are often related to the rapid changes in the partial shading pattern. Rapid changes of the partial shading pattern make the tracking of maximum power point (MPP) of the global peak through the local ones too difficult. An essential need to make a fast and efficient algorithm to detect the peaks values which always vary as the sun irradiance changes. This paper presents two algorithms based on the improved particle swarm optimization technique one of them with PID controller (IPSO-PID), and the other one with Brain Emotional Learning Based Intelligent Controller (IPSO-BELBIC). These techniques improve the maximum power point (MPP) tracking capabilities for photovoltaic (PV) system under partial shading circumstances. The main aim of these improved algorithms is to accelerate the velocity of IPSO to reach to (MPP) and increase its efficiency. These algorithms also improve the tracking time under complex irradiance conditions. Based on these conditions, the tracking time of these presented techniques improves to 2 msec, with an efficiency of 100%.
Improving maximum power point tracking of partially shaded photovoltaic system by using IPSO-BELBIC
Al-Alim El-Garhy, M. Abd; Mubarak, R. I.; El-Bably, M.
2017-08-01
Solar photovoltaic (PV) arrays in remote applications are often related to the rapid changes in the partial shading pattern. Rapid changes of the partial shading pattern make the tracking of maximum power point (MPP) of the global peak through the local ones too difficult. An essential need to make a fast and efficient algorithm to detect the peaks values which always vary as the sun irradiance changes. This paper presents two algorithms based on the improved particle swarm optimization technique one of them with PID controller (IPSO-PID), and the other one with Brain Emotional Learning Based Intelligent Controller (IPSO-BELBIC). These techniques improve the maximum power point (MPP) tracking capabilities for photovoltaic (PV) system under partial shading circumstances. The main aim of these improved algorithms is to accelerate the velocity of IPSO to reach to (MPP) and increase its efficiency. These algorithms also improve the tracking time under complex irradiance conditions. Based on these conditions, the tracking time of these presented techniques improves to 2 msec, with an efficiency of 100%.
Perspective: Maximum caliber is a general variational principle for dynamical systems.
Dixit, Purushottam D; Wagoner, Jason; Weistuch, Corey; Pressé, Steve; Ghosh, Kingshuk; Dill, Ken A
2018-01-07
We review here Maximum Caliber (Max Cal), a general variational principle for inferring distributions of paths in dynamical processes and networks. Max Cal is to dynamical trajectories what the principle of maximum entropy is to equilibrium states or stationary populations. In Max Cal, you maximize a path entropy over all possible pathways, subject to dynamical constraints, in order to predict relative path weights. Many well-known relationships of non-equilibrium statistical physics-such as the Green-Kubo fluctuation-dissipation relations, Onsager's reciprocal relations, and Prigogine's minimum entropy production-are limited to near-equilibrium processes. Max Cal is more general. While it can readily derive these results under those limits, Max Cal is also applicable far from equilibrium. We give examples of Max Cal as a method of inference about trajectory distributions from limited data, finding reaction coordinates in bio-molecular simulations, and modeling the complex dynamics of non-thermal systems such as gene regulatory networks or the collective firing of neurons. We also survey its basis in principle and some limitations.
Perspective: Maximum caliber is a general variational principle for dynamical systems
Dixit, Purushottam D.; Wagoner, Jason; Weistuch, Corey; Pressé, Steve; Ghosh, Kingshuk; Dill, Ken A.
2018-01-01
We review here Maximum Caliber (Max Cal), a general variational principle for inferring distributions of paths in dynamical processes and networks. Max Cal is to dynamical trajectories what the principle of maximum entropy is to equilibrium states or stationary populations. In Max Cal, you maximize a path entropy over all possible pathways, subject to dynamical constraints, in order to predict relative path weights. Many well-known relationships of non-equilibrium statistical physics—such as the Green-Kubo fluctuation-dissipation relations, Onsager's reciprocal relations, and Prigogine's minimum entropy production—are limited to near-equilibrium processes. Max Cal is more general. While it can readily derive these results under those limits, Max Cal is also applicable far from equilibrium. We give examples of Max Cal as a method of inference about trajectory distributions from limited data, finding reaction coordinates in bio-molecular simulations, and modeling the complex dynamics of non-thermal systems such as gene regulatory networks or the collective firing of neurons. We also survey its basis in principle and some limitations.
International Nuclear Information System (INIS)
Fathabadi, Hassan
2016-01-01
Highlights: • Novel high accurate sensorless dual-axis solar tracker. • It has the advantages of both sensor based and sensorless solar trackers. • It does not have the disadvantages of sensor based and sensorless solar trackers. • Tracking error of only 0.11° that is less than the tracking errors of others. • An increase of 28.8–43.6% depending on the seasons in the energy efficiency. - Abstract: In this study, a novel high accurate sensorless dual-axis solar tracker controlled by the maximum power point tracking unit available in almost all photovoltaic systems is proposed. The maximum power point tracking controller continuously calculates the maximum output power of the photovoltaic module/panel/array, and uses the altitude and azimuth angles deviations to track the sun direction where the greatest value of the maximum output power is extracted. Unlike all other sensorless solar trackers, the proposed solar tracking system is a closed loop system which means it uses the actual direction of the sun at any time to track the sun direction, and this is the contribution of this work. The proposed solar tracker has the advantages of both sensor based and sensorless dual-axis solar trackers, but it does not have their disadvantages. Other sensorless solar trackers all are open loop, i.e., they use offline estimated data about the sun path in the sky obtained from solar map equations, so low exactness, cloudy sky, and requiring new data for new location are their problems. A photovoltaic system has been built, and it is experimentally verified that the proposed solar tracking system tracks the sun direction with the tracking error of 0.11° which is less than the tracking errors of other both sensor based and sensorless solar trackers. An increase of 28.8–43.6% depending on the seasons in the energy efficiency is the main advantage of utilizing the proposed solar tracking system.
DEFF Research Database (Denmark)
Liu, Yan; Chen, Zhe
2013-01-01
With increasing application of both Line Commutated Converter based High Voltage Direct Current (LCC-HVDC) systems and Voltage Source Converter based HVDC (VSC-HVDC) links, a new type of system structure named Hybrid Multi-Infeed HVDC (HMIDC) system is formed in the modern power systems. This paper...... presents the operation and control method of the wind farm connected HMIDC system. The wind power fluctuation takes large influence to the system voltages. In order to reduce the voltage fluctuation of LCC-HVDC infeed bus caused by the wind power variation, a voltage sensitivity-based reactive power...
International Nuclear Information System (INIS)
Sarizah Mohamed Nor; Siti Hawa Md Zain; Muhd Izham Ahmad; Izuhan Ismail
2010-01-01
Nuclear counter system is a system monitoring and analysis of radioactivity used in scientific and technical research and development in the Malaysian Nuclear Agency. It consists of three basic parts, namely sensors, signal conditioning and monitoring. Nuclear counter system set up for use in the testing of nuclear detectors using radioactive sources such as 60 Co and 137 Cs and other radioactive sources. It can determine the types of scintillation detectors and the equivalent function properly, always operate in the range plateau high voltage and meet the specifications. Hence, it should be implemented on all systems in the Nuclear Nuclear counter Malaysia and documented as Standard Working Procedure (SWP) is a reference to the technicians, trainees IPTA / IPTS and related workers. (author)
Detection of high-impedance fault in low-voltage DC distribution system via mathematical morphology
Directory of Open Access Journals (Sweden)
Yun-Sik Oh
2016-01-01
Full Text Available This study presents a method for high-impedance fault (HIF detection in a low-voltage DC (LVDC distribution system via mathematical morphology (MM, which is composed of two elementary transformations, namely, dilation and erosion. Various MM-based filters are used to detect abnormal signals of current waveform. The LVDC distribution system, including power conversion devices, such as AC/DC and DC/DC converters, is modelled with electromagnetic transient program (EMTP software to verify the proposed method. The HIF arc model in the DC system is also implemented with EMTP/MODELS, which is a symbolic language interpreter for EMTP. Simulation results show that the proposed method can be applied to detect HIF effectively in the LVDC distribution system.
Directory of Open Access Journals (Sweden)
Palukuru NAGENDRA
2010-12-01
Full Text Available In this study, the use of artificial neural network (ANN based model, multi-layer perceptron (MLP network, to compute the transfer capabilities in a multi-area power system was explored. The input for the ANN is load status and the outputs are the transfer capability among the system areas, voltage magnitudes and voltage angles at concerned buses of the areas under consideration. The repeated power flow (RPF method is used in this paper for calculating the power transfer capability, voltage magnitudes and voltage angles necessary for the generation of input-output patterns for training the proposed MLP neural network. Preliminary investigations on a three area 30-bus system reveal that the proposed model is computationally faster than the conventional method.
An integrated low-voltage rated HTS DC power system with multifunctions to suit smart grids
Energy Technology Data Exchange (ETDEWEB)
Jin, Jian Xun, E-mail: jxjin@uestc.edu.cn [Center of Applied Superconductivity, School of Electrical Engineering and Automation, Tianjin University, Tianjin 300072 (China); Center of Applied Superconductivity and Electrical Engineering, School of Automation Engineering, University of Electronic Science and Technology of China, Chengdu 611731 (China); Chen, Xiao Yuan [School of Engineering, Sichuan Normal University, Chengdu 610101 (China); Qu, Ronghai; Fang, Hai Yang [School of Electrical and Electronic Engineering, Huazhong University of Science and Technology, Wuhan 430074 (China); Xin, Ying [Center of Applied Superconductivity, School of Electrical Engineering and Automation, Tianjin University, Tianjin 300072 (China)
2015-03-15
Highlights: • A novel LVDC HTS power transmission network is presented. • An integrated power system is achieved by using HTS DC cable and SMES. • DC superconducting cable is verified to achieve self-acting fault current limitation. • SMES is verified to achieve fast-response buffering effect under a power fluctuation. • SMES is verified to achieve favorable load voltage protection effect under a fault. - Abstract: A low-voltage rated DC power transmission network integrated with superconducting cables (SCs) and superconducting magnetic energy storage (SMES) devices has been studied with analytic results presented. In addition to the properties of loss-less and high current transportation capacity, the effectively integrated system is formed with a self-acting fault current limitation feature of the SC and a buffering effect of the SMES to power fluctuations. The results obtained show that the integrated system can achieve high-quality power transmission under common power fluctuation conditions with an advanced self-protection feature under short circuit conditions, which is identified to suit especially the smart grid applications.
International Nuclear Information System (INIS)
Santos Coelho, Leandro dos
2009-01-01
Despite the popularity, the tuning aspect of proportional-integral-derivative (PID) controllers is a challenge for researchers and plant operators. Various controllers tuning methodologies have been proposed in the literature such as auto-tuning, self-tuning, pattern recognition, artificial intelligence, and optimization methods. Chaotic optimization algorithms as an emergent method of global optimization have attracted much attention in engineering applications. Chaotic optimization algorithms, which have the features of easy implementation, short execution time and robust mechanisms of escaping from local optimum, is a promising tool for engineering applications. In this paper, a tuning method for determining the parameters of PID control for an automatic regulator voltage (AVR) system using a chaotic optimization approach based on Lozi map is proposed. Since chaotic mapping enjoys certainty, ergodicity and the stochastic property, the proposed chaotic optimization introduces chaos mapping using Lozi map chaotic sequences which increases its convergence rate and resulting precision. Simulation results are promising and show the effectiveness of the proposed approach. Numerical simulations based on proposed PID control of an AVR system for nominal system parameters and step reference voltage input demonstrate the good performance of chaotic optimization.
Hybrid HVDC (H2VDC System Using Current and Voltage Source Converters
Directory of Open Access Journals (Sweden)
José Rafael Lebre
2018-05-01
Full Text Available This paper presents an analysis of a new high voltage DC (HVDC transmission system, which is based on current and voltage source converters (CSC and VSC in the same circuit. This proposed topology is composed of one CSC (rectifier and one or more VSCs (inverters connected through an overhead transmission line in a multiterminal configuration. The main purpose of this Hybrid HVDC (H2VDC, as it was designed, is putting together the best benefits of both types of converters in the same circuit: no commutation failure and system’s black start capability in the VSC side, high power converter capability and low cost at the rectifier side, etc. A monopole of the H2VDC system with one CSC and two VSCs—here, the VSC is the Modular Multilevel Converter (MMC considered with full-bridge submodules—in multiterminal configuration is studied. The study includes theoretical analyses, development of the CSC and VSCs control philosophies and simulations. The H2VDC system’s behavior is analyzed by computational simulations considering steady-state operation and short-circuit conditions at the AC and DC side. The obtained results and conclusions show a promising system for very high-power multiterminal HVDC transmission.
Dual-Axis Solar Tracking System for Maximum Power Production in PV Systems
Directory of Open Access Journals (Sweden)
Muhd.Ikram Mohd. Rashid
2015-12-01
Full Text Available The power developed in a solar energy system depends fundamentally upon the amount of sunlight captured by the photovoltaic modules/arrays. This paper describes a simple electro-mechanical dual axis solar tracking system designed and developed in a study. The control of the two axes was achieved by the pulses generated from the data acquisition (DAQ card fed into four relays. This approach was so chosen to effectively avoid the error that usually arises in sensor-based methods. The programming of the mathematical models of the solar elevation and azimuth angles was done using Borland C++ Builder. The performance and accuracy of the developed system was evaluated with a PV panel at latitude 3.53o N and longitude 103.5o W in Malaysia. The results obtained reflect the effectiveness of the developed tracking system in terms of the energy yield when compared with that generated from a fixed panel. Overall, 20%, 23% and 21% additional energy were produced for the months of March, April and May respectively using the tracker developed in this study.
Directory of Open Access Journals (Sweden)
Wei Wang
2012-05-01
Full Text Available This paper proposes a novel optimal current given (OCG maximum power point tracking (MPPT control strategy based on the theory of power feedback and hill climb searching (HCS for a permanent magnet direct drive wind energy conversion system (WECS. The presented strategy not only has the advantages of not needing the wind speed and wind turbine characteristics of the traditional HCS method, but it also improves the stability and accuracy of MPPT by estimating the exact loss torque. The OCG MPPT control strategy is first carried out by simulation, then an experimental platform based on the dSPACE1103 controller is built and a 5.5 kW permanent magnet synchronous generator (PMSG is tested. Furthermore, the proposed method is compared experimentally with the traditional optimum tip speed ratio (TSR MPPT control. The experiments verify the effectiveness of the proposed OCG MPPT strategy and demonstrate its better performance than the traditional TSR MPPT control.
Comparison of P&O and INC Methods in Maximum Power Point Tracker for PV Systems
Chen, Hesheng; Cui, Yuanhui; Zhao, Yue; Wang, Zhisen
2018-03-01
In the context of renewable energy, the maximum power point tracker (MPPT) is often used to increase the solar power efficiency, taking into account the randomness and volatility of solar energy due to changes in temperature and photovoltaic. In all MPPT techniques, perturb & observe and incremental conductance are widely used in MPPT controllers, because of their simplicity and ease of operation. According to the internal structure of the photovoltaic cell and the output volt-ampere characteristic, this paper established the circuit model and establishes the dynamic simulation model in Matlab/Simulink with the preparation of the s function. The perturb & observe MPPT method and the incremental conductance MPPT method were analyzed and compared by the theoretical analysis and digital simulation. The simulation results have shown that the system with INC MPPT method has better dynamic performance and improves the output power of photovoltaic power generation.
DEFF Research Database (Denmark)
Lashab, Abderezak; Sera, Dezso; Guerrero, Josep M.
2018-01-01
The main objective of this work is to provide an overview and evaluation of discrete model predictive controlbased maximum power point tracking (MPPT) for PV systems. A large number of MPC based MPPT methods have been recently introduced in the literature with very promising performance, however......, an in-depth investigation and comparison of these methods have not been carried out yet. Therefore, this paper has set out to provide an in-depth analysis and evaluation of MPC based MPPT methods applied to various common power converter topologies. The performance of MPC based MPPT is directly linked...... with the converter topology, and it is also affected by the accurate determination of the converter parameters, sensitivity to converter parameter variations is also investigated. The static and dynamic performance of the trackers are assessed according to the EN 50530 standard, using detailed simulation models...
Dermoune, Azzouz; Simon, Eric Pierre
2017-12-01
This paper is a theoretical analysis of the maximum likelihood (ML) channel estimator for orthogonal frequency-division multiplexing (OFDM) systems in the presence of unknown interference. The following theoretical results are presented. Firstly, the uniqueness of the ML solution for practical applications, i.e., when thermal noise is present, is analytically demonstrated when the number of transmitted OFDM symbols is strictly greater than one. The ML solution is then derived from the iterative conditional ML (CML) algorithm. Secondly, it is shown that the channel estimate can be described as an algebraic function whose inputs are the initial value and the means and variances of the received samples. Thirdly, it is theoretically demonstrated that the channel estimator is not biased. The second and the third results are obtained by employing oblique projection theory. Furthermore, these results are confirmed by numerical results.
Directory of Open Access Journals (Sweden)
Bohui Zhu
2013-01-01
Full Text Available This paper presents a novel maximum margin clustering method with immune evolution (IEMMC for automatic diagnosis of electrocardiogram (ECG arrhythmias. This diagnostic system consists of signal processing, feature extraction, and the IEMMC algorithm for clustering of ECG arrhythmias. First, raw ECG signal is processed by an adaptive ECG filter based on wavelet transforms, and waveform of the ECG signal is detected; then, features are extracted from ECG signal to cluster different types of arrhythmias by the IEMMC algorithm. Three types of performance evaluation indicators are used to assess the effect of the IEMMC method for ECG arrhythmias, such as sensitivity, specificity, and accuracy. Compared with K-means and iterSVR algorithms, the IEMMC algorithm reflects better performance not only in clustering result but also in terms of global search ability and convergence ability, which proves its effectiveness for the detection of ECG arrhythmias.
Novel composite resonance DC-DC converter with voltage doubler rectifier
Kato, Hisatsugu; Matsuo, Hirohumi; Eguchi, Masaki; Sakamoto, Yukitaka; Nakaishi, Masaki
2009-01-01
This paper deals with a novel composite resonance DC-DC converter with the voltage doubler rectifier, which is developed to be applied to the power conditioner of the photovoltaic generation system. The proposed DC-DC converter has the current and voltage resonance functions. Therefore, the output voltage regulation can be achieved for the large variations of the input voltage and load. Also, this converter has the high power efficiency. The maximum power efficiency 96.1% can be realized.
DEFF Research Database (Denmark)
Choi, Uimin; Lee, June-Seok; Lee, Kyo-Beum
2014-01-01
This paper proposes a new modulation strategy that balances the neutral-point voltage for three-level neutral-clamped inverter systems. The proposed modulation replaces the P-type or N-type small switching states with other switching states that do not affect the neutral-point voltage. The zero...... and medium switching states are employed to help the neutral-point voltage balancing. This method little bit increases the switching events and output total harmonic distortion. However, this method has a strong balancing ability at all regions. Further, it is very simple to implement in both space vector...
Energy Technology Data Exchange (ETDEWEB)
Stroica, Paul Constantin; Merfu, Ion; Stroica, Mihail; Merfu, Marius; Cojocaru, Florian; Stefan, Dinu; Cojocaru, Mihai
2010-09-15
The paper presents the measurements of the switching over-voltages made in the Romanian Power System, at the 400/220/110 kV Urechesti substation at the disconnection of a 400 kV, 100 MVAr shunt reactor type DFAL, Siemens, Germany, in 3 consecutive versions. The first one is for shunt reactor controlled by live-tank oil circuit breaker, the second one is for shunt reactor controlled by SF6 circuit breaker, and the third one is for shunt reactor controlled by SF6 circuit breaker and synchronize device.
Design and Development of a control system for the Drift Tube Chamber High Voltage Power Supply
Leon Vega, Luis Gerardo
2017-01-01
This paper contains information related to the design and development of a control and data acquisition manager implemented in WinCC, a Siemens SCADA system. The goal was to manage a CAEN HV (High Voltage) system for powering a Drift Tube (DT) chamber of the CMS experiment. Basically, this manager consists of two sections: a friendly user interface and powerful scripts to manage the back-end. It is in charge of adjusting the power supply settings to the correct values needed for the DT Chamber operations (ON, OFF, Standby), depending of the requirements of the operator, managing automatically all the transition process. Also, the manager is in charge of configuring the archiving process for acquiring data and providing the history of the system. It also implements the monitoring of the status of each connected channel, alerting in case it is needed.
Extension of the Accurate Voltage-Sag Fault Location Method in Electrical Power Distribution Systems
Directory of Open Access Journals (Sweden)
Youssef Menchafou
2016-03-01
Full Text Available Accurate Fault location in an Electric Power Distribution System (EPDS is important in maintaining system reliability. Several methods have been proposed in the past. However, the performances of these methods either show to be inefficient or are a function of the fault type (Fault Classification, because they require the use of an appropriate algorithm for each fault type. In contrast to traditional approaches, an accurate impedance-based Fault Location (FL method is presented in this paper. It is based on the voltage-sag calculation between two measurement points chosen carefully from the available strategic measurement points of the line, network topology and current measurements at substation. The effectiveness and the accuracy of the proposed technique are demonstrated for different fault types using a radial power flow system. The test results are achieved from the numerical simulation using the data of a distribution line recognized in the literature.
Study on Communication Methods for Electric Power High-voltage Equipment Monitoring System
Directory of Open Access Journals (Sweden)
Jia Yu Chen
2018-02-01
Full Text Available Real-time monitoring of high-voltage equipment in substations is beneficial for early detection of faults. The use of wireless sensor networks to build monitoring system is an effective way, but the data collection is a difficult task. The author introduces a real-time monitoring system based on ZIGBEE and mobile communication technology. The system includes multiple monitoring points and terminal platforms. Each monitoring point consists of a number of sensor nodes to form a ZIGBEE network, detecting relevant parameters, coordinator node data collected one by one, known as linear transmission, and finally to the monitoring platform through the mobile communication network. This paper presents a fusion algorithm for monitoring cell data acquisition to reduce the amount of data uploaded to the base station. In addition, multi-hop routing algorithm based on opportunistic routing is proposed to balance network energy and improve network transmission rate and efficiency.
Bureau of Naval Personnel, Washington, DC.
In this module the student will learn to apply the rules previously learned for series and parallel circuits to more complex circuits called series-parallel circuits, discover the utility of a common reference when making reference to voltage values, and learn how to obtain a required voltage from a voltage divider network. The module is divided…
DEFF Research Database (Denmark)
Kerekes, Tamas; Liserre, Marco; Mastromauro, R. A.
2009-01-01
Future ancillary services provided by photovoltaic (PV) systems could facilitate their penetration in power systems. Also low power PV systems can be designed to improve the power quality. This paper presents a single-phase photovoltaic system that provides grid voltage support and compensation o...
Wang, Hui; Blencowe, M. P.; Armour, A. D.; Rimberg, A. J.
2017-09-01
We give a semiclassical analysis of the average photon number as well as photon number variance (Fano factor F ) for a Josephson junction (JJ) embedded microwave cavity system, where the JJ is subject to a fluctuating (i.e., noisy) bias voltage with finite dc average. Through the ac Josephson effect, the dc voltage bias drives the effectively nonlinear microwave cavity mode into an amplitude squeezed state (F Armour et al., Phys. Rev. Lett. 111, 247001 (2013), 10.1103/PhysRevLett.111.247001], but bias noise acts to degrade this squeezing. We find that the sensitivity of the Fano factor to bias voltage noise depends qualitatively on which stable fixed point regime the system is in for the corresponding classical nonlinear steady-state dynamics. Furthermore, we show that the impact of voltage bias noise is most significant when the cavity is excited to states with large average photon number.
Directory of Open Access Journals (Sweden)
Sang-Yun Yun
2014-02-01
Full Text Available This paper is a summary of the development and demonstration of an optimization program, voltage VAR optimization (VVO, in the Korean Smart Distribution Management System (KSDMS. KSDMS was developed to address the lack of receptivity of distributed generators (DGs, standardization and compatibility, and manual failure recovery in the existing Korean automated distribution system. Focusing on the lack of receptivity of DGs, we developed a real-time system analysis and control program. The KSDMS VVO enhances manual system operation of the existing distribution system and provides a solution with all control equipment operated at a system level. The developed VVO is an optimal power flow (OPF method that resolves violations, minimizes switching costs, and minimizes loss, and its function can vary depending on the operator’s command. The sequential mixed integer linear programming (SMILP method was adopted to find the solution of the OPF. We tested the precision of the proposed VVO on selected simulated systems and its applicability to actual systems at two substations on the Jeju Island. Running the KSDMS VVO on a regular basis improved system stability, and it also raised no issues regarding its applicability to actual systems.
DEFF Research Database (Denmark)
Ding, Tao; Kou, Yu; Yang, Yongheng
2017-01-01
. However, the intermittency of solar PV energy (e.g., due to passing clouds) may affect the PV generation in the district distribution network. To address this issue, the voltage magnitude constraints under the cloud shading conditions should be taken into account in the optimization model, which can...
Monte Carlo simulations for stereotactic radiotherapy system with various kilo-voltage x-ray energy
International Nuclear Information System (INIS)
Deloar, H.M.; Kunieda, E.; Kawase, T.; Kubo, Atsushi; Saitoh, H.; Myojoyama, A.; Ozaki, M.; Fujisaki, T.; Saito, K.
2005-01-01
Stereotactic radiotherapy (SRT) of lung tumors with a narrow and precise medium energy x-ray beam where the homogeneous high dose area will be confined within the tumors are desirable. A conventional x-ray CT with medium energy x-ray has been modified to develop a radiotherapy system for lung SRT. A cylindrical collimator (0.3 cm φ) made of tungsten was introduced to collimate the X-ray beam. The system was simulated with BEAMnrc(EGS4) Monte Carlo code and various x-ray energy spectra were generated to investigate the dose distributions with our kilo-voltage SRT system. Experiments were performed to acquire the energy spectra of 100, 120 and 135 kVp (kilo-voltage peak) from CT measurements and those results were compared with the spectra obtained from Monte Carlo simulations. Verifications of percentage of dose depth (PDD) for 120 and 147.5 kVp were investigated in a water phantom with experiments and Monte Carlo simulations. Finally dose distributions of 120, 135, 147.5, 200, 250, 300, 350, 400, 500 kVp spectra were investigated with lung phantom and human lung. The Percentage of Depth Dose (PDD) in the water phantom calculated from the experimental and simulated spectra of 120 and 147.5 kVp show good agreement with each other. The PDD of 147.5 and 120 kVp spectra at 9 cm depth was approximately 10% and 9%, respectively. Dose distributions around the lung tumor in the phantom and human for all x-ray energies were almost uniform but in the case of the human lung absorptions of dose at ribs for the energy lower than 135 kVp was more than 35% and those absorptions for the energy spectra of 147.5 kVp and above was less than 30%. This absorption gradually decreases with increasing x-ray energies. Uniform dose distributions in the lung region of human and thorax phantom demonstrated the possibility of SRT system with medium energy X-ray. A detail performance of this system as a kilo-voltage conformal radiotherapy is under investigations. (author)
Maximum likelihood versus likelihood-free quantum system identification in the atom maser
International Nuclear Information System (INIS)
Catana, Catalin; Kypraios, Theodore; Guţă, Mădălin
2014-01-01
We consider the problem of estimating a dynamical parameter of a Markovian quantum open system (the atom maser), by performing continuous time measurements in the system's output (outgoing atoms). Two estimation methods are investigated and compared. Firstly, the maximum likelihood estimator (MLE) takes into account the full measurement data and is asymptotically optimal in terms of its mean square error. Secondly, the ‘likelihood-free’ method of approximate Bayesian computation (ABC) produces an approximation of the posterior distribution for a given set of summary statistics, by sampling trajectories at different parameter values and comparing them with the measurement data via chosen statistics. Building on previous results which showed that atom counts are poor statistics for certain values of the Rabi angle, we apply MLE to the full measurement data and estimate its Fisher information. We then select several correlation statistics such as waiting times, distribution of successive identical detections, and use them as input of the ABC algorithm. The resulting posterior distribution follows closely the data likelihood, showing that the selected statistics capture ‘most’ statistical information about the Rabi angle. (paper)
Directory of Open Access Journals (Sweden)
Enrico Pagano
2013-03-01
Full Text Available The paper aims to contribute to the use of electric double layer capacitor (EDLC sets for boosting voltages of contact lines in urban and suburban railway traction systems. Different electrical configurations of contact lines are considered and investigated. For each of them, proper mathematical models are suggested to evaluate the electrical performances of the contact lines. They give rise, also, to sample design procedures for the sizing of the most appropriate energy storage systems, to be distributed along the lines, for boosting line voltages and avoiding undesired voltage drops. A numerical example based on the “Cumana” suburban Naples railway network is presented to give an idea of the weights and sizes of electric double layer capacitors needed to boost the voltage of a sample contact line. In particular, three different EDLC systems, for a overall installed energy of 9.6 kWh, have been placed nearby the stations presenting the highest voltage drops during the most representative situation of trains’ service. The new voltage drop is equal to 32% of that obtained in absence of EDLCs.
Energy Technology Data Exchange (ETDEWEB)
Iannuzzi, Diago [University of Federico II, Naples (Italy). Electrical Engineering Department; Pagano, Enrico [University of Federico II, Naples (Italy). Electrical Engineering Department; Tricoli, Pietro [University of Birmingham (United Kingdom). School of Electronic, Electrical and Computer Engineering
2013-04-15
The paper aims to contribute to the use of electric double layer capacitor (EDLC) sets for boosting voltages of contact lines in urban and suburban railway traction systems. Different electrical configurations of contact lines are considered and investigated. For each of them, proper mathematical models are suggested to evaluate the electrical performances of the contact lines. They give rise, also, to sample design procedures for the sizing of the most appropriate energy storage systems, to be distributed along the lines, for boosting line voltages and avoiding undesired voltage drops. A numerical example based on the “Cumana” suburban Naples railway network is presented to give an idea of the weights and sizes of electric double layer capacitors needed to boost the voltage of a sample contact line. In particular, three different EDLC systems, for a overall installed energy of 9.6 kWh, have been placed nearby the stations presenting the highest voltage drops during the most representative situation of trains’ service. The new voltage drop is equal to 32% of that obtained in absence of EDLCs.
Maximum entropy approach to H-theory: Statistical mechanics of hierarchical systems.
Vasconcelos, Giovani L; Salazar, Domingos S P; Macêdo, A M S
2018-02-01
A formalism, called H-theory, is applied to the problem of statistical equilibrium of a hierarchical complex system with multiple time and length scales. In this approach, the system is formally treated as being composed of a small subsystem-representing the region where the measurements are made-in contact with a set of "nested heat reservoirs" corresponding to the hierarchical structure of the system, where the temperatures of the reservoirs are allowed to fluctuate owing to the complex interactions between degrees of freedom at different scales. The probability distribution function (pdf) of the temperature of the reservoir at a given scale, conditioned on the temperature of the reservoir at the next largest scale in the hierarchy, is determined from a maximum entropy principle subject to appropriate constraints that describe the thermal equilibrium properties of the system. The marginal temperature distribution of the innermost reservoir is obtained by integrating over the conditional distributions of all larger scales, and the resulting pdf is written in analytical form in terms of certain special transcendental functions, known as the Fox H functions. The distribution of states of the small subsystem is then computed by averaging the quasiequilibrium Boltzmann distribution over the temperature of the innermost reservoir. This distribution can also be written in terms of H functions. The general family of distributions reported here recovers, as particular cases, the stationary distributions recently obtained by Macêdo et al. [Phys. Rev. E 95, 032315 (2017)10.1103/PhysRevE.95.032315] from a stochastic dynamical approach to the problem.
Directory of Open Access Journals (Sweden)
Yong Min
2013-06-01
Full Text Available In this paper, concepts and methods of hybrid control systems are adopted to establish a hierarchical dynamic automatic voltage control (HD-AVC system, realizing the dynamic voltage stability of power grids. An HD-AVC system model consisting of three layers is built based on the hybrid control method and discrete event-driven mechanism. In the Top Layer, discrete events are designed to drive the corresponding control block so as to avoid solving complex multiple objective functions, the power system’s characteristic matrix is formed and the minimum amplitude eigenvalue (MAE is calculated through linearized differential-algebraic equations. MAE is applied to judge the system’s voltage stability and security and construct discrete events. The Middle Layer is responsible for management and operation, which is also driven by discrete events. Control values of the control buses are calculated based on the characteristics of power systems and the sensitivity method. Then control values generate control strategies through the interface block. In the Bottom Layer, various control devices receive and implement the control commands from the Middle Layer. In this way, a closed-loop power system voltage control is achieved. Computer simulations verify the validity and accuracy of the HD-AVC system, and verify that the proposed HD-AVC system is more effective than normal voltage control methods.
Directory of Open Access Journals (Sweden)
Yufei Teng
2017-03-01
Full Text Available In order to improve the fault monitoring performance of grounding electrode lines in ultra-high voltage DC (UHVDC transmission systems, a novel fault monitoring approach based on the high-frequency voltage standing-wave ratio (VSWR is proposed in this paper. The VSWR is defined considering a lossless transmission line, and the characteristics of the VSWR under different conditions are analyzed. It is shown that the VSWR equals 1 when the terminal resistance completely matches the characteristic impedance of the line, and when a short circuit fault occurs on the grounding electrode line, the VSWR will be greater than 1. The VSWR will approach positive infinity under metallic earth fault conditions, whereas the VSWR in non-metallic earth faults will be smaller. Based on these analytical results, a fault supervision criterion is formulated. The effectiveness of the proposed VSWR-based fault supervision technique is verified with a typical UHVDC project established in Power Systems Computer Aided Design/Electromagnetic Transients including DC(PSCAD/EMTDC. Simulation results indicate that the proposed strategy can reliably identify the grounding electrode line fault and has strong anti-fault resistance capability.
Energy Technology Data Exchange (ETDEWEB)
Laagland, H.
2012-07-01
The electricity distribution sector in Finland is highly regulated and the return on investments in distribution networks is low. Low profits don't make the electricity distribution sector attractive to outside investors. During the second regulatory period of 2008-2011 incentives are included into the Finnish regulation model which allows higher profits for the network owners for right allocated network investments leading to lower operation and interruption costs. The goal of the thesis is to find cost-effective medium-voltage distribution system investment strategies for the Finnish power distribution companies with respect to the incentives of the second regulatory period. In this work the sectionalisation concept is further developed by deriving equations for a homogeneous electricity distribution system for the economical and reliability indices as a function of the number of sectionalisation zones. The cost-effective medium-voltage distribution system investment strategies are found by studying the technical and economic interaction of feeder automation on different network structures. Ten feeder automation schemes have been applied to six urban/rural area generic feeders and two real rural area feeders of a distribution company in western Finland. The analytical approach includes modelling of the feeders and feeder functions and calculation of the economical and reliability indices. The following investment areas are included: different electricity distribution systems, new substation, new switching station, central earth-fault current compensation, cabling and feeder automation. The value of the results of this work is that they reveal the influence that feeder automation has on the reliability and economy of different distribution structures. This created transparency enables a national and/or distribution company network investment strategy to optimise the economic benefits of investments. (orig.)
P. Selvam; S. Senthil Kumar
2016-01-01
Maximum Power Point Tracking (MPPT) has played a vital role to enhance the efficiency of solar photovoltaic (PV) power generation under varying atmospheric temperature and solar irradiation. However, it is hard to track the maximum power point using conventional linear controllers due to the natural inheritance of nonlinear I-V and P-V characteristics of solar PV systems. Fuzzy Logic Controller (FLC) is suitable for nonlinear system control applications and eliminating oscillations, circuit c...
Influence of Load Modes on Voltage Stability of Receiving Network at DC/AC System
Directory of Open Access Journals (Sweden)
Mao Chizu
2016-01-01
Full Text Available This paper analyses influence of load modes on DC/AC system. Because of widespread use of HVDC, DC/AC system become more complex than before and the present modes used in dispatch and planning departments are not fit in simulation anymore. So it is necessary to find load modes accurately reflecting characteristics of the system. For the sake of the voltage stability, commutation failure, etc. the practical example of the receiving network in a large DC/AC system in China is simulated with BPA, and the influence of Classical Load Mode (CLM and Synthesis load model (SLM on simulation results is studies. Furthermore, some important parameters of SLM are varied respectively among an interval to analyse how they affect the system. According to this practical examples, the result is closely related to load modes and their parameters, and SLM is more conservative but more reasonable than the present modes. The consequences indicate that at critical states, micro variation in parameters may give rise to change in simulation results radically. Thus, correct mode and parameters are important to enhance simulation accuracy of DC/AC system and researches on how they affect the system make senses.
The BaBar LST Detector High Voltage System: Design And Implementation
International Nuclear Information System (INIS)
Benelli, G.; Honscheid, K.; Lewis, E.A.; Regensburger, J.J.; Smith, D.S.; Ohio State U.
2006-01-01
In 2004, the first two sextants of the new Limited Streamer Tube (LST) detector were installed in the BABAR experiment to replace the ageing Resistive Plate Chambers (RPCs) as active detectors for the BABAR Instrumented Flux Return (IFR) muon system. Each streamer tube of the new detector consists of 8 cells. The cell walls are coated with graphite paint and a 100 (micro)m wire forms the anode. These wires are coupled in pairs inside the tubes resulting in 4 independent two-cell segments per LST. High voltage (HV) is applied to the 4 segments through a custom connector that also provides the decoupling capacitor to pick up the detector signals from the anode wires. The BABAR LST detector is operated at 5.5 kV. The high voltage system for the LST detector was designed and built at The Ohio State University (OSU HVPS). Each of the 25 supplies built for BaBar provides 80 output channels with individual current monitoring and overcurrent protection. For each group of 20 channels the HV can be adjusted between 0 and 6 kV. A 4-fold fan-out is integrated in the power supplies to provide a total of 320 outputs. The power supplies are controlled through built-in CANbus and Ethernet (TCP/IP) interfaces. In this presentation we will discuss the design and novel features of the OSU HVPS system and its integration into the BABAR EPICS detector control framework. Experience with the supplies operation during the LST extensive quality control program and their performance during the initial data taking period will be discussed
Hardware and software system for monitoring oil pump operation in power high-voltage transformers
Directory of Open Access Journals (Sweden)
Михайло Дмитрович Дяченко
2017-07-01
Full Text Available The article considers the basic prerequisites for the creation of an automated monitoring system for oil pumps of high-voltage transformers. This is due to the fact that the long operation of oil pumps results in deterioration and destruction of bearings, rubbing of the rotor, breakage and damage to the impeller, leakage, etc., which inevitably causes a significant decrease in the insulating properties of the transformer oil and leads to expenditures for its further recovery. False triggerings of gas protection sometimes occur. Continuous operation of the electric motor also requires additional equipment to protect the motor itself from various emergency situations, such as a short in the stator winding, a housing breakdown, an incomplete phase mode, etc. The use of stationary systems provides: diagnosing defects at an early stage of their development, increasing the reliability and longevity of the equipment components, increasing the overhaul period, decreasing the number of emergency stops, and adjusting the schedule of preventative maintenance. The basic principles of identification of the damaged part of the oil pump are given, the hardware and algorithmic solutions are considered in the work. The full-scale tests of the model sample on the power transformer of the high-voltage substation confirmed the assumption of the possibility of detecting the damaged unit separating it from the rest connected in one mechanical structure. A detailed analysis of the operation of each of the units is carried out by means of the general substation switchboard and displayed as graphs, diagrams and text messages. When the limit values of vibration are reached, faults in the operation of the unit are detected, the overlimit current values, a warning alarm is activated, and the command to disconnect the damaged unit is issued. The optimal solution for the organization of the information collection system using the principle of sensor networks, but combined
Directory of Open Access Journals (Sweden)
Hadi Heidari Gharehbolagh
2016-01-01
Full Text Available This study investigates a multiowner maximum-flow network problem, which suffers from risky events. Uncertain conditions effect on proper estimation and ignoring them may mislead decision makers by overestimation. A key question is how self-governing owners in the network can cooperate with each other to maintain a reliable flow. Hence, the question is answered by providing a mathematical programming model based on applying the triangular reliability function in the decentralized networks. The proposed method concentrates on multiowner networks which suffer from risky time, cost, and capacity parameters for each network’s arcs. Some cooperative game methods such as τ-value, Shapley, and core center are presented to fairly distribute extra profit of cooperation. A numerical example including sensitivity analysis and the results of comparisons are presented. Indeed, the proposed method provides more reality in decision-making for risky systems, hence leading to significant profits in terms of real cost estimation when compared with unforeseen effects.
Chernick, Julian A.; Perlovsky, Leonid I.; Tye, David M.
1994-06-01
This paper describes applications of maximum likelihood adaptive neural system (MLANS) to the characterization of clutter in IR images and to the identification of targets. The characterization of image clutter is needed to improve target detection and to enhance the ability to compare performance of different algorithms using diverse imagery data. Enhanced unambiguous IFF is important for fratricide reduction while automatic cueing and targeting is becoming an ever increasing part of operations. We utilized MLANS which is a parametric neural network that combines optimal statistical techniques with a model-based approach. This paper shows that MLANS outperforms classical classifiers, the quadratic classifier and the nearest neighbor classifier, because on the one hand it is not limited to the usual Gaussian distribution assumption and can adapt in real time to the image clutter distribution; on the other hand MLANS learns from fewer samples and is more robust than the nearest neighbor classifiers. Future research will address uncooperative IFF using fused IR and MMW data.
Increasing the maximum daily operation time of MNSR reactor by modifying its cooling system
International Nuclear Information System (INIS)
Khamis, I.; Hainoun, A.; Al Halbi, W.; Al Isa, S.
2006-08-01
thermal-hydraulic natural convection correlations have been formulated based on a thorough analysis and modeling of the MNSR reactor. The model considers detailed description of the thermal and hydraulic aspects of cooling in the core and vessel. In addition, determination of pressure drop was made through an elaborate balancing of the overall pressure drop in the core against the sum of all individual channel pressure drops employing an iterative scheme. Using this model, an accurate estimation of various timely core-averaged hydraulic parameters such as generated power, hydraulic diameters, flow cross area, ... etc. for each one of the ten-fuel circles in the core can be made. Furthermore, distribution of coolant and fuel temperatures, including maximum fuel temperature and its location in the core, can now be determined. Correlation among core-coolant average temperature, reactor power, and core-coolant inlet temperature, during both steady and transient cases, have been established and verified against experimental data. Simulating various operating condition of MNSR, good agreement is obtained for at different power levels. Various schemes of cooling have been investigated for the purpose of assessing potential benefits on the operational characteristics of the syrian MNSR reactor. A detailed thermal hydraulic model for the analysis of MNSR has been developed. The analysis shows that an auxiliary cooling system, for the reactor vessel or installed in the pool which surrounds the lower section of the reactor vessel, will significantly offset the consumption of excess reactivity due to the negative reactivity temperature coefficient. Hence, the maximum operating time of the reactor is extended. The model considers detailed description of the thermal and hydraulic aspects of cooling the core and its surrounding vessel. Natural convection correlations have been formulated based on a thorough analysis and modeling of the MNSR reactor. The suggested 'micro model
DEFF Research Database (Denmark)
Rakhshan, Mohsen; Vafamand, Navid; Khooban, Mohammad Hassan
2018-01-01
This paper introduces a polynomial fuzzy model (PFM)-based maximum power point tracking (MPPT) control approach to increase the performance and efficiency of the solar photovoltaic (PV) electricity generation. The proposed method relies on a polynomial fuzzy modeling, a polynomial parallel......, a direct maximum power (DMP)-based control structure is considered for MPPT. Using the PFM representation, the DMP-based control structure is formulated in terms of SOS conditions. Unlike the conventional approaches, the proposed approach does not require exploring the maximum power operational point...
Voltage-current characteristics of a pin-plate system with different plate configurations
International Nuclear Information System (INIS)
Feng, Zhuangbo; Long, Zhengwei
2013-01-01
In this paper, the voltage-current (V-I) characteristics of a pin-plate system with four types of collection plate configurations are studied experimentally. The collection plates consider a single metal plate, a metal plate with a fly ash cake layer, a metal plate with a clean filter media and a metal plate with a dirty filter media. The results show that the clean filter media has no obvious effect on the V-I characteristics. But the dirty filter media reduces the current density because of its high resistance. The thick fly ash cake layer increase current density because of the anti-corona effect but the increment is not very obvious.
The behaviour of the charging system of the Vivitron for the first voltage tests
International Nuclear Information System (INIS)
Helleboid, J.M.
1992-06-01
The charging system used for the initial commissioning of the Vivitron generator is a simplified temporary version of the final one. As the belt runs in a largely open structure performances could be possibly limited compared with the final design. The observed behaviour for the first high voltage tests was quite satisfying apart from the excessive parasitic currents at the rollers. That led us to study and test many solutions up to the point that a humidity level much higher than thought was discovered as the most probable cause of the problem. The further tests brought the confirmation as the parasitic currents at the supporting rollers not exceeded tens of microA under dry conditions as it had first been expected from the experimental design studies
Modelling, stability and control of voltage behaviour in power supply systems
Energy Technology Data Exchange (ETDEWEB)
Hill, David J [Sydney Univ., NSW (Australia). Dept. of Electrical Engineering; Hisken, Ian A [Newcastle Univ., NSW (Australia). Dept. of Electrical and Computer Engineering
1994-12-31
This paper gives an overview of a line of work on mid to long term voltages stability analysis and control in power systems. The results are based on use of a novel approach to dynamic load modelling using aggregate nonlinear structures. In general, the model for the transmission network and supply end dynamics is of the hybrid differential - algebraic - discrete kind. Various stability questions are precisely formulated and analysed in terms of network and load characteristics (steady-state and transient). The results are shown to be a useful framework for deriving criteria of the where, when and how much kind for various control actions such as load Thedding and tap-blocking. (author) 47 refs., 15 figs., 1 tab.
The Design of Integrated Information System for High Voltage Metering Lab
Ma, Yan; Yang, Yi; Xu, Guangke; Gu, Chao; Zou, Lida; Yang, Feng
2018-01-01
With the development of smart grid, intelligent and informatization management of high-voltage metering lab become increasingly urgent. In the paper we design an integrated information system, which automates the whole transactions from accepting instruments, make experiments, generating report, report signature to instrument claims. Through creating database for all the calibrated instruments, using two-dimensional code, integrating report templates in advance, establishing bookmarks and online transmission of electronical signatures, our manual procedures reduce largely. These techniques simplify the complex process of account management and report transmission. After more than a year of operation, our work efficiency improves about forty percent averagely, and its accuracy rate and data reliability are much higher as well.
Energy Technology Data Exchange (ETDEWEB)
Spahic, Ervin; Benz, Thomas; Goerner, Raphael; Sass, Florian [ABB AG, Mannheim (Germany)
2012-12-15
In September 2010 the German federal government announced its energy concept for an environmentally friendly, reliable and affordable energy supply. This concept describes a ''path into the era of renewable energy'' up to the year 2050, with electricity production from photovoltaics and wind power taking centre stage. Since the expansion of renewable energy production is mainly taking place in the North (wind power) and the South (PV), this poses a great challenge to the electricity networks. It necessitates the expansion of power transmission systems, notably for transporting electricity generated by wind power in the North to the consumer centres in Western and Southern Germany. However, progress to this end has been very slow. For this reason a technical question now presents itself, namely whether high-voltage direct current technology could possibly offer a solution to the electricity transport problems associated with the energy turnaround.
Systems and methods for process and user driven dynamic voltage and frequency scaling
Mallik, Arindam [Evanston, IL; Lin, Bin [Hillsboro, OR; Memik, Gokhan [Evanston, IL; Dinda, Peter [Evanston, IL; Dick, Robert [Evanston, IL
2011-03-22
Certain embodiments of the present invention provide a method for power management including determining at least one of an operating frequency and an operating voltage for a processor and configuring the processor based on the determined at least one of the operating frequency and the operating voltage. The operating frequency is determined based at least in part on direct user input. The operating voltage is determined based at least in part on an individual profile for processor.
High Voltage Hybrid Electric Propulsion - Multilayered Functional Insulation System (MFIS) NASA-GRC
Lizcano, M.
2017-01-01
High power transmission cables pose a key challenge in future Hybrid Electric Propulsion Aircraft. The challenge arises in developing safe transmission lines that can withstand the unique environment found in aircraft while providing megawatts of power. High voltage AC, variable frequency cables do not currently exist and present particular electrical insulation challenges since electrical arcing and high heating are more prevalent at higher voltages and frequencies. Identifying and developing materials that maintain their dielectric properties at high voltage and frequencies is crucial.
Artificial Neural Network In Maximum Power Point Tracking Algorithm Of Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Modestas Pikutis
2014-05-01
Full Text Available Scientists are looking for ways to improve the efficiency of solar cells all the time. The efficiency of solar cells which are available to the general public is up to 20%. Part of the solar energy is unused and a capacity of solar power plant is significantly reduced – if slow controller or controller which cannot stay at maximum power point of solar modules is used. Various algorithms of maximum power point tracking were created, but mostly algorithms are slow or make mistakes. In the literature more and more oftenartificial neural networks (ANN in maximum power point tracking process are mentioned, in order to improve performance of the controller. Self-learner artificial neural network and IncCond algorithm were used for maximum power point tracking in created solar power plant model. The algorithm for control was created. Solar power plant model is implemented in Matlab/Simulink environment.
DG Allocation Based on Reliability, Losses and Voltage Sag Considerations: an expert system approach
Directory of Open Access Journals (Sweden)
Sahar Abdel Moneim Moussa
2017-03-01
Full Text Available Expert System (ES as a branch of Artificial Intelligence (AI methodology can potentially help in solving complicated power system problems. This may be more appropriate methodology than conventional optimization techniques when contradiction between objectives appears in reaching the optimum solution. When this contradiction is the hindrance in reaching the required system operation through the application of traditional methods ES can give a hand in such case. In this paper, the knowledge- based ES technique is proposed to reach near-optimum solution which is further directed to the optimum solution through particle swarm optimization (PSO technique. This idea is known as Hybrid-Expert-System (HES. The proposed idea is used in getting the optimum allocation of a number of distributed generation (DG units on Distribution System (DS busbars taking into consideration three issues; reliability, voltage sag, and line losses. Optimality is assessed on the economic basis by calculating money benefits (or losses resulting from DG addition considering the three aforementioned issues. The effectiveness of the proposed technique is ascertained through example.
Energy Technology Data Exchange (ETDEWEB)
Akiyama, Kazuya; Matsumoto, Satoshi; Miyasaka, Akihiro; Shodai, Takahisa [NTT Energy and Environment System Laboratories, 3-1 Morinosato-Wakamiya Atsugi-shi, Kanagawa (Japan)
2009-01-01
A new strategy for increasing the power density of an air-breathing small proton exchange membrane fuel cell (PEMFC) system for the main energy source of portable consumer electronics is presented. The small PEMFC system is composed of a single cell. Utilizing the output voltage of the single cell, we introduce a newly designed ultra-low voltage input boost converter. The boost converter can generate 4.1 V output from input sources with low voltage ranges, such as under 1.0 V. The cathode plate is made from a thin SUS 316L stainless steel plate and has ribs that prevent the cathode from bending. The hydrogen is supplied by a metal hydride (MH) tank cartridge. The MH tank contains highly packed AB5-type MH. The MH tank cartridge has a volume of 13.2 cm{sup 3} and can absorb 6.7 L of hydrogen. The maximum power of the small PEMFC is 4.42 W at room temperature. Using 6.7 L of hydrogen, the small PEMFC can generate 11 Wh of electricity. The power density of the small PEMFC reaches 0.51 Wh cm{sup -3}. And the power density of the whole small PEMFC system, which contains the boost converter, a small Li-ion battery for a load absorber, and a case for the system, reaches 0.14 Wh cm{sup -3}. This value matches that of external Li-ion battery chargers for cell phones. We installed the small PEMFC system in a cell phone and confirmed the operations of calling, receiving, videophone, connecting to the Internet, and watching digital TV. And also confirmed that the small PEMFC system provides approximately 8.25 h of talk time, which is about three times as long as that for the original Li-ion battery. (author)
DEFF Research Database (Denmark)
Sun, Xiaofeng; Han, Ruijing; Shen, Hong
2016-01-01
voltages. This paper proposes a double-resistive active power filter (D-RAPF) system consisting of a terminal-RAPF and an attenuation-RAPF for each individual harmonic. The terminal-RAPF operating as the characteristic impedance of the feeder is installed at the end bus to suppress harmonic propagation......Harmonic propagation between power-factor correction capacitors and system inductors seriously deteriorates power quality in a radial power distribution feeder. Installation of a resistive active power filter (RAPF) at the end bus only suppresses harmonic propagation, not attenuates harmonic...... at all harmonic frequencies. The attenuation-RAPF, whose control gain can be set according to the requirements of the harmonic voltage distortion limit, is installed at a specific position for each individual harmonic to attenuate the corresponding harmonic voltages. The D-RAPF system not only suppresses...
Design and application of the high-voltage DC power-supply control system based on PLC
International Nuclear Information System (INIS)
Huang Yiyun; Zheng Guanghua; Wu Junshuan; Yang Chunsheng; Hu Huaichuan
2002-03-01
The design and application of A kind of high-voltage DC power-supply control system based on PLC is referred, in addition, KingView is used to monitor the system in real time and manage the man-machine conversation ideally
Design of High Voltage Electrical Breakdown Strength measuring system at 1.8K with a G-M cryocooler
Li, Jian; Huang, Rongjin; Li, Xu; Xu, Dong; Liu, Huiming; Li, Laifeng
2017-09-01
Impregnating resins as electrical insulation materials for use in ITER magnets and feeder system are required to be radiation stable, good mechanical performance and high voltage electrical breakdown strength. In present ITER project, the breakdown strength need over 30 kV/mm, for future DEMO reactor, it will be greater than this value. In order to develop good property insulation materials to satisfy the requirements of future fusion reactor, high voltage breakdown strength measurement system at low temperature is necessary. In this paper, we will introduce our work on the design of this system. This measuring system has two parts: one is an electrical supply system which provides the high voltage from a high voltage power between two electrodes; the other is a cooling system which consists of a G-M cryocooler, a superfluid chamber and a heat switch. The two stage G-M cryocooler pre-cool down the system to 4K, the superfluid helium pot is used for a container to depress the helium to superfluid helium which cool down the sample to 1.8K and a mechanical heat switch connect or disconnect the cryocooler and the pot. In order to provide the sufficient time for the test, the cooling system is designed to keep the sample at 1.8K for 300 seconds.
International Nuclear Information System (INIS)
Andrade, R.B. de
1990-01-01
Voltage and frequency monitoring concept for a Nuclear Power Plant Normal Power Supply System (PWR 1300 MWe) is described based on the phylosophy adopted for Angra 2 and e NPP's. Some suggested setpoints are only guidance values and can be modified during plant commissioning for a better performance of the whole protection system. (author) [pt
Load-Following Voltage Controller Design for a Static Space Nuclear Power System
International Nuclear Information System (INIS)
Parlos, Alexander G.; Onbasioglou, Fetiye O.; Metzger, John D.
2000-01-01
The reliability of static space nuclear power systems (SNPSs) could be improved through the use of backup devices in addition to shunt regulators, as currently proposed for load following. Shunt regulator failure leading to reactor shutdown is possible, as is the possible need to deliver somewhat higher power level to the load than originally expected. A backup system is proposed in SNPSs to eliminate the possibility of a single-point failure in the shunt regulators and to increase the overall system power delivery capability despite changing mission needs and component characteristics. The objective of this paper is to demonstrate the feasibility of such a backup device for voltage regulation in static SNPSs that is capable of overcoming system variations resulting from operation at different power levels. A dynamic compensator is designed using the Linear Quadratic Gaussian with Loop Transfer Recovery method. The resulting compensators are gain scheduled using the SNPS electric power as the scheduling variable, resulting in a nonlinear compensator. The performance of the gain-scheduled compensator is investigated extensively using an SNPS simulator. The simulations demonstrate the effects of the fuel temperature reactivity coefficient variations on the load-following capabilities of the SNPS. Robustness analysis results demonstrate that the proposed controller exhibits significant operational flexibility, and it can be considered for long-term space mission requiring significant levels of autonomy
Preventive voltage control actions to securely face load evolution in power systems
Energy Technology Data Exchange (ETDEWEB)
Marano Marcolini, A.; Martinez Ramos, J.L.; Romero Ramos, E.; Trigo Garcia, A.L. [Department of Electrical Engineering, University of Seville, Camino de los Descubrimientos s/n, 41092 Sevilla (Spain)
2010-04-15
One of the main aims of the System Operator (SO) is to maintain in every moment the system parameters between feasible operational margins. In certain periods of the day the load suffers fast changes which cause, specially when it tends to increase, a generalized voltage decrement and a more stressed condition for many reactive resources. In such cases, many devices may arrive to their operational limits, situation which translates into a weaker system. To avoid this negative effect the control variables should be rescheduled to maintain the normal operation conditions in the foreseeable future. This work proposes a useful tool to assist the SO when determining such actions. The main improvements are due to the implementation of a hybrid method that allows the comparison of different kinds of control variables and the inclusion of the operator background and experience in the algorithm that determines the actions. The performance of the proposed method is tested in both the IEEE 14-Bus and 118-Bus test systems. (author)
Energy Technology Data Exchange (ETDEWEB)
Campoccia, A.; Di Silvestre, M.L.; Incontrera, I.; Riva Sanseverino, E. [Dipartimento di Ingegneria Elettrica elettronica e delle Telecomunicazioni, Universita degli Studi di Palermo, viale delle Scienze, 90128 Palermo (Italy); Spoto, G. [Centro per la Ricerca Elettronica in Sicilia, Monreale, Via Regione Siciliana 49, 90046 Palermo (Italy)
2010-10-15
Service continuity is one of the major aspects in the definition of the quality of the electrical energy, for this reason the research in the field of faults diagnostic for distribution systems is spreading ever more. Moreover the increasing interest around modern distribution systems automation for management purposes gives faults diagnostics more tools to detect outages precisely and in short times. In this paper, the applicability of an efficient fault location and characterization methodology within a centralized monitoring system is discussed. The methodology, appropriate for any kind of fault, is based on the use of the analytical model of the network lines and uses the fundamental components rms values taken from the transient measures of line currents and voltages at the MV/LV substations. The fault location and identification algorithm, proposed by the authors and suitably restated, has been implemented on a microprocessor-based device that can be installed at each MV/LV substation. The speed and precision of the algorithm have been tested against the errors deriving from the fundamental extraction within the prescribed fault clearing times and against the inherent precision of the electronic device used for computation. The tests have been carried out using Matlab Simulink for simulating the faulted system. (author)
Energy Technology Data Exchange (ETDEWEB)
Skretas, Sotirios B.; Papadopoulos, Demetrios P. [Electrical Machines Laboratory, Department of Electrical and Computer Engineering, Democritos University of Thrace (DUTH), 12 V. Sofias, 67100 Xanthi (Greece)
2009-09-15
In this paper an efficient design along with modeling and simulation of a transformer-less small-scale centralized DC - bus Grid Connected Hybrid (Wind-PV) power system for supplying electric power to a single phase of a three phase low voltage (LV) strong distribution grid are proposed and presented. The main components of the hybrid system are: a PV generator (PVG); and an array of horizontal-axis, fixed-pitch, small-size, variable-speed wind turbines (WTs) with direct-driven permanent magnet synchronous generator (PMSG) having an embedded uncontrolled bridge rectifier. An overview of the basic theory of such systems along with their modeling and simulation via Simulink/MATLAB software package are presented. An intelligent control method is applied to the proposed configuration to simultaneously achieve three desired goals: to extract maximum power from each hybrid power system component (PVG and WTs); to guarantee DC voltage regulation/stabilization at the input of the inverter; to transfer the total produced electric power to the electric grid, while fulfilling all necessary interconnection requirements. Finally, a practical case study is conducted for the purpose of fully evaluating a possible installation in a city site of Xanthi/Greece, and the practical results of the simulations are presented. (author)
International Nuclear Information System (INIS)
Fumelli, M.; Jequier, F.; Pamela, J.
1988-01-01
A passive protection system against high voltage vacuum breakdowns has been developed. This system is based on the principle of oscillatory discharges in an RLC circuit coupled with the use of a diode. It allows the interruption of a vacuum breakdown in a few milliseconds. This study has been made for protecting some parts of the neutral beam injectors of the Tore Supra Tokamak experiment, but its field of application should be quite large. The conception of the whole high voltage electrical circuit developed for the Tore Supra injector prototype experiments is also presented
30 CFR 18.53 - High-voltage longwall mining systems.
2010-07-01
...-starter enclosure, with the exception of a controller on a high-voltage shearer, the disconnect device...) shielding between the primary and secondary windings. The shielding must be connected to equipment ground by... with a disconnect device installed to deenergize all high-voltage power conductors extending from the...
Bureau of Naval Personnel, Washington, DC.
This module covers the relationships between current and voltage; resistance in a series circuit; how to determine the values of current, voltage, resistance, and power in resistive series circuits; the effects of source internal resistance; and an introduction to the troubleshooting of series circuits. This module is divided into five lessons:…
Optimal Cooperative Management of Energy Storage Systems to Deal with Over- and Under-Voltages
DEFF Research Database (Denmark)
Mokhtari, Ghassem; Nourbakhsh, Ghavameddin; Anvari-Moghaddam, Amjad
2017-01-01
This paper presents an optimal cooperative voltage control approach, which coordinates storage units in a distribution network. This technique is developed for storage systems’ active power management with a local strategy to provide robust voltage control and a distributed strategy to deliver op...
Power System Stability Using Decentralized Under Frequency and Voltage Load Shedding
DEFF Research Database (Denmark)
Hoseinzadeh, Bakhtyar; Silva, Filipe Faria Da; Bak, Claus Leth
2014-01-01
information to shed the loads with higher voltage decay first. Therefore, this approach deals with coordination of voltage and frequency information instead of independent methods. Numerical simulations which are carried out in DigSilent PowerFactory software confirm the efficiency of proposed methodology...
Lower power by voltage stacking : a fine-grained system design approach
Blutman, K.; Kapoor, A.; Martinez, J.G.; Fatemi, S.H.; Pineda de Gyvez, J.
2016-01-01
Stacking voltage domains on top of each other is a design approach that is getting the attention of engineering communities due to the implicit high efficiency of the power delivery. Previous works have shown voltage stacking at the core level only. In this paper we present a more involved approach
Voltage protection scheme for MG sets used to drive inductive energy storage systems
International Nuclear Information System (INIS)
Campen, G.L.; Easter, R.B.
1977-01-01
A recent tokamak proposal at ORNL called for MG (motor-generator) sets to drive the ohmic heating (OH] coil, which was to be subjected to 20 kV immediately after coil charge-up to initiate the experiment. Since most rotating machinery is inherently low voltage, including the machines available at ORNL, a mechanism was necessary to isolate the generators from the high voltage portions of the circuit before the appearance of this voltage. It is not the expected 20 kV at the coil that causes difficulty, because the main interrupting switch handles this. The voltage induced in the armature due to di/dt and the possibility of faults are the greatest causes for concern and are responsible for the complexity of the voltage protection scheme, which must accommodate any possible combination of fault time and location. Such a protection scheme is presented in this paper
Methods and Strategies for Overvoltage Prevention in Low Voltage Distribution Systems with PV
DEFF Research Database (Denmark)
Hashemi Toghroljerdi, Seyedmostafa; Østergaard, Jacob
2016-01-01
to handle a high share of PV power. This paper provides an in-depth review of methods and strategies proposed to prevent overvoltage in LV grids with PV, and discusses the effectiveness, advantages, and disadvantages of them in detail. Based on the mathematical framework presented in the paper......, the overvoltage caused by high PV penetration is described, solutions to facilitate higher PV penetration are classified, and their effectiveness, advantages, and disadvantages are illustrated. The investigated solutions include the grid reinforcement, electrical energy storage application, reactive power...... absorption by PV inverters, application of active medium voltage to low voltage (MV/LV) transformers, active power curtailment, and demand response (DR). Coordination between voltage control units by localized, distributed, and centralized voltage control methods is compared using the voltage sensitivity...