International Nuclear Information System (INIS)
Joo, Hyung Kook; Noh, Jae Man; Lee, Hyung Chul; Yoo, Jae Woon
2006-01-01
In this report, we verified the NUREC code transient calculation capability using OECD NEA/US NRC PWR MOX/UO2 Core Transient Benchmark Problem. The benchmark problem consists of Part 1, a 2-D problem with given T/H conditions, Part 2, a 3-D problem at HFP condition, Part 3, a 3-D problem at HZP condition, and Part 4, a transient state initiated by a control rod ejection at HZP condition in Part 3. In Part 1, the results of NUREC code agreed well with the reference solution obtained from DeCART calculation except for the pin power distributions at the rodded assemblies. In Part 2, the results of NUREC code agreed well with the reference DeCART solutions. In Part 3, some results of NUREC code such as critical boron concentration and core averaged delayed neutron fraction agreed well with the reference PARCS 2G solutions. But the error of the assembly power at the core center was quite large. The pin power errors of NUREC code at the rodded assemblies was much smaller the those of PARCS code. The axial power distribution also agreed well with the reference solution. In Part 4, the results of NUREC code agreed well with those of PARCS 2G code which was taken as the reference solution. From the above results we can conclude that the results of NUREC code for steady states and transient states of the MOX loaded LWR core agree well with those of the other codes
Current interruption transients calculation
Peelo, David F
2014-01-01
Provides an original, detailed and practical description of current interruption transients, origins, and the circuits involved, and how they can be calculated Current Interruption Transients Calculationis a comprehensive resource for the understanding, calculation and analysis of the transient recovery voltages (TRVs) and related re-ignition or re-striking transients associated with fault current interruption and the switching of inductive and capacitive load currents in circuits. This book provides an original, detailed and practical description of current interruption transients, origins,
Transient anisotropic magnetic field calculation
International Nuclear Information System (INIS)
Jesenik, Marko; Gorican, Viktor; Trlep, Mladen; Hamler, Anton; Stumberger, Bojan
2006-01-01
For anisotropic magnetic material, nonlinear magnetic characteristics of the material are described with magnetization curves for different magnetization directions. The paper presents transient finite element calculation of the magnetic field in the anisotropic magnetic material based on the measured magnetization curves for different magnetization directions. For the verification of the calculation method some results of the calculation are compared with the measurement
A COMETHE version with transient capability
International Nuclear Information System (INIS)
Vliet, J. van; Lebon, G.; Mathieu, P.
1980-01-01
A version of the COMETHE code is under development to simulate transient situations. This paper focuses on some aspects of the transient heat transfer models. Initially the coupling between transient heat transfer and other thermomechanical models is discussed. An estimation of the thermal characteristic times shows that the cladding temperatures are often in quasi-steady state. In order to reduce the computing time, calculations are therefore switched from a transient to a quasi-static numerical procedure as soon as such a quasi-equilibrium is detected. The temperature calculation is performed by use of the Lebon-Lambermont restricted variational principle, with piecewise polynoms as trial functions. The method has been checked by comparison with some exact results and yields good agreement for transient as well as for quasi-static situations. This method therefore provides a valuable tool for the simulation of the transient behaviour of nuclear reactor fuel rods. (orig.)
Transient analysis capabilities at ABB-CE
International Nuclear Information System (INIS)
Kling, C.L.
1992-01-01
The transient capabilities at ABB-Combustion Engineering (ABB-CE) Nuclear Power are a function of the computer hardware and related network used, the computer software that has evolved over the years, and the commercial technical exchange agreements with other related organizations and customers. ABB-CEA is changing from a mainframe/personal computer network to a distributed workstation/personal computer local area network. The paper discusses computer hardware, mainframe computing, personal computers, mainframe/personal computer networks, workstations, transient analysis computer software, design/operation transient analysis codes, safety (licensed) analysis codes, cooperation with ABB-Atom, and customer support
Energy Technology Data Exchange (ETDEWEB)
Jaeger, Wadim; Manes, Jorge Perez; Imke, Uwe; Escalante, Javier Jimenez; Espinoza, Victor Sanchez, E-mail: victor.sanchez@kit.edu
2013-10-15
Highlights: • Simulation of BFBT turbine and pump transients at multiple scales. • CFD, sub-channel and system codes are used for the comparative study. • Heat transfer models are compared to identify difference between the code predictions. • All three scales predict results in good agreement to experiment. • Sub cooled boiling models are identified as field for future research. -- Abstract: The Institute for Neutron Physics and Reactor Technology (INR) at the Karlsruhe Institute of Technology (KIT) is involved in the validation and qualification of modern thermo hydraulic simulations tools at various scales. In the present paper, the prediction capabilities of four codes from three different scales – NEPTUNE{sub C}FD as fine mesh computational fluid dynamics code, SUBCHANFLOW and COBRA-TF as sub channels codes and TRACE as system code – are assessed with respect to their two-phase flow modeling capabilities. The subject of the investigations is the well-known and widely used data base provided within the NUPEC BFBT benchmark related to BWRs. Void fraction measurements simulating a turbine and a re-circulation pump trip are provided at several axial levels of the bundle. The prediction capabilities of the codes for transient conditions with various combinations of boundary conditions are validated by comparing the code predictions with the experimental data. In addition, the physical models of the different codes are described and compared to each other in order to explain the different results and to identify areas for further improvements.
Verification and validation of COBRA-SFS transient analysis capability
International Nuclear Information System (INIS)
Rector, D.R.; Michener, T.E.; Cuta, J.M.
1998-05-01
This report provides documentation of the verification and validation testing of the transient capability in the COBRA-SFS code, and is organized into three main sections. The primary documentation of the code was published in September 1995, with the release of COBRA-SFS, Cycle 2. The validation and verification supporting the release and licensing of COBRA-SFS was based solely on steady-state applications, even though the appropriate transient terms have been included in the conservation equations from the first cycle. Section 2.0, COBRA-SFS Code Description, presents a capsule description of the code, and a summary of the conservation equations solved to obtain the flow and temperature fields within a cask or assembly model. This section repeats in abbreviated form the code description presented in the primary documentation (Michener et al. 1995), and is meant to serve as a quick reference, rather than independent documentation of all code features and capabilities. Section 3.0, Transient Capability Verification, presents a set of comparisons between code calculations and analytical solutions for selected heat transfer and fluid flow problems. Section 4.0, Transient Capability Validation, presents comparisons between code calculations and experimental data obtained in spent fuel storage cask tests. Based on the comparisons presented in Sections 2.0 and 3.0, conclusions and recommendations for application of COBRA-SFS to transient analysis are presented in Section 5.0
RIA testing capability of the transient reactor test facility
International Nuclear Information System (INIS)
Crawford, D.C.; Swanson, R.W.
1999-01-01
The advent of high-burnup fuel implementation in LWRs has generated international interest in high-burnup LWR fuel performance. Recent testing under simulated RIA conditions has demonstrated that certain fuel designs fail at peak fuel enthalpy values that are below existing regulatory criteria. Because many of these tests were performed with non-prototypically aggressive test conditions (i.e., with power pulse widths less than 10 msec FWHM and with non-protoypic coolant configurations), the results (although very informative) do not indisputably identify failure thresholds and fuel behavior. The capability of the TREAT facility to perform simulated RIA tests with prototypic test conditions is currently being evaluated by ANL personnel. TREAT was designed to accommodate test loops and vehicles installed for in-pile transient testing. During 40 years of TREAT operation and fuel testing and evaluation, experimenters have been able to demonstrate and determine the transient behavior of several types of fuel under a variety of test conditions. This experience led to an evolution of test methodology and techniques which can be employed to assess RIA behavior of LWR fuel. A pressurized water loop that will accommodate RIA testing of LWR and CANDU-type fuel has completed conceptual design. Preliminary calculations of transient characteristics and energy deposition into test rods during hypothetical TREAT RIA tests indicate that with the installation of a pressurized water loop, the facility is quite capable of performing prototypic RIA testing. Typical test scenarios indicate that a simulated RIA with a 72 msec FWHM pulse width and energy deposition of 1200 kJ/kg (290 cal/gm) is possible. Further control system enhancements would expand the capability to pulse widths as narrow as 40 msec. (author)
Current capabilities of transient two-phase flow instruments
International Nuclear Information System (INIS)
Solbrig, C.W.; Kondic, N.N.
1979-01-01
The measurement of two phase flow phenomena in transient conditions representative of a Loss-of-Coolant Accident requires the use of sophisticated instruments and the further development of other instruments. Measurements made in large size pipes are often flow regime dependent. The flow regimes encountered depend upon the system geometry, transient effects, heat transfer, etc. The geometries in which these measurements must be made, the instruments which are currently used, new instruments being developed, the facilities used to calibrate these instruments, and the improvements which must be made to measurement capabilities are described
MCNP capabilities for nuclear well logging calculations
International Nuclear Information System (INIS)
Forster, R.A.; Little, R.C.; Briesmeister, J.F.; Hendricks, J.S.
1990-01-01
The Los Alamos Radiation Transport Code System (LARTCS) consists of state-of-the-art Monte Carlo and discrete ordinates transport codes and data libraries. This paper discusses how the general-purpose continuous-energy Monte Carlo code MCNP (Monte Carlo neutron photon), part of the LARTCS, provides a computational predictive capability for many applications of interest to the nuclear well logging community. The generalized three-dimensional geometry of MCNP is well suited for borehole-tool models. SABRINA, another component of the LARTCS, is a graphics code that can be used to interactively create a complex MCNP geometry. Users can define many source and tally characteristics with standard MCNP features. The time-dependent capability of the code is essential when modeling pulsed sources. Problems with neutrons, photons, and electrons as either single particle or coupled particles can be calculated with MCNP. The physics of neutron and photon transport and interactions is modeled in detail using the latest available cross-section data
Presentation of geometries and transient results of TRAC-calculations
International Nuclear Information System (INIS)
Lutz, A.; Lang, U.; Ruehle, R.
1985-02-01
The computer code TRAC is used to analyze the transient behaviour of nuclear reactors. The input of a TRAC-Calculation, as well as the produced result files serve for the graphical presentation of the geometries and transient results. This supports the search for errors during input generation and the understanding of complex processes by dynamic presentation of calculational result in colour. (orig.) [de
Calculation of transients in WWER power plant
International Nuclear Information System (INIS)
Macek, J.; Kyncl, M.
1981-01-01
A mathematical model is described for the computation of transient processes in a nuclear power plant as is the DYNAMIKA computer program. The program is used for computing two accident variants: rupture of the main steam collector and a failure of the main circulating pump. (H.S.)
International Nuclear Information System (INIS)
Buckner, M.R.; Hostetler, D.E.; Anderson, M.M.; Dodds, H.L.
1977-01-01
GRASS is a three-dimensional, coupled neutronic and engineering code for analysis of the radioisotope production reactors at the Savannah River Plant. The capabilities of GRASS are reviewed with emphasis on recent additions to model accident conditions involving the transport of molten fuel material and to accurately characterize neutronic and engineering feedback. The general application of GRASS to the Savannah River reactors is discussed, and results are presented for the analyses of severla reactor transient calculations
User effects on the transient system code calculations. Final report
International Nuclear Information System (INIS)
Aksan, S.N.; D'Auria, F.
1995-01-01
Large thermal-hydraulic system codes are widely used to perform safety and licensing analyses of nuclear power plants to optimize operational procedures and the plant design itself. Evaluation of the capabilities of these codes are accomplished by comparing the code predictions with the measured experimental data obtained from various types of separate effects and integral test facilities. In recent years, some attempts have been made to establish methodologies to evaluate the accuracy and the uncertainty of the code predictions and consequently judgement on the acceptability of the codes. In none of the methodologies has the influence of the code user on the calculated results been directly addressed. In this paper, the results of the investigations on the user effects for the thermal-hydraulic transient system codes is presented and discussed on the basis of some case studies. The general findings of the investigations show that in addition to user effects, there are other reasons that affect the results of the calculations and which are hidden under user effects. Both the hidden factors and the direct user effects are discussed in detail and general recommendations and conclusions are presented to control and limit them
THEBES: a thermal hydraulic code for the calculation of transient two phase flow in bundle geometry
International Nuclear Information System (INIS)
Camous, F.
1983-01-01
The three dimensional thermal hydraulic code THEBES, capable to calculate transient boiling of sodium in rod bundles is described here. THEBES, derived from the transient single phase code SABRE-2A, was developed in CADARACHE by the SIES to analyse the SCARABEE N loss of flow experiments. This paper also presents the results of tests which were performed against various types of experiments: (1) transient boiling in a 7 pin bundle simulating a partial blockage at the bottom of a subassembly (rapid transient SCARABEE 7.2 experiment), (2) transient boiling in a 7 pin bundle simulating a coolant coast down (slow transient SCARABEE 7.3 experiment), (3) steady local and generalised boiling in a 19 pin bundle (GR 19 I experiment), (4) transient boiling in a 19 pin bundle simulating a coolant coast down (GR 19 I experiment), (5) steady local boiling in a 37 pin bundle with internal blockage (MOL 7C experiment). Excellent agreement was found between calculated and experimental results for these different situations. Our conclusion is that THEBES is able to calculate transient boiling of sodium in rod bundles in a quite satisfying way
Energy Technology Data Exchange (ETDEWEB)
Laureau, A., E-mail: laureau.axel@gmail.com; Heuer, D.; Merle-Lucotte, E.; Rubiolo, P.R.; Allibert, M.; Aufiero, M.
2017-05-15
Highlights: • Neutronic ‘Transient Fission Matrix’ approach coupled to the CFD OpenFOAM code. • Fission Matrix interpolation model for fast spectrum homogeneous reactors. • Application for coupled calculations of the Molten Salt Fast Reactor. • Load following, over-cooling and reactivity insertion transient studies. • Validation of the reactor intrinsic stability for normal and accidental transients. - Abstract: In this paper we present transient studies of the Molten Salt Fast Reactor (MSFR). This generation IV reactor is characterized by a liquid fuel circulating in the core cavity, requiring specific simulation tools. An innovative neutronic approach called “Transient Fission Matrix” is used to perform spatial kinetic calculations with a reduced computational cost through a pre-calculation of the Monte Carlo spatial and temporal response of the system. Coupled to this neutronic approach, the Computational Fluid Dynamics code OpenFOAM is used to model the complex flow pattern in the core. An accurate interpolation model developed to take into account the thermal hydraulics feedback on the neutronics including reactivity and neutron flux variation is presented. Finally different transient studies of the reactor in normal and accidental operating conditions are detailed such as reactivity insertion and load following capacities. The results of these studies illustrate the excellent behavior of the MSFR during such transients.
International Nuclear Information System (INIS)
Laureau, A.; Heuer, D.; Merle-Lucotte, E.; Rubiolo, P.R.; Allibert, M.; Aufiero, M.
2017-01-01
Highlights: • Neutronic ‘Transient Fission Matrix’ approach coupled to the CFD OpenFOAM code. • Fission Matrix interpolation model for fast spectrum homogeneous reactors. • Application for coupled calculations of the Molten Salt Fast Reactor. • Load following, over-cooling and reactivity insertion transient studies. • Validation of the reactor intrinsic stability for normal and accidental transients. - Abstract: In this paper we present transient studies of the Molten Salt Fast Reactor (MSFR). This generation IV reactor is characterized by a liquid fuel circulating in the core cavity, requiring specific simulation tools. An innovative neutronic approach called “Transient Fission Matrix” is used to perform spatial kinetic calculations with a reduced computational cost through a pre-calculation of the Monte Carlo spatial and temporal response of the system. Coupled to this neutronic approach, the Computational Fluid Dynamics code OpenFOAM is used to model the complex flow pattern in the core. An accurate interpolation model developed to take into account the thermal hydraulics feedback on the neutronics including reactivity and neutron flux variation is presented. Finally different transient studies of the reactor in normal and accidental operating conditions are detailed such as reactivity insertion and load following capacities. The results of these studies illustrate the excellent behavior of the MSFR during such transients.
MCNP Perturbation Capability for Monte Carlo Criticality Calculations
International Nuclear Information System (INIS)
Hendricks, J.S.; Carter, L.L.; McKinney, G.W.
1999-01-01
The differential operator perturbation capability in MCNP4B has been extended to automatically calculate perturbation estimates for the track length estimate of k eff in MCNP4B. The additional corrections required in certain cases for MCNP4B are no longer needed. Calculating the effect of small design changes on the criticality of nuclear systems with MCNP is now straightforward
Calculation of Lightning Transient Responses on Wind Turbine Towers
Directory of Open Access Journals (Sweden)
Xiaoqing Zhang
2013-01-01
Full Text Available An efficient method is proposed in this paper for calculating lightning transient responses on wind turbine towers. In the proposed method, the actual tower body is simplified as a multiconductor grid in the shape of cylinder. A set of formulas are given for evaluating the circuit parameters of the branches in the multiconductor grid. On the basis of the circuit parameters, the multiconductor grid is further converted into an equivalent circuit. The circuit equation is built in frequency-domain to take into account the effect of the frequency-dependent characteristic of the resistances and inductances on lightning transients. The lightning transient responses can be obtained by using the discrete Fourier transform with exponential sampling to take the inverse transform of the frequency-domain solution of the circuit equation. A numerical example has been given for examining the applicability of the proposed method.
Improvement of RETRAN-MASTER-TORC transient capability and coupling optimization
International Nuclear Information System (INIS)
Cho, J. Y.; Song, J. S.; Joo, H. G.; Seo, K. W.; Whang, D. H.; Lee, C. C.; Zee, S. Q.
2003-11-01
This work is to improve MASTER-TORC transient calculation capability by complementing the previously developed consolidated code system RETRAN- MASTER-TORC, and to reduce the computing time by coupling optimization. The coupling soundness and optimization performance of the consolidated code system are evaluated by solving a YGN3 control bank ejection accident and the OECD Main Steam Line Break(MSLB) benchmark problems. The YGN3 control bank ejection accident is analyzed by the MASTER-TORC system. Most of all results including the transient core power, peak power and time are similar with those from the MASTER-COBRA system. In the computing time, the MASTER- TORC system is proved to be same as the MASTER-COBRA system, which means the coupling is sound and well-optimized. In the analysis of the OECD MSLB benchmark problem, the RETRAN-MASTER-TORC system shows the very similar results with the RETRAN-MASTER-COBRA system. However, minor differences due to fuel conductivity and thermal capacity model are noticed. In TORC, these parameters are treated as constants, while they are modeled as temperature dependent functions in COBRA. Therefore, in the future, TORC need to complement the temperature dependent thermal properties for accurate fuel and cladding temperature calculation. In the computing time for this problem, RETRAN-MASTER-TORC system shows a little bit faster than COBRA case
Available transfer capability calculation considering voltage stability margin
International Nuclear Information System (INIS)
Pan, Xiong; Xu, Guoyu
2005-01-01
To make the electricity trades carry out successfully, the calculation of available transfer capability (ATC) must coordinate the relationship between the security and economic benefits. In this paper, a model for ATC calculations accorded with trade-off mechanism in electricity market was set up. The impact of branch outage contingency on the static voltage stability margin was analyzed, and contingency ranking was performed through sensitivity indices of branch flows with respect to the loading margin. Optimal power flow based on primal-dual interior point method was applied to obtain ATC when the N-1 security constraints were included. The calculation results of IEEE 30-bus and IEEE 118-bus systems show that the proposed model and method are valid. (author) (N-1 security constraints; Electricity market; Available transfer capability; Optimal power flow; Voltage stability)
Uncertainty and sensitivity analysis applied to coupled code calculations for a VVER plant transient
International Nuclear Information System (INIS)
Langenbuch, S.; Krzykacz-Hausmann, B.; Schmidt, K. D.
2004-01-01
The development of coupled codes, combining thermal-hydraulic system codes and 3D neutron kinetics, is an important step to perform best-estimate plant transient calculations. It is generally agreed that the application of best-estimate methods should be supplemented by an uncertainty and sensitivity analysis to quantify the uncertainty of the results. The paper presents results from the application of the GRS uncertainty and sensitivity method for a VVER-440 plant transient, which was already studied earlier for the validation of coupled codes. For this application, the main steps of the uncertainty method are described. Typical results of the method applied to the analysis of the plant transient by several working groups using different coupled codes are presented and discussed The results demonstrate the capability of an uncertainty and sensitivity analysis. (authors)
Calculation of locomotive traction force in transient rolling contact
Directory of Open Access Journals (Sweden)
Voltr P.
2017-06-01
Full Text Available To represent thewheel-rail contact in numerical simulations of rail vehicles, simplified models (Fastsim, Pola´ch etc. are usually employed. These models are designed for steady rolling only, which is perfectly suitable in many cases. However, it is shown to be limiting for simulations at very low vehicle speeds, and therefore it does not actually allow simulation of vehicle running at arbitrarily variable speed. The simplified model of transient rolling, which involves calculation of the stress distribution in the discretised contact area, overcomes this disadvantage but might be unnecessarily complex for more simple simulations. In this paper, an approximative creep force computation method for transient rolling is presented. Its purpose is not to study the transient phenomena themselves but provide a simple and readily available way to prevent incorrect results of the numerical simulation when the vehicle speed approaches zero. The proper function of the proposed method is demonstrated by a simulation of start-up and interrupted sliding of a four-axle locomotive.
FLATT - a computer programme for calculating flow and temperature transients in nuclear fuels
International Nuclear Information System (INIS)
Venkat Raj, V.; Koranne, S.M.
1976-01-01
FLATT is a computer code written in Fortran language for BESM-6 computer. The code calculates the flow transients in the coolant circuit of a nuclear reactor, caused by pump failure, and the consequent temperature transients in the fuel, clad, and the coolant. In addition any desired flow transient can be fed into the programme and the resulting temperature transients can be calculated. A case study is also presented. (author)
On the intrinsic transient capability and limitations of solid oxide fuel cell systems
Mueller, F; Jabbari, F; Brouwer, J
2009-01-01
The intrinsic transient performance capability and limitation of integrated solid oxide fuel cell (SOFC) systems is evaluated based on the system balance-of-plant response and fuel cell operating requirements (i.e., allowable deviation from nominal operation). Specifically, non-dimensional relations are derived from conservation principles that quantify the maximum instantaneous current increase that a solid oxide fuel cell system can safely manage based on (1) the desired fuel cell operating...
A nonlinear analytic function expansion nodal method for transient calculations
Energy Technology Data Exchange (ETDEWEB)
Joo, Han Gyn; Park, Sang Yoon; Cho, Byung Oh; Zee, Sung Quun [Korea Atomic Energy Research Institute, Taejon (Korea, Republic of)
1998-12-31
The nonlinear analytic function expansion nodal (AFEN) method is applied to the solution of the time-dependent neutron diffusion equation. Since the AFEN method requires both the particular solution and the homogeneous solution to the transient fixed source problem, the derivation of the solution method is focused on finding the particular solution efficiently. To avoid complicated particular solutions, the source distribution is approximated by quadratic polynomials and the transient source is constructed such that the error due to the quadratic approximation is minimized, In addition, this paper presents a new two-node solution scheme that is derived by imposing the constraint of current continuity at the interface corner points. The method is verified through a series of application to the NEACRP PWR rod ejection benchmark problems. 6 refs., 2 figs., 1 tab. (Author)
A nonlinear analytic function expansion nodal method for transient calculations
Energy Technology Data Exchange (ETDEWEB)
Joo, Han Gyn; Park, Sang Yoon; Cho, Byung Oh; Zee, Sung Quun [Korea Atomic Energy Research Institute, Taejon (Korea, Republic of)
1999-12-31
The nonlinear analytic function expansion nodal (AFEN) method is applied to the solution of the time-dependent neutron diffusion equation. Since the AFEN method requires both the particular solution and the homogeneous solution to the transient fixed source problem, the derivation of the solution method is focused on finding the particular solution efficiently. To avoid complicated particular solutions, the source distribution is approximated by quadratic polynomials and the transient source is constructed such that the error due to the quadratic approximation is minimized, In addition, this paper presents a new two-node solution scheme that is derived by imposing the constraint of current continuity at the interface corner points. The method is verified through a series of application to the NEACRP PWR rod ejection benchmark problems. 6 refs., 2 figs., 1 tab. (Author)
The calculation of dryout during flow and pressure transients
International Nuclear Information System (INIS)
James, P.W.; Whalley, P.B.
1981-01-01
The method for predicting dryout in a round tube by means of an annular flow model (Whalley et al 1974) is extended to cover the case where both inlet mass flux and pressure are time-dependent. The qualitative effects of an inlet pressure transient are assessed by performing a 'numerical experiment' and it is found that the predictions of the model represent reasonable physical trends. The relative merits of wo numerical solution schemes are also discussed
Development of an Aeroelastic Modeling Capability for Transient Nozzle Side Load Analysis
Wang, Ten-See; Zhao, Xiang; Zhang, Sijun; Chen, Yen-Sen
2013-01-01
Lateral nozzle forces are known to cause severe structural damage to any new rocket engine in development during test. While three-dimensional, transient, turbulent, chemically reacting computational fluid dynamics methodology has been demonstrated to capture major side load physics with rigid nozzles, hot-fire tests often show nozzle structure deformation during major side load events, leading to structural damages if structural strengthening measures were not taken. The modeling picture is incomplete without the capability to address the two-way responses between the structure and fluid. The objective of this study is to develop a coupled aeroelastic modeling capability by implementing the necessary structural dynamics component into an anchored computational fluid dynamics methodology. The computational fluid dynamics component is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, while the computational structural dynamics component is developed in the framework of modal analysis. Transient aeroelastic nozzle startup analyses of the Block I Space Shuttle Main Engine at sea level were performed. The computed results from the aeroelastic nozzle modeling are presented.
Version of ORIGEN2 with automated sensitivity-calculation capability
International Nuclear Information System (INIS)
Worley, B.A.; Wright, R.Q.; Pin, F.G.
1986-01-01
ORIGEN2 is a widely used point-depletion and radioactive-decay computer code for use in simulating nuclear fuel cycles and/or spent fuel characteristics. The code calculates the amount of each nuclide being considered in the problem at a specified number of times, and upon request, a database of conversion factors relating mass compositions to specific material characteristics is used to calculate and print the total nuclide-dependent radioactivity, thermal power, and toxicity, as well as absorption, fission, neutron emission, and photon emission rates. The purpose of this paper is to report on the availability of a version of ORIGEN2 that will calculate, on option the derivative of all responses with respect to any variable used in the code
Computer program TMOC for calculating of pressure transients in fluid filled piping networks
International Nuclear Information System (INIS)
Siikonen, T.
1978-01-01
The propagation of a pressure wave in fluid filles tubes is significantly affected by the pipe wall motion and vice versa. A computer code TMOC (Transients by the Method of Characteristics) is being developed for the analysis of the coupled fluid and pipe wall transients. Because of the structural feedback, the pressure can be calculated more accurately than in the programs commonly used. (author)
UN_PAT: a software for calculating transient grounding potential
Directory of Open Access Journals (Sweden)
Johny Hernán Montaña
2006-09-01
Full Text Available This paper presents results from work done at the National University of Colombia and from a PhD thesis written there. This work was aimed at implementing software for analysing the transient behaviour of any configuration of grounding system buried in lineal, homogeneous and isotropic soil. The hybrid electromagnetic model (HEM was used because it presents high versatility and low computation time. The UN_PAT software was written in C++; it used free libraries with the aim of being free software so that it could be modified and improved in future work. The software results were validated with other software, with results from another analysis model and experimental results; some of these comparisons are given in this paper.
Blow.MOD2: a program for blowdown transient calculations
International Nuclear Information System (INIS)
Doval, A.
1990-01-01
The BLOW.MOD2 program has been developed to calculate the blowdown phase in a pressurized vessel after a break/valve is opened. It is a one volume model where break height and flow area are specified. Moody critical flow model was adopted under saturation conditions for flow calculation through the break. Heat transfer from structures and internals have been taken into account. Long term depressurization results and a more complex model are compared satisfactorily. (Author)
Air ingression calculations for selected plant transients using MELCOR
International Nuclear Information System (INIS)
Kmetyk, L.N.
1994-01-01
Two sets of MELCOR calculations have been completed studying the effects of air ingression on the consequences of various severe accident scenarios. One set of calculations analyzed a station blackout with surge line failure prior to vessel breach, starting from nominal operating conditions; the other set of calculations analyzed a station blackout occurring during shutdown (refueling) conditions. Both sets of analyses were for the Surry plant, a three-loop Westinghouse PWR. For both accident scenarios, a basecase calculation was done, and then repeated with air ingression from containment into the core region following core degradation and vessel failure. In addition to the two sets of analyses done for this program, a similar air-ingression sensitivity study was done as part of a low-power/shutdown PRA, with results summarized here; that PRA study also analyzed a station blackout occurring during shutdown (refueling) conditions, but for the Grand Gulf plant, a BWR/6 with Mark III containment. These studies help quantify the amount of air that would have to enter the core region to have a significant impact on the severe accident scenario, and demonstrate that one effect, of air ingression is substantial enhancement of ruthenium release. These calculations also show that, while the core clad temperatures rise more quickly due to oxidation with air rather than steam, the core also degrades and relocates more quickly, so that no sustained, enhanced core heatup is predicted to occur with air ingression
International Nuclear Information System (INIS)
Domijan, A.D. Jr.; Emami, M.V.
1990-01-01
This paper reports on a simulation of a MHO distance relay developed to study the effect of its operation under various system conditions. Simulation is accomplished using a state space approach and a modeling technique using ElectroMagnetic Transient Program (Transient Analysis of Control Systems). Furthermore, simulation results are compared with those obtained in another independent study as a control, to validate the results. A data code for the practical utilization of this simulation is given
Sample problem calculations related to two-phase flow transients in a PWR relief-piping network
International Nuclear Information System (INIS)
Shin, Y.W.; Wiedermann, A.H.
1981-03-01
Two sample problems related with the fast transients of water/steam flow in the relief line of a PWR pressurizer were calculated with a network-flow analysis computer code STAC (System Transient-Flow Analysis Code). The sample problems were supplied by EPRI and are designed to test computer codes or computational methods to determine whether they have the basic capability to handle the important flow features present in a typical relief line of a PWR pressurizer. It was found necessary to implement into the STAC code a number of additional boundary conditions in order to calculate the sample problems. This includes the dynamics of the fluid interface that is treated as a moving boundary. This report describes the methodologies adopted for handling the newly implemented boundary conditions and the computational results of the two sample problems. In order to demonstrate the accuracies achieved in the STAC code results, analytical solutions are also obtained and used as a basis for comparison
A Coupled Calculation Suite for Atucha II Operational Transients Analysis
International Nuclear Information System (INIS)
Mazzantini, O.; Schivo, M.; Cesare, J.D.; Garbero, R.; Rivero, M.; Theler, G.
2011-01-01
While more than a decade ago reactor and thermal hydraulic calculations were tedious and often needed a lot of approximations and simplifications that forced the designers to take a very conservative approach, computational resources available nowadays allow engineers to cope with increasingly complex problems in a reasonable time. The use of best-estimate calculations provides tools to justify convenient engineering margins, reduces costs, and maximises economic benefits. In this direction, a suite of coupled best-estimate specific calculation codes was developed to analyse the behaviour of the Atucha II nuclear power plant in Argentina. The developed tool includes three-dimensional spatial neutron kinetics, a channel-level model of the core thermal hydraulics with subcooled boiling correlations, a one-dimensional model of the primary and secondary circuits including pumps, steam generators, heat exchangers, and the turbine with all their associated control loops, and a complete simulation of the reactor control, limitation, and protection system working in closed-loop conditions as a faithful representation of the real power plant. In the present paper, a description of the coupling scheme between the codes involved is given, and some examples of their application to Atucha II are shown
International Nuclear Information System (INIS)
Fineschi, F.; Vanini, P.
1997-01-01
The Department of Mechanical and Nuclear Constructions of the University of Pisa has developed a computer code, HOCRA, which is able to make an initial evaluation of the capability of catalytic recombiners to remove hydrogen from the atmosphere of the safety containments of nuclear reactors in accident conditions. The code allows the analysis of the average concentration transient of hydrogen in a generic compartment of a safety containment in a nuclear reactor. The software is structured into two groups. The first, mode-1, analyses the average concentration in all the free volume of the containment before a possible venting., whereas the second, mode-2, analyses the average concentration transient in a containment compartment, assuming input and output flow rates into and from the compartment itself The first part of this paper outlines the physical and mathematical model of the code, the second part reports calculations made for an advanced PWR in cooperation with ENEL. (author)
Institute of Scientific and Technical Information of China (English)
张寅平; 梁新刚; 江忆; 狄洪发; 宁志军
2000-01-01
Degree of mixing of composite material is defined and the condition of using the effective thermal diffusivity for calculating the transient thermal performance of composite material is studied. The analytical result shows that for a prescribed precision of temperature, there is a condition under which the transient temperature distribution in composite material can be calculated by using the effective thermal diffusivity. As illustration, for the composite material whose temperatures of both ends are constant, the condition is presented and the factors affecting the relative error of calculated temperature of composite materials by using effective thermal diffusivity are discussed.
Coupled Tort-TD/CTF Capability for high-fidelity LWR core calculations - 321
International Nuclear Information System (INIS)
Christienne, M.; Avramova, M.; Perin, Y.; Seubert, A.
2010-01-01
This paper describes the developed coupling scheme between TORT-TD and CTF. TORT-TD is a time-dependent 3D discrete ordinates neutron transport code. TORT-TD is utilized for high-fidelity reactor core neutronics calculations while CTF is providing the thermal-hydraulics feedback information. CTF is an improved version of the advanced thermal-hydraulic sub-channel code COBRA-TF, which is widely used for best-estimate evaluations of LWR safety margins. CTF is a transient code based on a separated flow representation of the two-phase flow. The coupled code TORT-TD/CTF allows 3D pin-by-pin analyses of transients in few energy groups and anisotropic scattering by solving the time-dependent transport equation using the unconditionally stable implicit method. Steady-state and transient test cases, based on the OECD/NRC PWR MOX/UO 2 Core Transient Benchmark, have been calculated. The steady state cases are based on a quarter core model while the transient test case models a control rod ejection transient in a small PWR mini-core fuel assembly arrangement. The obtained results with TORT-TD/CTF are verified by a code-to-code comparison with the previously developed NEM/CTF and TORT-TD/ATHLET coupled code systems. The performed comparative analysis indicates the applicability and high-fidelity potential of the TORT-TD/CTF coupling. (authors)
DEFF Research Database (Denmark)
Rasmussen, Claus P.; Krejbjerg, Kristian; Michelsen, Michael Locht
2006-01-01
Approaches are presented for reducing the computation time spent on flash calculations in compositional, transient simulations. In a conventional flash calculation, the majority of the simulation time is spent on stability analysis, even for systems far into the single-phase region. A criterion has...
SCANAIR a transient fuel performance code Part two: Assessment of modelling capabilities
Energy Technology Data Exchange (ETDEWEB)
Georgenthum, Vincent, E-mail: vincent.georgenthum@irsn.fr; Moal, Alain; Marchand, Olivier
2014-12-15
Highlights: • The SCANAIR code is devoted to the study of irradiated fuel rod behaviour during RIA. • The paper deals with the status of the code validation for PWR rods. • During the PCMI stage there is a good agreement between calculations and experiments. • The boiling crisis occurrence is rather well predicted. • The code assessment during the boiling crisis has still to be improved. - Abstract: In the frame of their research programmes on fuel safety, the French Institut de Radioprotection et de Sûreté Nucléaire develops the SCANAIR code devoted to the study of irradiated fuel rod behaviour during reactivity initiated accident. A first paper was focused on detailed modellings and code description. This second paper deals with the status of the code validation for pressurised water reactor rods performed thanks to the available experimental results. About 60 integral tests carried out in CABRI and NSRR experimental reactors and 24 separated tests performed in the PATRICIA facility (devoted to the thermal-hydraulics study) have been recalculated and compared to experimental data. During the first stage of the transient, the pellet clad mechanical interaction phase, there is a good agreement between calculations and experiments: the clad residual elongation and hoop strain of non failed tests but also the failure occurrence and failure enthalpy of failed tests are correctly calculated. After this first stage, the increase of cladding temperature can lead to the Departure from Nucleate Boiling. During the film boiling regime, the clad temperature can reach a very high temperature (>700 °C). If the boiling crisis occurrence is rather well predicted, the calculation of the clad temperature and the clad hoop strain during this stage have still to be improved.
Directory of Open Access Journals (Sweden)
U. Schneider
2009-01-01
Full Text Available The paper presents the structural application of a new thermal induced strain model for concrete – the TIS-Model. An advanced transient concrete model (ATCM is applied with the material model of the TIS-Model. The non-linear model comprises thermal strain, elastic strain, plastic strain and transient temperature strains, and load history modelling of restraint concrete structures subjected to fire.The calculations by finite element analysis (FEA were done using the SAFIR structural code. The FEA software was basically new with respect to the material modelling derived to use the new TIS-Model (as a transient model considers thermal induced strain. The equations of the ATCM consider a lot of capabilities, especially for considering irreversible effects of temperature on some material properties. By considering the load history during heating up, increasing load bearing capacity may be obtained due to higher stiffness of the concrete. With this model, it is possible to apply the thermal-physical behaviour of material laws for calculation of structures under extreme temperature conditions.A tunnel cross section designed and built by the cut and cover method is calculated with a tunnel fire curve. The results are compared with the results of a calculation with the model of the Eurocode 2 (EC2-Model. The effect of load history in highly loaded structures under fire load will be investigated.A comparison of this model with the ordinary calculation system of Eurocode 2 (EC2 shows that a better evaluation of the safety level was achieved with the new model. This opens a space for optimizing concrete structure design with transient temperature conditions up to 1000 °C.
Point kinetics improvements to evaluate three-dimensional effects in transients calculation
International Nuclear Information System (INIS)
Castellotti, U.
1987-01-01
A calculation method, which considers the flux axial perturbations in the parameters related to the reactivity within a point kinetics model, is described. The method considered uses axial factors of consideration which act on the thermohydraulic variables included in the reactivity calculation. The PUMA three-dimensional code as reference model for the comparisons, is used. The limitations inherent to the reactivity balance of the point models used in the transients calculation, are given. (Author)
Development of a transient calculation model for a closed sodium natural circulation loop
International Nuclear Information System (INIS)
Chang, Won Pyo; Ha, Kwi Seok; Jeong, Hae Yong; Heo, Sun; Lee, Yong Bum
2003-09-01
A natural circulation loop has usually adopted for a Liquid Metal Reactor (LMR) because of its high reliability. Up-rating of the current KALIMER capacity requires an additional PDRC to the existing PVCS to remove its decay heat under an accident. As the system analysis code currently used for LMR in Korea does not feature a stand alone capability to simulate a closed natural circulation loop, it is not eligible to be applied to PDRC. To supplement its limitation, a steady state calculation model had been developed during the first phase, and development of the transient model has successively carried out to close the present study. The developed model will then be coupled with the system analysis code, SSC-K to assess a long term cooling for the new conceptual design. The incompressibility assumption of sodium which allows the circuit to be modeled with a single loop flow, makes the model greatly simplified comparing with LWR. Some thermal-hydraulic models developed during this study can be effectively applied to other system analysis codes which require such component models, and the present development will also contribute to establishment of a code system for the LMR analysis
Audit calculation of the limiting CESSAR feedwater-line-break transient with RELAP5/MOD1
International Nuclear Information System (INIS)
Chung, K.S.; Kennedy, M.F.; Guttmann, J.
1983-01-01
Argonne National Laboratory (ANL) performed a series of audit calculations of the limiting FLB transient presented in Appendix 15B to the CESSAR FSAR, supported by a limited number of additional calculations to investigate the sensitivity of the results (in terms of peak primary reactor system pressure) to break area and reactor trip time. The latter calculations were performed to quantify potential benefits in crediting reactor tip on low steam generator downcomer water level, which occurs earlier than the trip shown in the limiting FSAR transient, which tripped on high pressurizer pressure. These calculations were performed to verify the break spectrum results presented by C-E and to insure that C-E did indeed analyze the limiting transient. All of the ANL calculations were performed with RELAP5/MOD1 (cycle 18) using an input deck developed at ANL from CESSAR plant data provided by C-E. In this paper we compare the results and provide insight into the generic behavior of a Feedwater Line Break transient
International Nuclear Information System (INIS)
Howarth, W.L.
1976-01-01
Sodium flow enters the CRBR inlet plenum via three loops or inlets. An empirical equation was developed to calculate transient temperatures in the CRBR inlet plenum from known loop flows and temperatures. The constants in the empirical equation were derived from 1/4 scale Inlet Plenum Model tests using water as the test fluid. The sodium temperature distribution was simulated by an electrolyte. Step electrolyte transients at 100 percent model flow were used to calculate the equation constants. Step electrolyte runs at 50 percent and 10 percent flow confirmed that the constants were independent of flow. Also, a transient was tested which varied simultaneously flow rate and electrolyte. Agreement of the test results with the empirical equation results was good which verifies the empirical equation
Influence of transient flow in the formation of condensate and in the calculation of steam line
International Nuclear Information System (INIS)
Bazzo, E.
1989-01-01
The piping design is analyzed in unsteady-state conditions, with the main goal of minimizing operational costs and initial investments of a plant. All heat losses are calculated by applying the control volume method. The results confirm the applicability of the method and show that the influence of the transient regime on the condensation rate and economical insulation thickness must be considered. (author)
Approximative calculation of transient short-circuit currents in power-systems
Energy Technology Data Exchange (ETDEWEB)
Heuck, K; Rosenberger, R; Dettmann, K D; Kegel, R
1986-08-01
The paper shows that it is approximatively possible to calculate the transient short-circuit currents for symmetrical and asymmetrical faults in power-systems. For that purpose a simple equivalent network is found. Its error of approximation is small. For the important maximum short-circuit current limits of error are pointed out compared to VDE 0102.
A calculation method for transient flow distribution of SCWR(CSR1000)
International Nuclear Information System (INIS)
Chen, Juan; Zhou, Tao; Chen, Jie; Liu, Liang; Muhammad, Ali Shahzad; Muhammad, Zeeshan Ali; Xia, Bangyang
2017-01-01
The supercritical water reactor CSR1000 is selected for the study. A parallel channel flow transient flow distribution module is developed, which is used for solving unsteady nonlinear equations. The incorporated programs of SCAC-CSR1000 are executed on normal and abnormal operating conditions. The analysis shows that: 1. Transient flow distribution can incorporate parallel channel flow calculation, with an error less than 0.1%; 2. After a total loss of coolant flow, the flow of each channel shows a downward trend; 3. In the event of introducing a traffic accident, the first coolant flow shows an increasing trend.
DYNREL - the reference calculation (coupled code utilization on analysis of RIA-transient)
International Nuclear Information System (INIS)
Strmensky, C.; Darilek, P.
2003-01-01
DYNREL is coupled code, comprising DYN3D and RELAP5 programs. The coupled code has been developed during four years. Now DYNREL is tested on selected RIA and thermo-hydraulic transient calculations. This material describes some results from selected RIA transient calculation (initiated by control rod movement). DYNREL modelled the whole nuclear reactors. The core is modeled as 313 or 349 independent thermo-hydraulic channels with 10 or 20 axial layers. Thermo-hydraulic part contains about 700 components that covered the six loops' model of nuclear power plant in detail. The calculated results are compared with DYN3D/M3, DYN3D/H1.1 results (Authors)
Calculation of a thermostressed state for drum-separator vessels in transient regimes
International Nuclear Information System (INIS)
Il'in, Yu.V.; Kazakova, T.Yu.; Parafilo, L.M.; Shcherbakov, S.I.
1979-01-01
The temperature regime and stressed state of the drum-separator vessel in the transient regime with alternating pressure and water level are investigated using calculations. The temperature fields are calculated by the alternating directions method. Stresses and deformations are calculated by the method of finite elements. The stressed state of the vessel is determined for a series of fixed time moments tausub(i), when the T(tausub(i), r, phi) temperature distribution and P(tausub(i)) internal pressure are known. The methods described are used while developing the calculation program for the temperatures and stressed state (FORTRAN, EC-1050). Given are the calculation results obtained using these programs for the processes following the safety system response at the first block of the Bilibinsk NPP and the processes of power regulation in the ''Sever-2'' facility. The comparison of the obtained calculated curves with the experimental data confirms fitness of the proposed calculated scheme for description of the real processes taking place in the drum-separator vessels in the transient regimes. It is emphasized that the given scheme of solution of the equations describing a thermostressed state of the drum-separator vessels can be used while estimating their operation capacity
Energy Technology Data Exchange (ETDEWEB)
Coste, D. [Commissariat a l' Energie Atomique, Saclay (France). Centre d' Etudes Nucleaires
1964-07-01
With a view to determining the changes occurring in gas reactors after cooling accidents, a calculation programme is established for unidimensional gas flows with pressure drops, heat exchanges and in certain cases blowing, in a reticulated lattice. Any schematization can be taken into account by the use of a set of indices. This programme, of which the FORTRAN list is given, is applied to particular cases of sudden pressure drops in the circuits. The results obtained are in good agreement with those obtained both from the graphical method using the characteristics and from experimental recorded data. (author) [French] En vue de determiner les evolutions des reacteurs a gaz apres accident de refroidissement, on etablit un programme de calcul pour les ecoulements gazeux unidimensionnels avec pertes de charge, echanges thermiques et eventuellement soufflage, en reseau maille. Toute schematisation peut etre prise en compte grace a un jeu d'indices. Ce programme, dont la liste FORTRAN est presentee, est applique a des cas particuliers de degonflage brutal de circuits. Ses resultats sont en bon accord, d'une part avec ceux de la methode graphique des caracteristiques, d'autre part avec des enregistrements experimentaux. (auteur)
Energy Technology Data Exchange (ETDEWEB)
Coste, D [Commissariat a l' Energie Atomique, Saclay (France). Centre d' Etudes Nucleaires
1964-07-01
With a view to determining the changes occurring in gas reactors after cooling accidents, a calculation programme is established for unidimensional gas flows with pressure drops, heat exchanges and in certain cases blowing, in a reticulated lattice. Any schematization can be taken into account by the use of a set of indices. This programme, of which the FORTRAN list is given, is applied to particular cases of sudden pressure drops in the circuits. The results obtained are in good agreement with those obtained both from the graphical method using the characteristics and from experimental recorded data. (author) [French] En vue de determiner les evolutions des reacteurs a gaz apres accident de refroidissement, on etablit un programme de calcul pour les ecoulements gazeux unidimensionnels avec pertes de charge, echanges thermiques et eventuellement soufflage, en reseau maille. Toute schematisation peut etre prise en compte grace a un jeu d'indices. Ce programme, dont la liste FORTRAN est presentee, est applique a des cas particuliers de degonflage brutal de circuits. Ses resultats sont en bon accord, d'une part avec ceux de la methode graphique des caracteristiques, d'autre part avec des enregistrements experimentaux. (auteur)
Applications of supercomputing and the utility industry: Calculation of power transfer capabilities
International Nuclear Information System (INIS)
Jensen, D.D.; Behling, S.R.; Betancourt, R.
1990-01-01
Numerical models and iterative simulation using supercomputers can furnish cost-effective answers to utility industry problems that are all but intractable using conventional computing equipment. An example of the use of supercomputers by the utility industry is the determination of power transfer capability limits for power transmission systems. This work has the goal of markedly reducing the run time of transient stability codes used to determine power distributions following major system disturbances. To date, run times of several hours on a conventional computer have been reduced to several minutes on state-of-the-art supercomputers, with further improvements anticipated to reduce run times to less than a minute. In spite of the potential advantages of supercomputers, few utilities have sufficient need for a dedicated in-house supercomputing capability. This problem is resolved using a supercomputer center serving a geographically distributed user base coupled via high speed communication networks
International Nuclear Information System (INIS)
Kazakov, E.K.; Chernukhina, G.M.
1974-01-01
Results of calculation of the temperature distribution in an annular fuel element at transient thermal conductivity and heat release values are given. The calculation has been carried out by the mesh technique with the third-order boundary conditions for the inner surface assumed and with heat fluxes and temperatures at the zone boundaries to be equal. Three variants of solving the problem of a stationary temperature field are considered for failed fuel elements with clad flaking or cracks. The results obtained show the nonuniformity of the fuel element temperature field to depend strongly on the perturbation parameter at transient thermal conductivity and heat release values. In case of can flaking at a short length, the core temperature rises quickly after flaking. While evaluating superheating, one should take into account the symmetry of can flaking [ru
Calculation of transient potential rise on the wind turbine struck by lightning.
Xiaoqing, Zhang
2014-01-01
A circuit model is proposed in this paper for calculating the transient potential rise on the wind turbine struck by lightning. The model integrates the blade, sliding contact site, and tower and grounding system of the wind turbine into an equivalent circuit. The lightning current path from the attachment point to the ground can be fully described by the equivalent circuit. The transient potential responses are obtained in the different positions on the wind turbine by solving the circuit equations. In order to check the validity of the model, the laboratory measurement is made with a reduced-scale wind turbine. The measured potential waveform is compared with the calculated one and a better agreement is shown between them. The practical applicability of the model is also examined by a numerical example of a 2 MW Chinese-built wind turbine.
International Nuclear Information System (INIS)
McKinnis, C.J.; Toor, P.M.
1985-01-01
In structural analysis, assimilation of material, geometry, and service history input parameters is very cumbersome. Quite often with changing service history and revised material properties and geometry, an analysis has to be repeated. To overcome the above mentioned difficulties, a computer program was developed to provide the capability to establish a computerized library of all material, geometry, and service history parameters for components. The program also has the capability to calculate the structural integrity based on the Arrhenius type equations, including the probability calculations. This unique combination of computerized input information storage and automated analysis procedure assures consistency, efficiency, and accuracy when the hardware integrity has to be reassessed
International Nuclear Information System (INIS)
Carpenter, K.H.
1976-11-01
A description is given of FORTRAN programs for transient eddy current calculations in thin, non-magnetic conductors using a perturbation-polynomial expansion technique. Basic equations are presented as well as flow charts for the programs implementing them. The implementation is in two steps--a batch program to produce an intermediate data file and interactive programs to produce graphical output. FORTRAN source listings are included for all program elements, and sample inputs and outputs are given for the major programs
Calculation and Simulation Study on Transient Stability of Power System Based on Matlab/Simulink
Directory of Open Access Journals (Sweden)
Shi Xiu Feng
2016-01-01
Full Text Available The stability of the power system is destroyed, will cause a large number of users power outage, even cause the collapse of the whole system, extremely serious consequences. Based on the analysis in single machine infinite system as an example, when at the f point two phase ground fault occurs, the fault lines on either side of the circuit breaker tripping resection at the same time,respectively by two kinds of calculation and simulation methods of system transient stability analysis, the conclusion are consistent. and the simulation analysis is superior to calculation analysis.
Seymour, David C.; Martin, Michael A.; Nguyen, Huy H.; Greene, William D.
2005-01-01
The subject of mathematical modeling of the transient operation of liquid rocket engines is presented in overview form from the perspective of engineers working at the NASA Marshall Space Flight Center. The necessity of creating and utilizing accurate mathematical models as part of liquid rocket engine development process has become well established and is likely to increase in importance in the future. The issues of design considerations for transient operation, development testing, and failure scenario simulation are discussed. An overview of the derivation of the basic governing equations is presented along with a discussion of computational and numerical issues associated with the implementation of these equations in computer codes. Also, work in the field of generating usable fluid property tables is presented along with an overview of efforts to be undertaken in the future to improve the tools use for the mathematical modeling process.
International Nuclear Information System (INIS)
Almeida, Jose Carlos S. de; Schirru, Roberto; Pereira, Claudio M.N.A.; Universidade Federal, Rio de Janeiro, RJ
2002-01-01
This work describes a possibilistic approach for transient identification based on the minimum centroids set method, proposed in previous work, optimized by genetic algorithm. The idea behind this method is to split the complex classification problem into small and simple ones, so that the performance in the classification can be increased. In order to accomplish that, a genetic algorithm is used to learn, from realistic simulated data, the optimized time partitions, which the robustness and correctness in the classification are maximized. The use of a possibilistic classification approach propitiates natural and consistent classification rules, leading naturally to a good heuristic to handle the 'don't know 'response, in case of unrecognized transient, which is fairly desirable in transient classification systems where safety is critical. Application of the proposed approach to a nuclear transient indentification problem reveals good capability of the genetic algorithm in learning optimized possibilistic classification rules for efficient diagnosis including 'don't know' response. Obtained results are shown and commented. (author)
TEMP: a computer code to calculate fuel pin temperatures during a transient
International Nuclear Information System (INIS)
Bard, F.E.; Christensen, B.Y.; Gneiting, B.C.
1980-04-01
The computer code TEMP calculates fuel pin temperatures during a transient. It was developed to accommodate temperature calculations in any system of axi-symmetric concentric cylinders. When used to calculate fuel pin temperatures, the code will handle a fuel pin as simple as a solid cylinder or as complex as a central void surrounded by fuel that is broken into three regions by two circumferential cracks. Any fuel situation between these two extremes can be analyzed along with additional cladding, heat sink, coolant or capsule regions surrounding the fuel. The one-region version of the code accurately calculates the solution to two problems having closed-form solutions. The code uses an implicit method, an explicit method and a Crank-Nicolson (implicit-explicit) method
Hextran-Smabre calculation of the VVER-1000 coolant transient benchmark
Energy Technology Data Exchange (ETDEWEB)
Elina Syrjaelahti; Anitta Haemaelaeinen [VTT Processes, P.O.Box 1604, FIN-02044 VTT (Finland)
2005-07-01
Full text of publication follows: The VVER-1000 Coolant Transient benchmark is intended for validation of couplings of the thermal hydraulic codes and three dimensional neutron kinetic core models. It concerns a switching on a main coolant pump when the other three main coolant pumps are in operation. Problem is based on experiment performed in Kozloduy NPP in Bulgaria. In addition to the real plant transient, two extreme scenarios concerning control rod ejection after switching on a main coolant pump were calculated. In VTT the three-dimensional advanced nodal code HEXTRAN is used for the core kinetics and dynamics, and thermohydraulic system code SMABRE as a thermal hydraulic model for the primary and secondary loop. Parallelly coupled HEXTRAN-SMABRE code has been in production use since early 90's, and it has been extensively used for analysis of VVER NPPs. The SMABRE input model is based on the standard VVER-1000 input used in VTT. Last plant specific modifications to the input model have been made in EU projects. The whole core calculation is performed in the core with HEXTRAN. Also the core model is based on earlier VVER-1000 models. Nuclear data for the calculation was specified in the benchmark. The paper outlines the input models used for both codes. Calculated results are introduced both for the coupled core system with inlet and outlet boundary conditions and for the whole plant model. Sensitivity studies have been performed for selected parameters. (authors)
Hextran-Smabre calculation of the VVER-1000 coolant transient benchmark
International Nuclear Information System (INIS)
Elina Syrjaelahti; Anitta Haemaelaeinen
2005-01-01
Full text of publication follows: The VVER-1000 Coolant Transient benchmark is intended for validation of couplings of the thermal hydraulic codes and three dimensional neutron kinetic core models. It concerns a switching on a main coolant pump when the other three main coolant pumps are in operation. Problem is based on experiment performed in Kozloduy NPP in Bulgaria. In addition to the real plant transient, two extreme scenarios concerning control rod ejection after switching on a main coolant pump were calculated. In VTT the three-dimensional advanced nodal code HEXTRAN is used for the core kinetics and dynamics, and thermohydraulic system code SMABRE as a thermal hydraulic model for the primary and secondary loop. Parallelly coupled HEXTRAN-SMABRE code has been in production use since early 90's, and it has been extensively used for analysis of VVER NPPs. The SMABRE input model is based on the standard VVER-1000 input used in VTT. Last plant specific modifications to the input model have been made in EU projects. The whole core calculation is performed in the core with HEXTRAN. Also the core model is based on earlier VVER-1000 models. Nuclear data for the calculation was specified in the benchmark. The paper outlines the input models used for both codes. Calculated results are introduced both for the coupled core system with inlet and outlet boundary conditions and for the whole plant model. Sensitivity studies have been performed for selected parameters. (authors)
Numerical Calculation of Transient Thermal Characteristics in Gas-Insulated Transmission Lines
Directory of Open Access Journals (Sweden)
Hongtao Li
2013-11-01
Full Text Available For further knowledge of the thermal characteristics in gas-insulated transmission lines (GILs installed above ground, a finite-element model coupling fluid field and thermal field is established, in which the corresponding assumptions and boundary conditions are given. Â Transient temperature rise processes of the GIL under the conditions of variable ambient temperature, wind velocity and solar radiation are respectively investigated. Equivalent surface convective heat transfer coefficient and heat flux boundary conditions are updated in the analysis process. Unlike the traditional finite element methods (FEM, the variability of the thermal properties with temperature is considered. The calculation results are validated by the tests results reported in the literature. The conclusion provides method and theory basis for the knowledge of transient temperature rise characteristics of GILs in open environment.
International Nuclear Information System (INIS)
Mueller, R.G.
1987-06-01
Due to the strong influence of vapour bubbles on the nuclear chain reaction, an exact calculation of neutron physics and thermal hydraulics in light water reactors requires consideration of subcooled boiling. To this purpose, in the present study a dynamic model is derived from the time-dependent conservation equations. It contains new methods for the time-dependent determination of evaporation and condensation heat flow and for the heat transfer coefficient in subcooled boiling. Furthermore, it enables the complete two-phase flow region to be treated in a consistent manner. The calculation model was verified using measured data of experiments covering a wide range of thermodynamic boundary conditions. In all cases very good agreement was reached. The results from the coupling of the new calculation model with a neutron kinetics program proved its suitability for the steady-state and transient calculation of reactor cores. (orig.) [de
Meyerhoff, Hauke S; Gehrer, Nina A
2017-01-01
In order to obtain a coherent representation of the outside world, auditory and visual information are integrated during human information processing. There is remarkable variance among observers in the capability to integrate auditory and visual information. Here, we propose that visuo-perceptual capabilities predict detection performance for audiovisually coinciding transients in multi-element displays due to severe capacity limitations in audiovisual integration. In the reported experiment, we employed an individual differences approach in order to investigate this hypothesis. Therefore, we measured performance in a useful-field-of-view task that captures detection performance for briefly presented stimuli across a large perceptual field. Furthermore, we measured sensitivity for visual direction changes that coincide with tones within the same participants. Our results show that individual differences in visuo-perceptual capabilities predicted sensitivity for the presence of audiovisually synchronous events among competing visual stimuli. To ensure that this correlation does not stem from superordinate factors, we also tested performance in an unrelated working memory task. Performance in this task was independent of sensitivity for the presence of audiovisually synchronous events. Our findings strengthen the proposed link between visuo-perceptual capabilities and audiovisual integration. The results also suggest that basic visuo-perceptual capabilities provide the basis for the subsequent integration of auditory and visual information.
Ding, Ming; Zhu, Qianlong
2016-01-01
Hardware protection and control action are two kinds of low voltage ride-through technical proposals widely used in a permanent magnet synchronous generator (PMSG). This paper proposes an innovative clustering concept for the equivalent modeling of a PMSG-based wind power plant (WPP), in which the impacts of both the chopper protection and the coordinated control of active and reactive powers are taken into account. First, the post-fault DC link voltage is selected as a concentrated expression of unit parameters, incoming wind and electrical distance to a fault point to reflect the transient characteristics of PMSGs. Next, we provide an effective method for calculating the post-fault DC link voltage based on the pre-fault wind energy and the terminal voltage dip. Third, PMSGs are divided into groups by analyzing the calculated DC link voltages without any clustering algorithm. Finally, PMSGs of the same group are equivalent as one rescaled PMSG to realize the transient equivalent modeling of the PMSG-based WPP. Using the DIgSILENT PowerFactory simulation platform, the efficiency and accuracy of the proposed equivalent model are tested against the traditional equivalent WPP and the detailed WPP. The simulation results show the proposed equivalent model can be used to analyze the offline electromechanical transients in power systems.
Time-dependent anisotropic distributed source capability in transient 3-d transport code tort-TD
International Nuclear Information System (INIS)
Seubert, A.; Pautz, A.; Becker, M.; Dagan, R.
2009-01-01
The transient 3-D discrete ordinates transport code TORT-TD has been extended to account for time-dependent anisotropic distributed external sources. The extension aims at the simulation of the pulsed neutron source in the YALINA-Thermal subcritical assembly. Since feedback effects are not relevant in this zero-power configuration, this offers a unique opportunity to validate the time-dependent neutron kinetics of TORT-TD with experimental data. The extensions made in TORT-TD to incorporate a time-dependent anisotropic external source are described. The steady state of the YALINA-Thermal assembly and its response to an artificial square-wave source pulse sequence have been analysed with TORT-TD using pin-wise homogenised cross sections in 18 prompt energy groups with P 1 scattering order and 8 delayed neutron groups. The results demonstrate the applicability of TORT-TD to subcritical problems with a time-dependent external source. (authors)
Development of a simplified calculational model for the transient core bowing effect
International Nuclear Information System (INIS)
Yokoo, Takeshi
1997-01-01
A simplified method to analyze the transient core radial deformation has been developed based on a model that calculates the shape of a single representative fuel assembly on the outermost row. The plant transient code CERES has been revised utilizing this method so that a integrated calculational process for the core neutronics, thermal-hydraulics and deformation can be realized. Using CERES, the responses of a 1000MWe class pool type metal fuel FBR plant during a ULOF event are calculated. According to the results, it is clarified that a passive shutdown without coolant boiling is attainable by selecting appropriate values for major design parameters such as the gap width between load-pad and the pad material properties. The maximum coolant temperature during ULOF is found to be 790C when the above core load-pad gap is set to 0.05 mm, which can be regarded as the most likely valued. The temperature increases to 915C but is still lower than the boiling point when 40% of uncertainty is taken into account. (author)
User effects on the thermal-hydraulic transient system code calculations
International Nuclear Information System (INIS)
Aksan, S.N.; D'Auria, F.; Staedtke, H.
1993-01-01
In the paper, the results of the investigations on the user effects for the thermalhydraulic transient system codes will be presented and discussed on the basis of some case studies. The general findings of the investigations show that in addition to user effects, there are other reasons that affect the results of the calculations and which are hidden under user effects. Both the hidden factors and the direct user effects will be discussed in detail and general recommendations and conclusions will be presented to control and limit them. (orig.)
A CALCULATION METHOD OF TRANSIENT MODES OF ELECTRIC SHIPS’ PROPELLING ELECTRIC PLANTS
Directory of Open Access Journals (Sweden)
V. A. Yarovenko
2017-12-01
Full Text Available The purpose of the work is to develop the method for calculating the transient modes of electric ships’ propelling electric plants during maneuver. This will allow us to evaluate and improve the maneuverability of vessels with electric motion. Methodology. The solution to the problems is proposed to be carried out on the basis of mathematical modeling of maneuvering modes. The duration of transient modes in an electric power plant at electric ships’ maneuvers is commensurable with the transient operation modes of the vessel itself. Therefore, the analysis of the electric power plants’ maneuvering modes should be made in unity with all the components of the ship’s propulsion complex. Results. A specified mathematical model of transient regimes of electric ship’s propulsion complex, including thermal motors, synchronous generators, electric power converters, propulsion motors, propellers, rudder, ship’s hull is developed. The model is universal. It covers the vast majority of modern and promising electric ships with a traditional type of propulsors. It allows calculating the current values of the basic mode indicators and assessing the quality indicators of maneuvering. The model is made in relative units. Dimensionless parameters of the complex are obtained. These parameters influence the main indicators of the quality of maneuvering. The adequacy of the suggested specified mathematical model and the developed computation method based on it were confirmed. To do this, the results of mathematical modeling for a real electric ship were compared with the data obtained in the course of field experiments conducted by other researchers. Originality. The mathematical description of a generator unit, as an integral part of an indivisible ship’s propulsion complex, makes it possible to calculate the dynamic operation modes of electric power sources during electric vessels’ maneuvering. There is an opportunity to design the electric ships
International Nuclear Information System (INIS)
Nalezny, C.L.; Chapman, R.L.; Martinell, J.S.; Riordon, R.P.; Solbrig, C.W.
1979-01-01
Mass flow is an important measured variable in the Loss-of-Fluid Test (LOFT) Program. Large uncertainties in mass flow measurements in the LOFT piping during LOFT coolant experiments requires instrument testing in a transient two-phase flow loop that simulates the geometry of the LOFT piping. To satisfy this need, a transient two-phase flow loop has been designed and built. The load cell weighing system, which provides reference mass flow measurements, has been analyzed to assess its capability to provide the measurements. The analysis consisted of first performing a thermal-hydraulic analysis using RELAP4 to compute mass inventory and pressure fluctuations in the system and mass flow rate at the instrument location. RELAP4 output was used as input to a structural analysis code SAPIV which is used to determine load cell response. The computed load cell response was then smoothed and differentiated to compute mass flow rate from the system. Comparison between computed mass flow rate at the instrument location and mass flow rate from the system computed from the load cell output was used to evaluate mass flow measurement capability of the load cell weighing system. Results of the analysis indicate that the load cell weighing system will provide reference mass flows more accurately than the instruments now in LOFT
International Nuclear Information System (INIS)
Frick, G.; Osswald, F.; Heusch, B.
1996-01-01
Preliminary investigations showed clearly that, because of the discrete electrode structure of the Vivitron, important overvoltage leading to insulator damage can appear in case of a spark. The first high voltage tests showed damage connected with such events. This fact leads to a severe voltage limitation. This work describes, at first, studies made to understand the effects of transients and the associated over-voltage appearing in the Vivitron. Then we present the high voltage tests made with full size Vivitron components using the CN 6 MV machine as a pilot machine. Extensive field calculations were made. These involve simulations of static stresses and transient overvoltages, on insulating boards and electrodes. This work gave us the solutions for arrangements and modifications in the machine. After application, the Vivitron runs now without any sparks and damage at 20 MV. In the same manner, we tested column insulators of a new design and so we will find out how to get to higher voltages. Electric field calculation around the tie bars connecting the discrete electrodes together showed field enhancements when the voltages applied on the discrete electrodes are not equally distributed. This fact is one of the sources of discharges and voltage limitations. A scenario of a spark event is described and indications are given how to proceed towards higher voltages, in the 30 MV range. (orig.)
Nodal methods for calculating nuclear reactor transients, control rod patterns, and fuel pin powers
International Nuclear Information System (INIS)
Cho, Byungoh.
1990-01-01
Nodal methods which are used to calculate reactor transients, control rod patterns, and fuel pin powers are investigated. The 3-D nodal code, STORM, has been modified to perform these calculations. Several numerical examples lead to the following conclusions: (1) By employing a thermal leakage-to-absorption ratio (TLAR) approximation for the spatial shape of the thermal fluxes for the 3-D Langenbuch-Maurer-Werner (LMW) and the superprompt critical transient problems, the convergence of the conventional two-group scheme is accelerated. (2) By employing the steepest-ascent hill climbing search with heuristic strategies, Optimum Control Rod Pattern Searcher (OCRPS) is developed for solving control rod positioning problem in BWRs. Using the method of approximation programming the objective function and the nuclear and thermal-hydraulic constraints are modified as heuristic functions that guide the search. The test calculations have demonstrated that, for the first cycle of the Edwin Hatch Unit number-sign 2 reactor, OCRPS shows excellent performance for finding a series of optimum control rod patterns for six burnup steps during the operating cycle. (3) For the modified two-dimensional EPRI-9R problem, the least square second-order polynomial flux expansion method was demonstrated to be computationally about 30 times faster than a fine-mesh finite difference calculation in order to achieve comparable accuracy for pin powers. The basic assumption of this method is that the reconstructed flux can be expressed as a product of an assembly form function and a second-order polynomial function
International Nuclear Information System (INIS)
Yokobayashi, Masao; Yoshida, Kazuo
1991-01-01
An expert system DISKET has been developed at JAERI to apply knowledge engineering techniques to the transient diagnosis of nuclear power plant. The first version of DISKET programmed in UTILISP has been developed with the main-frame computer FACOM M-780 at JAERI. The LISP language is not suitable for on-line diagnostic systems because it is highly dependent on computer to be used and requires a large computer memory. The large mainframe computer is also not suitable because there are various restrictions as a multi-user computer system. The second version of DISKET for a practical use has been developed in FORTRAN to realize on-line real time diagnoses with limited computer resources. These two versions of DISKET with the same knowledge base have been compared in running capability, and it has been found that the LISP version of DISKET needs more than two times of memory and CPU time of FORTRAN version. From this result, it is shown that this approach is a practical one to develop expert systems for on-line real time diagnosis of transients with limited computer resources. (author)
International Nuclear Information System (INIS)
Faluomi, V.; Aksan, S.N.
2000-01-01
This paper summarizes the results of the qualification activity of RELAP5/Mod3.2 code performed using PANDA steady state and integral test experimental data. The steady state tests evaluate the PCC performances in removing decay heat power in presence and in absence of non-condensable gases, while the considered integral test (M3) simulates the transient following a break in the main steam line of the SBWR, using, as nominal initial conditions, those calculated for the SBWR under SSAR assumptions at one hour into the LOCA. The results obtained simulating both types of tests show a rather good and robust overall code behavior both in the simulation of steady state test and in the representation of the integral test considered: most of the main experimental results (WW/DW pressures, PCC heat exchange) were well represented by the code. The different studies performed indicated that: Different models of PCC pool lead a different trend of system pressure, and sometimes to an opening of vacuum breaker valves, that does not occur in the transient; The code underestimate the heat exchanged between PCC pool and tubes: n the considered test the system pressure is slightly overestimated (maximum 2% more than the experimental value). This fact is also proved by the differences in the temperature of the condensing mixture in the PCC, quite large in all the performed studies; The treatment of the non condensable gases, as implemented in the code, lead some errors in the calculation of the heat transfer coefficient in the PCC components and generally slow down the overall calculation. In general terms, the RELAP5/Mod3.2 was found to be suitable to represent the SBWR containment behavior under the conditions specified in the experimental side. (author)
International Nuclear Information System (INIS)
Mladin, Mirea; Mladin, Daniela; Prodea, Ilie
2010-01-01
In 2008, IAEA started a Coordinated Research Project for benchmarking the thermalhydraulic and neutronic computer codes for research reactor analysis against the experimental data. In this framework, for the first year of research contract, the Institute for Nuclear Research engaged in steady-state analysis of SPERT-III reactor and also in the simulation of the reactivity insertion tests performed in this reactor during mid sixties. In the first part, the paper describes a Monte Carlo input model of the oxide core selected for investigation and the results of the steady-state neutronic calculations with respect to hot and cold core reactivity excess and control rods worth. Also, prompt neutron life and reactivity feed-back coefficients were examined. These results were compared with the data provided in the reactor specification document concerning neutronic design calculated data. The second part of the paper is dedicated to calculation of the reactivity insertion transients with RELAP5 and CATHARE2 thermalhydraulic codes, both including point reactor kinetics models, and to comparison with experimental data. (authors)
International Nuclear Information System (INIS)
Green, C.
1979-12-01
A set of FORTRAN subroutines is described for calculating water thermodynamic properties. These were written for use in a transient thermal-hydraulics program, where speed of execution is paramount. The choice of which subroutines to optimise depends on the primary variables in the thermal-hydraulics code. In this particular case the subroutine which has been optimised is the one which calculates pressure and specific enthalpy given the specific volume and the specific internal energy. Another two subroutines are described which complete a self-consistent set. These calculate the specific volume and the temperature given the pressure and the specific enthalpy, and the specific enthalpy and the specific volume given the pressure and the temperature (or the quality). The accuracy is high near the saturation lines, typically less than 1% relative error, and decreases as the fluid becomes more subcooled in the liquid region or more superheated in the steam region. This behaviour is inherent in the method which uses quantities defined on the saturation lines and assumes that certain derivatives are constant for excursions away from these saturation lines. The accuracy and speed of the subroutines are discussed in detail in this report. (author)
BARS - a heterogeneous code for 3D pin-by-pin LWR steady-state and transient calculation
International Nuclear Information System (INIS)
Avvakumov, A.V.; Malofeev, V.M.
2000-01-01
A 3D pin-by-pin dynamic model for LWR detailed calculation was developed. The model is based on a coupling of the BARS neutronic code with the RELAP5/MOD3.2 thermal hydraulic code. This model is intended to calculate a fuel cycle, a xenon transient, and a wide range of reactivity initiated accidents in a WWER and a PWR. Galanin-Feinberg heterogeneous method was realized in the BARS code. Some results for a validation of the heterogeneous method are presented for reactivity coefficients, a pin-by-pin power distribution, and a fast pulse transient. (Authors)
New Three-Dimensional Neutron Transport Calculation Capability in STREAM Code
Energy Technology Data Exchange (ETDEWEB)
Zheng, Youqi [Xi' an Jiaotong University, Xi' an (China); Choi, Sooyoung; Lee, Deokjung [UNIST, Ulsan (Korea, Republic of)
2016-10-15
The method of characteristics (MOC) is one of the best choices for its powerful capability in the geometry modeling. To reduce the large computational burden in 3D MOC, the 2D/1D schemes were proposed and have achieved great success in the past 10 years. However, such methods have some instability problems during the iterations when the neutron leakage for axial direction is large. Therefore, full 3D MOC methods were developed. A lot of efforts have been devoted to reduce the computational costs. However, it still requires too much memory storage and computational time for the practical modeling of a commercial size reactor core. Recently, a new approach for the 3D MOC calculation without transverse integration has been implemented in the STREAM code. In this approach, the angular flux is expressed as a basis function expansion form of only axial variable z. A new approach based on the axial expansion and 2D MOC sweeping to solve the 3D neutron transport equation is implemented in the STREAM code. This approach avoids using the transverse integration in the traditional 2D/1D scheme of MOC calculation. By converting the 3D equation into the 2D form of angular flux expansion coefficients, it also avoids the complex 3D ray tracing. Current numerical tests using two benchmarks show good accuracy of the new method.
SPLOSH III. A code for calculating reactivity and flow transients in CSGHWR
International Nuclear Information System (INIS)
Halsall, M.J.; Course, A.F.; Sidell, J.
1979-09-01
SPLOSH is a time dependent, one dimensional, finite difference (in time and space) coupled neutron kinetics and thermal hydraulics code for studying pressurised faults and control transients in water reactor systems. An axial single channel model with equally spaced mesh intervals is used to represent the neutronics of the reactor core. A radial finite difference model is used for heat conduction through the fuel pin, gas gap and can. Appropriate convective, boiling or post-dryout heat transfer correlations are used at the can-coolant interface. The hydraulics model includes the important features of the SGHWR primary loop including 'slave' channels in parallel with the 'mean' channel. Standard mass, energy and momentum equations are solved explicitly. Circuit features modelled include pumps, spray cooling and the SGHWR steam drum. Perturbations to almost any feature of the circuit model may be specified by the user although blowdown calculations resulting in critical or reversed flows are not permitted. Automatic reactor trips may be defined and the ensuing actions of moderator dumping and rod firing can be specified. (UK)
Directory of Open Access Journals (Sweden)
Alireza Khoshfetrat
2018-05-01
Full Text Available Under transient flow condition, the behavior of water conveyance system varies according to their characteristics. In the present study, the pressure was measured using a fast and sensitive pressure gauge in Bukan and Piranshahr water conveyance system. The pressure simulation was conducted using Bentley Hammer software. The friction head loss was calculated by different methods. The results showed that Unsteady Vitkovsky method had minimum error comparing with other methods. Wave velocity increase had direct effect on maximum pressures while velocity decrease affected minimum pressures. In a shorter water conveyance system, the reduction of wave velocity had direct effect on maximum pressure. Destruction to the long conveyance system was more probable and maximum and minimum pressures occurred during the first period. Shorter conveyance system had more pressure fluctuations and the minimum pressure did not occur in the first period. Coincidence of periods happened at the beginning and continued untill the end of data recording in the longer conveyance system. However, as time passed by, such coincidence did not occure in shorter conveyance system.
Energy Technology Data Exchange (ETDEWEB)
Djukanovic, M [Inst. ' Nikola Tesla' , Belgrade (Yugoslavia); Sobajic, D J; Pao, Yohhan [Case Western Reserve Univ., Cleveland, OH (United States). Dept. of Electrical Engineering and Applied Physics Case Western Reserve Univ., Cleveland, OH (United States). Dept. of Computer Engineering and Science AI WARE inc., Cleveland, OH (United States)
1992-10-01
In heavily stressed power systems, post-fault transient voltage dips can lead to undesired tripping of industrial drives and large induction motors. The lowest transient voltage dips occur when fault clearing times are less than critical ones. In this paper, we propose a new iterative analytical methodology to obtain more accurate estimates of voltage dips at maximum angular swing in direct transient stability analysis. We also propose and demonstrate the possibility of storing the results of these computations in the associative memory (AM) system, which exhibits remarkable generalization capabilities. Feature-based models stored in the AM can be utilized for fast and accurate prediction of the location, duration and the amount of the worst voltage dips, thereby avoiding the need and cost for lengthy time-domain simulations. Numerical results obtained using the example of the New England power system are presented to illustrate our approach. (Author)
Calculations in the tokamak vacuum region: δWυ and diagnostic capabilities
International Nuclear Information System (INIS)
Chance, M.S.
1993-01-01
The calculational methods used for the magnetic energy, δW v , in the vacuum region surrounding tokamak plasmas permit a natural extension to more general toroidal configurations, and also for calculating useful ancillary quantities like the simulation of the Mirnov-loop measurements, and the eddy currents generated in the conducting materials outside the plasma discharge. The generalizations include the capabilities for topologically spherical shells, and toroidally symmetric unlinked (with respect to the plasma discharge) solid conductors. The former was motivated by spheromak-like configurations, and the latter for simulating the segmented shell of PBX-M. The collocation method and Green's second identity is used for solving ∇ 2 χ = 0 for the magnetic scalar potential. This lends itself readily to incorporating the necessary boundary conditions, and once χ is known on the surfaces, a second application of Green's identity enables the simulation of the Mirnov-loop measurements. The eddy currents on the surface of the conductors, K c , is given by n x ∇χ. This is useful for visualizing the proposed coil currents needed for stabilizing the external kink modes by feedback mechanisms, and also for estimating the stresses in the shell due to disruptions, etc. The code is modular and can be easily interfaced to various stability codes like the PEST, NOVA, GATO, etc. system of codes, or can be used in a stand-alone mode for diagnostic purposes. Details of the numerical method and results are presented. These include the efficient treatment of the singularities inherently present in the Green's function method
Improvement of neutronic calculations on a Masurca core using adaptive mesh refinement capabilities
International Nuclear Information System (INIS)
Fournier, D.; Archier, P.; Le Tellier, R.; Suteau, C.
2011-01-01
The simulation of 3D cores with homogenized assemblies in transport theory remains time and memory consuming for production calculations. With a multigroup discretization for the energy variable and a discrete ordinate method for the angle, a system of about 10"4 coupled hyperbolic transport equations has to be solved. For these equations, we intend to optimize the spatial discretization. In the framework of the SNATCH solver used in this study, the spatial problem is dealt with by using a structured hexahedral mesh and applying a Discontinuous Galerkin Finite Element Method (DGFEM). This paper shows the improvements due to the development of Adaptive Mesh Refinement (AMR) methods. As the SNATCH solver uses a hierarchical polynomial basis, p−refinement is possible but also h−refinement thanks to non conforming capabilities. Besides, as the flux spatial behavior is highly dependent on the energy, we propose to adapt differently the spatial discretization according to the energy group. To avoid dealing with too many meshes, some energy groups are joined and share the same mesh. The different energy-dependent AMR strategies are compared to each other but also with the classical approach of a conforming and highly refined spatial mesh. This comparison is carried out on different quantities such as the multiplication factor, the flux or the current. The gain in time and memory is shown for 2D and 3D benchmarks coming from the ZONA2B experimental core configuration of the MASURCA mock-up at CEA Cadarache. (author)
International Nuclear Information System (INIS)
Akimoto, Hajime; Ohnuki, Akira; Murao, Yoshio
1994-03-01
The REFLA/TRAC code is a best estimate code developed at Japan Atomic Energy Research Institute (JAERI) to provide advanced predictions of thermal hydraulic transient in light water reactors (LWRs). The REFLA/TRAC code uses the TRAC-PF1/MOD1 code as the framework of the code. The REFLA/TRAC code is expected to be used for the calibration of licensing codes, accident analysis, accident simulation of LWRs, and design of advanced LWRs. Several models have been implemented to the TRAC-PF1/MOD1 code at JAERI including reflood model, condensation model, interfacial and wall friction models, etc. These models have been verified using data from various separate effect tests. This report describes an assessment result of the REFLA/TRAC code, which was performed to assess the predictive capability for integral system behavior under large break loss of coolant accident (LBLOCA) using data from the LOFT L2-5 test. The assessment calculation confirmed that the REFLA/TRAC code can predict break mass flow rate, emergency core cooling water bypass and clad temperature excellently in the LOFT L2-5 test. The CPU time of the REFLA/TRAC code was about 1/3 of the TRAC-PF1/MOD1 code. The REFLA/TRAC code can perform stable and fast simulation of thermal hydraulic behavior in PWR LBLOCA with enough accuracy for practical use. (author)
International Nuclear Information System (INIS)
Goltsev, A.O.; Davidenko, V.D.; Tsibulsky, V.F.; Lekomtsev, A.A.
2003-01-01
The paper is devoted to the discussion of results of computational studies of transients for different ways of accounting the temperature of the fuel in the full-scale comprehensive calculations of neutron physics. The paper demonstrates that in calculation of the neutron physics, it is necessary to use the effective temperature of the fuel in order to provide for correct accounting of the fuel temperature feedback, since the value of volume-averaged temperature being used in calculations of neutron physics with feedbacks would result in underestimation of consequences of accidents, especially accidents involving the dispersion of radiation
International Nuclear Information System (INIS)
Aydogdu, K.
1998-01-01
Nine components determine the moderator-system heat load during full-power operation and during a reactor power transient in a CANDU reactor. The components that contribute to the total moderator-system heat load at any time consist of the heat generated in the calandria tubes, guide tubes and reactivity mechanisms, moderator and reflector; the heat transferred from calandria shell, the inner tubesheets and the fuel channels; and the heat gained from moderator pumps and heat lost from piping. The contributions from each of these components will vary with time during a reactor transient. The sources of heat that arise from the deposition of nuclear energy can be divided into two categories, viz., a) the neutronic component (which is directly proportional to neutronic power), which includes neutron energy absorption, prompt-fission gamma absorption and capture gamma absorption; and b) the fission-product decay-gamma component, which also varies with time after initiation of the transient. An equation was derived to calculate transient heat loads to the moderator. The equation includes two independent variables that are the neutronic power and fission-product decay-gamma power fractions during the transient and a constant term that represents the heat gained from moderator pumps and heat lost from piping. The calculated heat load in the moderator during steady-state full-power operation for a CANDU 6 reactor was compared with available measurements from the Point Lepreau, Wolsong 1 and Gentilly-2 nuclear generating stations. The calculated and measured values were in reasonably good agreement. (author)
International Nuclear Information System (INIS)
Shin, Y.W.; Wiedermann, A.H.
1984-02-01
A method was published, based on the integral method of characteristics, by which the junction and boundary conditions needed in computation of a flow in a piping network can be accurately formulated. The method for the junction and boundary conditions formulation together with the two-step Lax-Wendroff scheme are used in a computer program; the program in turn, is used here in calculating sample problems related to the blowdown transient of a two-phase flow in the piping network downstream of a PWR pressurizer. Independent, nearly exact analytical solutions also are obtained for the sample problems. Comparison of the results obtained by the hybrid numerical technique with the analytical solutions showed generally good agreement. The good numerical accuracy shown by the results of our scheme suggest that the hybrid numerical technique is suitable for both benchmark and design calculations of PWR pressurizer blowdown transients
Langensiepen, M.; Kupisch, M.; Wijk, van M.T.; Ewert, F.
2012-01-01
Transient type canopy chambers are still the only currently available practical solution for rapid screening of gas-exchange in agricultural fields. The technique has been criticized for its effect on canopy microclimate during measurement which affects the transport regime and regulation of plant
International Nuclear Information System (INIS)
Jesenik, M.; Gorican, V.; Trlep, M.; Hamler, A.; Stumberger, B.
2006-01-01
A lot of magnetic materials are anisotropic. In the 3D finite element method calculation, anisotropy of the material is taken into account. Anisotropic magnetic material is described with magnetization curves for different magnetization directions. The 3D transient calculation of the rotational magnetic field in the sample of the round rotational single sheet tester with circular sample considering eddy currents is made and compared with the measurement to verify the correctness of the method and to analyze the magnetic field in the sample
Bushland Reference ET Calculator with QA/QC capabilities and iPhone/iPad application
Accurate daily reference evapotranspiration (ET) values are needed to estimate crop water demand for irrigation management and hydrologic modeling purposes. The USDA-ARS Conservation and Production Research Laboratory at Bushland, Texas developed the Bushland Reference ET (BET) Calculator for calcul...
International Nuclear Information System (INIS)
Rivard, W.C.; Torrey, M.D.
1978-10-01
The transient, two-dimensional, two-fluid code K-FIX has been extended to perform three-dimensional calculations. This capability is achieved by adding five modification sets of FORTRAN statements to the basic two-dimensional code. The modifications are listed and described, and a complete listing of the three-dimensional code is provided. Results of an example problem are provided for verification
A model for the calculation of vent clearing transients in pressure suppression systems
International Nuclear Information System (INIS)
Brosche, D.
1975-01-01
For the layout of a pressure suppression system of a light water cooled reactor (boiling water reactor) it is important to know the time dependent behavior of the vent clearing transient after a loss-of-coolant accident for two main reasons: time of the end of the vent clearing transient influences strongly the pressure and temperature maxima in the drywell and wetwell. Time-dependent behavior of the vent clearing transient influences pressure loads in the condensation pool of the wetwell and therefore pressure induced stresses to the structure. The time-dependent behavior of the water masses in the vent pipes and wetwell are described by the basic equations for a nonstationary incompressible friction flow: momentum equation, continuity equation and a correlation for the variation of the state of the gas volume in the wetwell above the water level. After many algebraic operations and integrations along the flow path, a single ordinary nonlinear differential equation for the variations of the water levels in the vent pipes and wetwell is obtained. Therefore the time-dependent velocities and accelerations of the water levels and the moment of the end clearing transient are known. The time-dependent pressure behavior in the drywell, geometrical conditions, initial submergence depth of the vent pipes and different friction and pressure loss factors are presented. The theoretical model has been tested at corresponding experiments performed at a full scale 1/48 segment of the Humboldt Bay pressure suppression containment in the USA and at the pressure suppression containment at the Marviken nuclear power station in Sweden. All these comparisons have shown good agreement between theory and experiment
Comparison of rod-ejection transient calculations in hexagonal-Z geometry
International Nuclear Information System (INIS)
Knight, M.P.; Brohan, P.; Finnemann, H.; Huesken, J.
1995-01-01
This paper proposes a set of 3-dimensional benchmark rod ejection problems for a VVER reactor, based on the well-known NEACRP PWR rod-ejection problems defined by Siemens/KWU. Predictions for these benchmarks derived using three hexagonal-z nodal transient codes, the PANTHER code of Nuclear Electric, the HEXTIME code of Siemens/KWU, and the DYN3D code of FZ-Rossendorf are presented and compared
Transient calculation performance of the MASTER code for control rod ejection problem
International Nuclear Information System (INIS)
Cho, B. O.; Joo, H. G.; Yoo, Y. J.; Park, S. Y.; Zee, S. Q.
1999-01-01
The accuracy and the effectiveness of the solution methods of the MASTER code for reactor transient problems were analyzed with a set of NEACRP PWR control rod ejection benchmark problems. A series of sensitivity study for the effects on the solution by the neutronic solution methods and the neutronic and thermal-hydraulic model parameters were thus investigated. The MASTER results were then compared with the reference PANTHER results. This indicates that the MASTER solution is sufficiently accurate and the computing time is fast enough for nuclear design application
Transient calculation performance of the MASTER code for control rod ejection problem
Energy Technology Data Exchange (ETDEWEB)
Cho, B. O.; Joo, H. G.; Yoo, Y. J.; Park, S. Y.; Zee, S. Q. [KAERI, Taejon (Korea, Republic of)
1999-10-01
The accuracy and the effectiveness of the solution methods of the MASTER code for reactor transient problems were analyzed with a set of NEACRP PWR control rod ejection benchmark problems. A series of sensitivity study for the effects on the solution by the neutronic solution methods and the neutronic and thermal-hydraulic model parameters were thus investigated. The MASTER results were then compared with the reference PANTHER results. This indicates that the MASTER solution is sufficiently accurate and the computing time is fast enough for nuclear design application.
International Nuclear Information System (INIS)
Cahalan, J.E.; Ama, T.; Palmiotti, G.; Taiwo, T.A.; Yang, W.S.
2000-01-01
The VARIANT-K and DIF3D-K nodal spatial kinetics computer codes have been coupled to the SAS4A and SASSYS-1 liquid metal reactor accident and systems analysis codes. SAS4A and SASSYS-1 have been extended with the addition of heavy liquid metal (Pb and Pb-Bi) thermophysical properties, heat transfer correlations, and fluid dynamics correlations. The coupling methodology and heavy liquid metal modeling additions are described. The new computer code suite has been applied to analysis of neutron source and thermal-hydraulics transients in a model of an accelerator-driven minor actinide burner design proposed in an OECD/NEA/NSC benchmark specification. Modeling assumptions and input data generation procedures are described. Results of transient analyses are reported, with emphasis on comparison of P1 and P3 variational nodal transport theory results with nodal diffusion theory results, and on significance of spatial kinetics effects
3-D transient eddy current calculations for the FELIX cylinder experiments
International Nuclear Information System (INIS)
Davey, K.R.; Turner, L.R.
1986-12-01
The three-dimensional eddy current transient field problem is formulated first using the U-V method. This method breaks the vector Helmholtz equation into two scalar Helmholtz equations. Null field integral equations and the appropriate boundary conditions are used to set up an identification matrix which is independent of null field point locations. Embedded in the identification matrix are the unknown eigenvalues of the problem representing its impulse response in time. These eigenvalues are found by equating the determinant of the identification matrix to zero. When this initial forcing function is Fourier decomposed into its spatial harmonics, each Fourier component can be associated with a unique eigenvalue by this technique. The true transient solution comes through a convolution of the impulse response so obtained with the particular external field decay governing the problem at hand. The technique is applied to the FELIX cylinder experiments; computed results are compared to data. A pseudoanalytic confirmation of the eigenvalues so obtained is formulated to validate the procedure
Use of ELOCA.Mk5 to calculate transient fission product release from CANDU fuel elements
International Nuclear Information System (INIS)
Walker, J.R.; de Vaal, J.W.; Arimescu, V.I.; McGrady, T.G.; Wong, C.
1992-04-01
A change in fuel element power output, or a change in heat transfer conditions, will result in an immediate change in the temperature distribution in a fuel element. The temperature distribution change will be accompanied by concomitant changes in fuel stress distribution that lead, in turn, to a release of fission products to the fuel-to-sheath gap. It is important to know the inventory of fission products in the fuel-to-sheath gap, because this inventory is a major component of the source term for many postulated reactor accidents. ELOCA.Mk5 is a FORTRAN-77 computer code that has been developed to estimate transient releases to the fuel-to-sheath gap in CANDU reactors. ELOCA.Mk5 is an integration of the FREEDOM fission product release model into the ELOCA fuel element thermo-mechanical code. The integration of FREEDOM into ELOCA allows ELOCA.Mk5 to model the feedback mechanisms between the fission product release and the thermo-mechanical response of the fuel element. This paper describes the physical model, gives details of the ELOCA.Mkt code, and describes the validation of the model. We demonstrate that the model gives good agreement with experimental results for both steady state and transient conditions
Institute of Scientific and Technical Information of China (English)
2012-01-01
The integrated power generation system of wind, photovoltaic （PV） and energy storage is composed of several wind turbines, PV units and energy storage units. The detailed model of integrated generation is not suitable for the large-scale powe.r system simulation because of the model＇s complexity and long computation time. An equivalent method for power flow calculation and transient simulation of the integrated generation system is proposed based on actual projects, so as to establish the foundation of such integrated system simulation and analysis.
Directory of Open Access Journals (Sweden)
Palukuru NAGENDRA
2010-12-01
Full Text Available In this study, the use of artificial neural network (ANN based model, multi-layer perceptron (MLP network, to compute the transfer capabilities in a multi-area power system was explored. The input for the ANN is load status and the outputs are the transfer capability among the system areas, voltage magnitudes and voltage angles at concerned buses of the areas under consideration. The repeated power flow (RPF method is used in this paper for calculating the power transfer capability, voltage magnitudes and voltage angles necessary for the generation of input-output patterns for training the proposed MLP neural network. Preliminary investigations on a three area 30-bus system reveal that the proposed model is computationally faster than the conventional method.
International Nuclear Information System (INIS)
Han, H.C.; Davey, K.R.; Turner, L.
1985-08-01
The transient eddy current problem is characteristically computationally intensive. The motivation for this research was to realize an efficient, accurate, solution technique involving small matrices via an eigenvalue approach. Such a technique is indeed realized and tested using the null field integral technique. Using smart (i.e., efficient, global) basis functions to represent unknowns in terms of a minimum number of unknowns, homogeneous eigenvectors and eigenvalues are first determined. The general excitatory response is then represented in terms of these eigenvalues/eigenvectors. Excellent results are obtained for the Argonne Felix cylinder experiments using a 4 x 4 matrix. Extension to the 3-D problem (short cylinder) is set up in terms of an 8 x 8 matrix
FABGEN, a transient power-generation and isotope birth rate calculator
International Nuclear Information System (INIS)
Roland, H.C.
1975-04-01
A description is given of the FABGEN program, a fast-running program for calculating fuel element power-generation rates and selected fission product birth rates in a known neutron flux as functions of time. A first forward difference calculation is used, and the time step is one day. Provisions are made for including various fuel element lengths, variation of thermal flux with time, and use of different fertile isotopes. Five different fission products may be specified for birth-rate calculations. A daily summary may be output, or totals by days may be accumulated for final output. (U.S.)
Clamens, Olivier; Lecerf, Johann; Hudelot, Jean-Pascal; Duc, Bertrand; Cadiou, Thierry; Blaise, Patrick; Biard, Bruno
2018-01-01
CABRI is an experimental pulse reactor, funded by the French Nuclear Safety and Radioprotection Institute (IRSN) and operated by CEA at the Cadarache research center. It is designed to study fuel behavior under RIA conditions. In order to produce the power transients, reactivity is injected by depressurization of a neutron absorber (3He) situated in transient rods inside the reactor core. The shapes of power transients depend on the total amount of reactivity injected and on the injection speed. The injected reactivity can be calculated by conversion of the 3He gas density into units of reactivity. So, it is of upmost importance to properly master gas density evolution in transient rods during a power transient. The 3He depressurization was studied by CFD calculations and completed with measurements using pressure transducers. The CFD calculations show that the density evolution is slower than the pressure drop. Surrogate models were built based on CFD calculations and validated against preliminary tests in the CABRI transient system. Studies also show that it is harder to predict the depressurization during the power transients because of neutron/3He capture reactions that induce a gas heating. This phenomenon can be studied by a multiphysics approach based on reaction rate calculation thanks to Monte Carlo code and study the resulting heating effect with the validated CFD simulation.
Directory of Open Access Journals (Sweden)
Clamens Olivier
2018-01-01
Full Text Available CABRI is an experimental pulse reactor, funded by the French Nuclear Safety and Radioprotection Institute (IRSN and operated by CEA at the Cadarache research center. It is designed to study fuel behavior under RIA conditions. In order to produce the power transients, reactivity is injected by depressurization of a neutron absorber (3He situated in transient rods inside the reactor core. The shapes of power transients depend on the total amount of reactivity injected and on the injection speed. The injected reactivity can be calculated by conversion of the 3He gas density into units of reactivity. So, it is of upmost importance to properly master gas density evolution in transient rods during a power transient. The 3He depressurization was studied by CFD calculations and completed with measurements using pressure transducers. The CFD calculations show that the density evolution is slower than the pressure drop. Surrogate models were built based on CFD calculations and validated against preliminary tests in the CABRI transient system. Studies also show that it is harder to predict the depressurization during the power transients because of neutron/3He capture reactions that induce a gas heating. This phenomenon can be studied by a multiphysics approach based on reaction rate calculation thanks to Monte Carlo code and study the resulting heating effect with the validated CFD simulation.
Theoretical calculation of rapid x-ray transients and radius expansion
International Nuclear Information System (INIS)
Starrfield, S.; Sparks, W.; Truran, J.; Kenyon, S.
1984-01-01
We present the results of a calculation of a thermonuclear runaway on a 10 km neutron star which produced a precursor, radius expansion, and after the envelope had begun to shrink, a seconds x-ray burst about 2500 second later. Although such an event has not yet been observed, decreasing the initial envelope mass should bring the calculations into better agreement with the observations
Hybrid PN-SN Calculations with SAAF for the Multiscale Transport Capability in Rattlesnake
Energy Technology Data Exchange (ETDEWEB)
Wang, Yaqi; Schunert, Sebastian; DeHart, Mark; Martineau, Richard
2016-05-01
Two interface conditions, the Lagrange multiplier method and the upwinding method, for hybrid \\pn-\\sn calculations is proposed for the self-adjoint angular flux (SAAF) formulation of the transport equation using the continuous finite element method (FEM) for spatial discretization. These interface conditions are implemented in Rattlesnake, the radiation transport application built on MOOSE, for the on-going multiscale transport simulation effort at INL. For smoothing the solution at the interface for the Lagrange multiplier method, a method based on \\sn Lagrange interpolation on the sphere is proposed. Numerical results indicate that the interface conditions give the expected convergence.
International Nuclear Information System (INIS)
Thorlaksen, B.
1981-05-01
Nuclear cross sections for fuel assemblies of the more recent Westinghouse designs, representing two different PWR reactor cores, are calculated as functions of average fuel temperature, moderator density, and moderator poison concentration. The cross-section functions are verified by referring to Westinghouse power-shape calculations and other analysis. Computations on the side reflector resulted in significantly higher albedo values than used previously for BWR's in similar nodal codes. This led to an investigation of the influence of the internodal coupling coefficients on the power shape. It is concluded that the calculated power shape is strongly dependent, on the choise of coupling coefficients. However, it is shown that ''the correct'' set of coupling coefficients depends mostly on the nodal configuration, and that it is fairly independent of the power condition. (author)
Summary of transient high-voltage calculations for the FRX-C experiment
International Nuclear Information System (INIS)
Kewish, R.W. Jr.; Rej, D.J.
1982-06-01
Calculations of the electrical circuit equations are performed over a wide range of parameters corresponding to the FRX-C field-reversed THETA-pinch experiment at Los Alamos. Without any plasma or external damping, serious voltage doubling and quadrupling of the main capacitor bank charge voltage are observed. These oscillating high voltages are found to be adequately suppressed by the strategic placement of external snubber circuitry. On the other hand, no doubling of the THETA-pinch preionization bank charge voltage is found. Calculations of the equations for the z-pinch preionization circuit are also performed
Baglivo, Ilaria; Esposito, Sabrina; De Cesare, Lucia; Sparago, Angela; Anvar, Zahra; Riso, Vincenzo; Cammisa, Marco; Fattorusso, Roberto; Grimaldi, Giovanna; Riccio, Andrea; Pedone, Paolo V
2013-05-21
In the mouse, ZFP57 contains three classical Cys2His2 zinc finger domains (ZF) and recognizes the methylated TGC(met)CGC target sequence using the first and the second ZFs. In this study, we demonstrate that the human ZFP57 (hZFP57) containing six Cys2His2 ZFs, binds the same methylated sequence through the third and the fourth ZFs, and identify the aminoacids critical for DNA interaction. In addition, we present evidences indicating that hZFP57 mutations and hypomethylation of the TNDM1 ICR both associated with Transient Neonatal Diabetes Mellitus type 1 result in loss of hZFP57 binding to the TNDM1 locus, likely causing PLAGL1 activation. Copyright © 2013 Federation of European Biochemical Societies. Published by Elsevier B.V. All rights reserved.
COMETHE III-M for transient fuel rod behaviour prediction
International Nuclear Information System (INIS)
Billaux, M.; Vliet, J. van
1983-01-01
The COMETHE III-M version is being developed in order to provide fuel rod behaviour prediction capability both in steady-state and in transient situations. It also allows to estimate the fuel rod enthalpy evolution versus time or burnup which may be important in core-related safety studies. This paper describes the transient heat transfer models, including transient heat conduction inside the fuel rod, and a subchannel model providing transient flow as well as enthalpy calculation capability. Transient fission gas release is also modelled on basis of the change rate of oxide temperature. The models are illustrated by a few calculation examples. (author)
Aquilante, Francesco; Autschbach, Jochen; Carlson, Rebecca K; Chibotaru, Liviu F; Delcey, Mickaël G; De Vico, Luca; Fdez Galván, Ignacio; Ferré, Nicolas; Frutos, Luis Manuel; Gagliardi, Laura; Garavelli, Marco; Giussani, Angelo; Hoyer, Chad E; Li Manni, Giovanni; Lischka, Hans; Ma, Dongxia; Malmqvist, Per Åke; Müller, Thomas; Nenov, Artur; Olivucci, Massimo; Pedersen, Thomas Bondo; Peng, Daoling; Plasser, Felix; Pritchard, Ben; Reiher, Markus; Rivalta, Ivan; Schapiro, Igor; Segarra-Martí, Javier; Stenrup, Michael; Truhlar, Donald G; Ungur, Liviu; Valentini, Alessio; Vancoillie, Steven; Veryazov, Valera; Vysotskiy, Victor P; Weingart, Oliver; Zapata, Felipe; Lindh, Roland
2016-02-15
In this report, we summarize and describe the recent unique updates and additions to the Molcas quantum chemistry program suite as contained in release version 8. These updates include natural and spin orbitals for studies of magnetic properties, local and linear scaling methods for the Douglas-Kroll-Hess transformation, the generalized active space concept in MCSCF methods, a combination of multiconfigurational wave functions with density functional theory in the MC-PDFT method, additional methods for computation of magnetic properties, methods for diabatization, analytical gradients of state average complete active space SCF in association with density fitting, methods for constrained fragment optimization, large-scale parallel multireference configuration interaction including analytic gradients via the interface to the Columbus package, and approximations of the CASPT2 method to be used for computations of large systems. In addition, the report includes the description of a computational machinery for nonlinear optical spectroscopy through an interface to the QM/MM package Cobramm. Further, a module to run molecular dynamics simulations is added, two surface hopping algorithms are included to enable nonadiabatic calculations, and the DQ method for diabatization is added. Finally, we report on the subject of improvements with respects to alternative file options and parallelization. © 2015 Wiley Periodicals, Inc.
Energy Technology Data Exchange (ETDEWEB)
Vitruk, S.G.; Korsun, A.S. [Moscow Engineering Physics Institute (Russian Federation); Ushakov, P.A. [Institute of Physics and Power Engineering, Obninsk (R)] [and others
1995-09-01
The multilevel mathematical model of neutron thermal hydrodynamic processes in a passive safety core without assemblies duct walls and appropriate computer code SKETCH, consisted of thermal hydrodynamic module THEHYCO-3DT and neutron one, are described. A new effective discretization technique for energy, momentum and mass conservation equations is applied in hexagonal - z geometry. The model adequacy and applicability are presented. The results of the calculations show that the model and the computer code could be used in conceptual design of advanced reactors.
International Nuclear Information System (INIS)
Vitruk, S.G.; Korsun, A.S.; Ushakov, P.A.
1995-01-01
The multilevel mathematical model of neutron thermal hydrodynamic processes in a passive safety core without assemblies duct walls and appropriate computer code SKETCH, consisted of thermal hydrodynamic module THEHYCO-3DT and neutron one, are described. A new effective discretization technique for energy, momentum and mass conservation equations is applied in hexagonal - z geometry. The model adequacy and applicability are presented. The results of the calculations show that the model and the computer code could be used in conceptual design of advanced reactors
Buoyancy effects in overcooling transients calculated for the NRC pressurized thermal shock study
International Nuclear Information System (INIS)
Theofanous, T.G.; Iyer, K.; Nourbakhsh, H.P.; Gherson, P.
1986-05-01
The thermal-hydraulic responses of three PWRs (Oconee, Calvert Cliffs, and H.B. Robinson), to postulated Pressurized Thermal Shock (PTS) scenarios, which were originally determined by RELAP5 and TRAC calculations, are being further developed here with regard to buoyancy/stratification effects. These three PWRs were the subject of the NRC PTS study, and the present results helped define the thermal-hydraulic conditions utilized in the fracture mechanics calculations carried out at ORNL. The computer program REMIX, which is based on the Regional Mixing Model (RMM), was the analytical tool employed, while Purdue's 1/2-Scale HPI Thermal Mixing facility provided the basis for experimental support. Important mixing and wall heat transfer regimes are delineated on the basis of these results. We conclude that stratification is important only in cases of complete loop stagnation and that mixed-convection effects are important for downcomer flow velocities below approx.0.25 m/s. The stratification is small in magnitude, however it is important in creating a recirculating flow pattern which activates the lower plenum, pump and loop seal volumes, to participate in the mixing process. This mixing process together with the heat input from the wall metal significantly impact the cooldown rates. Heat transfer in the plume region is dominated by forced convection. On the other hand, the presence of the Reactor Pressure Vessel (RPV) wall cladding and wall conduction significantly dampen the free convection effects in the low velocity, mixed-convection, regime. For the stagnant loop cases, all locations outside the plume region are included in this regime. In the presence of natural loop circulation and a uniformly distributed downcomer flow, the mixed convection regime is also expected, however, the forced convection regime can also be observed in highly asymmetric flow behavior
Directory of Open Access Journals (Sweden)
Khedr Ahmed
2005-01-01
Full Text Available The safety evaluation of nuclear power and re search reactors is a very important step before their construction and during their operation. This evaluation based on the best estimate calculations requires qualified codes qualified users, and qualified nodalizations. The effect of code users on the RELAP5 results during the analysis of loss of flow transient in MTR research reactors is presented in this pa per. To clarify this effect, two nodalizations for research reactor different in the simulation of the open water surface boundary conditions of the reactor pool have been used. Very different results are obtained with few choices for code users. The core natural circulation flow with the be ginning of core boiling doesn't stop but in creases. The in creasing in the natural circulation flow shifts out the boiling from the core and the clad temperature decreases be low the local saturation temperature.
A three-dimensional transient calculation for the reactor model RAMONA using the COMMIX-2(V) code
International Nuclear Information System (INIS)
Weinberg, D.; Frey, H.H.; Tschoeke, H.
1993-01-01
The safety graded decay heat removal system of the European Fast Reactor needs a high availability. This system operates entirely under natural convection. To guarantee a proper design, experiments are carried out to verify thermal-hydraulic computer codes able to predict precisely local temperature loadings of the components and the reactor tank in the transition region from nominal operation under forced convection to the decay heat removal operation. - With the COMMIX-2 (V) code three-dimensional transient calculations have been performed to simulate experiments in the 360 deg. reactor model RAMONA, scaled 1:20 to the reality with water as simulant fluid for sodium. The computed average and local temperatures as well as the velocity distributions show a good agreement with the experimental results. Further efforts are necessary to reduce the computation time. (orig.)
International Nuclear Information System (INIS)
Soysal, A.O.; Semlyen, A.
1994-01-01
A general methodology is presented for the state equation approximation of a multiple input-output linear system from transfer matrix data. A complex transformation matrix, obtained by eigen analysis at a fixed frequency, is used for diagonalization of the transfer matrix over the whole frequency range. A scalar estimation procedure is applied for identification of the modal transfer functions. The state equations in the original coordinates are obtained by inverse transformation. An iterative Gauss-Newton refinement process is used to reduce the overall error of the approximation. The developed methodology is applied to the phase domain modeling of untransposed transmission lines. The approach makes it possible to perform EMTP calculations directly in the phase domain. This results in conceptual simplification and savings in computation time since modal transformations are not needed in the sequences of the transient analysis. The presented procedure is compared with the conventional modal approach in terms of accuracy and computation time
International Nuclear Information System (INIS)
Marinelli, V.; Pellei, A.; Vallero, P.; Vitanza, C.
1975-01-01
The calculations performed in comparison of the ''Lagrangian point of view'', by means of the DOLCE computer code with the local space--time approach of the ''Eulerian point of view'' indicate that the two methods give substantially equivalent results and predict satisfactorily the onset of the transient CHF for the Centro Informazioni Studi Esperienze annuli experimental data and General Electric Company 16-rod bundles data under typical boiling water reactor transients, including loss-of-coolant accident simulations. 9 references
International Nuclear Information System (INIS)
Komatsu, Y; Brus, G; Szmyd, J S; Kimijima, S
2012-01-01
The present paper reports the experimental study on the dynamic behavior of a solid oxide fuel cell (SOFC). The cell stack consists of planar type cells with standard power output 300W. A Major subject of the present study is characterization of the transient response to the electric current change, assuming load-following operation. The present studies particularly focus on fuel provision control to the load change. Optimized fuel provision improves power generation efficiency. However, the capability of SOFC must be restricted by a few operative parameters. Fuel utilization factor, which is defined as the ratio of the consumed fuel to the supplied fuel is adopted for a reference in the control scheme. The fuel flow rate was regulated to keep the fuel utilization at 50%, 60% and 70% during the current ramping. Lower voltage was observed with the higher fuel utilization, but achieved efficiency was higher. The appropriate mass flow control is required not to violate the voltage transient behavior. Appropriate fuel flow manipulation can contribute to moderate the overshoot on the voltage that may appear to the current change. The overshoot on the voltage response resulted from the gradual temperature behavior in the SOFC stack module.
Komatsu, Y.; Brus, G.; Kimijima, S.; Szmyd, J. S.
2012-11-01
The present paper reports the experimental study on the dynamic behavior of a solid oxide fuel cell (SOFC). The cell stack consists of planar type cells with standard power output 300W. A Major subject of the present study is characterization of the transient response to the electric current change, assuming load-following operation. The present studies particularly focus on fuel provision control to the load change. Optimized fuel provision improves power generation efficiency. However, the capability of SOFC must be restricted by a few operative parameters. Fuel utilization factor, which is defined as the ratio of the consumed fuel to the supplied fuel is adopted for a reference in the control scheme. The fuel flow rate was regulated to keep the fuel utilization at 50%, 60% and 70% during the current ramping. Lower voltage was observed with the higher fuel utilization, but achieved efficiency was higher. The appropriate mass flow control is required not to violate the voltage transient behavior. Appropriate fuel flow manipulation can contribute to moderate the overshoot on the voltage that may appear to the current change. The overshoot on the voltage response resulted from the gradual temperature behavior in the SOFC stack module.
International Nuclear Information System (INIS)
Jinaphanh, A.
2012-01-01
Monte Carlo criticality calculation allows to estimate the effective multiplication factor as well as local quantities such as local reaction rates. Some configurations presenting weak neutronic coupling (high burn up profile, complete reactor core,...) may induce biased estimations for k eff or reaction rates. In order to improve robustness of the iterative Monte Carlo methods, a coupling with a deterministic code was studied. An adjoint flux is obtained by a deterministic calculation and then used in the Monte Carlo. The initial guess is then automated, the sampling of fission sites is modified and the random walk of neutrons is modified using splitting and russian roulette strategies. An automated convergence detection method has been developed. It locates and suppresses the transient due to the initialization in an output series, applied here to k eff and Shannon entropy. It relies on modeling stationary series by an order 1 auto regressive process and applying statistical tests based on a Student Bridge statistics. This method can easily be extended to every output of an iterative Monte Carlo. Methods developed in this thesis are tested on different test cases. (author)
Directory of Open Access Journals (Sweden)
Gracey Lia E
2010-07-01
Full Text Available Abstract Background The physiological function of eukaryotic DNA occurs in the context of nucleosomal arrays that can expose or obscure defined segments of the genome. Certain DNA sequences are capable of strongly positioning a nucleosome in vitro, suggesting the possibility that favorable intrinsic signals might reproducibly structure chromatin segments. As high-throughput sequencing analyses of nucleosome coverage in vitro and in vivo have become possible, a vigorous debate has arisen over the degree to which intrinsic DNA:nucleosome affinities orchestrate the in vivo positions of nucleosomes, thereby controlling physical accessibility of specific sequences in DNA. Results We describe here the in vivo consequences of placing a synthetic high-affinity nucleosome-positioning signal, the 601 sequence, into a DNA plasmid vector in mice. Strikingly, the 601 sequence was sufficient to position nucleosomes during an early phase after introduction of the DNA into the mice (when the plasmid vector transgene was active. This positioning capability was transient, with a loss of strong positioning at a later time point when the transgenes had become silent. Conclusions These results demonstrate an ability of DNA sequences selected solely for nucleosome affinity to organize chromatin in vivo, and the ability of other mechanisms to overcome these interactions in a dynamic nuclear environment.
Directory of Open Access Journals (Sweden)
Möhlenkamp Stefan
2006-06-01
Full Text Available Abstract Background The pressure drop – flow relations in myocardial bridges and the assessment of vascular heart disease via fractional flow reserve (FFR have motivated many researchers the last decades. The aim of this study is to simulate several clinical conditions present in myocardial bridges to determine the flow reserve and consequently the clinical relevance of the disease. From a fluid mechanical point of view the pathophysiological situation in myocardial bridges involves fluid flow in a time dependent flow geometry, caused by contracting cardiac muscles overlying an intramural segment of the coronary artery. These flows mostly involve flow separation and secondary motions, which are difficult to calculate and analyse. Methods Because a three dimensional simulation of the haemodynamic conditions in myocardial bridges in a network of coronary arteries is time-consuming, we present a boundary layer model for the calculation of the pressure drop and flow separation. The approach is based on the assumption that the flow can be sufficiently well described by the interaction of an inviscid core and a viscous boundary layer. Under the assumption that the idealised flow through a constriction is given by near-equilibrium velocity profiles of the Falkner-Skan-Cooke (FSC family, the evolution of the boundary layer is obtained by the simultaneous solution of the Falkner-Skan equation and the transient von-Kármán integral momentum equation. Results The model was used to investigate the relative importance of several physical parameters present in myocardial bridges. Results have been obtained for steady and unsteady flow through vessels with 0 – 85% diameter stenosis. We compare two clinical relevant cases of a myocardial bridge in the middle segment of the left anterior descending coronary artery (LAD. The pressure derived FFR of fixed and dynamic lesions has shown that the flow is less affected in the dynamic case, because the distal
Validation of SCALE4.4a for Calculation of Xe-Sm Transients After a Scram of the BR2 Reactor
International Nuclear Information System (INIS)
Kalcheva, S.; Ponsard, B.; Koonen, E.
2007-01-01
The aim of this report is to validate the computational modules system SCALE4.4a for evaluation of reactivity changes, macroscopic absorption cross sections and calculations of the positions of the Control Rods during their motion in Xe-Sm transient after a scram of the BR-2 reactor. The rapid shutting down of the reactor by inserting of negative reactivity by the Control Rods is known as a reactor scram. Following reactor scram, a large xenon and samarium buildup occur in the reactor, which may appreciably affect the multiplication factor of the core due to enormous neutron absorption. The validation of the calculations of Xe-Sm transients by SCALE4.4a has been performed on the measurements of the positions of the Control Rods during their motion in Xe-Sm transients of the BR-2 reactor and on comparison with the calculations by the standard procedure XESM, developed at the BR-2 reactor. A final conclusion is made that the SCALE4.4a modules system can be used for evaluation of Xe-Sm transients of the BR-2 reactor. The utilization of the code is simple, the computational time takes from few seconds.
Energy Technology Data Exchange (ETDEWEB)
Galindo, J.; Lujan, J.M.; Serrano, J.R.; Dolz, V. [CMT-Motores Termicos, Universidad Politecnica de Valencia, Valencia (Spain); Guilain, S. [Renault s.a.s., Lardy (France)
2006-01-15
This paper describes a heat transfer model to be implemented in a global engine 1-D gas-dynamic code to calculate reciprocating internal combustion engine performance in steady and transient operations. A trade off between simplicity and accuracy has been looked for, in order to fit with the stated objective. To validate the model, the temperature of the exhaust manifold wall in a high-speed direct injection (HSDI) turbocharged diesel engine has been measured during a full load transient. In addition, an indirect assessment of the exhaust gas temperature during this transient process has been carried out. The results show good agreement between the measured and modelled data with good accuracy to predict the engine performance. A dual-walled air gap exhaust manifold has been tested in order to quantify the potential of exhaust gas thermal energy saving on engine transient performance. The experimental results together with the heat transfer model have been used to analyse the influence of thermal energy saving on dynamic performance during the load transient of an HSDI turbocharged diesel engine. (author)
International Nuclear Information System (INIS)
Niklaus, F.; Korteniemi, V.
1996-01-01
At the Department of Energy Technology at Lappeenranta University of Technology a CATHARE model of one unit of the St. Petersburg (RBMK) nuclear power plant has been generated. The investigations have been done in order to understand better the thermal-hydraulic behaviour of RBMK type reactors and in order to see how far the French thermal-hydraulic safety code CATHARE can predict the physical phenomena during various RBMK transients. (12 refs.)
International Nuclear Information System (INIS)
Zhu, Ang; Xu, Yunlin; Downar, Thomas
2016-01-01
Three-dimensional, full core transport modeling with pin-resolved detail for reactor dynamic simulation is important for some multi-physics reactor applications. However, it can be computationally intensive due to the difficulty in maintaining accuracy while minimizing the number of time steps. A recently proposed Transient Multi-Level (TML) methodology overcomes this difficulty by use multi-level transient solvers to capture the physical phenomenal in different time domains and thus maximize the numerical accuracy and computational efficiency. One major problem with the TML method is the negative flux/precursor number density generated using large time steps for the MOC solver, which is due to the Backward Euler discretization scheme. In this paper, the stability issue of Backward Euler discretization is first investigated using the Point Kinetics Equations (PKEs), and the predicted maximum allowed time step for SPERT test 60 case is shown to be less than 10 ms. To overcome this difficulty, linear and exponential transformations are investigated using the PKEs. The linear transformation is shown to increase the maximum time step by a factor of 2, and the exponential transformation is shown to increase the maximum time step by a factor of 5, as well as provide unconditionally stability above a specified threshold. The two sets of transformations are then applied to TML scheme in the MPACT code, and the numerical results presented show good agreement for standard, linear transformed, and exponential transformed maximum time step between the PKEs model and the MPACT whole core transport solution for three different cases, including a pin cell case, a 3D SPERT assembly case and a row of assemblies (“striped assembly case”) from the SPERT model. Finally, the successful whole transient execution of the stripe assembly case shows the ability of the exponential transformation method to use 10 ms and 20 ms time steps, which all failed using the standard method.
Raffray, A. René; Federici, Gianfranco
1997-04-01
RACLETTE (Rate Analysis Code for pLasma Energy Transfer Transient Evaluation), a comprehensive but relatively simple and versatile model, was developed to help in the design analysis of plasma facing components (PFCs) under 'slow' high power transients, such as those associated with plasma vertical displacement events. The model includes all the key surface heat transfer processes such as evaporation, melting, and radiation, and their interaction with the PFC block thermal response and the coolant behaviour. This paper represents part I of two sister and complementary papers. It covers the model description, calibration and validation, and presents a number of parametric analyses shedding light on and identifying trends in the PFC armour block response to high plasma energy deposition transients. Parameters investigated include the plasma energy density and deposition time, the armour thickness and the presence of vapour shielding effects. Part II of the paper focuses on specific design analyses of ITER plasma facing components (divertor, limiter, primary first wall and baffle), including improvements in the thermal-hydraulic modeling required for better understanding the consequences of high energy deposition transients in particular for the ITER limiter case.
International Nuclear Information System (INIS)
Raffray, A.R.; Federici, G.
1997-01-01
For pt.II see ibid., p.101-30, 1997. RACLETTE (Rate Analysis Code for pLasma Energy Transfer Transient Evaluation), a comprehensive but relatively simple and versatile model, was developed to help in the design analysis of plasma facing components (PFCs) under 'slow' high power transients, such as those associated with plasma vertical displacement events. The model includes all the key surface heat transfer processes such as evaporation, melting, and radiation, and their interaction with the PFC block thermal response and the coolant behaviour. This paper represents part I of two sister and complementary papers. It covers the model description, calibration and validation, and presents a number of parametric analyses shedding light on and identifying trends in the PFC armour block response to high plasma energy deposition transients. Parameters investigated include the plasma energy density and deposition time, the armour thickness and the presence of vapour shielding effects. Part II of the paper focuses on specific design analyses of ITER plasma facing components (divertor, limiter, primary first wall and baffle), including improvements in the thermal-hydraulic modeling required for better understanding the consequences of high energy deposition transients in particular for the ITER limiter case. (orig.)
Energy Technology Data Exchange (ETDEWEB)
Osswald, F.; Roumie, M.; Frick, G.; Heusch, B.
1994-11-01
Calculations have been made to increase the high voltage performance of some components and to explain electrical failures of the Vivitron. These involve simulations of static stresses and transient over voltages, especially on insulating boards and electrodes occurring before or during breakdowns. Developments made to the structure of the machine over the last years and new ideas to improve the static and dynamic behaviour are presented. The application of this study and HV tests led recently to a nominal potential near 20 MV without sparks. (author). 49 refs., 25 figs., 2 tabs.
International Nuclear Information System (INIS)
Osswald, F.; Roumie, M.; Frick, G.; Heusch, B.
1994-11-01
Calculations have been made to increase the high voltage performance of some components and to explain electrical failures of the Vivitron. These involve simulations of static stresses and transient over voltages, especially on insulating boards and electrodes occurring before or during breakdowns. Developments made to the structure of the machine over the last years and new ideas to improve the static and dynamic behaviour are presented. The application of this study and HV tests led recently to a nominal potential near 20 MV without sparks. (author). 49 refs., 25 figs., 2 tabs
International Nuclear Information System (INIS)
Martin, A.; Alvarez, D.; Cases, F.
1996-03-01
The paper explains the chronological account and the first results obtained in the R and D program on the mixing in the 900 MW PWR vessels. After the presentation of the plant type simulated, we define the numerical tool, the (Finite Element Modelling) FEM N3S code. Two results are presented with a comparison with the experiment results issued of the BORA BORA mock up. The first case is dealing with the isothermal steady state mixing in the vessel with the three loops mass flow rate balanced. This case identified as a validation of our numerical tool shows a good agreement. The second case is dealing with the transient mixing of a clear plug in the vessel when one primary pump starts-up. We compare the numerical and experiment results giving the mean boron concentration at the core inlet for several clear water plugs. The results show again a good agreement. (authors). 12 refs., 10 figs., 1 tab
International Nuclear Information System (INIS)
Dahlfors, Marcus
2003-05-01
This text is a summary of two studies the author has performed within the field of 3-D Monte Carlo calculations of Accelerator Driven Systems (ADS) for transmutation of nuclear waste. The simulations were carried out with the state-of-the-art computer code package EA-MC, developed by C. Rubbia and his group at CERN. The concept studied is ANSALDOs 80 MWth Energy Amplifier Demonstration Facility based on classical MOX-fuel technology and on molten Lead-Bismuth Eutectic cooling. A review of neutron cross section sensitivity in numerical calculations of an ADS and a comparative assessment relevant to the transmutation efficiency of plutonium and minor actinides in fusion/fission hybrids and ADS are presented
Energy Technology Data Exchange (ETDEWEB)
Dahlfors, Marcus
2003-05-01
This text is a summary of two studies the author has performed within the field of 3-D Monte Carlo calculations of Accelerator Driven Systems (ADS) for transmutation of nuclear waste. The simulations were carried out with the state-of-the-art computer code package EA-MC, developed by C. Rubbia and his group at CERN. The concept studied is ANSALDOs 80 MWth Energy Amplifier Demonstration Facility based on classical MOX-fuel technology and on molten Lead-Bismuth Eutectic cooling. A review of neutron cross section sensitivity in numerical calculations of an ADS and a comparative assessment relevant to the transmutation efficiency of plutonium and minor actinides in fusion/fission hybrids and ADS are presented.
International Nuclear Information System (INIS)
Ventura, Mirta A.
2002-01-01
The accidental sequences corresponding to the initiating events associated to T15 group are modeled. This group is defined in the Probabilistic Risk Assessment final report. The code used was RELAP5/MOD3. The representative event of the group is the complete loss of UK system, the complementary safety cooling system of the CNA-I. The transient determined from different availability conditions of systems involved in the event is analyzed. Besides the initiating event, the results coming from the event tree heading failures are also studied. Finally, the sequences corresponding to safe shutdown of the plant, and the sequences involved in core damage are determined. (author)
International Nuclear Information System (INIS)
Liang, T.K.S.; Huan-Jen, Hung; Chin-Jang, Chang; Lance, Wang
2001-01-01
In light water reactors, particularly the pressurized water reactor (PWR), the severity of a LOCA (loss of coolant accident) will limit how high the reactor power can operate. Although the best-estimate LOCA licensing methodology can provide the greatest margin on the PCT (peak cladding temperature) evaluation during LOCA, it generally takes more resources to develop. Instead, implementation of evaluation models required by the Appendix K of 10 CFR 50 upon an advanced thermal-hydraulic platform can also enlarge significant margin between the highest calculated PCT and the safety limit of 2200 F. The compliance of the current RELAP5-3D code with Appendix K of 10 CFR50 has been evaluated, and it was found that there are ten areas where code assessment and/or further modifications were required to satisfy the requirements set forth in the Appendix K of 10 CFR 50. The associated models for LOCA consequent phenomenon analysis should follow the major concern of regulation and be expected to give more conservative results than those by the best-estimate methodology. They were required to predict the decay power level, the blowdown hydraulics, the blowdown heat transfer, the flooding rate, and the flooding heat transfer. All of the ten areas included in above classified simulations have been further evaluated and the RELAP5-3D has been successfully modified to fulfill the associated requirements. In addition, to verify and assess the development of the Appendix K version of RELAP5-3D, nine separate-effect experiments were adopted. Through the assessments against separate-effect experiments, the success of the code modification in accordance with the Appendix K of 10 CFR 50 was demonstrated. We will apply another six sets of integral-effect experiments in the next step to assure the integral conservatism of the Appendix K version of RELAP5-3D on LOCA licensing evaluation. (authors)
Bartczak, Witold M.; Kroh, Jerzy
The simulation of the transient d.c. conductivity in a quasi one-dimensional system of charges produced by a pulse of ionizing radiation in a solid sample has been performed. The simulation is based on the macroscopic conductivity equations and can provide physical insight into d.c. conductivity measurements, particularly for the case of transient currents in samples with internal space charge. We consider the system of mobile (negative) and immobile (positive) charges produced by a pulse of ionizing radiation in the sample under a fixed external voltage V0. The presence of space charge results in an electric field which is a function of both the spatial and the time variable: E( z, t). Given the space charge density, the electric field can be calculated from the Poisson equation. However, for an arbitrary space charge distribution, the corresponding equations can only be solved numerically. The two non-trivial cases for which approximate analytical solutions can be provided are: (i) The density of the current carriers n( z, t) is negligible in comparison with the density of immobile space charge N( z). A general analytical solution has been found for this case using Green's functions. The solutions for two cases, viz. the homogeneous distribution of space charge N( z) = N, and the non-homogeneous exponential distribution N( z) = A exp(- Bz), have been separately discussed. (ii) The space charge created in the pulse without any space charge present prior to the irradiation.
International Nuclear Information System (INIS)
Lu, X; Tervola, P; Viljanen, M
2005-01-01
This paper provides an efficient analytical tool for solving the heat conduction equation in a multi-dimensional composite slab subject to generally time-dependent boundary conditions. A temporal Laplace transformation and novel separation of variables are applied to the heat equation. The time-dependent boundary conditions are approximated with Fourier series. Taking advantage of the periodic properties of Fourier series, the corresponding analytical solution is obtained and expressed explicitly through employing variable transformations. For such conduction problems, nearly all the published works necessitate numerical work such as computing residues or searching for eigenvalues even for a one-dimensional composite slab. In this paper, the proposed method involves no numerical iteration. The final closed form solution is straightforward; hence, the physical parameters are clearly shown in the formula. The accuracy of the developed analytical method is demonstrated by comparison with numerical calculations
International Nuclear Information System (INIS)
Kussmaul, K.; Kobes, E.; Diem, H.; Schrammel, D.; Brosi, S.
1994-01-01
Within the scope of the German HDR safety programme, several tests were carried out to investigate transient pipe loading initiated by a simulated double-ended guillotine break event, and subsequent closure of a feedwater check valve (water hammer, blow-down). Numerical analyses by means of finite element programmes were performed in parallel to the experiments. Using water hammer tests of a DN 425 piping system with predamaged components, the procedure of such analyses will be demonstrated. The results are presented, beginning with structural dynamic calculations of the undamaged piping; followed by coupling of structural dynamics and fracture mechanics computations with simple flaw elements (line spring); and finishing with costly three-dimensional fracture mechanics analyses. A good description of the real piping behaviour can be made by the numerical methods, even in the case of high plastification processes. ((orig.))
International Nuclear Information System (INIS)
Jimenez, J.; Herrero, J. J.; Cuervo, D.; Aragones, J. M.
2010-10-01
Nowadays coupled 3-dimensional neutron kinetics and thermal-hydraulic core calculations are performed by applying a radial average channel approach using a meshing of one quarter of assembly in the best case. This approach does not take into account the subchannels effects due to the averaging of the physical fields and the loose of heterogeneity in the thermal-hydraulic model. Therefore the models do not have enough resolution to predict those subchannels effects which are important for the fuel design safety margins, because it is in the local scale, where we can search the hottest pellet or the maximum heat flux. The Polytechnic University of Madrid advanced multi-scale neutron-kinetics and thermal-hydraulics methodologies being implemented in COBAYA3 include domain decomposition by alternate core dissections for the local 3-dimensional fine-mesh scale problems (pin cells/subchannels) and an analytical nodal diffusion solver for the coarse mesh scale coupled with the thermal-hydraulic using a model of one channel per assembly or per quarter of assembly. In this work, we address the domain decomposition by the alternate core dissections methodology applied to solve coupled 3-dimensional neutronic-thermal-hydraulic problems at the fine-mesh scale. The neutronic-thermal-hydraulic coupling at the cell-subchannel scale allows the treatment of the effects of the detailed thermal-hydraulic feedbacks on cross-sections, thus resulting in better estimates of the local safety margins at the pin level. (Author)
Energy Technology Data Exchange (ETDEWEB)
Gerhard, G.; Ioffe, A. [Gerhard-Mercator-Univ.-GH Duisburg (Germany). Fachgebiet Elektrische Energieuebertragung
1997-10-20
The transient electromagnetic field occured from the overvoltages in a slip-on cable termination was calculated by using the FDTD-method. The electric field strength in a gap between the cable shield and the stress cone was studied. (orig.) [Deutsch] Mit Hilfe des FDTD-Feldberechnungsverfahrens wird das transiente elektromagnetische Feld in einem Aufschiebeendverschluss untersucht, wobei ein Luftspalt zwischen den leitenden Teilen der Kabelader und dem Feldsteuerelement beruecksichtigt wird. (orig.)
International Nuclear Information System (INIS)
Hoefer, I.
1980-12-01
For the calculation of flows in high-temperature reactors and of their temperature behavior the equations of the method of turbulent flow in the primitive form are derived for inhomogeneous regions. This system of equations is appropriate for the investigation of transient and quasi-stationary phenomena in pebble beds. By modification of the flow function in parallel arranged reflector channels a parallel flow can be simulated. For simplification the flow in region with a smaller pressure loss is assumed to be a potential flow. For the numerical solution of the time-dependent convective parts of the system of equations a number of explicit and implicit difference methods are compared. If the method using UP-WIND differences is taken to be an interpolation method the introduction of an extension becomes possible, which together with preliminary integration of the fictional terms allows to apply larger time steps. The algebraic system of equations for numerical calculation of a steady flow field also is established by formation of UP-WIND differences for the convective terms. By mathematical verification of some examples the applicability of the mathematical model for flow problems in pebble beds with forced or natural convection is shown. (orig.) [de
International Nuclear Information System (INIS)
Ball, D.G.; Drake, J.B.; Cheverton, R.D.; Iskander, S.K.
1984-02-01
The OCA-II computer code, like its predecessor OCA-I, performs the thermal, stress, and linear elastic fracture-mechanics analysis for long flaws on the surface of a cylinder that is subjected to thermal and pressure transients. OCA-II represents a revised and expanded version of OCA-I and includes as new features (1) cladding as a discrete region, (2) a finite-element subroutine for calculating the stresses, and (3) the ability to calculate stress intensity factors for certain three-dimensional flaws, for two-dimensional circumferential flaws on the inner surface, and for both axial and circumferential flaws on the outer surface. OCA-I considered only inner-surface flaws. An option is included in OCA-II that permits a search for critical values of fluence or nil-ductility reference temperature corresponding to a specified failure criterion. These and other features of OCA-II are described in the report, which also includes user instructions for the code
Directory of Open Access Journals (Sweden)
Xiaoyi Zhang
2016-02-01
Full Text Available Characterizing the geometric and electronic structures of individual photoexcited dye molecules in solution is an important step towards understanding the interfacial properties of photo-active electrodes. The broad family of “red sensitizers” based on osmium(II polypyridyl compounds often undergoes small photo-induced structural changes which are challenging to characterize. In this work, X-ray transient absorption spectroscopy with picosecond temporal resolution is employed to determine the geometric and electronic structures of the photoexcited triplet state of [Os(terpy2]2+ (terpy: 2,2′:6′,2″-terpyridine solvated in methanol. From the EXAFS analysis, the structural changes can be characterized by a slight overall expansion of the first coordination shell [OsN6]. DFT calculations supports the XTA results. They also provide additional information about the nature of the molecular orbitals that contribute to the optical spectrum (with TD-DFT and the near-edge region of the X-ray spectra.
Energy Technology Data Exchange (ETDEWEB)
Oyama, Y [Hitachi Car Engineering, Ltd., Tokyo (Japan); Nishimura, Y; Osuga, M; Yamauchi, T [Hitachi, Ltd., Tokyo (Japan)
1997-10-01
Air flow characteristics of hot-wire air flow meters for gasoline fuel-injection systems with supercharging and exhaust gas recycle during transient conditions were investigated to analyze a simple method for calculating air mass in cylinder. It was clarified that the air mass in cylinder could be calculated by compensating for the change of air mass in intake system by using aerodynamic models of intake system. 3 refs., 6 figs., 1 tab.
International Nuclear Information System (INIS)
Rana, S.B.
1973-12-01
The report contains a user's description of the 3-dimensional programme POISON 1 for calculating reactivity transients due to fission-product poisoning during changes of reactor power. The chapter dealing with Xe poisoning contains a description of Xe tables, the method of operational determination of Xe poisoning, use of Xe transients for calibrating control rods and means of shutting down the reactor without being overriden by Xe poisoning. Sm poisoning is determined continuously on the basis of the power diagram of reactor operation. In conclusion a possibility of using the programme in a process computer in combination with self-powered detectors as local power sensors is indicated. (author)
International Nuclear Information System (INIS)
Saha, P.
1984-01-01
This chapter reviews the papers on the pressurized water reactor (PWR) and boiling water reactor (BWR) transient analyses given at the American Nuclear Society Topical Meeting on Anticipated and Abnormal Plant Transients in Light Water Reactors. Most of the papers were based on the systems calculations performed using the TRAC-PWR, RELAP5 and RETRAN codes. The status of the nuclear industry in the code applications area is discussed. It is concluded that even though comprehensive computer codes are available for plant transient analysis, there is still a need to exercise engineering judgment, simpler tools and even hand calculations to supplement these codes
Claassen, R.J.G.|info:eu-repo/dai/nl/269266224
A capability approach prescribes paternalist government actions to the extent that it requires the promotion of specific functionings, instead of the corresponding capabilities. Capability theorists have argued that their theories do not have much of these paternalist implications, since promoting
International Nuclear Information System (INIS)
Ercan, Y.; Hoeld, A.; Lupas, O.
1982-04-01
A program description of the code GARLIC-B is given. The code is based on a nonlinear transient model for BWR nuclear power plants which consist of a 3D-core, a top plenum, steam removal and feed water systems and a downcomer with main coolant recirculation pumps. The core is subdivided into a number of superboxes and flow channels with different coolant mass flow rates. Subcooled boiling within these channels has an important reactivity feed back effect and has to be taken also into account. The code computes the local and global core and plant transient situation as dependent on both the inherent core dynamics and external control actions, i.e., disturbances such as motions of control rod banks, changes of mass flow rates of coolant, feed water and steam outlet. The case of a pressure-controlled reactor operation is also considered. (orig./GL) [de
Initial Implementation of Transient VERA-CS
Energy Technology Data Exchange (ETDEWEB)
Gerlach, Andrew [Univ. of Michigan, Ann Arbor, MI (United States); Kochunas, Brendan [Univ. of Michigan, Ann Arbor, MI (United States); Salko, Robert [Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States); Wysocki, Aaron J. [Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States)
2017-11-01
In this milestone the capabilities of both CTF and MPACT were extended to perform coupled transient calculations. This required several small changes in MPACT to setup the problems correctly, perform the edits correctly, and call the appropriate CTF interfaces in the right order. For CTF, revisions and corrections to the transient timestepping algorithm were made, as well as the addition of a new interface subroutine to allow MPACT to drive CTF at each timestep. With the modifications completed, the initial coupled capability was demonstrated on some problems used for code verification, a hypothetical small mini-core, and a Watts Bar demonstration problem. For each of these cases the results showed good agreement with the previous MPACT internal TH feedback model that relied on a simplified fuel heat conduction model and simplified coolant treatment. After the pulse the results are notably different as expected, where the effects of convection of heat to the coolant can be observed. Areas for future work were discussed, including assessment and development of the CTF dynamic fuel deformation and gap conductance models, addition of suitable transient boiling and CHF models for the rapid heating and cooling rates seen in RIAs, additional validation and demonstration work, and areas for improvement to the code input and output capabilities.
PWR systems transient analysis
International Nuclear Information System (INIS)
Kennedy, M.F.; Peeler, G.B.; Abramson, P.B.
1985-01-01
Analysis of transients in pressurized water reactor (PWR) systems involves the assessment of the response of the total plant, including primary and secondary coolant systems, steam piping and turbine (possibly including the complete feedwater train), and various control and safety systems. Transient analysis is performed as part of the plant safety analysis to insure the adequacy of the reactor design and operating procedures and to verify the applicable plant emergency guidelines. Event sequences which must be examined are developed by considering possible failures or maloperations of plant components. These vary in severity (and calculational difficulty) from a series of normal operational transients, such as minor load changes, reactor trips, valve and pump malfunctions, up to the double-ended guillotine rupture of a primary reactor coolant system pipe known as a Large Break Loss of Coolant Accident (LBLOCA). The focus of this paper is the analysis of all those transients and accidents except loss of coolant accidents
Robeyns, Ingrid
2012-01-01
textabstractThe capability approach is one of the most recent additions to the landscape of normative theories in ethics and political philosophy. Yet in its present stage of development, the capability approach is not a full-blown normative theory, in contrast to utilitarianism, deontological theories, virtue ethics, or pragmatism. As I will argue in this chapter, at present the core of the capability approach is an account of value, which together with some other (more minor) normative comm...
International Nuclear Information System (INIS)
Muir, M.D.
1975-01-01
The design and design philosophy of a high performance, extremely versatile transient analyzer is described. This sub-system was designed to be controlled through the data acquisition computer system which allows hands off operation. Thus it may be placed on the experiment side of the high voltage safety break between the experimental device and the control room. This analyzer provides control features which are extremely useful for data acquisition from PPPL diagnostics. These include dynamic sample rate changing, which may be intermixed with multiple post trigger operations with variable length blocks using normal, peak to peak or integrate modes. Included in the discussion are general remarks on the advantages of adding intelligence to transient analyzers, a detailed description of the characteristics of the PPPL transient analyzer, a description of the hardware, firmware, control language and operation of the PPPL transient analyzer, and general remarks on future trends in this type of instrumentation both at PPPL and in general
Advanced thermohydraulic simulation code for transients in LMFBRs (SSC-L code)
Energy Technology Data Exchange (ETDEWEB)
Agrawal, A.K.
1978-02-01
Physical models for various processes that are encountered in preaccident and transient simulation of thermohydraulic transients in the entire liquid metal fast breeder reactor (LMFBR) plant are described in this report. A computer code, SSC-L, was written as a part of the Super System Code (SSC) development project for the ''loop''-type designs of LMFBRs. This code has the self-starting capability, i.e., preaccident or steady-state calculations are performed internally. These results then serve as the starting point for the transient simulation.
Advanced thermohydraulic simulation code for transients in LMFBRs (SSC-L code)
International Nuclear Information System (INIS)
Agrawal, A.K.
1978-02-01
Physical models for various processes that are encountered in preaccident and transient simulation of thermohydraulic transients in the entire liquid metal fast breeder reactor (LMFBR) plant are described in this report. A computer code, SSC-L, was written as a part of the Super System Code (SSC) development project for the ''loop''-type designs of LMFBRs. This code has the self-starting capability, i.e., preaccident or steady-state calculations are performed internally. These results then serve as the starting point for the transient simulation
Schweig, Armin; Diehl, Frank; Kesper, Karl; Meyer, Hermann
1989-07-01
The electronic absorption spectra of benzo[b]thiete ( 1) and of transient o-thiobenzoquinonemethide ( 2) have been obtained. Semiempirical valence-electron calculations using the CNDO/S SECI, CNDO/S PERTCI and LNDO/S PERTCI methods and correlation diagrams using suitable reference compounds ad aniline, thiophenol, thioanisole, all-trans-octatetraene and o-xylylene are applied to the interpretation of the spectra. The results clearly reveal 1 as a typically donor-substituted benzene derivative and 2 as a polyene-like system closely related to o-xylylene.
International Nuclear Information System (INIS)
Adamik, V.; Matejovic, P.
1989-01-01
The problems are discussed of nonstationary, nonlinear dynamics of the continuum. A survey is presented of calculation methods in the given area with emphasis on the area of impact problems. A description is presented of the explicit finite elements method and its application to two-dimensional Cartesian and cylindrical configurations. Using the method the explicit calculation code FINEDAN was written which was tested in a series of verification calculations for different configurations and different types of continuum. The main characteristics are presented of the code and of some, of its practical applications. Envisaged trends of the development of the code and its possible applications in the technology of nuclear reactors are given. (author). 9 figs., 4 tabs., 10 refs
DEFF Research Database (Denmark)
Grünbaum, Niels Nolsøe; Stenger, Marianne
2013-01-01
The findings reveal a positive relationship between dynamic capabilities and innovation performance in the case enterprises, as we would expect. It was, however, not possible to establish a positive relationship between innovation performance and profitability. Nor was there any positive...... relationship between dynamic capabilities and profitability....
I.A.M. Robeyns (Ingrid)
2012-01-01
textabstractThe capability approach is one of the most recent additions to the landscape of normative theories in ethics and political philosophy. Yet in its present stage of development, the capability approach is not a full-blown normative theory, in contrast to utilitarianism, deontological
Peach Bottom Turbine Trip Simulations with RETRAN Using INER/TPC BWR Transient Analysis Method
International Nuclear Information System (INIS)
Kao Lainsu; Chiang, Show-Chyuan
2005-01-01
The work described in this paper is benchmark calculations of pressurization transient turbine trip tests performed at the Peach Bottom boiling water reactor (BWR). It is part of an overall effort in providing qualification basis for the INER/TPC BWR transient analysis method developed for the Kuosheng and Chinshan plants. The method primarily utilizes an advanced system thermal hydraulics code, RETRAN02/MOD5, for transient safety analyses. Since pressurization transients would result in a strong coupling effect between core neutronic and system thermal hydraulics responses, the INER/TPC method employs the one-dimensional kinetic model in RETRAN with a cross-section data library generated by the Studsvik-CMS code package for the transient calculations. The Peach Bottom Turbine Trip (PBTT) tests, including TT1, TT2, and TT3, have been successfully performed in the plant and assigned as standards commonly for licensing method qualifications for years. It is an essential requirement for licensing purposes to verify integral capabilities and accuracies of the codes and models of the INER/TPC method in simulating such pressurization transients. Specific Peach Bottom plant models, including both neutronics and thermal hydraulics, are developed using modeling approaches and experiences generally adopted in the INER/TPC method. Important model assumptions in RETRAN for the PBTT test simulations are described in this paper. Simulation calculations are performed with best-estimated initial and boundary conditions obtained from plant test measurements. The calculation results presented in this paper demonstrate that the INER/TPC method is capable of calculating accurately the core and system transient behaviors of the tests. Excellent agreement, both in trends and magnitudes between the RETRAN calculation results and the PBTT measurements, shows reliable qualifications of the codes/users/models involved in the method. The RETRAN calculated peak neutron fluxes of the PBTT
International Nuclear Information System (INIS)
Porter, W.H.L.
1976-05-01
This paper gives an appreciation and commentary of the basic calculation methods under development at AEE Winfrith for the analysis of multicompartment total containments. The assumptions introduced and the effects of their variation are important in establishing a parametric survey of the range of possible conditions which the containment may be required to meet. These aspects of the performance will be discussed as each individual factor in the train of events is examined in turn. (U.K.)
International Nuclear Information System (INIS)
Sim, Suk K.; Chang, W. P.; Kim, K. D.; Lee, S. J.; Kim, H. C.; Yoon, H. Y.
1997-02-01
The development of TASS 1.0 code has been completed and validated its capability in applying for the licensing transient analyses of the CE and Westinghouse type operating reactors as well as the PWR plants under construction in Korea. The validation of the TASS 1.0 code has been achieved through the comparison calculations of the FSAR transients, loss of AC power transient plant data, load rejection and startup test data for the reference plants as well as the BETHSY loop steam generator tube rupture test data. TASS 1.0 calculation agrees well with the best FSAR transient and shows its capability in simulating plant transient analyses. (author). 12 refs., 32 tabs., 132 figs
DEFF Research Database (Denmark)
Mogensen, Martin; Frey, Davide; Guerraoui, Rachid
Gossip-based protocols are now acknowledged as a sound basis to implement collaborative high-bandwidth content dissemination: content location is disseminated through gossip, the actual contents being subsequently pulled. In this paper, we present HEAP, HEterogeneity Aware gossip Protocol, where...... nodes dynamically adjust their contribution to gossip dissemination according to their capabilities. Using a continuous, itself gossip-based, approximation of relative capabilities, HEAP dynamically leverages the most capable nodes by (a) increasing their fanouts (while decreasing by the same proportion...... declare a high capability in order to augment their perceived quality without contributing accordingly. We evaluate HEAP in the context of a video streaming application on a 236 PlanetLab nodes testbed. Our results shows that HEAP improves the quality of the streaming by 25% over a standard gossip...
Effect of pressure on the transient swelling rate of oxide fuel
International Nuclear Information System (INIS)
Gruber, E.E.
1982-04-01
An analysis of the transient swelling rate of oxide fuel, based on fission-gas bubble conditions calculated with the FRAS3 code, has been developed and implemented in the code. The need for this capability arises in the coupling of the FRAS3 fission-gas analysis code to the FPIN fuel-pin mechanics code. An efficient means of closely coupling the calculations of swelling strains and stresses between the modules is required. The present analysis provides parameters that allow the FPIN calculation to proceed through a fairly large time step, using estimated swelling rates, to calculate the stresses. These stress values can then be applied in the FRAS3 detailed calculation to refine the swelling calculation, and to provide new values for the parameters to estimate the swelling in the next time step. The swelling rates were calculated for two representative transients and used to estimate swelling over a short time period for various stress levels
Capability to model reactor regulating system in RFSP
Energy Technology Data Exchange (ETDEWEB)
Chow, H C; Rouben, B; Younis, M H; Jenkins, D A [Atomic Energy of Canada Ltd., Mississauga, ON (Canada); Baudouin, A [Hydro-Quebec, Montreal, PQ (Canada); Thompson, P D [New Brunswick Electric Power Commission, Point Lepreau, NB (Canada). Point Lepreau Generating Station
1996-12-31
The Reactor Regulating System package extracted from SMOKIN-G2 was linked within RFSP to the spatial kinetics calculation. The objective is to use this new capability in safety analysis to model the actions of RRS in hypothetical events such as in-core LOCA or moderator drain scenarios. This paper describes the RRS modelling in RFSP and its coupling to the neutronics calculations, verification of the RRS control routine functions, sample applications and comparisons to SMOKIN-G2 results for the same transient simulations. (author). 7 refs., 6 figs.
DEFF Research Database (Denmark)
Jensen, Niels Rosendal; Kjeldsen, Christian Christrup
Lærebogen er den første samlede danske præsentation af den af Amartya Sen og Martha Nussbaum udviklede Capability Approach. Bogen indeholder en præsentation og diskussion af Sen og Nussbaums teoretiske platform. I bogen indgår eksempler fra såvel uddannelse/uddannelsespolitik, pædagogik og omsorg....
Nuclear power plant transients: where are we
International Nuclear Information System (INIS)
Majumdar, D.
1984-05-01
This document is in part a postconference review and summary of the American Nuclear Society sponsored Anticipated and Abnormal Plant Transients in Light Water Reactors Conference held in Jackson, Wyoming, September 26-29, 1983, and in part a reflection upon the issues of plant transients and their impact on the viability of nuclear power. This document discusses state-of-the-art knowledge, deficiencies, and future directions in the plant transients area as seen through this conference. It describes briefly what was reported in this conference, emphasizes areas where it is felt there is confidence in the nuclear industry, and also discusses where the experts did not have a consensus. Areas covered in the document include major issues in operational transients, transient management, transient events experience base, the status of the analytical tools and their capabilities, probabilistic risk assessment applications in operational transients, and human factors impact on plant transients management
DEFF Research Database (Denmark)
Rasmussen, Lauge Baungaard; Nielsen, Thorkild
2003-01-01
The aim of this article is to analyse entrepreneurship from an action research perspective. What is entrepreneurship about? Which are the fundamental capabilities and processes of entrepreneurship? To answer these questions the article includes a case study of a Danish entrepreneur and his networ....... Finally, the article discuss, how more long term action research methods could be integrated into the entrepreneurial processes and the possible impacts of such an implementation?...
Energy Technology Data Exchange (ETDEWEB)
Glaeser, H.; Graf, U.; Herb, J.; and others
2012-02-15
The project RS1184 „Thermal-hydraulic Calculation Methods for Transients and Accidents of the Reactor Cooling System Under Special Consideration of Multi-Dimensional Flows (ATHLET, FLUBOX, CFX)'' consists of four work packages: 1. Further development of the computer code ATHLET 2. Termination of FLUBOX development and development of an ATHLET-internal 3D module 3. Coupling of ATHLET and CFD code ANSYS CFX as well as CFX model development to simulate three-dimensional flows in the reactor coolant system 4. Prediction capability of computer code ATHLET. One of the superior objectives of the project is to improve the prediction capability of the thermal-hydraulic system code ATHLET, including the simulation of multi-dimensional flow in the reactor vessel. The constitutive equations in ATHLET, especially the momentum equations in ATHLET, are written in one-dimensional form. It was planned to develop the 2D/3D module FLUBOX further and couple it with ATHLET. Due to reasons given in chapter 3, the FLUBOX development was terminated. Instead, the decision was made to develop a fast running internal ATHLET-module. The 2D/3D equations for ATHLET have been derived and were implemented. That strategy allows using all ATHLET models and the ATHLET code structure. An additional advantage is that different numerical schemes of different codes, and consequently a loss of efficiency, will be avoided. A second possibility is the coupling of ATHLET with the CFD code ANSYS CFX. Such a coupled code system will be used in those cases when a part of the simulation area is needed to be calculated with high resolution. Such a detailed modelling cannot be provided by ATHLET-3D. A complete representation of the cooling system by a CFD code cannot be performed due to calculation time. In order to calculate the complete system behavior still with ATHLET, that part to be investigated in more detail, will be replaced by a CFX model. Several new models and improvements of existing
Current limiting capability of diffused resistors
International Nuclear Information System (INIS)
Shedd, W.; Cappelli, J.
1979-01-01
An experimental evaluation of the current limiting capability of dielectrically isolated diffused resistors at transient ionizing dose rates up to 6*10 12 rads(Si)/sec is presented. Existing theoretical predictions of the transient response of diffused resistors are summarized and compared to the experimentally measured values. The test resistors used allow the effects of sheet resistance and geometry on the transient response to be determined. The experimental results show that typical dielectrically isolated diffused resistors maintain adequate current limiting capability for use in radiation hardened integrated circuits
Final report for the H3 transient overpower failure threshold experiment
International Nuclear Information System (INIS)
Wright, A.E.; Rothman, A.B.; Stahl, D.; Agrawal, A.K.; Deitrich, L.W.; Chen, S.S.
1975-06-01
Test H3 was the first transient overpower failure-threshold experiment in TREAT to use irradiated fuel and to employ a TREAT transient shaped to produce sample-temperature distributions typical of steady state prior to the overpower excursion. A seven-pin assembly was tested within the Mark-II TREAT sodium loop. The experiment was performed successfully with satisfactory TREAT power transient and loop performance, and demonstrated the capability of intermediate-power EBR-II-irradiated fuel at low burnup (no central void) to withstand a mild overpower transient that terminated with fuel temperatures just short of the solidus without cladding strain. Calculated values of outlet coolant temperature and amount of molten fuel generally agree well with the test data. Posttest thermalhydraulic and mechanical analyses of the fuel pins are reported. Results of detailed nondestructive and destructive examinations of the preirradiated central pin and a fresh peripheral pin are presented. (U.S.)
Transient voltage oscillations in coils
International Nuclear Information System (INIS)
Chowdhuri, P.
1985-01-01
Magnet coils may be excited into internal voltage oscillations by transient voltages. Such oscillations may electrically stress the magnet's dielectric components to many times its normal stress. This may precipitate a dielectric failure, and the attendant prolonged loss of service and costly repair work. Therefore, it is important to know the natural frequencies of oscillations of a magnet during the design stage, and to determine whether the expected switching transient voltages can excite the magnet into high-voltage internal oscillations. The series capacitance of a winding significantly affects its natural frequencies. However, the series capacitance is difficult to calculate, because it may comprise complex capacitance network, consisting of intra- and inter-coil turn-to-turn capacitances of the coil sections. A method of calculating the series capacitance of a winding is proposed. This method is rigorous but simple to execute. The time-varying transient voltages along the winding are also calculated
International Nuclear Information System (INIS)
Bang, Young Seok; Kim, Kap; Seul, Kwang Won; Kim, Hho Jung
1997-01-01
A transient natural circulation behavior during a LOCA at hot-standby operation is evaluated for YGN Units 3/4. The plant initial condition is determined within the EOP limitation as suitable to hot-standby mode and the transient scenario is prepared as relevant to evaluation of transient natural circulation. A 0.4% cold leg break with loss of off-site power is calculated with RELAP5/MOD3.2, whose predictability has been verified for SBLOCA natural circulation test, S-NC-8B. Through one hour transient analysis, it is found that the plant has its own decay heat removal capability by natural circulation following a LOCA at hot-standby mode. Additional calculation is performed to investigate an effect of HPSI flow on natural circulation
Energy Technology Data Exchange (ETDEWEB)
Shim, Suk Koo; Jang, Won Pyo; Kim, Heui Chul; Kim, Kyung Doo; Lee, Sung Jae; Hah, Kyooi Suk; Song, Soon Jah; Um, Kil Sub; Yoon, Han Yung; Kim, Doo Il; Yoo, Hyung Keun; Choi, Jae Don; Lee, Byung Il; Kim, Jung Jin [Korea Atomic Energy Research Institute, Taejon (Korea, Republic of)
1994-07-01
During the third year of the project the development of TASS 1.0 code has been completed and validated its capability in applying for the licensing transient analyses of the Westinghouse and CE type operating reactors as well as the PWR reactors under construction in Korea. The validation of the TASS 1.0 code has been achieved through the comparison calculations of the YGN-3/4 FSAR transients, Kori-3 loss of AC power transient, plant data, Kori-4 load rejection and YGN-3 startup test data as well as the BETHSY loop steam generator tube rupture test data. TASS 1.0 calculation agrees well with the best estimate RELAP5/MOD 3.1 calculation for the YGN-3/4 FASR transients and shows its capability in simulating plant transient and startup data as well as the thermal hydraulic transient test data. Topical reports on TASS 1.0 code have been prepared and will be submitted to Korea Institute of Nuclear Safety for its licensing application to Westinghouse and CE type PWR transient analyses. The development of TASS 2.0 code has been head started in this year to timely utilize the TASS 2.0 code for the KNGR design certification. 65 figs, 30 tabs, 44 refs. (Author).
Whole-core thermal-hydraulic transient code development and verification for LMFBR analysis
International Nuclear Information System (INIS)
Spencer, D.R.
1979-04-01
Predicted performance during both steady state and transient reactor operation determines the steady state operating limits on LMFBRs. Unnecessary conservatism in performance predictions will not contribute to safety, but will restrict the reactor to more conservative, less economical steady state operation. The most general method for reducing analytical conservatism in LMFBR's without compromising safety is to develop, validate and apply more sophisticated computer models to the limiting performance analyses. The purpose of the on-going Natural Circulation Verification Program (NCVP) is to develop and validate computer codes to analyze natural circulation transients in LMFBRs, and thus, replace unnecessary analytical conservatism with demonstrated calculational capability
Atmospheric release advisory capability
International Nuclear Information System (INIS)
Sullivan, T.J.
1981-01-01
The ARAC system (Atmospheric Release Advisory Capability) is described. The system is a collection of people, computers, computer models, topographic data and meteorological input data that together permits a calculation of, in a quasi-predictive sense, where effluent from an accident will migrate through the atmosphere, where it will be deposited on the ground, and what instantaneous and integrated dose an exposed individual would receive
Transient pseudohypoaldosteronism
Directory of Open Access Journals (Sweden)
Stajić Nataša
2011-01-01
Full Text Available Introduction. Infants with urinary tract malformations (UTM presenting with urinary tract infection (UTI are prone to develop transient type 1 pseudohypoaldosteronism (THPA1. Objective. Report on patient series with characteristics of THPA1, UTM and/or UTI and suggestions for the diagnosis and therapy. Methods. Patients underwent blood and urine electrolyte and acid-base analysis, serum aldosterosterone levels and plasma rennin activity measuring; urinalysis, urinoculture and renal ultrasound were done and medical and/or surgical therapy was instituted. Results. Hyponatraemia (120.9±5.8 mmol/L, hyperkalaemia (6.9±0.9 mmol/L, metabolic acidosis (plasma bicarbonate, 11±1.4 mmol/L, and a rise in serum creatinine levels (145±101 μmol/L were associated with inappropriately high urinary sodium (51.3±17.5 mmol/L and low potassium (14.1±5.9 mmol/L excretion. Elevated plasma aldosterone concentrations (170.4±100.5 ng/dL and the very high levels of the plasma aldosterone to potassium ratio (25.2±15.6 together with diminished urinary K/Na values (0.31±0.19 indicated tubular resistance to aldosterone. After institution of appropriate medical and/or surgical therapy, serum electrolytes, creatinine, and acid-base balance were normalized. Imaging studies showed ureteropyelic or ureterovesical junction obstruction in 3 and 2 patients, respectively, posterior urethral valves in 3, and normal UT in 1 patient. According to our knowledge, this is the first report on THPA1 in the Serbian literature. Conclusion. Male infants with hyponatraemia, hyperkalaemia and metabolic acidosis have to have their urine examined and the renal ultrasound has to be done in order to avoid both, the underdiagnosis of THPA1 and the inappropriate medication.
Development of a transient criticality evaluation method
International Nuclear Information System (INIS)
Pain, C.C.; Eaton, M.D.; Miles, B.; Ziver, A.K.; Gomes, J.L.M.A.; Umpleby, A.P.; Piggott, M.D.; Goddard, A.J.H.; Oliveira, C.R.E. de
2005-01-01
In developing a transient criticality evaluation method we model, in full spatial/temporal detail, the neutron fluxes and consequent power and the evolving material properties - their flows, energies, phase changes etc. These methods are embodied in the generic method FETCH code which is based as far as possible on basic principles and is capable of use in exploring safety-related situations somewhat beyond the range of experiment. FETCH is a general geometry code capable of addressing a range of criticality issues in fissile materials. The code embodies both transient radiation transport and transient fluid dynamics. Work on powders, granular materials, porous media and solutions is reviewed. The capability for modelling transient criticality for chemical plant, waste matrices and advanced reactors is also outlined. (author)
TRAWA, a transient analysis code for water reactions
International Nuclear Information System (INIS)
Rajamaeki, M.
1976-06-01
TRAWA is a transient analysis code for water reactors. It solves the two-group neutron diffusion equations simultaneously with the heat conduction equations and the two-phase hydraulic equations for one or more channels. At most one-dimensional submodels are used. Neither thermal nor hydraulic mixing appear between channels. Doppler, coolant density, coolant temperature, and soluble poison density feedbacks due to the thermohydraulics of the channels are described by using polynomial expansions for the group constants. The hydraulic circuit outside the reactor core consists of by-pass channel and risers with two-phase flow and of pump lines with incompressible flow. Nontrivial implicit methods are employed in the discretization of the equations to allow for sparse spatial mesh and flexible choice of time steps. Various transients can be calculated by applying external disturbances. The code is extensively supplied by input and output capabilities. TRAWA is written in FORTRAN V for UNIVAC 1108 computer. (author)
Dose rate calculations for a reconnaissance vehicle
International Nuclear Information System (INIS)
Grindrod, L.; Mackey, J.; Salmon, M.; Smith, C.; Wall, S.
2005-01-01
A Chemical Nuclear Reconnaissance System (CNRS) has been developed by the British Ministry of Defence to make chemical and radiation measurements on contaminated terrain using appropriate sensors and recording equipment installed in a land rover. A research programme is under way to develop and validate a predictive capability to calculate the build-up of contamination on the vehicle, radiation detector performance and dose rates to the occupants of the vehicle. This paper describes the geometric model of the vehicle and the methodology used for calculations of detector response. Calculated dose rates obtained using the MCBEND Monte Carlo radiation transport computer code in adjoint mode are presented. These address the transient response of the detectors as the vehicle passes through a contaminated area. Calculated dose rates were found to agree with the measured data to be within the experimental uncertainties, thus giving confidence in the shielding model of the vehicle and its application to other scenarios. (authors)
APR1400 Locked Rotor Transient Analysis using KNAP
International Nuclear Information System (INIS)
Lee, Dong-Hyuk; Kim, Yo-Han; Ha, Sang Jun
2007-01-01
KEPRI (Korea Electric Power Research Institute) has developed safety analysis methodology for non-LOCA (Loss Of Coolant Accident) analysis of OPR1000 (Optimized Power Reactor 1000, formerly KSNP). The new methodology, named KNAP (Korea Non-LOCA Analysis Package), uses RETRAN as the main system analysis code for most transients. For locked rotor transient DNBR analysis, UNICORN-TM code is used. UNICORN-TM is the unified code of RETRAN, MASTER and TORC. The UNICORN-TM has 1-D and 3-D neutron kinetics calculation capability. For locked rotor DNBR analysis, 1-D neutron kinetics is used. In this paper, we apply KNAP methodology to APR1400 (Advanced Power Reactor 1400) locked rotor analysis and compare the results with those in the APR1400 SSAR(Standard Safety Analysis Report). The locked rotor transient is one of the 'decrease in reactor coolant system flow rate' events and the results are typically described in the chapter 15.3.3 of SAR (Safety Analysis Report). In this study, to confirm the applicability of the KNAP methodology and code system to APR1400, locked rotor transient is analyzed using UNICORN-TM code and the results are compared with those from APR1400 SSAR
APR1400 Locked Rotor Transient Analysis using KNAP
Energy Technology Data Exchange (ETDEWEB)
Lee, Dong-Hyuk; Kim, Yo-Han; Ha, Sang Jun [Korea Electric Power Research Institute, Daejeon (Korea, Republic of)
2007-07-01
KEPRI (Korea Electric Power Research Institute) has developed safety analysis methodology for non-LOCA (Loss Of Coolant Accident) analysis of OPR1000 (Optimized Power Reactor 1000, formerly KSNP). The new methodology, named KNAP (Korea Non-LOCA Analysis Package), uses RETRAN as the main system analysis code for most transients. For locked rotor transient DNBR analysis, UNICORN-TM code is used. UNICORN-TM is the unified code of RETRAN, MASTER and TORC. The UNICORN-TM has 1-D and 3-D neutron kinetics calculation capability. For locked rotor DNBR analysis, 1-D neutron kinetics is used. In this paper, we apply KNAP methodology to APR1400 (Advanced Power Reactor 1400) locked rotor analysis and compare the results with those in the APR1400 SSAR(Standard Safety Analysis Report). The locked rotor transient is one of the 'decrease in reactor coolant system flow rate' events and the results are typically described in the chapter 15.3.3 of SAR (Safety Analysis Report). In this study, to confirm the applicability of the KNAP methodology and code system to APR1400, locked rotor transient is analyzed using UNICORN-TM code and the results are compared with those from APR1400 SSAR.
RETRAN sensitivity studies of light water reactor transients. Final report
International Nuclear Information System (INIS)
Burrell, N.S.; Gose, G.C.; Harrison, J.F.; Sawtelle, G.R.
1977-06-01
This report presents the results of sensitivity studies performed using the RETRAN/RELAP4 transient analysis code to identify critical parameters and models which influence light water reactor transient predictions. Various plant transients for both boiling water reactors and pressurized water reactors are examined. These studies represent the first detailed evaluation of the RETRAN/RELAP4 transient code capability in predicting a variety of plant transient responses. The wide range of transients analyzed in conjunction with the parameter and modeling studies performed identify several sensitive areas as well as areas requiring future study and model development
Recent development of transient electronics
Directory of Open Access Journals (Sweden)
Huanyu Cheng
2016-01-01
Full Text Available Transient electronics are an emerging class of electronics with the unique characteristic to completely dissolve within a programmed period of time. Since no harmful byproducts are released, these electronics can be used in the human body as a diagnostic tool, for instance, or they can be used as environmentally friendly alternatives to existing electronics which disintegrate when exposed to water. Thus, the most crucial aspect of transient electronics is their ability to disintegrate in a practical manner and a review of the literature on this topic is essential for understanding the current capabilities of transient electronics and areas of future research. In the past, only partial dissolution of transient electronics was possible, however, total dissolution has been achieved with a recent discovery that silicon nanomembrane undergoes hydrolysis. The use of single- and multi-layered structures has also been explored as a way to extend the lifetime of the electronics. Analytical models have been developed to study the dissolution of various functional materials as well as the devices constructed from this set of functional materials and these models prove to be useful in the design of the transient electronics.
Upgrading of TREAT experimental capabilities
International Nuclear Information System (INIS)
Dickerman, C.E.; Rose, D.; Bhattacharyya, S.K.
1982-01-01
The TREAT facility at the Argonne National Laboratory site in the Idaho National Engineering Laboratory is being upgraded to provide capabilities for fast-reactor-safety transient experiments not possible at any other experimental facility. Principal TREAT Upgrade (TU) goal is provision for 37-pin size experiments on energetics of core-disruptive accidents (CDA) in fast breeder reactor cores with moderate sodium void coefficients. this goal requires a significant enhancement of the capabilities of the TREAT facility, specifically including reactor control, hardened neutron spectrum incident on the test sample, and enlarged building. The upgraded facility will retain the capability for small-size experiments of the types currently being performed in TREAT. Reactor building and crane upgrading have been completed. TU schedules call for the components of the upgraded reactor system to be finished in 1984, including upgraded TREAT fuel and control system, and expanded coverage by the hodoscope fuel-motion diagnostics system
Olejarski, Michael; Appleton, Amy; Deltorchio, Stephen
2009-01-01
The Group Capability Model (GCM) is a software tool that allows an organization, from first line management to senior executive, to monitor and track the health (capability) of various groups in performing their contractual obligations. GCM calculates a Group Capability Index (GCI) by comparing actual head counts, certifications, and/or skills within a group. The model can also be used to simulate the effects of employee usage, training, and attrition on the GCI. A universal tool and common method was required due to the high risk of losing skills necessary to complete the Space Shuttle Program and meet the needs of the Constellation Program. During this transition from one space vehicle to another, the uncertainty among the critical skilled workforce is high and attrition has the potential to be unmanageable. GCM allows managers to establish requirements for their group in the form of head counts, certification requirements, or skills requirements. GCM then calculates a Group Capability Index (GCI), where a score of 1 indicates that the group is at the appropriate level; anything less than 1 indicates a potential for improvement. This shows the health of a group, both currently and over time. GCM accepts as input head count, certification needs, critical needs, competency needs, and competency critical needs. In addition, team members are categorized by years of experience, percentage of contribution, ex-members and their skills, availability, function, and in-work requirements. Outputs are several reports, including actual vs. required head count, actual vs. required certificates, CGI change over time (by month), and more. The program stores historical data for summary and historical reporting, which is done via an Excel spreadsheet that is color-coded to show health statistics at a glance. GCM has provided the Shuttle Ground Processing team with a quantifiable, repeatable approach to assessing and managing the skills in their organization. They now have a common
Pressure transient in liquid lines
International Nuclear Information System (INIS)
Sun, J.G.; Wang, X.Q.
1995-01-01
The pressure surge that results from a step change of flow in liquid pipelines, commonly known as water hammer, was analyzed by an eigenfunction method. A differential-integral Pressure wave equation and a linearized velocity equation were derived from the equations of mass and momentum conservation. Waveform distortion due to viscous dissipation and pipe-wall elastic expansion is characterized by a dimensionless transmission number K. The pressure surge condition, which is mathematically singular, was used in the solution procedure. The exact solutions from numerical calculation of the differential-integral equation provide a complete Pressure transient in the pipe. The problems are also calculated With the general-purpose computer code COMMIX, which solves the exact mass conservation equation and Navier-Stokes equations. These solutions were compared with published experimental results, and agreement was good. The effect of turbulence on the pressure transient is discussed in the light of COMMIX calculational results
Atucha I nuclear power plant transients analysis
International Nuclear Information System (INIS)
Castano, J.; Schivo, M.
1987-01-01
A program for the transients simulation thermohydraulic calculation without loss of coolant (KWU-ENACE development) to evaluate Atucha I nuclear power plant behaviour is used. The program includes systems simulation and nuclear power plants control bonds with real parameters. The calculation results show a good agreement with the output 'protocol' of various transients of the nuclear power plant, keeping the error, in general, lesser than ± 10% from the variation of the nuclear power plant's state variables. (Author)
AIREKMOD-RR, Reactivity Transients in Nuclear Research Reactors
International Nuclear Information System (INIS)
Baggoura, B.; Mazrou, H.
2001-01-01
1 - Description of program or function: AIREMOD-RR is a point kinetics code which can simulate fast transients in nuclear research reactor cores. It can also be used for theoretical reactor dynamics studies. It is used for research reactor kinetic analysis and provides a point neutron kinetic capability. The thermal hydraulic behavior is governed by a one-dimensional heat balance equation. The calculations are restricted to a single equivalent unit cell which consists of fuel, clad and coolant. 2 - Method of solution: For transient reactor kinetic calculations a modified Runge Kutta numerical method is used. The external reactivity insertion, specified as a function of time, is converted in dollar ($) unit. The neutron density, energy release and feedback variables are given at each time step. The two types of reactivity feedback considered are: Doppler effect and moderator effect. A new expression for the reactivity dependence on the feedback variables has been introduced in the present version of the code. The feedback reactivities are fitted in power series expression. 3 - Restrictions on the complexity of the problem: The number of delayed neutron groups and the total number of equations are limited only by computer storage capabilities. - Coolant is always in liquid phase. - Void reactivity feedback is not considered
TRANSPA: a code for transient thermal analysis of a single fuel pin
International Nuclear Information System (INIS)
Prenger, F.C.
1985-02-01
An analytical model (TRANSPA) for the transient thermal analysis of a single uranium carbide fuel pin was developed. This model uses thermal boundary conditions obtained from COBRA-WC output and calculates the transient thermal response of a single fuel pin to changes in internal power generation, coolant flowrate, or fuel pin physical configuration. The model uses the MITAS finite difference thermal analyzer. MITAS provides the means to input separate conductance models through the use of a user subroutine input capability. The model is a lumped-mass representation of the fuel pin using 26 nodes and 42 conductors. Run time for each transient analysis is approximately one minute of central processor time on the NOS operating system
Steady-state and transient fission gas release and swelling model for LIFE-4
International Nuclear Information System (INIS)
Villalobos, A.; Liu, Y.Y.; Rest, J.
1984-06-01
The fuel-pin modeling code LIFE-4 and the mechanistic fission gas behavior model FASTGRASS have been coupled and verified against gas release data from mixed-oxide fuels which were transient tested in the TREAT reactor. Design of the interface between LIFE-4 and FASTGRASS is based on an earlier coupling between an LWR version of LIFE and the GRASS-SST code. Fission gas behavior can significantly affect steady-state and transient fuel performance. FASTGRASS treats fission gas release and swelling in an internally consistent manner and simultaneously includes all major mechanisms thought to influence fission gas behavior. The FASTGRASS steady-state and transient analysis has evolved through comparisons of code predictions with fission-gas release and swelling data from both in- and ex-reactor experiments. FASTGRASS was chosen over other fission-gas behavior models because of its availability, its compatibility with the LIFE-4 calculational framework, and its predictive capability
PC-Reactor-core transient simulation code
International Nuclear Information System (INIS)
Nakata, H.
1989-10-01
PC-REATOR, a reactor core transient simulation code has been developed for the real-time operator training on a IBM-PC microcomputer. The program presents capabilities for on-line exchange of the operating parameters during the transient simulation, by friendly keyboard instructions. The model is based on the point-kinetics approximation, with 2 delayed neutron percursors and up to 11 decay power generating groups. (author) [pt
Transient survivability of LMR oxide fuel pins
International Nuclear Information System (INIS)
Weber, E.T.; Pitner, A.L.; Bard, F.E.; Culley, G.E.; Hunter, C.W.
1986-01-01
Fuel pin integrity during transient events must be assessed for both the core design and safety analysis phases of a reactor project. A significant increase in the experience related to limits of integrity for oxide fuel pins in transient overpower events has been realized from testing of fuel pins irradiated in FFTF and PFR. Fourteen FFTF irradiated fuel pins were tested in TREAT, representing a range of burnups, overpower ramp rates and maximum overpower conditions. Results of these tests along with similar testing in the PFR/TREAT program, provide a demonstration of significant safety margins for oxide fuel pins. Useful information applied in analytical extrapolation of fuel pin test data have been developed from laboratory transient tests on irradiated fuel cladding (FCTT) and on unirradiated fuel pellet deformation. These refinements in oxide fuel transient performance are being applied in assessment of transient capabilities of long lifetime fuel designs using ferritic cladding
Nuclear reactors transients identification and classification system
International Nuclear Information System (INIS)
Bianchi, Paulo Henrique
2008-01-01
This work describes the study and test of a system capable to identify and classify transients in thermo-hydraulic systems, using a neural network technique of the self-organizing maps (SOM) type, with the objective of implanting it on the new generations of nuclear reactors. The technique developed in this work consists on the use of multiple networks to do the classification and identification of the transient states, being each network a specialist at one respective transient of the system, that compete with each other using the quantization error, that is a measure given by this type of neural network. This technique showed very promising characteristics that allow the development of new functionalities in future projects. One of these characteristics consists on the potential of each network, besides responding what transient is in course, could give additional information about that transient. (author)
Extensions of the MCNP5 and TRIPOLI4 Monte Carlo Codes for Transient Reactor Analysis
Hoogenboom, J. Eduard; Sjenitzer, Bart L.
2014-06-01
To simulate reactor transients for safety analysis with the Monte Carlo method the generation and decay of delayed neutron precursors is implemented in the MCNP5 and TRIPOLI4 general purpose Monte Carlo codes. Important new variance reduction techniques like forced decay of precursors in each time interval and the branchless collision method are included to obtain reasonable statistics for the power production per time interval. For simulation of practical reactor transients also the feedback effect from the thermal-hydraulics must be included. This requires coupling of the Monte Carlo code with a thermal-hydraulics (TH) code, providing the temperature distribution in the reactor, which affects the neutron transport via the cross section data. The TH code also provides the coolant density distribution in the reactor, directly influencing the neutron transport. Different techniques for this coupling are discussed. As a demonstration a 3x3 mini fuel assembly with a moving control rod is considered for MCNP5 and a mini core existing of 3x3 PWR fuel assemblies with control rods and burnable poisons for TRIPOLI4. Results are shown for reactor transients due to control rod movement or withdrawal. The TRIPOLI4 transient calculation is started at low power and includes thermal-hydraulic feedback. The power rises about 10 decades and finally stabilises the reactor power at a much higher level than initial. The examples demonstrate that the modified Monte Carlo codes are capable of performing correct transient calculations, taking into account all geometrical and cross section detail.
Transient drainage summary report
International Nuclear Information System (INIS)
1996-09-01
This report summarizes the history of transient drainage issues on the Uranium Mill Tailings Remedial Action (UMTRA) Project. It defines and describes the UMTRA Project disposal cell transient drainage process and chronicles UMTRA Project treatment of the transient drainage phenomenon. Section 4.0 includes a conceptual cross section of each UMTRA Project disposal site and summarizes design and construction information, the ground water protection strategy, and the potential for transient drainage
PSH Transient Simulation Modeling
Energy Technology Data Exchange (ETDEWEB)
Muljadi, Eduard [National Renewable Energy Laboratory (NREL), Golden, CO (United States)
2017-12-21
PSH Transient Simulation Modeling presentation from the WPTO FY14 - FY16 Peer Review. Transient effects are an important consideration when designing a PSH system, yet numerical techniques for hydraulic transient analysis still need improvements for adjustable-speed (AS) reversible pump-turbine applications.
LOFT Augmented Operator Capability Program
International Nuclear Information System (INIS)
Hollenbeck, D.A.; Krantz, E.A.; Hunt, G.L.; Meyer, O.R.
1980-01-01
The outline of the LOFT Augmented Operator Capability Program is presented. This program utilizes the LOFT (Loss-of-Fluid Test) reactor facility which is located at the Idaho National Engineering Laboratory and the LOFT operational transient experiment series as a test bed for methods of enhancing the reactor operator's capability for safer operation. The design of an Operational Diagnotics and Display System is presented which was backfit to the existing data acquisition computers. Basic color-graphic displays of the process schematic and trend type are presented. In addition, displays were developed and are presented which represent safety state vector information. A task analysis method was applied to LOFT reactor operating procedures to test its usefulness in defining the operator's information needs and workload
Kohler, Lars; Hadt, Ryan G.; Zhang, Xiaoyi; Liu, Cunming
2017-01-01
The kinetics of photoinduced electron and energy transfer in a family of tetrapyridophenazine-bridged heteroleptic homo- and heterodinuclear copper(i) bis(phenanthroline)/ruthenium(ii) polypyridyl complexes were studied using ultrafast optical and multi-edge X-ray transient absorption spectroscopies. This work combines the synthesis of heterodinuclear Cu(i)–Ru(ii) analogs of the homodinuclear Cu(i)–Cu(i) targets with spectroscopic analysis and electronic structure calculations to first disentangle the dynamics at individual metal sites by taking advantage of the element and site specificity of X-ray absorption and theoretical methods. The excited state dynamical models developed for the heterodinuclear complexes are then applied to model the more challenging homodinuclear complexes. These results suggest that both intermetallic charge and energy transfer can be observed in an asymmetric dinuclear copper complex in which the ground state redox potentials of the copper sites are offset by only 310 meV. We also demonstrate the ability of several of these complexes to effectively and unidirectionally shuttle energy between different metal centers, a property that could be of great use in the design of broadly absorbing and multifunctional multimetallic photocatalysts. This work provides an important step toward developing both a fundamental conceptual picture and a practical experimental handle with which synthetic chemists, spectroscopists, and theoreticians may collaborate to engineer cheap and efficient photocatalytic materials capable of performing coulombically demanding chemical transformations. PMID:29629153
Material motion capabilities for SAREF
International Nuclear Information System (INIS)
DeVolpi, A.
1976-01-01
The SAREF program requires a panoply of diagnostic techniques in order to obtain needed experimental information. After surveying various fuel motion monitoring techniques, the hodoscope has been chosen as the reference device because of its proven record and because data extrapolations and calculations indicate adequate response for small and large test sections. A hodoscope system for STF would be designed to perform both fuel and clad monitoring during transients. It would also provide distinctive fuel and clad radiographic information before and after transients. Large-test resolution of less than 100 gm and time resolution down to 0.1 msec are projected. Two orthogonal collimators for three-dimensional viewing would each cover 180 x 31 cm viewing area with a combined total of 6000 detectors
International Nuclear Information System (INIS)
Wnek, W.J.; Ramshaw, J.D.; Trapp, J.A.; Hughes, E.D.; Solbrig, C.W.
1975-11-01
A mathematical model and a numerical solution scheme for thermal-hydraulic analysis of fuel rod arrays are given. The model alleviates the two major deficiencies associated with existing rod array analysis models, that of a correct transverse momentum equation and the capability of handling reversing and circulatory flows. Possible applications of the model include steady state and transient subchannel calculations as well as analysis of flows in heat exchangers, other engineering equipment, and porous media
Simulating fission product transients via the history-based local-parameter methodology
International Nuclear Information System (INIS)
Jenkins, D.A.; Rouben, B.; Salvatore, M.
1993-01-01
This paper describes the fission-product-calculation capacity of the history-based local-parameter methodology for evaluating lattice properties for use in core-tracking calculations in CANDU reactors. In addition to taking into account the individual past history of each bundles flux/power level, fuel temperature, and coolant density and temperature that the bundle has seen during its stay in the core, the latest refinement of the history-based method provides the capability of fission-product-drivers. It allows the bundle-specific concentrations of the three basic groups of saturating fission products to be calculated in steady state or following a power transient, including long shutdowns. The new capability is illustrated by simulating the startup period following a typical long-shutdown, starting from a snapshot in the Point Lepreau operating history. 9 refs., 7 tabs
Rights, goals, and capabilities
van Hees, M.V.B.P.M
This article analyses the relationship between rights and capabilities in order to get a better grasp of the kind of consequentialism that the capability theory represents. Capability rights have been defined as rights that have a capability as their object (rights to capabilities). Such a
Federal Laboratory Consortium — The Electrical Power Mobile Test capabilities are utilized to conduct electrical power quality testing on aircraft and helicopters. This capability allows that the...
Transient phenomena in electrical power systems
Venikov, V A; Higinbotham, W
1964-01-01
Electronics and Instrumentation, Volume 24: Transient Phenomena in Electrical Power Systems presents the methods for calculating the stability and the transient behavior of systems with forced excitation control. This book provides information pertinent to the analysis of transient phenomena in electro-mechanical systems.Organized into five chapters, this volume begins with an overview of the principal requirements in an excitation system. This text then explains the electromagnetic and electro-mechanical phenomena, taking into account the mutual action between the components of the system. Ot
PSB-VVER simulation of Kozloduy NPP 'loss of feed water transient'
Energy Technology Data Exchange (ETDEWEB)
Groudev, P.P. [Institute for Nuclear Research and Nuclear Energy, Tzarigradsko Shaussee 72, Sofia 1784 (Bulgaria)]. E-mail: pavlinpg@inrne.bas.bg; Stefanova, A.E. [Institute for Nuclear Research and Nuclear Energy, Tzarigradsko Shaussee 72, Sofia 1784 (Bulgaria)]. E-mail: antoanet@inrne.bas.bg; Gencheva, R.V. [Institute for Nuclear Research and Nuclear Energy, Tzarigradsko Shaussee 72, Sofia 1784 (Bulgaria)]. E-mail: roseh@inrne.bas.bg; Pavlova, M.P. [Institute for Nuclear Research and Nuclear Energy, Tzarigradsko Shaussee 72, Sofia 1784 (Bulgaria)]. E-mail: pavlova@inrne.bas.bg
2005-04-01
This paper provides a comparison between the PSB test facility experimental results obtained during the simulation of loss of feed water transient (LOFW) and the calculation results received by INRNE computer model of the same test facility. Integral thermal-hydraulic PSB-VVER test facility located at Electrogorsk Research and Engineering Center on NPPs Safety (EREC) was put in operation in 1998. The structure of the test facility allows experimental studies under steady state, transient and accident conditions. RELAP5/MOD3.2 computer code has been used to simulate the loss of feed water transient in a PSB-VVER model. This model was developed at the Institute for Nuclear Research and Nuclear Energy for simulation of loss of feed water transient. The objective of the experiment 'loss of feed water', which has been performed at PSB-VVER test facility is simulation of Kozloduy NPP LOFW transient. One of the main requirements to the experiment scenario has been to reproduce all main events and phenomena that occurred in Kozloduy NPP during the LOFW transient. Analyzing the PSB-VVER test with a RELAP5/MOD3.2 computer code as a standard problem allows investigating the phenomena included in the VVER code validation matrix as 'integral system effects' and 'natural circulation'. For assessment of the RELAP5 capability to predict the 'Integral system effect' phenomenon the following RELAP5 quantities are compared with external trends: the primary pressure and the hot and cold leg temperatures. In order to assess the RELAP5 capability to predict the 'Natural circulation' phenomenon the hot and cold leg temperatures behavior have been investigated. This report was possible through the participation of leading specialists from Kozloduy NPP and with the support of Argonne National Laboratory (ANL), under the International Nuclear Safety Program (INSP) of the United States Department of Energy.
STEADY STATE MODELING OF THE MINIMUM CRITICAL CORE OF THE TRANSIENT REACTOR TEST FACILITY
Energy Technology Data Exchange (ETDEWEB)
Anthony L. Alberti; Todd S. Palmer; Javier Ortensi; Mark D. DeHart
2016-05-01
With the advent of next generation reactor systems and new fuel designs, the U.S. Department of Energy (DOE) has identified the need for the resumption of transient testing of nuclear fuels. The DOE has decided that the Transient Reactor Test Facility (TREAT) at Idaho National Laboratory (INL) is best suited for future testing. TREAT is a thermal neutron spectrum, air-cooled, nuclear test facility that is designed to test nuclear fuels in transient scenarios. These specific scenarios range from simple temperature transients to full fuel melt accidents. DOE has expressed a desire to develop a simulation capability that will accurately model the experiments before they are irradiated at the facility. It is the aim for this capability to have an emphasis on effective and safe operation while minimizing experimental time and cost. The multi physics platform MOOSE has been selected as the framework for this project. The goals for this work are to identify the fundamental neutronics properties of TREAT and to develop an accurate steady state model for future multiphysics transient simulations. In order to minimize computational cost, the effect of spatial homogenization and angular discretization are investigated. It was found that significant anisotropy is present in TREAT assemblies and to capture this effect, explicit modeling of cooling channels and inter-element gaps is necessary. For this modeling scheme, single element calculations at 293 K gave power distributions with a root mean square difference of 0.076% from those of reference SERPENT calculations. The minimum critical core configuration with identical gap and channel treatment at 293 K resulted in a root mean square, total core, radial power distribution 2.423% different than those of reference SERPENT solutions.
Experimental and numerical investigation of the coolant mixing during fast deboration transients
International Nuclear Information System (INIS)
Hoehne, T.; Rohde, U.; Weiss, F.P.
1999-01-01
For the analysis of boron dilution transients and main steam line break scenarios the modeling of the coolant mixing inside the reactor vessel is important, because the reactivity insertion strongly depends on boron acid concentration or the coolant temperature distribution. Calculations for steady state flow conditions for the VVER-440 were performed with a CFD code (CFX-4). The comparison with experimental data and an analytical mixing model which is implemented in the neutron-kinetic code DYN3D showed a good agreement for near-nominal conditions. First experiments at the Rossendorf Mixing Test Facility ROCOM were performed simulating the start-up of the first main coolant pump. The reference reactor for the geometrically 1:5 scaled Plexiglas model is the German Konvoi type PWR. After demonstrating the capability of the CFD code to simulate these complicated flow transients, calculations were performed for the start-up of the first pump in a VVER-440 type reactor. These calculations are a first step of understanding the coolant mixing in the RPV of a VVER-440 type reactor under transient conditions. The results of the calculation show a very complex flow in the downcomer. A high downcomer of VVER-440 and the existence of the lower control rod chamber support coolant mixing is concluded. (author)
TRANSIENT ELECTRONICS CATEGORIZATION
2017-08-24
AFRL-RY-WP-TR-2017-0169 TRANSIENT ELECTRONICS CATEGORIZATION Dr. Burhan Bayraktaroglu Devices for Sensing Branch Aerospace Components & Subsystems...SUBTITLE TRANSIENT ELECTRONICS CATEGORIZATION 5a. CONTRACT NUMBER In-house 5b. GRANT NUMBER N/A 5c. PROGRAM ELEMENT NUMBER N/A 6. AUTHOR(S) Dr. Burhan...88ABW-2017-3747, Clearance Date 31 July 2017. Paper contains color. 14. ABSTRACT Transient electronics is an emerging technology area that lacks proper
Capabilities for Strategic Adaptation
DEFF Research Database (Denmark)
Distel, Andreas Philipp
This dissertation explores capabilities that enable firms to strategically adapt to environmental changes and preserve competitiveness over time – often referred to as dynamic capabilities. While dynamic capabilities being a popular research domain, too little is known about what these capabiliti...
Cortical computations via transient attractors.
Directory of Open Access Journals (Sweden)
Oliver L C Rourke
Full Text Available The ability of sensory networks to transiently store information on the scale of seconds can confer many advantages in processing time-varying stimuli. How a network could store information on such intermediate time scales, between typical neurophysiological time scales and those of long-term memory, is typically attributed to persistent neural activity. An alternative mechanism which might allow for such information storage is through temporary modifications to the neural connectivity which decay on the same second-long time scale as the underlying memories. Earlier work that has explored this method has done so by emphasizing one attractor from a limited, pre-defined set. Here, we describe an alternative, a Transient Attractor network, which can learn any pattern presented to it, store several simultaneously, and robustly recall them on demand using targeted probes in a manner reminiscent of Hopfield networks. We hypothesize that such functionality could be usefully embedded within sensory cortex, and allow for a flexibly-gated short-term memory, as well as conferring the ability of the network to perform automatic de-noising, and separation of input signals into distinct perceptual objects. We demonstrate that the stored information can be refreshed to extend storage time, is not sensitive to noise in the system, and can be turned on or off by simple neuromodulation. The diverse capabilities of transient attractors, as well as their resemblance to many features observed in sensory cortex, suggest the possibility that their actions might underlie neural processing in many sensory areas.
Cortical computations via transient attractors.
Rourke, Oliver L C; Butts, Daniel A
2017-01-01
The ability of sensory networks to transiently store information on the scale of seconds can confer many advantages in processing time-varying stimuli. How a network could store information on such intermediate time scales, between typical neurophysiological time scales and those of long-term memory, is typically attributed to persistent neural activity. An alternative mechanism which might allow for such information storage is through temporary modifications to the neural connectivity which decay on the same second-long time scale as the underlying memories. Earlier work that has explored this method has done so by emphasizing one attractor from a limited, pre-defined set. Here, we describe an alternative, a Transient Attractor network, which can learn any pattern presented to it, store several simultaneously, and robustly recall them on demand using targeted probes in a manner reminiscent of Hopfield networks. We hypothesize that such functionality could be usefully embedded within sensory cortex, and allow for a flexibly-gated short-term memory, as well as conferring the ability of the network to perform automatic de-noising, and separation of input signals into distinct perceptual objects. We demonstrate that the stored information can be refreshed to extend storage time, is not sensitive to noise in the system, and can be turned on or off by simple neuromodulation. The diverse capabilities of transient attractors, as well as their resemblance to many features observed in sensory cortex, suggest the possibility that their actions might underlie neural processing in many sensory areas.
Electromagnetic Transients in Power Cables
DEFF Research Database (Denmark)
Silva, Filipe Faria Da; Bak, Claus Leth
. The chapter ends by proposing a systematic method that can be used when doing the insulation co-ordination study for a line, as well as the modelling requirements, both modelling depth and modelling detail of the equipment, for the study of the different types of transients followed by a step-by-step generic...... typically used for the screens of cables (both-ends bonding and cross-boding) and also presents methods that can be used to estimate the maximum current of a cable for different types of soils, i.e. thermal calculations. The end of the chapter introduces the shunt reactor, which is an important element...... detail of the equipment, for the study of the different types of transients followed by a step-by-step generic example....
Lachugin, V. F.; Kulikov, A. L.; Platonov, P. S.; Vucolov, V. Yu.
2017-12-01
The specifics of generation of the signals of current and voltage in the circuits of a directional element of wave relay protection during short circuit (SC) in overhead power transmission lines are considered. The computing method of transient processes in the protection circuits, including frequency filters, that attenuate the parameters of currents and voltages of the mode taking into account the higher harmonic components and probable deviations of the frequency of transmission line from the rated value is presented. It is revealed that it is advisable to implement the measuring circuits of the directional elements of wave relay protection with the three-section filter attenuating the frequencies from 45 to 55 Hz and the low pass filter with cutoff frequency that does not exceed 1 kHz.
Dynamic capabilities, Marketing Capability and Organizational Performance
Directory of Open Access Journals (Sweden)
Adriana Roseli Wünsch Takahashi
2017-01-01
Full Text Available The goal of the study is to investigate the influence of dynamic capabilities on organizational performance and the role of marketing capabilities as a mediator in this relationship in the context of private HEIs in Brazil. As a research method we carried out a survey with 316 IES and data analysis was operationalized with the technique of structural equation modeling. The results indicate that the dynamic capabilities have influence on organizational performance only when mediated by marketing ability. The marketing capability has an important role in the survival, growth and renewal on educational services offerings for HEIs in private sector, and consequently in organizational performance. It is also demonstrated that mediated relationship is more intense for HEI with up to 3,000 students and other organizational profile variables such as amount of courses, the constitution, the type of institution and type of education do not significantly alter the results.
Operational transients: A regional administrator's view
International Nuclear Information System (INIS)
Collins, J.T.; Johnson, E.H.
1984-01-01
This chapter discusses the response of the regional US NRC to operational transients. Three of the major lessons learned from the Three Mile Island-2 accident are reviewed. The need to consider the more probable events of lesser consequences in addition to the significant events is now realized. The importance of the operator in the course of an operational event has been recognized. Three Mile Island also pointed out the many design and hardware deficiencies. Topics considered include the industry capability to meet the challenge of operational transients, the region's capability, and the capability of the utility. It is recommended that technical drills be developed, that plant-specific technical competence be improved, that operator training and education be improved, and that the attitude changes on the part of utilities and the nuclear industry in general be accelerated
Qualitative assessment of the fission product release capability of ELOCA.Mk5
International Nuclear Information System (INIS)
Klein, M.E.; Carlucci, L.N.; Arimescu, V.I.
1995-01-01
A qualitative assessment of the fission product release capability of the ELOCA.Mk5 computer code was performed by simulating two transients from the sweep-gas experiment, FIO-133. Improved agreement between calculated and experimental trends in release was obtained by applying an interface pressure stress component to the pellet center. As well, results show that the current system for defining the reference temperature distribution for the thermal stress component is not always realistic. These results are being used in the development of a new, mechanistic pellet stress model. (author)
Xia, D.; Xia, Z.
2017-12-01
The ability for the excitation system to adjust quickly plays a very important role in maintaining the normal operation of superconducting machines and power systems. However, the eddy currents in the electromagnetic shield of superconducting machines hinder the exciting magnetic field change and weaken the adjustment capability of the excitation system. To analyze this problem, a finite element calculation model for the transient electromagnetic field with moving parts is established. The effects of three different electromagnetic shields on the exciting magnetic field are analyzed using finite element method. The results show that the electromagnetic shield hinders the field changes significantly, the better its conductivity, the greater the effect on the superconducting machine excitation.
Modelling of an ULOF transient in a sodium fast reactor
International Nuclear Information System (INIS)
Droin, Jean-Baptiste
2016-01-01
Within the framework of the Generation IV Sodium-cooled Fast Reactor (SFR) R and D program of CEA (French Commissariat a l'Energie Atomique et aux Energies Alternatives), safety in case of severe accidents is assessed.Such transients are usually simulated with mechanistic codes (such as SAS-SFR and SIMMER III). as a complement to these codes, which give reference accidental transient calculations, a new physico-statistical approach is currently followed by the CEA; its final objective being to derive the variability of the main results of interest for safety. This approach involves a fast-running description of extended accident sequences coupling physical models for the main phenomena to advanced statistical analysis techniques. It enables to perform a large number of simulations in a reasonable computational time and to describe all the possible bifurcations of the accident transient.In this context, this PhD work presents the physical tool (models and results assessment) dedicated to the initiation and primary phases of an Unprotected Loss Of Flow accident (i.e. until the end of sub-assemblies degradation and before large molten pools formation). The accident phenomenology during these phases is described and illustrated by numerous experimental evidences.It is underlined that the features of the new heterogeneous core concept (called CFV of the French ASTRID prototype) leads to different kinds of ULOF transients than those occurring in the previous past homogeneous cores (SuperPhenix, Phenix...). Indeed, its negative void effect drops the nuclear power when sodium heats-up and possibly boils. This enables three types of ULOF transients characterized by various core final states; the first two types leading to final coolable core states in natural circulation flow (the first one in single phase, the second one in stabilized two-phase flow) whereas the core undergoes a flow excursion followed by sub-assemblies degradation in the last type. In this study, a
Spectroscopic classification of transients
DEFF Research Database (Denmark)
Stritzinger, M. D.; Fraser, M.; Hummelmose, N. N.
2017-01-01
We report the spectroscopic classification of several transients based on observations taken with the Nordic Optical Telescope (NOT) equipped with ALFOSC, over the nights 23-25 August 2017.......We report the spectroscopic classification of several transients based on observations taken with the Nordic Optical Telescope (NOT) equipped with ALFOSC, over the nights 23-25 August 2017....
Advanced Instrumentation for Transient Reactor Testing
Energy Technology Data Exchange (ETDEWEB)
Corradini, Michael L.; Anderson, Mark; Imel, George; Blue, Tom; Roberts, Jeremy; Davis, Kurt
2018-01-31
Transient testing involves placing fuel or material into the core of specialized materials test reactors that are capable of simulating a range of design basis accidents, including reactivity insertion accidents, that require the reactor produce short bursts of intense highpower neutron flux and gamma radiation. Testing fuel behavior in a prototypic neutron environment under high-power, accident-simulation conditions is a key step in licensing nuclear fuels for use in existing and future nuclear power plants. Transient testing of nuclear fuels is needed to develop and prove the safety basis for advanced reactors and fuels. In addition, modern fuel development and design increasingly relies on modeling and simulation efforts that must be informed and validated using specially designed material performance separate effects studies. These studies will require experimental facilities that are able to support variable scale, highly instrumented tests providing data that have appropriate spatial and temporal resolution. Finally, there are efforts now underway to develop advanced light water reactor (LWR) fuels with enhanced performance and accident tolerance. These advanced reactor designs will also require new fuel types. These new fuels need to be tested in a controlled environment in order to learn how they respond to accident conditions. For these applications, transient reactor testing is needed to help design fuels with improved performance. In order to maximize the value of transient testing, there is a need for in-situ transient realtime imaging technology (e.g., the neutron detection and imaging system like the hodoscope) to see fuel motion during rapid transient excursions with a higher degree of spatial and temporal resolution and accuracy. There also exists a need for new small, compact local sensors and instrumentation that are capable of collecting data during transients (e.g., local displacements, temperatures, thermal conductivity, neutron flux, etc.).
The economic impact of reactor transients
International Nuclear Information System (INIS)
Rossin, A.D.; Vine, G.L.
1984-01-01
This chapter discusses the cost estimation of transients and the causal relationship between transients and accidents. It is suggested that the calculation of the actual cost of a transient that has occurred is impossible without computerized records. Six months of operating experience reports, based on a survey of pressurized water reactors (PWRs) and boiling water reactors (BWRs) conducted by the Nuclear Safety Analysis Center (NSAC), are analyzed. The significant costs of a reactor transient are the repair costs resulting from severe damage to plant equipment, the cost of scrams (the actions the system is designed to take to avoid safety risks), US NRC fines, negative publicity, utility rates and revenues. It is estimated that the Three Mile Island-2 accident cost the US over $100 billion in nuclear plant delays and cancellations, more expensive fuel, oil imports, backfits, bureaucratic, administrative and legal costs, and lost productivity
RFSP simulations of Darlington FINCH refuelling transient
International Nuclear Information System (INIS)
Carruthers, E.V.; Chow, H.C.
1997-01-01
Immediately after refuelling of a channel, the fresh bundles are free of fission products. Xenon-135, the most notable of the saturating fission products, builds up to an equilibrium level in about 30 h. The channel power of the refuelled channel would therefore initially peak and then drop to a steady-state level. The RFSP code can track saturating-fission-product transients and power transients. The Fully INstrumented CHannels (FINCHs) in Darlington NGS provides channel power data on the refuelling power transients. In this paper, such data has been used to identify the physical evidence of the fission-product transient effect on channel power, and to validate RFSP fission-product-driver calculation results. (author)
Pressurizer and steam-generator behavior under PWR transient conditions
International Nuclear Information System (INIS)
Wahba, A.B.; Berta, V.T.; Pointner, W.
1983-01-01
Experiments have been conducted in the Loss-of-Fluid Test (LOFT) pressurized water reactor (PWR), at the Idaho National Engineering Laboratory, in which transient phenomena arising from accident events with and without reactor scram were studied. The main purpose of the LOFT facility is to provide data for the development of computer codes for PWR transient analyses. Significant thermal-hydraulic differences have been observed between the measured and calculated results for those transients in which the pressurizer and steam generator strongly influence the dominant transient phenomena. Pressurizer and steam generator phenomena that occurred during four specific PWR transients in the LOFT facility are discussed. Two transients were accompanied by pressurizer inflow and a reduction of the heat transfer in the steam generator to a very small value. The other two transients were accompanied by pressurizer outflow while the steam generator behavior was controlled
International Nuclear Information System (INIS)
Ebert, D.
1997-07-01
This is a report on the CSNI Workshop on Transient Thermal-Hydraulic and Neutronic Codes Requirements held at Annapolis, Maryland, USA November 5-8, 1996. This experts' meeting consisted of 140 participants from 21 countries; 65 invited papers were presented. The meeting was divided into five areas: (1) current and prospective plans of thermal hydraulic codes development; (2) current and anticipated uses of thermal-hydraulic codes; (3) advances in modeling of thermal-hydraulic phenomena and associated additional experimental needs; (4) numerical methods in multi-phase flows; and (5) programming language, code architectures and user interfaces. The workshop consensus identified the following important action items to be addressed by the international community in order to maintain and improve the calculational capability: (a) preserve current code expertise and institutional memory, (b) preserve the ability to use the existing investment in plant transient analysis codes, (c) maintain essential experimental capabilities, (d) develop advanced measurement capabilities to support future code validation work, (e) integrate existing analytical capabilities so as to improve performance and reduce operating costs, (f) exploit the proven advances in code architecture, numerics, graphical user interfaces, and modularization in order to improve code performance and scrutibility, and (g) more effectively utilize user experience in modifying and improving the codes
Energy Technology Data Exchange (ETDEWEB)
Ebert, D.
1997-07-01
This is a report on the CSNI Workshop on Transient Thermal-Hydraulic and Neutronic Codes Requirements held at Annapolis, Maryland, USA November 5-8, 1996. This experts` meeting consisted of 140 participants from 21 countries; 65 invited papers were presented. The meeting was divided into five areas: (1) current and prospective plans of thermal hydraulic codes development; (2) current and anticipated uses of thermal-hydraulic codes; (3) advances in modeling of thermal-hydraulic phenomena and associated additional experimental needs; (4) numerical methods in multi-phase flows; and (5) programming language, code architectures and user interfaces. The workshop consensus identified the following important action items to be addressed by the international community in order to maintain and improve the calculational capability: (a) preserve current code expertise and institutional memory, (b) preserve the ability to use the existing investment in plant transient analysis codes, (c) maintain essential experimental capabilities, (d) develop advanced measurement capabilities to support future code validation work, (e) integrate existing analytical capabilities so as to improve performance and reduce operating costs, (f) exploit the proven advances in code architecture, numerics, graphical user interfaces, and modularization in order to improve code performance and scrutibility, and (g) more effectively utilize user experience in modifying and improving the codes.
Searching for MHz Transients with the VLA Low-band Ionosphere and Transient Experiment (VLITE)
Polisensky, Emil; Peters, Wendy; Giacintucci, Simona; Clarke, Tracy; Kassim, Namir E.; hyman, Scott D.; van der Horst, Alexander; Linford, Justin; Waldron, Zach; Frail, Dale
2018-01-01
NRL and NRAO have expanded the low frequency capabilities of the VLA through the VLA Low-band Ionosphere and Transient Experiment (VLITE, http://vlite.nrao.edu/ ), effectively making the instrument two telescopes in one. VLITE is a commensal observing system that harvests data from the prime focus in parallel with normal Cassegrain focus observing on a subset of VLA antennas. VLITE provides over 6000 observing hours per year in a > 5 square degree field-of-view using 64 MHz bandwidth centered on 352 MHz. By operating in parallel, VLITE offers invaluable low frequency data to targeted observations of transient sources detected at higher frequencies. With arcsec resolution and mJy sensitivity, VLITE additionally offers great potential for blind searches of rarer radio-selected transients. We use catalog matching software on the imaging products from the daily astrophysics pipeline and the LOFAR Transients Pipeline (TraP) on repeated observations of the same fields to search for coherent and incoherent astronomical transients on timescales of a few seconds to years. We present the current status of the VLITE transient science program from its initial deployment on 10 antennas in November 2014 through its expansion to 16 antennas in the summer of 2017. Transient limits from VLITE’s first year of operation (Polisensky et al. 2016) are updated per the most recent analysis.
Transients: The regulator's view
International Nuclear Information System (INIS)
Sheron, B.W.; Speis, T.P.
1984-01-01
This chapter attempts to clarify the basis for the regulator's concerns for transient events. Transients are defined as both anticipated operational occurrences and postulated accidents. Recent operational experience, supplemented by improved probabilistic risk analysis methods, has demonstrated that non-LOCA transient events can be significant contributors to overall risk. Topics considered include lessons learned from events and issues, the regulations governing plant transients, multiple failures, different failure frequencies, operator errors, and public pressure. It is concluded that the formation of Owners Groups and Regulatory Response Groups within the owners groups are positive signs of the industry's concern for safety and responsible dealing with the issues affecting both the US NRC and the industry
Simulation of hot-channel transients for PHWR reactors
International Nuclear Information System (INIS)
Masriera, N.A.
1988-01-01
For the simulation of transients a whole-plant code is needed. These codes model the core in a very simplified way. When local variables have to be calculated a different kind of code is needed: a subchannel-code. This report studies the use of the cobra code as a subchannel-code, for the simulation of a PHWR fuel channel, considering that this code was developed for PWR cores calculation. A special effort is made to obtain optimized models for different calculations: steady state, soft transients and severe transients. These models differ in number of subchannels, axial nodes, and the choice of the most important variables. (Author) [es
Transient multivariable sensor evaluation
Energy Technology Data Exchange (ETDEWEB)
Vilim, Richard B.; Heifetz, Alexander
2017-02-21
A method and system for performing transient multivariable sensor evaluation. The method and system includes a computer system for identifying a model form, providing training measurement data, generating a basis vector, monitoring system data from sensor, loading the system data in a non-transient memory, performing an estimation to provide desired data and comparing the system data to the desired data and outputting an alarm for a defective sensor.
Energy Technology Data Exchange (ETDEWEB)
Page, R.; Jones, J.R.
1997-07-01
Ensuring that safety analysis needs are met in the future is likely to lead to the development of new codes and the further development of existing codes. It is therefore advantageous to define standards for data interfaces and to develop software interfacing techniques which can readily accommodate changes when they are made. Defining interface standards is beneficial but is necessarily restricted in application if future requirements are not known in detail. Code interfacing methods are of particular relevance with the move towards automatic grid frequency response operation where the integration of plant dynamic, core follow and fault study calculation tools is considered advantageous. This paper describes the background and features of a new code TALINK (Transient Analysis code LINKage program) used to provide a flexible interface to link the RELAP5 thermal hydraulics code with the PANTHER neutron kinetics and the SIBDYM whole plant dynamic modelling codes used by Nuclear Electric. The complete package enables the codes to be executed in parallel and provides an integrated whole plant thermal-hydraulics and neutron kinetics model. In addition the paper discusses the capabilities and pedigree of the component codes used to form the integrated transient analysis package and the details of the calculation of a postulated Sizewell `B` Loss of offsite power fault transient.
International Nuclear Information System (INIS)
Page, R.; Jones, J.R.
1997-01-01
Ensuring that safety analysis needs are met in the future is likely to lead to the development of new codes and the further development of existing codes. It is therefore advantageous to define standards for data interfaces and to develop software interfacing techniques which can readily accommodate changes when they are made. Defining interface standards is beneficial but is necessarily restricted in application if future requirements are not known in detail. Code interfacing methods are of particular relevance with the move towards automatic grid frequency response operation where the integration of plant dynamic, core follow and fault study calculation tools is considered advantageous. This paper describes the background and features of a new code TALINK (Transient Analysis code LINKage program) used to provide a flexible interface to link the RELAP5 thermal hydraulics code with the PANTHER neutron kinetics and the SIBDYM whole plant dynamic modelling codes used by Nuclear Electric. The complete package enables the codes to be executed in parallel and provides an integrated whole plant thermal-hydraulics and neutron kinetics model. In addition the paper discusses the capabilities and pedigree of the component codes used to form the integrated transient analysis package and the details of the calculation of a postulated Sizewell 'B' Loss of offsite power fault transient
A proof-of-concept transient diagnostic expert system for BWRs [Boiling Water Reactors
International Nuclear Information System (INIS)
Yoshida, K.; Naser, J.A.
1988-05-01
A proof-of-concept transient diagnostic expert system has been developed to identify the cause and the type of an abnormal transient in a boiling water nuclear power plant. For this expert system development, the calculational results of the simulation code RETRAN were used as the knowledge source. The knowledge extracted from the RETRAN analyses was transformed into IF-THEN rules in the knowledge base for the expert system. An important feature of this expert system is the introduction of certainty factors to allow diagnosis even in the cases where data may be either missing or marked as invalid. To increase the capability of this diagnostic system to distinguish between similiar transients, backward chaining reasoning is used to support the forward chaining reasoning with certainty factors. Through this effort, it has been demonstrated that an expert system can be successfully used to create a transient diagnostic system. It has also successfully demonstrated that RETRAN can be used as the knowledge source for developing the knowledge base of the diagnostic system
HTR core physics and transient analyses by the Panthermix code system
Energy Technology Data Exchange (ETDEWEB)
Haas, J.B.M. de; Kuijper, J.C.; Oppe, J. [NRG - Fuels, Actinides and Isotopes group, Petten (Netherlands)
2005-07-01
At NRG Petten, core physics analyses on High Temperature gas-cooled Reactors (HTRs) are mainly performed by means of the PANTHERMIX code system. Since some years NRG is developing the HTR reactor physics code system WIMS/PANTHERMIX, based on the lattice code WIMS (Serco Assurance, UK), the 3-dimensional steady-state and transient core physics code PANTHER (British Energy, UK) and the 2-dimensional R-Z HTR thermal hydraulics code THERMIX-DIREKT (Research Centre FZJ Juelich, Germany). By means of the WIMS code nuclear data are being generated to suit the PANTHER code's neutronics. At NRG the PANTHER code has been interfaced with THERMIX-DIREKT to form PANTHERMIX, to enable core-follow/fuel management and transient analyses in a consistent manner on pebble bed type HTR systems. Also provisions have been made to simulate the flow of pebbles through the core of a pebble bed HTR, according to a given (R-Z) flow pattern. As examples of the versatility of the PANTHERMIX code system, calculations are presented on the PBMR, the South African pebble bed reactor design, to show the transient capabilities, and on a plutonium burning MEDUL-reactor, to demonstrate the core-follow/fuel management capabilities. For the investigated cases a good agreement is observed with the results of other HTR core physics codes.
HTR core physics and transient analyses by the Panthermix code system
International Nuclear Information System (INIS)
Haas, J.B.M. de; Kuijper, J.C.; Oppe, J.
2005-01-01
At NRG Petten, core physics analyses on High Temperature gas-cooled Reactors (HTRs) are mainly performed by means of the PANTHERMIX code system. Since some years NRG is developing the HTR reactor physics code system WIMS/PANTHERMIX, based on the lattice code WIMS (Serco Assurance, UK), the 3-dimensional steady-state and transient core physics code PANTHER (British Energy, UK) and the 2-dimensional R-Z HTR thermal hydraulics code THERMIX-DIREKT (Research Centre FZJ Juelich, Germany). By means of the WIMS code nuclear data are being generated to suit the PANTHER code's neutronics. At NRG the PANTHER code has been interfaced with THERMIX-DIREKT to form PANTHERMIX, to enable core-follow/fuel management and transient analyses in a consistent manner on pebble bed type HTR systems. Also provisions have been made to simulate the flow of pebbles through the core of a pebble bed HTR, according to a given (R-Z) flow pattern. As examples of the versatility of the PANTHERMIX code system, calculations are presented on the PBMR, the South African pebble bed reactor design, to show the transient capabilities, and on a plutonium burning MEDUL-reactor, to demonstrate the core-follow/fuel management capabilities. For the investigated cases a good agreement is observed with the results of other HTR core physics codes
Analysis of loss of offsite power transient using RELAP5/MOD1/NSC
International Nuclear Information System (INIS)
Kim, Hho Jung; Chung, Bub Dong; Lee, Young Jin; Kim, Jin Soo
1986-01-01
System thermal-hydraulic parameters and simulated, using the best-estimate system code(RELAP5/MOD1/NSC), based upon the sequence of events for the KNU1( Korea Nuclear Unit 1) loss of offsite power transient at 77.5% power which occurred on June 9,1981. The results are compared with the actual plant transient data and show good agreements. After the flow coastdown following the trips of both reactor coolant pumps, the establishment of natural circulation by the temperature difference between the hot and the cold legs is confirmed. The calculated reactor coolant flowrate closely approximate the plant data indicating the validity of relevant thermal-hydraulic models in the RELAP5/MOD1/NSC. Results also show that the sufficient heat removal capability is secured by the appropriate supply of the auxiliary feedwater without the operation of S/G PORVs. In addition, a scenario accident at full power, based upon the same sequence of events described above, is also analysed and the results confirmed that the safety of KNU1 is secured by the appropriate operation of the S/G PORVs coupled with the supply of auxiliary feedwater which ensures sufficient heat removal capability. The characteristics of the non-safety related components such as the turbine stop valve closing time, S/G PORV setting etc. are recognized to be important in the transient analyses on a bestestimate basis. (Author)
Building Service Provider Capabilities
DEFF Research Database (Denmark)
Brandl, Kristin; Jaura, Manya; Ørberg Jensen, Peter D.
2015-01-01
In this paper we study whether and how the interaction between clients and the service providers contributes to the development of capabilities in service provider firms. In situations where such a contribution occurs, we analyze how different types of activities in the production process...... process. We find that clients influence the development of human capital capabilities and management capabilities in reciprocally produced services. While in sequential produced services clients influence the development of organizational capital capabilities and management capital capabilities....... of the services, such as sequential or reciprocal task activities, influence the development of different types of capabilities. We study five cases of offshore-outsourced knowledge-intensive business services that are distinguished according to their reciprocal or sequential task activities in their production...
Extensions of the MCNP5 and TRIPOLI4 Monte Carlo codes for transient reactor analysis
International Nuclear Information System (INIS)
Hoogenboom, J.E.
2013-01-01
To simulate reactor transients for safety analysis with the Monte Carlo method the generation and decay of delayed neutron precursors is implemented in the MCNP5 and TRIPOLI4 general purpose Monte Carlo codes. Important new variance reduction techniques like forced decay of precursors in each time interval and the branch-less collision method are included to obtain reasonable statistics for the power production per time interval. For simulation of practical reactor transients also the feedback effect from the thermal-hydraulics must be included. This requires the coupling of the Monte Carlo code with a thermal-hydraulics (TH) code, providing the temperature distribution in the reactor, which affects the neutron transport via the cross section data. The TH code also provides the coolant density distribution in the reactor, directly influencing the neutron transport. Different techniques for this coupling are discussed. As a demonstration a 3*3 mini fuel assembly with a moving control rod is considered for MCNP5 and a mini core existing of 3*3 PWR fuel assemblies with control rods and burnable poisons for TRIPOLI4. Results are shown for reactor transients due to control rod movement or withdrawal. The TRIPOLI4 transient calculation is started at low power and includes thermal-hydraulic feedback. The power rises about 10 decades and finally stabilises the reactor power at a much higher level than initial. The examples demonstrate that the modified Monte Carlo codes are capable of performing correct transient calculations, taking into account all geometrical and cross section detail. (authors)
Gain reduction measurements in transient stimulated Raman scattering
Heeman, R.J.; Godfried, H.P
1995-01-01
Threshold energy measurements of transient rotational stimulated Raman scattering are compared to Raman conversion calculations from semiclassical theories using a simple concept of a gain reduction factor which expresses the reduction of the gain from its steady-state value due to transient
International Nuclear Information System (INIS)
Hsu, T.R.; Bertels, A.W.M.; Banerjee, S.; Harrison, W.C.
1976-07-01
This report presents the theoretical basis for a transient thermal elastic-plastic stress analysis of a nuclear reactor fuel element subject to severe transient thermo-mechanical loading. A finite element formulation is used for both the non-linear stress analysis and thermal analysis. These two major components are linked together to form an integrated program capable of predicting fuel element transient behaviour in two dimensions. Specific case studies are presented to illustrate capabilities of the analysis. (author)
Reactor physics calculations on the Dutch small HTR concept
International Nuclear Information System (INIS)
Kuijper, J.C.; Haas, J.B.M. de; Klippel, H.T.; Hogenbirk, A.; Oppe, J.; Sciolla, C.M.; Stad, R.C.L. van der; Zhang, B.C.
1997-06-01
As part of the activities within the framework of the development of INCOGEN, a 'Dutch' conceptual design of a smaller HTR, the ECN reactor physics code system has been extended with the capability to perform combined neutronics and thermal hydraulics steady-state, burnup and transient core calculations on pebble-bed type HTRs, by joining the general purpose reactor code PANTHER and the HTR thermal hydraulics code THERMIX/DIREKT in the PANTHERMIX code combination. The validation of the ECN code system for HTR applications is still in progress, but some promising first calculation results on unit cell and whole core geometries are presented, which indicate that the extended ECN code system is quite suitable for performing the pebble-bed HTR core calculations, required in the INCOGEN core design and optimization process. (orig.)
Reactor physics calculations on the Dutch small HTR concept
International Nuclear Information System (INIS)
Kuijper, J.C.; Hass, J.B.M. De; Klippel, H.Th.; Hogenbirk, A.; Oppe, J.; Sciolla, C.; Stad, R.C.L. Van Der; Zhang, B.C.
1997-01-01
As part of the activities within the framework of the development of INCOGEN, a ''Dutch'' conceptual design of a small HTR, the ECN reactor physics code system has been extended with the capability to perform combined neutronics and thermal hydraulics steady-state, burnup and transient core calculations on pebble-bed type HTRS, by joining the general purpose reactor code PANTHER and the HTR thermal hydraulics code THERMIX/DIREKT in the PANTHERMIX code combination. The validation of the ECN code system for HTR applications is still in progress, but some promising first calculation results on unit cell and whole core geometries are presented, which indicate that the extended ECN code system is quite suitable for performing the pebble-bed HTR core calculations, required in the INCOGEN core design and optimization process. (author)
Some new directions in system transient simulation
International Nuclear Information System (INIS)
Ransom, V.H.
1986-01-01
The current research in system transient simulation at the Idaho National Engineering Laboratory (INEL) is summarized in this paper and three new directions that are emerging from this work are discussed. The new directions are: development of an Advanced Thermal Hydraulic Energy Network Analyzer (ATHENA) having new modeling capability, use of expert systems for enhancing simulation methods, and the trend to individual workstations for simulation
Capability Handbook- offline metrology
DEFF Research Database (Denmark)
Islam, Aminul; Marhöfer, David Maximilian; Tosello, Guido
This offline metrological capability handbook has been made in relation to HiMicro Task 3.3. The purpose of this document is to assess the metrological capability of the HiMicro partners and to gather the information of all available metrological instruments in the one single document. It provides...
Dynamic Capabilities and Performance
DEFF Research Database (Denmark)
Wilden, Ralf; Gudergan, Siegfried P.; Nielsen, Bo Bernhard
2013-01-01
are contingent on the competitive intensity faced by firms. Our findings demonstrate the performance effects of internal alignment between organizational structure and dynamic capabilities, as well as the external fit of dynamic capabilities with competitive intensity. We outline the advantages of PLS...
Developing Alliance Capabilities
DEFF Research Database (Denmark)
Heimeriks, Koen H.; Duysters, Geert; Vanhaverbeke, Wim
This paper assesses the differential performance effects of learning mechanisms on the development of alliance capabilities. Prior research has suggested that different capability levels could be identified in which specific intra-firm learning mechanisms are used to enhance a firm's alliance...
Telematics Options and Capabilities
Energy Technology Data Exchange (ETDEWEB)
Hodge, Cabell [National Renewable Energy Laboratory (NREL), Golden, CO (United States)
2017-09-05
This presentation describes the data tracking and analytical capabilities of telematics devices. Federal fleet managers can use the systems to keep their drivers safe, maintain a fuel efficient fleet, ease their reporting burden, and save money. The presentation includes an example of how much these capabilities can save fleets.
Reactor operational transient analysis
International Nuclear Information System (INIS)
Shin, W.K.; Chae, S.K.; Han, K.I.; Yang, K.S.; Chung, H. D.; Kim, H.G.; Moon, H.J.; Ryu, Y.H.
1983-01-01
To build up efficient capability of safety review and inspection for the nuclear power plants, four area of studies have performed as follows: 1) In order to search the most optimized operating method during load follow operating schemes, automatic control and normal control, are compared each other under the CAOC condition. The analysis performed by DDID code has shown that the reactor has to be controlled by the operator manually during load follow operation. 2) Through the sensitivity analysis by COBRA code, the operating parameters, such as coolant pressure, flow rate, inlet temperature, and power distribution are shown to be important to the determination of DNBR. Expecially, inlet temperature of primary coolant system is appeared as the most senstive parameter on DNBR. 3) FRAPCON code is adapted to study the sensitivity of several operational parameters on the mechanical properties of reactor fuel rod. 4) The calculations procedure which is required to be obtained the neutron fluence at the reactor vessel and the spectrum at the surveillance capsule is established. The results of computation are conpared with those of FSAR and SWRI report and proved its applicability to reactor surveillance program. (Author)
Tacina, R. R.
1984-01-01
Non-steady combustion problems can result from engine sources such as accelerations, decelerations, nozzle adjustments, augmentor ignition, and air perturbations into and out of the compressor. Also non-steady combustion can be generated internally from combustion instability or self-induced oscillations. A premixed-prevaporized combustor would be particularly sensitive to flow transients because of its susceptability to flashback-autoignition and blowout. An experimental program, the Transient Flow Combustion Study is in progress to study the effects of air and fuel flow transients on a premixed-prevaporized combustor. Preliminary tests performed at an inlet air temperature of 600 K, a reference velocity of 30 m/s, and a pressure of 700 kPa. The airflow was reduced to 1/3 of its original value in a 40 ms ramp before flashback occurred. Ramping the airflow up has shown that blowout is more sensitive than flashback to flow transients. Blowout occurred with a 25 percent increase in airflow (at a constant fuel-air ratio) in a 20 ms ramp. Combustion resonance was found at some conditions and may be important in determining the effects of flow transients.
Integrated tokamak modelling with the fast-ion Fokker–Planck solver adapted for transient analyses
International Nuclear Information System (INIS)
Toma, M; Hamamatsu, K; Hayashi, N; Honda, M; Ide, S
2015-01-01
Integrated tokamak modelling that enables the simulation of an entire discharge period is indispensable for designing advanced tokamak plasmas. For this purpose, we extend the integrated code TOPICS to make it more suitable for transient analyses in the fast-ion part. The fast-ion Fokker–Planck solver is integrated into TOPICS at the same level as the bulk transport solver so that the time evolutions of the fast ion and the bulk plasma are consistent with each other as well as with the equilibrium magnetic field. The fast-ion solver simultaneously handles neutral beam-injected ions and alpha particles. Parallelisation of the fast-ion solver in addition to its computational lightness owing to a dimensional reduction in the phase space enables transient analyses for long periods in the order of tens of seconds. The fast-ion Fokker–Planck calculation is compared and confirmed to be in good agreement with an orbit following a Monte Carlo calculation. The integrated code is applied to ramp-up simulations for JT-60SA and ITER to confirm its capability and effectiveness in transient analyses. In the integrated simulations, the coupled evolution of the fast ions, plasma profiles, and equilibrium magnetic fields are presented. In addition, the electric acceleration effect on fast ions is shown and discussed. (paper)
Analysis of forced convective transient boiling by homogeneous model of two-phase flow
International Nuclear Information System (INIS)
Kataoka, Isao
1985-01-01
Transient forced convective boiling is of practical importance in relation to the accident analysis of nuclear reactor etc. For large length-to-diameter ratio, the transient boiling characteristics are predicted by transient two-phase flow calculations. Based on homogeneous model of two-phase flow, the transient forced convective boiling for power and flow transients are analysed. Analytical expressions of various parameters of transient two-phase flow have been obtained for several simple cases of power and flow transients. Based on these results, heat flux, velocity and time at transient CHF condition are predicted analytically for step and exponential power increases, and step, exponential and linear velocity decreases. The effects of various parameters on heat flux, velocity and time at transient CHF condition have been clarified. Numerical approach combined with analytical method is proposed for more complicated cases. Solution method for pressure transient are also described. (author)
International Nuclear Information System (INIS)
Rohatgi, U.S.; Cheng, H.S.; Khan, H.J.; Mallen, A.N.; Neymotin, L.Y.
1998-03-01
This document is the User's Manual for the Boiling Water Reactor (BWR), and Simplified Boiling Water Reactor (SBWR) systems transient code RAMONA-4B. The code uses a three-dimensional neutron-kinetics model coupled with a multichannel, nonequilibrium, drift-flux, phase-flow model of the thermal hydraulics of the reactor vessel. The code is designed to analyze a wide spectrum of BWR core and system transients. Chapter 1 gives an overview of the code's capabilities and limitations; Chapter 2 describes the code's structure, lists major subroutines, and discusses the computer requirements. Chapter 3 is on code, auxillary codes, and instructions for running RAMONA-4B on Sun SPARC and IBM Workstations. Chapter 4 contains component descriptions and detailed card-by-card input instructions. Chapter 5 provides samples of the tabulated output for the steady-state and transient calculations and discusses the plotting procedures for the steady-state and transient calculations. Three appendices contain important user and programmer information: lists of plot variables (Appendix A) listings of input deck for sample problem (Appendix B), and a description of the plotting program PAD (Appendix C). 24 refs., 18 figs., 11 tabs
From transient response of a compact photobioreactor for microalgae cultivation
Energy Technology Data Exchange (ETDEWEB)
Dilay, Emerson; Ribeiro, Robert Luis Lara; Pulliam, Raevon; Mariano, Andre Bellin [Universidade Federal do Parana (UFPR), Curitiba, PR (Brazil). Nucleo de Pesquisa e Desenvolvimento em Energia Auto-Sustentavel; Ordonez, Juan Carlos [Florida State University, Tallahassee, FL (United States). Dept. of Mechanical Engineering and Center for Advanced Power Systems], E-mail: ordonez@caps.fsu.edu; Vargas, Jose Viriato Coelho [Universidade Federal do Parana (UFPR), Curitiba, PR (Brazil). Dept. de Engenharia Mecanica
2010-07-01
Biofuels from microalgae are currently the subject of funded scientific research in many countries due to their high productivity of oil when compared with other crops. Microalgae can also be used in many important applications such as to obtain compounds of interest for food, chemicals, and pharmaceuticals. The high productivity of microalgae when compared with other crops is achieved because agricultural land is not mandatory for their cultivation, since they can be grown in open ponds, sea or vertical photo bioreactors. In this paper, a mathematical model is introduced for assessing the transient microalgae growth as a function of variable light intensity, temperature and environmental conditions in the daily cycle. Photo bioreactor geometry is considered as well. Light intensity is obtained from sun position, photo bioreactor geometry, and the installation location in the world. The photo bioreactor was discretized in space by the the volume element method. Balances of energy and species together with thermodynamics, heat transfer and chemistry empirical and theoretical correlations are applied to each volume element. Therefore, a system of ordinary differential equations with respect to time only is capable of delivering temperatures and concentrations as functions of space and time, even with a coarse mesh. The numerical results are capable of predicting the transient and steady state photo bioreactor biomass production with low computational time. Microalgae specific growth rate as a function of average light intensity inside the tubes and time was calculated. As a result, the model is expected to be a useful tool for simulation, design, and optimization of compact photo bioreactors. (author)
FMEF/experimental capabilities
International Nuclear Information System (INIS)
Burgess, C.A.; Dronen, V.R.
1981-01-01
The Fuels and Materials Examination Facility (FMEF), under construction at the Hanford site north of Richland, Washington, will be one of the most modern facilities offering irradiated fuels and materials examination capabilities and fuel fabrication development technologies. Scheduled for completion in 1984, the FMEF will provide examination capability for fuel assemblies, fuel pins and test pins irradiated in the FFTF. Various functions of the FMEF are described, with emphasis on experimental data-gathering capabilities in the facility's Nondestructive and Destructive examination cell complex
KSC Technical Capabilities Website
Nufer, Brian; Bursian, Henry; Brown, Laurette L.
2010-01-01
This document is the website pages that review the technical capabilities that the Kennedy Space Center (KSC) has for partnership opportunities. The purpose of this information is to make prospective customers aware of the capabilities and provide an opportunity to form relationships with the experts at KSC. The technical capabilities fall into these areas: (1) Ground Operations and Processing Services, (2) Design and Analysis Solutions, (3) Command and Control Systems / Services, (4) Materials and Processes, (5) Research and Technology Development and (6) Laboratories, Shops and Test Facilities.
International Nuclear Information System (INIS)
Dawes, W.R. Jr.; Fischer, T.A.; Huang, C.C.C.; Meyer, W.J.; Smith, C.S.; Blanchard, R.A.; Fortier, T.J.
1986-01-01
N-channel power FETs offer significant advantages in power conditioning circuits. Similiarily to all MOS technologies, power FET devices are vulnerable to ionizing radiation, and are particularily susceptible to burn-out in high dose rate irradiations (>1E10 rads(Si)/sec.), which precludes their use in many military environments. This paper will summarize the physical mechanisms responsible for burn-out, and discuss various fabrication techniques designed to improve the transient hardness of power FETs. Power FET devices were fabricated with several of these techniques, and data will be presented which demonstrates that transient hardness levels in excess of 1E12 rads(Si)/sec. are easily achievable
International Nuclear Information System (INIS)
Cooke, C.M.; Frick, G.; Roumie, M.
1993-01-01
Electrical measurements are presented for the construction of a model for the study of transients in the Vivitron. Observation of the transmission of electrical pulses in the porticos clearly shows transmission-line behaviour. Measurements of the vector impedance of the outer porticos show the same transmission-line properties, but also gives a description of the modification from a pure transmission line due to the circular electrodes. The results of this investigation should allow the construction of a computer model which predicts the evolution of the transients in the case of a spark in the Vivitron. (orig.)
Separative performance transients in a gas centrifuge
International Nuclear Information System (INIS)
Olander, D.R.
1979-01-01
A general method has been developed to calculate the behavior of the exit compositions from a gas centrifuge under unsteady conditions. The method utilizes the basic enrichment gradient equations derived by Cohen, which, in this case, contain time derivatives of the partial 235 U inventories. These partial differential equations are converted to ordinary differential equations by a linear approximation to the axial concentration distribution for use in the inventory terms only. With this simplification, analytical solution is possible for the feed concentration transient. The transient driven by a change in the feed flow rate, however, requires numerical solution. For analysis of ideal cascades in the unsteady state, the transient flow and separation characteristics of the centrifuge must be combined with total uranium and 235 U material balances on each stage
Transient effects in friction fractal asperity creep
Goedecke, Andreas
2013-01-01
Transient friction effects determine the behavior of a wide class of mechatronic systems. Classic examples are squealing brakes, stiction in robotic arms, or stick-slip in linear drives. To properly design and understand mechatronic systems of this type, good quantitative models of transient friction effects are of primary interest. The theory developed in this book approaches this problem bottom-up, by deriving the behavior of macroscopic friction surfaces from the microscopic surface physics. The model is based on two assumptions: First, rough surfaces are inherently fractal, exhibiting roughness on a wide range of scales. Second, transient friction effects are caused by creep enlargement of the real area of contact between two bodies. This work demonstrates the results of extensive Finite Element analyses of the creep behavior of surface asperities, and proposes a generalized multi-scale area iteration for calculating the time-dependent real contact between two bodies. The toolset is then demonstrated both...
Characterization of electrical appliances in transient state
Wójcik, Augustyn; Winiecki, Wiesław
2017-08-01
The article contains the study about electrical appliance characterization on the basis of power grid signals. To represent devices, parameters of current and voltage signals recorded during transient states are used. In this paper only transients occurring as a result of switching on devices are considered. The way of data acquisition performed in specialized measurement setup developed for electricity load monitoring is described. The paper presents the method of transients detection and the method of appliance parameters calculation. Using the set of acquired measurement data and appropriate software the set of parameters for several household appliances operating in different operating conditions was processed. Usefulness of appliances characterization in Non-Intrusive Appliance Load Monitoring System (NIALMS) with the use of proposed method is discussed focusing on obtained results.
Resources, constraints and capabilities
Dhondt, S.; Oeij, P.R.A.; Schröder, A.
2018-01-01
Human and financial resources as well as organisational capabilities are needed to overcome the manifold constraints social innovators are facing. To unlock the potential of social innovation for the whole society new (social) innovation friendly environments and new governance structures
African Journals Online (AJOL)
efforts towards gender equality in education as a means of achieving social justice. ... should mean that a lot of capability approach-oriented commentators are ... processes, their forms of exercising power, and their rules, unwritten cultures, ...
Engineering Capabilities and Partnerships
Poulos, Steve
2010-01-01
This slide presentation reviews the engineering capabilities at Johnson Space Center, The presentation also reviews the partnerships that have resulted in successfully designed and developed projects that involved commercial and educational institutions.
Brandishing Cyberattack Capabilities
2013-01-01
Advertising cyberwar capabilities may be helpful. It may back up a deterrence strategy. It might dissuade other states from conventional mischief or...to enable the attack.5 Many of the instruments of the attack remain with the target system, nestled in its log files, or even in the malware itself...debat- able. Even if demonstrated, what worked yesterday may not work today. But difficult does not mean impossible. Advertising cyberwar capabilities
CASL Dakota Capabilities Summary
Energy Technology Data Exchange (ETDEWEB)
Adams, Brian M. [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States); Simmons, Chris [Univ. of Texas, Austin, TX (United States); Williams, Brian J. [Los Alamos National Lab. (LANL), Los Alamos, NM (United States)
2017-10-10
The Dakota software project serves the mission of Sandia National Laboratories and supports a worldwide user community by delivering state-of-the-art research and robust, usable software for optimization and uncertainty quantification. These capabilities enable advanced exploration and riskinformed prediction with a wide range of computational science and engineering models. Dakota is the verification and validation (V&V) / uncertainty quantification (UQ) software delivery vehicle for CASL, allowing analysts across focus areas to apply these capabilities to myriad nuclear engineering analyses.
Analysis of a station blackout transient at the Kori units 3/4
International Nuclear Information System (INIS)
Bang, Young Seok; Kim, Hho Jung
1992-01-01
A transient analysis of station blackout accident is performed to evaluate the plant specific capability to cope with the accident at the Kori Units 3/4. The RELAP5/MOD3/5m5 code and full three loop modelling scheme are used in the calculation. The leak flow from reactor coolant system due to a failure of reactor coolant pump seal following the accident is assumed to be 25 gpm and the turbine driven aux feedwater unavailable. As a result, it is found that no core uncovery occurs in the plant until 7100 sec following a station blackout, the steam generator has a decay heat removal capability until 3100 sec, and the natural circulation over the reactor coolant loop until the complete loop seal voiding are observed. And the Nuclear Plant Analyzer is used and found to be effective in improving the phenomenological understanding on the accident
Transient behaviour of small HTR for cogeneration
International Nuclear Information System (INIS)
Verkerk, E.C.; Van Heek, A.I.
2000-01-01
The Dutch market for combined generation of heat and power identifies a unit size of 40 MW thermal for the conceptual design of a nuclear cogeneration plant. The ACACIA system provides 14 MWe electricity combined with 17 t/h of high temperature steam (220 deg C, 10 bar) with a pebble-bed high temperature reactor directly coupled with a helium compressor and a helium turbine. The design of this small CHP unit that is used for industrial applications is mainly based on a pre-feasibility study in 1996, performed by a joint working group of five Dutch organisations, in which technical feasibility was shown. Thermal hydraulic and reactor physics analyses show favourable control characteristics during normal operation and a benign response to loss of helium coolant and loss of flow conditions. Throughout the response on these highly infrequent conditions, ample margin exists between the highest fuel temperatures and the temperature above which fuel degradation will occur. To come to quantitative statements about the ACACIA transient behaviour, a calculational coupling between the high temperature reactor core analysis code package PANTHER/DIREKT and the thermal hydraulic code RELAP5 for the energy conversion system has been made. This coupling offers a more realistic simulation of the entire system, since it removes the necessity of forcing boundary conditions on the simulation models at the data transfer points. In this paper, the models used for the dynamic components of the energy conversion system are described, and the results of the calculation for two operational transients in order to demonstrate the effects of the interaction between reactor core and its energy conversion system are shown. Several transient cases that are representative as operational transients for an HTR will be discussed, including one representing a load rejection case that shows the functioning of the control system, in particular the bypass valve. Another transient is a load following
Transient performance of EBR-II driver fuel
International Nuclear Information System (INIS)
Buzzell, J.A.; Hudman, G.D.; Porter, D.L.
1981-01-01
The first phases of qualification of the EBR-II driver fuel for repeated transient overpower operation have recently been completed. The accomplishments include prediction of the transient fuel and cladding performance through ex-core testing and fuel-element modeling studies, localized in-core power testing during steady-state operation, and whole-core multiple transient testing. The metallic driver fuel successfully survived 56 transients, spaced over a 45-day period, with power increases of approx. 160% at rates of approx. 1%/s with a 720-second hold at full power. The performance results obtained from both ex-core and n-core tests indicate that the fuel is capable of repeated transient operation
DEFF Research Database (Denmark)
Rode, Carsten
1998-01-01
Analytical theory of transient heat conduction.Fourier's law. General heat conducation equation. Thermal diffusivity. Biot and Fourier numbers. Lumped analysis and time constant. Semi-infinite body: fixed surface temperature, convective heat transfer at the surface, or constant surface heat flux...
Transient cavitation in pipelines
Kranenburg, C.
1974-01-01
The aim of the present study is to set up a one-dimensional mathematical model, which describes the transient flow in pipelines, taking into account the influence of cavitation and free gas. The flow will be conceived of as a three-phase flow of the liquid, its vapour and non-condensible gas. The
Transient particle emission measurement with optical techniques
Bermúdez, Vicente; Luján, José M.; Serrano, José R.; Pla, Benjamín
2008-06-01
Particulate matter is responsible for some respiratory and cardiovascular diseases. In addition, it is one of the most important pollutants of high-speed direct injection (HSDI) passenger car engines. Current legislation requires particulate dilution tunnels for particulate matter measuring. However for development work, dilution tunnels are expensive and sometimes not useful since they are not able to quantify real-time particulate emissions during transient operation. In this study, the use of a continuous measurement opacimeter and a fast response HFID is proven to be a good alternative to obtain instantaneous particle mass emissions during transient operation (due to particulate matter consisting mainly of soot and SOF). Some methods and correlations available from literature, but developed for steady conditions, are evaluated during transient operation by comparing with mini-tunnel measurements during the entire MVEG-A transient cycle. A new correlation was also derived from this evaluation. Results for soot and SOF (obtained from the new correlation proposed) are compared with soot and SOF captured with particulate filters, which have been separated by means of an SOF extraction method. Finally, as an example of ECU design strategies using these sort of correlations, the EGR valve opening is optimized during transient operation. The optimization is performed while simultaneously taking into account instantaneous fuel consumption, particulate emissions (calculated with the proposed correlation) and other regulated engine pollutants.
GVTRAN-PC-a steam generator transient simulator
International Nuclear Information System (INIS)
Nakata, H.
1991-02-01
Since an accuracy and inexpensive analysis capability is one of the desirable requirement in the reactor licensing procedure and, also, in instances when a severe accident sequence and its degree of severity must be estimated, the present work tries partially to fulfill that present need by developing a fast and acceptably accurate simulator. The present report presents the methodology utilized to develop GVTRAN-PC program, the steam generator simulation program for the microcomputer environment, which possess a capability to reproduce the experimental data with accuracies comparable to those of the mainframe simulators. The methodology is based on the mass and energy conservation in the control volumes which represents both the primary and the secondary fluid in the U-tube steam generator. The quasi-static momentum conservation in the secondary fluid control volumes determines in a semi-iterative scheme the liquid level in the feedwater chamber. The implementation of the moving boundary technique has allowed the tracking of the boundary of bulk boiling region with the utilization of a reduced number of control volumes in the tube region. GVTRAN-PC program has been tested against typical PWR pump trip transient experimental data and the calculation results showed good agreement in most representative parameters, viz. the feedchamber water-level and the steam dome pressure. (author)
Sun, Qilin
2017-04-01
High resolution transient/3D imaging technology is of high interest in both scientific research and commercial application. Nowadays, all of the transient imaging methods suffer from low resolution or time consuming mechanical scanning. We proposed a new method based on TCSPC and Compressive Sensing to achieve a high resolution transient imaging with a several seconds capturing process. Picosecond laser sends a serious of equal interval pulse while synchronized SPAD camera\\'s detecting gate window has a precise phase delay at each cycle. After capturing enough points, we are able to make up a whole signal. By inserting a DMD device into the system, we are able to modulate all the frames of data using binary random patterns to reconstruct a super resolution transient/3D image later. Because the low fill factor of SPAD sensor will make a compressive sensing scenario ill-conditioned, We designed and fabricated a diffractive microlens array. We proposed a new CS reconstruction algorithm which is able to denoise at the same time for the measurements suffering from Poisson noise. Instead of a single SPAD senor, we chose a SPAD array because it can drastically reduce the requirement for the number of measurements and its reconstruction time. Further more, it not easy to reconstruct a high resolution image with only one single sensor while for an array, it just needs to reconstruct small patches and a few measurements. In this thesis, we evaluated the reconstruction methods using both clean measurements and the version corrupted by Poisson noise. The results show how the integration over the layers influence the image quality and our algorithm works well while the measurements suffer from non-trival Poisson noise. It\\'s a breakthrough in the areas of both transient imaging and compressive sensing.
Space Logistics: Launch Capabilities
Furnas, Randall B.
1989-01-01
The current maximum launch capability for the United States are shown. The predicted Earth-to-orbit requirements for the United States are presented. Contrasting the two indicates the strong National need for a major increase in Earth-to-orbit lift capability. Approximate weights for planned payloads are shown. NASA is studying the following options to meet the need for a new heavy-lift capability by mid to late 1990's: (1) Shuttle-C for near term (include growth versions); and (2) the Advanced Lauching System (ALS) for the long term. The current baseline two-engine Shuttle-C has a 15 x 82 ft payload bay and an expected lift capability of 82,000 lb to Low Earth Orbit. Several options are being considered which have expanded diameter payload bays. A three-engine Shuttle-C with an expected lift of 145,000 lb to LEO is being evaluated as well. The Advanced Launch System (ALS) is a potential joint development between the Air Force and NASA. This program is focused toward long-term launch requirements, specifically beyond the year 2000. The basic approach is to develop a family of vehicles with the same high reliability as the Shuttle system, yet offering a much greater lift capability at a greatly reduced cost (per pound of payload). The ALS unmanned family of vehicles will provide a low end lift capability equivalent to Titan IV, and a high end lift capability greater than the Soviet Energia if requirements for such a high-end vehicle are defined.In conclusion, the planning of the next generation space telescope should not be constrained to the current launch vehicles. New vehicle designs will be driven by the needs of anticipated heavy users.
Energy Technology Data Exchange (ETDEWEB)
Bianchi, Paulo Henrique
2008-07-01
This work describes the study and test of a system capable to identify and classify transients in thermo-hydraulic systems, using a neural network technique of the self-organizing maps (SOM) type, with the objective of implanting it on the new generations of nuclear reactors. The technique developed in this work consists on the use of multiple networks to do the classification and identification of the transient states, being each network a specialist at one respective transient of the system, that compete with each other using the quantization error, that is a measure given by this type of neural network. This technique showed very promising characteristics that allow the development of new functionalities in future projects. One of these characteristics consists on the potential of each network, besides responding what transient is in course, could give additional information about that transient. (author)
Energy Technology Data Exchange (ETDEWEB)
Adams, C. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Arsenlis, T. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Bailey, A. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Bergman, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Brase, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Brenner, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Camara, L. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Carlton, H. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Cheng, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Chrzanowski, P. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Colson, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); East, D. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Farrell, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Ferranti, L. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Gursahani, A. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Hansen, R. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Helms, L. L. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Hernandez, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Jeffries, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Larson, D. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Lu, K. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); McNabb, D. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Mercer, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Skeate, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Sueksdorf, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Zucca, B. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Le, D. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Ancria, R. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Scott, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Leininger, L. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Gagliardi, F. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Gash, A. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Bronson, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Chung, B. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Hobson, B. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Meeker, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Sanchez, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Zagar, M. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Quivey, B. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Sommer, S. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States); Atherton, J. [Lawrence Livermore National Lab. (LLNL), Livermore, CA (United States)
2017-06-06
Lawrence Livermore National Laboratory Campus Capability Plan for 2018-2028. Lawrence Livermore National Laboratory (LLNL) is one of three national laboratories that are part of the National Nuclear Security Administration. LLNL provides critical expertise to strengthen U.S. security through development and application of world-class science and technology that: Ensures the safety, reliability, and performance of the U.S. nuclear weapons stockpile; Promotes international nuclear safety and nonproliferation; Reduces global danger from weapons of mass destruction; Supports U.S. leadership in science and technology. Essential to the execution and continued advancement of these mission areas are responsive infrastructure capabilities. This report showcases each LLNL capability area and describes the mission, science, and technology efforts enabled by LLNL infrastructure, as well as future infrastructure plans.
Technological Capability's Predictor Variables
Directory of Open Access Journals (Sweden)
Fernanda Maciel Reichert
2011-03-01
Full Text Available The aim of this study was to identify the factors that influence in configuration of the technological capability of companies in sectors with medium-low technological intensity. To achieve the goal proposed in this article a survey was carried out. Based on the framework developed by Lall (1992 which classifies firms in basic, intermediate and advanced level of technological capability; it was found that the predominant technological capability is intermediate, with 83.7% of respondent companies (plastics companies in Brazil. It is believed that the main contribution of this study is the finding that the dependent variable named “Technological Capability” can be explained at a rate of 65% by six variables: development of new processes; selection of the best equipment supplier; sales of internally developed new technology to third parties; design and manufacture of equipment; study of the work methods and perform inventory control; and improvement of product quality.
DEFF Research Database (Denmark)
Nielsen, Peter; Nielsen, Rene Nesgaard; Bamberger, Simon Grandjean
2012-01-01
is a survey that collected information from 601 firms belonging to the private urban sector in Denmark. The survey was carried out in late 2010. Keywords: dynamic capabilities/innovation/globalization/employee/employer cooperation/Nordic model Acknowledgment: The GOPA study was financed by grant 20080053113......Technological developments combined with increasing levels of competition related to the ongoing globalization imply that firms find themselves in dynamic, changing environments that call for dynamic capabilities. This challenges the internal human and organizational resources of firms in general...
Barnett, Ralph L; Liber, Theodore
2006-02-22
Use of unassisted human push capability arises from time to time in the areas of crowd and animal control, the security of locked doors, the integrity of railings, the removal of tree stumps and entrenched vehicles, the manoeuvering of furniture, and athletic pursuits such as US football or wrestling. Depending on the scenario, human push capability involves strength, weight, weight distribution, push angle, footwear/floor friction, and the friction between the upper body and the pushed object. Simple models are used to establish the relationships among these factors.
Robeyns, Ingrid
2011-01-01
textabstract In its most general description, the capability approach is a flexible and multi-purpose normative framework, rather than a precise theory of well-being, freedom or justice. At its core are two normative claims: first, the claim that the freedom to achieve well-being is of primary moral importance, and second, that freedom to achieve well-being is to be understood in terms of people’s capabilities, that is, their real opportunities to do and be what they have reason to value. Thi...
Energy Technology Data Exchange (ETDEWEB)
Muller, Richard P. [Sandia National Lab. (SNL-NM), Albuquerque, NM (United States)
2017-07-01
Sandia National Laboratories has developed a broad set of capabilities in quantum information science (QIS), including elements of quantum computing, quantum communications, and quantum sensing. The Sandia QIS program is built atop unique DOE investments at the laboratories, including the MESA microelectronics fabrication facility, the Center for Integrated Nanotechnologies (CINT) facilities (joint with LANL), the Ion Beam Laboratory, and ASC High Performance Computing (HPC) facilities. Sandia has invested $75 M of LDRD funding over 12 years to develop unique, differentiating capabilities that leverage these DOE infrastructure investments.
Directory of Open Access Journals (Sweden)
Mahesh M Choudhary
2015-01-01
Full Text Available We report a case of transient osteoporosis of the hip (TOH in a 50-year-old man including the clinical presentation, diagnostic studies, management, and clinical progress. TOH is a rare self-limiting condition that typically affects middle-aged men or, less frequently, women in the third trimester of pregnancy. Affected individuals present clinically with acute hip pain, limping gait, and limited ranges of hip motion. TOH may begin spontaneously or after a minor trauma. Radiographs are typically unremarkable but magnetic resonance (MR imaging studies yield findings consistent with bone marrow edema. TOH is referred to as regional migratory osteoporosis (RMO if it travels to other joints or the contralateral hip. TOH often resembles osteonecrosis but the two conditions must be differentiated due to different prognoses and management approaches. The term TOH is often used interchangeably and synonymously with transient bone marrow edema (TBME.
RETRAN's role in the development of Northeast Utilities' analytical capabilities
International Nuclear Information System (INIS)
Bonaca, M.V.; Gharakhani, A.; Sterner, R.W.
1983-01-01
The RETRAN code plays an important role in Northeast Utilities' (NUSCO's) safety analysis capabilities. Its ability to predict plant response to operational transients has been shown by several benchmarking efforts. Additionally, it has been utilized in performing both design-basis and bestestimate analyses for NUSCO's operating plants. The decision to use RETRAN as a major contributor to reload analysis efforts at NUSCO was justified by the results of numerous analyses proving RETRAN's capabilities and credibility
A transient model to the thermal detonation
International Nuclear Information System (INIS)
Karachalios, K.
1987-04-01
The model calculates the escalation dynamics and the long time behavior of thermal detonation waves depending on the initial and boundary conditions (data of the premixture, ignition at a solid wall or at an open end, etc.). Especially, for a given mixture and a certain fragmentation behavior more than one stable steady-state cases resulted, depending on the applied ignition energy. Investigations showed a very good consistency between the transient model and a steady-state model which is based on the same physical description and includes an additional stability criterion. Also the influence of effects such as e.g. non-homogeneous coolant heating, spherical instead of plane wave propagation and inhomogeneities of the premixture on the development of the wave were investigated. Comparison calculations with large scale experiments showed that they can be well explained by means of the thermal detonation theory, especially considering the transient phase of the wave development. (orig./HP) [de
Stability of Ignition Transients
V.E. Zarko
1991-01-01
The problem of ignition stability arises in the case of the action of intense external heat stimuli when, resulting from the cut-off of solid substance heating, momentary ignition is followed by extinction. Physical pattern of solid propellant ignition is considered and ignition criteria available in the literature are discussed. It is shown that the above mentioned problem amounts to transient burning at a given arbitrary temperature distribution in the condensed phase. A brief survey...
Transient FDTD simulation validation
Jauregui Tellería, Ricardo; Riu Costa, Pere Joan; Silva Martínez, Fernando
2010-01-01
In computational electromagnetic simulations, most validation methods have been developed until now to be used in the frequency domain. However, the EMC analysis of the systems in the frequency domain many times is not enough to evaluate the immunity of current communication devices. Based on several studies, in this paper we propose an alternative method of validation of the transients in time domain allowing a rapid and objective quantification of the simulations results.
ISOPHOT - Capabilities and performance
DEFF Research Database (Denmark)
Lemke, D.; Klaas, U.; Abolins, J.
1996-01-01
ISOPHOT covers the largest wavelength range on ISO from 2.5 to 240 mu m. Its scientific capabilities include multi filter and multi-aperture photometry, polarimetry, imaging and spectrophotometry. All modes can optionally include a focal plane chopper. The backbone of the photometric calibration...
Capabilities for Intercultural Dialogue
Crosbie, Veronica
2014-01-01
The capabilities approach offers a valuable analytical lens for exploring the challenge and complexity of intercultural dialogue in contemporary settings. The central tenets of the approach, developed by Amartya Sen and Martha Nussbaum, involve a set of humanistic goals including the recognition that development is a process whereby people's…
Capabilities and Special Needs
DEFF Research Database (Denmark)
Kjeldsen, Christian Christrup
into international consideration in relation to the implementation of the UN convention on the rights of persons with disabilities. As for the theoretical basis, the research makes use of the sociological open-ended and relational concepts of Pierre Bourdieu and the normative yardstick of the Capability Approach...
Metrology Measurement Capabilities
Energy Technology Data Exchange (ETDEWEB)
Dr. Glen E. Gronniger
2007-10-02
This document contains descriptions of Federal Manufacturing & Technologies (FM&T) Metrology capabilities, traceability flow charts, and the measurement uncertainty of each measurement capability. Metrology provides NIST traceable precision measurements or equipment calibration for a wide variety of parameters, ranges, and state-of-the-art uncertainties. Metrology laboratories conform to the requirements of the Department of Energy Development and Production Manual Chapter 13.2, ANSI/ISO/IEC ANSI/ISO/IEC 17025:2005, and ANSI/NCSL Z540-1. FM&T Metrology laboratories are accredited by NVLAP for the parameters, ranges, and uncertainties listed in the specific scope of accreditation under NVLAP Lab code 200108-0. See the Internet at http://ts.nist.gov/Standards/scopes/2001080.pdf. These parameters are summarized. The Honeywell Federal Manufacturing & Technologies (FM&T) Metrology Department has developed measurement technology and calibration capability in four major fields of measurement: (1) Mechanical; (2) Environmental, Gas, Liquid; (3) Electrical (DC, AC, RF/Microwave); and (4) Optical and Radiation. Metrology Engineering provides the expertise to develop measurement capabilities for virtually any type of measurement in the fields listed above. A strong audit function has been developed to provide a means to evaluate the calibration programs of our suppliers and internal calibration organizations. Evaluation includes measurement audits and technical surveys.
I.A.M. Robeyns (Ingrid)
2011-01-01
textabstract In its most general description, the capability approach is a flexible and multi-purpose normative framework, rather than a precise theory of well-being, freedom or justice. At its core are two normative claims: first, the claim that the freedom to achieve well-being is of primary
Henriksson, Jakob; Bermudez, Luis; Satapathy, Goutam
2013-04-01
There is a large amount of sensor data generated today by various sensors, from in-situ buoys to mobile underwater gliders. Providing sensor data to the users through standardized services, language and data model is the promise of OGC's Sensor Web Enablement (SWE) initiative. As the amount of data grows it is becoming difficult for data providers, planners and managers to ensure reliability of data and services and to monitor critical data changes. Intelligent Automation Inc. (IAI) is developing a net-centric alerting capability to address these issues. The capability is built on Sensor Observation Services (SOSs), which is used to collect and monitor sensor data. The alerts can be configured at the service level and at the sensor data level. For example it can alert for irregular data delivery events or a geo-temporal statistic of sensor data crossing a preset threshold. The capability provides multiple delivery mechanisms and protocols, including traditional techniques such as email and RSS. With this capability decision makers can monitor their assets and data streams, correct failures or be alerted about a coming phenomena.
MHD aspects of coronal transients
International Nuclear Information System (INIS)
Anzer, U.
1979-10-01
If one defines coronal transients as events which occur in the solar corona on rapid time scales (< approx. several hours) then one would have to include a large variety of solar phenomena: flares, sprays, erupting prominences, X-ray transients, white light transients, etc. Here we shall focus our attention on the latter two phenomena. (orig.) 891 WL/orig. 892 RDG
MASTER-2.0: Multi-purpose analyzer for static and transient effects of reactors
Energy Technology Data Exchange (ETDEWEB)
Cho, Byung Oh; Song, Jae Seung; Joo, Han Gyu [Korea Atomic Energy Research Institute, Taejon (Korea)
1999-01-01
MASTER-2.0 (Multi-purpose Analyzer for Static and Transient Effects of Reactors) is a nuclear design code based on the two group diffusion theory to calculate the steady-state and transient pressurized water reactor core in a 3-dimensional Cartesian or hexagonal geometry. Its neutronics model solves the space-time dependent neutron diffusion equations with NIM(Nodal Integration Method), NEM (Nodal Expansion Method), AFEN (Analytic Function Expansion Nodal Method)/NEM Hybrid Method, NNEM (Non-linear Nodal Expansion Method) or NANM (Non-linear Analytic Nodal Method) for a Cartesian geometry and with AFEN/NEM Hybrid Method or NLFM (Non-linear Local Fine-Mesh Method) for a hexagonal one. Coarse mesh rebalancing, Krylov Subspace method and asymptotic extrapolation method are implemented to accelerate the convergence of iteration process. Master-2.0 performs microscopic depletion calculations using microscopic cross sections provided by CASMO-3 or HELIOS and also has the reconstruction capability of pin information by use of MSS-IAS (Method of Successive Smoothing with Improved Analytic Solution). For the thermal-hydraulic calculation, fuel temperature table or COBRA3-C/P model can be used selectively. In addition, MASTER-2.0 is designed to cover various PWRs including SMART as well as WH-and CE-type reactors, providing all data required in their design procedures. (author). 39 refs., 12 figs., 4 tabs.
Master-3.0: multi-purpose analyzer for static and transient effects of reactors
International Nuclear Information System (INIS)
Cho, Byung Oh; Joo, Han Gyu; Cho, Jin Young; Song, Jae Seung; Zee, Sung Quun
2002-03-01
MASTER-3.0 (Multi-purpose Analyzer for Static and Transient Effects of Reactors) is a nuclear design code based on the multi-group diffusion theory to calculate the steady-state and transient pressurized water reactor core in a 3-dimensional Cartesian or hexagonal geometry. Its neutronics model solves the space-time dependent neutron diffusion equations with NIM (Nodal Integration Method), NEM (Nodal Expansion Method), AFEN (Analytic Function Expansion Nodal Method)/NEM Hybrid Method, NNEM (Non-linear Nodal Expansion Method) or NANM (Non-linear Analytic Nodal Method) for a Cartesian geometry and with NTPEN (Non-linear Triangle-based Polynomial Expansion Nodal Method), AFEN (Analytic Function Expansion Nodal)/NEM Hybrid Method or NLFM (Non-linear Local Fine-Mesh Method) for a hexagonal one. Coarse mesh rebalancing, Krylov Subspace method, energy group restriction/prolongation method and asymptotic extrapolation method are implemented to accelerate the convergence of iteration process. MASTER-3.0 performs microscopic depletion calculations using microscopic cross sections provided by CASMO-3 or HELIOS and also has the reconstruction capability of pin information by use of MSS-IAS (Method of Successive Smoothing with Improved Analytic Solution). For the thermal-hydraulic calculation, fuel temperature table or COBRA3-C/P or MATRA model can be used selectively. In addition, MASTER-3.0 is designed to cover various PWRs including SMART as well as WH- and CE-type reactors, providing all data required in their design procedures
Numerical calculation of transient field effects in quenching superconducting magnets
International Nuclear Information System (INIS)
Schwerg, Juljan Nikolai
2010-01-01
The maximum obtainable magnetic induction of accelerator magnets, relying on normal conducting cables and iron poles, is limited to around 2 T because of ohmic losses and iron saturation. Using superconducting cables, and employing permeable materials merely to reduce the fringe field, this limit can be exceeded and fields of more than 10 T can be obtained. A quench denotes the sudden transition from the superconducting to the normal conducting state. The drastic increase in electrical resistivity causes ohmic heating. The dissipated heat yields a temperature rise in the coil and causes the quench to propagate. The resulting high voltages and excessive temperatures can result in an irreversible damage of the magnet - to the extend of a cable melt-down. The quench behavior of a magnet depends on numerous factors, e.g. the magnet design, the applied magnet protection measures, the external electrical network, electrical and thermal material properties, and induced eddy current losses. The analysis and optimization of the quench behavior is an integral part of the construction of any superconducting magnet. The dissertation is divided in three complementary parts, i.e. the thesis, the detailed treatment and the appendix. In the thesis the quench process in superconducting accelerator magnets is studied. At first, we give an overview over features of accelerator magnets and physical phenomena occurring during a quench. For all relevant effects numerical models are introduced and adapted. The different models are weakly coupled in the quench algorithm and solved by means of an adaptive time-stepping method. This allows to resolve the variation of material properties as well as time constants. The quench model is validated by means of measurement data from magnets of the Large Hadron Collider. In a second step, we show results of protection studies for future accelerator magnets. The thesis ends with a summary of the results and a critical outlook on aspects which could be subjected to further studies. Common definitions and concepts in the design of superconducting magnets, derivations of electromagnetic models, and explanations of typical effects are collected in the detailed treatment. We introduce, e.g., the temperature margin to quench and the MIITs, and define the magnetic energy and inductance in case of materials exhibiting hysteresis and diffusive behavior. The momentarily dissipated hysteresis losses are derived for the critical state model of hard superconductors. Furthermore, we review magnet protection methods and the voltages occurring during a quench. The appendix contains all information required for the reproduction of the presented results. It comprises material properties such as the electrical resistivity or the heat capacity for a temperature range spanning from cryogenic temperatures to some hundred kelvins. The model and simulation parameters for the magnets used for this work are collected at the end.
Numerical calculation of transient field effects in quenching superconducting magnets
Schwerg, Nikolai; Russenschuck, Stephan
2009-01-01
The maximum obtainable magnetic induction of accelerator magnets, relying on normal conducting cables and iron poles, is limited to around 2 T because of ohmic losses and iron saturation. Using superconducting cables, and employing permeable materials merely to reduce the fringe field, this limit can be exceeded and fields of more than 10 T can be obtained. A quench denotes the sudden transition from the superconducting to the normal conducting state. The drastic increase in electrical resistivity causes ohmic heating. The dissipated heat yields a temperature rise in the coil and causes the quench to propagate. The resulting high voltages and excessive temperatures can result in an irreversible damage of the magnet - to the extend of a cable melt-down. The quench behavior of a magnet depends on numerous factors, e.g. the magnet design, the applied magnet protection measures, the external electrical network, electrical and thermal material properties, and induced eddy current losses. The analysis and optimizat...
Numerical calculation of transient field effects in quenching superconducting magnets
Energy Technology Data Exchange (ETDEWEB)
Schwerg, Juljan Nikolai
2010-07-01
The maximum obtainable magnetic induction of accelerator magnets, relying on normal conducting cables and iron poles, is limited to around 2 T because of ohmic losses and iron saturation. Using superconducting cables, and employing permeable materials merely to reduce the fringe field, this limit can be exceeded and fields of more than 10 T can be obtained. A quench denotes the sudden transition from the superconducting to the normal conducting state. The drastic increase in electrical resistivity causes ohmic heating. The dissipated heat yields a temperature rise in the coil and causes the quench to propagate. The resulting high voltages and excessive temperatures can result in an irreversible damage of the magnet - to the extend of a cable melt-down. The quench behavior of a magnet depends on numerous factors, e.g. the magnet design, the applied magnet protection measures, the external electrical network, electrical and thermal material properties, and induced eddy current losses. The analysis and optimization of the quench behavior is an integral part of the construction of any superconducting magnet. The dissertation is divided in three complementary parts, i.e. the thesis, the detailed treatment and the appendix. In the thesis the quench process in superconducting accelerator magnets is studied. At first, we give an overview over features of accelerator magnets and physical phenomena occurring during a quench. For all relevant effects numerical models are introduced and adapted. The different models are weakly coupled in the quench algorithm and solved by means of an adaptive time-stepping method. This allows to resolve the variation of material properties as well as time constants. The quench model is validated by means of measurement data from magnets of the Large Hadron Collider. In a second step, we show results of protection studies for future accelerator magnets. The thesis ends with a summary of the results and a critical outlook on aspects which could be subjected to further studies. Common definitions and concepts in the design of superconducting magnets, derivations of electromagnetic models, and explanations of typical effects are collected in the detailed treatment. We introduce, e.g., the temperature margin to quench and the MIITs, and define the magnetic energy and inductance in case of materials exhibiting hysteresis and diffusive behavior. The momentarily dissipated hysteresis losses are derived for the critical state model of hard superconductors. Furthermore, we review magnet protection methods and the voltages occurring during a quench. The appendix contains all information required for the reproduction of the presented results. It comprises material properties such as the electrical resistivity or the heat capacity for a temperature range spanning from cryogenic temperatures to some hundred kelvins. The model and simulation parameters for the magnets used for this work are collected at the end.
Ulrich, Dave; Smallwood, Norm
2004-06-01
By making the most of organizational capabilities--employees' collective skills and fields of expertise--you can dramatically improve your company's market value. Although there is no magic list of proficiencies that every organization needs in order to succeed, the authors identify 11 intangible assets that well-managed companies tend to have: talent, speed, shared mind-set and coherent brand identity, accountability, collaboration, learning, leadership, customer connectivity, strategic unity, innovation, and efficiency. Such companies typically excel in only three of these capabilities while maintaining industry parity in the other areas. Organizations that fall below the norm in any of the 11 are likely candidates for dysfunction and competitive disadvantage. So you can determine how your company fares in these categories (or others, if the generic list doesn't suit your needs), the authors explain how to conduct a "capabilities audit," describing in particular the experiences and findings of two companies that recently performed such audits. In addition to highlighting which intangible assets are most important given the organization's history and strategy, this exercise will gauge how well your company delivers on its capabilities and will guide you in developing an action plan for improvement. A capabilities audit can work for an entire organization, a business unit, or a region--indeed, for any part of a company that has a strategy to generate financial or customer-related results. It enables executives to assess overall company strengths and weaknesses, senior leaders to define strategy, midlevel managers to execute strategy, and frontline leaders to achieve tactical results. In short, it helps turn intangible assets into concrete strengths.
Removing fuelling transient using neutron absorbers
Energy Technology Data Exchange (ETDEWEB)
Paquette, S.; Chan, P.K.; Bonin, H.W., E-mail: Stephane.Paquette@rmc.ca [Royal Military College of Canada, Chemistry and Chemical Engineering Dept., Kingston, Ontario (Canada); Pant, A. [Cameco Fuel Manufacturing, Port Hope, Ontario (Canada)
2012-07-01
Preliminary criticality and burnup calculation results indicate that by employing a small amount of neutron absorber the fuelling transient, currently occurring in a CANDU 37-element fuel bundle, can be significantly reduced. A parametric study using the Los Alamos National Laboratories' MCNP 5 code and Atomic Energy of Canada Limited's WIMS-AECL 3.1 is presented in this paper. (author)
Ultraviolet photoelectron spectroscopy of transient species
International Nuclear Information System (INIS)
Leeuw, D.M. de.
1979-01-01
Transient species are studied in the isolation of the gas phase using ultraviolet photoelectron spectroscopy (PES). A description of the equipment used and a discussion of some theoretical topics, which play a role in the interpretation of PE spectra, are given. Koopmans' theorem, Hartree-Fock-Slater (HFS) calculations and the sum rule are discussed. A versatile ultraviolet PE spectrometer, designed specifically for this purpose, has been built and the construction and performance of this instrument are described. (Auth.)
Directory of Open Access Journals (Sweden)
Li Zhang
2017-12-01
Full Text Available In recent years, with the rapid development of offshore wind turbines (WTs, the problem of lightning strikes has become more and more prominent. In order to reduce the failure rate caused by the transient overvoltage of lightning struck offshore WTs, the influencing factors and the response rules of transient overvoltage are analyzed. In this paper, a new integrated electromagnetic transient model of offshore WTs is established by using the numerical calculation method of the electromagnetic field first. Then, based on the lightning model and considering the impedance of the lightning channel, the transient overvoltage of lightning is analyzed. Last, the electromagnetic transient model of offshore WTs is simulated and analyzed by using the alternative transients program electro-magnetic transient program (ATP-EMTP software. The influence factors of lightning transient overvoltage are studied. The main influencing factors include the sea depth, the blade length, the tower height, the lightning flow parameters, the lightning strike point, and the blade rotation position. The simulation results show that the influencing factors mentioned above have different effects on the lightning transient overvoltage. The results of the study have some guiding significance for the design of the lightning protection of the engine room.
National Oceanic and Atmospheric Administration, Department of Commerce — Declination is calculated using the current International Geomagnetic Reference Field (IGRF) model. Declination is calculated using the current World Magnetic Model...
RELAP5 nuclear plant analyzer capabilities
International Nuclear Information System (INIS)
Wagner, R.J.; Ransom, V.H.
1982-01-01
An interactive execution capability has been developed for the RELAP5 code which permits it to be used as a Nuclear Plant Analyzer. This capability has been demonstrated using a simplified primary and secondary loop model of a PWR. A variety of loss-of-feed-water accidents have been simulated using this model. The computer execution time on a CDC Cyber 176 is one half of the transient simulation time so that the results can be displayed in real time. The results of the demonstration problems are displayed in digital form on a color schematic of the plant model using a Textronics 4027 CRT terminal. The interactive feature allows the user to enter commands in much the same manner as a reactor operator
Parametric analyses of DEMO Divertor using two dimensional transient thermal hydraulic modelling
Domalapally, Phani; Di Caro, Marco
2018-05-01
Among the options considered for cooling of the Plasma facing components of the DEMO reactor, water cooling is a conservative option because of its high heat removal capability. In this work a two-dimensional transient thermal hydraulic code is developed to support the design of the divertor for the projected DEMO reactor with water as a coolant. The mathematical model accounts for transient 2D heat conduction in the divertor section. Temperature-dependent properties are used for more accurate analysis. Correlations for single phase flow forced convection, partially developed subcooled nucleate boiling, fully developed subcooled nucleate boiling and film boiling are used to calculate the heat transfer coefficients on the channel side considering the swirl flow, wherein different correlations found in the literature are compared against each other. Correlation for the Critical Heat Flux is used to estimate its limit for a given flow conditions. This paper then investigates the results of the parametric analysis performed, whereby flow velocity, diameter of the coolant channel, thickness of the coolant pipe, thickness of the armor material, inlet temperature and operating pressure affect the behavior of the divertor under steady or transient heat fluxes. This code will help in understanding the basic parameterś effect on the behavior of the divertor, to achieve a better design from a thermal hydraulic point of view.
Atmospheric Release Advisory Capability
International Nuclear Information System (INIS)
Dickerson, M.H.; Gudiksen, P.H.; Sullivan, T.J.
1983-02-01
The Atmospheric Release Advisory Capability (ARAC) project is a Department of Energy (DOE) sponsored real-time emergency response service available for use by both federal and state agencies in case of a potential or actual atmospheric release of nuclear material. The project, initiated in 1972, is currently evolving from the research and development phase to full operation. Plans are underway to expand the existing capability to continuous operation by 1984 and to establish a National ARAC Center (NARAC) by 1988. This report describes the ARAC system, its utilization during the past two years, and plans for its expansion during the next five to six years. An integral part of this expansion is due to a very important and crucial effort sponsored by the Defense Nuclear Agency to extend the ARAC service to approximately 45 Department of Defense (DOD) sites throughout the continental US over the next three years
Transient photoconductivity in amorphous semiconductors
International Nuclear Information System (INIS)
Mpawenayo, P.
1997-07-01
Localized states in amorphous semiconductors are divided in disorder induced shallow trap levels and dangling bonds deep states. Dangling bonds are assumed here to be either neutral or charged and their energy distribution is a single gaussian. Here, it is shown analytically that transient photocurrent in amorphous semiconductors is fully controlled by charge carriers transitions between localized states for one part and tunneling hopping carriers on the other. Localized dangling bonds deep states act as non radiative recombination centres, while hopping tunnelling is assisted by the Coulomb interaction between defects sites. The half-width of defects distribution is the disorder parameter that determines the carrier hopping time between defects sites. The macroscopic time that explains the long decay response times observed will all types of amorphous semiconductors is duly thought to be temperature dependent. Basic equations developed by Longeaud and Kleider are solved for the general case of a semiconductor after photo-generation. It turns out that the transient photoconductivity decay has two components; one with short response times from carriers trap-release transitions between shallow levels and extended states and a hopping component made of inter-dependent exponentials whose time constants span in larger ranges depending on disorder. The photoconductivity hopping component appears as an additional term to be added to photocurrents derived from existing models. The results of the present study explain and complete the power law decay derived in the multiple trapping models developed 20 years ago only in the approximation of the short response time regime. The long response time regime is described by the hopping macroscopic time. The present model is verified for all samples of amorphous semiconductors known so far. Finally, it is proposed to improved the modulated photoconductivity calculation techniques by including the long-lasting hopping dark documents
Expeditionary Rubber Removal Capability
2006-12-31
the modified spray unit or system with equivalent capabilities. 24 25 9.8. A pressure sensor or caster wheels should be incorporated into the...DISCUSSION 18 8.0 CONCLUSIONS 23 9.0 RECOMMENDATIONS 24 APPENDIX A – DETAILED LIST OF EQUIPMENT AND MODIFICATIONS 26 APPENDIX B – LIST OF SOURCES FOR...tall Weight – 4820 lb (No Attachments) Top Speed – 18 mph High Flow Hydraulics (Optional) – 26 gpm Steering – All Wheel Steering Cargo Max Load
Safety analysis of loss of flow transients in a typical research reactor by RELAP5/MOD3.3
International Nuclear Information System (INIS)
Di Maro, B.; Pierro, F.; Adorni, M.; Bousbia Salah, A.; D'Auria, F.
2003-01-01
The main aim of the following study is to assess the RELAP5/MOD3.3 code capability in simulating transient dynamic behaviour in nuclear research reactors. For this purpose typical loss of flow transient in a representative MTR (Metal Test Reactor) fuel type Research Reactor is considered. The transient herein considered is a sudden pump trip followed by the opening of a safety valve in order to allow passive decay heat removal by natural convection. During such transient the coolant flow decay, originally downward, leads to a flow reversal and the cooling process of the core passes from forced, mixed and finally to natural circulation. This fact makes it suitable for evaluating the new features of RELAP5 to simulate such specific operating conditions. The instantaneous reactor power is derived through the point kinetic calculation, both protected and unprotected cases are considered (with and without Scram). The results obtained from this analysis were also compared with previous results obtained by old version RELAP5/MOD2 code. (author)
Transient electromagnetic analysis in tokamaks using TYPHOON code
International Nuclear Information System (INIS)
Belov, A.V.; Duke, A.E.; Korolkov, M.D.; Kotov, V.L.; Kukhtin, V.P.; Lamzin, E.A.; Sytchevsky, S.E.
1996-01-01
The transient electromagnetic analysis of conducting structures in tokamaks is presented. This analysis is based on a three-dimensional thin conducting shell model. The finite element method has been used to solve the corresponding integrodifferential equation. The code TYPHOON has been developed to calculate transient processes in tokamaks. Calculation tests and the code verification have been carried out. The calculation results of eddy current and force distibution and a.c. losses for different construction elements for both ITER and TEXTOR tokamaks magnetic systems are presented. (orig.)
Electromagnetic validation of fault-ride through capabilities of wind turbines
DEFF Research Database (Denmark)
Arana Aristi, Iván; Garcia-Valle, Rodrigo; Sharma, Ranjan
2010-01-01
Scope of the present project is the development and validation of electro-magnetic transient model of fixed-speed wind turbines. The research work is focused on the development of a fixed-speed wind turbine model with fault-ride through capabilities during transient over-voltages. The model is de...
An analysis of power transients observed in SPERT I reactors
International Nuclear Information System (INIS)
Clancy, B.E.; Connolly, J.W.; Harrington, B.V.
1976-04-01
The analytical method described in Part I of this series has been applied to the calculation of spert I transients performed with higher initial moderator temperatures and also to those performed in a highly undermoderated core. Reasonable agreement has been obtained between calculated and experimental burst data. (author)
International Nuclear Information System (INIS)
Zirin, H.; Tanaka, K.
1981-01-01
We present data on magnetic transients (mgtr's) observed in flares on 1980 July 1 and 5 with Big Bear videomagnetograph (VMG). The 1980 July 1 event was a white light flare in which a strong bipolar mgtr was observed, and a definite change in the sunspots occurred at the time of the flare. In the 1980 July 5 flare, a mgtr was observed in only one polarity, and, although no sunspot changes occurred simultaneous with the flare, major spot changes occurred in a period of hours
Familial Transient Global Amnesia
Directory of Open Access Journals (Sweden)
R.Rhys Davies
2012-12-01
Full Text Available Following an episode of typical transient global amnesia (TGA, a female patient reported similar clinical attacks in 2 maternal aunts. Prior reports of familial TGA are few, and no previous account of affected relatives more distant than siblings or parents was discovered in a literature survey. The aetiology of familial TGA is unknown. A pathophysiological mechanism akin to that in migraine attacks, comorbidity reported in a number of the examples of familial TGA, is one possibility. The study of familial TGA cases might facilitate the understanding of TGA aetiology.
High temperature transient deformation of mixed oxide fuels
International Nuclear Information System (INIS)
Slagle, O.D.
1986-01-01
The purpose of this paper is to present recent experimental results on fuel creep under transient conditions at high temperatures. The effect of temperature, stress, heating rate, density and grain size were considered. An empirical formulation is derived for the relationship between strain, stress, temperature and heating rate. This relationship provides a means for incorporating stress relief into the analysis of fuel-cladding interaction during an overpower transient. The effect of sample density and initial grain size is considered by varying the sample parameters. Previously derived steady-state creep relationships for the high temperature creep of mixed oxide fuel were combined with the time dependency of creep found for UO 2 to calculate a transient creep relationship for mixed oxide fuel. These calculated results were found to be in good agreement with the measured high temperature transient creep results
The evolution of alliance capabilities
Heimeriks, K.H.; Duysters, G.M.; Vanhaverbeke, W.P.M.
2004-01-01
This paper assesses the effectiveness and differential performance effects of learning mechanisms on the evolution of alliance capabilities. Relying on the concept of capability lifecycles, prior research has suggested that different capability levels could be identified in which different
Fuel-pin cladding transient failure strain criterion
International Nuclear Information System (INIS)
Bard, F.E.; Duncan, D.R.; Hunter, C.W.
1983-01-01
A criterion for cladding failure based on accumulated strain was developed for mixed uranium-plutonium oxide fuel pins and used to interpret the calculated strain results from failed transient fuel pin experiments conducted in the Transient Reactor Test (TREAT) facility. The new STRAIN criterion replaced a stress-based criterion that depends on the DORN parameter and that incorrectly predicted fuel pin failure for transient tested fuel pins. This paper describes the STRAIN criterion and compares its prediction with those of the stress-based criterion
Thermal-hydraulic analysis of PWR cores in transient condition
International Nuclear Information System (INIS)
Silva Galetti, M.R. da.
1984-01-01
A calculational methodology for thermal - hydraulic analysis of PWR cores under steady-state and transient condition was selected and made available to users. An evaluation of the COBRA-IIIP/MIT code, used for subchannel analysis, was done through comparison of the code results with experimental data on steady state and transient conditions. As a result, a comparison study allowing spatial and temporal localization of critical heat flux was obtained. A sensitivity study of the simulation model to variations in some empirically determined parameter is also presented. Two transient cases from Angra I FSAR were analysed, showing the evolution of minimum DNBR with time. (Author) [pt
A numerical method for a transient two-fluid model
International Nuclear Information System (INIS)
Le Coq, G.; Libmann, M.
1978-01-01
The transient boiling two-phase flow is studied. In nuclear reactors, the driving conditions for the transient boiling are a pump power decay or/and an increase in heating power. The physical model adopted for the two-phase flow is the two fluid model with the assumption that the vapor remains at saturation. The numerical method for solving the thermohydraulics problems is a shooting method, this method is highly implicit. A particular problem exists at the boiling and condensation front. A computer code using this numerical method allow the calculation of a transient boiling initiated by a steady state for a PWR or for a LMFBR
Steady state and transient critical heat flux examinations
International Nuclear Information System (INIS)
Szabados, L.
1978-02-01
In steady state conditions within the P.W.R. parameter range the critical heat flux correlations based on local parameters reproduce the experimental data with less deviations than those based on system parameters. The transient experiments were restricted for the case of power transients. A data processing method for critical heat flux measurements has been developed and the applicability of quasi steady state calculation has been verified. (D.P.)
Additional 5 kWe thermoelectric system temperature transients
International Nuclear Information System (INIS)
Halfen, F.J.
1972-01-01
Several additional system transients have been calculated for the 5 kW(e) TE system and are reported in this document. They include a startup transient with a reactivity rate of 0.005 cents/sec, several startup accidents, a step reactivity insertion at full power and a loss of electrical load. These data are intended for input to system design analyses and for possible use in the protected accident section of the safety report. (U.S.)
System transient analysis code development for low pressure and low power
International Nuclear Information System (INIS)
Kim, Hee Cheol
1998-02-01
A real time reactor system analysis code, ARTIST, based on drift flux model has been developed to investigate the transient system behavior under low pressure, low flow and low power conditions with noncondensable gas present in the system. The governing equations of the ARTIST code consist of three mass continuity equations (steam, liquid and noncondensable), two energy equations (gas and mixture) and one momentum equation (mixture) constituted with the drift flux model. The capability of ARTIST in predicting two-phase flow void distribution in the system has been validated against experimental data. The results of the ARTIST axial void distribution at low pressure and low flow, are far better than the results of both the homogeneous model of TASS code and the two-fluid model of RELAP5/MOD3 code. Also, RELAP5/MOD3 calculation shows the large amplitude of void fraction oscillations at low pressure. These results imply that interfacial momentum transfer terms in the two-fluid model formulation should be carefully constituted, especially for the low pressure condition due to the big density differences between steam and water. Thermal-hydraulic state solution scheme is developed when noncondensable gas exists. Numerical consistency and convergence of obtaining equilibrium state is tested with the ideal problems for various situations including very low partial pressure conditions. Calculated thermal-hydraulic state for each test shows consistent and expected behaviour. A new multi-layer back propagation network algorithm for calculating the departure from nucleate boiling ratio (DNBR) is developed and adopted in ARTIST code in order to have real-time DNBR evaluation by eliminating the tandem procedure of the transient DNBR calculation. The algorithm trained by different patterns generated by latin hypercube sampling method on the performance space is tested for the randomly sampled untrained data and the transient DNBR data. The uncertainty of the algorithm is
DEFF Research Database (Denmark)
Adeyemi, Oluseyi
2013-01-01
Many western companies have moved part of their operations to China in order to take advantage of cheap resources and/or to gain access to a high potential market. Depending on motive, offshore facilities usually start either as “sales-only” of products exported by headquarters or “production......-only”, exporting parts and components back to headquarter for sales in the home country. In the course of time, the role of offshore subsidiaries in a company’s operations network tends to change and, with that, the capabilities, of the subsidiaries. Focusing on Danish subsidiaries in China, the objective...
DEFF Research Database (Denmark)
Adeyemi, Oluseyi
Many western companies have moved part of their operations to China in order to take advantage of cheap resources and/or to gain access to a high potential market. Depending on motive, offshore facilities usually start either as “sales-only” of products exported by headquarters or “production......-only”, exporting parts and components back to headquarter for sales in the home country. In the course of time, the role of offshore subsidiaries in a company’s operations network tends to change and, with that, the capabilities, of the subsidiaries. Focusing on Danish subsidiaries in China, the objective...
Irradiation creep transients in Ni-4 at.% Si
International Nuclear Information System (INIS)
Nagakawa, J.
1983-01-01
In the course of irradiation creep experiments on Ni-4 at.% Si alloy, two types of creep transients were observed on the termination of irradiation. The short term transient was completed within one minute while the long term transient persisted for nearly ten hours. A change in the temperature distribution was excluded from the possible causes, partly because the stress dependence of the observed transient strains was not linear, and partly because the strain increase expected from the temperature change was much smaller than the observed value. Transient behavior of point defects was examined in conjunction with the climb-glide mechanism and the steady-state irradiation creep data. Calculated creep transient due to excess vacancy flux to dislocations was in good agreement with the observed short term transient. The long term transient appears to be a result of dislocation microstructure change. The present results suggest an enhanced irradiation creep under cyclic irradiation conditions which will be encountered in the early generations of fusion reactors. (orig.)
Measurand transient signal suppressor
Bozeman, Richard J., Jr. (Inventor)
1994-01-01
A transient signal suppressor for use in a controls system which is adapted to respond to a change in a physical parameter whenever it crosses a predetermined threshold value in a selected direction of increasing or decreasing values with respect to the threshold value and is sustained for a selected discrete time interval is presented. The suppressor includes a sensor transducer for sensing the physical parameter and generating an electrical input signal whenever the sensed physical parameter crosses the threshold level in the selected direction. A manually operated switch is provided for adapting the suppressor to produce an output drive signal whenever the physical parameter crosses the threshold value in the selected direction of increasing or decreasing values. A time delay circuit is selectively adjustable for suppressing the transducer input signal for a preselected one of a plurality of available discrete suppression time and producing an output signal only if the input signal is sustained for a time greater than the selected suppression time. An electronic gate is coupled to receive the transducer input signal and the timer output signal and produce an output drive signal for energizing a control relay whenever the transducer input is a non-transient signal which is sustained beyond the selected time interval.
Transient regional osteoporosis
Directory of Open Access Journals (Sweden)
F. Trotta
2011-09-01
Full Text Available Transient osteoporosis of the hip and regional migratory osteoporosis are uncommon and probably underdiagnosed bone diseases characterized by pain and functional limitation mainly affecting weight-bearing joints of the lower limbs. These conditions are usually self-limiting and symptoms tend to abate within a few months without sequelae. Routine laboratory investigations are unremarkable. Middle aged men and women during the last months of pregnancy or in the immediate post-partum period are principally affected. Osteopenia with preservation of articular space and transitory edema of the bone marrow provided by magnetic resonance imaging are common to these two conditions, so they are also known by the term regional transitory osteoporosis. The appearance of bone marrow edema is not specific to regional transitory osteoporosis but can be observed in several diseases, i.e. trauma, reflex sympathetic dystrophy, avascular osteonecrosis, infections, tumors from which it must be differentiated. The etiology of this condition is unknown. Pathogenesis is still debated in particular the relationship with reflex sympathetic dystrophy, with which regional transitory osteoporosis is often identified. The purpose of the present review is to remark on the relationship between transient osteoporosis of the hip and regional migratory osteoporosis with particular attention to the bone marrow edema pattern and relative differential diagnosis.
The new MCNP6 depletion capability
International Nuclear Information System (INIS)
Fensin, M. L.; James, M. R.; Hendricks, J. S.; Goorley, J. T.
2012-01-01
The first MCNP based in-line Monte Carlo depletion capability was officially released from the Radiation Safety Information and Computational Center as MCNPX 2.6.0. Both the MCNP5 and MCNPX codes have historically provided a successful combinatorial geometry based, continuous energy, Monte Carlo radiation transport solution for advanced reactor modeling and simulation. However, due to separate development pathways, useful simulation capabilities were dispersed between both codes and not unified in a single technology. MCNP6, the next evolution in the MCNP suite of codes, now combines the capability of both simulation tools, as well as providing new advanced technology, in a single radiation transport code. We describe here the new capabilities of the MCNP6 depletion code dating from the official RSICC release MCNPX 2.6.0, reported previously, to the now current state of MCNP6. NEA/OECD benchmark results are also reported. The MCNP6 depletion capability enhancements beyond MCNPX 2.6.0 reported here include: (1) new performance enhancing parallel architecture that implements both shared and distributed memory constructs; (2) enhanced memory management that maximizes calculation fidelity; and (3) improved burnup physics for better nuclide prediction. MCNP6 depletion enables complete, relatively easy-to-use depletion calculations in a single Monte Carlo code. The enhancements described here help provide a powerful capability as well as dictate a path forward for future development to improve the usefulness of the technology. (authors)
The New MCNP6 Depletion Capability
International Nuclear Information System (INIS)
Fensin, Michael Lorne; James, Michael R.; Hendricks, John S.; Goorley, John T.
2012-01-01
The first MCNP based inline Monte Carlo depletion capability was officially released from the Radiation Safety Information and Computational Center as MCNPX 2.6.0. Both the MCNP5 and MCNPX codes have historically provided a successful combinatorial geometry based, continuous energy, Monte Carlo radiation transport solution for advanced reactor modeling and simulation. However, due to separate development pathways, useful simulation capabilities were dispersed between both codes and not unified in a single technology. MCNP6, the next evolution in the MCNP suite of codes, now combines the capability of both simulation tools, as well as providing new advanced technology, in a single radiation transport code. We describe here the new capabilities of the MCNP6 depletion code dating from the official RSICC release MCNPX 2.6.0, reported previously, to the now current state of MCNP6. NEA/OECD benchmark results are also reported. The MCNP6 depletion capability enhancements beyond MCNPX 2.6.0 reported here include: (1) new performance enhancing parallel architecture that implements both shared and distributed memory constructs; (2) enhanced memory management that maximizes calculation fidelity; and (3) improved burnup physics for better nuclide prediction. MCNP6 depletion enables complete, relatively easy-to-use depletion calculations in a single Monte Carlo code. The enhancements described here help provide a powerful capability as well as dictate a path forward for future development to improve the usefulness of the technology.
Laboratory microfusion capability study
International Nuclear Information System (INIS)
1993-05-01
The purpose of this study is to elucidate the issues involved in developing a Laboratory Microfusion Capability (LMC) which is the major objective of the Inertial Confinement Fusion (ICF) program within the purview of the Department of Energy's Defense Programs. The study was initiated to support a number of DOE management needs: to provide insight for the evolution of the ICF program; to afford guidance to the ICF laboratories in planning their research and development programs; to inform Congress and others of the details and implications of the LMC; to identify criteria for selection of a concept for the Laboratory Microfusion Facility and to develop a coordinated plan for the realization of an LMC. As originally proposed, the LMC study was divided into two phases. The first phase identifies the purpose and potential utility of the LMC, the regime of its performance parameters, driver independent design issues and requirements, its development goals and requirements, and associated technical, management, staffing, environmental, and other developmental and operational issues. The second phase addresses driver-dependent issues such as specific design, range of performance capabilities, and cost. The study includes four driver options; the neodymium-glass solid state laser, the krypton fluoride excimer gas laser, the light-ion accelerator, and the heavy-ion induction linear accelerator. The results of the Phase II study are described in the present report
Energy Technology Data Exchange (ETDEWEB)
Tél, Tamás [Institute for Theoretical Physics, Eötvös University, and MTA-ELTE Theoretical Physics Research Group, Pázmány P. s. 1/A, Budapest H-1117 (Hungary)
2015-09-15
We intend to show that transient chaos is a very appealing, but still not widely appreciated, subfield of nonlinear dynamics. Besides flashing its basic properties and giving a brief overview of the many applications, a few recent transient-chaos-related subjects are introduced in some detail. These include the dynamics of decision making, dispersion, and sedimentation of volcanic ash, doubly transient chaos of undriven autonomous mechanical systems, and a dynamical systems approach to energy absorption or explosion.
Transient osteoporosis of the hip
International Nuclear Information System (INIS)
McWalter, Patricia; Hassan Ahmed
2007-01-01
Transient osteoporosis of the hip is an uncommon cause of hip pain, mostly affecting healthy middle-aged men and also women in the third trimester of pregnancy. We present a case of transient osteoporosis of the hip in a 33-year-old non-pregnant female patient. This case highlights the importance of considering a diagnosis of transient osteoporosis of the hip in patients who present with hip pain. (author)
The ZTF Bright Transient Survey
Fremling, C.; Sharma, Y.; Kulkarni, S. R.; Miller, A. A.; Taggart, K.; Perley, D. A.; Gooba, A.
2018-06-01
As a supplement to the Zwicky Transient Facility (ZTF; ATel #11266) public alerts (ATel #11685) we plan to report (following ATel #11615) bright probable supernovae identified in the raw alert stream from the ZTF Northern Sky Survey ("Celestial Cinematography"; see Bellm & Kulkarni, 2017, Nature Astronomy 1, 71) to the Transient Name Server (https://wis-tns.weizmann.ac.il) on a daily basis; the ZTF Bright Transient Survey (BTS; see Kulkarni et al., 2018; arXiv:1710.04223).
Tél, Tamás
2015-09-01
We intend to show that transient chaos is a very appealing, but still not widely appreciated, subfield of nonlinear dynamics. Besides flashing its basic properties and giving a brief overview of the many applications, a few recent transient-chaos-related subjects are introduced in some detail. These include the dynamics of decision making, dispersion, and sedimentation of volcanic ash, doubly transient chaos of undriven autonomous mechanical systems, and a dynamical systems approach to energy absorption or explosion.
Transient Infrared Emission Spectroscopy
Jones, Roger W.; McClelland, John F.
1989-12-01
Transient Infrared Emission Spectroscopy (TIRES) is a new technique that reduces the occurrence of self-absorption in optically thick solid samples so that analytically useful emission spectra may be observed. Conventional emission spectroscopy, in which the sample is held at an elevated, uniform temperature, is practical only for optically thin samples. In thick samples the emission from deep layers of the material is partially absorbed by overlying layers.1 This self-absorption results in emission spectra from most optically thick samples that closely resemble black-body spectra. The characteristic discrete emission bands are severely truncated and altered in shape. TIRES bypasses this difficulty by using a laser to heat only an optically thin surface layer. The increased temperature of the layer is transient since the layer will rapidly cool and thicken by thermal diffusion; hence the emission collection must be correlated with the laser heating. TIRES may be done with both pulsed and cw lasers.2,3 When a pulsed laser is used, the spectrometer sampling must be synchronized with the laser pulsing so that only emission during and immediately after each laser pulse is observed.3 If a cw laser is used, the sample must move rapidly through the beam. The hot, transient layer is then in the beam track on the sample at and immediately behind the beam position, so the spectrometer field of view must be limited to this region near the beam position.2 How much self-absorption the observed emission suffers depends on how thick the heated layer has grown by thermal diffusion when the spectrometer samples the emission. Use of a pulsed laser synchronized with the spectrometer sampling readily permits reduction of the time available for heat diffusion to about 100 acs .3 When a cw laser is used, the heat-diffusion time is controlled by how small the spectrometer field of view is and by how rapidly the sample moves past within this field. Both a very small field of view and a
Energy Technology Data Exchange (ETDEWEB)
Rohatgi, U.S.; Cheng, H.S.; Khan, H.J.; Mallen, A.N.; Neymotin, L.Y.
1998-03-01
This document is the User`s Manual for the Boiling Water Reactor (BWR), and Simplified Boiling Water Reactor (SBWR) systems transient code RAMONA-4B. The code uses a three-dimensional neutron-kinetics model coupled with a multichannel, nonequilibrium, drift-flux, phase-flow model of the thermal hydraulics of the reactor vessel. The code is designed to analyze a wide spectrum of BWR core and system transients. Chapter 1 gives an overview of the code`s capabilities and limitations; Chapter 2 describes the code`s structure, lists major subroutines, and discusses the computer requirements. Chapter 3 is on code, auxillary codes, and instructions for running RAMONA-4B on Sun SPARC and IBM Workstations. Chapter 4 contains component descriptions and detailed card-by-card input instructions. Chapter 5 provides samples of the tabulated output for the steady-state and transient calculations and discusses the plotting procedures for the steady-state and transient calculations. Three appendices contain important user and programmer information: lists of plot variables (Appendix A) listings of input deck for sample problem (Appendix B), and a description of the plotting program PAD (Appendix C). 24 refs., 18 figs., 11 tabs.
Transient performance of S-prism
International Nuclear Information System (INIS)
Dubberley, A.E.; Boardman, C.E.; Gamble, R.E.; Hiu, M.M.; Lipps, A.J.; Wu, T.
2001-01-01
S-PRISM is an advanced Fast Reactor plant design that utilizes compact modular pool-type reactors sized to enable factory fabrication and an affordable prototype test of a single Nuclear Steam Supply System (NSSS) for design certification at minimum cost and risk. Based on the success of the previous DOE sponsored Advanced Liquid Metal Reactor (ALMR) program GE has continued to develop and assess the technical viability and economic potential of an up-rated plant called SuperPRISM (S-PRISM). This paper presents the results of transient analyses performed to assess the ability of S-PRISM to accommodate severe accident initiator events. A unique safety capability of S-PRISM is accommodation of the ''higher probability'' accident initiators that led to core melt accidents in prior large LMRs. These events, the Anticipated Transients Without Scram (ATWS) events, are thus the focus of passive safety confirmation analyses. The events included in this assessment are: Unprotected Loss of Flow, Unprotected Loss of Heat Sink, Unprotected Loss of Flow and Heat sink, Unprotected Transient Overpower and Unprotected Safe Shutdown Earthquake. (author)
Aeroelastic Modeling of a Nozzle Startup Transient
Wang, Ten-See; Zhao, Xiang; Zhang, Sijun; Chen, Yen-Sen
2014-01-01
Lateral nozzle forces are known to cause severe structural damage to any new rocket engine in development during test. While three-dimensional, transient, turbulent, chemically reacting computational fluid dynamics methodology has been demonstrated to capture major side load physics with rigid nozzles, hot-fire tests often show nozzle structure deformation during major side load events, leading to structural damages if structural strengthening measures were not taken. The modeling picture is incomplete without the capability to address the two-way responses between the structure and fluid. The objective of this study is to develop a tightly coupled aeroelastic modeling algorithm by implementing the necessary structural dynamics component into an anchored computational fluid dynamics methodology. The computational fluid dynamics component is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, while the computational structural dynamics component is developed under the framework of modal analysis. Transient aeroelastic nozzle startup analyses at sea level were performed, and the computed transient nozzle fluid-structure interaction physics presented,
Transient compressible flows in porous media
International Nuclear Information System (INIS)
Morrison, F.A. Jr.
1975-09-01
Transient compressible flow in porous media was investigated analytically. The major portion of the investigation was directed toward improving and understanding of dispersion in these flows and developing rapid accurate numerical techniques for predicting the extent of dispersion. The results are of interest in the containment of underground nuclear experiments. The transient one-dimensional transport of a trace component in a gas flow is analyzed. A conservation equation accounting for the effects of convective transport, dispersive transport, and decay, is developed. This relation, as well as a relation governing the fluid flow, is used to predict trace component concentration as a function of position and time. A detailed analysis of transport associated with the isothermal flow of an ideal gas is done. Because the governing equations are nonlinear, numerical calculations are performed. The ideal gas flow is calculated using a highly stable implicit iterative procedure with an Eulerian mesh. In order to avoid problems of anomolous dispersion associated with finite difference calculation, trace component convection and dispersion are calculated using a Lagrangian mesh. Details of the Eulerian-Lagrangian numerical technique are presented. Computer codes have been developed and implemented on the Lawrence Livermore Laboratory computer system
Scaling Laws in the Transient Dynamics of Firefly-like Oscillators
International Nuclear Information System (INIS)
Rubido, N; Cabeza, C; Marti, A; Ramirez Avila, G M
2011-01-01
Fireflies constitute a paradigm of pulse-coupled oscillators. In order to tackle the problems related to synchronisation transients of pulse-coupled oscillators, a Light-Controlled Oscillator (LCO) model is presented. A single LCO constitutes a one-dimensional relaxation oscillator described by two distinct time-scales meant to mimic fireflies in the sense that: it is capable of emitting light in a pulse-like fashion and detect the emitted by others in order to adjust its oscillation. We present dynamical results for two interacting LCOs in the torus for all possible coupling configurations. Transient times to the synchronous limit cycle are obtained experimentally and numerically as a function of initial conditions and coupling strengths. Scaling laws are found based on dimensional analysis and critical exponents calculated, thus, global dynamic is restricted. Furthermore, an analytical orthogonal transformation that allows to calculate Floquet multipliers directly from the time series is presented. As a consequence, local dynamics is also fully characterized. This transformation can be easily extended to a system with an arbitrary number of interacting LCOs.
Intermediate Leg SBLOCA - Long Lasting Pressure Transient
International Nuclear Information System (INIS)
Konjarek, D.; Bajs, T.; Vukovic, J.
2010-01-01
The basic phenomenology of Small Break Loss of Coolant Accident (SBLOCA) for PWR plant is described with focus on analysis of scenario in which reactor coolant pressure decreases below secondary system pressure. Best estimate light water reactor transient analysis code RELAP5/mod3.3 was used in calculation. Rather detailed model of the plant was used. The break occurs in intermediate leg on lowest elevation near pump suction. The size of the break is chosen to be small enough to cause cycling of safety valves (SVs) on steam generators (SGs) for some time, but, afterwards, it is large enough to remove decay heat through the break, causing cooling the secondary side. In this case of SBLOCA, when primary pressure decreases below secondary pressure, long lasting pressure transients with significant amplitude occur. Reasons for such behavior are explained.(author).
Development of a system code for transient analysis in a HTGR
International Nuclear Information System (INIS)
Lee, Tae Beom
2004-02-01
A GAMMA (GAs Multi-component Multi-dimensional Analysis) code is developed for transient analysis and air ingress analysis in High Temperature Gas-cooled Reactors (HTGR). The PBMR of ESKOM is selected as a reference plant for the High Temperature Gas-cooled Reactor here, which uses a direct helium cycle and pebble fuel. Physical models included in GAMMA are the pebble conduction model, radiation heat transfer model, point kinetics model, decay heat model, and component models for break flow, valve, pump, cooler, power conversion unit model. The temperature distribution and the flow distribution of the PBMR are calculated for initial and accident core in the present study. In the accident analysis, typical design basis accident (DBA), including the load transient accident and depressurization accident into the system are selected and analyzed in detail. The predictions by GAMMA for PBMR at 100% power are compared with those by VSOP and PBR S IM. It turns out that the temperature in the upper region in the third channel predicted by GAMMA is about 62 .deg. C at maximum higher than that by VSOP, but is pretty close to that by PBR S IM. The center temperature of the fuel shows that that predicted by considering swelling effect is higher than that without swelling effect by about 10 .deg. C. The net efficiency of direct system is higher than that of indirect system due to an effect of the circulator power. The transient capability of GAMMA is validated through analytical solution and PBR S IM analyzing the depressurization (Loss Of Coolant Accident, LOCA) and load transient accident. After the LOCA the system pressure decreases dramatically from 8MPa to 0.4MPa within 2 sec. After the PI (Proportional-plus-Integral) controller senses that the power shaft is over the set-point of 3,600 rpm, the bypass valve makes shaft speed back to the set-point
Anticipated transients without scram
International Nuclear Information System (INIS)
Lellouche, G.S.
1980-01-01
This article discusses in various degrees of depth the publications WASH-1270, WASH-1400, and NUREG-0460, and has as its purpose a description of the technical work done by Electric Power Research Institute (EPRI) personnel and its contractors on the subject of anticipated transients without scram (ATWS). It demonstrates the close relation between the probability of scram failure derived from historical scram data and that derived from the use of component data in a model of a system (the so-called synthesis method), such as was done in WASH-1400. The inherent conservatism of these models is demonstrated by showing that they predict significantly more events than have in fact occurred and that such models still predict scram failure probabilities low enough to make ATWS an insignificant contributor to accident risk
International Nuclear Information System (INIS)
Roche, L.; Schmitz, F.
1982-10-01
The observation of micrographic documents from fuel after a CABRI test leads to postulate a specific mode of transient fuel melting during a rapid nuclear power excursion. When reaching the melt threshold, the bands which are characteristic for the solid state are broken statistically over a macroscopic region. The time of maintaining the fuel at the critical enthalpy level between solid and liquid is too short to lead to a phase separation. A significant life-time (approximately 1 second) of this intermediate ''unsolide'' state would have consequences on the variation of physical properties linked to the phase transition solid/liquid: viscosity, specific volume and (for the irradiated fuel) fission gas release [fr
Transient osteoporosis of pregnancy.
Maliha, George; Morgan, Jordan; Vrahas, Mark
2012-08-01
Transient osteoporosis of pregnancy (TOP) is a rare yet perhaps under-reported condition that has affected otherwise healthy pregnancies throughout the world. The condition presents suddenly in the third trimester of a usually uneventful pregnancy and progressively immobilizes the mother. Radiographic studies detect drastic loss of bone mass, elevated rates of turnover in the bone, and oedema in the affected portion. Weakness of the bone can lead to fractures during delivery and other complications for the mother. Then, within weeks of labour, symptoms and radiological findings resolve. Aetiology is currently unknown, although neural, vascular, haematological, endocrine, nutrient-deficiency, and other etiologies have been proposed. Several treatments have also been explored, including simple bed rest, steroids, bisphosphonates, calcitonin, induced termination of pregnancy, and surgical intervention. The orthopedist plays an essential role in monitoring the condition (and potential complications) as well as ensuring satisfactory outcomes for both the mother and newborn. Copyright © 2012 Elsevier Ltd. All rights reserved.
Trace analysis of auxiliary feedwater capacity for Maanshan PWR loss-of-normal-feedwater transient
Energy Technology Data Exchange (ETDEWEB)
Chen, Che-Hao; Shih, Chunkuan [National Tsing Hua Univ., Taiwan (China). Inst. of Nuclear Engineering and Science; Wang, Jong-Rong; Lin, Hao-Tzu [Atomic Energy Council, Taiwan (China). Inst. of Nuclear Energy Research
2013-07-01
Maanshan nuclear power plant is a Westinghouse PWR of Taiwan Power Company (Taipower, TPC). A few years ago, TPC has made many assessments in order to uprate the power of Maanshan NPP. The assessments include NSSS (Nuclear Steam Supply System) parameters calculation, uncertainty acceptance, integrity of pressure vessel, reliability of auxiliary systems, and transient analyses, etc. Since the Fukushima Daiichi accident happened, it is necessary to consider transients with multiple-failure. Base on the analysis, we further study the auxiliary feedwater capability for Loss-of-Normal-Feedwater (LONF) transient. LONF is the limiting transient of non-turbine trip initiated event for ATWS (Anticipated Transient Without Scram) which results in a reduction in capability of the secondary system to remove the heat generated in the reactor core. If the turbine fails to trip immediately, the secondary water inventory will decrease significantly before the actuation of auxiliary feedwater (AFW) system. The heat removal from the primary side decreases, and this leads to increases of primary coolant temperature and pressure. The water level of pressurizer also increases subsequently. The heat removal through the relief valves and the auxiliary feedwater is not sufficient to fully cope with the heat generation from primary side. The pressurizer will be filled with water finally, and the RCS pressure might rise above the set point of relief valves for water discharge. RCS pressure depends on steam generator inventory, primary coolant temperature, negative reactivity feedback, and core power, etc. The RCS pressure may reach its peak after core power reduction. According to ASME Code Level C service limit criteria, the Reactor Coolant System (RCS) pressure must be under 22.06 MPa. The USNRC is developing an advanced thermal hydraulic code named TRACE for nuclear power plant safety analysis. The development of TRACE is based on TRAC and integrating with RELAP5 and other programs. SNAP
Trace analysis of auxiliary feedwater capacity for Maanshan PWR loss-of-normal-feedwater transient
International Nuclear Information System (INIS)
Chen, Che-Hao; Shih, Chunkuan; Wang, Jong-Rong; Lin, Hao-Tzu
2013-01-01
Maanshan nuclear power plant is a Westinghouse PWR of Taiwan Power Company (Taipower, TPC). A few years ago, TPC has made many assessments in order to uprate the power of Maanshan NPP. The assessments include NSSS (Nuclear Steam Supply System) parameters calculation, uncertainty acceptance, integrity of pressure vessel, reliability of auxiliary systems, and transient analyses, etc. Since the Fukushima Daiichi accident happened, it is necessary to consider transients with multiple-failure. Base on the analysis, we further study the auxiliary feedwater capability for Loss-of-Normal-Feedwater (LONF) transient. LONF is the limiting transient of non-turbine trip initiated event for ATWS (Anticipated Transient Without Scram) which results in a reduction in capability of the secondary system to remove the heat generated in the reactor core. If the turbine fails to trip immediately, the secondary water inventory will decrease significantly before the actuation of auxiliary feedwater (AFW) system. The heat removal from the primary side decreases, and this leads to increases of primary coolant temperature and pressure. The water level of pressurizer also increases subsequently. The heat removal through the relief valves and the auxiliary feedwater is not sufficient to fully cope with the heat generation from primary side. The pressurizer will be filled with water finally, and the RCS pressure might rise above the set point of relief valves for water discharge. RCS pressure depends on steam generator inventory, primary coolant temperature, negative reactivity feedback, and core power, etc. The RCS pressure may reach its peak after core power reduction. According to ASME Code Level C service limit criteria, the Reactor Coolant System (RCS) pressure must be under 22.06 MPa. The USNRC is developing an advanced thermal hydraulic code named TRACE for nuclear power plant safety analysis. The development of TRACE is based on TRAC and integrating with RELAP5 and other programs. SNAP
Study on shadowing effect caused by transient rods at NSRR
International Nuclear Information System (INIS)
Nakamura, T.; Yachi, S.; Ishijima, K.
1992-01-01
Irregularly inserted three control rods created so called shadowing effects on some of the neutronic instruments at the Nuclear Safety Research Reactor (NSRR). During operations at the reactor power of up to 10 MW, the three control rods called transient rods, could be fully or partly inserted into the NSRR core. Reactor power monitors located outside of the core at the direction of deeply inserted transient rods indicated lower power in such operations. Power profiles of the reactor and neutron fluxes at power monitor locations were calculated with a three dimensional neutron diffusion code, CITATION. The calculation indicated that the real reactor power could be smaller than the measured maximum power by as mush as 30 % in such operations. The calculated neutron fluxes well described the changes in the apparent power monitor indications as a function of the transient rod position. (author)
Transient Go: A Mobile App for Transient Astronomy Outreach
Crichton, D.; Mahabal, A.; Djorgovski, S. G.; Drake, A.; Early, J.; Ivezic, Z.; Jacoby, S.; Kanbur, S.
2016-12-01
Augmented Reality (AR) is set to revolutionize human interaction with the real world as demonstrated by the phenomenal success of `Pokemon Go'. That very technology can be used to rekindle the interest in science at the school level. We are in the process of developing a prototype app based on sky maps that will use AR to introduce different classes of astronomical transients to students as they are discovered i.e. in real-time. This will involve transient streams from surveys such as the Catalina Real-time Transient Survey (CRTS) today and the Large Synoptic Survey Telescope (LSST) in the near future. The transient streams will be combined with archival and latest image cut-outs and other auxiliary data as well as historical and statistical perspectives on each of the transient types being served. Such an app could easily be adapted to work with various NASA missions and NSF projects to enrich the student experience.
Thermonuclear model for high energy transients
International Nuclear Information System (INIS)
Woosley, S.E.
1982-01-01
The thermonuclear model for x- and γ-ray bursts is discussed. Different regimes of nuclear burning are reviewed, each appropriate to a given range of (steady state) accretion rate. Accretion rates in the range 10 -14 to 10 -8 Msub solar y -1 all appear capable of producing x-ray transients of various durations and intervals. Modifications introduced by radiatively driven mass loss, the thermal inertia of the envelope, different burning mechanisms, and two-dimensional considerations are discussed as are difficulties encountered when the thermonuclear model is confronted with observations of rapidly recurrent bursts (less than or equal to 10 min), and super-Eddington luminosities and temperatures. Results from a numerical simulation of a combined hydrogen-helium runaway initiated at pycnonuclear density are presented for the first time. The thermonuclear model for γ-ray bursts is also reviewed and updated, particularly with regard to the breakdown of the steady state hypothesis employed in previous work. Solely on the basis of nuclear instability, γ-ray bursts of various types appear possible for a very broad variety of accretion rates (approx. 10 -17 to approx. 10 -11 Msub solar y -1 ) although other considerations may restrict this range. The thermonuclear model appears capable of yielding a great diversity of high energy transient phenomena for various accretion rates, magnetic field configurations, and neutron star envelope histories
EP1000 anticipated transient without scram analyses
International Nuclear Information System (INIS)
Saiu, G.; Frogheri, M.; Schulz, T.L.
2001-01-01
The present paper summarizes the main results of the Anticipated Transient Without Scram (ATWS) analysis activity, performed for the European Passive Plant Program (EPP). The behavior of the EP1000 plant following an ATWS has been analyzed by means of the RELAP5/Mod3.2 code. An ATWS is defined as an Anticipated Transient accompanied by a common mode failure in the reactor protection system, such that the control rods do not scram as required to mitigate the consequences of the transient. According to the experience gained in PWR design, the limiting ATWS events, in a PWR, have been found to be the heatup transients caused by a reduction of heat removal capability by the secondary side of the plant. For this reason, the Loss of Normal Feedwater initiating event, to which the failure of the reactor scram is associated, has been analyzed. The purpose of the study is to verify the performance requirements set for the core feedback characteristics (that is to evaluate the effect of the low boron core neutron kinetic parameters), the overpressure protection system, and boration systems to cope with the EUR Acceptance Criteria for ATWS. Another purpose of this analysis was to support development of revised PSA success criteria that would reduce the contribution of ATWS to the large release frequency (LRF). The low boron core improved the basic EP1000 response to an ATWS event. In particular, the peak pressure was significantly lower than that which would result from a standard core configuration. The improved ATWS analysis results also permitted improved ATWS PSA success criteria. For example, the reduced peak pressure allows the use of other plant features to mitigate the event, including manual initiation of feed-bleed cooling in the event of PRHR HX failure. As a result, the core melt frequency and especially the LRF are significantly reduced. (author)
International Nuclear Information System (INIS)
Scholtyssek, W.
1995-01-01
In the first phase of a benchmark comparison, the CONTAIN code was used to calculate an assumed EPR accident 'medium-sized leak in the cold leg', especially for the first two days after initiation of the accident. The results for global characteristics compare well with those of FIPLOC, MELCOR and WAVCO calculations, if the same materials data are used as input. However, significant differences show up for local quantities such as flows through leakages. (orig.)
Thermohydraulic calculations of PWR primary circuits
International Nuclear Information System (INIS)
Botelho, D.A.
1984-01-01
Some mathematical and numerical models from Retran computer codes aiming to simulate reactor transients, are presented. The equations used for calculating one-dimensional flow are integrated using mathematical methods from Flash code, with steam code to correlate the variables from thermodynamic state. The algorithm obtained was used for calculating a PWR reactor. (E.G.) [pt
Calculation methods for analysing nuclear power plant accidents and its qualification
International Nuclear Information System (INIS)
Sacco, W.
1986-01-01
A methodology of transient and accident analyses able to carried out calculations for all transients and accidents required to support operation and operation licensing of Angra-1 reactor reload, is presented. (M.C.K.) [pt
Pressure transients in pipeline systems
DEFF Research Database (Denmark)
Voigt, Kristian
1998-01-01
This text is to give an overview of the necessary background to do investigation of pressure transients via simulations. It will describe briefly the Method of Characteristics which is the defacto standard for simulating pressure transients. Much of the text has been adopted from the book Pressur...
Aircraft Capability Management
Mumaw, Randy; Feary, Mike
2018-01-01
This presentation presents an overview of work performed at NASA Ames Research Center in 2017. The work concerns the analysis of current aircraft system management displays, and the initial development of an interface for providing information about aircraft system status. The new interface proposes a shift away from current aircraft system alerting interfaces that report the status of physical components, and towards displaying the implications of degradations on mission capability. The proposed interface describes these component failures in terms of operational consequences of aircraft system degradations. The research activity was an effort to examine the utility of different representations of complex systems and operating environments to support real-time decision making of off-nominal situations. A specific focus was to develop representations that provide better integrated information to allow pilots to more easily reason about the operational consequences of the off-nominal situations. The work is also seen as a pathway to autonomy, as information is integrated and understood in a form that automated responses could be developed for the off-nominal situations in the future.
Production capability and supply
International Nuclear Information System (INIS)
Klemenic, J.
1977-01-01
The strong market for uranium of recent years is about to usher in a new era in domestic uranium production. The spot market price of uranium has remained relatively stable at a little over $40/lb for more than 18 months. Many of the recent contracts for delivery in the early 1980s are calling for prices in the range of $40 to $65 per lb in year-of-delivery dollars. Low-grade, high-cost projects, such as uranium recovery from mill tailings and the reopening of ''mined-out'' ore bodies, have already been initiated. New underground mines to produce at greater depths, and new surface mines to recover lower grade ores, are being developed or seriously planned. In keeping with this movement to recover uranium from low-grade ore and other high cost materials, the Grand Junction Office has examined, for the first time, the production capability of the domestic industry assuming a $30/lb (or less) ''forward cost'' resource base. As in the past, keep in mind that the market price needed to stimulate full production of a given resource base may be significantly higher than the estimated forward cost of producing that resource. Results of the $30/lb study are presented
LHC Capabilities for Quarkonia
Petrushanko, Sergey
2008-01-01
The measurement of the charmonium and bottomonium resonances in nucleus-nucleus collisions provides crucial information on high-density QCD matter. First, the suppression of quarkonia production is generally agreed to be one of the most direct probes of quark-gluon plasma formation. The observation of anomalous J/$\\psi$ suppression at the CERN-SPS and at RHIC is well established but the clarification of some important remaining questions requires equivalent studies of the $\\Upsilon$ family, only possible at the LHC energies. Second, the production of heavy-quarks proceeds mainly via gluon-gluon fusion processes and, as such, is sensitive to saturation of the gluon density at low-x in the nucleus. Measured departures from the expected vacuum quarkonia cross-sections in Pb+Pb collisions at the LHC will thus provide valuable information not only on the thermodynamical state of the produced partonic medium, but also on the initial-state modifications of the nuclear parton distribution functions. The capabilities ...
Mobile systems capability plan
International Nuclear Information System (INIS)
1996-09-01
This plan was prepared to initiate contracting for and deployment of these mobile system services. 102,000 cubic meters of retrievable, contact-handled TRU waste are stored at many sites around the country. Also, an estimated 38,000 cubic meters of TRU waste will be generated in the course of waste inventory workoff and continuing DOE operations. All the defense TRU waste is destined for disposal in WIPP near Carlsbad NM. To ship TRU waste there, sites must first certify that the waste meets WIPP waste acceptance criteria. The waste must be characterized, and if not acceptable, subjected to additional processing, including repackaging. Most sites plan to use existing fixed facilities or open new ones between FY1997-2006 to perform these functions; small-quantity sites lack this capability. An alternative to fixed facilities is the use of mobile systems mounted in trailers or skids, and transported to sites. Mobile systems will be used for all characterization and certification at small sites; large sites can also use them. The Carlsbad Area Office plans to pursue a strategy of privatization of mobile system services, since this offers a number of advantages. To indicate the possible magnitude of the costs of deploying mobile systems, preliminary estimates of equipment, maintenance, and operating costs over a 10-year period were prepared and options for purchase, lease, and privatization through fixed-price contracts considered
Strength capability while kneeling.
Haslegrave, C M; Tracy, M F; Corlett, E N
1997-12-01
Work sometimes has to be carried out kneeling, particularly where jobs are performed in confined spaces as is common for miners, aircraft baggage handlers and maintenance workers. In order to assess the risks in performing forceful tasks under such conditions, data is needed on strength capabilities of kneeling subjects. A study was undertaken to measure isometric strength in single-handed exertions for male subjects and to investigate the effects on this of task layout factors (direction of force exertion, reach distance, height of the workpiece and orientation relative to the subject's sagittal plane). The data has been tabulated to show the degree to which strength may be reduced in different situations and analysis of the task factors showed their influence to be complex with direction of exertion and reach distance having the greatest effect. The results also suggest that exertions are weaker when subjects are kneeling on two knees than when kneeling on one knee, although this needs to be confirmed by direct experimental comparison.
Peach Bottom transient analysis with BWR TRACB02
International Nuclear Information System (INIS)
Alamgir, M.; Sutherland, W.A.
1984-01-01
TRAC calculations have been performed for a Turbine Trip transient (TT1) in the Peach Bottom BWR power plant. This study is a part of the qualification of the BWR-TRAC code. The simulation is aimed at reproducing the observed thermal hydraulic behavior in a pressurization transient. Measured core power is an input to the calculation. Comparison with data show the code reasonably well predicts the generation and propagation of the pressure waves in the main steam line and associated pressurization of the reactor vessel following the closure of the turbine stop valve
Transient Dynamics of Electric Power Systems: Direct Stability Assessment and Chaotic Motions
Chu, Chia-Chi
A power system is continuously experiencing disturbances. Analyzing, predicting, and controlling transient dynamics, which describe transient behaviors of the power system following disturbances, is a major concern in the planning and operation of a power utility. Important conclusions and decisions are made based on the result of system transient behaviors. As today's power network becomes highly interconnected and much more complex, it has become essential to enhance the fundamental understanding of transient dynamics, and to develop fast and reliable computational algorithms. In this thesis, we emphasize mathematical rigor rather than physical insight. Nonlinear dynamical system theory is applied to study two fundamental topics: direct stability assessment and chaotic motions. Conventionally, power system stability is determined by calculating the time-domain transient behaviors for a given disturbance. In contrast, direct methods identify whether or not the system will remain stable once the disturbance is removed by comparing the corresponding energy value of the post-fault system to a calculated threshold value. Direct methods not only avoid the time-consuming numerical integration of the time domain approach, but also provide a quantitative measure of the degree of system stability. We present a general framework for the theoretical foundations of direct methods. Canonical representations of network-reduction models as well as network-preserving models are proposed to facilitate the analysis and the construction of energy functions of various power system models. An advanced and practical method, called the boundary of stability region based controlling unstable equilibrium point method (BCU method), of computing the controlling unstable equilibrium point is proposed along with its theoretical foundation. Numerical solution algorithms capable of supporting on-line applications of direct methods are provided. Further possible improvements and enhancements are
Transient Analyses for a Molten Salt Transmutation Reactor Using the Extended SIMMER-III Code
International Nuclear Information System (INIS)
Wang, Shisheng; Rineiski, Andrei; Maschek, Werner; Ignatiev, Victor
2006-01-01
Recent developments extending the capabilities of the SIMMER-III code for the dealing with transient and accidents in Molten Salt Reactors (MSRs) are presented. These extensions refer to the movable precursor modeling within the space-time dependent neutronics framework of SIMMER-III, to the molten salt flow modeling, and to new equations of state for various salts. An important new SIMMER-III feature is that the space-time distribution of the various precursor families with different decay constants can be computed and took into account in neutron/reactivity balance calculations and, if necessary, visualized. The system is coded and tested for a molten salt transmuter. This new feature is also of interest in core disruptive accidents of fast reactors when the core melts and the molten fuel is redistributed. (authors)
Results of LWR core transient benchmarks
International Nuclear Information System (INIS)
Finnemann, H.; Bauer, H.; Galati, A.; Martinelli, R.
1993-10-01
LWR core transient (LWRCT) benchmarks, based on well defined problems with a complete set of input data, are used to assess the discrepancies between three-dimensional space-time kinetics codes in transient calculations. The PWR problem chosen is the ejection of a control assembly from an initially critical core at hot zero power or at full power, each for three different geometrical configurations. The set of problems offers a variety of reactivity excursions which efficiently test the coupled neutronic/thermal - hydraulic models of the codes. The 63 sets of submitted solutions are analyzed by comparison with a nodal reference solution defined by using a finer spatial and temporal resolution than in standard calculations. The BWR problems considered are reactivity excursions caused by cold water injection and pressurization events. In the present paper, only the cold water injection event is discussed and evaluated in some detail. Lacking a reference solution the evaluation of the 8 sets of BWR contributions relies on a synthetic comparative discussion. The results of this first phase of LWRCT benchmark calculations are quite satisfactory, though there remain some unresolved issues. It is therefore concluded that even more challenging problems can be successfully tackled in a suggested second test phase. (authors). 46 figs., 21 tabs., 3 refs
International Nuclear Information System (INIS)
Hall, D.G.; Watkins, J.C.
1987-01-01
This report documents an evaluation of the TRAC-PF1/MOD1 reactor safety analysis computer code during computer simulations of feedwater line break transients. The experimental data base for the evaluation included the results of three bottom feedwater line break tests performed in the Semiscale Mod-2C test facility. The tests modeled 14.3% (S-FS-7), 50% (S-FS-11), and 100% (S-FS-6B) breaks. The test facility and the TRAC-PF1/MOD1 model used in the calculations are described. Evaluations of the accuracy of the calculations are presented in the form of comparisons of measured and calculated histories of selected parameters associated with the primary and secondary systems. In addition to evaluating the accuracy of the code calculations, the computational performance of the code during the simulations was assessed. A conclusion was reached that the code is capable of making feedwater line break transient calculations efficiently, but there is room for significant improvements in the simulations that were performed. Recommendations are made for follow-on investigations to determine how to improve future feedwater line break calculations and for code improvements to make the code easier to use
Transient regional osteoporosis.
Cano-Marquina, Antonio; Tarín, Juan J; García-Pérez, Miguel-Ángel; Cano, Antonio
2014-04-01
Transient regional osteoporosis (TRO) is a disease that predisposes to fragility fracture in weight bearing joints of mid-life women and men. Pregnant women may also suffer the process, usually at the hip. The prevalence of TRO is lower than the systemic form, associated with postmenopause and advanced age, but may be falsely diminished by under-diagnosis. The disease may be uni- or bilateral, and may migrate to distinct joints. One main feature of TRO is spontaneous recovery. Pain and progressive limitation in the functionality of the affected joint(s) are key symptoms. In the case of the form associated with pregnancy, difficulties in diagnosis derive from the relatively young age at presentation and from the clinical overlapping with the frequent aches during gestation. Densitometric osteoporosis in the affected region is not always present, but bone marrow edema, with or without joint effusion, is detected by magnetic resonance. There are not treatment guidelines, but the association of antiresorptives to symptomatic treatment seems to be beneficial. Surgery or other orthopedic interventions can be required for specific indications, like hip fracture, intra-medullary decompression, or other. Copyright © 2014 Elsevier Ireland Ltd. All rights reserved.
Chaudhry, M Hanif
2014-01-01
This book covers hydraulic transients in a comprehensive and systematic manner from introduction to advanced level and presents various methods of analysis for computer solution. The field of application of the book is very broad and diverse and covers areas such as hydroelectric projects, pumped storage schemes, water-supply systems, cooling-water systems, oil pipelines and industrial piping systems. Strong emphasis is given to practical applications, including several case studies, problems of applied nature, and design criteria. This will help design engineers and introduce students to real-life projects. This book also: · Presents modern methods of analysis suitable for computer analysis, such as the method of characteristics, explicit and implicit finite-difference methods and matrix methods · Includes case studies of actual projects · Provides extensive and complete treatment of governed hydraulic turbines · Presents design charts, desi...
International Nuclear Information System (INIS)
Cheon, Se Woo; Kim, Wan Joo; Chang, Soon Heung; Roh, Myung Sub
1991-01-01
The Back-propagation Neural Network (BPN) algorithm is applied to connectionist expert system for the identification of BWR transients. Several powerful features of neural network-based expert systems over traditional rule-based expert systems are described. The general mapping capability of the neural networks enables to identify transients easily. A number of case studies were performed with emphasis on the applicability of the neural networks to the diagnostic domain. It is revealed that the BPN algorithm can identify transients properly, even when incomplete or untrained symptoms are given. It is also shown that multiple transients are easily identified
PWR plant transient analyses using TRAC-PF1
International Nuclear Information System (INIS)
Ireland, J.R.; Boyack, B.E.
1984-01-01
This paper describes some of the pressurized water reactor (PWR) transient analyses performed at Los Alamos for the US Nuclear Regulatory Commission using the Transient Reactor Analysis Code (TRAC-PF1). Many of the transient analyses performed directly address current PWR safety issues. Included in this paper are examples of two safety issues addressed by TRAC-PF1. These examples are pressurized thermal shock (PTS) and feed-and-bleed cooling for Oconee-1. The calculations performed were plant specific in that details of both the primary and secondary sides were modeled in addition to models of the plant integrated control systems. The results of these analyses show that for these two transients, the reactor cores remained covered and cooled at all times posing no real threat to the reactor system nor to the public
Kinetics of transient electroluminescence in organic light emitting diodes
Shukla, Manju; Kumar, Pankaj; Chand, Suresh; Brahme, Nameeta; Kher, R. S.; Khokhar, M. S. K.
2008-08-01
Mathematical simulation on the rise and decay kinetics of transient electroluminescence (EL) in organic light emitting diodes (OLEDs) is presented. The transient EL is studied with respect to a step voltage pulse. While rising, for lower values of time, the EL intensity shows a quadratic dependence on (t - tdel), where tdel is the time delay observed in the onset of EL, and finally attains saturation at a sufficiently large time. When the applied voltage is switched off, the initial EL decay shows an exponential dependence on (t - tdec), where tdec is the time when the voltage is switched off. The simulated results are compared with the transient EL performance of a bilayer OLED based on small molecular bis(2-methyl 8-hydroxyquinoline)(triphenyl siloxy) aluminium (SAlq). Transient EL studies have been carried out at different voltage pulse amplitudes. The simulated results show good agreement with experimental data. Using these simulated results the lifetime of the excitons in SAlq has also been calculated.
Radio pulsars and transients in the Galactic center
International Nuclear Information System (INIS)
Lazio, Joseph; Deneva, J S; Bower, Geoffrey C; Cordes, J M; Hyman, Scott D; Backer, D C; Bhat, R; Chatterjee, S; Demorest, P; Ransom, S M; Vlemmings, W
2006-01-01
Radio pulsars and transients provide powerful probes of the star formation history, interstellar medium, and gravitational potential of the Galactic center. Historical radio observations of the Galactic center have not emphasized the time domain aspect of observing this region. We summarize a series of recent searches for and observations of radio transients and pulsars that make use of two advances in technology. The first is the formation of large fields of view (∼> 1 0 ) at relatively longer wavelengths (λ > 1 m), and the second is the construction of receivers and instruments capable of collecting data on microsecond time scales at relatively short wavelengths (∼ 3 cm)
Confirmatory simulation of safety and operational transients in LMFBR systems
International Nuclear Information System (INIS)
Guppy, J.G.; Agrawal, A.K.
1978-01-01
Operational and safety transients that may originate anywhere in an LMFBR system must be adequately simulated to assist in safety evaluation and plant design efforts. This paper describes an advanced thermohydraulic transient code, the Super System Code (SSC), that may be used for confirmatory safety evaluations of plant wide events, such as assurance of adequate decay heat removal capability under natural circulation conditions, and presents results obtained with SSC illustrating the degree of modelling detail present in the code as well as the computing efficiency. (author)
The Transient High Energy Sky and Early Universe Surveyor
O'Brien, P. T.
2016-04-01
The Transient High Energy Sky and Early Universe Surveyor is a mission which will be proposed for the ESA M5 call. THESEUS will address multiple components in the Early Universe ESA Cosmic Vision theme:4.1 Early Universe,4.2 The Universe taking shape, and4.3 The evolving violent Universe.THESEUS aims at vastly increasing the discovery space of the high energy transient phenomena over the entire cosmic history. This is achieved via a unique payload providing an unprecedented combination of: (i) wide and deep sky monitoring in a broad energy band(0.3 keV-20 MeV; (ii) focusing capabilities in the soft X-ray band granting large grasp and high angular resolution; and (iii) on board near-IR capabilities for immediate transient identification and first redshift estimate.The THESEUS payload consists of: (i) the Soft X--ray Imager (SXI), a set of Lobster Eye (0.3--6 keV) telescopes with CCD detectors covering a total FOV of 1 sr; (ii) the X--Gamma-rays spectrometer (XGS), a non-imaging spectrometer (XGS) based on SDD+CsI, covering the same FOV than the Lobster telescope extending the THESEUS energy band up to 20 MeV; and (iii) a 70cm class InfraRed Telescope (IRT) observing up to 2 microns with imaging and moderate spectral capabilities.The main scientific goals of THESEUS are to:(a) Explore the Early Universe (cosmic dawn and reionization era) by unveiling the Gamma--Ray Burst (GRBs) population in the first billion years}, determining when did the first stars form, and investigating the re-ionization epoch, the interstellar medium (ISM) and the intergalactic medium (IGM) at high redshifts.(b) Perform an unprecedented deep survey of the soft X-ray transient Universe in order to fill the present gap in the discovery space of new classes of transient; provide a fundamental step forward in the comprehension of the physics of various classes of Galactic and extra--Galactic transients, and provide real time trigger and accurate locations of transients for follow-up with next
Transient study of a PWR pressurizer
International Nuclear Information System (INIS)
Sotoma, H.
1973-01-01
An appropriate method for the calculation and transient performance of the pressurizer of a pressurized water reactor is presented. The study shows a digital program of simulation of pressurizer dynamics based on the First Law of Thermodynamic and Laws of Heat and Mass Transfer. The importance of the digital program that was written for a pressurizer of PWR, lies in the fact that, this can be of practical use in the safety analysis of a reactor of Angra dos Reis type with a power of about 500 M We. (author)
Transient gas flow through layered porous media
International Nuclear Information System (INIS)
Morrison, F.A. Jr.
1975-01-01
Low Reynolds number isothermal flow of an ideal gas through layered porous material was investigated analytically. Relations governing the transient flow in one dimension are obtained. An implicit, iterative, unconditionally stable finite difference scheme is developed for calculation of such flows. A computer code, SIROCCO, employing this technique has been written and implemented on the LLL computer system. A listing of the code is included. This code may be effectively applied to the evaluation of stemming plans for underground nuclear experiments. (U.S.)
Beam induced rf cavity transient voltage
International Nuclear Information System (INIS)
Kramer, S.L.; Wang, J.M.
1998-10-01
The authors calculate the transient voltage induced in a radio frequency cavity by the injection of a relativistic bunched beam into a circular accelerator. A simplified model of the beam induced voltage, using a single tone current signal, is generated and compared with the voltage induced by a more realistic model of a point-like bunched beam. The high Q limit of the bunched beam model is shown to be related simply to the simplified model. Both models are shown to induce voltages at the resonant frequency ω r of the cavity and at an integer multiple of the bunch revolution frequency (i.e. the accelerating frequency for powered cavity operation) hω ο . The presence of two nearby frequencies in the cavity leads to a modulation of the carrier wave exp(hω ο t). A special emphasis is placed in this paper on studying the modulation function. These models prove useful for computing the transient voltage induced in superconducting rf cavities, which was the motivation behind this research. The modulation of the transient cavity voltage discussed in this paper is the physical basis of the recently observed and explained new kinds of longitudinal rigid dipole mode which differs from the conventional Robinson mode
International Nuclear Information System (INIS)
1975-09-01
Sandia Laboratories is an engineering laboratory in which research, development, testing, and evaluation capabilities are integrated by program management for the generation of advanced designs. In fulfilling its primary responsibility to ERDA, Sandia Laboratories has acquired extensive research and development capabilities. The purpose of this series of documents is to catalog the many technical capabilities of the Laboratories. After the listing of capabilities, supporting information is provided in the form of highlights, which show applications. This document deals with auxiliary capabilities, in particular, environmental health and information science. (11 figures, 1 table) (RWR)
Sandia Laboratories technical capabilities: testing
International Nuclear Information System (INIS)
Lundergan, C.D.
1975-12-01
The testing capabilities at Sandia Laboratories are characterized. Selected applications of these capabilities are presented to illustrate the extent to which they can be applied in research and development programs
Sandia Laboratories technical capabilities: electronics
International Nuclear Information System (INIS)
Lundergan, C.D.
1975-12-01
This report characterizes the electronics capabilities at Sandia Laboratories. Selected applications of these capabilities are presented to illustrate the extent to which they can be applied in research and development programs
Structural Capability of an Organization toward Innovation Capability
DEFF Research Database (Denmark)
Nielsen, Susanne Balslev; Momeni, Mostafa
2016-01-01
The scholars in the field of strategic management have developed two major approaches for attainment of competitive advantage: an approach based on environmental opportunities, and another one based on internal capabilities of an organization. Some investigations in the last two decades have...... indicated that the advantages relying on the internal capabilities of organizations may determine the competitive position of organizations better than environmental opportunities do. Characteristics of firms shows that one of the most internal capabilities that lead the organizations to the strongest...... competitive advantage in the organizations is the innovation capability. The innovation capability is associated with other organizational capabilities, and many organizations have focused on the need to identify innovation capabilities.This research focuses on recognition of the structural aspect...
Future Transient Testing of Advanced Fuels
Energy Technology Data Exchange (ETDEWEB)
Jon Carmack
2009-09-01
The transient in-reactor fuels testing workshop was held on May 4–5, 2009 at Idaho National Laboratory. The purpose of this meeting was to provide a forum where technical experts in transient testing of nuclear fuels could meet directly with technical instrumentation experts and nuclear fuel modeling and simulation experts to discuss needed advancements in transient testing to support a basic understanding of nuclear fuel behavior under off-normal conditions. The workshop was attended by representatives from Commissariat à l'Énergie Atomique CEA, Japanese Atomic Energy Agency (JAEA), Department of Energy (DOE), AREVA, General Electric – Global Nuclear Fuels (GE-GNF), Westinghouse, Electric Power Research Institute (EPRI), universities, and several DOE national laboratories. Transient testing of fuels and materials generates information required for advanced fuels in future nuclear power plants. Future nuclear power plants will rely heavily on advanced computer modeling and simulation that describes fuel behavior under off-normal conditions. TREAT is an ideal facility for this testing because of its flexibility, proven operation and material condition. The opportunity exists to develop advanced instrumentation and data collection that can support modeling and simulation needs much better than was possible in the past. In order to take advantage of these opportunities, test programs must be carefully designed to yield basic information to support modeling before conducting integral performance tests. An early start of TREAT and operation at low power would provide significant dividends in training, development of instrumentation, and checkout of reactor systems. Early start of TREAT (2015) is needed to support the requirements of potential users of TREAT and include the testing of full length fuel irradiated in the FFTF reactor. The capabilities provided by TREAT are needed for the development of nuclear power and the following benefits will be realized by
Future Transient Testing of Advanced Fuels
International Nuclear Information System (INIS)
Carmack, Jon
2009-01-01
The transient in-reactor fuels testing workshop was held on May 4-5, 2009 at Idaho National Laboratory. The purpose of this meeting was to provide a forum where technical experts in transient testing of nuclear fuels could meet directly with technical instrumentation experts and nuclear fuel modeling and simulation experts to discuss needed advancements in transient testing to support a basic understanding of nuclear fuel behavior under off-normal conditions. The workshop was attended by representatives from Commissariat energie Atomique CEA, Japanese Atomic Energy Agency (JAEA), Department of Energy (DOE), AREVA, General Electric - Global Nuclear Fuels (GE-GNF), Westinghouse, Electric Power Research Institute (EPRI), universities, and several DOE national laboratories. Transient testing of fuels and materials generates information required for advanced fuels in future nuclear power plants. Future nuclear power plants will rely heavily on advanced computer modeling and simulation that describes fuel behavior under off-normal conditions. TREAT is an ideal facility for this testing because of its flexibility, proven operation and material condition. The opportunity exists to develop advanced instrumentation and data collection that can support modeling and simulation needs much better than was possible in the past. In order to take advantage of these opportunities, test programs must be carefully designed to yield basic information to support modeling before conducting integral performance tests. An early start of TREAT and operation at low power would provide significant dividends in training, development of instrumentation, and checkout of reactor systems. Early start of TREAT (2015) is needed to support the requirements of potential users of TREAT and include the testing of full length fuel irradiated in the FFTF reactor. The capabilities provided by TREAT are needed for the development of nuclear power and the following benefits will be realized by the
Explosive and radio-selected Transients: Transient Astronomy with ...
Indian Academy of Sciences (India)
40
sitive measurements will lead to very accurate mass loss estimation in these supernovae. .... transients are powerful probes of intervening media owing to dispersion ...... A., & Chandra, P. 2011, Nature Communications,. 2, 175. Chakraborti, S.
The Capability to Hold Property
Claassen, Rutger
2015-01-01
This paper discusses the question of whether a capability theory of justice (such as that of Martha Nussbaum) should accept a basic “capability to hold property.” Answering this question is vital for bridging the gap between abstract capability theories of justice and their institutional
Transient leak detection in crude oil pipelines
Energy Technology Data Exchange (ETDEWEB)
Beushausen, R.; Tornow, S.; Borchers, H. [Nord-West Oelleitung, Wilhelmshaven (Germany); Murphy, K.; Zhang, J. [Atmos International Ltd., Manchester (United Kingdom)
2004-07-01
Nord-West Oelleitung (NWO) operates 2 crude oil pipelines from Wilhemshaven to Koln and Hamburg respectively. German regulations for transporting flammable substances stipulate that 2 independent continuously working procedures be used to detect leaks. Leak detection pigs are used routinely to complement the surveillance system. This paper described the specific issues of transient leak detection in crude oil pipelines. It was noted that traditional methods have failed to detect leaks that occur immediately after pumps are turned on or off because the pressure wave generated by the transient dominates the pressure wave that results from the leak. Frequent operational changes in a pipeline are often accompanied by an increased number of false alarms and failure to detect leaks due to unsteady operations. NWO therefore decided to have the Atmos statistical pipeline leak detection (SPLD) system installed on their pipelines. The key to the SPLD system is the sequential probability ratio test. Comprehensive data validation is performed following reception of pipeline data from the supervisory control and data acquisition (SCADA) system. The validated data is then used to calculate the corrected flow imbalance, which is fed into the SPRT to determine if there is an increase in the flow imbalance. Pattern recognition is then used to distinguish a leak from operational changes. The SPLD is unique because it uses 3 computational pipeline monitoring methods simultaneously, namely modified volume balance, statistical analysis, and pressure and flow monitoring. The successful installation and testing of the SPLD in 2 crude oil pipelines was described along with the main difficulties associated with transient leaks. Field results were presented for both steady-state and transient conditions. 5 refs., 2 tabs., 16 figs.
Transient-Switch-Signal Suppressor
Bozeman, Richard J., Jr.
1995-01-01
Circuit delays transmission of switch-opening or switch-closing signal until after preset suppression time. Used to prevent transmission of undesired momentary switch signal. Basic mode of operation simple. Beginning of switch signal initiates timing sequence. If switch signal persists after preset suppression time, circuit transmits switch signal to external circuitry. If switch signal no longer present after suppression time, switch signal deemed transient, and circuit does not pass signal on to external circuitry, as though no transient switch signal. Suppression time preset at value large enough to allow for damping of underlying pressure wave or other mechanical transient.
Electromagnetic transients in power cables
da Silva, Filipe Faria
2013-01-01
From the more basic concepts to the most advanced ones where long and laborious simulation models are required, Electromagnetic Transients in Power Cables provides a thorough insight into the study of electromagnetic transients and underground power cables. Explanations and demonstrations of different electromagnetic transient phenomena are provided, from simple lumped-parameter circuits to complex cable-based high voltage networks, as well as instructions on how to model the cables.Supported throughout by illustrations, circuit diagrams and simulation results, each chapter contains exercises,
SOLA-VOF: a solution algorithm for transient fluid flow with multiple free boundaries
International Nuclear Information System (INIS)
Nichols, B.D.; Hirt, C.W.; Hotchkiss, R.S.
1980-08-01
In this report a simple, but powerful, computer program is presented for the solution of two-dimensional transient fluid flow with free boundaries. The SOLA-VOF program, which is based on the concept of a fractional volume of fluid (VOF), is more flexible and efficient than other methods for treating arbitrary free boundaries. SOLA-VOF has a variety of user options that provide capabilities for a wide range of applications. Its basic mode of operation is for single fluid calculations having multiple free surfaces. However, SOLA-VOF can also be used for calculations involving two fluids separated by a sharp interface. In either case, the fluids may be treated as incompressible or as having limited compressibility. Surface tension forces with wall adhesion are permitted in both cases. Internal obstacles may be defined by blocking out any desired combination of cells in the mesh, which is composed of rectangular cells of variable size. SOLA-VOF is an easy-to-use program. Its logical parts are isolated in separate subroutines, and numerous special features have been included to simplify its operation, such as an automatic time-step control, a flexible mesh generator, extensive output capabilities, a variety of optional boundary conditions, and instructive internal documentation
Capability-based computer systems
Levy, Henry M
2014-01-01
Capability-Based Computer Systems focuses on computer programs and their capabilities. The text first elaborates capability- and object-based system concepts, including capability-based systems, object-based approach, and summary. The book then describes early descriptor architectures and explains the Burroughs B5000, Rice University Computer, and Basic Language Machine. The text also focuses on early capability architectures. Dennis and Van Horn's Supervisor; CAL-TSS System; MIT PDP-1 Timesharing System; and Chicago Magic Number Machine are discussed. The book then describes Plessey System 25
Calculation Method of Steam Generator Level for swelling and shrinking effects in YGN 1/2 Simulator
International Nuclear Information System (INIS)
Hwang, Do Hyun; Seo, In Yong; Park, Weon Seo; Suh, Jae Seung
2007-01-01
In August 2006, the development of new simulator for YGN 1/2 Simulator was completed. The NSSS (Nuclear Steam Supply System) T/H(Thermal- Hydraulic) module in this simulator was developed with ARTS code based on RETRAN, which is a best estimate thermal-hydraulic code designed to analyze several operational transients by EPRI(Electric Power Research Institute). RETRAN, however, has some limitations in real-time calculation capability and its robustness to be used in the simulator for some transient conditions. To overcome these limitations, its robustness and real-time calculation capability have been improved with simplifications and removing of discontinuities of the physical correlations of the RETRAN code. And some supplements are also developed to extend its simulation scope of the ARTS code. In comparison to KNPEC(Kori Nuclear Power Education Center) no.2 simulator, the simulator based on Younggwang Unit 1 developed in the year 2001, the ARTS code was upgraded that it extended its calculating region to the steam line and common header before turbine while it had calculated to the steam generator exit before steam line in KNPEC no.2 simulator. Consequently, the number of volume and fill/normal junction in ARTS nodalization increased to 109 and 174 from 62 and 125, respectively
International Nuclear Information System (INIS)
Li, D.
1980-01-01
Reviewed is the effect of heat flux of different system parameters on critical density in order to give an initial view on the value of several parameters. A thorough analysis of different equations is carried out to calculate burnout is steam-water flows in uniformly heated tubes, annular, and rectangular channels and rod bundles. Effect of heat flux density distribution and flux twisting on burnout and storage determination according to burnout are commended [ru
Transforming organizational capabilities in strategizing
DEFF Research Database (Denmark)
Jørgensen, Claus; Friis, Ole Uhrskov; Koch, Christian
2014-01-01
Offshored and networked enterprises are becoming an important if not leading organizational form and this development seriously challenges their organizational capabilities. More specifically, over the last years, SMEs have commenced entering these kinds of arrangements. As the organizational...... capabilities of SMEs are limited at the outset, even more emphasis is needed regarding the issues of developing relevant organizational capabilities. This paper aims at investigating how capabilities evolve during an offshoring process of more than 5 years in two Danish SMEs, i.e. not only short- but long......-term evolvements within the companies. We develop our framework of understanding organizational capabilities drawing on dynamic capability, relational capability and strategy as practice concepts, appreciating the performative aspects of developing new routines. Our two cases are taken from one author’s Ph...
International Nuclear Information System (INIS)
Richet, Y.; Jacquet, O.; Bay, X.
2005-01-01
The accuracy of an Iterative Monte Carlo calculation requires the convergence of the simulation output process. The present paper deals with a post processing algorithm to suppress the transient due to initialization applied on criticality calculations. It should be noticed that this initial transient suppression aims only at obtaining a stationary output series, then the convergence of the calculation needs to be guaranteed independently. The transient suppression algorithm consists in a repeated truncation of the first observations of the output process. The truncation of the first observations is performed as long as a steadiness test based on Brownian bridge theory is negative. This transient suppression method was previously tuned for a simplified model of criticality calculations, although this paper focuses on the efficiency on real criticality calculations. The efficiency test is based on four benchmarks with strong source convergence problems: 1) a checkerboard storage of fuel assemblies, 2) a pin cell array with irradiated fuel, 3) 3 one-dimensional thick slabs, and 4) an array of interacting fuel spheres. It appears that the transient suppression method needs to be more widely validated on real criticality calculations before any blind using as a post processing in criticality codes
Transient or permanent fisheye views
DEFF Research Database (Denmark)
Jakobsen, Mikkel Rønne; Hornbæk, Kasper
2012-01-01
Transient use of information visualization may support specific tasks without permanently changing the user interface. Transient visualizations provide immediate and transient use of information visualization close to and in the context of the user’s focus of attention. Little is known, however......, about the benefits and limitations of transient visualizations. We describe an experiment that compares the usability of a fisheye view that participants could call up temporarily, a permanent fisheye view, and a linear view: all interfaces gave access to source code in the editor of a widespread...... programming environment. Fourteen participants performed varied tasks involving navigation and understanding of source code. Participants used the three interfaces for between four and six hours in all. Time and accuracy measures were inconclusive, but subjective data showed a preference for the permanent...
Transient thyrotoxicosis during nivolumab treatment
van Kooten, M. J.; van den Berg, G.; Glaudemans, A. W. J. M.; Hiltermann, T. J. N.; Groen, H. J. M.; Rutgers, A.; Links, T. P.
Two patients presented with transient thyrotoxicosis within 2-4 weeks after starting treatment with nivolumab. This thyrotoxicosis turned into hypothyroidism within 6-8 weeks. Temporary treatment with a beta blocker may be sufficient.
Couston, L.; Mei, C.; Alam, M.
2013-12-01
A large number of lakes are surrounded by steep and unstable mountains with slopes prone to failure. As a result, landslides are likely to occur and impact water sitting in closed reservoirs. These rare geological phenomena pose serious threats to dam reservoirs and nearshore facilities because they can generate unexpectedly large tsunami waves. In fact, the tallest wave experienced by contemporary humans occurred because of a landslide in the narrow bay of Lituya in 1958, and five years later, a deadly landslide tsunami overtopped Lake Vajont's dam, flooding and damaging villages along the lakefront and in the Piave valley. If unstable slopes and potential slides are detected ahead of time, inundation maps can be drawn to help people know the risks, and mitigate the destructive power of the ensuing waves. These maps give the maximum wave runup height along the lake's vertical and sloping boundaries, and can be obtained by numerical simulations. Keeping track of the moving shorelines along beaches is challenging in classical Eulerian formulations because the horizontal extent of the fluid domain can change over time. As a result, assuming a solid slide and nonbreaking waves, here we develop a nonlinear shallow-water model equation in the Lagrangian framework to address the problem of transient landslide-tsunamis. In this manner, the shorelines' three-dimensional motion is part of the solution. The model equation is hyperbolic and can be solved numerically by finite differences. Here, a 4th order Runge-Kutta method and a compact finite-difference scheme are implemented to integrate in time and spatially discretize the forced shallow-water equation in Lagrangian coordinates. The formulation is applied to different lake and slide geometries to better understand the effects of the lake's finite lengths and slide's forcing mechanism on the generated wavefield. Specifically, for a slide moving down a plane beach, we show that edge-waves trapped by the shoreline and free
International Nuclear Information System (INIS)
Hsu, Y.Y.
1974-01-01
The following papers related to two-phase flow are summarized: current assumptions made in two-phase flow modeling; two-phase unsteady blowdown from pipes, flow pattern in Laval nozzle and two-phase flow dynamics; dependence of radial heat and momentum diffusion; transient behavior of the liquid film around the expanding gas slug in a vertical tube; flooding phenomena in BWR fuel bundles; and transient effects in bubble two-phase flow. (U.S.)
Fast reactor fuel pin behavior analyses in a LOF type transient event
International Nuclear Information System (INIS)
Mizuno, Tomoyasu; Koyama, Shin-ichi; Kaito, Takeji; Uwaba, Tomoyuki; Tanaka, Kenya
2013-06-01
In order to evaluate integrity limiting parameters of fuel pins during fast reactor core transient events, such as fuel center line temperature and cladding maximum temperature, fuel pin behavior calculations were made using the fast reactor fuel pin performance code CEDAR. The temperature histories of fuel pins during a loss of flow (LOF) type transient events was calculated based on Ross and Stoute type gap conductance model and constant gap conductance model, which is used in a core transient calculation code like HIPRAC. The calculated maximum temperatures of cladding and adjacent coolant channel were lower in the case with Ross and Stoute type model than in the case of constant gap conductance model due to the dynamic change of gap conductance of former case. It is indicated that core transient calculations with constant gap conductance give conservative cladding and coolant temperatures than that with Ross and Stoute type gap conductance model which is thought to be realistic. (author)
Impact of Personnel Capabilities on Organizational Innovation Capability
DEFF Research Database (Denmark)
Nielsen, Susanne Balslev; Momeni, Mostafa
2016-01-01
in this rapidly changing world. This research focuses on definition of the personnel aspect of innovation capability, and proposes a conceptual model based on the scientific articles of academic literature on organisations innovation capability. This paper includes an expert based validation in three rounds...... of the Delphi method. And for the purpose of a better appreciation of the relationship dominating the factors of the model, it has distributed the questionnaire to Iranian companies in the Food industry. This research proposed a direct relationship between Innovation Capability and the Personnel Capability...
Vibrational Analysis of (SCN)2 and the Transient (SCN)2
DEFF Research Database (Denmark)
Jensen, N. H.; Wilbrandt, Robert Walter; Pagsberg, Palle Bjørn
1979-01-01
The vibrational spectra of thiocyanogen and the transient radical anion (SCN)2− are interpreted in detail through molecular orbital and normal coordinate calculations. The results support the assignment of (SCN)2− to the anion of thiocyanogen and indicate a substantial weakening of the S–S and C......≡N bonds in going from the parent molecule to its radical anion....
International Nuclear Information System (INIS)
Barhen, J.; Bjerke, M.A.; Cacuci, D.G.; Mullins, C.B.; Wagschal, G.G.
1982-01-01
An advanced methodology for performing systematic uncertainty analysis of time-dependent nonlinear systems is presented. This methodology includes a capability for reducing uncertainties in system parameters and responses by using Bayesian inference techniques to consistently combine prior knowledge with additional experimental information. The determination of best estimates for the system parameters, for the responses, and for their respective covariances is treated as a time-dependent constrained minimization problem. Three alternative formalisms for solving this problem are developed. The two ''off-line'' formalisms, with and without ''foresight'' characteristics, require the generation of a complete sensitivity data base prior to performing the uncertainty analysis. The ''online'' formalism, in which uncertainty analysis is performed interactively with the system analysis code, is best suited for treatment of large-scale highly nonlinear time-dependent problems. This methodology is applied to the uncertainty analysis of a transient upflow of a high pressure water heat transfer experiment. For comparison, an uncertainty analysis using sensitivities computed by standard response surface techniques is also performed. The results of the analysis indicate the following. Major reduction of the discrepancies in the calculation/experiment ratios is achieved by using the new methodology. Incorporation of in-bundle measurements in the uncertainty analysis significantly reduces system uncertainties. Accuracy of sensitivities generated by response-surface techniques should be carefully assessed prior to using them as a basis for uncertainty analyses of transient reactor safety problems
Comparison and analysis on transient characteristics of integral pressurized water reactors
International Nuclear Information System (INIS)
Zhang, Guoxu; Xie, Heng
2017-01-01
Highlights: • Two IPWR Relap5 models with different PSS design were developed. • Postulated SBO and SBLOCA were analyzed. • PRHRS in primary PSS design showed stable performance under different scenarios. • Secondary PRHRS design faced flow instability. - Abstract: In the present work, the similarities and differences of representative IPWRs (integral pressurized water reactor) are studied, and two typical reactor design schemes are summarized. To get a comprehensive understanding of their transient characteristics, SBO (station blackout) and SBLOCA (small break LOCA) are simulated and analyzed respectively by using Relap5/Mod3.2. The calculation results show that, both designs are effective in keeping reactor safe. However, the transient features of the two designs show significant differences. In the primary side passive safety system (PSS) connection design, PRHRS (passive residual heat removal system) shows a roughly congruent performance in removing residual heat under various accidents. While in secondary side PSS connection design, the capability of PRHRS is closely related to primary coolant circulation condition. In SBLOCA analysis, different design approach shows different primary coolant water inventory change trend. And primary PSS connection design could potentially keep reactor core well covered for a longer time.
A fast reactor transient analysis methodology for personal computers
International Nuclear Information System (INIS)
Ott, K.O.
1993-01-01
A simplified model for a liquid-metal-cooled reactor (LMR) transient analysis, in which point kinetics as well as lumped descriptions of the heat transfer equations in all components are applied, is converted from a differential into an integral formulation. All 30 differential balance equations are implicitly solved in terms of convolution integrals. The prompt jump approximation is applied as the strong negative feedback effectively keeps the net reactivity well below prompt critical. After implicit finite differencing of the convolution integrals, the kinetics equation assumes a new form, i.e., the quadratic dynamics equation. In this integral formulation, the initial value problem of typical LMR transients can be solved with large item steps (initially 1 s, later up to 256 s). This then makes transient problems amenable to a treatment on personal computer. The resulting mathematical model forms the basis for the GW-BASIC program LMR transient calculation (LTC) program. The LTC program has also been converted to QuickBASIC. The running time for a 10-h transient overpower transient is then ∼40 to 10 s, depending on the hardware version (286, 386, or 486 with math coprocessors)
International Nuclear Information System (INIS)
Petersen, K.E.
1986-03-01
Risk and reliability analysis is increasingly being used in evaluations of plant safety and plant reliability. The analysis can be performed either during the design process or during the operation time, with the purpose to improve the safety or the reliability. Due to plant complexity and safety and availability requirements, sophisticated tools, which are flexible and efficient, are needed. Such tools have been developed in the last 20 years and they have to be continuously refined to meet the growing requirements. Two different areas of application were analysed. In structural reliability probabilistic approaches have been introduced in some cases for the calculation of the reliability of structures or components. A new computer program has been developed based upon numerical integration in several variables. In systems reliability Monte Carlo simulation programs are used especially in analysis of very complex systems. In order to increase the applicability of the programs variance reduction techniques can be applied to speed up the calculation process. Variance reduction techniques have been studied and procedures for implementation of importance sampling are suggested. (author)
McCarty, George
1982-01-01
How THIS BOOK DIFFERS This book is about the calculus. What distinguishes it, however, from other books is that it uses the pocket calculator to illustrate the theory. A computation that requires hours of labor when done by hand with tables is quite inappropriate as an example or exercise in a beginning calculus course. But that same computation can become a delicate illustration of the theory when the student does it in seconds on his calculator. t Furthermore, the student's own personal involvement and easy accomplishment give hi~ reassurance and en couragement. The machine is like a microscope, and its magnification is a hundred millionfold. We shall be interested in limits, and no stage of numerical approximation proves anything about the limit. However, the derivative of fex) = 67.SgX, for instance, acquires real meaning when a student first appreciates its values as numbers, as limits of 10 100 1000 t A quick example is 1.1 , 1.01 , 1.001 , •••• Another example is t = 0.1, 0.01, in the functio...
Yamashita, Hideo; Nakamae, Eihachiro; Namera, Akihiro; Cingoski, Vlatko; Kitamura, Hideo
1998-01-01
This paper deals with design improvements on graded insulation of power transformers using transient electric field analysis and a visualization technique. The calculation method for transient electric field analysis inside a power transformer impressed with impulse voltage is presented: Initially, the concentrated electric network for the power transformer is concentrated by dividing transformer windings into several blocks and by computing the electric circuit parameters.
A fast reactor transient analysis methodology for PCs
International Nuclear Information System (INIS)
Ott, K.O.
1991-10-01
This Manual describes a PC program for LMR Transient Calculations, LTC, written in GW-BASIC. It calculates the power and temperature trajectories for unscrammed TOP and LOHS transients. The LOF transient treatment is not operational in the GW-BASIC program because of storage limitations. The corresponding mathematical model, which allows a rapid treatment of the kinetics and the various feedback effects, is described in Ref. 1. It is briefly reviewed in Sec. 1. The program structure is outlined in Sec. 2, followed by a more detailed description in Sec. 3. Computational details are presented in Appendix A. A complete listing of the GW-BASIC program is given in Appendix B. Appendix C shows input-echo and output for a TOP sample problem, and Appendix D is a Glossary of all quantities used in the LTC program. The limitations of the GW-BASIC storage (to about 60K) are removed if it is run within Quick-BASIC. This then allows the extension of this program to treat LOF transients. Running LTC in Quick-BASIC permits also larger ''Dimensions'' for TOP and LOHS transients
People Capability Maturity Model. SM.
1995-09-01
tailored so it consumes less time and resources than a traditional software process assessment or CMU/SEI-95-MM-02 People Capability Maturity Model...improved reputation or customer loyalty. CMU/SEI-95-MM-02 People Capability Maturity Model ■ L5-17 Coaching Level 5: Optimizing Activity 1...Maturity Model CMU/SEI-95-MM-62 Carnegie-Mellon University Software Engineering Institute DTIC ELECTE OCT 2 7 1995 People Capability Maturity
Vacuum system transient simulator and its application to TFTR
International Nuclear Information System (INIS)
Sredniawski, J.
1978-01-01
The vacuum system transient simulator (VSTS) models transient gas transport throughout complex networks of ducts, valves, traps, vacuum pumps, and other related vacuum system components. VSTS is capable of treating gas models of up to 10 species, for all flow regimes from pure molecular to continuum. Viscous interactions between species are considered as well as non-uniform temperature of a system. Although this program was specifically developed for use on the Tokamak Fusion Test Reactor (TFTR) project at Princeton, it is a generalized tool capable of handling a broad range of vacuum system problems. During the TFTR engineering design phase, VSTS has been used in many applications. Two applications selected for presentation are: (1) torus vacuum pumping system performance between 400 Ci tritium pulses and (2) tritium backstreaming to neutral beams during pulses
Vacuum system transient simulator and its application to TFTR
International Nuclear Information System (INIS)
Sredniawski, J.
1977-01-01
The vacuum system transient simulator (VSTS) models transient gas transport throughout complex networks of ducts, valves, traps, vacuum pumps, and other related vacuum system components. VSTS is capable of treating gas models of up to 10 species, for all flow regimes from pure molecular to continuum. Viscous interactions between species are considered as well as non-uniform temperature of a system. Although this program was specifically developed for use on the Tokamak Fusion Test Reactor (TFTR) project at Princeton, it is a generalized tool capable of handling a broad range of vacuum system problems. During the TFTR engineering design phase, VSTS has been used in many applications. Two applications selected for presentation are: torus vacuum pumping system performance between 400 Ci tritium pulses and tritium backstreaming to neutral beams during pulses
Transient magnetoviscosity of dilute ferrofluids
International Nuclear Information System (INIS)
Soto-Aquino, Denisse; Rinaldi, Carlos
2011-01-01
The magnetic field induced change in the viscosity of a ferrofluid, commonly known as the magnetoviscous effect and parameterized through the magnetoviscosity, is one of the most interesting and practically relevant aspects of ferrofluid phenomena. Although the steady state behavior of ferrofluids under conditions of applied constant magnetic fields has received considerable attention, comparatively little attention has been given to the transient response of the magnetoviscosity to changes in the applied magnetic field or rate of shear deformation. Such transient response can provide further insight into the dynamics of ferrofluids and find practical application in the design of devices that take advantage of the magnetoviscous effect and inevitably must deal with changes in the applied magnetic field and deformation. In this contribution Brownian dynamics simulations and a simple model based on the ferrohydrodynamics equations are applied to explore the dependence of the transient magnetoviscosity for two cases: (I) a ferrofluid in a constant shear flow wherein the magnetic field is suddenly turned on, and (II) a ferrofluid in a constant magnetic field wherein the shear flow is suddenly started. Both simulations and analysis show that the transient approach to a steady state magnetoviscosity can be either monotonic or oscillatory depending on the relative magnitudes of the applied magnetic field and shear rate. - Research Highlights: →Rotational Brownian dynamics simulations were used to study the transient behavior of the magnetoviscosity of ferrofluids. →Damped and oscillatory approach to steady state magnetoviscosity was observed for step changes in shear rate and magnetic field. →A model based on the ferrohydrodynamics equations qualitatively captured the damped and oscillatory features of the transient response →The transient behavior is due to the interplay of hydrodynamic, magnetic, and Brownian torques on the suspended particles.
DEFF Research Database (Denmark)
Petersen, Kurt Erling
1986-01-01
Risk and reliability analysis is increasingly being used in evaluations of plant safety and plant reliability. The analysis can be performed either during the design process or during the operation time, with the purpose to improve the safety or the reliability. Due to plant complexity and safety...... and availability requirements, sophisticated tools, which are flexible and efficient, are needed. Such tools have been developed in the last 20 years and they have to be continuously refined to meet the growing requirements. Two different areas of application were analysed. In structural reliability probabilistic...... approaches have been introduced in some cases for the calculation of the reliability of structures or components. A new computer program has been developed based upon numerical integration in several variables. In systems reliability Monte Carlo simulation programs are used especially in analysis of very...
DETECTION OF FAST TRANSIENTS WITH RADIO INTERFEROMETRIC ARRAYS
International Nuclear Information System (INIS)
Bhat, N. D. R.; Chengalur, J. N.; Gupta, Y.; Prasad, J.; Roy, J.; Kudale, S. S.; Cox, P. J.; Bailes, M.; Burke-Spolaor, S.; Van Straten, W.
2013-01-01
Next-generation radio arrays, including the Square Kilometre Array (SKA) and its pathfinders, will open up new avenues for exciting transient science at radio wavelengths. Their innovative designs, comprising a large number of small elements, pose several challenges in digital processing and optimal observing strategies. The Giant Metre-wave Radio Telescope (GMRT) presents an excellent test-bed for developing and validating suitable observing modes and strategies for transient experiments with future arrays. Here we describe the first phase of the ongoing development of a transient detection system for GMRT that is planned to eventually function in a commensal mode with other observing programs. It capitalizes on the GMRT's interferometric and sub-array capabilities, and the versatility of a new software backend. We outline considerations in the plan and design of transient exploration programs with interferometric arrays, and describe a pilot survey that was undertaken to aid in the development of algorithms and associated analysis software. This survey was conducted at 325 and 610 MHz, and covered 360 deg 2 of the sky with short dwell times. It provides large volumes of real data that can be used to test the efficacies of various algorithms and observing strategies applicable for transient detection. We present examples that illustrate the methodologies of detecting short-duration transients, including the use of sub-arrays for higher resilience to spurious events of terrestrial origin, localization of candidate events via imaging, and the use of a phased array for improved signal detection and confirmation. In addition to demonstrating applications of interferometric arrays for fast transient exploration, our efforts mark important steps in the roadmap toward SKA-era science.
Detection of Fast Transients with Radio Interferometric Arrays
Bhat, N. D. R.; Chengalur, J. N.; Cox, P. J.; Gupta, Y.; Prasad, J.; Roy, J.; Bailes, M.; Burke-Spolaor, S.; Kudale, S. S.; van Straten, W.
2013-05-01
Next-generation radio arrays, including the Square Kilometre Array (SKA) and its pathfinders, will open up new avenues for exciting transient science at radio wavelengths. Their innovative designs, comprising a large number of small elements, pose several challenges in digital processing and optimal observing strategies. The Giant Metre-wave Radio Telescope (GMRT) presents an excellent test-bed for developing and validating suitable observing modes and strategies for transient experiments with future arrays. Here we describe the first phase of the ongoing development of a transient detection system for GMRT that is planned to eventually function in a commensal mode with other observing programs. It capitalizes on the GMRT's interferometric and sub-array capabilities, and the versatility of a new software backend. We outline considerations in the plan and design of transient exploration programs with interferometric arrays, and describe a pilot survey that was undertaken to aid in the development of algorithms and associated analysis software. This survey was conducted at 325 and 610 MHz, and covered 360 deg2 of the sky with short dwell times. It provides large volumes of real data that can be used to test the efficacies of various algorithms and observing strategies applicable for transient detection. We present examples that illustrate the methodologies of detecting short-duration transients, including the use of sub-arrays for higher resilience to spurious events of terrestrial origin, localization of candidate events via imaging, and the use of a phased array for improved signal detection and confirmation. In addition to demonstrating applications of interferometric arrays for fast transient exploration, our efforts mark important steps in the roadmap toward SKA-era science.
International Nuclear Information System (INIS)
Chvetsov, I.; Volkov, A.
2000-01-01
For advanced fast reactors (EFR, BN-600M, BN-1600, CEFR) the special complementary loop is envisaged in order to ensure the decay heat removal from the core in the case of LOF accidents. This complementary loop includes immersion coolers that are located in the hot reactor plenum. To analyze the transient process in the reactor when immersion coolers come into operation one needs to involve 3-D thermal hydraulics code. Furthermore sometimes the problem becomes more complicated due to necessity of simulation of the thermal hydraulics processes into the core interwrapper space. For example on BN-600M and CEFR reactors it is supposed to ensure the effective removal of decay heat from core subassemblies by specially arranged internal circulation circuit: 'inter-wrapper space'. For thermal hydraulics analysis of the transients in the core and in the whole reactor including hot plenum with immersion coolers and considering heat and mass exchange between the main sodium flow and sodium that moves in the inter-wrapper space the code GRIFIC (the version of GRIF code family) was developed in IPPE. GRIFIC code was tested on experimental data obtained on RAMONA rig under conditions simulating decay heat removal of a reactor with the use of immersion coolers. Comparison has been made of calculated and experimental result, such as integral characteristics (flow rate through the core and water temperature at the core inlet and outlet) and the local temperatures (at thermocouple location) as well. In order to show the capabilities of the code some results of the transient analysis of heat removal from the core of BN-600M - type reactor under loss-of-flow accident are presented. (author)
RELAP5/MOD2: for PWR transient analysis
International Nuclear Information System (INIS)
Ransom, V.H.
1983-01-01
RELAP5 is a light water reactor system transient simulation code for use in nuclear plant safety analysis. Development of a new version, RELAP5/MOD2, has been completed and will be released to the United States Nuclear Regulatory Commission during September of 1983. The new and improved modeling capability of RELAP5/MOD2 is described and some developmental assessment results are presented. The future plans for extension to severe accident modeling are briefly discussed
Oxide fuel pin transient performance analysis and design with the TEMECH code
International Nuclear Information System (INIS)
Bard, F.E.; Dutt, S.P.; Hinman, C.A.; Hunter, C.W.; Pitner, A.L.
1986-01-01
The TEMECH code is a fast-running, thermal-mechanical-hydraulic, analytical program used to evaluate the transient performance of LMR oxide fuel pins. The code calculates pin deformation and failure probability due to fuel-cladding differential thermal expansion, expansion of fuel upon melting, and fission gas pressurization. The mechanistic fuel model in the code accounts for fuel cracking, crack closure, porosity decrease, and the temperature dependence of fuel creep through the course of the transient. Modeling emphasis has been placed on results obtained from Fuel Cladding Transient Test (FCTT) testing, Transient Fuel Deformation (TFD) tests and TREAT integral fuel pin experiments
Pressure transients across HEPA filters
International Nuclear Information System (INIS)
Gregory, W.; Reynolds, G.; Ricketts, C.; Smith, P.R.
1977-01-01
Nuclear fuel cycle facilities require ventilation for health and safety reasons. High efficiency particulate air (HEPA) filters are located within ventilation systems to trap radioactive dust released in reprocessing and fabrication operations. Pressure transients within the air cleaning systems may be such that the effectiveness of the filtration system is questioned under certain accident conditions. These pressure transients can result from both natural and man-caused phenomena: atmospheric pressure drop caused by a tornado or explosions and nuclear excursions initiate pressure pulses that could create undesirable conditions across HEPA filters. Tornado depressurization is a relatively slow transient as compared to pressure pulses that result from combustible hydrogen-air mixtures. Experimental investigation of these pressure transients across air cleaning equipment has been undertaken by Los Alamos Scientific Laboratory and New Mexico State University. An experimental apparatus has been constructed to impose pressure pulses across HEPA filters. The experimental equipment is described as well as preliminary results using variable pressurization rates. Two modes of filtration of an aerosol injected upstream of the filter is examined. A laser instrumentation for measuring the aerosol release, during the transient, is described
Wide Field Radio Transient Surveys
Bower, Geoffrey
2011-04-01
The time domain of the radio wavelength sky has been only sparsely explored. Nevertheless, serendipitous discovery and results from limited surveys indicate that there is much to be found on timescales from nanoseconds to years and at wavelengths from meters to millimeters. These observations have revealed unexpected phenomena such as rotating radio transients and coherent pulses from brown dwarfs. Additionally, archival studies have revealed an unknown class of radio transients without radio, optical, or high-energy hosts. The new generation of centimeter-wave radio telescopes such as the Allen Telescope Array (ATA) will exploit wide fields of view and flexible digital signal processing to systematically explore radio transient parameter space, as well as lay the scientific and technical foundation for the Square Kilometer Array. Known unknowns that will be the target of future transient surveys include orphan gamma-ray burst afterglows, radio supernovae, tidally-disrupted stars, flare stars, and magnetars. While probing the variable sky, these surveys will also provide unprecedented information on the static radio sky. I will present results from three large ATA surveys (the Fly's Eye survey, the ATA Twenty CM Survey (ATATS), and the Pi GHz Survey (PiGSS)) and several small ATA transient searches. Finally, I will discuss the landscape and opportunities for future instruments at centimeter wavelengths.
Chernobyl reactor transient simulation study
International Nuclear Information System (INIS)
Gaber, F.A.; El Messiry, A.M.
1988-01-01
This paper deals with the Chernobyl nuclear power station transient simulation study. The Chernobyl (RBMK) reactor is a graphite moderated pressure tube type reactor. It is cooled by circulating light water that boils in the upper parts of vertical pressure tubes to produce steam. At equilibrium fuel irradiation, the RBMK reactor has a positive void reactivity coefficient. However, the fuel temperature coefficient is negative and the net effect of a power change depends upon the power level. Under normal operating conditions the net effect (power coefficient) is negative at full power and becomes positive under certain transient conditions. A series of dynamic performance transient analysis for RBMK reactor, pressurized water reactor (PWR) and fast breeder reactor (FBR) have been performed using digital simulator codes, the purpose of this transient study is to show that an accident of Chernobyl's severity does not occur in PWR or FBR nuclear power reactors. This appears from the study of the inherent, stability of RBMK, PWR and FBR under certain transient conditions. This inherent stability is related to the effect of the feed back reactivity. The power distribution stability in the graphite RBMK reactor is difficult to maintain throughout its entire life, so the reactor has an inherent instability. PWR has larger negative temperature coefficient of reactivity, therefore, the PWR by itself has a large amount of natural stability, so PWR is inherently safe. FBR has positive sodium expansion coefficient, therefore it has insufficient stability it has been concluded that PWR has safe operation than FBR and RBMK reactors
Exploring transient X-ray sky with Einstein Probe
Yuan, W.; Zhang, C.; Ling, Z.; Zhao, D.; Chen, Y.; Lu, F.; Zhang, S.
2017-10-01
The Einstein Probe is a small satellite in time-domain astronomy to monitor the soft X-ray sky. It is a small mission in the space science programme of the Chinese Academy of Sciences. It will carry out systematic survey and characterisation of high-energy transients at unprecedented sensitivity, spatial resolution, Grasp and monitoring cadence. Its wide-field imaging capability is achieved by using established technology of micro-pore lobster-eye X-ray focusing optics. Complementary to this is X-ray follow-up capability enabled by a narrow-field X-ray telescope. It is capable of on-board triggering and real time downlink of transient alerts, in order to trigger fast follow-up observations at multi-wavelengths. Its scientific goals are concerned with discovering and characterising diverse types of X-ray transients, including tidal disruption events, supernova shock breakouts, high-redshift GRBs, and of particular interest, X-ray counterparts of gravitational wave events.
Simulation of LOFT anticipated-transient experiments L6-1, L6-2, and L6-3 using TRAC-PF1/MOD1
International Nuclear Information System (INIS)
Sahota, M.S.
1984-01-01
Anticipated-transient experiments L6-1, L6-2, and L6-3, performed at the Loss-of-fluid Test (LOFT) facility, are analyzed using the latest released version of the Transient Reactor Analysis Code (TRAC-PF1/MOD1). The results are used to assess TRAC-PF1/MOD1 trip and control capabilities, and predictions of thermal-hydraulic phenomena during slow transients. Test L6-1 simulated a loss-of-stream load in a large pressurized-water reactor (PWR), and was initiated by closing the main steam-flow control valve (MSFCV) at its maximum rate, which reduced the heat removal from the secondary-coolant system and increased the primary-coolant system pressure that initiated a reactor scram. Test L6-2 simulated a loss-of-primary coolant flow in a large PWR, and was initiated by tripping the power to the primary-coolant pumps (PCPs) allowing the pumps to coast down. The reduced primary-coolant flow caused a reactor scram. Test L6-3 simulated an excessive-load increase incident in a large PWR, and was initiated by opening the MSFCV at its maximum rate, which increased the heat removal from the secondary-coolant system and decreased the primary-coolant system pressure that initiated a reactor scram. The TRAC calculations accurately predict most test events. The test data and the calculated results for most parameters of interest also agree well
Technological Dynamics and Social Capability
DEFF Research Database (Denmark)
Fagerberg, Jan; Feldman, Maryann; Srholec, Martin
2014-01-01
for the sample as a whole between 1998 and 2008. The results indicate that social capabilities, such as well-developed public knowledge infrastructure, an egalitarian distribution of income, a participatory democracy and prevalence of public safety condition the growth of technological capabilities. Possible...
A business analytics capability framework
Directory of Open Access Journals (Sweden)
Ranko Cosic
2015-09-01
Full Text Available Business analytics (BA capabilities can potentially provide value and lead to better organisational performance. This paper develops a holistic, theoretically-grounded and practically relevant business analytics capability framework (BACF that specifies, defines and ranks the capabilities that constitute an organisational BA initiative. The BACF was developed in two phases. First, an a priori conceptual framework was developed based on the Resource-Based View theory of the firm and a thematic content analysis of the BA literature. Second, the conceptual framework was further developed and refined using a three round Delphi study involving 16 BA experts. Changes from the Delphi study resulted in a refined and confirmed framework including detailed capability definitions, together with a ranking of the capabilities based on importance. The BACF will help academic researchers and industry practitioners to better understand the capabilities that constitute an organisational BA initiative and their relative importance. In future work, the capabilities in the BACF will be operationalised to measure their as-is status, thus enabling organisations to identify key areas of strength and weakness and prioritise future capability improvement efforts.
Identifying 21st Century Capabilities
Stevens, Robert
2012-01-01
What are the capabilities necessary to meet 21st century challenges? Much of the literature on 21st century skills focuses on skills necessary to meet those challenges associated with future work in a globalised world. The result is a limited characterisation of those capabilities necessary to address 21st century social, health and particularly…
Modelling transient energy release from molten fuel coolant interaction debris
International Nuclear Information System (INIS)
Fletcher, D.F.
1984-05-01
A simple model of transient energy release in a Molten Fuel Coolant Interaction is presented. A distributed heat transfer model is used to examine the effect of heat transfer coefficient, time available for rapid energy heat transfer and particle size on transient energy release. The debris is assumed to have an Upper Limit Lognormal distribution. Model predictions are compared with results from the SUW series of experiments which used thermite-generated uranium dioxide molybdenum melts released below the surface of a pool of water. Uncertainties in the physical principles involved in the calculation of energy transfer rates are discussed. (author)
An investigation of loads generated by temperature transients in pipes
International Nuclear Information System (INIS)
Maneschy, C.E.
1988-12-01
An analysis is presented of the effect of a transient temperature on the stress distribution due to a fluid flowing through a pipe, is analytically determined using the definition of a variable called in this paper as ''shifted time''. This variable, which is related to the axial coordinate, the average fluid velocity and the real time, is defined to make the transient thermal problem one-dimensional. The stresses are then calculated from the temperature solution using the linear theory of viscoelasticity. (author) [pt
Developing Collaborative Product Development Capabilities
DEFF Research Database (Denmark)
Mahnke, Volker; Tran, Yen
2012-01-01
innovation strategies’. Our analyses suggest that developing such collaboration capabilities benefits from the search for complementary practices, the combination of learning styles, and the development of weak and strong ties. Results also underscore the crucial importance of co-evolution of multi......Collaborative product development capabilities support a company’s product innovation activities. In the context of the fast fashion sector, this paper examines the development of the product development capabilities (PDC) that align product development capabilities in a dual innovation context......, one, slow paced, where the firm is well established and the other, fast paced, which represents a new competitive arena in which the company competes. To understand the process associated with collaborative capability development, we studied three Scandinavian fashion companies pursuing ‘dual...
Marketing Capability in Strategy Research
DEFF Research Database (Denmark)
Ritter, Thomas; Distel, Andreas Philipp
Following the call for a demand-side perspective of strategic management (e.g., Priem et al., 2012), a firm’s marketing capability, i.e. its ability to interact with down-stream stakeholders, becomes a pivotal element in explaining a firm’s competitiveness. While marketing capability is recognized...... in the strategic management literature as an important driver of firm performance, our review of 86 articles reveals a lack of a generally accepted definition of marketing capability, a lack of a common conceptualization as well as differences in the measurement of marketing capability. In order to build a common...... ground for advancing marketing capability research and thus supporting the demand-side perspective in strategic management, we develop an integrative framework to explain the differences and propose a research agenda for developing the field....
HEDL experimental transient overpower program
International Nuclear Information System (INIS)
Hikido, T.; Culley, G.E.
1976-01-01
HEDL is conducting a series of experiments to evaluate the performance of Fast Flux Test Facility (FFTF) prototypic fuel pins up to the point of cladding breach. A primary objective of the program is to demonstrate the adequacy of fuel pin and Plant Protective System (PPS) designs for terminated transients. Transient tests of prototypic FFTF fuel pins previously irradiated in the Experimental Breeder Reactor-II (EBR-II) have demonstrated the adequacy of the PPS and fuel pin designs and indicate that a very substantial margin exists between PPS-terminated transients and that required to produce fuel pin cladding failure. Additional experiments are planned to extend the data base to high burnup, high fluence fuel pin specimens
Transient analysis of DTT rakes
International Nuclear Information System (INIS)
Kamath, P.S.; Lahey, R.T. Jr.
1981-01-01
This paper presents an analytical model for the determination of the cross-sectionally averaged transient mass flux of a two-phase fluid flowing in a conduit instrumented by a Drag-Disk Turbine Transducer (DTT) Rake and a multibeam gamma densitometer. Parametric studies indicate that for a typical blowdown transient, dynamic effects such as rotor inertia can be important for the turbine-meter. In contrast, for the drag-disk, a frequency response analysis showed that the quasisteady solution is valid below a forcing frequency of about 10 Hz, which is faster than the time scale normally encountered during blowdowns. The model showed reasonably good agreement with full scale transient rake data, where the flow regimes were mostly homogeneous or stratified, thus indicating that the model is suitable for the analysis of a DTT rake. (orig.)
Capabilities and Incapabilities of the Capabilities Approach to Health Justice.
Selgelid, Michael J
2016-01-01
This first part of this article critiques Sridhar Venkatapuram's conception of health as a capability. It argues that Venkatapuram relies on the problematic concept of dignity, implies that those who are unhealthy lack lives worthy of dignity (which seems politically incorrect), sets a low bar for health, appeals to metaphysically problematic thresholds, fails to draw clear connections between appealed-to capabilities and health, and downplays the importance/relevance of health functioning. It concludes by questioning whether justice entitlements should pertain to the capability for health versus health achievements, challenging Venkatapuram's claims about the strength of health entitlements, and demonstrating that the capabilities approach is unnecessary to address social determinants of health. © 2016 John Wiley & Sons Ltd.
Analysis and study on core power capability with margin method
International Nuclear Information System (INIS)
Liu Tongxian; Wu Lei; Yu Yingrui; Zhou Jinman
2015-01-01
Core power capability analysis focuses on the power distribution control of reactor within the given mode of operation, for the purpose of defining the allowed normal operating space so that Condition Ⅰ maneuvering flexibility is maintained and Condition Ⅱ occurrences are adequately protected by the reactor protection system. For the traditional core power capability analysis methods, such as synthesis method or advanced three dimension method, usually calculate the key safety parameters of the power distribution, and then verify that these parameters meet the design criteria. For PWR with on-line power distribution monitoring system, core power capability analysis calculates the most power level which just meets the design criteria. On the base of 3D FAC method of Westinghouse, the calculation model of core power capability analysis with margin method is introduced to provide reference for engineers. The core power capability analysis of specific burnup of Sanmen NPP is performed with the margin method. The results demonstrate the rationality of the margin method. The calculation model of the margin method not only helps engineers to master the core power capability analysis for AP1000, but also provides reference for engineers for core power capability analysis of other PWR with on-line power distribution monitoring system. (authors)
DEFF Research Database (Denmark)
Li, H.; Zhao, B.; Yang, C.
2011-01-01
based on normal form theory is proposed. The transient models of the wind turbine generation system including the flexible drive train model are derived based on the direct transient stability estimation method. A method of critical clearing time (CCT) calculation is developed for the transient......Increasing levels of wind energy in modern electrical power system is initiating a need for accurate analysis and estimation of transient stability of wind turbine generation systems. This paper investigates the transient behaviors and possible direct methods for transient stability evaluation...... of a grid-connected wind turbine with squirrel cage induction generator (SCIG). Firstly, by using an equivalent lump mass method, a three-mass wind turbine equivalent model is proposed considering both the blades and the shaft flexibility of the wind turbine drive train system. Combined with the detailed...
Transient analysis of multicavity klystrons
International Nuclear Information System (INIS)
Lavine, T.L.; Miller, R.H.; Morton, P.L.; Ruth, R.D.
1988-09-01
We describe a model for analytic analysis of transients in multicavity klystron output power and phase. Cavities are modeled as resonant circuits, while bunching of the beam is modeled using linear space-charge wave theory. Our analysis has been implemented in a computer program which we use in designing multicavity klystrons with stable output power and phase. We present as examples transient analysis of a relativistic klystron using a magnetic pulse compression modulator, and of a conventional klystron designed to use phase shifting techniques for RF pulse compression. 4 refs., 4 figs
Transient formation of forbidden lines
International Nuclear Information System (INIS)
Rosmej, F.B.; Rosmej, O.N.
1996-01-01
An explanation of anomalously long time scales in the transient formation of forbidden lines is proposed. The concept is based on a collisionally induced density dependence of the relaxation times of metastable level populations in transient plasma. Generalization leads to an incorporation of diffusion phenomena. We demonstrate this new concept for the simplest atomic system: the He-like isoelectronic sequence. A new interpretation of the observed long duration and anomalously high intensity of spin-forbidden emission in hot plasmas is given. (author)
Transient formation of forbidden lines
Energy Technology Data Exchange (ETDEWEB)
Rosmej, F.B. [Bochum Univ., Ruhr (Germany). Inst. fuer Experimentalphysik V; Rosmej, O.N. [VNIIFTRI, Moscow Region (Russian Federation). MISDC
1996-05-14
An explanation of anomalously long time scales in the transient formation of forbidden lines is proposed. The concept is based on a collisionally induced density dependence of the relaxation times of metastable level populations in transient plasma. Generalization leads to an incorporation of diffusion phenomena. We demonstrate this new concept for the simplest atomic system: the He-like isoelectronic sequence. A new interpretation of the observed long duration and anomalously high intensity of spin-forbidden emission in hot plasmas is given. (author).
A Design Method for Graded Insulation of Transformers by Transient Electric Field Intensity Analysis
Yamashita, Hideo; Cingoski, Vlatko; Namera, Akihiro; Nakamae, Eihachiro; Kitamura, Hideo
2000-01-01
In this paper, a calculation method for transient electric field distribution inside a transformer impressed with voltage is proposed: The concentrated electric network for the transformer is constructed by dividing transformer windings into several blocks, and the transient voltage and electric field intensity distributions inside the transformer are calculated by using the axisymmetrical finite element method. Moreover, an animated display of the distributions is realized: The visualization...
Energy Technology Data Exchange (ETDEWEB)
Vazquez, M.; Martin-Fuertes, F.
2013-07-01
As a complement to the attached code 3D neutron-CIEMAT thermohydraulic added a module to simulate transient. Temporary kinetics is resolved by factoring flow in a spatial part and another storm. MCNP provides the reactivity and updated spatial function and COBRA-IV calculates the temperature distribution. Temporary dependence of amplitude is calculated using time delayed neutron Kinetic equations. As an example of application, examines a transient loss of flow in MYRRHA, a lead-cooled experimental reactor.
Shielding calculations for NET
International Nuclear Information System (INIS)
Verschuur, K.A.; Hogenbirk, A.
1991-05-01
In the European Fusion Technology Programme there is only a small activity on research and development for fusion neutronics. Never-the-less, looking further than blanket design now, as ECN is getting involved in design of radiation shields for the coils and biological shields, it becomes apparent that fusion neutronics as a whole still needs substantial development. Existing exact codes for calculation of complex geometries like MCNP and DORT/TORT are put over the limits of their numerical capabilities, whilst approximate codes for complex geometries like FURNACE and MERCURE4 are put over the limits of their modelling capabilities. The main objective of this study is just to find out how far we can get with existing codes in obtaining reliable values for the radiation levels inside and outside the cryostat/shield during operation and after shut-down. Starting with a 1D torus model for preliminary parametric studies, more dimensional approximation of the torus or parts of it including the main heterogeneities should follow. Regular contacts with the NET-Team are kept, to be aware of main changes in NET design that might affect our calculation models. Work on the contract started 1 July 1990. The technical description of the contract is given. (author). 14 refs.; 4 figs.; 1 tab
A coupled RELAPS-3D/CFD methodology with a proof-of-principle calculation; TOPICAL
International Nuclear Information System (INIS)
Aumiller, D.L.; Tomlinson, E.T.; Bauer, R.C.
2000-01-01
The RELAP5-3D computer code was modified to make the explicit coupling capability in the code fully functional. As a test of the modified code, a coupled RELAP5/RELAP5 analysis of the Edwards-O'Brien blowdown problem was performed which showed no significant deviations from the standard RELAP5-3D predictions. In addition, a multiphase Computational Fluid Dynamics (CFD) code was modified to permit explicit coupling to RELAP5-3D. Several calculations were performed with this code. The first analysis used the experimental pressure history from a point just upstream of the break as a boundary condition. This analysis showed that a multiphase CFD code could calculate the thermodynamic and hydrodynamic conditions during a rapid blowdown transient. Finally, a coupled RELAP5/CFD analysis was performed. The results are presented in this paper
Transient redistribution of intragranular fission gas in irradiated mixed oxide
International Nuclear Information System (INIS)
Hinman, C.A.; Randklev, E.H.
1981-01-01
Safety analyses for an LMFBR require a knowledge of the fuel and fission gas behavior under transient conditions. Analyses of microstructural data derived from transiently heated, irradiated, mixed oxide fuel specimens have allowed the calculation of the degree of nonequilibrium of intragranular bubbles formed during the transient. It is hypothesized that the observed over-pressurization of the intragranular bubbles mechanically loads the fuel within the grain, leading to a stress gradient derived force upon near-grain-surface bubbles, driving them preferentially to the grain boundaries. Using existing models for forced diffusion it can be estimated that the stress derived forces on bubbles are within the same magnitude, and possibly greater, than the forces derived from the thermal gradient
Transient two-phase performance of LOFT reactor coolant pumps
International Nuclear Information System (INIS)
Chen, T.H.; Modro, S.M.
1983-01-01
Performance characteristics of Loss-of-Fluid Test (LOFT) reactor coolant pumps under transient two-phase flow conditions were obtained based on the analysis of two large and small break loss-of-coolant experiments conducted at the LOFT facility. Emphasis is placed on the evaluation of the transient two-phase flow effects on the LOFT reactor coolant pump performance during the first quadrant operation. The measured pump characteristics are presented as functions of pump void fraction which was determined based on the measured density. The calculated pump characteristics such as pump head, torque (or hydraulic torque), and efficiency are also determined as functions of pump void fractions. The importance of accurate modeling of the reactor coolant pump performance under two-phase conditions is addressed. The analytical pump model, currently used in most reactor analysis codes to predict transient two-phase pump behavior, is assessed
Cernavoda unit2 recirculated cooling water system transient analysis
International Nuclear Information System (INIS)
Nita, I. P.; Pancef, R.
2015-01-01
The paper is an approach to calculate the response of Cernavoda NPP Unit 2 RCW System to transient regimes during normal and abnormal regimes. Then one started to analyse the system response to reactor trip on class III and IV of power, LOCA on class IV of power, LOCA on class III power, LOIA on class IV of power, and LOIA on class III power. Moreover, one analysed the system transient due to requirement of changeover of a RCW operating pump, planned and unplanned changeover. This is the first transient approach to this system that took in consideration all building of the system, obtaining a very large system model, with over 900 pipe, 4 pumps, 50 consumers, 21 control valves. The changeover procedure was required to be analysed in order to change the nominal operating mode for Unit 2, from current 2 pumps in operation to 3 pump operations during summer operating mode. (authors)
Transient and stationary eddies in differing GCM climates
International Nuclear Information System (INIS)
Hall, N.M.J.; Valdes, P.J.
1994-01-01
The response of transients to changing forcing/boundary conditions can be just as striking as the response of mean fields such as surface temperature. Indeed the two are intimately linked and the extent to which the transients are either controlled by, or shape the mean flow is difficult to quantify. Diagnostics are presented from several GCM equilibrium climate simulations using the UGAMP GCM. These include representations of the present climate: The Last Glacial Maximum and the Jurassic climate (150 M years ago). Changes in the distribution of transient eddy activity are compared with changes in low level baroclinicity to assess the direct response of the storm tracks to local conditions. Budget calculations are also presented to identify the changing roles of different components of the atmospheric circulation in transporting heat and moisture from equator to pole
Loss-of-feedwater transients in PWRs
International Nuclear Information System (INIS)
Burns, R.D. III.
1980-01-01
Recent severe accident sequence analysis (SASA) work in LASL's Multifault Accident Analysis Section has focused on loss-of-feedwater (LOFW) transients at a 4-loop Westinghouse nuclear power reactor. In all transients studied, the initiator was loss of main feedwater and reactor coolant pump (RCP) trip, caused by temporary loss of off-site power. Subsequent automatic actions included reactor scram, closure of the main steam isolation valves, and initiation of auxiliary feedwater (AFW) flow. TRAC-PD2 calculations were designed to study the consequences of AFW delivery rates below the minimum specified in the emergency operating procedures (EOPs) for the reference 4-loop plant. Six types of LOFW scenarios have been studied, including (1) zero AFW availability (nominal case), (2) initially zero AFW but full recovery after 2 h, (3) zero AFW with steam generator (SG) atmospheric relief valve (ARV) malfunction, (4) zero AFW with high pressure charging flow initiated after 2 h, and (5) zero AFW with delay in reactor scram. Additional cases were considered to study the effects of uncertainties in pressurizer heater/spray operation, operator manual initiation of high pressure charging flow, reactor initial conditions, and RCP and power coastdown characteristics. Nominal case results, rationale for selections of other cases, and lessons learned are summarized
The modelling of BLEVE fireball transients
Energy Technology Data Exchange (ETDEWEB)
Shield, S.R. [Shell Research Ltd., Chester (United Kingdom). Thornton Research Centre
1995-12-31
An existing physically based BLEVE fireball model has been developed to predict the shape of the transient heat pulse to a receiver, to model ``cold`` BLEVEs, and to assess the consequences to structures and people. This has been achieved by finding a correlation to predict the size of a characteristic liquid drop within the flashing cloud. These drops burn out to predict the time to fireball break-up and extinction, and their height is tracked to find the rise of the fireball, agreement with small and large scale data being satisfactory. The model is semi-empirical in that, when the level of pre-heating is low, a heat balance cannot predict the development of fireball temperature with time since the fuel is pyrolising. Also, the modelling of the transition from ``cold`` BLEVE fireball to pool fire is a cautious best estimate. Using both traditional and more recent models, the prediction of pain, burns and fatality have been incorporated into the model. Whatever criterion for a safety distance is used, the effect of modelling the transient is to reduce the calculated safety distances by up to a factor of two, which brings fatality predictions for real incidents much more in line with the historical record. (author)
Short-term depression and transient memory in sensory cortex.
Gillary, Grant; Heydt, Rüdiger von der; Niebur, Ernst
2017-12-01
Persistent neuronal activity is usually studied in the context of short-term memory localized in central cortical areas. Recent studies show that early sensory areas also can have persistent representations of stimuli which emerge quickly (over tens of milliseconds) and decay slowly (over seconds). Traditional positive feedback models cannot explain sensory persistence for at least two reasons: (i) They show attractor dynamics, with transient perturbations resulting in a quasi-permanent change of system state, whereas sensory systems return to the original state after a transient. (ii) As we show, those positive feedback models which decay to baseline lose their persistence when their recurrent connections are subject to short-term depression, a common property of excitatory connections in early sensory areas. Dual time constant network behavior has also been implemented by nonlinear afferents producing a large transient input followed by much smaller steady state input. We show that such networks require unphysiologically large onset transients to produce the rise and decay observed in sensory areas. Our study explores how memory and persistence can be implemented in another model class, derivative feedback networks. We show that these networks can operate with two vastly different time courses, changing their state quickly when new information is coming in but retaining it for a long time, and that these capabilities are robust to short-term depression. Specifically, derivative feedback networks with short-term depression that acts differentially on positive and negative feedback projections are capable of dynamically changing their time constant, thus allowing fast onset and slow decay of responses without requiring unrealistically large input transients.
TACT1- TRANSIENT THERMAL ANALYSIS OF A COOLED TURBINE BLADE OR VANE EQUIPPED WITH A COOLANT INSERT
Gaugler, R. E.
1994-01-01
As turbine-engine core operating conditions become more severe, designers must develop more effective means of cooling blades and vanes. In order to design reliable, cooled turbine blades, advanced transient thermal calculation techniques are required. The TACT1 computer program was developed to perform transient and steady-state heat-transfer and coolant-flow analyses for cooled blades, given the outside hot-gas boundary condition, the coolant inlet conditions, the geometry of the blade shell, and the cooling configuration. TACT1 can analyze turbine blades, or vanes, equipped with a central coolant-plenum insert from which coolant-air impinges on the inner surface of the blade shell. Coolant-side heat-transfer coefficients are calculated with the heat transfer mode at each station being user specified as either impingement with crossflow, forced convection channel flow, or forced convection over pin fins. A limited capability to handle film cooling is also available in the program. The TACT1 program solves for the blade temperature distribution using a transient energy equation for each node. The nodal energy balances are linearized, one-dimensional, heat-conduction equations which are applied at the wall-outer-surface node, at the junction of the cladding and the metal node, and at the wall-inner-surface node. At the mid-metal node a linear, three-dimensional, heat-conduction equation is used. Similarly, the coolant pressure distribution is determined by solving the set of transfer momentum equations for the one-dimensional flow between adjacent fluid nodes. In the coolant channel, energy and momentum equations for one-dimensional compressible flow, including friction and heat transfer, are used for the elemental channel length between two coolant nodes. The TACT1 program first obtains a steady-state solution using iterative calculations to obtain convergence of stable temperatures, pressures, coolant-flow split, and overall coolant mass balance. Transient
Indigenous Technological Innovation : Capability and ...
International Development Research Centre (IDRC) Digital Library (Canada)
Indigenous Technological Innovation : Capability and Competitiveness in China's ... IDRC and key partners will showcase critical work on adaptation and ... Call for new OWSD Fellowships for Early Career Women Scientists now open.
LMFBR system-wide transient analysis: the state of the art and US validation needs
International Nuclear Information System (INIS)
Khatib-Rahbar, M.; Guppy, J.G.; Cerbone, R.J.
1982-01-01
This paper summarizes the computational capabilities in the area of liquid metal fast breeder reactor (LMFBR) system-wide transient analysis in the United States, identifies various numerical and physical approximations, the degree of empiricism, range of applicability, model verification and experimental needs for a wide class of protected transients, in particular, natural circulation shutdown heat removal for both loop- and pool-type plants
A simple dynamic model and transient simulation of the nuclear power reactor on microcomputers
Energy Technology Data Exchange (ETDEWEB)
Han, Yang Gee; Park, Cheol [Korea Atomic Energy Research Institute, Taejon (Korea, Republic of)
1997-12-31
A simple dynamic model is developed for the transient simulation of the nuclear power reactor. The dynamic model includes the normalized neutron kinetics model with reactivity feedback effects and the core thermal-hydraulics model. The main objective of this paper demonstrates the capability of the developed dynamic model to simulate various important variables of interest for a nuclear power reactor transient. Some representative results of transient simulations show the expected trends in all cases, even though no available data for comparison. In this work transient simulations are performed on a microcomputer using the DESIRE/N96T continuous system simulation language which is applicable to nuclear power reactor transient analysis. 3 refs., 9 figs. (Author)
A simple dynamic model and transient simulation of the nuclear power reactor on microcomputers
Energy Technology Data Exchange (ETDEWEB)
Han, Yang Gee; Park, Cheol [Korea Atomic Energy Research Institute, Taejon (Korea, Republic of)
1998-12-31
A simple dynamic model is developed for the transient simulation of the nuclear power reactor. The dynamic model includes the normalized neutron kinetics model with reactivity feedback effects and the core thermal-hydraulics model. The main objective of this paper demonstrates the capability of the developed dynamic model to simulate various important variables of interest for a nuclear power reactor transient. Some representative results of transient simulations show the expected trends in all cases, even though no available data for comparison. In this work transient simulations are performed on a microcomputer using the DESIRE/N96T continuous system simulation language which is applicable to nuclear power reactor transient analysis. 3 refs., 9 figs. (Author)
Transient attenuation in optical fibers
International Nuclear Information System (INIS)
Hopkins, A.A.; Kelly, R.E.; Looney, L.D.; Lyons, P.B.
1984-01-01
Low and high energy pulsed electron beams were used to generate radiation-induced transient attenuation in high-OH, Suprasil core, PCS fibers, demonstrating the energy dependence of the radiation damage and recovery mechanisms. A radiation resistant low-OH fiber was studied and its performance contrasted to that of high-OH materials. Several fibers with differing core compositions were also studied
Charging transient in polyvinyl formal
Indian Academy of Sciences (India)
Unknown
401–406. © Indian Academy of Sciences. 401. Charging transient in polyvinyl formal. P K KHARE*, P L JAIN† and R K PANDEY‡. Department of Postgraduate Studies & Research in Physics & Electronics, Rani Durgavati University,. Jabalpur 482 001, India. †Department of Physics, Government PG College, Damoh 470 ...
Transient filament stretching rheometer II
DEFF Research Database (Denmark)
Kolte, Mette Irene; Rasmussen, Henrik K.; Hassager, Ole
1997-01-01
The Lagrangian sspecification is used to simulate the transient stretching filament rheometer. Simulations are performed for dilute PIB-solutions modeled as a four mode Oldroyd-B fluid and a semidilute PIB-solution modeled as a non-linear single integral equation. The simulations are compared...
Fuel rod behaviour during transients
International Nuclear Information System (INIS)
Hughes, H.; Haste, T.J.; Cameron, R.F.; Sinclair, J.E.
1982-04-01
The fuel pin performance code SLEUTH, the transient codes FRAP-T5 and TRAFIC and the clad deformation code CANSWEL-2 are described. It is shown how the codes treat gas release, pin cooling, cladding deformation and interaction, gap conductance etc. The materials properties used are indicated. (author)
Simulation Model of a Transient
DEFF Research Database (Denmark)
Jauch, Clemens; Sørensen, Poul; Bak-Jensen, Birgitte
2005-01-01
This paper describes the simulation model of a controller that enables an active-stall wind turbine to ride through transient faults. The simulated wind turbine is connected to a simple model of a power system. Certain fault scenarios are specified and the turbine shall be able to sustain operati...
Stationary and Transient Response Statistics
DEFF Research Database (Denmark)
Madsen, Peter Hauge; Krenk, Steen
1982-01-01
The covariance functions for the transient response of a linear MDOF-system due to stationary time limited excitation with an arbitrary frequency content are related directly to the covariance functions of the stationary response. For rational spectral density functions closed form expressions fo...
Earth Science Capability Demonstration Project
Cobleigh, Brent
2006-01-01
A viewgraph presentation reviewing the Earth Science Capability Demonstration Project is shown. The contents include: 1) ESCD Project; 2) Available Flight Assets; 3) Ikhana Procurement; 4) GCS Layout; 5) Baseline Predator B Architecture; 6) Ikhana Architecture; 7) UAV Capability Assessment; 8) The Big Picture; 9) NASA/NOAA UAV Demo (5/05 to 9/05); 10) NASA/USFS Western States Fire Mission (8/06); and 11) Suborbital Telepresence.
Core power capability verification for PWR NPP
International Nuclear Information System (INIS)
Xian Chunyu; Liu Changwen; Zhang Hong; Liang Wei
2002-01-01
The Principle and methodology of pressurized water reactor nuclear power plant core power capability verification for reload are introduced. The radial and axial power distributions of normal operation (category I or condition I) and abnormal operation (category II or condition II) are simulated by using neutronics calculation code. The linear power density margin and DNBR margin for both categories, which reflect core safety, are analyzed from the point view of reactor physics and T/H, and thus category I operating domain and category II protection set point are verified. Besides, the verification results of reference NPP are also given
Analysis of piping response to thermal and operational transients
International Nuclear Information System (INIS)
Wang, C.Y.
1987-01-01
The reactor piping system is an extremely complex three-dimensional structure. Maintaining its structural integrity is essential to the safe operation of the reactor and the steam-supply system. In the safety analysis, various transient loads can be imposed on the piping which may cause plastic deformation and possible damage to the system, including those generated from hydrodynamic wave propagations, thermal and operational transients, as well as the seismic events. At Argonne National Laboratory (ANL), a three-dimensional (3-D) piping code, SHAPS, aimed for short-duration transients due to wave propagation, has been developed. Since 1984, the development work has been shifted to the long-duration accidents originating from the thermal and operational transient. As a result, a new version of the code, SHAPS-2, is being established. This paper describes many features related to this later development. To analyze piping response generated from thermal and operational transients, a 3-D implicit finite element algorithm has been developed for calculating the hoop, flexural, axial, and torsional deformations induced by the thermomechanical loads. The analysis appropriately accounts for stresses arising from the temperature dependence of the elastic material properties, the thermal expansion of the materials, and the changes in the temperature-dependent yield surface. Thermal softening, failure, strain rate, creep, and stress ratching can also be considered
AITRAC: Augmented Interactive Transient Radiation Analysis by Computer. User's information manual
International Nuclear Information System (INIS)
1977-10-01
AITRAC is a program designed for on-line, interactive, DC, and transient analysis of electronic circuits. The program solves linear and nonlinear simultaneous equations which characterize the mathematical models used to predict circuit response. The program features 100 external node--200 branch capability; conversional, free-format input language; built-in junction, FET, MOS, and switch models; sparse matrix algorithm with extended-precision H matrix and T vector calculations, for fast and accurate execution; linear transconductances: beta, GM, MU, ZM; accurate and fast radiation effects analysis; special interface for user-defined equations; selective control of multiple outputs; graphical outputs in wide and narrow formats; and on-line parameter modification capability. The user describes the problem by entering the circuit topology and part parameters. The program then automatically generates and solves the circuit equations, providing the user with printed or plotted output. The circuit topology and/or part values may then be changed by the user, and a new analysis, requested. Circuit descriptions may be saved on disk files for storage and later use. The program contains built-in standard models for resistors, voltage and current sources, capacitors, inductors including mutual couplings, switches, junction diodes and transistors, FETS, and MOS devices. Nonstandard models may be constructed from standard models or by using the special equations interface. Time functions may be described by straight-line segments or by sine, damped sine, and exponential functions. 42 figures, 1 table
[Transient amnesia in the elderly].
Sellal, François
2006-03-01
The two main aetiologies of transient amnesia in the elderly are idiopathic transient global amnesia (TGA) and iatrogenic or toxic amnesia. Vascular and epileptic amnesia are less common. According to the literature, transient psychogenic amnesia, which is a frequent cause of amnesia at age 30 to 50, is very rare in the elderly. TGA is the prototypical picture of transient amnesia. It occurs more often after age 50, with no identified cause, even if some authors accept emotional stress or minor head trauma as occasional precipitants. The mechanism of TGA remains a matter of discussion. It may be the consequence of a spreading depression similar to that described in migraine with aura, but other arguments support an ischemic mechanism. Iatrogenic amnesias are mainly caused by benzodiazepines (BZs) or anticholinergics. The former may occur in a non-anxious subject, who is not a usual consumer of BZ and takes a single dose. The latter are more often due to a hypersensitivity to anticholinergic drugs, in particular in patients presenting with a covert, incipient Alzheimer's disease. A vascular origin must be considered when amnesia is accompanied by other neurological symptoms, and when the regression of the amnesic disorder is slow, lasting several days. It results from lesions involving various mechanisms and locations, mainly subcortical. Partial seizures, most often mesio-temporal, more rarely frontal, may be the cause of transient amnesia in the elderly, in the absence of a past history of epilepsy. The red flag supportive of an epileptic origin is the repetition of stereotyped amnesic episodes. EEG demonstration of seizures may be difficult and the response to antiepileptic drugs effective on partial seizures is usually good.
Research of the transient management in TQNPC
International Nuclear Information System (INIS)
Guo Longzhang; Lin Chuanqing
2008-01-01
Transient management is the basic technical subject in nuclear power plant. Since the Third Qinshan nuclear power company (TQNPC) successful completes the commissioning in 2003, the transient management work start at the transient management item selection and the flow definition. Now TQNPC have a complete transient management system and the management flow. In the last two years, TNQPC have finished the historic transient data collection for two units, and confirmed that the plant's key systems and equipments are at safe state. The development of the transient management subject would build a reliable foundation for the plant safe operation, plant lifetime management and periodic safety review. (author)
Transient dynamic and inelastic analysis of shells of revolution
International Nuclear Information System (INIS)
Svalbonas, V.
1975-01-01
Advances in the limits of structural use in the aerospace and nuclear power industries over the past years have increased the requirements upon the applicable analytical computer programs to include accurate capabilities for inelastic and transient dynamic analyses. In many minds, however, this advanced capability is unequivocally linked with the large scale, general purpose, finite element programs. This idea is also combined with the view that, therefore, such analyses are prohibitively expensive and should be relegated to the 'last resort' classification. While this, in the general sense, may indeed be the case, if however, the user needs only to analyze structures falling into limited categories, he may find that a variety of smaller special purpose programs are available, which do not put an undue strain upon his resources. One such structural category is shells of revolution. This survey of programs will concentrate upon the analytical tools which have been developed predominantly for shells of revolution. The survey will be subdivided into three parts: a) consideration of programs for transient dynamic analysis, b) consideration of programs for inelastic analysis, and finally, c) consideration of programs capable of dynamic plasticity analysis. In each part, programs based upon finite difference, finite element, and numerical integration methods will be considered. The programs will be compared on the basis of analytical capabilities, and ease of idealization and use. In each part of the survey sample problems will be utilized to exemplify the state-of-the-art. (orig.) [de
Enhancing the ABAQUS Thermomechanics Code to Simulate Steady and Transient Fuel Rod Behavior
International Nuclear Information System (INIS)
Williamson, R.L.; Knoll, D.A.
2009-01-01
A powerful multidimensional fuels performance capability, applicable to both steady and transient fuel behavior, is developed based on enhancements to the commercially available ABAQUS general-purpose thermomechanics code. Enhanced capabilities are described, including: UO2 temperature and burnup dependent thermal properties, solid and gaseous fission product swelling, fuel densification, fission gas release, cladding thermal and irradiation creep, cladding irradiation growth, gap heat transfer, and gap/plenum gas behavior during irradiation. The various modeling capabilities are demonstrated using a 2D axisymmetric analysis of the upper section of a simplified multi-pellet fuel rod, during both steady and transient operation. Computational results demonstrate the importance of a multidimensional fully-coupled thermomechanics treatment. Interestingly, many of the inherent deficiencies in existing fuel performance codes (e.g., 1D thermomechanics, loose thermo-mechanical coupling, separate steady and transient analysis, cumbersome pre- and post-processing) are, in fact, ABAQUS strengths.
Runaway transient simulation of a model Kaplan turbine
Energy Technology Data Exchange (ETDEWEB)
Liu, S; Liu, D; Wu, Y [State Key Laboratory of Hydroscience and Engineering, Department of Thermal Eng., Tsinghua University, Beijing, 100084 (China); Zhou, D [Water Conservancy and Hydropower Eng., Hohai University, Nanjing. 210098 (China); Nishi, M, E-mail: liushuhong@tsinghua.edu.c [Kyushu Inst. Tech. Senior Academy, Kitakyushu, 804-8550 (Japan)
2010-08-15
The runaway transient is a typical transient process of a hydro power unit, where the rotational speed of a turbine runner rapidly increases up to the runaway speed under a working head as the guide vanes cannot be closed due to some reason at the load rejection. In the present paper, the characteristics of the runaway transient of a model Kaplan turbine having ns = 479(m-kW) is simulated by using a time-dependent CFD technique where equation of rotational motion of runner, continuity equation and unsteady RANS equations with RNG k-{epsilon} turbulence model are solved iteratively. In the calculation, unstructured mesh is used to the whole flow passage, which consists of several sub-domains: entrance, casing, stay vanes + guide vanes, guide section, runner and draft tube. And variable speed sliding mesh technique is used to exchange interface flow information between moving part and stationary part, and three-dimensional unstructured dynamic mesh technique is also adopted to ensure mesh quality. Two cases were treated in the simulation of runaway transient characteristics after load rejection: one is the rated operating condition as the initial condition, and the other is the condition at the maximum head. Regarding the runaway speed, the experimental speed is 1.45 times the initial speed and the calculation is 1.47 times the initial for the former case. In the latter case, the experiment and the calculation are 1.67 times and 1.69 times respectively. From these results, it is recognized that satisfactorily prediction will be possible by using the present numerical method. Further, numerical results show that the swirl in the draft-tube flow becomes stronger in the latter part of the transient process so that a vortex rope will occur in the draft tube and its precession will cause the pressure fluctuations which sometimes affect the stability of hydro power system considerably.
Runaway transient simulation of a model Kaplan turbine
Liu, S.; Zhou, D.; Liu, D.; Wu, Y.; Nishi, M.
2010-08-01
The runaway transient is a typical transient process of a hydro power unit, where the rotational speed of a turbine runner rapidly increases up to the runaway speed under a working head as the guide vanes cannot be closed due to some reason at the load rejection. In the present paper, the characteristics of the runaway transient of a model Kaplan turbine having ns = 479(m-kW) is simulated by using a time-dependent CFD technique where equation of rotational motion of runner, continuity equation and unsteady RANS equations with RNG k-epsilon turbulence model are solved iteratively. In the calculation, unstructured mesh is used to the whole flow passage, which consists of several sub-domains: entrance, casing, stay vanes + guide vanes, guide section, runner and draft tube. And variable speed sliding mesh technique is used to exchange interface flow information between moving part and stationary part, and three-dimensional unstructured dynamic mesh technique is also adopted to ensure mesh quality. Two cases were treated in the simulation of runaway transient characteristics after load rejection: one is the rated operating condition as the initial condition, and the other is the condition at the maximum head. Regarding the runaway speed, the experimental speed is 1.45 times the initial speed and the calculation is 1.47 times the initial for the former case. In the latter case, the experiment and the calculation are 1.67 times and 1.69 times respectively. From these results, it is recognized that satisfactorily prediction will be possible by using the present numerical method. Further, numerical results show that the swirl in the draft-tube flow becomes stronger in the latter part of the transient process so that a vortex rope will occur in the draft tube and its precession will cause the pressure fluctuations which sometimes affect the stability of hydro power system considerably.
Runaway transient simulation of a model Kaplan turbine
International Nuclear Information System (INIS)
Liu, S; Liu, D; Wu, Y; Zhou, D; Nishi, M
2010-01-01
The runaway transient is a typical transient process of a hydro power unit, where the rotational speed of a turbine runner rapidly increases up to the runaway speed under a working head as the guide vanes cannot be closed due to some reason at the load rejection. In the present paper, the characteristics of the runaway transient of a model Kaplan turbine having ns = 479(m-kW) is simulated by using a time-dependent CFD technique where equation of rotational motion of runner, continuity equation and unsteady RANS equations with RNG k-ε turbulence model are solved iteratively. In the calculation, unstructured mesh is used to the whole flow passage, which consists of several sub-domains: entrance, casing, stay vanes + guide vanes, guide section, runner and draft tube. And variable speed sliding mesh technique is used to exchange interface flow information between moving part and stationary part, and three-dimensional unstructured dynamic mesh technique is also adopted to ensure mesh quality. Two cases were treated in the simulation of runaway transient characteristics after load rejection: one is the rated operating condition as the initial condition, and the other is the condition at the maximum head. Regarding the runaway speed, the experimental speed is 1.45 times the initial speed and the calculation is 1.47 times the initial for the former case. In the latter case, the experiment and the calculation are 1.67 times and 1.69 times respectively. From these results, it is recognized that satisfactorily prediction will be possible by using the present numerical method. Further, numerical results show that the swirl in the draft-tube flow becomes stronger in the latter part of the transient process so that a vortex rope will occur in the draft tube and its precession will cause the pressure fluctuations which sometimes affect the stability of hydro power system considerably.
The validation of neutron kinetic calculations of CEGB reactors
International Nuclear Information System (INIS)
Emmett, J.C.A.; Hutt, P.K.; Nunn, D.L.; Waterson, R.H.
1982-01-01
Reactor kinetic calculations are required by the CEGB to predict space and time varying neutron fluxes through the course of various hypothesized core transients. These transients arise through flow or reactivity perturbations occurring in a part of the core. A description is given of the results of dual programmes of work undertaken at BNL to validate such calculations. Firstly, analyses have been carried out to establish how data for these calculations should best be derived. Secondly, experimental measurements have been compared against the predictions of such calculations with data derived in the recommended way. (author)
Advanced methods for BWR transient and stability analysis
Energy Technology Data Exchange (ETDEWEB)
Schmidt, A; Wehle, F; Opel, S; Velten, R [AREVA, AREVA NP, Erlangen (Germany)
2008-07-01
The design of advanced Boiling Water Reactor (BWR) fuel assemblies and cores is governed by the basic requirement of safe, reliable and flexible reactor operation with optimal fuel utilization. AREVA NP's comprehensive steady state and transient BWR methodology allows the designer to respond quickly and effectively to customer needs. AREVA NP uses S-RELAP5/RAMONA as the appropriate methodology for the representation of the entire plant. The 3D neutron kinetics and thermal-hydraulics code has been developed for the prediction of system, fuel and core behavior and provides additional margins for normal operation and transients. Of major importance is the extensive validation of the methodology. The validation is based on measurements at AREVA NP's test facilities, and comparison of the predictions with a great wealth of measured data gathered from BWR plants during many years of operation. Three of the main fields of interest are stability analysis, operational transients and reactivity initiated accidents (RIAs). The introduced 3D methodology for operational transients shows significant margin regarding the operational limit of critical power ratio, which has been approved by the German licensing authority. Regarding BWR stability a large number of measurements at different plants under various conditions have been performed and successfully post-calculated with RAMONA. This is the basis of reliable pre-calculations of the locations of regional and core-wide stability boundaries. (authors)
Advanced methods for BWR transient and stability analysis
International Nuclear Information System (INIS)
Schmidt, A.; Wehle, F.; Opel, S.; Velten, R.
2008-01-01
The design of advanced Boiling Water Reactor (BWR) fuel assemblies and cores is governed by the basic requirement of safe, reliable and flexible reactor operation with optimal fuel utilization. AREVA NP's comprehensive steady state and transient BWR methodology allows the designer to respond quickly and effectively to customer needs. AREVA NP uses S-RELAP5/RAMONA as the appropriate methodology for the representation of the entire plant. The 3D neutron kinetics and thermal-hydraulics code has been developed for the prediction of system, fuel and core behavior and provides additional margins for normal operation and transients. Of major importance is the extensive validation of the methodology. The validation is based on measurements at AREVA NP's test facilities, and comparison of the predictions with a great wealth of measured data gathered from BWR plants during many years of operation. Three of the main fields of interest are stability analysis, operational transients and reactivity initiated accidents (RIAs). The introduced 3D methodology for operational transients shows significant margin regarding the operational limit of critical power ratio, which has been approved by the German licensing authority. Regarding BWR stability a large number of measurements at different plants under various conditions have been performed and successfully post-calculated with RAMONA. This is the basis of reliable pre-calculations of the locations of regional and core-wide stability boundaries. (authors)
International Nuclear Information System (INIS)
Diamond, D.J.
1988-08-01
The EPRI Reactor Analysis Support Package (RASP) consists of computer codes and documentation for calculating core performance and plant transients. This report was written to help a utility to use these tools properly for reload design and safety evaluations. The emphasis is on the steps that the utility can take to develop a methodology that is approved by the Nuclear Regulatory Commission for reload licensing submittals. The report treats both the planning and the implementation of this type of calculational capability. With regard to planning, there is discussion defining objectives, resource requirements, organization and scheduling. In order to help the engineering staff implement the plan there is discussion of the development of a methodology for event analysis, qualification of the methods, and the writing of design control procedures and topical reports. The experience of utilities, and especially of GPU Nuclear Corporation (GPUN), in developing a reload licensing capability is cited throughout the report and extracts from GPUN design control procedures are included in the appendices. 16 refs., 23 figs., 9 tabs
Accelerator and Electrodynamics Capability Review
International Nuclear Information System (INIS)
Jones, Kevin W.
2010-01-01
Los Alamos National Laboratory (LANL) uses capability reviews to assess the science, technology and engineering (STE) quality and institutional integration and to advise Laboratory Management on the current and future health of the STE. Capability reviews address the STE integration that LANL uses to meet mission requirements. The Capability Review Committees serve a dual role of providing assessment of the Laboratory's technical contributions and integration towards its missions and providing advice to Laboratory Management. The assessments and advice are documented in reports prepared by the Capability Review Committees that are delivered to the Director and to the Principal Associate Director for Science, Technology and Engineering (PADSTE). Laboratory Management will use this report for STE assessment and planning. LANL has defined fifteen STE capabilities. Electrodynamics and Accelerators is one of the seven STE capabilities that LANL Management (Director, PADSTE, technical Associate Directors) has identified for review in Fiscal Year (FY) 2010. Accelerators and electrodynamics at LANL comprise a blend of large-scale facilities and innovative small-scale research with a growing focus on national security applications. This review is organized into five topical areas: (1) Free Electron Lasers; (2) Linear Accelerator Science and Technology; (3) Advanced Electromagnetics; (4) Next Generation Accelerator Concepts; and (5) National Security Accelerator Applications. The focus is on innovative technology with an emphasis on applications relevant to Laboratory mission. The role of Laboratory Directed Research and Development (LDRD) in support of accelerators/electrodynamics will be discussed. The review provides an opportunity for interaction with early career staff. Program sponsors and customers will provide their input on the value of the accelerator and electrodynamics capability to the Laboratory mission.
Accelerator and electrodynamics capability review
Energy Technology Data Exchange (ETDEWEB)
Jones, Kevin W [Los Alamos National Laboratory
2010-01-01
Los Alamos National Laboratory (LANL) uses capability reviews to assess the science, technology and engineering (STE) quality and institutional integration and to advise Laboratory Management on the current and future health of the STE. Capability reviews address the STE integration that LANL uses to meet mission requirements. The Capability Review Committees serve a dual role of providing assessment of the Laboratory's technical contributions and integration towards its missions and providing advice to Laboratory Management. The assessments and advice are documented in reports prepared by the Capability Review Committees that are delivered to the Director and to the Principal Associate Director for Science, Technology and Engineering (PADSTE). Laboratory Management will use this report for STE assessment and planning. LANL has defined fifteen STE capabilities. Electrodynamics and Accelerators is one of the seven STE capabilities that LANL Management (Director, PADSTE, technical Associate Directors) has identified for review in Fiscal Year (FY) 2010. Accelerators and electrodynamics at LANL comprise a blend of large-scale facilities and innovative small-scale research with a growing focus on national security applications. This review is organized into five topical areas: (1) Free Electron Lasers; (2) Linear Accelerator Science and Technology; (3) Advanced Electromagnetics; (4) Next Generation Accelerator Concepts; and (5) National Security Accelerator Applications. The focus is on innovative technology with an emphasis on applications relevant to Laboratory mission. The role of Laboratory Directed Research and Development (LDRD) in support of accelerators/electrodynamics will be discussed. The review provides an opportunity for interaction with early career staff. Program sponsors and customers will provide their input on the value of the accelerator and electrodynamics capability to the Laboratory mission.
Recent developments in evaluating xenon induced flux transients in large HTRs
Energy Technology Data Exchange (ETDEWEB)
Lauer, A.
1974-03-15
A description is provided of the two-dimensional finite-difference xenon code system ASTERIX (A System for Transient Evaluation of Reactor instabilities Induced by Xenon) that was designed for very exact computations of space dependent xenon transients in HTR's and their control. By its modular structure, the code allows for a most flexible use in calculating load following transients, xenon oscillations in x/y, r/z and r/theta geometries and various control operations with either homogeneous poison or discrete rod representations with flux boundary conditions. The most recent upgrade ASTERIX-T includes a detailed temperature feedback option for azimuthal HTR transient calculations, based on an iterative procedure for the evaluation of the power distribution in each time step with succeeding diffusion, temperature and spectrum calculations for the group constants in every spectral region, thus avoiding earlier more problematic approximations of the temperature dependence of the cross sections.
Performance assessment calculational exercises
International Nuclear Information System (INIS)
Barnard, R.W.; Dockery, H.A.
1990-01-01
The Performance Assessment Calculational Exercises (PACE) are an ongoing effort coordinated by Yucca Mountain Project Office. The objectives of fiscal year 1990 work, termed PACE-90, as outlined in the Department of Energy Performance Assessment (PA) Implementation Plan were to develop PA capabilities among Yucca Mountain Project (YMP) participants by calculating performance of a Yucca Mountain (YM) repository under ''expected'' and also ''disturbed'' conditions, to identify critical elements and processes necessary to assess the performance of YM, and to perform sensitivity studies on key parameters. It was expected that the PACE problems would aid in development of conceptual models and eventual evaluation of site data. The PACE-90 participants calculated transport of a selected set of radionuclides through a portion of Yucca Mountain for a period of 100,000 years. Results include analyses of fluid-flow profiles, development of a source term for radionuclide release, and simulations of contaminant transport in the fluid-flow field. Later work included development of a problem definition for perturbations to the originally modeled conditions and for some parametric sensitivity studies. 3 refs
THYDE-P, PWR LOCA Thermohydraulic Transient Analysis
International Nuclear Information System (INIS)
Asahi, Yoshiro
2001-01-01
1 - Description of problem or function: THYDE-P1 analyzes the behaviour of LWR plants in response to various disturbances, including the thermal hydraulic transient following a break of the primary coolant pipe system, generally referred to as a loss-of-coolant-accident (LOCA). LOCA can be considered as the most critical condition for testing the methods and models for plant dynamics, since thermal hydraulic conditions in the system change drastically during the transient. THYDE-P is capable of a complete LOCA calculation from start to complete reflooding of the core by subcooled water. The program performs steady-state adjustment, which is complete in the sense that the steady state obtained is a set of exact solutions of all the transient equations without time derivatives, not only for plant hydraulics but also for all the other phenomena in the simulation of a PWR plant. THYDE-P2 contains among others the following improvements over THYDE-P1: (1) not only the mass and momentum equations but also the energy equation are included in the non-linear implicit scheme; (2) the valve model is implemented; (3) the relaxation equation for void fraction is theoretically derived; (4) vectorized programming is implemented; (5) both EM (evaluation mode) and BE (best estimate) calculations are possible. THYDE-W is an improved version of THYDE-P2 and contains the following additional features: (a) analysis of multiple number of disjoint loops is possible; (b) a control system simulation model is included; (c) the trip model has been improved; (d) heavy water is allowed as coolant; (e) the effect of drift flux is accounted for in the steady state calculation; (f) boron transport is included; (g) to obtain steady state loop heat balance, the option of adjusting the enthalpy distribution is prepared included in addition to that of adjusting heat exchanger areas; (h) to obtain steady state pressure distribution, three other options are prepared in addition to the original ones
Materials and processing approaches for foundry-compatible transient electronics
Chang, Jan-Kai; Fang, Hui; Bower, Christopher A.; Song, Enming; Yu, Xinge; Rogers, John A.
2017-07-01
Foundry-based routes to transient silicon electronic devices have the potential to serve as the manufacturing basis for “green” electronic devices, biodegradable implants, hardware secure data storage systems, and unrecoverable remote devices. This article introduces materials and processing approaches that enable state-of-the-art silicon complementary metal-oxide-semiconductor (CMOS) foundries to be leveraged for high-performance, water-soluble forms of electronics. The key elements are (i) collections of biodegradable electronic materials (e.g., silicon, tungsten, silicon nitride, silicon dioxide) and device architectures that are compatible with manufacturing procedures currently used in the integrated circuit industry, (ii) release schemes and transfer printing methods for integration of multiple ultrathin components formed in this way onto biodegradable polymer substrates, and (iii) planarization and metallization techniques to yield interconnected and fully functional systems. Various CMOS devices and circuit elements created in this fashion and detailed measurements of their electrical characteristics highlight the capabilities. Accelerated dissolution studies in aqueous environments reveal the chemical kinetics associated with the underlying transient behaviors. The results demonstrate the technical feasibility for using foundry-based routes to sophisticated forms of transient electronic devices, with functional capabilities and cost structures that could support diverse applications in the biomedical, military, industrial, and consumer industries.
Fatigue status assessment for reactor pressure vessel based on actual operational transient
International Nuclear Information System (INIS)
Zhu Guangqiang; Liao Changbin; Dai Bing; Gui Chun
2013-01-01
Background: Fatigue is an important aging mechanism in RPV and it must be contained to aging management working range. Purpose: In order to ensure the safety operation of nuclear power plants, as extension of RPV service time, it is necessary to assess the fatigue damage caused by actual operation transient. Methods: Based on monitoring data of actual operation during the past eleven years, refer to design transient, the statistic analysis for types and occurrence times of actual transient is carried out, at the same time, every transients are combined as different operation cycles and the temperature field and stress field of typical components are analyzed by FEM. Results: Based on these information, fatigue analysis and assessment are finished, if later-actual transients are similar with the previous transients, the calculation result shows that the ratio between maximum of cumulative usage factors and design calculation value is 0.4967 the design transients is conservative. Conclusions: Fatigue status of RPV could be assessed and traced quickly through fatigue status assessment method in this paper based on actual operational transient and assessment result would be a good reference for RPV aging management. (authors)
The development of a transient neutron flux solution in the PANTHER code
International Nuclear Information System (INIS)
Hutt, P.K.; Knight, M.P.
1990-01-01
In the United Kingdom a new three-dimensional, two-group, homogeneous reactor diffusion code, PANTHER, has been developed for the analysis of pressurized water reactors (PWRs) and advanced gas-cooled reactors (AGRs). The code can perform a comprehensive range of calculations, steady state, depletion, and transient with either a finite difference or analytic nodal flux solution. The nodal solution allows the representation of within-node burnup variation and pin-power reconstruction in either steady-state or transient mode. Specific steady-state and transient thermal feedback modules are included for both PWRs and AGRs. The code is being developed to perform a complete range of reactor calculations from online operational support to fuel management and fault transient analysis. In the area of transient analysis, the code is currently being used for a number of PWR fault transient assessments, including rod ejection and steam-line break. In addition, work is proceeding to incorporate the PANTHER 3D nodal transient solution in the TRAC-P code. This paper outlines the development of the transient flux solutions within PANTHER
Technological Capability and Firm Performance
Directory of Open Access Journals (Sweden)
Fernanda Maciel Reichert
2014-08-01
Full Text Available This research aims to investigate the relationship between investments in technological capability and economic performance in Brazilian firms. Based on economic development theory and on developed countries history, it is assumed that this relationship is positive. Through key indicators, 133 Brazilian firms have been analyzed. Given the economic circumstances of an emerging economy, which the majority of businesses are primarily based on low and medium-low-technology industries, it is not possible to affirm the existence of a positive relation between technological capability and firm performance. There are other elements that allow firms to achieve such results. Firms of lower technological intensity industries performed above average in the economic performance indicators, adversely, they invested below average in technological capability. These findings do not diminish the merit of firms’ and country’s success. They in fact confirm a historical tradition of a country that concentrates its efforts on basic industries.
Functional capability of piping systems
International Nuclear Information System (INIS)
Terao, D.; Rodabaugh, E.C.
1992-11-01
General Design Criterion I of Appendix A to Part 50 of Title 10 of the Code of Federal Regulations requires, in part, that structures, systems, and components important to safety be designed to withstand the effects of earthquakes without a loss of capability to perform their safety function. ne function of a piping system is to convey fluids from one location to another. The functional capability of a piping system might be lost if, for example, the cross-sectional flow area of the pipe were deformed to such an extent that the required flow through the pipe would be restricted. The objective of this report is to examine the present rules in the American Society of Mechanical Engineers Boiler and Pressure Vessel Code, Section III, and potential changes to these rules, to determine if they are adequate for ensuring the functional capability of safety-related piping systems in nuclear power plants
Directory of Open Access Journals (Sweden)
Dong Pei
2018-02-01
Full Text Available The prioritization of capability gaps for weapon system of systems is the basis for design and capability planning in the system of systems development process. In order to address input information uncertainties, the prioritization of capability gaps is computed in two steps using the conditional evidential network method. First, we evaluated the belief distribution of degree of required satisfaction for capabilities, and then calculated the reverse conditional belief function between capability hierarchies. We also provided verification for the feasibility and effectiveness of the proposed method through a prioritization of capability gaps calculation using an example of a spatial-navigation-and-positioning system of systems.
Nonlinear Diffusion and Transient Osmosis
International Nuclear Information System (INIS)
Igarashi, Akira; Rondoni, Lamberto; Botrugno, Antonio; Pizzi, Marco
2011-01-01
We investigate both analytically and numerically the concentration dynamics of a solution in two containers connected by a narrow and short channel, in which diffusion obeys a porous medium equation. We also consider the variation of the pressure in the containers due to the flow of matter in the channel. In particular, we identify a phenomenon, which depends on the transport of matter across nano-porous membranes, which we call ''transient osmosis . We find that nonlinear diffusion of the porous medium equation type allows numerous different osmotic-like phenomena, which are not present in the case of ordinary Fickian diffusion. Experimental results suggest one possible candidate for transiently osmotic processes. (electromagnetism, optics, acoustics, heat transfer, classical mechanics, and fluid dynamics)
Fast thermal transients on valve
International Nuclear Information System (INIS)
Ferjancic, M.; Stok, B.; Halilovic, M.; Koc, P.; Mole, N.; Otrin, Z.; Kotar, A.
2007-01-01
One of the regulatory body methods to supervise nuclear safety of a nuclear power plant is a review of plant modifications and evaluation of their impact on plant operating experience. The Slovenian Nuclear Safety Administration (SNSA) licensed in April 2003 the use of leak-before-break (LBB) methodology in the Krsko NPP for the primary loop including surge line and connecting pipelines with minimal diameter of 6 inch. The SNSA decision based also on fracture mechanics analyses that include direct pipe failure mechanisms such as water hammer, creep damage, erosion and corrosion, fatigue and environmental conditions over the entire life of the plant. The evaluation of the operating transients pointed out, that presumed loadings, used for the LBB analysis, did not incorporate all the fast thermal transients data. For that purpose the SNSA requested Faculty of Mechanical Engineering (FS) in Ljubljana to perform additional analyses. The results of the analysis shall confirm the validity of the LBB analysis. (author)
Superresolution microscopy with transient binding.
Molle, Julia; Raab, Mario; Holzmeister, Susanne; Schmitt-Monreal, Daniel; Grohmann, Dina; He, Zhike; Tinnefeld, Philip
2016-06-01
For single-molecule localization based superresolution, the concentration of fluorescent labels has to be thinned out. This is commonly achieved by photophysically or photochemically deactivating subsets of molecules. Alternatively, apparent switching of molecules can be achieved by transient binding of fluorescent labels. Here, a diffusing dye yields bright fluorescent spots when binding to the structure of interest. As the binding interaction is weak, the labeling is reversible and the dye ligand construct diffuses back into solution. This approach of achieving superresolution by transient binding (STB) is reviewed in this manuscript. Different realizations of STB are discussed and compared to other localization-based superresolution modalities. We propose the development of labeling strategies that will make STB a highly versatile tool for superresolution microscopy at highest resolution. Copyright © 2015 Elsevier Ltd. All rights reserved.
International Nuclear Information System (INIS)
Cacciabue, P.C.; Fremont, R. de; Renard, A.
1982-01-01
The Report gives the results of comparative calculations performed by the Whole Core Accident Codes Group which is a subgroup of the Safety Working Group of the Fast Reactor Coordinating Committee for a hypothetical transient overpower accident in an irradiated LMFBR core. Different computer codes from members of the European Community and the United States were used. The calculations are based on a Benchmark problem, using commonly agreed input data for the most important phenomena, such as the fuel pin failure threshold, FCl parameters, etc. Beside this, results with alternative assumptions for theoretical modelling are presented with the scope to show in a parametric way the influence of more advanced modelling capabilities and/or better (so-called best estimate) input data for the most important phenomena on the accident sequences
Nanofabrication principles, capabilities and limits
Cui, Zheng
2017-01-01
This second edition of Nanofabrication is one of the most comprehensive introductions on nanofabrication technologies and processes. A practical guide and reference, this book introduces readers to all of the developed technologies that are capable of making structures below 100nm. The principle of each technology is introduced and illustrated with minimum mathematics involved. Also analyzed are the capabilities of each technology in making sub-100nm structures, and the limits of preventing a technology from going further down the dimensional scale. This book provides readers with a toolkit that will help with any of their nanofabrication challenges.
Judgmental Forecasting of Operational Capabilities
DEFF Research Database (Denmark)
Hallin, Carina Antonia; Tveterås, Sigbjørn; Andersen, Torben Juul
This paper explores a new judgmental forecasting indicator, the Employee Sensed Operational Capabilities (ESOC). The purpose of the ESOC is to establish a practical prediction tool that can provide early signals about changes in financial performance by gauging frontline employees’ sensing...... of changes in the firm’s operational capabilities. We present the first stage of the development of ESOC by applying a formative measurement approach to test the index in relation to financial performance and against an organizational commitment scale. We use distributed lag models to test whether the ESOC...
Improved statistical confirmation of margins for setpoints and transients
International Nuclear Information System (INIS)
Nutt, W.T.
2001-01-01
Framatome ANP Richland, Inc. has developed an integrated, automated, statistical methodology for Pressurized Water Reactors (PWRs). Margins for transients and calculated trips are confirmed using several new applications of probability theory. The methods used for combining statistics reduces the conservatisms inherent in conventional methods and avoids the numerical limitations and time constraints imposed by Monte Carlo techniques. The new methodology represents the state of the art in the treatment of uncertainties for reactor protection systems. It all but eliminates concerns with the calculated trips for PWRs and by improving the margin for all transients will allow for far more aggressive peaking limits and fuel management schemes. The automated nature of the bulk of this process saves Framatome ANP time and effort, minimizes the potential for errors and makes the analysis for all cycles and plants consistent. The enhanced margins remove analytical limitations from the customer and allow for more economical operation of the plant. (authors)
Transient thermal stress problem for a circumferentially cracked hollow cylinder
Nied, H. F.; Erdogan, F.
1982-01-01
The transient thermal stress problem for a hollow elasticity cylinder containing an internal circumferential edge crack is considered. It is assumed that the problem is axisymmetric with regard to the crack geometry and the loading, and that the inertia effects are negligible. The problem is solved for a cylinder which is suddenly cooled from inside. First the transient temperature and stress distributions in an uncracked cylinder are calculated. By using the equal and opposite of this thermal stress as the crack surface traction in the isothermal cylinder the crack problem is then solved and the stress intensity factor is calculated. The numerical results are obtained as a function of the Fourier number tD/b(2) representing the time for various inner-to-outer radius ratios and relative crack depths, where D and b are respectively the coefficient of diffusivity and the outer radius of the cylinder.
An overview of optimization of structures subjected to transient loads
International Nuclear Information System (INIS)
Kang, Byung Soo; Park, Gyung Jin
2005-01-01
Various aspects of structural optimization techniques under transient loads are extensively reviewed. The main themes of the paper are treatment of time dependent constraints, calculation of design sensitivity, and approximation. Each subject is reviewed with the corresponding papers that have been published since 1970s. The treatment of time dependent constraints in both the direct method and the transformation method is discussed. Two ways of calculating design sensitivity of a structure under transient loads are discussed-direct differentiation method and adjoint variable method. The approximation concept mainly focuses on response surface method in crashworthiness and local approximation with the intermediate variable. Especially, as an approximated optimization technique, equivalent static load method which takes advantage of the well-established static response optimization technique is introduced. And as an application area of dynamic response optimization technique, the structural optimization in flexible multibody dynamic system is reviewed in the viewpoint of the above three themes
LLL transient-electromagnetics-measurement facility
International Nuclear Information System (INIS)
Deadrick, F.J.; Miller, E.K.; Hudson, H.G.
1975-01-01
The operation and hardware of the Lawrence Livermore Laboratory's transient-electromagnetics (EM)-measurement facility are described. The transient-EM range is useful for determining the time-domain transient responses of structures to incident EM pulses. To illustrate the accuracy and utility of the EM-measurement facility, actual experimental measurements are compared to numerically computed values
Learning from anticipated and abnormal plant transients
International Nuclear Information System (INIS)
Varnado, B.
1983-01-01
A report is given of the American Nuclear Society topical meeting on Anticipated and Abnormal Transients in Light Water Reactors held in Jackson, Wyoming in September 1983. Industry involvement in the evaluation of operating experience, human error contributions, transient management, thermal hydraulic modelling, the role of probabilistic risk assessment and the cost of transient incidents are discussed. (U.K.)