#### Sample records for small once-through boiler

1. Modelling transition states of a small once-through boiler

Energy Technology Data Exchange (ETDEWEB)

Talonpoika, T [Lappeenranta Univ. of Technology (Finland). Dept. of Energy Technology

1998-12-31

This article presents a model for the unsteady dynamic behaviour of a once-through counter flow boiler that uses an organic working fluid. The boiler is a compact waste-heat boiler without a furnace and it has a preheater, a vaporiser and a superheater. The relative lengths of the boiler parts vary with the operating conditions since they are all parts of a single tube. The boiler model is presented using a selected example case that uses toluene as the process fluid and flue gas from natural gas combustion as the heat source. The dynamic behaviour of the boiler means transition from the steady initial state towards another steady state that corresponds to the changed process conditions. The solution method chosen is to find such a pressure of the process fluid that the mass of the process fluid in the boiler equals the mass calculated using the mass flows into and out of the boiler during a time step, using the finite difference method. A special method of fast calculation of the thermal properties is used, because most of the calculation time is spent in calculating the fluid properties. The boiler is divided into elements. The values of the thermodynamic properties and mass flows are calculated in the nodes that connect the elements. Dynamic behaviour is limited to the process fluid and tube wall, and the heat source is regarded as to be steady. The elements that connect the preheater to the vaporiser and the vaporiser to the superheater are treated in a special way that takes into account a flexible change from one part to the other. The initial state of the boiler is received from a steady process model that is not a part of the boiler model. The known boundary values that may vary during the dynamic calculation were the inlet temperature and mass flow rates of both the heat source fluid and the process fluid. The dynamic boiler model is analysed for linear and step charges of the entering fluid temperatures and flow rates. The heat source side tests show that

2. Modelling transition states of a small once-through boiler

Energy Technology Data Exchange (ETDEWEB)

Talonpoika, T. [Lappeenranta Univ. of Technology (Finland). Dept. of Energy Technology

1997-12-31

This article presents a model for the unsteady dynamic behaviour of a once-through counter flow boiler that uses an organic working fluid. The boiler is a compact waste-heat boiler without a furnace and it has a preheater, a vaporiser and a superheater. The relative lengths of the boiler parts vary with the operating conditions since they are all parts of a single tube. The boiler model is presented using a selected example case that uses toluene as the process fluid and flue gas from natural gas combustion as the heat source. The dynamic behaviour of the boiler means transition from the steady initial state towards another steady state that corresponds to the changed process conditions. The solution method chosen is to find such a pressure of the process fluid that the mass of the process fluid in the boiler equals the mass calculated using the mass flows into and out of the boiler during a time step, using the finite difference method. A special method of fast calculation of the thermal properties is used, because most of the calculation time is spent in calculating the fluid properties. The boiler is divided into elements. The values of the thermodynamic properties and mass flows are calculated in the nodes that connect the elements. Dynamic behaviour is limited to the process fluid and tube wall, and the heat source is regarded as to be steady. The elements that connect the preheater to the vaporiser and the vaporiser to the superheater are treated in a special way that takes into account a flexible change from one part to the other. The initial state of the boiler is received from a steady process model that is not a part of the boiler model. The known boundary values that may vary during the dynamic calculation were the inlet temperature and mass flow rates of both the heat source fluid and the process fluid. The dynamic boiler model is analysed for linear and step charges of the entering fluid temperatures and flow rates. The heat source side tests show that

3. Constrained control of a once-through boiler with recirculation

DEFF Research Database (Denmark)

Trangbæk, K

2008-01-01

There is an increasing need to operate power plants at low load for longer periods of time. When a once-through boiler operates at a sufficiently low load, recirculation is introduced, significantly altering the control structure. This paper illustrates the possibilities for using constrained con...

4. Study of flue-gas temperature difference in supercritical once-through boiler

Science.gov (United States)

Kang, Yanchang; Li, Bing; Song, Ang

2018-02-01

The 600 MW coal-fired once-through Boilers with opposed firing at a power plant are found to experience marked temperature variation and even overtemperature on the wall of the heating surface as a result of flue-gas temperature (FGT) variation in the boiler. In this study, operational adjustments were made to the pulverizing, combustion, and secondary air box systems in these boilers, in order to solve problems in internal combustion. The adjustments were found to reduce FGT difference and optimize the boiler’ combustion conditions. The results of this study can provide a reference for optimization of coal-fired boiler of the same type in similar conditions.

5. Chemical and hydrothermal studies on once through boilers using a full scale replica

International Nuclear Information System (INIS)

Penfold, D.; Gill, G.M.; Greene, J.C.; Harrison, G.S.; Walker, M.A.

1987-01-01

The paper describes the scope of research work carried out on once through boilers on the test rig at Wythenshawe, United Kingdom. The latter rig was designed and built to replicate the chemical, metallurgical and hydrothermal conditions on single tube test sections of Heysham 1 (AGR) and Wylfa (Magnox) boilers. A description is given of the rig, along with the facilities for obtaining the research data. Research studies on the once through boilers include: Heysham 1 boiler inlet, oxygen stress corrosion risk in post trip operation, Wylfa two phase erosion-corrosion risk in post trip operation, Wylfa two phase erosion-corrosion, dryout phenomena in a helical coil, and heat transfer co-efficients. (UK)

6. Low Load Model of a Once-through Boiler with Recirculation

DEFF Research Database (Denmark)

Trangbæk, Klaus

2006-01-01

A dynamic simulation model of a once-through boiler in low to medium load is developed. When the system is in low load, water from the evaporator is recirculated through a bottle. This recirculation system is included in the model, which is then shown to fit closed-loop data from a real plant...

7. The orificing of once-through boilers for gas-cooled reactors

International Nuclear Information System (INIS)

Collier, J.G.; Whitmarsh-Everiss, M.J.

1986-01-01

The boilers at Hinkley Point B, Hunterston B (which are built to a common design) and Hartlepool and Heysham (which are identical to each other although different from Hinkley B/Hunterston B) are discussed. Heysham II and Torness have boilers developed from the Hinkley B/Hunterston B design. The boiler design is explained and the problems encountered are presented. The study presented in this address highlights the potential sensitivity of the performance of once-through boilers to the following factors - the uniformity of the gas inlet temperature profile, the choice of the operating point on the boiler characteristic (preferably this should be where the performance of the unit is not too sensitive to the primary side temperature and flow distribution); this can be achieved by greater levels of orificing reducing the steady state gains, and the various plant operating states which introduce asymmetries into the boundary conditions for the boiler. A number of computer codes have been used to model boiler performance. Using these, a new design was proposed for boiler feed regulating orifices and these revised orifices were installed during outages on the two Heysham reactors in 1985. (U.K.)

8. The early operation of the helical once-through boilers at Heysham 1 and Hartlepool

International Nuclear Information System (INIS)

Mathews, A.J.

1988-01-01

The Heysham 1 and Hartlepool AGR Reactors are equipped with 'pod' boilers set into the walls of the Pre-stressed Concrete Pressure Vessel. Each Reactor unit has eight pod boilers, which are of a somewhat unique single pressure, once through, helically wound type incorporating a reheater. The pods are provided with a limited amount of strain gauge and thermocouple instrumentation concentrated mainly in two specially instrumented boilers at each site. During Commissioning prior to power raising, extensive noise and vibration tests utilising the special attain gauge instrumented boilers, gave encouraging results. This has led to an increase in coolant gas mass flow of 5% above the design level. Following power raising in 1983 and 1984, detailed boiler performance testing, mainly using the special thermocouple instrumented boilers, showed that the actual behaviour differed from the computer design predictions. A major temperature tilt existed across the boiler tubes resulting in higher than predicted temperatures in the outer radius rows of tubes and the reverse situation in the inner tubes. The effect differed in magnitude between Hartlepool Reactor 1 and the other three Reactors probably due to construction differences. As a result output was initially limited to approximately 58% of design (380 MW (Generated)). A major programme of altering the flow control ferrules was carried out during the first statutory overhauls in 1985 and 1986. The initial results from Heysham 1 were not very encouraging (a gain of 70 MW(e)) but further computer model correlations led to revised patterns in Heysham and Hartlepool Reactor 2 which have since yielded improvements in output potential of up to 200 MW(e). The paper discusses the commissioning test results described above and describes the details of the extensive work carried out to achieve higher output. (author)

9. Materials and boiler rig testing to support chemical cleaning of once-through AGR boilers

International Nuclear Information System (INIS)

Tice, D.R.; Platts, N.; Raffel, A.S.; Rudge, A.

2002-01-01

An extensive programme of work has been carried out to evaluate two candidate inhibited cleaning solutions for possible implementation on plant, which would be the first chemical clean of an AGR boiler. The two candidate cleaning solutions considered were a Stannine-inhibited citric acid/formic acid mixture (GOM106) and inhibited hydrofluoric acid. Citric acid-based cleaning processes are widely used within the UK Power Industry. The GOM106 solution, comprising a mixture of 3% citric acid, 0.5% formic acid and 0.05% Stannine LTP inhibitor, buffered with ammonia to pH 3.5, was developed specifically for the AGR boilers during the 1970's. Although a considerable amount of materials testing work was carried out by British Energy's predecessor companies to produce a recommended cleaning procedure there were some remaining concerns with the use of GOM106, from these earlier studies, for example, an increased risk of pitting attack associated with the removal of thick 9Cr oxide deposits and a risk of unacceptable damage in critical locations such as the upper transition joints and other weld locations. Hence, additional testing was still required to validate the solution for use on plant. Inhibited hydrofluoric acid (HFA) was also evaluated as an alternative reagent to GOM106. HFA has been used extensively for cleaning mild and low'alloy steel boiler tubes in fossil-fired plant in the UK and elsewhere in Europe and is known to remove oxide quickly. Waste treatment is also easier than for the GOM106 process and some protection against damage to the boiler tube materials is provided by complexing of fluoride with ferric ion. Validation of the potential reagents and inhibitors was achieved by assessing the rate and effectiveness of oxide removal from specimens of helical boiler tubing and welds, together with establishing the extent of any metal loss or localised damage. The initial materials testing resulted in the inhibited ammoniated citric / formic acid reagent being

10. Dynamic Simulation of the Water-steam System in Once-through Boilers - Sub-critical Power Boiler Case -

Energy Technology Data Exchange (ETDEWEB)

Kim, Seongil; Choi, Sangmin [Korea Advanced Institute of Science and Technology, Daejeon (Korea, Republic of)

2017-05-15

The dynamics of a water-steam system in a once-through boiler was simulated based on the physics-based modeling approach, representing the system in response to large load change or scale disturbance simulations. The modeling considered the mass, energy conservation, and momentum equation in the water pipe and the focus was limited to the sub-critical pressure region. An evaporator tube modeling was validated against the reference data. A simplified boiler system consisting of economizer, evaporator, and superheater was constructed to match a 500 MW power boiler. The dynamic response of the system following a disturbance was discussed along with the quantitative response characteristics. The dynamic response of the boiler system was further evaluated by checking the case of an off-design point operation of the feedwater-to-fuel supply ratio. The results re-emphasized the significance of controlling the feedwater-to-fuel supply ratio and additional design requirements of the water-steam separator and spray attemperator.

11. Dynamic Simulation of the Water-steam System in Once-through Boilers - Sub-critical Power Boiler Case -

International Nuclear Information System (INIS)

Kim, Seongil; Choi, Sangmin

2017-01-01

The dynamics of a water-steam system in a once-through boiler was simulated based on the physics-based modeling approach, representing the system in response to large load change or scale disturbance simulations. The modeling considered the mass, energy conservation, and momentum equation in the water pipe and the focus was limited to the sub-critical pressure region. An evaporator tube modeling was validated against the reference data. A simplified boiler system consisting of economizer, evaporator, and superheater was constructed to match a 500 MW power boiler. The dynamic response of the system following a disturbance was discussed along with the quantitative response characteristics. The dynamic response of the boiler system was further evaluated by checking the case of an off-design point operation of the feedwater-to-fuel supply ratio. The results re-emphasized the significance of controlling the feedwater-to-fuel supply ratio and additional design requirements of the water-steam separator and spray attemperator.

12. A dynamic model used for controller design of a coal fired once-through boiler-turbine unit

International Nuclear Information System (INIS)

Liu, Ji-Zhen; Yan, Shu; Zeng, De-Liang; Hu, Yong; Lv, You

2015-01-01

Supercritical OTB (once-through boiler) units with high steam temperature and pressure have been widely used in modern power plants due to their high cycle efficiency and less emissions. To ensure the effective operation of such power generation systems, it is necessary to build a model for the design of the overall control system. There are already detailed models of once-through boilers; however, their complexity prevents them from being applied in the controller design. This study describes a lumped parameter dynamic model that has a relatively low complexity while faithfully capturing the essential overall plant dynamics. The model structure was derived by fundamental physical laws utilizing reasonable simplifications and data analysis to avoid the phase transition position problem. Parameter identification for the model structure was completed using operational data from a 1000 MW ultra-supercritical OTB. The model was determined to be reasonable by comparison tests between computed data and measured data for both steady and dynamic states. The simplified model is verified to have appropriate fidelity in control system design to achieve effective and economic operation of the unit. - Highlights: • A simplified dynamic model of once-through boiler-turbine unit is given. • The essential dynamics of active power and throttle pressure is presented. • The change of phase transition position is avoided in modeling process. • The model has appropriate complexity and fidelity for controller design.

13. 46 CFR 63.25-1 - Small automatic auxiliary boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Small automatic auxiliary boilers. 63.25-1 Section 63.25... AUXILIARY BOILERS Requirements for Specific Types of Automatic Auxiliary Boilers § 63.25-1 Small automatic auxiliary boilers. Small automatic auxiliary boilers defined as having heat-input ratings of 400,000 Btu/hr...

14. Evaluation of conditions of SNCR in small boilers

International Nuclear Information System (INIS)

Kullendorff, A.; Lorentzon, K.

1996-04-01

The report describes the first part of a project 'SNCR for small boilers', supported by Vaermeforsk (Thermal Engineering Research Institute), with the purpose of assessing the potential for SNCR in small boilers. Given favourable conditions, the project was to be continued in a second part with the demonstration of a SNCR system in a small boiler (or several boilers). During the base establishment, the temperatures in four locations per boiler, in a couple of horizontal or vertical levels and at 2-3 thermal outputs, were measured. Out of the four locations two showed temperatures mainly within the theoretical temperature window for SNCR. These locations were used during the try-out tests to inject urea and ammonia. The locations and the equipment used during the try-out tests together with existing operation strategies seem to limit the reduction levels to approximately 10-20% at acceptable levels of ammonia slip. The measurements and try-out tests carried out does not provide enough basis for forming any general conclusions concerning SNCR in small boilers. Neither the base establishment nor the try-out tests included any optimisation of the boilers regarding the operation strategy or, for the try-out tests, locations and equipment (drop size, flow shape and direction). Therefore, it is likely to believe that better results can be obtained, given other conditions of operation and using well established SNCR technology, adapted to the circumstances. 2 refs, 27 figs, 5 tabs

15. Development of once-through type densitometer

International Nuclear Information System (INIS)

Onozawa, Atsushi; Kushida, Teruo; Kanazawa, Hiroyuki

2004-11-01

The swelling (volume change) observed on irradiated fuels is caused by the accumulation of fission products (FP) and irradiation defects. The swelling ratio could be changed along with radius region in the pellet due to burn up difference and irradiation temperature. Hence the density of the pellet is different between the center and outer regions of the pellet cross section. To investigate the swelling behavior at the small area of the pellet, it is needed to measure the density of fuel fragments picked from an irradiated pellet. However, the conventional densitometer for irradiated specimens in Reactor Fuel Examination Facility is designed for measuring the whole fuel pellet and is not available for precise density measurement of the small size specimen. In this circumstance, once-through type densitometer was developed to measure the density of the small irradiated specimen precisely and to handle the samples easily with remote control systems. Aimed accuracy is within 1.0%TD and precision is within 1.0% on a φ3 x 1t mm specimen. Several kinds of metallic and ceramic standard specimens are prepared to investigate the dependence of the sample weight, density and porosity on the accuracy. The results of characteristic examination using these specimens indicate that this densitometer has enough accuracy. In addition, some parts of this apparatus are controlled by motor drive units, which made it possible to measure the density full-automatically. In near future, this apparatus will be installed in a hot cell to investigate the swelling behavior at the small area of irradiated fuels and materials. (author)

16. Minimum load reduction for once-through boiler power plants

International Nuclear Information System (INIS)

Colombo, P.; Godina, G.; Manganelli, R.

2001-01-01

In Italy the liberalization process of energy market is giving particular importance to the optimization of power plants performances; especially for those that will be called to satisfy grid peak demands. On those plants some techniques have been experimented for the reduction of minimum load; these techniques, investigated and tested by an engineering dynamic simulator, have been sequentially tested on plant. The minimum load for up 320 MW of Tavazzano power plants has been diminished from 140 down to 80 MW without plant modification [it

17. Modelling and verification of once-through subcritical heat recovery steam generator

International Nuclear Information System (INIS)

Lee, Chae Soo; Choi, Young Jun; Kim, Hyun Gee; Yang, Ok Chul; Chong Chae Hon

2004-01-01

The once-through heat recovery steam generator is ideally matched to very high temperature and pressure, well into the supercritical range. Moreover this type of boiler is structurally simpler than drum type boiler. In drum type boiler, each tube play a well-defined role: water preheating, vaporization, superheating. Empirical equations are available to predict the average heat transfer coefficient for each regime. For once-through heat recovery steam generator, this is no more the case and mathematical models have to be adapted to account for the disappearance of drum type economizer, boiler, superheater. General equations have to be used for each tube of boiler, and actual heat transfer condition in each tube has to be identified

18. Numerical simulation of a small-scale biomass boiler

International Nuclear Information System (INIS)

Collazo, J.; Porteiro, J.; Míguez, J.L.; Granada, E.; Gómez, M.A.

2012-01-01

Highlights: ► Simplified model for biomass combustion was developed. ► Porous zone conditions are used in the bed. ► Model is fully integrated in a commercial CFD code to simulate a small scale pellet boiler. ► Pollutant emissions are well predicted. ► Simulation provides extensive information about the behaviour of the boiler. - Abstract: This paper presents a computational fluid dynamic simulation of a domestic pellet boiler. Combustion of the solid fuel in the burner is an important issue when discussing the simulation of this type of system. A simplified method based on a thermal balance was developed in this work to introduce the effects provoked by pellet combustion in the boiler simulation. The model predictions were compared with the experimental measurements, and a good agreement was found. The results of the boiler analysis show that the position of the water tubes, the distribution of the air inlets and the air infiltrations are the key factors leading to the high emission levels present in this type of system.

19. Optimal Combustion Conditions for a Small-scale Biomass Boiler

Directory of Open Access Journals (Sweden)

Viktor Plaček

2012-01-01

Full Text Available This paper reports on an attempt to achieve maximum efficiency and lowest possible emissions for a small-scale biomass boiler. This aim can be attained only by changing the control algorithm of the boiler, and in this way not raising the acquisition costs for the boiler. This paper describes the experimental facility, the problems that arose while establishing the facility, and how we have dealt with them. The focus is on discontinuities arising after periodic grate sweeping, and on finding the parameters of the PID control loops. Alongside these methods, which need a lambda probe signal for proper functionality, we inroduce another method, which is able to intercept the optimal combustion working point without the need to use a lambda sensor.

20. The heat exchanger of small pellet boiler for phytomass

Science.gov (United States)

Mičieta, Jozef; Lenhard, Richard; Jandačka, Jozef

2014-08-01

Combustion of pellets from plant biomass (phytomass) causes various troubles. Main problem is slagging ash because of low melting temperature of ash from phytomass. This problem is possible to solve either improving energetic properties of phytomass by additives or modification of boiler construction. A small-scale boiler for phytomass is different in construction of heat exchanger and furnace mainly. We solve major problem - slagging ash, by decreasing combustion temperature via redesign of pellet burner and boiler body. Consequence of lower combustion temperature is also lower temperature gradient of combustion gas. It means that is necessary to design larger heat exchanging surface. We plane to use underfed burner, so we would utilize circle symmetry heat exchanger. Paper deals design of heat exchanger construction with help of CFD simulation. Our purpose is to keep uniform water flux and combustion gas flux in heat exchanger without zone of local overheating and excess cooling.

1. Specific Emissions of Harmful Substances from Small Boilers

Directory of Open Access Journals (Sweden)

Horák Jiøí

1998-09-01

Full Text Available Coal is on of the most important energy source and its significance will increase in a future. In Czech republic coal is except else widely used as a fuel for combustion in a small boilers (up to 50 kW. Low efficiency of the small boilers which is often below 50% together with high emissions of the harmful substances into near surroundings cause in average 40  70% of total local air pollution. The research was performed in a scope of the Grant no. 101/98/0820 of Grant Agency of Czech Republic was focused on quality of combustion process related to combustion efficiency and creation of harmful substances at combustion of domestic fuels. Experiments were performed to compare combustion of brown coal, clack coal, coke and black coal slurry. Extremely high creation of harmful substances (CO, NOX, solid particles and organic substances was measured when the black coal slurry was used as a fuel, measured in kg of emissions per GJ of burned fuel. Combustion of brown coal produced significant emissions of solid particles which bond harmful substances as metals, polyaromatic hydrocarbons and others together with high emissions of SO2 . Strong dependence between emissions of CO and low quality of combustion given by low combustion temperature, shortage of combustion air, not suitable design of after-combustion chamber and short duration of fuel presence in a combustion area was found out. Emissions of wide range of metals were investigated. The results of the research grant project describe and explain the combustion process and creation of harmful substances in small boilers plus give suggestions and recommendations leading to rational operation of the small boilers and lowering their negative impact to environment.

2. Low temperature corrosion in bark fuelled, small boilers

Energy Technology Data Exchange (ETDEWEB)

Lindau, Leif; Goldschmidt, Barbara

2008-05-15

A number of small (3-12 MW), new biofuel boiler plants in southern Sweden, and (at least) in Austria, have suffered a high (wastage of mm/yrs) corrosion rate on the low temperature boiler side. This problem has been investigated with respect to its occurrence and its character by contacts with operators, by plant inspections, and by analysis of cold-side deposits. The plants affected have low feed water temperatures (< 100 deg C). The plants fire most types of Swedish biofuel: chips, bark, hog fuel, and 'GROT' (=twigs and tops). The results found give basis for a hypothesis that the corrosion results from the presence of an aqueous phase in the deposits, this phase being stabilized by dissolved salts having high solubility. It then follows that for each salt, there is a critical relative humidity (calculated from the flue gas water partial pressure and the cooling surface temperature as is common practice among boiler engineers) for both the presence of the aqueous phase and the corrosion. Some critical single salts, ZnCl{sub 2} and CaCl{sub 2} have been identified, and they give critical 'relative humidities' of 5% and 18% respectively. These figures are a lower bound. The corresponding figure, derived from the practical experience and the reported plant operational data, is between 20 and 30%. Corrosion tests have been carried out by exposing an air-cooled probe in the flue gases at a 12 MW boiler at Saevelundsverket in Alingsaas, and the material wastage at different temperatures has been measured with a profilometer. The high corrosion rates were reproduced in the tests for high relative humidities. The corrosion rate was small and not measurable (<0.1 mm/year) for relative humidity <22%. The work shows by means of indirect evidence that the corrosion critical components are ZnCl{sub 2} and possibly CaCl{sub 2} as well. The practical engineering design criterion derived from the work is that the relative humidity (calculated from the flue

3. Life cycle analysis of small scale pellet boilers characterized by high efficiency and low emissions

International Nuclear Information System (INIS)

Monteleone, B.; Chiesa, M.; Marzuoli, R.; Verma, V.K.; Schwarz, M.; Carlon, E.; Schmidl, C.; Ballarin Denti, A.

2015-01-01

Highlights: • LCA was performed on innovative small scale pellet boilers. • Pellet boilers impacts were compared to oil and natural gas boilers impacts. • Both literature and experimental data were used for life cycle analysis. • The environmental impact due to all life cycle phases was envisaged. • Sensitivity tests evidenced realistic ways for pellet boilers impact reduction. - Abstract: This study focuses on the environmental impact assessment through Life Cycle Analysis (LCA) of two innovative 10 kW pellet boilers. In particular, the second boiler represents a technological evolution of the first one developed to improve its performance in terms of efficiency and environmental impact. For both boilers, emission factors measured during laboratory tests (full load tests and specific load cycle tests representative of real life boiler operation) have been used as input data in the life cycle analysis. The SimaPro software (v.8.0.4.30) was used for the LCA and the ReCiPe Midpoint method (European version H) was chosen to assess the environmental impact of all boilers (according to LCA ISO standards). In addition, the ReCiPe Endpoint method was used to compare the final results of all 5 boilers with literature data. The pelletisation process represented the most relevant share of the overall environmental impact followed by the operational phase, the manufacturing phase and the disposal phase. A sensitivity analysis performed on the most efficient pellet boiler evidenced the variation of the boiler’s environmental impact as a function of PM10 and NO X emission factors with respect to emission factors monitored during boiler full load operation. Moreover, the reduction of the boiler’s weight and the adoption of new electronic components led to a consistent reduction (−18%) of its environmental impact with respect to the previous technology. A second LCA has been carried on for a 15 kW oil boiler, a 15 kW natural gas boiler and a 15 kW pellet boiler

4. Increase of efficiency and reliability of liquid fuel combustion in small-sized boilers

Science.gov (United States)

Roslyakov, P. V.; Proskurin, Yu V.; Ionkin, I. L.

2017-11-01

One of the ways to increase the efficiency of using fuels is to create highly efficient domestic energy equipment, in particular small-sized hot-water boilers in autonomous heating systems. Increasing the efficiency of the boiler requires a reduction in the temperature of the flue gases leaving, which, in turn, can be achieved by installing additional heating surfaces. The purpose of this work was to determine the principal design solutions and to develop a draft design for a high-efficiency 3-MW hot-water boiler using crude oil as its main fuel. Ensuring a high efficiency of the boiler is realized through the use of an external remote economizer, which makes it possible to reduce the dimensions of the boiler, facilitate the layout of equipment in a limited size block-modular boiler house and virtually eliminate low-temperature corrosion of boiler heat exchange surfaces. In the article the variants of execution of the water boiler and remote economizer are considered and the preliminary design calculations of the remote economizer for various schemes of the boiler layout in the Boiler Designer software package are made. Based on the results of the studies, a scheme was chosen with a three-way boiler and a two-way remote economizer. The design of a three-way fire tube hot water boiler and an external economizer with an internal arrangement of the collectors, providing for its location above the boiler in a block-modular boiler house and providing access for servicing both a remote economizer and a hot water boiler, is proposed. Its mass-dimensional and design parameters are determined. In the software package Boiler Designer thermal, hydraulic and aerodynamic calculations of the developed fire tube boiler have been performed. Optimization of the boiler design was performed, providing the required 94% efficiency value for crude oil combustion. The description of the developed flue and fire-tube hot water boiler and the value of the main design and technical and

5. Test of a small domestic boiler using different pellets

International Nuclear Information System (INIS)

Dias, J.; Costa, M.; Azevedo, J.L.T.

2004-01-01

This paper presents results from an experimental study performed on a 13 kW th commercial domestic boiler using pellets as fuel. Four different types of pellets were used and, for each one, the boiler was tested as a function of its capacity and the fan regulation affecting excess air. Measurements were performed for boiler heat load, pellet consumption rate, flue-gas temperature and composition. Mass balances allowed the calculation of the flue-gas flow rate and associated heat losses. Losses from incomplete combustion have also been quantified. Under boiler steady-state conditions the flue-gas O 2 concentration changes with boiler load and ventilation due to the regulation scheme of the boiler. Flue-gas CO shows a minimum for values of O 2 in the flue-gases of about 13%. NO x emissions are independent of excess air for low values of nitrogen in the fuel whereas, for larger values, NO x emissions increase with the O 2 present in the combustion products. The fractional conversion of the pellet nitrogen into NO x is in line with literature data. The boiler start-up was characterised by the temperature evolution inside and above the bed showing the propagation of combustion in the bed during about 10 min. During boiler start-up, a maximum in CO emissions was observed which is associated with the maximum combustion intensity, as typified by the flue-gas O 2 concentration and temperature, regardless the pellet type. (Author)

6. Boilers, evaporators, and condensers

International Nuclear Information System (INIS)

Kakac, S.

1991-01-01

This book reports on the boilers, evaporators and condensers that are used in power plants including nuclear power plants. Topics included are forced convection for single-phase side heat exchangers, heat exchanger fouling, industrial heat exchanger design, fossil-fuel-fired boilers, once through boilers, thermodynamic designs of fossil fuel-first boilers, evaporators and condensers in refrigeration and air conditioning systems (with respect to reducing CFC's) and nuclear steam generators

7. Once-through integral system (OTIS): Final report

International Nuclear Information System (INIS)

Gloudemans, J.R.

1986-09-01

A scaled experimental facility, designated the once-through integral system (OTIS), was used to acquire post-small break loss-of-coolant accident (SBLOCA) data for benchmarking system codes. OTIS was also used to investigate the application of the Abnormal Transient Operating Guidelines (ATOG) used in the Babcock and Wilcox (B and W) designed nuclear steam supply system (NSSS) during the course of an SBLOCA. OTIS was a single-loop facility with a plant to model power scale factor of 1686. OTIS maintained the key elevations, approximate component volumes, and loop flow resistances, and simulated the major component phenomena of a B and W raised-loop nuclear plant. A test matrix consisting of 15 tests divided into four categories was performed. The largest group contained 10 tests and was defined to parametrically obtain an extensive set of plant-typical experimental data for code benchmarking. Parameters such as leak size, leak location, and high-pressure injection (HPI) shut-off head were individually varied. The remaining categories were specified to study the impact of the ATOGs (2 tests), to note the effect of guard heater operation on observed phenomena (2 tests), and to provide a data set for comparison with previous test experience (1 test). A summary of the test results and a detailed discussion of Test 220100 is presented. Test 220100 was the nominal or reference test for the parametric studies. This test was performed with a scaled 10-cm 2 leak located in the cold leg suction piping

8. Dynamic and control of a once through steam generator

International Nuclear Information System (INIS)

Gomes, Arivaldo Vicente

1979-01-01

This paper presents a non linear distributed parameter model for the dynamics and feedback control of a large countercurrent heat exchanger used as a once through steam generator for a breeder reactor power plant. A convergent, implicit method has been developed to solve simultaneously the equations of conservation of mass, momentum and energy. The model, applicable to heat exchanger systems in general, has been used specifically to study the performance of a once-through steam generator with respect to its load following ability and stability of throttle steam temperature and pressure. (author)

9. Once-through cycle, supercritical-pressure light water cooled reactor concept

Energy Technology Data Exchange (ETDEWEB)

Oka, Y.; Koshizuka, S. [Tokyo Univ., Tokai, Ibaraki (Japan). Nuclear Engineering Research Lab

2001-07-01

Concept of once-through cycle, supercritical-pressure light water cooled reactors was developed. The research covered major aspects of conceptual design such as cores of thermal and fast reactors, plant system and heat balance, safety system and criteria, accident and transient analysis, LOCA, PSA, plant control and start-up. The advantages of the reactor lie in the compactness of the plant from high specific enthalpy of supercritical water, the simplicity of the once-through cycle and the experiences of major component technologies which are based on supercritical fossil-fired power plants and LWRs. The operating temperatures of the major components are within the experience in spite of high coolant outlet temperature. The once-through cycle is compatible with the tight fuel lattice fast reactor because of high head pumps and small coolant flow rate. (author)

10. Once-through cycle, supercritical-pressure light water cooled reactor concept

International Nuclear Information System (INIS)

Oka, Y.; Koshizuka, S.

2001-01-01

Concept of once-through cycle, supercritical-pressure light water cooled reactors was developed. The research covered major aspects of conceptual design such as cores of thermal and fast reactors, plant system and heat balance, safety system and criteria, accident and transient analysis, LOCA, PSA, plant control and start-up. The advantages of the reactor lie in the compactness of the plant from high specific enthalpy of supercritical water, the simplicity of the once-through cycle and the experiences of major component technologies which are based on supercritical fossil-fired power plants and LWRs. The operating temperatures of the major components are within the experience in spite of high coolant outlet temperature. The once-through cycle is compatible with the tight fuel lattice fast reactor because of high head pumps and small coolant flow rate. (author)

11. Air emissions of small-scale (< 10 MW) biomass boilers. Review of three field tests

International Nuclear Information System (INIS)

Autret, E.

2011-01-01

Objectives of greenhouse gases emission reduction, which encourages bio-energy development for heat purposes, are compatible with air-quality policies if the concept of clean biomass combustion is applied. This paper presents actual emission levels of atmospheric pollutants of small-scale ( 2 , NO x , fine particulate matters, metallic compounds. Installation design (power, flue-gas cleaning techno logy) also has a major impact on organic pollutants and fine particulate matter emissions. A large majority of boilers have very low emission levels. Guidelines are finally stated to keep on promoting small-scale biomass boilers in order to be air-quality compatible and efficient to fight climate change. (author)

12. DYNAM, Once Through Boiling Flow with Steam Superheat, Laplace Transformation

International Nuclear Information System (INIS)

Schlueter, G.; Efferding, L.E.

1973-01-01

1 - Description of problem or function: DYNAM performs a dynamic analysis of once-through boiling flow oscillations with steam superheat. The model describing the superheat regime (single- phase, variable density fluid) for subcritical pressure operation is also applicable to the study of once-through operation using supercritical pressure water. 2 - Method of solution: Linearized partial differential conservation equations are solved using Laplace transformation of the temporal terms and integration of the spatial variations. DYNAM is written in complex variable notation. 3 - Restrictions on the complexity of the problem - Maxima of: 30 intervals used to describe the power distribution in the non-boiling and boiling regions, 29 boiling nodes, 7 intervals and corresponding friction multipliers read in per case, 14 exit qualities read in per case, 40 superheat nodes, 10 coefficients read in for the phi 2 vs, x-polynomial fit, 48 frequencies at which open-loop frequency response is desired, 48 frequencies at which signal output is desired

13. Uranium savings on a once through PWR fuel cycle

International Nuclear Information System (INIS)

Cupo, J.V.

1980-01-01

A number of alternatives which have the greatest potential for near term savings with minimum plant and fuel modifications have been examined at Westinghouse as part of continued internal assessment and part of NASAP study conducted for DOE pertaining to uranium utilization in a once through PWR fuel cycle. The alternatives which could be retrofitted to existing reactors were examined in more detail in the evaluation since they would have the greater near term impact on U savings

14. Heavy water reactors on the once-through uranium cycle

International Nuclear Information System (INIS)

1978-05-01

This paper presents preliminary technical and economic data to INFCE on the once-through uranium fuel cycle for use in early comparisons of alternate nuclear systems. The denatured thorium fuel cycle is discussed in a companion paper. Information for this paper was developed under an ongoing program, and more complete reporting of the evaluation of the heavy water reactor and its fuel cycles is planned toward the end of the year

15. Comparative analysis of heat pump and biomass boiler for small detached house heating

Directory of Open Access Journals (Sweden)

Olkowski Tomasz

2017-01-01

Full Text Available The purpose of the work is to answer the question - which of the two selected heat sources is more economically beneficial for small detached house: heat pump or biomass boiler fuelled with wood-pellets? The comparative analysis of these sources was carried out to discuss the issue. First, cost of both, equipment and operation of selected heat systems were analysed. Additionally, CO2 emission levels associated with these heat systems were determined. The comparative analysis of the costs of both considered heat systems showed that equipment cost of heat pump system is considerably bigger than the cost of biomass boiler system. The comparison of annual operation costs showed that heat pump operation cost is slightly lower than operation cost of biomass boiler. The analysis of above results shows that lower operation cost of heat pump in comparison with biomass boiler cost lets qualify heat pump as more economically justified only after 38 years of work. For both analysed devices, CO2 emission levels were determined. The considerations take into account the fact that heat pump consumes electricity. It is mostly generated through combustion of coal in Poland. The results show that in Poland biomass boiler can be described as not only more economically justified system but also as considerably more ecological.

16. Comparative analysis of heat pump and biomass boiler for small detached house heating

Science.gov (United States)

Olkowski, Tomasz; Lipiński, Seweryn; Olędzka, Aneta

2017-10-01

The purpose of the work is to answer the question - which of the two selected heat sources is more economically beneficial for small detached house: heat pump or biomass boiler fuelled with wood-pellets? The comparative analysis of these sources was carried out to discuss the issue. First, cost of both, equipment and operation of selected heat systems were analysed. Additionally, CO2 emission levels associated with these heat systems were determined. The comparative analysis of the costs of both considered heat systems showed that equipment cost of heat pump system is considerably bigger than the cost of biomass boiler system. The comparison of annual operation costs showed that heat pump operation cost is slightly lower than operation cost of biomass boiler. The analysis of above results shows that lower operation cost of heat pump in comparison with biomass boiler cost lets qualify heat pump as more economically justified only after 38 years of work. For both analysed devices, CO2 emission levels were determined. The considerations take into account the fact that heat pump consumes electricity. It is mostly generated through combustion of coal in Poland. The results show that in Poland biomass boiler can be described as not only more economically justified system but also as considerably more ecological.

17. Design of a small scale boiler package for testing high moisture content biofuels

Energy Technology Data Exchange (ETDEWEB)

Proctor, Andrew

2005-07-01

This report presents the results of a project to design a prototype, small-scale boiler (0.88 MWth output) to enable clean and efficient combustion of high moisture content (>30%) biomass fuels. The boiler was based on an open bottom smoke tube design, modified to incorporate water tubes in the combustion chamber running from front to back. These were added to support refractory bricks to create an extra pass in the boiler combustion chamber such that the reflected heat from the refractory increased the rate of evaporation of moisture from the fuel. A chain grate stoker was employed. The combustion tests involved three biofuels: wood pellets with a low moisture content (8-10%) (to provide combustion rates for a commercially proven biofuel); wood chips from forestry waste with a 30-40% moisture content; and spent mushroom compost with 70-75% moisture. The tests on the wood chips required a number of modifications to the fuel feeding system and to the boiler in order to achieve limited success and the tests with the mushroom compost were unsuccessful due to the combination of the high moisture content and the fuel's low calorific value. Experience gained with the wood chips suggested a number of improvements for a future boiler design. As well as describing the experimental work and test results, the report offers an economic analysis (capital costs, fuel costs, running costs) of the scheme.

18. Once-through hybrid sulfur process for nuclear hydrogen production

International Nuclear Information System (INIS)

Jeong, Y. H.

2008-01-01

Increasing concern about the global climate change spurs the development of low- or zero-carbon energy system. Nuclear hydrogen production by water electrolysis would be the one of the short-term solutions, but low efficiency and high production cost (high energy consumption) is the technical hurdle to be removed. In this paper the once-through sulfur process composed of the desulfurization and the water electrolysis systems is proposed. Electrode potential for the conventional water electrolysis (∼2.0 V) can be reduced significantly by the anode depolarization using sulfur dioxide: down to 0.6 V depending on the current density This depolarized electrolysis is the electrolysis step of the hybrid sulfur process originally proposed by the Westinghouse. However; recycling of sulfur dioxide requires a high temperature heat source and thus put another technical hurdle on the way to nuclear hydrogen production: the development of high temperature nuclear reactors and corresponding sulfuric acid decomposition system. By the once-through use of sulfur dioxide rather than the closed recycle, the hurdle can be removed. For the sulfur feed, the desulfurization system is integrated into the water electrolysis system. Fossil fuels include a few percent of sulfur by weight. During the refinement or energy conversion, most of the sulfur should be separated The separated sulfur can be fed to the water electrolysis system and the final product would be hydrogen and sulfuric acid, which is number one chemical in the world by volume. Lowered electrode potential and additional byproduct, the sulfuric acid, can provide economically affordable hydrogen. In this study, the once-through hybrid sulfur process for hydrogen production was proposed and the process was optimized considering energy consumption in electrolysis and sulfuric acid concentration. Economic feasibility of the proposed process was also discussed. Based on currently available experimental data for the electrode

19. Once-through thorium cycles in Candu reactors

International Nuclear Information System (INIS)

Milgram, M.S.

1982-01-01

In once-through thorium cycles pure thorium fuel bundles can be irradiated conjointly with uranium fuel bundles in a CANDU reactor with parameters judiciously chosen such that the overall fuel cycle cost is competitive with other possibilities - notably low-enriched uranium. Uranium 233 can be created and stockpiled for possible future use with no imperative that it be used unless future conditions warrant, and a stockpile can be begun independently of the state of reprocessing technology. The existence and general properties of these cycles are discussed

20. CFD Modelling of Biomass Combustion in Small-Scale Boilers. Final Report

Energy Technology Data Exchange (ETDEWEB)

Xue-Song Bai; Griselin, Niklas; Klason, Torbern; Nilsson, Johan [Lund Inst. of Tech. (Sweden). Dept. of Heat and Power Engineering

2002-10-01

This project deals with CFD modeling of combustion of wood in fixed bed boilers. A flamelet model for the interaction between turbulence and chemical reactions is developed and applied to study small-scale boiler. The flamelet chemistry employs 43 reactive species and 174 elementary reactions. It gives detailed distributions of important species such as CO and NO{sub x} in the flow field and flue gas. Simulation of a small-scale wood fired boiler measured at SP Boraas (50 KW) shows that the current flamelet model yields results agreeable to the available experimental data. A detailed chemical kinetic model is developed to study the bed combustion process. This model gives boundary conditions for the CFD analysis of gas phase volatile oxidation in the combustion chambers. The model combines a Functional Group submodel with a Depolymerisation, Vaporisation and Crosslinking submodel. The FG submodel simulates how functional groups decompose and form light gas species. The DVC submodell predicts depolymerisation and vaporisation of the macromolecular network and this includes bridge breaking and crosslinking processes, where the wood structure breaks down to fragments. The light fragments form tar and the heavy ones form metaplast. Two boilers firing wood log/chips are studied using the FG-DVC model, one is the SP Boraas small-scale boiler (50 KW) and the other is the Sydkraft Malmoe Vaerme AB's Flintraennan large-scale boiler (55 MW). The fix bed is assumed to be two zones, a partial equilibrium drying/devolatilisation zone and an equilibrium zone. Three typical biomass conversion modes are simulated, a lean fuel combustion mode, a near-stoichiometric combustion and a fuel rich gasification mode. Detailed chemical species and temperatures at different modes are obtained. Physical interpretation is provided. Comparison of the computational results with experimental data shows that the model can reasonably simulate the fixed bed biomass conversion process. CFD

1. Supercritical-pressure, once-through cycle light water cooled reactor concept

International Nuclear Information System (INIS)

Oka, Yoshiaki; Koshizuka, Seiichi

2001-01-01

The purpose of the study is to develop new reactor concepts for the innovation of light water reactors (LWR) and fast reactors. Concept of the once-through coolant cycle, supercritical-pressure light water cooled reactor was developed. Major aspects of reactor design and safety were analysed by the computer codes which were developed by ourselves. It includes core design of thermal and fast reactors, plant system, safety criteria, accident and transient analysis, LOCA, PSA, plant control, start up and stability. High enthalpy rise as supercritical boiler was achieved by evaluating the cladding temperature directly during transients. Fundamental safety principle of the reactor is monitoring coolant flow rate instead of water level of LWR. The reactor system is compact and simple because of high specific enthalpy of supercritical water and the once-through cycle. The major components are similar to those of LWR and supercritical thermal plant. Their temperature are within the experiences in spite of the high outlet coolant temperature. The reactor is compatible with tight fuel lattice fast reactor because of the high head pumps and low coolant flow rate. The power rating of the fast reactor is higher than the that of thermal reactor because of the high power density. (author)

2. Digital simulation for nuclear once-through steam generators

International Nuclear Information System (INIS)

Chen, A.T.

1976-01-01

Mathematical models for calculating the dynamic response of the Oconee type once through steam generator (OTSG) and the integral economizer once through steam generator (IEOTSG) was developed and presented in this dissertation. Linear and nonlinear models of both steam generator types were formulated using the state variable, lumped parameter approach. Transient and frequency responses of system parameters were calculated for various perturbations from both the primary coolant side and the secondary side. Transients of key parameters, including primary outlet temperature, superheated steam outlet temperature, boiling length/subcooled length and steam pressure, were generated, compared and discussed for both steam generator types. Frequency responses of delta P/sub s//deltaT/sub pin/ of the linear OTSG model were validated by using the dynamic testing results obtained at the Oconee I nuclear power station. A sensitivity analysis in both the time and the frequency domains was performed. It was concluded that the mathematical and computer models developed in this dissertation for both the OTSG and the IEOTSG are suitable for overall plant performance evaluation and steam generator related component/system design analysis for nuclear plants using either type of steam generator

3. 'Once through' cycles in the pebble bed HTR

International Nuclear Information System (INIS)

Teuchert, E.

1977-12-01

In the pebble bed HTR the 'Once Through' cycles achieve a favorable conservation of uranium resources due to their high burnup and due to the relatively low fissile inventory. A detailed study is given for cycles with highly enriched uranium and thorium, 20% enriched uranium and thorium, and for the low (approximately 8%) enriched cycle. The recommended cycle is based on the known THTR fuel element in the Th/U (93%) cycle. The variant with separate Seed elements and Breed elements presents the best pioneer in view of later recycling and thermal breeding. The minimum proliferation risk is achieved in the Th/U (20%) cycle basing on the fuel element type of the AVR, due to the low amount and high denaturization of the disloaded plutonium. (orig.) [de

4. Once-through uranium thorium fuel cycle in CANDU reactors

International Nuclear Information System (INIS)

Ozdemir, S.; Cubukcu, E.

2000-01-01

In this study, the performance of the once-through uranium-thorium fuel cycle in CANDU reactors is investigated. (Th-U)O 2 is used as fuel in all fuel rod clusters where Th and U are mixed homogeneously. CANDU reactors have the advantage of being capable of employing various fuel cycle options because of its good neutron economy, continuous on line refueling ability and axial fuel replacement possibility. For lattice cell calculations transport code WIMS is used. WIMS cross-section library is modified to achieve precise lattice cell calculations. For various enrichments and Th-U mixtures, criticality, heavy element composition changes, diffusion coefficients and cross-sections are calculate. Reactor core is modeled by using the diffusion code CITATION. We conclude that an overall saving of 22% in natural uranium demand can be achieved with the use of Th cycle. However, slightly enriched U cycle still consumes less natural Uranium and is a lot less complicated. (author)

5. Small-Scale Pellet Boiler with Thermoelectric Generator

Energy Technology Data Exchange (ETDEWEB)

Moser, Wilhelm; Friedl, Guenther; Haslinger, Walter [Austrian Bioenergy Centre GmbH, Wieselburg (Austria); Hofbauer, Hermann [Vienna Univ. of Technology (Austria). Inst. of Chemical Engineering

2006-07-15

Pellet burners need auxiliary electrical power to provide CO{sub 2}-balanced heat in a comfortable and environment-friendly way. The idea is to produce this and some extra electricity within the furnace in order to save resources and to gain operation reliability and independency. Thermoelectric generators (TEGs) allow the direct conversion of heat to electrical power to a certain extent. They have the advantages of a maintenance-free long life and soundless operation without moving parts or any working fluid. A novel kind of decentralised small-scale biomass-based combined heat and power generation will be developed. The basic system allows grid-independent operation of automatically running biomass furnaces including fuel delivery from storage and circulating the cooling respectively heating water or air. The advanced system also provides electricity for network supply or for other electrical devices and is an additional benefit.

6. Technical and economic feasibility of alternative fuel use in process heaters and small boilers

Energy Technology Data Exchange (ETDEWEB)

1980-02-01

The technical and economic feasibility of using alternate fuels - fuels other than oil and natural gas - in combustors not regulated by the Powerplant and Industrial Fuel Use Act of 1978 (FUA) was evaluated. FUA requires coal or alternate fuel use in most large new boilers and in some existing boilers. Section 747 of FUA authorizes a study of the potential for reduced oil and gas use in combustors not subject to the act: small industrial boilers with capacities less than 100 MMBtu/hr, and process heat applications. Alternative fuel use in combustors not regulated by FUA was examined and the impact of several measures to encourage the substitution of alternative fuels in these combustors was analyzed. The primary processes in which significant fuel savings can be achieved are identified. Since feedstock uses of oil and natural gas are considered raw materials, not fuels, feedstock applications are not examined in this analysis. The combustors evaluated in this study comprise approximately 45% of the fuel demand projected in 1990. These uses would account for more than 3.5 million barrels per day equivalent fuel demand in 1990.

7. Technical-and-Economic Efficiency of Draft Enriched with Oxygen in Small-Capacity Heating Boilers

Directory of Open Access Journals (Sweden)

P. Ratnikov

2013-01-01

Full Text Available Data on complex experimental and theoretical investigations pertaining to efficiency of oxygen-enriched draft in the small-capacity heating boilers as exemplified by the plant HEIZA (HW-S-10/K have been presented in the paper. The paper provides a calculation model of heating processes in heat generator burner (as exemplified by HEIZA plant. Simulation of heating processes in the operational zone has been executed in paper. The experimental data have proved model adequacy. The calculation scheme of the plant will be used in future for determination of power and ecological efficiency of draft enrichment with oxygen.

8. Test firing and emissions analysis of densified RDF (d-RDF) in a small power boiler

International Nuclear Information System (INIS)

1991-01-01

A test program to determine the feasibility of burning densified refuse-derived fuel in a small power boiler has been successfully completed. The first phase of the contract entailed assembly and assessment of information on d-RDF combustion from other studies, compilation of existing and proposed regulations for the seven sponsoring Great Lakes states: Illinois, Indiana, Iowa, Michigan, Minnesota, Ohio, and Wisconsin, location of d-RDF and waste paper pellet manufacturers in the region, and fuel supply/test site selection. The second phase entailed conducting test burns with two types of d-RDF composed of municipal solid waste (MSW) and one type of d-RDF composed of waste cardboard. The tests were conducted at a small boiler located at Dordt College in Sioux Center, Iowa. The boiler is not equipped with any pollution control equipment and the emission measurements therefore represent those from an uncontrolled source. Results demonstrated that a particulate control system is required to meet the standard set by Iowa for less than 0.6 lbs particulate matter per million BTU heat input. With the planned addition of a baghouse system for control, the facility should meet all existing State limits for emissions levels. Air toxics concentrations including metals, dioxins, furans, and PCBs were low relative to other municipal waste combustors and will be further reduced after installation of baghouse filter equipment. The key remaining concerns relate to the acceptable level of HCl emissions which are a strong function of the plastic content of fuel raw material and SO 2 which varies widely with fuel raw material composition

9. Use of grey relational analysis to assess and optimize small biomass boilers

International Nuclear Information System (INIS)

Moran, J.; Granada, E.; Miguez, J.L.; Porteiro, J.

2006-01-01

This paper presents a new methodology for the evaluation of the environmental and economic feasibility of combustion of different biomass fuels in small boilers. The study focuses on pellets as the basic co-firing product and forest residues as the complementary product. Although the co-firing of forest residues can be economically profin, it is difficult to evaluate the general economic advantages due to the worsening of combustion in terms of performance and emissions caused by the presence of the forest residues in the fuel mixture. The grey relational analysis of different energetic and emission variables and also residue prices allows for the definition of a new single variable called the grey relational grade. Thus, evaluation and optimization of complicated multiple responses can be converted into the optimization of a standardised single variable. Experimental analyses by means of the Grey theory of different forest residues have revealed the possibility of co-firing crust of pine combined with wood pellets as a way of reducing fuel costs, keeping performance and emissions within average standards in small pellet boilers. (author)

10. Low temperature corrosion in bark fuelled, small boilers; Laagtemperaturkorrosion i barkeldade, mindre pannor

Energy Technology Data Exchange (ETDEWEB)

Lindau, Leif; Goldschmidt, Barbara [Sycon Energikonsult AB, Malmoe (Sweden)

2002-04-01

A number of small (3-12 MW), new biofuel boiler plants in South Sweden, and (at least) in Austria, have suffered a high (wastage of mm/yrs.) corrosion rate on the low temperature boiler side. This problem has been investigated with respect to its occurrence and its character by contacts with operators, by plant inspections, and by analysis of cold side deposits. The plants affected have low feed water temperatures (< 100 deg C ). The plants fire most types of Swedish biofuel: chips, bark, hog fuel, and 'GROT'(=twigs and tops). The results found give basis for a hypothesis that the corrosion results from the presence of an aqueous phase in the deposits, this phase being stabilized by dissolved salts having high solubility. It then follows that for each salt, there is a critical relative humidity (calculated from the flue gas water partial pressure and the cooling surface temperature as is common practice among boiler engineers) for both the presence of the aqueous phase and the corrosion. Some critical single salts, ZnC12 and CaC12 have been identified, and they give critical 'relative humidities' of 5% and 18% respectively. These figures are a lower bound. The corresponding figure, derived from the practical experience and the reported plant operational data, is between 20 and 30%. Corrosion tests have been carried out by exposing an air-cooled probe in the fluegases at a 12 MW boiler at Saevelundsverket in Alingsaas, and the material wastage at different temperatures has been measured with a profilometer. The high corrosion rates were reproduced in the tests for high relative humidities. The corrosion rate was small and not measurable (<0.1 mm/yr) for relative humidity < 22%. The work shows by means of indirect evidence that the corrosion critical components are ZnCl{sub 2} and possibly CaCl{sub 2} as well. The practical engineering design criterion derived from the work is that the relative humidity (calculated from the flue gas water partial

11. Thermal-Hydraulic Analysis of a Once-Through Steam Generator Considering Performance Degradation

Energy Technology Data Exchange (ETDEWEB)

Han, Hun Sik; Kang, Han Ok; Yoon, Ju Hyeon; Kim, Young In; Song, Jae Seung; Kim, Keung Koo [KAERI, Daejeon (Korea, Republic of)

2016-05-15

Several countries have entered into a global race for the commercialization of SMRs, and considerable research and development have been implemented. Among the various reactor designs, many SMRs have adopted an integral type pressurized water reactor (PWR) to enhance the nuclear safety and system reliability. In the integral reactor design, a single reactor pressure vessel contains primary system components such as fuel and core, steam generators, pumps, and a pressurizer. For the component integration into a reactor vessel, it is important to design each component as small as possible. Thus, it is a common practice to employ a once-through steam generator in the integral reactor design due to its advantages in compactness. In general, gradual degradation in thermal-hydraulic performance of the steam generator occurs with time, and it changes slowly the operating point of the steam generator during plant lifetime. Numerical solutions are acquired to evaluate the thermal-hydraulic performance of the steam generator at various AUFs. The design results obtained show that the average tube length of the steam generator is augmented with the increase of design margin to compensate for the design uncertainties and heat transfer area reduction by plugging, fouling, etc. A helically coiled tube once-through steam generator with 30% design margin is considered for comparison of thermal-hydraulic performances according to the degradation rate.

12. Thermal-Hydraulic Analysis of a Once-Through Steam Generator Considering Performance Degradation

International Nuclear Information System (INIS)

Han, Hun Sik; Kang, Han Ok; Yoon, Ju Hyeon; Kim, Young In; Song, Jae Seung; Kim, Keung Koo

2016-01-01

Several countries have entered into a global race for the commercialization of SMRs, and considerable research and development have been implemented. Among the various reactor designs, many SMRs have adopted an integral type pressurized water reactor (PWR) to enhance the nuclear safety and system reliability. In the integral reactor design, a single reactor pressure vessel contains primary system components such as fuel and core, steam generators, pumps, and a pressurizer. For the component integration into a reactor vessel, it is important to design each component as small as possible. Thus, it is a common practice to employ a once-through steam generator in the integral reactor design due to its advantages in compactness. In general, gradual degradation in thermal-hydraulic performance of the steam generator occurs with time, and it changes slowly the operating point of the steam generator during plant lifetime. Numerical solutions are acquired to evaluate the thermal-hydraulic performance of the steam generator at various AUFs. The design results obtained show that the average tube length of the steam generator is augmented with the increase of design margin to compensate for the design uncertainties and heat transfer area reduction by plugging, fouling, etc. A helically coiled tube once-through steam generator with 30% design margin is considered for comparison of thermal-hydraulic performances according to the degradation rate

13. A creep life assessment method for boiler pipes using small punch creep test

International Nuclear Information System (INIS)

Izaki, Toru; Kobayashi, Toshimi; Kusumoto, Junichi; Kanaya, Akihiro

2009-01-01

The small punch creep (SPC) test is considered as a highly useful method for creep life assessment for high temperature plant components. SPC uses miniature-sized specimens and does not cause any serious sampling damages, and its assessment accuracy is at a high level. However, in applying the SPC test to the residual creep life assessment of the boiler in service, there are some issues to be studied. In order to apply SPC test to the residual creep life assessment of the 2.25Cr-1Mo steel boiler pipe, the relationship between uniaxial creep stress and the SPC test load has been studied. The virgin material, pre-crept, weldment and service aged samples of 2.25Cr-1Mo steel were tested. It was confirmed that the relationship between uniaxial creep stress and the SPC test load at the same rupture time can be described as a single straight line independent of test conditions and materials. Therefore a life assessment is possible by using SPC test in place of uniaxial creep tests. The creep life assessment using SPC was applied to actual thermal power plant components which are in service.

14. Combustion of Corn Stover Bales in a Small 146-kW Boiler

Directory of Open Access Journals (Sweden)

Joey Villeneuve

2011-07-01

Full Text Available Spring harvested corn stover was used for direct combustion in a 146 kW dual chamber boiler designed for wood logs. Stover had a very low moisture content (6.83 ± 0.17%, a gross calorific value (GCV of 18.57 MJ/kg of dry matter (±0.32 MJ/kg DM and an ash content of 5.88% (±1.15%. Small stover bales (8.83 ± 0.90 kg were placed manually in the upper combustion chamber at a rate of 10.5 to 12.8 kg/h over a 24-h period, with three replications, and compared to a control wood combustion trial (12.1 kg/h during 24 h. The overall heat transfer efficiency for stover was lower than for wood (57% vs. 77%. Stover bales produced on average 7.5% ash which included about 2% of unburned residues while wood produced 1.7% ash. CO gas emissions averaged 1324 mg/m³ for stover (118 mg/m³ for wood. The corn stover showed a good calorific potential, but it would have to be densified and the boiler should be modified to improve airflow, completeness of combustion and handling of the large amount of ash formed.

15. Time-resolved analysis of primary volatile emissions and secondary aerosol formation potential from a small-scale pellet boiler

Science.gov (United States)

Czech, Hendryk; Pieber, Simone M.; Tiitta, Petri; Sippula, Olli; Kortelainen, Miika; Lamberg, Heikki; Grigonyte, Julija; Streibel, Thorsten; Prévôt, André S. H.; Jokiniemi, Jorma; Zimmermann, Ralf

2017-06-01

Small-scale pellet boilers and stoves became popular as a wood combustion appliance for domestic heating in Europe, North America and Asia due to economic and environmental aspects. Therefore, an increasing contribution of pellet boilers to air pollution is expected despite their general high combustion efficiency. As emissions of primary organic aerosol (POA) and permanent gases of pellet boilers are well investigated, the scope of this study was to investigate the volatile organic emissions and the formation potential of secondary aerosols for this type of appliance. Fresh and aged emissions were analysed by a soot-particle aerosol time-of-flight mass spectrometry (SP-AMS) and the molecular composition of the volatile precursors with single-photon ionisation time-of-flight mass spectrometry (SPI-TOFMS) at different pellet boiler operation conditions. Organic emissions in the gas phase were dominated by unsaturated hydrocarbons while wood-specific VOCs, e.g. phenolic species or substituted furans, were only detected during the starting phase. Furthermore, organic emissions in the gas phase were found to correlate with fuel grade and combustion technology in terms of secondary air supply. Secondary organic aerosols of optimised pellet boiler conditions (OPT, state-of-the-art combustion appliance) and reduced secondary air supply (RSA, used as a proxy for pellet boilers of older type) were studied by simulating atmospheric ageing in a Potential Aerosol Mass (PAM) flow reactor. Different increases in OA mass (55% for OPT, 102% for RSA), associated with higher average carbon oxidation state and O:C, could be observed in a PAM chamber experiment. Finally, it was found that derived SOA yields and emission factors were distinctly lower than reported for log wood stoves.

16. Development and test of small-scale batch-fired straw boilers in Denmark

International Nuclear Information System (INIS)

Kristensen, E.F.; Kristensen, J.K.

2004-01-01

In Denmark, government subsidies for the testing and installation of biomass-fired boilers were available for the period from 1995 until 2002. Each boiler type had to pass an official approval test to achieve subsidy. The combustion abilities of the boiler were optimized prior to the test. The main aim of this subsidy was to encourage the development of energy-efficient and environmentally friendly boilers. The scheme was therefore organized in such a way that the greatest subsidies were awarded for boilers with high efficiency and low emissions. This goal has in effect been achieved for batch-fired straw boilers, where the typical efficiency has been increased from about 75% in 1995 to about 87% in 2002. Similarly, the carbon monoxide emissions have been reduced from 5000 ppm (reference value 10% O 2 ) in 1995 to less than 1000 ppm in 2002. These improvements are mainly due to better insulation inside the combustion chamber, more efficient techniques for supplying air to the combustion process, improved cooling of the flue gas, and optimization of the electronic control unit for the air supply

17. Boiler water regime

Science.gov (United States)

Khavanov, Pavel; Chulenyov, Anatoly

2017-10-01

Active development of autonomous heating the past 25 years has led to the widespread use of hot-water boilers of small capacity up to 2.5 MW. Rational use of the design of autonomous sources of heating boilers design features significantly improve their technical, economic and operational performance. This publication reviewed and analyzed a number of features of the design, operation and exploitation of boilers of small capacity, significantly affecting the efficiency and reliability of their application.

18. Study on the structure optimization scheme design of a double-tube once-through steam

International Nuclear Information System (INIS)

Wei, Xinyu; Wu, Shifa; Wang, Pengfei; Zhao, Fuyu

2016-01-01

A double-tube once-through steam generator (DOTSG) consisting of an outer straight tube and an inner helical tube is studied in this work. First, the structure of the DOTSG is optimized by considering two different objective functions. The tube length and the total pressure drop are considered as the first and second objective functions, respectively. Because the DOTSG is divided into the subcooled, boiling, and superheated sections according to the different secondary fluid states, the pitches in the three sections are defined as the optimization variables. A multi-objective optimization model is established and solved by particle swarm optimization. The optimization pitch is small in the subcooled region and superheated region, and large in the boiling region. Considering the availability of the optimum structure at power levels below 100% full power, we propose a new operating scheme that can fix the boundaries between the three heat-transfer sections. The operation scheme is proposed on the basis of data for full power, and the operation parameters are calculated at low power level. The primary inlet and outlet temperatures, as well as flow rate and secondary outlet temperature are changed according to the operation procedure

19. Study on the structure optimization scheme design of a double-tube once-through steam

Energy Technology Data Exchange (ETDEWEB)

Wei, Xinyu; Wu, Shifa; Wang, Pengfei; Zhao, Fuyu [Dept. of Nuclear Science and Technology, Xi' an Jiaotong University, Xi' an (China)

2016-08-15

A double-tube once-through steam generator (DOTSG) consisting of an outer straight tube and an inner helical tube is studied in this work. First, the structure of the DOTSG is optimized by considering two different objective functions. The tube length and the total pressure drop are considered as the first and second objective functions, respectively. Because the DOTSG is divided into the subcooled, boiling, and superheated sections according to the different secondary fluid states, the pitches in the three sections are defined as the optimization variables. A multi-objective optimization model is established and solved by particle swarm optimization. The optimization pitch is small in the subcooled region and superheated region, and large in the boiling region. Considering the availability of the optimum structure at power levels below 100% full power, we propose a new operating scheme that can fix the boundaries between the three heat-transfer sections. The operation scheme is proposed on the basis of data for full power, and the operation parameters are calculated at low power level. The primary inlet and outlet temperatures, as well as flow rate and secondary outlet temperature are changed according to the operation procedure.

20. Elements of Design Consideration of Once-Through Cycle, Supercritical-Pressure Light Water Cooled Reactor

International Nuclear Information System (INIS)

Yoshiaki Oka; Sei-ichi Koshizuka; Yuki Ishiwatari; Akifumi Yamaji

2002-01-01

The paper describes elements of design consideration of supercritical-pressure, light water cooled reactors as well as the status and prospects of the research and development. It summarizes the results of the conceptual design study at the University of Tokyo from 1989. The research and development started in Japan, Europe and USA. The major advantages of the reactors are 1. Compact reactor and turbines due to high specific enthalpy of supercritical water 2.Simple plant system because of the once-through coolant cycle 3.Use of the experience of LWR and fossil-fired power plants. The temperatures of the major components such as reactor pressure vessel, coolant pipes, pumps and turbines are within the experience, in spite of the high outlet coolant temperature. 4.Similarity to LWR safety design and criteria, but no burnout phenomenon 5.Potential cost reduction due to smaller material expenditure and short construction period 6.The smallest reactor not in power rating, but in plant sizes. 7.High-thermal efficiency and low coolant flow rate because of high enthalpy rise. 8.Water cooled reactors potentially free from SCC (stress corrosion cracking) problems. 9.Compatibility of tight-fuel-lattice fast reactor core due to small coolant flow rate, potentially easy shift to fast breeder reactor without changing coolant technology. 10.Potential of producing energy products such as hydrogen and high quality hydro carbons. (authors)

1. CFD modeling of small biomass-fired boilers, second stage; CFD-modellering av mindre biobraenslepannor, etapp 2

Energy Technology Data Exchange (ETDEWEB)

Loennermark, A. [Swedish National Testing and Research Inst., Boraas (Sweden); Leckner, B. [Chalmers Univ. of Techn., Goeteborg (Sweden). Dept. of Energy Technology

2001-11-01

The purpose of the project is to study how the design of the gas combustion chamber in a small boiler for biomass affects the emissions and how computer simulations can be used to decrease harmful emissions. The aim of the first part of the project was to investigate how phenomena and processes, important for the combustion, depend on various parameters. Within the frame of that part the temperature distribution, the flow pattern and the mixing processes have been studied. In the second part the combustion and the different reactions have been studied. A number of well-equipped combustion experiments in a small biomass-fired boiler have also been conducted to obtain better information about the boundary conditions. The results have been used to verify the simulations. The gas combustion chamber of a modern boiler using down draught firing has been simulated by using two Computational Fluid Dynamics codes, SOFIE and FLUENT. The results from the simulations show that with literature values for the reaction parameters, the reaction rates are controlled by mixing. This means that the reactions are fast and all the CO and the hydrocarbons were consumed. By varying the activation energy, it is possible to reach data that are more comparable with experimental data. The effects of the bowl in the gas combustion chamber on the combustion and mixing are discussed. The effects of the temperature and the radiation are also presented.

2. The once-through mode of steam generator reflux condensation in loss of coolant accident scenarios

International Nuclear Information System (INIS)

Liao, Y.; Guentay, S.; Suckow, D.

2009-01-01

The once-through mode of steam generator reflux condensation in the presence of noncondensable gases and/or aerosols for LOCA scenarios is introduced. This phenomenon is planned to be investigated at Paul Scherrer Institute in the ARTIST/RFLX experimental program. The plausible accident scenarios associated with the once-through reflux condensation are analyzed with MELCOR to study the safety significance and the boundary conditions of this phenomenon. This work presents the recent PSI experimental and analytical work on reflux condensation: the progress of modification to the ARTIST test facility for the purpose to study reflux condensation, and the analytical model for the once-through reflux condensation in the presence of noncondensable gas using the heat and mass transfer analogy approach. Future experimental and analytical work on reflux condensation is also outlined. (author)

3. Preliminary analysis of the PreFlexMS molten salt once-through steam generator dynamics and control strategy

Science.gov (United States)

Trabucchi, Stefano; Casella, Francesco; Maioli, Tommaso; Elsido, Cristina; Franzini, Davide; Ramond, Mathieu

2017-06-01

Concentrated Solar Power plants (CSP) coupled with thermal storage have the potential to guarantee both flexible and continuous energy production, thus being competitive with conventional fossil fuel and hydro power plants, in terms of dispatchability and provision of ancillary services. Hence, the plant equipment and control design have to be focused on flexible operation on one hand, and on plant safety concerning the molten salt freezing on the other hand. The PreFlexMS European project aims to introduce a molten salt Once-Through Steam Generator (OTSG) within a Rankine cycle based power unit, a technology that has greater flexibility potential if compared to steam drum boilers, currently used in CSP plants. The dynamic modelling and simulation from the early design stages is, thus, of paramount importance, to assess the plant dynamic behavior and controllability, and to predict the achievable closed-loop dynamic performance, potentially saving money and time during the detailed design, construction and commissioning phases. The present paper reports the main results of the analysis carried out during the first part of the project, regarding the system analysis and control design. In particular, two different control systems have been studied and tested with the plant dynamic model: a decentralized control strategy based on PI controllers and a Linear Model Predictive Control (LMPC).

4. Data base for a CANDU-PHW operating on a once-through natural uranium cycle

International Nuclear Information System (INIS)

1979-07-01

This report, prepared for INFCE, describes a standard 600 MW(e) CANDU-PHW reactor operating on a once-through natural uranium fuel cycle. Subsequently, data are given for an extrapolated 1000 MW(e) design (the nominal capacity adopted for the INFCE study) operating on the same fuel cycle. (author)

5. Feasibility assessment of the once-through thorium fuel cycle for the PTVM LWR concept

International Nuclear Information System (INIS)

Rachamin, R.; Fridman, E.; Galperin, A.

2015-01-01

Highlights: • The PTVM LWR is an innovation reactor concept operating in a “breed & burn” mode. • An advanced once-through thorium fuel cycle for the PTVM LWR concept is proposed. • The PTVM LWR concept makes use of a seed-blanket geometry. • A novel fuel management scheme based on two separate fuel flow routes is analyzed. • The analysis indicates a potential for utilizing the fuel in an efficient manner. - Abstract: This paper investigates the feasibility of a once-through thorium fuel cycle for the novel reactor-design concept named the pressure tube light water reactor with variable moderator control (PTVM LWR). The PTVM LWR operates in a “breed & burn” mode, which makes it an attractive system for utilizing thorium fuel in a once-through mode. The “breed & burn” mode can emphasize the in situ generation as well as incineration of 233 U, which are the basic foundations of the once-through thorium fuel cycle. The PTVM LWR concept makes use of a seed–blanket geometry, whereby the core is divided into separated regions of thorium-based fuel channel assemblies (blanket) and low-enriched uranium (LEU) based fuel channel assemblies (seed). A novel fuel in-core management scheme based on two separate fuel flow routes (i.e., seed route and blanket route) is proposed and analyzed. Neutronic performance analysis indicates that the proposed novel fuel in-core management scheme has the potential to utilize both LEU- and thorium-based fuel in an efficient manner. The once-through thorium cycle, presented and discussed in this paper, provide interesting research leads and can serve as a bridge between current LEU-based fuel cycles and a thorium fuel cycle based on recycling of 233 U

6. Dynamic analysis of once-through and closed fuel cycle economics using Monte Carlo simulation

Energy Technology Data Exchange (ETDEWEB)

Choi, Sungyeol, E-mail: csy@kaeri.re.kr; Lee, Hyo Jik, E-mail: hyojik@kaeri.re.kr; Ko, Won Il, E-mail: nwiko@kaeri.re.kr

2014-10-01

Highlights: • Dynamic behavior of system costs, both reactor and fuel cycle costs, is analyzed. • Relative economics of once-through and closed fuel cycles is explored. • Probabilistic approaches are adopted for levelized electricity generation costs. • Main cost drivers for cost gaps between once-through and closed cycles are identified. - Abstract: Although no consensus about the best approach to manage spent fuels has been achieved, economics is one of the major criteria for assessing and selecting acceptable management options. This study compares the reactor and fuel cycle costs of the closed system associated with sodium-cooled fast reactors and pyroprocessing versus the once-through system. We specifically investigated the fuel cycle transition cases of the Republic of Korea from 2013 to 2100. The results revealed that the closed system (34.00 mills/kWh as a mean value) could be more expensive than the once-through system (32.75 mills/kWh). In contrast, the once-through fuel cycle costs (8.31 mills/kWh), excluding reactor costs, were projected to be greater than the closed fuel cycle costs (7.77 mills/kWh) because of the increased costs of interim storage estimated by the Korean government and the limited contribution of backend fuel cycle components to the discounted costs. The capital cost of sodium-cooled fast reactor is the largest component contributing to the cost gap between the two systems. Among fuel cycle components, pyroprocessing has the largest uncertainty contribution to the cost gap. We also calculated the breakeven unit costs of SFR capital cost and PWR spent fuel pyroprocessing cost.

7. A study on the performance valuation of small size water storage electric boiler

International Nuclear Information System (INIS)

Mo, Joung Gun; Shin, Jae Ho; Bae, Chul Whan; Suh, Jeong Se; Chung, Han Shik; Jeong, Hyo Min

2003-01-01

We was made 150L a water storage electric boiler and obtained various performances of the storage, radiant and keeping by experimentation. The storage performance is that the heat were off about 50 minutes after heating start. Then the temperature of outlet was arrived the stead state at 91 deg. C and the storage performance was appeared 93.64%. In the radiant performance, the water temperature was decreased from 90 .deg. C to 44.8 deg. C after 960 minutes. Then the calorific value changed from 675kcal/h to 72kcal/h and the temperature decreased about 50%. The keeping performance showed mean temperature, 67.06 .deg. C according to progress 800 minutes and the maximum temperature drop were 0.2 .deg. C. By the results of the performance valuation, the water storage electric boiler was verified fitted quality on the test prescription of KERI (Korea Electrotechnology Research Institute.)

8. FY 1999 achievement report on the development of high performance boilers. R and D on high performance industrial furnaces, etc.; 1999 nendo koseino boiler no kaihatsu ni kansuru kenkyu seika hokokusho. Koseino kogyoro nado ni kansuru kenkyu kaihatsu

Energy Technology Data Exchange (ETDEWEB)

NONE

2000-03-01

This project started in FY 1993 to survey the actual state of industrial use boilers. Based on the results of the survey, in fiscal 1995, 1996 and 1997, no improvement of the present technology which has limits, but the development was made of the oxygen combustion and element technology which are factors for heightening boiler performance with a new idea first in the world. In fiscal 1998, a target for the overall thermal efficiency of 105% was settled by testing a pilot plant where the element technology was integrated into the small once-through boiler, flue/smoke tube boiler, water tube boiler, etc. In fiscal 1999, the target of the overall thermal efficiency of boiler was reached by a pilot plant test to clarify combustion characteristics, heat transfer characteristics, environmental characteristics, etc. Further, effects of energy saving were increased by the adoption method of oxygen supply equipment. Concretely, an overall boiler efficiency of 105.73% exceeding the targeted value of 105% was achieved at a pilot plant of actual scale, by concentrating the results of each of the element technologies such as 'oxygen combustion,' 'condensation type flue gas heat exchanger,' 'high performance combustion control device,' and 'rapid rotating auxiliary machine.' (NEDO)

9. An assessment of once-through homogeneous thorium fuel economics for light water reactors

International Nuclear Information System (INIS)

Joo, Hyung Kook; Noh, Jae Man; Yoo, Jae Woon

2001-01-01

The fuel economics of an once-through homogeneous thorium fuel concept for PWR was assessed by doing a detailed core analysis. In addition to this, the fuel economics assessment was also performed for two other ways enhancing the economic potential of thorium fuel; thorium utilization in the mixed core with uranium fuel assembly and Duplex thorium fuel concepts. As a results of fuel economics assessment, the thorium fuel cycle does not show any economic incentives in preference to uranium fuel cycle under the 18-months fuel cycle for PWR. However, the utilization of thorium is the mixed core with uranium fuel assembly and Duplex thorium fuel cycle and show superior fuel economics to uranium fuel under the longer fuel cycle scheme. The economic potential of once-through thorium fuel cycle is expected to be increased further by utilizing the Duplex thorium fuel in the mixed core with uranium fuel assembly

10. Conceptual design of once-through helical steam generator for SMART

Energy Technology Data Exchange (ETDEWEB)

Kim, Yong Wan; Kim, J. I.; Kim, J. H. [Korea Atomic Energy Research Institute, Taejon (Korea)

1999-12-01

Conceptual design of once-through helical steam generator for the integral reactor SMART is developed. The once-through helical steam generator requires quite different design concepts from the steam generators used in loop type commercial reactors. In this study the design requirements satisfying the operating conditions of the steam generator are derived, and the arrangements and the dimensions of the major parts are determined. By describing the design procedure, the cost of redesign and the costs of developments of similar new steam generators are minimized. The three dimensional models developed make it possible to preview the interferences of the steam generator components and to minimize the possibility of significant design changes in the next design stage by the preliminary strength analysis of the major parts. A methodology for evaluation of flow induced vibration of steam generator tubes has been developed and a preliminary flow induced vibration analysis has been performed. 24 refs., 54 figs., 9 tabs. (Author)

11. Sliding mode fuzzy control for a once-through stream generator

International Nuclear Information System (INIS)

Zhang Guifeng; Shi Xiaocheng; Sun Tieli; Xiong Jinkui; Zhang Hongguo

2007-01-01

A once-through steam generator is important equipment in nuclear power plant, so its control level is high. A Sliding Mode Fuzzy Controller inherits the robustness property of Sliding Mode Control and the interpolation property of Fuzzy Logic Control. The robustness property of variable structure system makes the control system insensitive for different burthen variety and different outside disturbance. Fuzzy control predigests the device of control system and alleviates the chattering which variable structure system causes. So the control system can be made more ideal. The paper describes the design method of Sliding Mode Fuzzy Controller without its system model for a once-through steam generator. And the simulation results show that satisfying control results can be got. (authors)

12. Intelligent information data base of flow boiling characteristics in once-through steam generator for integrated type marine water reactor

International Nuclear Information System (INIS)

Inasaka, Fujio; Nariai, Hideki

1998-01-01

Valuable experimental knowledge with flow boiling characteristics of the helical-coil type once-through steam generator was converted into an intelligent information data base program. The program was created as a windows application using the Visual Basic. Main functions of the program are as follows: (1) steady state flow boiling analysis of any helical-coil type once-through steam generator, (2) analysis and comparison with the experimental data, (3) reference and graph display of the steady state experimental data, (4) reference of the flow instability experimental data and display of the instability threshold correlated by each parameter, (5) summary of the experimental apparatus. (6) menu bar such as a help and print. In the steady state analysis, the region lengths of subcooled boiling, saturated boiling, and super-heating, and the temperature and pressure distributions etc. for secondary water calculated. Steady state analysis results agreed well with the experimental data, with the exception of the pressure drop at high mass velocity. The program will be useful for the design of not only the future integrated type marine water reactor but also the small sized water reactor with helical-coil type steam generator

13. Modeling and simulation of once-through steam generator of casing pipes

International Nuclear Information System (INIS)

Niu Guanglin; Fu Mingyu; Yan Changqi; Nan Jingfu

2009-01-01

Adynamic model about the double casing pipes structure of double-face heat transfer is accepted in new type once-through steam generator (OTSG) is established. The model,which can be applied to any steady and dynamic conditions of OSTG in different flowing and heat transferring characteristic,is developed. It provides the bases for the design and operation of control system, analysis and treatment of abnormal conditions and faults, and development of operation rules. (authors)

14. Fuel utilization potential in light water reactors with once-through fuel irradiation (AWBA Development Program)

International Nuclear Information System (INIS)

Rampolla, D.S.; Conley, G.H.; Candelore, N.R.; Cowell, G.K.; Estes, G.P.; Flanery, B.K.; Duncombe, E.; Dunyak, J.; Satterwhite, D.G.

1979-07-01

Current commercial light water reactor cores operate without recylce of fuel, on a once-through fuel cycle. To help conserve the limited nuclear fuel resources, there is interest in increasing the energy yield and, hence, fuel utilization from once-through fuel irradiation. This report evaluates the potential increase in fuel utilization of light water reactor cores operating on a once-through cycle assuming 0.2% enrichment plant tails assay. This evaluation is based on a large number of survey calculations using techniques which were verified by more detailed calculations of several core concepts. It is concluded that the maximum fuel utilization which could be achieved by practical once-through pressurized light water reactor cores with either uranium or thorium is about 17 MWYth/ST U 3 O 8 (Megawatt Years Thermal per Short Ton of U 3 O 8 ). This is about 50% higher than that of current commercial light water reactor cores. Achievement of this increased fuel utilization would require average fuel burnup beyond 50,000 MWD/MT and incorporation of the following design features to reduce parasitic losses of neutrons: reflector blankets to utilize neutrons that would otherwise leak out of the core; fuel management practices in which a smaller fraction of the core is replaced at each refueling; and neutron economic reactivity control, such as movable fuel control rather than soluble boron control. For a hypothetical situation in which all neutron leakage and parasitic losses are eliminated and fuel depletion is not limited by design considerations, a maximum fuel utilization of about 20 MWYth/ST U 3 O 8 is calculated for either uranium or thorium. It is concluded that fuel utilization for comparable reactor designs is better with uranium fuel than with thorium fuel for average fuel depletions of 30,000 to 35,000 MWD/MT which are characteristic of present light water reactor cores

15. Fuel-management simulations for once-through thorium fuel cycle in CANDU reactors

International Nuclear Information System (INIS)

Chan, P.S.W.; Boczar, P.G.; Ellis, R.J.; Ardeshiri, F.

1999-01-01

High neutron economy, on-power refuelling and a simple fuel bundle design result in unsurpassed fuel cycle flexibility for CANDU reactors. These features facilitate the introduction and exploitation of thorium fuel cycles in existing CANDU reactors in an evolutionary fashion. Detailed full-core fuel-management simulations concluded that a once-through thorium fuel cycle can be successfully implemented in an existing CANDU reactor without requiring major modifications. (author)

16. Global freshwater thermal emissions from steam-electric power plants with once-through cooling systems

International Nuclear Information System (INIS)

Raptis, Catherine E.; Pfister, Stephan

2016-01-01

Large quantities of heat are rejected into freshwater bodies from power plants employing once-through cooling systems, often leading to temperature increases that disturb aquatic ecosystems. The objective of this work was to produce a high resolution global picture of power-related freshwater thermal emissions and to analyse the technological, geographical and chronological patterns behind them. The Rankine cycle was systematically solved for ∼2400 generating units with once-through cooling systems, distinguishing between simple and cogenerative cycles, giving the rejected heat as a direct output. With large unit sizes, low efficiencies, and high capacity factors, nuclear power plants reject 3.7 GW heat into freshwater on average, contrasting with 480 MW rejected from coal and gas power plants. Together, nuclear and coal-fuelled power plants from the 1970s and 1980s account for almost 50% of the rejected heat worldwide, offering motivation for their phasing out in the future. Globally, 56% of the emissions are rejected into rivers, pointing to potential areas of high thermal pollution, with the rest entering lakes and reservoirs. The outcome of this work can be used to further investigate the identified thermal emission hotspots, and to calculate regionalized water temperature increase and related impacts in environmental, energy-water nexus studies and beyond. - Highlights: • The thermodynamic cycles of ∼2400 power units with once-through cooling were solved. • Global freshwater heat emissions depend on technology, geography & chronology. • Half the global emissions come from nuclear and coal plants from the 70s & 80s. • Hotspots of freshwater thermal emissions were identified globally. • Global georeferenced emissions are available for use in water temperature models.

17. LEU and thorium fuel cycles for the high temperature reactor (once-through and recycle)

International Nuclear Information System (INIS)

1978-09-01

Sets of performance parameters, optimised for minimum costs within the bounds of current technical confidence, are presented for each of the four fuel cycle variants mentioned in the title. The overall cost of the HEU once-through system is found to be significantly more expensive than the other three which are similar. Data are presented on fissile material utilisation, on the isotopic composition of discharged fuel, and on fuel cycle costs. Comments are made on technical status, development needs, safety, environmental concerns including the storage and disposal of irradiated fuel, and on characteristics relevant to proliferation control

18. Fuel utilization improvements in a once-through PWR fuel cycle. Final report on Task 6

International Nuclear Information System (INIS)

Dabby, D.

1979-06-01

In studying the position of the United States Department of Energy, Non-proliferation Alternative Systems Assessment Program, this report determines the uranium saving associated with various improvement concepts applicable to a once-through fuel cycle of a standard four-loop Westinghouse Pressurized Water Reactor. Increased discharged fuel burnup from 33,000 to 45,000 MWD/MTM could achieve a 12% U 3 O 8 saving by 1990. Improved fuel management schemes combined with coastdown to 60% power, could result in U 3 O 8 savings of 6%

19. Once-through CANDU reactor models for the ORIGEN2 computer code

International Nuclear Information System (INIS)

Croff, A.G.; Bjerke, M.A.

1980-11-01

Reactor physics calculations have led to the development of two CANDU reactor models for the ORIGEN2 computer code. The model CANDUs are based on (1) the existing once-through fuel cycle with feed comprised of natural uranium and (2) a projected slightly enriched (1.2 wt % 235 U) fuel cycle. The reactor models are based on cross sections taken directly from the reactor physics codes. Descriptions of the reactor models, as well as values for the ORIGEN2 flux parameters THERM, RES, and FAST, are given

20. Assessment of the once-through cooling alternative for central steam-electric generating stations

Energy Technology Data Exchange (ETDEWEB)

Paddock, R. A.; Ditmars, J. D.

1978-12-01

The efficacy of the disposal of waste heat from steam-electric power generation by means of once-through cooling systems was examined in the context of the physical aspects of water quality standards and guidelines for thermal discharges. Typical thermal standards for each of the four classes of water bodies (rivers, lakes, estuaries, and coastal waters) were identified. The mixing and dilution characteristics of various discharge modes ranging from simple, shoreline surface discharges to long, submerged multiport diffusers were examined in terms of the results of prototype measurements, analytical model predictions, and physical model studies. General guidelines were produced that indicate, for a given plant capacity, a given type of receiving water body, and a given discharge mode, the likelihood that once-through cooling can be effected within the restrictions of typical thermal standards. In general, it was found that shoreline surface discharges would not be adequate for large power plants (greater than or equal to 500 MW) at estuarine and marine coastal sites, would be marginally adequate at lake sites, and would be acceptable only at river sites with large currents and river discharges. Submerged multiport diffusers were found to provide the greatest likelihood of meeting thermal standards in all receiving water environments.

1. Transmutation Capability of a Once-Through Molten-Salt and Other Transmuting Reactors

International Nuclear Information System (INIS)

Greenspan, E.; Lowenthal, M.; Barnes, D.; Kawasaki, D.; Kimball, D.; Matsumoto, H.; Sagara, H.; Vietez, E.R.

2002-01-01

A preliminary assessment is done of the transmutation characteristics of three reactor technologies: a multi-batch liquid metal (LM) cooled transmuter, a once-through molten-salt (MS) transmuter and a pebble bed (PB) transmuter. It was found that for the same fractional transmutation and same k eff drop with burnup (Δk effBU ), lead-bismuth offers smaller peak-to-average core power density, and it requires a smaller pumping power but a larger and heavier core than a sodium cooled transmuter. 99 Tc cannot effectively serve as a burnable absorber to reduce Δk effBU of LM transmuters. However, addition of thorium can greatly flatten k eff and almost double the fractional transmutation of the LWR spent fuel from ∼20% to ∼40%. If the 'once-through' MS transmuter is operated with continuous complete removal of fission products, it can achieve ∼85% fractional transmutation provided that the equilibrium concentration of actinides in the MS can reach 4 mole %. If the fission products are not actively removed, the fractional transmutation is reduced to ∼75%. The fractional transmutation of a PB transmuter can exceed 40%. More thorough analysis is required to better quantify the transmutation capability of the different transmuter technologies. (authors)

2. Assessment of the once-through cooling alternative for central steam-electric generating stations

International Nuclear Information System (INIS)

1978-12-01

The efficacy of the disposal of waste heat from steam-electric power generation by means of once-through cooling systems was examined in the context of the physical aspects of water quality standards and guidelines for thermal discharges. Typical thermal standards for each of the four classes of water bodies (rivers, lakes, estuaries, and coastal waters) were identified. The mixing and dilution characteristics of various discharge modes ranging from simple, shoreline surface discharges to long, submerged multiport diffusers were examined in terms of the results of prototype measurements, analytical model predictions, and physical model studies. General guidelines were produced that indicate, for a given plant capacity, a given type of receiving water body, and a given discharge mode, the likelihood that once-through cooling can be effected within the restrictions of typical thermal standards. In general, it was found that shoreline surface discharges would not be adequate for large power plants (greater than or equal to 500 MW) at estuarine and marine coastal sites, would be marginally adequate at lake sites, and would be acceptable only at river sites with large currents and river discharges. Submerged multiport diffusers were found to provide the greatest likelihood of meeting thermal standards in all receiving water environments

3. Spectral shift controlled reactor, UO2 once-through cycle optimized

International Nuclear Information System (INIS)

1978-05-01

This paper presents technical and economic data on the SSCR which may be of use in the International Fuel Cycle Evaluation Program to intercompare alternative nuclear systems. Included in this data is information on the optimized UO 2 once-through fuel cycle. The ''optimized'' cycle refers to a UO 2 once-through cycle which has better fuel resource utilization than the conventional UO 2 cycle employed in current design PWRs. This fuel cycle uses more in-core batches and a higher discharge exposure than current PWR fuel management schemes. The proposed cycle is not optimal in a mathematical sense, however, since additional resource savings can be obtained if the discharge exposure is extended to even higher values and the number of in-core fuel batches is increased further. The present cycle was selected as ''optimal'' based on the assumption that it can be achieved with only an extension of fuel design technology and can therefore be deployed in a relatively short time frame. In the longer term, modification to reactor geometry as well as further extensions of discharge burnup might be considered to realize additional reduction in uranium resource requirements. The data contained in this paper has been developed by an ongoing program which at the present time is only 50% complete. The data presented here should therefore be considered preliminary and will be updated in the future as required

4. The small scale use of poultry litter as a boiler fuel

Energy Technology Data Exchange (ETDEWEB)

1990-03-01

Annual savings of between Pound 62,200 and Pound 78,200 have been achieved by a broiler chicken production company to burn chicken litter as a fuel following the retrofitting of a semi-pyrolytic precombustor unit to an existing boiler. The capital cost of installing the combustion system and associated plant was Pound 76,500, giving a payback period of between 12 and 15 months on the initial investment. The heat produced is used to generate steam which is then used to heat seven broiler houses, each holding 30,000 birds, and half an acre of glasshouse for the year round growing of chrysanthemums. With the availability of cheap heat, it has been possible to increase ventilation rates while still maintaining the required temperature in the broiler houses. This has resulted in much drier bedding, greatly improved carcass grading and better control of the general health of the birds. The measured primary energy savings were 17,800 GJ/year (658 tonnes of coal equivalent). This takes into account the increased electricity consumption. The energy savings are worth approximately Pound 42,000/year. Investigations into the method of stockpiling and compositing of litter for re-use and/or burning were undertaken. These show that sufficient heat is being generated in the stacks to destroy any poultry pathogens likely to be present. Furthermore no trace of actinomycetes spores which are responsible for Farmers Lung was found. (author).

5. Model-free adaptive control of supercritical circulating fluidized-bed boilers

Science.gov (United States)

Cheng, George Shu-Xing; Mulkey, Steven L

2014-12-16

A novel 3-Input-3-Output (3.times.3) Fuel-Air Ratio Model-Free Adaptive (MFA) controller is introduced, which can effectively control key process variables including Bed Temperature, Excess O2, and Furnace Negative Pressure of combustion processes of advanced boilers. A novel 7-input-7-output (7.times.7) MFA control system is also described for controlling a combined 3-Input-3-Output (3.times.3) process of Boiler-Turbine-Generator (BTG) units and a 5.times.5 CFB combustion process of advanced boilers. Those boilers include Circulating Fluidized-Bed (CFB) Boilers and Once-Through Supercritical Circulating Fluidized-Bed (OTSC CFB) Boilers.

6. Research on Group Operation Mode of Once-through Steam Generator

International Nuclear Information System (INIS)

Hao, Cheng Ming; Liu, Xinkai; Peng, Min Jun; Xia, Genglei

2011-01-01

Integrated Pressurized Water Reactor (IPWR) owns more than one once-through steam generators (OTSGs). Flow instability may occur in secondary side of OTSG under certain conditions. Trying to avoid the occurrence of flow instability is of great important for the safe and stable operation of OTSG. Because of the fact that flow instability often occurs in certain regions, so when OTSGs operate with low load, OTSGs can be separated into several groups, which can avoid flow instability. In this paper, operational characteristics of IPWR are analyzed by RELAP5/MOD3.4 code and during the discussion of group operation, a rapid change load operation scheme using OTSG group operation mode which can be used in IPWR is proposed

7. Research on Group Operation Mode of Once-through Steam Generator

Energy Technology Data Exchange (ETDEWEB)

Hao, Cheng Ming; Liu, Xinkai; Peng, Min Jun; Xia, Genglei [Harbin Engineering University, Harbin (China)

2011-08-15

Integrated Pressurized Water Reactor (IPWR) owns more than one once-through steam generators (OTSGs). Flow instability may occur in secondary side of OTSG under certain conditions. Trying to avoid the occurrence of flow instability is of great important for the safe and stable operation of OTSG. Because of the fact that flow instability often occurs in certain regions, so when OTSGs operate with low load, OTSGs can be separated into several groups, which can avoid flow instability. In this paper, operational characteristics of IPWR are analyzed by RELAP5/MOD3.4 code and during the discussion of group operation, a rapid change load operation scheme using OTSG group operation mode which can be used in IPWR is proposed.

8. Once-through thorium fuel cycle evaluation for TVA's Browns Ferry-3 Boiling Water Reactor

International Nuclear Information System (INIS)

Hopkins, G.C.

1982-05-01

This report documents benchmark evaluations to test thorium lattice predictive methods and neutron cross sections against available data and summarizes specific evaluations of the once-through thorium cycle when applied to the Browns Ferry-3 BWR. It was concluded that appreciable uncertainties in thorium cycle nuclear data cloud the ability to reliably predict the fuel cycle performance and that power reactor irradiations of ThO 2 rods in BWRs are desirable to resolve uncertainties. Benchmark evaluations indicated that the ENDF/B-IV data used in the evaluations should cause an underprediction of U-233/ThO 2 fuel reactivity, and, therefore, the results of the preliminary evaluations completed under the program should be conservative

9. Optimum thermal sizing and operating conditions for once through steam generator

Energy Technology Data Exchange (ETDEWEB)

Yi, Kunwoo; Ju, Kyongin; Im, Inyoung; Kim, Eunkee [KEPCO Engineering and Construction Company., Inc., Daejeon (Korea, Republic of)

2014-10-15

The steam generator is designed to be optimized so as to remove heat and to produce steam vapor. Because of its importance, theoretical and experimental researches have been performed on forced convection boiling heat transfer. The purpose of this study is to predict the thermal behavior and to perform optimum thermal sizing of once through steam generator. To estimate the tube thermal sizing and operating conditions of the steam generator, the analytical modeling is employed on the basis of the empirical correlation equations and theory. The optimized algorithm model, Non-dominated Sorting Genetic Algorithm (NSGA)-II, uses for this analysis. This research is focused on the design of in-vessel steam generator. An one dimensional analysis code is developed to evaluate previous researches and to optimize steam generator design parameters. The results of one-dimensional analysis need to be verified with experimental data. Goals of multi-objective optimization are to minimize tube length, pressure drop and tube number. Feedwater flow rate up to 115.425kg/s is selected so as to have margin of feedwater temperature 20 ..deg. C. For the design of 200MWth once through steam generator, it is evaluated that the tube length shall be over 12.0m for the number of tubes, 2500ea, and the length of the tube shall be over 8.0m for the number of tubes, 4500ea. The parallel coordinates chart can be provided to determine the optimal combination of number of tube, pressure drop, tube diameter and length.

10. Once-through reactor with smooth hollow fuel elements for a manoeuvrable nuclear power plant

International Nuclear Information System (INIS)

Smolin, V.N.; Esikov, V.I.; Mityaev, Yu.I.; Vasil'ev, S.A.

1980-01-01

Studied are results of experimental investigation of the top capacity of hollow fuel element imitators, which has been carried out to substantiate possibilities of creation of nuclear energetic once-through type installation with subcritical parameters of heat carrier and smooth hollow fuel elements designed for operation in the regulatory regime of loading. Principal technological scheme of such NPP and approximate calculation characteristics of the reactor are presented. The investigation has been made using closed circular installation. Electro-heated tubes out of corrosion-resistant steel with the wall thickness variable as to the length are used as fuel element imitators. The experiments have been conducted using imitators with inner diameter of 14.6; 18 and 22 mm and the length of 6000 mm under the pressure (P) from 7.85 to 15.7 MPa, mass rate from 250 to 2000 kg/(m 2 xs); heat-carrier temperature at the entrance from 80 deg C up to the temperature 10-15 deg C lower than saturation temperature under the given pressure. The experiments have shown that under the pressure of 7.85-9.8 MPa in the heat carrier mass rates of 250-350 kg/(cm 2 xs) deteriorated regime of heat output appears only balance mass vapor content somewhat exceeding 1. It follows from the analysis of experimental data that the following parameters of heat-carrier are optimum: (from the viewpoint of maximum capacity in crisis-free regime of fuel element work) the pressure of 6-9 MPa; mass rate - 250-300 kg/(m 2 xs) at fuel element inner diameter of 25-20 mm respectively. Conclusion is made, that the investigations conducted create precondition for manoeuvrable NPP with once-through reactor

11. Two phase flow problems in power station boilers

International Nuclear Information System (INIS)

Firman, E.C.

1974-01-01

The paper outlines some of the waterside thermal and hydrodynamic phenomena relating to design and operation of large boilers in central power stations. The associated programme of work is described with an outline of some results already obtained. By way of introduction, the principal features of conventional and nuclear drum boilers and once-through nuclear heat exchangers are described in so far as they pertain to this area of work. This is followed by discussion of the relevant physical phenomena and problems which arise. For example, the problem of steam entrainment from the drum into the tubes connecting it to the furnace wall tubes is related to its effects on circulation and possible mechanisms of tube failure. Other problems concern the transient associated with start-up or low load operation of plant. The requirement for improved mathematical representation of steady and dynamic performance is mentioned together with the corresponding need for data on heat transfer, pressure loss, hydrodynamic stability, consequences of deposits, etc. The paper concludes with reference to the work being carried out within the C.E.G.B. in relation to the above problems. The facilities employed and the specific studies being made on them are described: these range from field trials on operational boilers to small scale laboratory investigations of underlying two phase flow mechanisms and include high pressure water rigs and a freon rig for simulation studies

12. An overview of CFD modelling of small-scale fixed-bed biomass pellet boilers with preliminary results from a simplified approach

International Nuclear Information System (INIS)

Chaney, Joel; Liu Hao; Li Jinxing

2012-01-01

Highlights: ► Overview of the overall approach of modelling fixed-bed biomass boilers in CFD. ► Bed sub-models of moisture evaporation, devolatisation and char combustion reviewed. ► A method of embedding a combustion model in discrete fuel zones within the CFD is suggested. ► Includes sample of preliminary results for a 50 kW pellet boiler. ► Clear physical trends predicted. - Abstract: The increasing global energy demand and mounting pressures for CO 2 mitigation call for increased efficient utilization of biomass, particularly for heating domestic and commercial buildings. The authors of the present paper are investigating the optimization of the combustion performance and NO x emissions of a 50 kW biomass pellet boiler fabricated by a UK manufacturer. The boiler has a number of adjustable parameters including the ratio of air flow split between the primary and secondary supplies, the orientation, height, direction and number of the secondary inlets. The optimization of these parameters provides opportunities to improve both the combustion efficiency and NO x emissions. When used carefully in conjunction with experiments, Computational Fluid Dynamics (CFD) modelling is a useful tool for rapidly and at minimum cost examining the combustion performance and emissions from a boiler with multiple variable parameters. However, modelling combustion and emissions of a small-scale biomass pellet boiler is not trivial and appropriate fixed-bed models that can be coupled with the CFD code are required. This paper reviews previous approaches specifically relevant to simulating fixed-bed biomass boilers. In the first part it considers approaches to modelling the heterogeneous solid phase and coupling this with the gas phase. The essential components of the sub-models are then overviewed. Importantly, for the optimization process a model is required that has a good balance between accuracy in predicting physical trends, with low computational run time. Finally, a

13. thermal analysis of a small scale solid waste-fired steam boiler

African Journals Online (AJOL)

user

Thermal analysis of a small scale solid waste-fired steam generator is presented in this paper. The analysis was based on the chosen design specifications which are operating steam ... include: wind, bio-energy, geothermal, solar thermal,.

14. Studi Awal Desain Pebble Bed Reactor Berbasis Htr-pm Dengan Skema Resirkulasi Bahan Bakar Once-through-then-out

OpenAIRE

Setiadipura, Topan; Pane, Jupiter Sitorus; Zuhair, Zuhair

2016-01-01

STUDI AWAL DESAIN PEBBLE BED REACTOR BERBASIS HTR-PM DENGAN RESIRKULASI BAHAN BAKAR ONCE-THROUGH-THEN-OUT. Reaktor nuklir tipe pebble bed reactor (PBR) adalah salah satu reaktor canggih dengan fitur keselamatan pasif yang kuat. Pada desain tipe ini berpotensi untuk dilakukan kogenerasi yang bermanfaat untuk pengolahan berbagai mineral di berbagai pulau di Indonesia. Operasi PBR dapat lebih disederhanakan dengan menerapkan skema pengisian bahan bakar once-through-then-out (OTTO) dimana bahan b...

15. An evaluation of designed Start-up System (SUS) for once-through steam generators

International Nuclear Information System (INIS)

Yu, Dali; Peng, Minjun; Xia, Genglei; Mao, Wanchao; Yang, Yang

2014-01-01

Highlights: • Four SUS solutions are established to help reactors complete the start-up process. • Solutions C and D lead to superior behaved than Solutions A and B. • Solution C is fit for propulsion reactors and Solution D for nuclear power reactors. - Abstract: In this paper, we report on research that has been carried out both on the comparison and evaluation of four designed Start-up Systems (SUSs), which are proposed to improve reliability and economy during the reactor start-up process. Firstly, four SUS solutions are established to satisfy demands and detailed descriptions are introduced. Then, four reactor systems, which include SUS, are modeled by the estimate code JTopmeret. Furthermore besides, the JTopmeret code is validated for the once-through steam generators (OTSG). Finally, the behaviors of SUS and the steady and transient performance of OTSG are investigated. The results show that the designed SUS can successfully improve the economy and the OTSG operational safety. Suggestion is made in this paper to apply Solution C in propulsion-purposed reactors, and Solution D in nuclear power reactors

16. Uranium resource utilization improvements in the once-through PWR fuel cycle

International Nuclear Information System (INIS)

Matzie, R.A.

1980-04-01

In support of the Nonproliferation Alternative Systems Assessment Program (NASAP), Combustion Engineering, Inc. performed a comprehensive analytical study of potential uranium utilization improvement options that can be backfit into existing PWRs operating on the once-through uranium fuel cycle. A large number of potential improvement options were examined as part of a preliminary survey of candidate options. The most attractive of these, from the standpoint of uranium utilization improvement, economic viability, and ease of implementation, were then selected for detailed analysis and were included in a single composite improvement case. This composite case represents an estimate of the total savings in U 3 O 8 consumption that can be achieved in current-design PWRs by implementing improvements which can be developed and demonstrated in the near term. The improvement options which were evaluated in detail and included in the composite case were a new five-batch, extended-burnup fuel management scheme, low-leakage fuel management, modified lattice designs, axial blankets, reinsertion of initial core batches, and end-of-cycle stretchout

17. Design and fuel management of PWR cores to optimize the once-through fuel cycle

International Nuclear Information System (INIS)

Fujita, E.K.; Driscoll, M.J.; Lanning, D.D.

1978-08-01

The once-through fuel cycle has been analyzed to see if there are substantial prospects for improved uranium ore utilization in current light water reactors, with a specific focus on pressurized water reactors. The types of changes which have been examined are: (1) re-optimization of fuel pin diameter and lattice pitch, (2) axial power shaping by enrichment gradation in fresh fuel, (3) use of 6-batch cores with semi-annual refueling, (4) use of 6-batch cores with annual refueling, hence greater extended (approximately doubled) burnup, (5) use of radial reflector assemblies, (6) use of internally heterogeneous cores (simple seed/blanket configurations), (7) use of power/temperature coastdown at the end of life to extend burnup, (8) use of metal or diluted oxide fuel, (9) use of thorium, and (10) use of isotopically separated low sigma/sub a/ cladding material. State-of-the-art LWR computational methods, LEOPARD/PDQ-7/FLARE-G, were used to investigate these modifications

18. Modeling and field studies of fouling in once-through steam generators

International Nuclear Information System (INIS)

Thompson, R.; Gaudreau, T.

1995-01-01

Efforts of the past 10 years to minimize fouling of the Crystal River-3 once-through steam generators are reviewed. The major focus has been on improving at-temperature pH control in the secondary cycle. Various concentrations of different pH control agents were tested in the field for hundreds of days to determine their effect on steam generator fouling. High concentrations of morpholine (50--100 ppm) in the feedwater were found to apparently produce de-fouling of the steam generators without an associated decrease in feedwater iron concentration as compared to that at lower levels of morpholine. Computer modeling of the pH(t) within the OTSG for the various chemistries tested indicates that the pH can change significantly with elevation within the steam generator by varying the pH control agent or its concentration. It is postulated that these variations in pH may change the surface charge of the tubes, tube support plates, and/or corrosion product particles in solution, to favor either deposition or repulsion of the particles, and thereby producing conditions that either favor fouling or de-fouling of the OTSG. Crystal River-3 experience indicates that corrosion product deposition and release processes inside the steam generator can be chemically manipulated to favor release, and thereby maximize plant performance, and delay or avoid costly hydraulic or chemical cleanings

19. A Differential-Algebraic Model for the Once-Through Steam Generator of MHTGR-Based Multimodular Nuclear Plants

Directory of Open Access Journals (Sweden)

Zhe Dong

2015-01-01

Full Text Available Small modular reactors (SMRs are those fission reactors whose electrical output power is no more than 300 MWe. SMRs usually have the inherent safety feature that can be applicable to power plants of any desired power rating by applying the multimodular operation scheme. Due to its strong inherent safety feature, the modular high temperature gas-cooled reactor (MHTGR, which uses helium as coolant and graphite as moderator and structural material, is a typical SMR for building the next generation of nuclear plants (NGNPs. The once-through steam generator (OTSG is the basis of realizing the multimodular scheme, and modeling of the OTSG is meaningful to study the dynamic behavior of the multimodular plants and to design the operation and control strategy. In this paper, based upon the conservation laws of mass, energy, and momentum, a new differential-algebraic model for the OTSGs of the MHTGR-based multimodular nuclear plants is given. This newly-built model can describe the dynamic behavior of the OTSG in both the cases of providing superheated steam and generating saturated steam. Numerical simulation results show the feasibility and satisfactory performance of this model. Moreover, this model has been applied to develop the real-time simulation software for the operation and regulation features of the world first underconstructed MHTGR-based commercial nuclear plant—HTR-PM.

20. Emission of nitrogen oxides from small biomass-fired grate boilers - a literature survey

International Nuclear Information System (INIS)

Olsson, Daniel

1999-05-01

A literature study has been carried out to find mechanisms for control of nitrogen oxide emissions from small-scale biomass fired combustion devices. The underlying nitrogen chemistry has been studied. Three paths of nitrogen oxide formation has been identified: 1. Thermal NO x , 2, Prompt NO x , and, 3. Fuel NO x . Out of these three mechanisms only fuel NO x is of interest, and the others are neglected at the temperature level concerned. The results from this study have been used to identify limitations and possibilities for NO x and CO abatement. A beacon has been to find efficient methods for NO x abatement at the same time as complete burn-out of the fuel is of greatest importance. The NO x abatement work of many of the Swedish manufacturers of small-scale combustion devices is described. This gives valuable insight in the practical possibilities and limitations in strive for low NOx emissions. From the literature and the contacts with manufacturers some factors of great importance for NO x emission control have been identified. These are: * The fuel (nitrogen content, shape, size, the height of the fuel layer and the tendency of the fuel to stick), * The stoichiometry in the volume above the fuel bed (should be 0.6 - 0.8), * The mixing of the gases above the fuel bed, * The mixing of tertiary air into the main gas flow, and * The thermal load of the combustion chamber (residence time). All the secondary measures studied but selective catalytic reduction have been rejected. Selective catalytic reduction could be a possible solution to the NO x emission problem if it is necessary to further lower the emissions from these small-scale biomass combustion devices despite the cost Project report from the program: Small scale combustion of biofuels. 22 refs, 30 figs, 4 tabs

1. HR boiler

Energy Technology Data Exchange (ETDEWEB)

1982-08-01

A number of manufacturers of central heating boilers in the Netherlands have produced high-efficiency boilers, all carrying the GIVEG-HR seal of approval (GIVEG is the manufacturers' association in the Netherlands, and HR stands for 'hoog rendement': high efficiency). Efficiences were considerably improved by reducing flue, idling and radiation losses. Control and safety, discharges of flue gases and condensate need special attention. Whether installation of a GIVEG-HR boiler is profitable in view of the cost/profit ratio, will have to be determined from case to case. N.V. Nederlandse Gasunie felt it was time to present the facts so far in a way specially aimed at the construction industry. This special edition of 'Gas and Architecture' answers a number of questions which the architect or consultant engineer might have in particular before advising on the installation of the new boiler in houses and other buildings in the interests of energy saving. A technical description of the HR boiler covers the backgrounds of its development and considers the role of the Netherlands government as regards to the introduction of the boiler.

2. Combustion of mediterranean agro-forest biomasses in small and medium scale pellet boilers: strategies for minimizing ash fusion and slagging

Energy Technology Data Exchange (ETDEWEB)

Vega-Nieva, Daniel J.; Dopazo, Raquel; Ortiz, Luis [Forest Engineering Univ. School. Univ. of Vigo, Pontevedra (Spain)], e-mail: DanielJVN@gmail.com

2012-11-01

The slagging and fouling risk remain as important barriers that are currently limiting the use of various agricultural residues and potential energy crops feedstocks (e.g. [1-3]), which remain largely unutilized, particularly in Mediterranean countries. In this oral communication, the main results from the VI Framework European Project Domoheat on the combustion of mediterranean biomasses and its mixtures on small and medium size domestic pellet boilers, are presented, together with the goals of the ongoing VII Framework European Project AshMelT focusing on the definition of objective criteria and tests for ash slagging in domestic pellet boilers. The utilization of ash slagging indices based on ash composition and the definition of biomass mixtures based on such ash indices are presented as potentially useful tools for minimizing the occurrence of ash fusion and slagging during combustion.

3. Chemical cleaning of UK AGR boilers

International Nuclear Information System (INIS)

Rudge, A.; Turner, P.; Ghosh, A.; Clary, W.; Tice, D.

2002-01-01

For the first time in their operational lives, UK advanced gas-cooled reactor once-through boilers have been chemically cleaned. Chemical cleaning was necessary to avoid lost output resulting from boiler pressure drops, which had been increasing for a number of years. Chemical cleaning of these boilers presents a number of unique difficulties. These include lack of access to the boilers, highly sensitised 316H superheater sections that cannot be excluded from the cleaning flow path, relatively thin boiler tube walls and an intolerance to boiler tube failure because of the role of the boilers in nuclear decay heat removal. The difficulties were overcome by implementing the clean in a staged manner, starting with an extensive materials testwork programme to select and then to substantiate the cleaning process. The selected process was based on ammoniated citric acid plus formic acid for the principal acid cleaning stage. Materials testwork was followed by an in-plant trial clean of six boiler tubes, further materials testwork and the clean of a boiler tube in a full-scale test rig. An overview is presented of the work that was carried out to demonstrate that the clean could be carried out safely, effectively and without leading to unacceptable corrosion losses. Full-scale chemical cleaning was implemented by using as much of the existing plant as possible. Careful control and monitoring was employed to ensure that the cleaning was implemented according to the specified design, thus ensuring that a safe and effective clean was carried out. Full-scale cleaning has resulted in significant boiler pressure drop recovery, even though the iron burden was relatively low and cleaning was completed in a short time. (orig.)

4. Development of once-through hybrid sulfur process for nuclear hydrogen production

International Nuclear Information System (INIS)

Jung, Yong Hun

2010-02-01

Humanity has been facing major energy challenges such as the severe climate change, threat of energy security and global energy shortage especially for the developing world. Particularly, growing awareness of the global warming has led to efforts to develop the sustainable energy technologies for the harmony of the economy, social welfare and environment. Water-splitting nuclear hydrogen production is expected to help to resolve those challenges, when high energy efficiency and low cost for hydrogen production become possible. Once-through Hybrid Sulfur process (Ot-HyS), proposed in this work, produces hydrogen using the same SO 2 Depolarized water Electrolysis (SDE) process found in the original Hybrid Sulfur cycle (HyS) proposed by Westinghouse, which has the sulfuric acid decomposition (SAD) process using high temperature heat source in order to recover sulfur dioxide for the SDE process. But Ot-HyS eliminated this technical hurdle by replacing it with well-established sulfur combustion process to feed sulfur dioxide to the SDE process. Because Ot-HyS has less technical challenges, Ot-HyS is expected to advance the realization of the large-scale nuclear hydrogen production by feeding an initial nuclear hydrogen stock. Most of the elemental sulfur, at present, is supplied by desulfurization process for environmental reasons during the processing of natural gas and petroleum refining and expected to increase significantly. This recovered sulfur will be burned with oxygen in the sulfur combustion process so that produced sulfur dioxide could be supplied to the SDE process to produce hydrogen. Because the sulfur combustion is a highly exothermic reaction releasing 297 kJ/mol of combustion heat resulting in a large temperature rise, efficiency of the Ot-HyS is expected to be high by recovering this great amount of high grade excess heat with nuclear energy. Sulfuric acid, which is a byproduct of the SDE process, could be sent to the neighboring consumers with or even

5. Data base for a CANDU-PHW operating on a once-through, natural uranium fuel cycle

International Nuclear Information System (INIS)

1979-07-01

This report, prepared for INFCE, describes a standard 600 MW(e) CANDU-PHW reactor operating on a once-through natural uranium fuel cycle. Subsequently, data are given for an extrapolated 1000 MW(e) design (the nominal capacity adopted for the INFCE study) operating on the same fuel cycle. (author)

6. Numerical simulation of dryout and post-dryout heat transfer in a straight-pipe once-through steam generator

International Nuclear Information System (INIS)

Shi, Jianxin; Sun, Baozhi; Han, Wenjing; Zhang, Guolei; Li, Yanjun; Yang, Longbin

2016-01-01

Highlights: • Two-fluid three-flow-field model is developed to predict dryout in steam generator. • The empirical correlation is used to correct dryout criterion. • The interactions between three-flow-fields and the wall are considered. • Dryout and post-dryout heat transfer mechanisms are discussed through the results. - Abstract: Accurately predicting dryout and post-dryout heat transfer characteristics is critical for proper design of once-through steam generators. This paper provides a reasonable and simple method for this prediction by introducing a two-fluid, three-flow-field mathematical model and improving the dryout criterion-critical quality, and conducts a numerical simulation of dryout and post-dryout heat transfer in a once-through steam generator to prove the model’s performance. The results show that the critical quality in a once-through steam generator is about 0.82, with the heat transfer capacity significantly reducing and the wall temperature sharply increasing in a non-linear form by approximately 30 K when dryout occurs. Part of the steam is superheated in the post-dryout region, resulting in a deviation from thermodynamic equilibrium between the vapor and liquid phases. Dryout and post-dryout heat transfer in the once-through steam generator operate between complete deviation from thermodynamic equilibrium and complete thermodynamic equilibrium. Therefore, the presence of droplets has a significant influence on the mass, momentum and energy transfer between the film and vapor phases.

7. Data base for a CANDU-PHW operating on a once-through, slightly enriched uranium cycle (AECL-6594)

International Nuclear Information System (INIS)

1979-07-01

This report, prepared for INFCE, gives data for an extrapolated 1000 MW(e) CANDU-PHW design operating on a once-through fuel cycle with a feed fuel of slightly enriched uranium - 1.2 weight % U-235 in uranium. The effects of varying fuel enrichment, maximum channel power, and economic parameters are also discussed

8. Efficient boiler operations sourcebook

Energy Technology Data Exchange (ETDEWEB)

Payne, F.W. (comp.)

1985-01-01

This book emphasizes the practical aspects of industrial and commercial boiler operations. It starts with a comprehensive review of general combustion and boiler fundamentals and then deals with specific efficiency improvement methods, and the cost savings which result. The book has the following chapter headings: boiler combustion fundamentals; boiler efficiency goals; major factors controlling boiler efficiency; boiler efficiency calculations; heat loss; graphical solutions; preparation for boiler testing; boiler test procedures; efficiency-related boiler maintenance procedures; boiler tune-up; boiler operational modifications; effect of water side and gas side scale deposits; load management; auxillary equipment to increase boiler efficiency; air preheaters and economizers; other types of auxillary equipment; combustion control systems and instrumentation; boiler O/sub 2/ trim controls; should you purchase a new boiler.; financial evaluation procedures; case studies. The last chapter includes a case study of a boiler burning pulverized coal and a case study of stoker-fired coal.

9. Model tests of a once-through steam generator for land-blocker assessment and THEDA code verification. Final report

International Nuclear Information System (INIS)

Carter, H.R.; Childerson, M.T.; Moskal, T.E.

1983-06-01

The Babcock and Wilcox Company (B and W) operating Once-Through Steam Generators (OTSGs) have experienced leaking tubes in a region adjacent to the untubed inspection lane. The tube leaks have been attributed to an environmentally-assisted fatigue mechanism with moisture transported up the inspection lane being a major factor in the tube-failure process. B and W has developed a hardware modification (lane blockers) to mitigate the detrimental effects of inspection lane moisture. A 30-tube Laboratory Once-through Steam Generator (Designated OTSGC) was designed, fabricated, and tested. Tests were performed with and without five flat-plate lane blockers installed on tube-support plates (TSPs) 10, 11, 12, 13, and 14. The test results were utilized to determine the effectiveness of lane blockers for eliminating moisture transport to the upper tubesheet in the inspection lanes and to benchmark the predictive capabilities of a three-dimensional steam-generator computer code, THEDA

10. Wythenshawe boiler rig. Thirty years of support to the UK nuclear power industry

International Nuclear Information System (INIS)

Rudge, Andy; Woolsey, Ian S.; Moore, Andrew

2010-01-01

The Wythenshawe Boiler Rig in Manchester, UK, recently celebrated thirty years of operation in support of the UK nuclear power industry. The Boiler Rig, owned by EDF Energy and operated on EDF Energy's behalf by Serco plc, is a full scale once-through boiler test facility for the investigation of chemistry and corrosion related topics. This paper presents an overview of the design and operation of the Boiler Rig together with some of the technical highlights from its thirty years of operation, many of which have relevance to power plant operations beyond those plants for which the work was performed. (orig.)

11. Dynamic performance investigation of once-through-type steam generator for NPP using a large-scale model

International Nuclear Information System (INIS)

Kats, F.M.; Ostrovskij, L.A.; Ehskin, N.B.

1985-01-01

An experimental bench is described as well as the results of dynamic performance investigation of mass- and heat transfer of the once-through type steam generator for the NPP with weak superheat. Coolant for the primary and secondary circuit is water. Under investigation conditions the possibility of changin.o primary and secondary circuit temperatures has been supphed as well as the primary circuit flow rate and the secondary circuit pressure changes. Transients for differen.t operating conditions are considered. The possibility for construction of the steam generator automatic control system is based

12. OTSGI--a program analysing two-phase flow instabilities in helical tubes of once-through steam generator

International Nuclear Information System (INIS)

Shi Shaoping; Zhou Fangde; Wang Maohua

1998-01-01

The author has studied the two-phases flow instabilities of the helical tubes of once-through steam generator. Using liner-frequency-domain analytical method, the authors have derived out a mathematical model and designed the program. In this model, the authors also have considered the thermal dynamic characteristics of the tube's wall. The program is used to calculate the threshold of the stability and the influences of some factors, such as entrance throttling coefficient, system pressure, entrance supercooling degree, et al. The outcomes are compared with other studies

13. Wood burning stoves and small boilers - particle emissions and reduction initiatives; Braendeovne og smae kedler - partikelemissioner og reduktionstiltag

Energy Technology Data Exchange (ETDEWEB)

Illerup, J B; Capral Henriksen, T; Lundhede, T [Danmarks Miljoeundersoegelser, Aarhus Universitet, Aarhus (Denmark); Breugel, C van; Zoellner Jensen, N [Miljoestyrelsen, Copenhagen (Denmark)

2007-06-15

Pollution from burning wood in private households, and the environmental and health consequences of this is determined in practice by a complicated interaction between a number of factors, including firing habits, fuel, type of stove/boiler, chimney and location of the chimney in relation to the surroundings. This report maps out the technologies used today for burning wood in private households, how these technologies contribute to particle emissions and which technologies may potentially reduce emissions of particles from burning wood in households in Denmark. Moreover, the possible emissions reductions and the financial costs incurred by consumers from different initiatives have been estimated. This report does not deal with possible initiatives for improvement of firing habits, fuel quality and chimneys. (au)

14. Steady-state and transient prediction of a 19-tube once-through steam generator using RELAP5/MOD1

International Nuclear Information System (INIS)

Hassan, Y.A.; Morgan, C.D.

1983-01-01

Comparisons of the predictions of RELAP5/MOD1 to data obtained from a 19-tube model of a once-through steam generator (OTSG) were performed. The initial results were not satisfactory since the predicted outlet steam temperature was much too low. This discrepancy was traced to the inappropriate use of the modified Zuber critical heat flux (CHF) correlation for the conditions occurring during integral economizer OTSG operation. A study of available low-flow CHF correlations was performed that showed that either the Macbeth or Biasi correlations used in conjunction with RELAP5/MOD1 would produce good agreement with both the steadystate and transient data for the integral economizertype OTSG. The Macbeth correlation was the best for the OTSG with a recirculation path; however, it was not entirely satisfactory due to a slight delay in its prediction of CHF. A loss-of-feedwater transient was modeled using the Macbeth CHF correlation and compared to experimental data with satisfactory results

15. A data base for PHW reactor operating on a once-through, low enriched uranium-thorium cycle

International Nuclear Information System (INIS)

Lungu, S.

1984-04-01

The study of a detailed data base for a new once-through uranium-thorium cycle using low enriched uranium (4 and 5,5% wt. U-235) and distinct UO 2 and ThO 2 fuel channels has been performed. With reference to a standard 638 MWe CANDU-type PHWR with 380 channels, evaluation of economics, fuel behaviour and safety has been performed. The Feinberg-Galanin method (code FEINGAL) has been used for calculation of axial flux distribution. All parameters have been provided by LATREP code following up the irradiation history. Economical assessment has shown that this fuel cycle is competitive with the natural uranium fuel cycle for 1979-based values of the parameters. Fuel behaviour and safety features modelling has shown that core behaviour of the uranium-thorium reactor under abnormal and accident conditions would be at least as good as that of the standard natural uranium reactor

16. Air emissions of small-scale (< 10 MW) biomass boilers. Review of three field tests; Developpement d'un calorimetre a eau pour la dosimetrie au LNE-LNHB

Energy Technology Data Exchange (ETDEWEB)

Autret, E. [Agence de l' Environnement et de la Maitrise de l' Energie, ADEME, 49 - Angers (France)

2011-01-15

Objectives of greenhouse gases emission reduction, which encourages bio-energy development for heat purposes, are compatible with air-quality policies if the concept of clean biomass combustion is applied. This paper presents actual emission levels of atmospheric pollutants of small-scale (< 10 MW) biomass boilers from a review of three field tests carried out between 2007 and 2009. 31 biomass boilers have been audited to cover the large diversity of sites under operation in terms of fuels, power, flue-gas cleaning devices.. Results are compared to actual and forecasted regulations. The review shows that fuel quality and operation are key issues to ensure low emissions of organic pollutants (OC, VOC, CnHm, PCDD/F, PAH, PCB, HCB), SO{sub 2}, NO{sub x}, fine particulate matters, metallic compounds. Installation design (power, flue-gas cleaning techno logy) also has a major impact on organic pollutants and fine particulate matter emissions. A large majority of boilers have very low emission levels. Guidelines are finally stated to keep on promoting small-scale biomass boilers in order to be air-quality compatible and efficient to fight climate change. (author)

17. The mechanical design and validation of the helical tube boilers for Hartlepool and Heysham AGR stations

International Nuclear Information System (INIS)

Skinner, V.R.

1983-01-01

The 32 helically coiled once-through boiler units at Hartlepool and Heysham represent a major advance in the technologies of boiler design, manufacture and site construction. They are particularly complex in that they incorporate integral reheaters; they employ three different tubing materials and five different structural materials, each with operating temperature limitations; and they must fit compactly into pods in the reactor pressure vessel walls. A general description of the boilers is followed by a review of external factors which influenced the mechanical design and validation programme over 15 years. Against this background selected components are discussed in detail in terms of particular loading conditions and stress analysis. (author)

18. Fuel cycle performance indices in a high-converting LWR core design with once-through thorium fuel cycle

International Nuclear Information System (INIS)

Kim, Myung-Hyun; Kim, Kwan-Hee; Kim, Young-il

2004-01-01

A design concept of pressure-tube type light water cooled reactor (HCPLWR) core was proposed as a thermal high-conversion reactor using a thorium based once-through cycle strategy. In a previous work, fuel cycle economics and nuclear safety were confirmed. In this work, HCPLWR was evaluated in the aspects of proliferation resistance and transmutation capability. Evaluation was done as a direct comparison of indices with PWR, CANDU and Radkowsky Thorium Fuel (RTF). Conversion ratio was measured by fissile inventory ratio and fissile gain. Proliferation resistance of plutonium composition from spent seed and blanket fuels was measured by bare critical mass, spontaneous neutron source rate, and thermal heat generation rate. For the evaluation of long-lived minor actinide transmutation was measured by a new parameter, effective fission half-life. Two-dimensional calculation for the assembly-wise unit module showed each parameter values. Even though conversion capability of HCPLWR was higher than one of RTF, it was concluded that current HCPLWR design was not favorable than RTF. Design optimization is required for the future work. (author)

19. Preliminary design study of pebble bed reactor HTR-PM base using once-through-then-out fuel recirculation

International Nuclear Information System (INIS)

Topan Setiadipura; Jupiter S Pane; Zuhair

2016-01-01

Pebble Bed Reactor (PBR) is one of the advanced reactor type implementing strong passive safety feature. In this type of design has the potential to do a cogeneration useful for the treatment of various minerals in various islands in Indonesia. The operation of the PBR can be simplified by implementing once-through-then-out (OTTO) fuel recirculation scheme in which pebble fuel only pass the core once time. The purpose of this research is to understand quantitative influence of the changing of fuel element recirculation on the PBR core performance and to find preliminary optimization design of PBR type reactor with OTTO recirculation scheme. PEBBED software was used to find PBR equilibrium core. The calculation result gives quantitative data on the impact of implementing a different fuel recirculation, especially using OTTO scheme. Furthermore, an early optimized PBR design based on HTR-PM using OTTO scheme was obtained where the power must be downgraded into 115 MWt in order to preserve the safety feature. The simplicity of the reactor operation and the reduction of reactor component with OTTO scheme still make this early optimized design an interesting alternative design, despite its power reduction from the reference design. (author)

20. RELAP5/MOD2 code modifications to obtain better predictions for the once-through steam generator

International Nuclear Information System (INIS)

Blanchat, T.; Hassan, Y.

1989-01-01

The steam generator is a major component in pressurized water reactors. Predicting the response of a steam generator during both steady-state and transient conditions is essential in studying the thermal-hydraulic behavior of a nuclear reactor coolant system. Therefore, many analytical and experimental efforts have been performed to investigate the thermal-hydraulic behavior of the steam generators during operational and accident transients. The objective of this study is to predict the behavior of the secondary side of the once-through steam generator (OTSG) using the RELAP5/MOD2 computer code. Steady-state conditions were predicted with the current version of the RELAP5/MOD2 code and compared with experimental plant data. The code predictions consistently underpredict the degree of superheat. A new interface friction model has been implemented in a modified version of RELAP5/MOD2. This modification, along with changes to the flow regime transition criteria and the heat transfer correlations, correctly predicts the degree of superheat and matches plant data

1. Investigation of economics of nuclear fuel cycle options in the Republic of Korea based on once-through - 5468

International Nuclear Information System (INIS)

Cho, S.K.; Yim, M.S.

2015-01-01

This study performs an economic evaluation of future nuclear fuel cycle options based on once-through strategy. Various factors of the future development in Korea are also considered including nuclear phase-out, continuous use of nuclear energy at varying growth rate, and the reunification of the Korean peninsula. A spreadsheet model is developed as part of the methodology of screening material flow and economic evaluation and results are discussed for policy planning for Korea as well as for nuclear developing countries. Results indicated that economics improves as the size of nuclear power system increases. We found some significant factors that affect LCOE (levelized cost of electricity) of the back end fuel cycle. Expanded nuclear power program with further construction of nuclear power plant (continuous use and/or the reunification) is a major political variable for LCOE. To keep the cost of nuclear power as low as possible, it is very important to have a proper strategy for the back-end fuel cycle including decommissioning. For continued use of nuclear energy, the Korea needs to develop soon a long-term policy for the back-end fuel cycle rather than taking the 'sit and watch' approach to make best out of the use of nuclear power into the future

2. Friction pressure drop and heat transfer coefficient of two-phase flow in helically coiled tube once-through steam generator for integrated type marine water reactor

International Nuclear Information System (INIS)

Nariai, Hideki; Kobayashi, Michiyuki; Matsuoka, Takeshi.

1982-01-01

Two-phase friction pressure drop and heat transfer coefficients in a once-through steam generator with helically coiled tubes were investigated with the model test rig of an integrated type marine water reactor. As the dimensions of the heat transfer tubes and the thermal-fluid conditions are almost the same as those of real reactors, the data applicable directly to the real reactor design were obtained. As to the friction pressure drop, modified Kozeki's prediction which is based on the experimental data by Kozeki for coiled tubes, agreed the best with the experimental data. Modified Martinelli-Nelson's prediction which is based on Martinelli-Nelson's multiplier using Ito's equation for single-phase flow in coiled tube, agreed within 30%. The effect of coiled tube on the average heat transfer coefficients at boiling region were small, and the predictions for straight tube could also be applied to coiled tube. Schrock-Grossman's correlation agreed well with the experimental data at the pressures of lower than 3.5 MPa. It was suggested that dryout should be occurred at the quality of greater than 90% within the conditions of this report. (author)

3. Chemical and physical properties of cyclone fly ash from the grate-fired boiler incinerating forest residues at a small municipal district heating plant (6MW).

Science.gov (United States)

Pöykiö, R; Rönkkömäki, H; Nurmesniemi, H; Perämäki, P; Popov, K; Välimäki, I; Tuomi, T

2009-03-15

In Finland, the new limit values for maximal allowable heavy metal concentrations for materials used as an earth construction agent came into force in July 2006. These limit values are applied if ash is utilized, e.g. in roads, cycling paths, pavements, car parks, sport fields, etc. In this study we have determined the most important chemical and physical properties of the cyclone fly ash originating from the grate-fired boiler incinerating forest residues (i.e. wood chips, sawdust and bark) at a small municipal district heating plant (6 MW), Northern Finland. This study clearly shows that elements are enriched in cyclone fly ash, since the total element concentrations in the cyclone fly ash were within 0.2-10 times higher than those in the bottom ash. The total concentrations of Cd (25 mg kg(-1); d.w.), Zn (3630 mg kg(-1); d.w.), Ba (4260 mg kg(-1); d.w.) and Hg (1.7 mg kg(-1); d.w.) exceeded the limit values, and therefore the cyclone fly ash cannot be used as an earth construction agent. According to the leached amounts of Cr (38 mg kg(-1); d.w.), Zn (51 mg kg(-1); d.w.) and sulphate (50,000 mg kg(-1); d.w.), the cyclone fly ash is classified as a hazardous waste, and it has to be deposited in a hazardous waste landfill.

4. Performance evaluation of a once-through multi-stage flash distillation system: Impact of brine heater fouling

International Nuclear Information System (INIS)

Baig, Hasan; Antar, Mohamed A.; Zubair, Syed M.

2011-01-01

Multi-stage flash distillation (MSF) system modeling involves a number of process variables. An estimation of all these process variables requires both analytical solutions and experimental/field analysis. However, the accurate estimate of variables related to the brine heater operation in a MSF system is very important for a reliable operation of the system. For example, steam operating conditions as well as the brine properties including fouling of the brine heater tubes have a significant effect on the heat transfer characteristics of the brine heater, which in turn influence the distillate output from the system. In this study, the effect of various design as well as operating conditions on the performance ratio (PR), brine temperature and salinity as it leaves the last flash stage are investigated in a once-through system. Increasing the number of stages from 24 to 32 has a significant effect on the PR, it ranges between 79% (for ΔT = 1.5) and 327% (for ΔT = 2.3) for a top-brine temperature of 106 o C. This value increase as the top-brine temperature increases. Increasing the stage-to-stage temperature difference increases the water salinity as it leaves the final stage and reduces its temperature that would imply better energy utilization within the plant. Results show that brine side heat exchanger fouling has a significant effect in decreasing the overall heat transfer coefficient, which reduces the production rate as the fouling increases with time. A sensitivity analysis to identify the key parameters, which can have a significant influence on the desalination plant performance, is carried out in an attempt to contribute a better understanding and operation of MSF desalination processes.

5. Development of a novel once-through flow visualization technique for kinetic study of bulk and surface scaling

Science.gov (United States)

Sanni, O.; Bukuaghangin, O.; Huggan, M.; Kapur, N.; Charpentier, T.; Neville, A.

2017-10-01

There is a considerable interest to investigate surface crystallization in order to have a full mechanistic understanding of how layers of sparingly soluble salts (scale) build on component surfaces. Despite much recent attention, a suitable methodology to improve on the understanding of the precipitation/deposition systems to enable the construction of an accurate surface deposition kinetic model is still needed. In this work, an experimental flow rig and associated methodology to study mineral scale deposition is developed. The once-through flow rig allows us to follow mineral scale precipitation and surface deposition in situ and in real time. The rig enables us to assess the effects of various parameters such as brine chemistry and scaling indices, temperature, flow rates, and scale inhibitor concentrations on scaling kinetics. Calcium carbonate (CaCO3) scaling at different values of the saturation ratio (SR) is evaluated using image analysis procedures that enable the assessment of surface coverage, nucleation, and growth of the particles with time. The result for turbidity values measured in the flow cell is zero for all the SR considered. The residence time from the mixing point to the sample is shorter than the induction time for bulk precipitation; therefore, there are no crystals in the bulk solution as the flow passes through the sample. The study shows that surface scaling is not always a result of pre-precipitated crystals in the bulk solution. The technique enables both precipitation and surface deposition of scale to be decoupled and for the surface deposition process to be studied in real time and assessed under constant condition.

6. Effects on potential once-through improvements on the uranium utilisation in the closed LWR cycle assuming self-generated recycling of uranium and plutonium

International Nuclear Information System (INIS)

1979-01-01

This paper describes the mode of operation of a reference 1300 MW(e) PWR operating on self-generating U/Pu recycle and then considers the uranium saving which might be achieved by introducing a number of improvements in design and operation which have been suggested for the once-through cycle. These are: Increased burnup, lattice changes, spectrum shift, enrichment zoning including blankets, full use of early batches of start-up core, improved fuel management and control design, end of cycle coastdown, reconstitution and inversion of BWR fuel, more frequent refueling. The paper concludes that if both the once-through cycle and recycle in the SGR mode were improved to the optimum extent recycle would offer 25-30% uranium savings compared to the once-through cycle

7. Development of a 1D thermal-hydraulic analysis code for once-through steam generator in SMRs using straight tubes

Energy Technology Data Exchange (ETDEWEB)

Park, Youngjae; Kim, Iljin; Kim, Hyungdae [Kyung Hee University, Yongin (Korea, Republic of)

2015-10-15

Diverse integral/small-modular reactors (SMRs) have been developed. Once-through steam generator (OTSG) which generates superheated steam without steam separator and dryer was used in the SMRs to reduce volume of steam generator. It would be possible to design a new steam generator with best estimate thermal-hydraulic codes such as RELAP and MARS. However, it is not convenience to use the general purpose thermal-hydraulic analysis code to design a specific component of nuclear power plants. A widely used simulation tool for thermal-hydraulic analysis of drum-type steam generators is ATHOS, which allows 3D analysis. On the other hand, a simple 1D thermal-hydraulic analysis code might be accurate enough for the conceptual design of OTSG. In this study, thermal-hydraulic analysis code for conceptual design of OTSG was developed using 1D homogeneous equilibrium model (HEM). A benchmark calculation was also conducted to verify and validate the prediction accuracy of the developed code by comparing with the analysis results with MARS. Finally, conceptual design of OTSG was conducted by the developed code. A simple 1D thermal-hydraulic analysis code was developed for the purpose of conceptual design OTSG for SMRs. A set of benchmark calculations was conducted to verify and validate the analysis accuracy of the developed code by comparing results obtained with a best-estimated thermal-hydraulic analysis code, MARS. Finally, analysis of two different OTSG design concepts with superheating and recirculation was demonstrated using the developed code.

8. Fluidized bed boiler feed system

Science.gov (United States)

Jones, Brian C.

1981-01-01

A fluidized bed boiler feed system for the combustion of pulverized coal. Coal is first screened to separate large from small particles. Large particles of coal are fed directly to the top of the fluidized bed while fine particles are first mixed with recycled char, preheated, and then fed into the interior of the fluidized bed to promote char burnout and to avoid elutriation and carryover.

9. Boiler conversions for biomass

Energy Technology Data Exchange (ETDEWEB)

Kinni, J [Tampella Power Inc., Tampere (Finland)

1997-12-31

Boiler conversions from grate- and oil-fired boilers to bubbling fluidized bed combustion have been most common in pulp and paper industry. Water treatment sludge combustion, need for additional capacity and tightened emission limits have been the driving forces for the conversion. To accomplish a boiler conversion for biofuel, the lower part of the boiler is replaced with a fluidized bed bottom and new fuel, ash and air systems are added. The Imatran Voima Rauhalahti pulverized-peat-fired boiler was converted to bubbling fluidized bed firing in 1993. In the conversion the boiler capacity was increased by 10 % to 295 MWth and NO{sub x} emissions dropped. In the Kymmene Kuusankoski boiler, the reason for conversion was the combustion of high chlorine content biosludge. The emissions have been under general European limits. During the next years, the emission limits will tighten and the boilers will be designed for most complete combustion and compounds, which can be removed from flue gases, will be taken care of after the boiler. (orig.) 3 refs.

10. Boiler conversions for biomass

Energy Technology Data Exchange (ETDEWEB)

Kinni, J. [Tampella Power Inc., Tampere (Finland)

1996-12-31

Boiler conversions from grate- and oil-fired boilers to bubbling fluidized bed combustion have been most common in pulp and paper industry. Water treatment sludge combustion, need for additional capacity and tightened emission limits have been the driving forces for the conversion. To accomplish a boiler conversion for biofuel, the lower part of the boiler is replaced with a fluidized bed bottom and new fuel, ash and air systems are added. The Imatran Voima Rauhalahti pulverized-peat-fired boiler was converted to bubbling fluidized bed firing in 1993. In the conversion the boiler capacity was increased by 10 % to 295 MWth and NO{sub x} emissions dropped. In the Kymmene Kuusankoski boiler, the reason for conversion was the combustion of high chlorine content biosludge. The emissions have been under general European limits. During the next years, the emission limits will tighten and the boilers will be designed for most complete combustion and compounds, which can be removed from flue gases, will be taken care of after the boiler. (orig.) 3 refs.

11. Design and performance of the helically coiled boilers of two AGR power stations in the United Kingdom

International Nuclear Information System (INIS)

El-Nagdy, M.; Papa, A.D.

1988-01-01

The Hartlepool and Heysham-I AGR stations have been commissioned and operating since 1983. The main features, of the design of the helical once-through boilers raising the steam for power generation, are outlined. The modifications to the feed inlet flow ferrules, necessary to improve the boiler performance and optimize the power output, have been described. Comparisons between the thermal and hydrodynamic performance of the boilers before and following these alterations are given. The improvements in the computer code predictions of the plant performance have also been presented. (author)

12. Occurrence and prevention of enhanced oxide deposition in boiler flow control orifices

International Nuclear Information System (INIS)

Woolsey, I.S.; Thomas, D.M.; Garbett, K.; Bignold, G.J.

1989-10-01

Once-through boilers, such as those of the AGRs, incorporate flow control orifices at the boiler inlet to ensure a satisfactory flow distribution and stability in the parallel flow paths of the boiler. Deposition of corrosion products in the flow control orifice leads to changes in the orifice pressure loss characteristics, which could lead to problems of flow maldistribution within the boiler, and any adverse consequences resulting from this, such as tube overheating. To date, AGR boiler inlet orifices have not suffered significant fouling due to corrosion products in the boiler feedwater. However, oxide deposition in orifices has been observed in other plants, and in experimental loops operating under conditions very similar to those at inlet to AGR boilers. The lack of deposition in AGR flow control orifices is therefore somewhat surprising. This Report describes studies carried out to examine the factors controlling oxide deposition in flow control orifices, the intention of the work being to explain why deposition has not occurred in AGR boilers to date, and to provide means of preventing deposition in the future should this prove necessary. (author)

13. Electric utility CFB boilers

International Nuclear Information System (INIS)

Fairbanks, D.A.

1991-01-01

This paper reports on Circulating Fluidized Bed (CFB) boiler technology which caught the attention of boiler users: first for its technical advantages of reduced air emissions and low grade fuel tolerance, then later for its problems in becoming a reliable process. Refractory longevity and fuel feed reliability plagued a number of new installations. The efficacy of CFB technology is now more assured with the recent success of Texas-New Mexico Power Company's 160 MWe CFB based units, the world's largest operating CFB boilers. Most of the more notable CFB development problems have been successfully addressed by these units. The TNP units have demonstrated that CFB's can reliable produce high capacity factors at low emission rates using a fuel that has traditionally hampered the operation of pulverized coal (PC) boilers and without the attendant problems associated with sulfur scrubbers required by PC boilers

14. Final stage of first supercritical 460MW{sub e} CFB boiler construction. First experience

Energy Technology Data Exchange (ETDEWEB)

Goral, Damian [Foster Wheeler Energia Polska (Poland); Ostrowski, Waldemar [PKE (Poland)

2009-07-01

Circulating fluidized bed (CFB) boiler technology has been growing in size and number over the past two decades and it has established its position as utility scale boiler technology. Plant sizes up to 300 MW{sub e} are in operation today and designs for larger boilers are being developed. The next natural step for CFB technology is to go for supercritical steam parameters and larger boiler sizes. A Polish utility company Poludniowy Koncern Energetyczny SA (PKE) placed an order to Foster Wheeler Energia Oy for a 460 MW{sub e} supercritical CFB boiler for their Lagisza power plant. Contract was signed at the end of year 2002 and the engineering work is now ongoing. This will be the first supercritical once-through CFB boiler in the world. A modern power plant is designed for high efficiency not only for economical reasons but also for enhanced environmental performance in terms of reduced emissions and quantity of ash generated due to lower fuel consumption. Cutting CO{sub 2} emissions is one of the main drivers. To achieve these goals, supercritical steam parameters have been applied. Now this technology is available also for CFB technology. This combines a high plant efficiency with the other well known benefits of CFB technology, such as: fuel flexibility, low emissions and high availability. The boiler design for 460 MW{sub e} Lagisza power plant utilizes low mass flux BENSON Vertical once-through technology developed and licensed by Siemens AG, Germany. CFB boiler with low and uniform furnace heat flux is extremely well suited for the Benson technology providing a stable operation of the boiler also during load changes and abnormal operation conditions. The paper describes the 460 MW{sub e} supercritical CFB boiler concept and presents the technical solutions of the boiler design with auxiliary equipment, as well as first experiences from boiler erection period and commissioning. In spite of achieving this remarkable milestone the development of the CFB

15. Assessment of physical workload in boiler operations.

Science.gov (United States)

Rodrigues, Valéria Antônia Justino; Braga, Camila Soares; Campos, Julio César Costa; Souza, Amaury Paulo de; Minette, Luciano José; Sensato, Guilherme Luciano; Moraes, Angelo Casali de; Silva, Emília Pio da

2012-01-01

The use of boiler wood-fired is fairly common equipment utilized in steam generation for energy production in small industries. The boiler activities are considered dangerous and heavy, mainly due to risks of explosions and the lack of mechanization of the process. This study assessed the burden of physical labor that operators of boilers are subjected during the workday. Assessment of these conditions was carried out through quantitative and qualitative measurements. A heart rate monitor, a wet-bulb globe thermometer (WBGT), a tape-measure and a digital infrared camera were the instruments used to collect the quantitative data. The Nordic Questionnaire and the Painful Areas Diagram were used to relate the health problems of the boiler operator with activity. With study, was concluded that the boiler activity may cause pains in the body of intensity different, muscle fatigue and diseases due to excessive weight and the exposure to heat. The research contributed to improve the boiler operator's workplace and working conditions.

16. On the evaluation of lifetime of evaporative tubes of once-through steam generators at steam-generating surface temperature oscillations in the burnout region

International Nuclear Information System (INIS)

Vorob'ev, V.A.; Loshchinin, V.M.; Remizov, O.V.

1978-01-01

Suggested is a method for evaluation of a stressed state of evaporation tubes of once-through steam generators at temperature oscillations in the burnout region. Calculated is the amplitude of steam-generating surface temperature oscillations in the burnout region depending on the frequency of a liquid-steam boundary transfer and on this basis determined are thermal stresses in a tube wall. Knowing a fatigue curve gives the possibility to evaluate a heat transfer tube lifetime

17. Effects of potential once-through improvements on the uranium utilization in the closed LWR cycle assuming self generated recycling of uranium and plutonium

International Nuclear Information System (INIS)

1979-06-01

This paper is concerned with potential improvements to the resource utilization of current generation light water reactors operating on a closed U/Pu fuel cycle. Only those modifications to existing systems layout and fuel cycle practise are discussed that have been considered in Working Group 8 A for the once-through cycle. The objective is to give an impression how much the difference in resource utilization between the once-through and the closed U/Pu cycle were changed if both cycles were reoptimized independantly from each other with respect to uranium consumption. No commercial recycling of U/Pu has been taken place to date in 1300 MWe light water reactors. The feasibility of thermal recycling has been demonstrated however on an industrial scale in reactors of the 300 MWe class. (Obrigheim, Gundremmingen). From this experience and from extensive design calculations it has been concluded that for Pu bearing fuel assemblies of 1300 MWe plants it would be favorable to use the same structural layout and similar fuel management procedures as for uranium assemblies. This would result in plant life-time averaged uranium savings on the order of 35 - 40 % relative to the once-through cycle in case of the Self Generated Recycling Mode

18. CECIL lances Bruce's boilers

International Nuclear Information System (INIS)

Malaugh, J.; Monaghan, D.

1994-01-01

Over the past few years Ontario Hydro has become increasingly concerned about accumulations of sludge in its nuclear plant boilers, so a comprehensive sludge management programme has been instituted to combat build-up. This included developing the tele-operated robot CECIL (Consolidated Edison Combined Inspection and Lancing) equipment, originally designed for work in PWRs, for CANDU boilers. This required a significantly reconfigured robotic system as well as modifications to the boilers themselves. Work on the Bruce A reactor is described. (4 figures). (author)

19. Water Boiler Change-Over in Mini-TPP Mode

Directory of Open Access Journals (Sweden)

B. A. Bayrashevsky

2011-01-01

Full Text Available The paper considers water boiler modernization by its change-over in mini-TPP mode with an expansion tank and a heating turbine of small capacity.  A software complex permitting to evaluate competitive ability of such water boiler modernization in comparison with a cogeneration plant.

20. ENERGY STAR Certified Boilers

Data.gov (United States)

U.S. Environmental Protection Agency — Certified models meet all ENERGY STAR requirements as listed in the Version 3.0 ENERGY STAR Program Requirements for Boilers that are effective as of October 1,...

1. Charting the boiler market

International Nuclear Information System (INIS)

2003-01-01

The ''boiler market'' of electricity, sometimes called unsecured transmission, is electric power consumption that in public statistics is restricted by the obligation of the customers to cut their consumption at short notice and therefore are granted some discount on the network lease. The present document is part of a project that aims to provide a better understanding of the flexibility in the Norwegian power market, limited by the power-intensive industry and the boiler market. It discusses the boiler market. It begins with a discusses of the available statistics, where different sources show very dissimilar consumption figures. Then it examines how the consumption in the boiler market developed during the winter 2002/2003. Finally, there is a description of the regulations of unsecured transmission and how the various network owners adapt to the regulations.

2. Dynamic Boiler Performance

DEFF Research Database (Denmark)

Sørensen, Kim

Traditionally, boilers have been designed mainly focussing on the static operation of the plant. The dynamic capability has been given lower priority and the analysis has typically been limited to assuring that the plant was not over-stressed due to large temperature gradients. New possibilities...... developed. Analyzing boilers for dynamic operation gives rise to a number of opposing aims: shrinking and swelling, steam quality, stress levels, control system/philosophy, pressurization etc. Common for these opposing aims is that an optimum can be found for selected operation conditions. The framework has...... for buying and selling energy has increased the focus on the dynamic operation capability, efciency, emissions etc. For optimizing the design of boilers for dynamic operation a quantication of the dynamic capability is needed. A framework for optimizing design of boilers for dynamic operation has been...

3. MODELLING, SIMULATING AND OPTIMIZING BOILERS

DEFF Research Database (Denmark)

Sørensen, Kim; Condra, Thomas Joseph; Houbak, Niels

2004-01-01

In the present work a framework for optimizing the design of boilers for dynamic operation has been developed. A cost function to be minimized during the optimization has been formulated and for the present design variables related to the Boiler Volume and the Boiler load Gradient (i.e. ring rate...... on the boiler) have been dened. Furthermore a number of constraints related to: minimum and maximum boiler load gradient, minimum boiler size, Shrinking and Swelling and Steam Space Load have been dened. For dening the constraints related to the required boiler volume a dynamic model for simulating the boiler...... performance has been developed. Outputs from the simulations are shrinking and swelling of water level in the drum during for example a start-up of the boiler, these gures combined with the requirements with respect to allowable water level uctuations in the drum denes the requirements with respect to drum...

4. Control Properties of Bottom Fired Marine Boilers

DEFF Research Database (Denmark)

Solberg, Brian; Andersen, Palle; Karstensen, Claus M. S.

2007-01-01

This paper focuses on model analysis of a dynamic model of a bottom fired one-pass smoke tube boiler. Linearized versions of the model are analyzed and show large variations in system gains at steady state as function of load whereas gain variations near the desired bandwidth are small. An analys...

5. Boiler house modernization through shared savings program

Energy Technology Data Exchange (ETDEWEB)

Breault, R.W. [Tecogen, Waltham, MA (United States)

1995-12-31

Throughout Poland as well as the rest of Eastern Europe, communities and industries rely on small heat only boilers to provide district and process heat. Together these two sectors produce about 85,000 MW from boilers in the 2 to 35 MW size range. The bulk of these units were installed prior to 1992 and must be completely overhauled to meet the emission regulations which will be coming into effect on January 1, 1998. Since the only practical fuel is coal in most cases, these boilers must be either retrofit with emission control technology or be replaced entirely. The question that arises is how to accomplish this given the current tight control of capital in Poland and other East European countries. A solution that we have for this problem is shared savings. These boilers are typically operating with a quiet low efficiency as compared to western standards and with excessive manual labor. Installing modernization equipment to improve the efficiency and to automate the process provides savings. ECOGY provides the funds for the modernization to improve the efficiency, add automation and install emission control equipment. The savings that are generated during the operation of the modernized boiler system are split between the client company and ECOGY for a number of years and then the system is turned over in entirety to the client. Depending on the operating capacity, the shared savings agreement will usually span 6 to 10 years.

6. Physico-chemical characteristics of eight different biomass fuels and comparison of combustion and emission results in a small scale multi-fuel boiler

International Nuclear Information System (INIS)

Forbes, E.G.A.; Easson, D.L.; Lyons, G.A.; McRoberts, W.C.

2014-01-01

Highlights: • Physical parameters of the eight biomass fuels examined were all different. • Significant differences were found in Proximate, Ultimate and TGA results. • Energy outputs were not proportionate to dry matter energy content. • Highest flue ash production from fuels with highest fines content. • Flue gas emissions varied significantly, NOx levels correlated with fuel N content. - Abstract: This study describes the results from the investigation of 7 different biomass fuel types produced on a farm, and a commercial grade wood pellet, for their physical, chemical, thermo-gravimetric and combustion properties. Three types of short rotation coppice (SRC) willow, two species of conifers, forest residues (brash), commercially produced wood-pellets and a chop harvested energy grass crop Miscanthus giganteus spp., (elephant grass) were investigated. Significant differences (p < 0.05) were found in most of the raw fuel parameters examined using particle distribution, Thermogravimetric, Ultimate and Proximate analysis. Combustion tests in a 120 kW multi-fuel boiler revealed differences, some significant, in the maximum output, energy conversion efficiency, gaseous emission profiles and ash residues produced from the fuels. It was concluded that some of the combustion results could be directly correlated with the inherent properties of the different fuels. Ash production and gaseous emissions were the aspects of performance that were clearly and significantly different though effects on energy outputs were more varied and less consistent. The standard wood pellet fuel returned the best overall performance and miscanthus produced the largest amount of total ash and clinker after combustion in the boiler

7. Super Boiler: First Generation, Ultra-High Efficiency Firetube Boiler

Energy Technology Data Exchange (ETDEWEB)

None

2006-06-01

This factsheet describes a research project whose goal is to develop and demonstrate a first-generation ultra-high-efficiency, ultra-low emissions, compact gas-fired package boiler (Super Boiler), and formulate a long-range RD&D plan for advanced boiler technology out to the year 2020.

8. Mitigating the Risk of Stress Corrosion of Austenitic Stainless Steels in Advanced Gas Cooled Reactor Boilers

International Nuclear Information System (INIS)

Bull, A.; Owen, J.; Quirk, G.; G, Lewis; Rudge, A.; Woolsey, I.S.

2012-09-01

Advanced Gas-Cooled Reactors (AGRs) operated in the UK by EDF Energy have once-through boilers, which deliver superheated steam at high temperature (∼500 deg. C) and pressure (∼150 bar) to the HP turbine. The boilers have either a serpentine or helical geometry for the tubing of the main heat transfer sections of the boiler and each individual tube is fabricated from mild steel, 9%Cr1%Mo and Type 316 austenitic stainless steel tubing. Type 316 austenitic stainless steel is used for the secondary (final) superheater and steam tailpipe sections of the boiler, which, during normal operation, should operate under dry, superheated steam conditions. This is achieved by maintaining a specified margin of superheat at the upper transition joint (UTJ) between the 9%Cr1%Mo primary superheater and the Type 316 secondary superheater sections of the boiler. Operating in this mode should eliminate the possibility of stress corrosion cracking of the Type 316 tube material on-load. In recent years, however, AGRs have suffered a variety of operational problems with their boilers that have made it difficult to maintain the specified superheat margin at the UTJ. In the case of helical boilers, the combined effects of carbon deposition on the gas side and oxide deposition on the waterside of the tubing have resulted in an increasing number of austenitic tubes operating with less than the specified superheat margin at the UTJ and hence the possibility of wetting the austenitic section of the boiler. Some units with serpentine boilers have suffered creep-fatigue damage of the high temperature sections of the boiler, which currently necessitates capping the steam outlet temperature to prevent further damage. The reduction in steam outlet temperature has meant that there is an increased risk of operation with less than the specified superheat margin at the UTJ and hence stress corrosion cracking of the austenitic sections of the boiler. In order to establish the risk of stress

9. Solved and unsolved problems in boiler systems. Learning from accidents

International Nuclear Information System (INIS)

Ozawa, Mamoru

2000-01-01

This paper begins with a brief review on the similarity law of conventional fossil-fuel-fired boilers. The concept is based on the fact that the heat release due to combustion in the furnace is restricted by the furnace volume but the heat absorption is restricted by the heat transfer surface area. This means that a small-capacity boiler has relatively high specific furnace heat release rate, about 10 MW/m 3 , and on the contrary a large-capacity boiler has lower value. The surface-heat-flux limit is mainly dominated by the CHF inside the water-wall tubes of the boiler furnace, about 350 kW/m 2 . This heat-flux limit is almost the same order independently on the capacity of boilers. For the safety of water-walls, it is essential to retain suitable water circulation, i.e. circulation ratio and velocity of water. This principle is a common knowledge of boiler designer, but actual situation is not the case. Newly designed boilers often suffer from similar accidents, especially burnout due to circulation problems. This paper demonstrates recent accidents encountered in practical boilers, and raises problems of rather classical but important two-phase flow and heat transfer. (author)

10. Flow-induced vibration analysis of Three Mile Island Unit-2 once-through steam generator tubes. Volume 1. Final report

International Nuclear Information System (INIS)

Johnson, J.R.; Brown, J.C.; Harris, C.E.; McGuinn, E.J.; Simonis, J.C.; Thoren, D.E.

1981-06-01

Tube responses to flow-induced vibration were measured in the top two spans and the tenth span in the B once-through steam generator at Three Mile Island, Unit 2. This program evaluated the effects of flow-induced biration of OTSG tubes during steady-state and transient operation. Twenty-three tubes were instrumented with accelerometers and strain gages in tubes located along the open lane, in the bundle, and at the tenth span. Tube displacements, frequencies, dynamic strains, and mode shapes were determined during steady-state and transient operation. Pressure sensors were installed in the OTSG to measure pressure fluctuations and plant parameters, which were recorded for correlation with tube response. Data analysis results indicate that the steady-state tube response increases with increasing reactor power, with the maximum response (12 mils peak to peak at midspan) at the outer perimeter of the generator in the 16th span

11. Steady-state simulations of a 30-tube once-through steam generator with the RELAP5/MOD3 and RELAP5/MOD2 computer codes

International Nuclear Information System (INIS)

Hassan, Y.A.; Salim, P.

1991-01-01

This paper reports on a steady-state analysis of a 30-tube once-through steam generator that has been performed on the RELAPS/MOD3 and RELAPS/MOD2 computer codes for 100, 75, and 65% loads. Results obtained are compared with experimental data. The RELAP5/MOD3 results for the test facility generally agree reasonably well with the data for the primary-side temperature profiles. The secondary-side temperature profile predicted by RELAP5/MOD3 at 75 and 65% loads agrees fairly well with the data and is better than the RELAP5/MOD2 results. However, the RELAP5/MOD3 calculated secondary-side temperature profile does not compare well with the 100% load data

12. Comparative assessment of nuclear fuel cycles. Light-water reactor once-through, classical fast breeder reactor, and symbiotic fast breeder reactor cycles

International Nuclear Information System (INIS)

Hardie, R.W.; Barrett, R.J.; Freiwald, J.G.

1980-06-01

The object of the Alternative Nuclear Fuel Cycle Study is to perform comparative assessments of nuclear power systems. There are two important features of this study. First, this evaluation attempts to encompass the complete, integrated fuel cycle from mining of uranium ore to disposal of waste rather than isolated components. Second, it compares several aspects of each cycle - energy use, economics, technological status, proliferation, public safety, and commercial potential - instead of concentrating on one or two assessment areas. This report presents assessment results for three fuel cycles. These are the light-water reactor once-through cycle, the fast breeder reactor on the classical plutonium cycle, and the fast breeder reactor on a symbiotic cycle using plutonium and 233 U as fissile fuels. The report also contains a description of the methodology used in this assessment. Subsequent reports will present results for additional fuel cycles

13. Optimising boiler performance.

Science.gov (United States)

Mayoh, Paul

2009-01-01

Soaring fuel costs continue to put the squeeze on already tight health service budgets. Yet it is estimated that combining established good practice with improved technologies could save between 10% and 30% of fuel costs for boilers. Paul Mayoh, UK technical manager at Spirax Sarco, examines some of the practical measures that healthcare organisations can take to gain their share of these potential savings.

14. A Comparative Study of Fouling and Bottom Ash from Woody Biomass Combustion in a Fixed-Bed Small-Scale Boiler and Evaluation of the Analytical Techniques Used

Directory of Open Access Journals (Sweden)

Lara Febrero

2015-05-01

Full Text Available In this work, fouling and bottom ash were collected from a low-power boiler after wood pellet combustion and studied using several analytical techniques to characterize and compare samples from different areas and determine the suitability of the analysis techniques employed. TGA results indicated that the fouling contained a high amount of organic matter (70%. The XRF and SEM-EDS measurements revealed that Ca and K are the main inorganic elements and exhibit clear tendency in the content of Cl that is negligible in the bottom ash and increased as it penetrated into the innermost layers of the fouling. Calcite, magnesia and silica appeared as the major crystalline phases in all the samples. However, the bottom ash was primarily comprised of calcium silicates. The KCl behaved identically to the Cl, preferably appeared in the adhered fouling samples. This salt, which has a low melting point, condenses upon contact with the low temperature tube and played a crucial role in the early stages of fouling formation. XRD was the most useful technique applied, which provided a semi-quantitative determination of the crystalline phases. FTIR was proven to be inadequate for this type of sample. The XRF and SEM-EDS, techniques yield similar results despite being entirely different.

15. The impact of co-combustion of polyethylene plastics and wood in a small residential boiler on emissions of gaseous pollutants, particulate matter, PAHs and 1,3,5- triphenylbenzene.

Science.gov (United States)

Tomsej, Tomas; Horak, Jiri; Tomsejova, Sarka; Krpec, Kamil; Klanova, Jana; Dej, Milan; Hopan, Frantisek

2018-04-01

The aim of this study was to simulate a banned but widely spread practice of co-combustion of plastic with wood in a small residential boiler and to quantify its impact on emissions of gaseous pollutants, particulate matter (PM), polycyclic aromatic hydrocarbons (PAHs), and 1,3,5-triphenylbenzene (135TPB), a new tracer of polyethylene plastic combustion. Supermarket polyethylene shopping bags (PE) and polyethylene terephthalate bottles (PET) were burnt as supplementary fuels with beech logs (BL) in an old-type 20 kW over-fire boiler both at a nominal and reduced heat output. An impact of co-combustion was more pronounced at the nominal heat output: an increase in emissions of PM, total organic carbon (TOC), toxic equivalent (TEQ) of 7 carcinogenic PAHs (c-PAHs) and a higher ratio of c-PAHs TEQ in particulate phase was observed during co-combustion of both plastics. 135TPB was found in emissions from both plastics both at a nominal and reduced output. In contrast to findings reported in the literature, 135TPB was a dominant compound detected by mass spectrometry on m/z 306 exclusively in emissions from co-combustion of PE. Surprisingly, six other even more abundant compounds of unknown identity were found on this m/z in emissions from co-combustion of PET. One of these unknown compounds was identified as p-quaterphenyl (pQ). Principal component analysis revealed strong correlation among 135TPB, pQ and five unknown compounds. pQ seems to be suitable tracers of polyethylene terephthalate plastic co-combustion, while 135TPB proved its suitability to be an all-purpose tracer of polyethylene plastics combustion. Copyright © 2017 Elsevier Ltd. All rights reserved.

16. Production of high quality distillate to meet a fit-for-purpose boiler feedwater specification

Energy Technology Data Exchange (ETDEWEB)

Minnich, K. [Veolia Water Solutions Oil and Gas, Calgary, AB (Canada); Neu, D. [Veolia Water Solutions and Technologies/HPD, Pewaukee, WI (United States); Drone, J.L. [Veolia Water Solutions and Technologies/HPD, Plainfield, IL (United States)

2009-07-01

Veolia Water Solutions and Technologies has significant experience managing boiler water chemistry and is the world's largest manufacturer of evaporation systems. The company has conducted extensive testing and analysis for produced water evaporation distillate from multiple facilities. In order to produce boiler feed water, evaporation of produced water is used at several steam assisted gravity drainage (SAGD) facilities. There are no official guidelines for the required quality of evaporator distillate to feed a once through steam generator (OTSG) or high pressure industrial watertube boiler (IWT) that will produce injection steam. This paper presented a basis for a fit-for-purpose specification for IWT boilers as well as data on the performance of a Vapor Washer, which produces high quality distilled water that meets fit-for-purpose specifications even during normal variations in feed conditions. Specifically, the paper discussed boiler water requirements for steam injection IWTs; the quality of distillate from a produced water evaporator; the benefits of vapour washing to maintain distillate quality; and suggested boiler chemistry limits for a fit-for-purpose specification. Oxygen, iron, and copper were discussed as being implicated with corrosion and reaction in boilers. Hardness contaminants such as calcium and magnesium were also presented. Suggested limits for boiler water in the fit-for-purpose specification were also presented for silica, total alkalinity, free OH alkalinity, and total dissolved solids in steam. It was concluded that foaming episodes can occur in produced water evaporators due to normal variations, and the distillate can fail to meet the fit-for-purpose specification during foam upsets. 3 refs., 9 figs.

17. A study by simulation of dynamic instability in boilers using the NUMEL/DYMEL suite of programmes

International Nuclear Information System (INIS)

Jeffries, T.O.

1985-01-01

Tube-to-tube instability in a once through sodium heated boiler has been studied using the finite difference model developed by the CEGB and embodied in the NUMEL and DYMEL compute codes. The method used was to simulate the boiler and then carry out frequency response tests, as one would on a real boiler. The advantages of using the simulation model compared with using the real system are the ease with which experiments may be performed and the ease of access to a wide range of parameters which could only be obtained approximately, if at all, from a real boiler. The advantage is that validation of the model is only approximate though in the case of sodium heated boilers, conditions are similar to those in electrically heated rigs used for validation. The study led to an understanding of how such a boiler should be operated to avoid tube-to-tube instability and with the detailed temperature profiles available from NUMEL it was possible to develop existing theory to predict boiler transfer functions similar to those observed in the frequency response tests. (author)

18. The potential of fission nuclear power in resolving global climate change under the constraints of nuclear fuel resources and once-through fuel cycles

International Nuclear Information System (INIS)

Knapp, Vladimir; Pevec, Dubravko; Matijevic, Mario

2010-01-01

Nuclear fission is receiving new attention as a developed source of carbon-free energy. A much larger number of nuclear reactors would be needed for a major impact on carbon emission. The crucial question is whether it can be done without increasing the risk of nuclear proliferation. Specifically, can a larger nuclear share in world energy production, well above the present 6%, be achieved in the next few decades without adding the proliferation-sensitive technologies of reprocessing spent fuel and recycling plutonium to the problems of the unavoidable use of enrichment technology? The answer depends on the available uranium resources. We first looked for the maximum possible nuclear build-up in the 2025-2065 period under the constraints of the estimated uranium resources and the use of once-through nuclear fuel technology. Our results show that nuclear energy without reprocessing could reduce carbon emission by 39.6% of the total reduction needed to bring the WEO 2009 Reference Scenario prediction of total GHG emissions in 2065 to the level of the WEO 450 Scenario limiting global temperature increase to 2 deg. C. The less demanding strategy of the nuclear replacement of all non-CCS coal power plants retiring during the 2025-2065 period would reduce emission by 26.1%.

19. Nuclear fuel cycle risk assessment: survey and computer compilation of risk-related literature. [Once-through Cycle and Plutonium Recycle

Energy Technology Data Exchange (ETDEWEB)

Yates, K.R.; Schreiber, A.M.; Rudolph, A.W.

1982-10-01

The US Nuclear Regulatory Commission has initiated the Fuel Cycle Risk Assessment Program to provide risk assessment methods for assistance in the regulatory process for nuclear fuel cycle facilities other than reactors. Both the once-through cycle and plutonium recycle are being considered. A previous report generated by this program defines and describes fuel cycle facilities, or elements, considered in the program. This report, the second from the program, describes the survey and computer compilation of fuel cycle risk-related literature. Sources of available information on the design, safety, and risk associated with the defined set of fuel cycle elements were searched and documents obtained were catalogued and characterized with respect to fuel cycle elements and specific risk/safety information. Both US and foreign surveys were conducted. Battelle's computer-based BASIS information management system was used to facilitate the establishment of the literature compilation. A complete listing of the literature compilation and several useful indexes are included. Future updates of the literature compilation will be published periodically. 760 annotated citations are included.

20. Fouling control in biomass boilers

Energy Technology Data Exchange (ETDEWEB)

Romeo, Luis M.; Gareta, Raquel [Centro de Investigacion de Recursos y Consumos Energeticos (CIRCE), Universidad de Zaragoza, Centro Politecnico Superior, Maria de Luna, 3, 50018 Zaragoza (Spain)

2009-05-15

One of the important challenges for biomass combustion in industrial applications is the fouling tendency and how it affects to the boiler performance. The classical approach for this question is to activate sootblowing cycles with different strategies to clean the boiler (one per shift, one each six hours..). Nevertheless, it has been often reported no effect on boiler fouling or an excessive steam consumption for sootblowing. This paper illustrates the methodology and the application to select the adequate time for activating sootblowing in an industrial biomass boiler. The outcome is a control strategy developed with artificial intelligence (Neural Network and Fuzzy Logic Expert System) for optimizing the biomass boiler cleaning and maximizing heat transfer along the time. Results from an optimize sootblowing schedule show savings up to 12 GWh/year in the case-study biomass boiler. Extra steam generation produces an average increase of turbine power output of 3.5%. (author)

1. 1300°F 800 MWe USC CFB Boiler Design Study

Science.gov (United States)

Robertson, Archie; Goidich, Steve; Fan, Zhen

Concern about air emissions and the effect on global warming is one of the key factors for developing and implementing new advanced energy production solutions today. One state-of-the-art solution is circulating fluidized bed (CFB) combustion technology combined with a high efficiency once-through steam cycle. Due to this extremely high efficiency, the proven CFB technology offers a good solution for CO2 reduction. Its excellent fuel flexibility further reduces CO2 emissions by co-firing coal with biomass. Development work is under way to offer CFB technology up to 800MWe capacities with ultra-supercritical (USC) steam parameters. In 2009 a 460MWe once-through supercritical (OTSC) CFB boiler designed and constructed by Foster Wheeler will start up. However, scaling up the technology further to 600-800MWe with net efficiency of 45-50% is needed to meet the future requirements of utility operators. To support the move to these larger sizes, an 800MWe CFB boiler conceptual design study was conducted and is reported on herein. The use of USC conditions (˜11 00°F steam) was studied and then the changes, that would enable the unit to generate 1300°F steam, were identified. The study has shown that by using INTREX™ heat exchangers in a unique internal-external solids circulation arrangement, Foster Wheeler's CFB boiler configuration can easily accommodate 1300°F steam and will not require a major increase in heat transfer surface areas.

2. Mixture of working fluids in ORC plants with pool boiler evaporator

International Nuclear Information System (INIS)

Rajabloo, Talieh; Iora, Paolo; Invernizzi, Costante

2016-01-01

Highlights: • We assess the feasibility of pool boiler in ORCs operating with mixture working fluids. • We consider hydrocarbon and siloxane mixtures for low and high temperature ORCs. • Plants with pool boiler show comparable performances to once through evaporator. - Abstract: Power generation using Organic Rankine Cycle was studied in this paper in case of both low and high temperature cycles, exploiting respectively a geothermal heat source available at 167 °C, and heat available at 300 °C from the combustion of biomass. In particular we assess the feasibility of employing mixture of working fluids, in the case of replacing the typical once-through (OT) evaporator with the pool boiler (PB) technology, typically adopted for pure fluids. The analysis evidenced that in general the OT evaporator shows a slightly improved cycle performance in comparison to the PB and it results in some cases advantageous with respect to the pure working fluid. For instance in case of low temperature cycle, the best thermodynamic performances are obtained with mixture of i-C_5 and 75% n-C_4 in case of OT evaporator, yielding a recovery efficiency higher than the case with pure i-C_5 (7.7 vs. 7.4%) given the relatively higher values of both the recovery factor and cycle efficiency. Implementation of PB did not affect the plant performance significantly which shows the feasibility of having PB with potentially easier control.

3. Mod increases AGR boiler output

International Nuclear Information System (INIS)

Jones, W.K.C.; Rider, G.; Taylor, D.E.

1986-01-01

During the commissioning runs of the first reactor units at Heysham I and Hartlepool Advanced Gas-cooled Reactors (AGRs), non-uniform temperature distributions were observed across individual boiler units which were more severe than those predicted from the design analysis. This article describes the re-orificing (referruling) of the boilers to overcome this problem. The referruling has reduced boiler sensitivity and resulted in an increase of load of 7 or 8%. (U.K.)

4. Competing pathways in drug metabolism. I. Effect of input concentration on the conjugation of gentisamide in the once-through in situ perfused rat liver preparation

International Nuclear Information System (INIS)

Morris, M.E.; Yuen, V.; Tang, B.K.; Pang, K.S.

1988-01-01

Sulfation and glucuronidation are two parallel pathways for the metabolism of phenolic substrates. Gentisamide (GAM) was used as a model compound to examine the effects of parallel competing pathways on drug disappearance and metabolite formation in the once-through perfused rat liver preparation. GAM was found to form one glucuronide (GAM-5G) and two sulfate (GAM-2S and GAM-5S) conjugates. These GAM conjugates were biosynthesized in recirculating rat liver preparations, and were isolated by preparative high-performance liquid chromatography. Specific incorporation of 35S-sodium sulfate and [14C]glucose into GAM sulfate and glucuronide conjugates revealed corresponding elution patterns as labeled GAM metabolites. Their identities were characterized by enzymatic and acid hydrolyses and by NMR spectroscopy. Gentisamide-5-sulfate (GAM-5S) and gentisamide-5-glucuronide (GAM-5G) are major metabolites, and gentisamide-2-sulfate (GAM-2S) is a minor metabolite. Single-pass rat liver perfusions were used to examine the effect of stepwise increases/decreases of input GAM concentration (CIn) on the extraction ratio (E) of GAM and formation of metabolites. The E of GAM remained constant (about 0.89) at input concentrations from 0.9 to 120 microM and decreased at CIn greater than 120 microM. Metabolite patterns, however, changed with GAM CIn, even when E was constant at CIn up to 120 microM. GAM-5S was present as the major metabolite of GAM at all GAM CInS in most liver preparations but the proportions of GAM-5S and GAM-2S decreased at increasing CIn; the proportion of GAM-5G, a minor metabolite at low CIn, increased with increasing CIn. Biliary excretion rates at steady state accounted for 5.3 +/- 2.7% (mean +/- S.D.) of the input rate: GAM-5G was the predominant metabolite found

5. On the design of residential condensing gas boilers

Energy Technology Data Exchange (ETDEWEB)

Naeslund, M.

1997-02-01

Two main topics are dealt with in this thesis. Firstly, the performance of condensing boilers with finned tube heat exchangers and premix burners is evaluated. Secondly, ways of avoiding condensate formation in the flue system are evaluated. In the first investigation, a transient heat transfer approach is used to predict performance of different boiler configurations connected to different heating systems. The smallest efficiency difference between heat loads and heating systems is obtained when the heat exchanger gives a small temperature difference between flue gases and return water, the heat transfer coefficient is low and the thermostat hysteresis is large. Taking into account heat exchanger size, the best boiler is one with higher heat transfer per unit area which only causes a small efficiency loss. The total heating cost at part load, including gas and electricity, has a maximum at the lowest simulated heat load. The heat supplied by the circulation heat pump is responsible for this. The second investigation evaluates methods of drying the flue gases. Reheating the flue gases in different ways and water removal in an adsorbent bed are evaluated. Reheating is tested in two specially designed boilers. The necessary reheating is calculated to approximately 100-150 deg C if an uninsulated masonry chimney is used. The tested boilers show that it is possible to design a proper boiler. The losses, stand-by and convective/radiative, must be kept at a minimum in order to obtain a high efficiency. 86 refs, 70 figs, 16 tabs

6. Boiler tube failure prevention in fossil fired boilers

International Nuclear Information System (INIS)

Townsend, R.D.

1993-01-01

It is the common experience of power generating companies worldwide that the main causes of forced outages on power plant are those due to boiler tube failures on fossil units. The main reason for the large number of failures are the severe environmental conditions in fossil boilers as the effects of stress, temperature, temperature gradients, corrosion, erosion and vibration combine to produce degradation of the tube steel. Corrosion by oxidation, by combustion products and by impure boiler water can significantly reduce the tube wall thickness and result in failure of a tube many years before its designed service life. Errors can also occur in the design manufacturer, storage, operation, and maintenance of boiler tubing and the wrong material installed in a critical location can lead to premature failure. Altogether, experts in the US and UK, from many different disciplines, have identified seven broad categories of boiler tube failure mechanisms. 1 tab., 2 figs

7. Improved nuclear boiler

International Nuclear Information System (INIS)

Pierart, Robert.

1980-01-01

The improved nuclear boiler concerned in this invention is of the kind comprising, inter alia, a nuclear reactor supported by a metallic structure and of which the vessel is at least enclosed in part by a casing acting as a protective containment integrated in this structure. It is essentially characterized in that this casing is fitted into and maintained in position in the metallic structure by removable locking devices which enable the casing to be withdrawn from the remainder of the structure. Hence, after the casing has been withdrawn or removed from the metallic structure, access to the reactor vessel is readily obtained for inspection and/or testing from without [fr

8. Sampling practices and analytical techniques used in the monitoring of steam and water in CEGB nuclear boilers

International Nuclear Information System (INIS)

Goodfellow, G.I.

1978-01-01

The steam and water in CEGB Magnox and AGR nuclear boilers are continuously monitored, using both laboratory techniques and on-line instrumentation, in order to maintain the chemical quality within pre-determined limits. The sampling systems in use and some of the difficulties associated with sampling requirements are discussed. The relative merits of chemical instruments installed either locally in various parts of the plant or in centralized instrument rooms are reviewed. The quality of water in nuclear boilers, as with all high-pressure steam-raising plant, is extremely high; consequently very sensitive analytical procedures are required, particularly for monitoring the feed-water of 'once-through boiler' systems. Considerable progress has been made in this field and examples are given of some of the techniques developed for analyses at the 'μ/kg' level together with some of the current problems.(author)

9. Research of power fuel low-temperature vortex combustion in industrial boiler based on numerical modelling

Directory of Open Access Journals (Sweden)

Orlova K.Y.

2017-01-01

Full Text Available The goal of the presented research is to perform numerical modelling of fuel low-temperature vortex combustion in once-through industrial steam boiler. Full size and scaled-down furnace model created with FIRE 3D software and was used for the research. All geometrical features were observed. The baseline information for the low-temperature vortex furnace process are velocity and temperature of low, upper and burner blast, air-fuel ratio, fuel consumption, coal dust size range. The obtained results are: temperature and velocity three dimensional fields, furnace gases and solid fuel ash particles concentration.

10. Investigation of economics of back-end nuclear fuel cycle options in the Republic of Korea based on Once-through

Energy Technology Data Exchange (ETDEWEB)

Cho, Seok-Ki; Yim, Man-Sung [Korea Advance Institute of Science and Technology, Daejeon (Korea, Republic of)

2015-05-15

The purpose of this study is to examine these questions and perform economic evaluations of various cases of Once-through back-end fuel cycles in the ROK. Therefore, the study is to support decision making in terms of how the long term spent nuclear fuel (SNF) management strategy should be developed. A spreadsheet model was developed to plan reactor construction, the interim storage and the HLW repository construction within engineered constraints, based on the estimation of the spent fuel flow and the energy supply of the nuclear power program. The model computes the back-end levelized costs for various fuel cycle choices. The scenarios assumed in the model include (1) 0 year/10year/20year of licensed operation period extension; (2) the phase-out of NPP program and the continuous use including the reunification of Korean peninsula; (3) reactor decommissioning and construction lead times - 10 years and 5 years respectively in this study; (4) geological constraints of siting for a new reactor - 38 for without the reunification and 70 for with the reunification; (5) the first initiation of reactor decommissioning and operation of HLW repository - assumed to be 2020 and 2050; and (6) capacity factor of reactor operation and the on-site wet storage pool capacity - 0.85 and 0.498 MTHM per MWe which is equivalent with APR1400. The capacity factor for PHWR reactors was assumed at 0.85 and the plan for PHWR was fixed as phase-out. The spreadsheet model conducts computation for annual expenditures of the back-end fuel cycle and calculates the levelized costs. Licensed operation period extension enhances not only economic efficiency, stable energy supply, but also reduces burden of siting for a new reactor and waste disposal. And regardless the reunification, continuous use of nuclear energy lowers the back-end fuel cycle cost. With projection that a large portion of social cost is included in the current back-end fuel cycle cost, nuclear energy likely has more competency in

11. The Concept of Steam Pressure Control by Changing the Feedwater Flow during Heatup Operation for an Integral Reactor with a Once-Through Steam Generator

International Nuclear Information System (INIS)

Seo, Jae Kwang; Choi, Ki Yong; Kang, Han Ok; Kim, Young In; Yoon, Ju Hyeon; Zee, Sung Qunn

2005-01-01

The design features of a once-through steam generator (OTSG) for an integral reactor are significantly different from the commercial U-tube type steam generator from several aspects such as the general arrangement, size, operation conditions, and so on. Therefore a sufficient understanding of the thermal-hydraulic characteristics of the OTSG is essential for the design of the nuclear steam supply system (NSSS) and the power conversion system (PCS). It is also necessary to develop operation procedures complying to the unique design features of the OTSG of interest. The OTSG is sized to produce a sufficiently superheated steam during a normal power operation and therefore the secondary system can be simple relative to that of the other types of steam generators. For the plant adopting the OTSG, the steam pressure in the secondary circuit (tube side of the OTSG) is controlled to be constant during a normal power operation. Constant steam pressure is realized by regulating the control valve on the main steam line dedicated for this purpose. However during a heatup operation, at which the fluid state at the exit of the OTSG is a single phase hot water or two phases, it is not proper to use the control valve on the main steam line due to a control problem at low and multi-phase flow conditions and possibly an erosion problem. For these reasons, another dedicated line called a startup cooling line is used during a heatup condition. There may be several operational conditions for the secondary fluid required to pass through during heatup operation, depending on the design of the PCS. In general, there are two conditions: One is a condition for a vacuum operation for the condenser and another is an entry condition for a steam pressure control operation for an auxiliary power system. In this study, the concept of using a simple startup cooling line with a fixed flow resistance and changing the feedwater flow for the pressure control of the PCS during a heatup period are

12. Market review. Pellet wood gasification boiler / combination boiler. 8. ed.; Marktuebersicht. Scheitholzvergaser-/Kombikessel

Energy Technology Data Exchange (ETDEWEB)

Uth, Joern

2012-01-15

In the market review under consideration on pellet wood gasification boilers and combination boilers, the Federal Ministry of Food, Agriculture and Consumer Protection (Bonn, Federal Republic of Germany) reports on planning and installation of wood-fired heating systems, recommendations regarding to the technical assessment of boiler systems, buffers/combination boilers, prices of pellet wood gasification boilers, data sheets of the compared pellet wood gasification boilers, pellet wood combination boilers, prices of pellet wood combination boilers, data sheets of the compared pellet wood gasification boilers, list of providers.

13. Pellet wood gasification boiler / Combination boiler. Market review. 7. ed.; Scheitholzvergaser-/Kombikessel. Marktuebersicht

Energy Technology Data Exchange (ETDEWEB)

Uth, Joern

2010-08-15

In the market review under consideration on pellet wood gasification boilers and combination boilers, the Federal Ministry of Food, Agriculture and Consumer Protection (Bonn, Federal Republic of Germany) report on planning and installation of wood-fired heating systems, recommendations regarding to the technical assessment of boiler systems, buffers/combination boilers, prices of pellet wood gasification boilers, data sheets of the compared pellet wood gasification boilers, pellet wood combination boilers, prices of pellet wood combination boilers, data sheets of the compared pellet wood gasification boilers, list of providers.

14. A study on the boiler efficiency influenced by the boiler operation parameter in fossil power plant

International Nuclear Information System (INIS)

Kwon, Y. S.; Suh, J. S.

2002-01-01

The main reason to analyze the boiler operation parameter in fossil power plant is to increase boiler high efficiency and energy saving movement in the government. This study intends to have trend and analyze the boiler efficiency influenced by the boiler parameter in sub-critical and super-critical type boiler

15. Demonstration of coal reburning for cyclone boiler NO{sub x} control. Appendix, Book 1

Energy Technology Data Exchange (ETDEWEB)

1994-06-01

Based on the industry need for a pilot-scale cyclone boiler simulator, Babcock Wilcox (B&W) designed, fabricated, and installed such a facility at its Alliance Research Center (ARC) in 1985. The project involved conversion of an existing pulverized coal-fired facility to be cyclone-firing capable. Additionally, convective section tube banks were installed in the upper furnace in order to simulate a typical boiler convection pass. The small boiler simulator (SBS) is designed to simulate most fireside aspects of full-size utility boilers such as combustion and flue gas emissions characteristics, fireside deposition, etc. Prior to the design of the pilot-scale cyclone boiler simulator, the various cyclone boiler types were reviewed in order to identify the inherent cyclone boiler design characteristics which are applicable to the majority of these boilers. The cyclone boiler characteristics that were reviewed include NO{sub x} emissions, furnace exit gas temperature (FEGT) carbon loss, and total furnace residence time. Previous pilot-scale cyclone-fired furnace experience identified the following concerns: (1) Operability of a small cyclone furnace (e.g., continuous slag tapping capability). (2) The optimum cyclone(s) configuration for the pilot-scale unit. (3) Compatibility of NO{sub x} levels, carbon burnout, cyclone ash carryover to the convection pass, cyclone temperature, furnace residence time, and FEGT.

16. 49 CFR 230.47 - Boiler number.

Science.gov (United States)

2010-10-01

... 49 Transportation 4 2010-10-01 2010-10-01 false Boiler number. 230.47 Section 230.47..., DEPARTMENT OF TRANSPORTATION STEAM LOCOMOTIVE INSPECTION AND MAINTENANCE STANDARDS Boilers and Appurtenances Steam Gauges § 230.47 Boiler number. (a) Generally. The builder's number of the boiler, if known, shall...

17. 30 CFR 77.413 - Boilers.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Boilers. 77.413 Section 77.413 Mineral... Mechanical Equipment § 77.413 Boilers. (a) Boilers shall be equipped with guarded, well-maintained water... the gages shall be kept clean and free of scale and rust. (b) Boilers shall be equipped with automatic...

18. 30 CFR 56.13030 - Boilers.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Boilers. 56.13030 Section 56.13030 Mineral... HEALTH SAFETY AND HEALTH STANDARDS-SURFACE METAL AND NONMETAL MINES Compressed Air and Boilers § 56.13030 Boilers. (a) Fired pressure vessels (boilers) shall be equipped with water level gauges, pressure gauges...

19. 30 CFR 57.13030 - Boilers.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Boilers. 57.13030 Section 57.13030 Mineral... HEALTH SAFETY AND HEALTH STANDARDS-UNDERGROUND METAL AND NONMETAL MINES Compressed Air and Boilers § 57.13030 Boilers. (a) Fired pressure vessels (boilers) shall be equipped with water level gauges, pressure...

20. CFB boilers in multifuel application

International Nuclear Information System (INIS)

Goral, D.; Krzton, B.

2007-01-01

Fuel flexibility characteristic for CFB boilers plays an important rule in industrial and utility size applications. Possibility to use wider range of fuels that has been long time considered as by-products or wastes and possibility to design boilers able to operate with alternative fuels is an important factor that improves fuel delivery security and plant economy. Presented article is based on similar publications that present Foster Wheeler's experience in design and delivery of the CFB boilers for wide range of coals and cofiring by- products of crude oil refining and coal processing. Aspects of biomass cofiring will be also presented. (author)

1. Investigating the effects of heat exchanger on flame transfer function in a simplified boiler

NARCIS (Netherlands)

Hosseini, N.; Kornilov, V.N.; Teerling, O. J.; Lopez Arteaga, I.; de Goey, Ph.

2015-01-01

The goal of the present work is to investigate the effects the heat exchanger can have on the acoustic response of the flames(flame transfer function) in a boiler. In compact condensing boilers the distance between the burner and heat exchanger is small enough to cause intense interactions. That is

2. 46 CFR 61.05-10 - Boilers in service.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Boilers in service. 61.05-10 Section 61.05-10 Shipping... INSPECTIONS Tests and Inspections of Boilers § 61.05-10 Boilers in service. (a) Each boiler, including superheater, reheater, economizer, auxiliary boiler, low-pressure heating boiler, and unfired steam boiler...

3. ENERGY STAR Certified Commercial Boilers

Data.gov (United States)

U.S. Environmental Protection Agency — Certified models meet all ENERGY STAR requirements as listed in the Version 1.0 ENERGY STAR Program Requirements for Commercial Boilers that are effective as of...

4. Hybrid model of steam boiler

International Nuclear Information System (INIS)

Rusinowski, Henryk; Stanek, Wojciech

2010-01-01

In the case of big energy boilers energy efficiency is usually determined with the application of the indirect method. Flue gas losses and unburnt combustible losses have a significant influence on the boiler's efficiency. To estimate these losses the knowledge of the operating parameters influence on the flue gases temperature and the content of combustible particles in the solid combustion products is necessary. A hybrid model of a boiler developed with the application of both analytical modelling and artificial intelligence is described. The analytical part of the model includes the balance equations. The empirical models express the dependence of the flue gas temperature and the mass fraction of the unburnt combustibles in solid combustion products on the operating parameters of a boiler. The empirical models have been worked out by means of neural and regression modelling.

5. Boiler-turbine life extension

Energy Technology Data Exchange (ETDEWEB)

Natzkov, S. [TOTEMA, Ltd., Sofia (Bulgaria); Nikolov, M. [CERB, Sofia (Bulgaria)

1995-12-01

The design life of the main power equipment-boilers and turbines is about 105 working hours. The possibilities for life extension are after normatively regulated control tests. The diagnostics and methodology for Boilers and Turbines Elements Remaining Life Assessment using up to date computer programs, destructive and nondestructive control of metal of key elements of units equipment, metal creep and low cycle fatigue calculations. As well as data for most common damages and some technical decisions for elements life extension are presented.

6. CFD Simulation On CFBC Boiler

Directory of Open Access Journals (Sweden)

Amol S. Kinkar

2015-02-01

Full Text Available Abstract Heavy industrialization amp modernization of society demands in increasing of power cause to research amp develop new technology amp efficient utilization of existing power units. Variety of sources are available for power generation such as conventional sources like thermal hydro nuclear and renewable sources like wind tidal biomass geothermal amp solar. Out of these most common amp economical way for producing the power is by thermal power stations. Various industrial boilers plays an important role to complete the power generation cycle such as CFBC Circulating Fluidized Bed Combustion FBC Fluidized Bed Combustion AFBC Atmospheric Fluidized Bed Combustion Boiler CO Boiler RG amp WHR Boiler Waster heat recovery Boiler. This paper is intended to comprehensively give an account of knowledge related to refractory amp its failure in CFBC boiler with due effect of flue gas flow during operation on refractory by using latest technology of CAD Computer aided Design amp CAE Computer aided Engineering. By conceptual application of these technology the full scale model is able to analyze in regards the flow of flue gas amp bed material flow inside the CFBC loop via CFD Computational Fluid Dynamics software. The results obtained are helpful to understand the impact of gas amp particles on refractory in different areas amp also helped to choose suitable refractory material in different regions.

7. Exergy analysis on industrial boiler energy conservation and emission evaluation applications

Science.gov (United States)

Li, Henan

2017-06-01

Industrial boiler is one of the most energy-consuming equipments in china, the annual consumption of energy accounts for about one-third of the national energy consumption. Industrial boilers in service at present have several severe problems such as small capacity, low efficiency, high energy consumption and causing severe pollution on environment. In recent years, our country in the big scope, long time serious fog weather, with coal-fired industrial boilers is closely related to the regional characteristics of high strength and low emissions [1]. The energy-efficient and emission-reducing of industry boiler is of great significance to improve China’s energy usage efficiency and environmental protection. Difference in thermal equilibrium theory is widely used in boiler design, exergy analysis method is established on the basis of the first law and second law of thermodynamics, by studying the cycle of the effect of energy conversion and utilization, to analyze its influencing factors, to reveal the exergy loss of location, distribution and size, find out the weak links, and a method of mining system of the boiler energy saving potential. Exergy analysis method is used for layer combustion boiler efficiency and pollutant emission characteristics analysis and evaluation, and can more objectively and accurately the energy conserving potential of the mining system of the boiler, find out the weak link of energy consumption, and improve equipment performance to improve the industrial boiler environmental friendliness.

8. Boiler using combustible fluid

Science.gov (United States)

Baumgartner, H.; Meier, J.G.

1974-07-03

A fluid fuel boiler is described comprising a combustion chamber, a cover on the combustion chamber having an opening for introducing a combustion-supporting gaseous fluid through said openings, means to impart rotation to the gaseous fluid about an axis of the combustion chamber, a burner for introducing a fluid fuel into the chamber mixed with the gaseous fluid for combustion thereof, the cover having a generally frustro-conical configuration diverging from the opening toward the interior of the chamber at an angle of between 15/sup 0/ and 55/sup 0/; means defining said combustion chamber having means defining a plurality of axial hot gas flow paths from a downstream portion of the combustion chamber to flow hot gases into an upstream portion of the combustion chamber, and means for diverting some of the hot gas flow along paths in a direction circumferentially of the combustion chamber, with the latter paths being immersed in the water flow path thereby to improve heat transfer and terminating in a gas outlet, the combustion chamber comprising at least one modular element, joined axially to the frustro-conical cover and coaxial therewith. The modular element comprises an inner ring and means of defining the circumferential, radial, and spiral flow paths of the hot gases.

9. Studies Concerning Water-Surface Deposits in Recovery Boilers

Energy Technology Data Exchange (ETDEWEB)

Strandberg, O; Arvesen, J; Dahl, L

1971-11-15

The Feed-water Committee of the Stiftelsen Svensk Cellulosaforskning (Foundation for Swedish Cellulose Research) has initiated research and investigations which aim to increase knowledge about water-surface deposits in boiler tubes, and the resulting risks of gas-surface corrosion in chemical recovery boilers (sulphate pulp industry). The Committee has arranged with AB Atomenergi, Studsvik, for investigations into the water-surface deposits on tubes from six Scandinavian boilers. These investigations have included direct measurements of the thermal conductivity of the deposits, and determinations of their quantity, thickness and structure have been carried out. Previous investigations have shown that gas-surface corrosion can occur at tube temperatures above 330 deg C. The measured values for the thermal conductivity of the deposits indicate that even with small quantities of deposit (c. 1 g/dm2 ) and a moderate boiler pressure (40 atm), certain types of deposit can give rise to the above-mentioned surface temperature, at which the risk of gas-surface corrosion becomes appreciable. For higher boiler pressures the risk is great even with a minimal layer of deposit. The critical deposit thickness can be as low as 0.1 mm

10. New controls spark boiler efficiency

Energy Technology Data Exchange (ETDEWEB)

Engels, T. (Monsanto, University Park, IL (United States))

1993-09-01

Monsanto's NutraSweet plant in University Park, IL, produces aspartame, the patented NutraSweet artificial sweetener product. Until recently, boiler control was managed by a '60s-era Fireye jackshaft system in which air and natural gas were mechanically linked with an offset to compensate for oxygen trim. The interlocking devices on the Fireye system were becoming obsolete, and the boiler needed a new front end retrofitted for low emissions. In order to improve boiler control efficiency, we decided to modernize and automate the entire boiler control system. We replaced the original jackshaft system, and installed a Gordon-Piet burner system, including gas valves, air dampers, blowers, and burner. The upgrade challenges included developing a control strategy and selecting and implementing a process control system. Since our plant has standardized on the PROVOX process management information system from Fisher Controls (now Fisher-Rosemount Systems) to support most of our process, it was a natural and logical choice for boiler controls as well. 2 figs.

11. Failure analysis of boiler tube

International Nuclear Information System (INIS)

Mehmood, K.; Siddiqui, A.R.

2007-01-01

Boiler tubes are energy conversion components where heat energy is used to convert water into high pressure superheated steam, which is then delivered to a turbine for electric power generation in thermal power plants or to run plant and machineries in a process or manufacturing industry. It was reported that one of the tubes of a fire-tube boiler used in a local industry had leakage after the formation of pits at the external surface of the tube. The inner side of the fire tube was working with hot flue gasses with a pressure of 10 Kg/cm/sup 2/ and temperature 225 degree C. The outside of the tube was surrounded by feed water. The purpose of this study was to determine the cause of pits developed at the external surface of the failed boiler tube sample. In the present work boiler tube samples of steel grade ASTM AI61/ASTM A192 were analyzed using metallographic analysis, chemical analysis, and mechanical testing. It was concluded that the appearance of defects on the boiler tube sample indicates cavitation type corrosion failure. Cavitation damage superficially resembled pitting, but surface appeared considerably rougher and had many closely spaced pits. (author)

12. Structured Mathematical Modeling of Industrial Boiler

Directory of Open Access Journals (Sweden)

Abdullah Nur Aziz

2014-04-01

Full Text Available As a major utility system in industry, boilers consume a large portion of the total energy and costs. Significant reduction of boiler cost operation can be gained through improvements in efficiency. In accomplishing such a goal, an adequate dynamic model that comprehensively reflects boiler characteristics is required. This paper outlines the idea of developing a mathematical model of a water-tube industrial boiler based on first principles guided by the bond graph method in its derivation. The model describes the temperature dynamics of the boiler subsystems such as economizer, steam drum, desuperheater, and superheater. The mathematical model was examined using industrial boiler performance test data.It can be used to build a boiler simulator or help operators run a boiler effectively.

13. Emission analysis of the best available wood-fired central heating boilers on the market

International Nuclear Information System (INIS)

Axell, M.; Gustavsson, Lennart; Persson, Henrik; Leckner, B.

1998-01-01

The purpose of the present project is to study the emissions from some of the best available wood-fired central heating boilers on the market. The aim is to identify the critical factors which determine the emission levels by means of emission measurements as well as temperature measurements in the combustion chamber. Four boilers with different design characteristics have been included in the project. All boilers use reversed combustion and fan-assisted combustion air supply, and have shown low tar emissions in earlier environmental tests. Boiler A is a boiler with a rather large mass of ceramics in the grate and in the burn-out zone, and a large volume of water. Boiler B has a smaller mass in the cast-iron grate and in the burn-out zone and a small water volume. Boiler C is a boiler with tertiary air and an incorporated accumulator tank. Boiler D has a zirconia-cell probe for continuous control of the air-excess ratio. The measurements have been made with the boilers in accumulator operation, i.e. at maximum heat output, since they are intended for this type of operation. Tests have, in addition to normal operating conditions, been made with high fuel moisture contents, high draught and a low boiler temperature at the start of the test. Measurements have been made of excess-air ratios, contents of CO, total hydrocarbons (THC), NO x and a number of volatile organic compounds (VOC) in the flue gases as well as of combustion temperatures below the grate

14. The pressure cold wind system on the impact of industrial boiler economy and security

Science.gov (United States)

Li, Henan; Qian, Hongli; Jiang, Lei; Yu, Dekai; Li, Guannan; Yuan, Hong

2017-05-01

Industrial boiler is one of the most energy-consuming equipment in china, the annual consumption of energy accounts for about one-third of the national energy consumption.Industrial boiler in service at present have several severe problems such as small capacity, low efficiency, high energy consumption and causing severe pollution on environment, the average industrial boiler operation efficiency is only 65%. If the efficiency increased by 15% ∼ 20%, which meet the international advanced level, each year 70 million tons of coal saving and reduce environmental pollution[1]. As energy conservation and emissions reduction becomes the basic national policy of our country, improving the efficiency of industrial boiler energy is facing opportunities and challenges, optimizing the operation mode of the existing units, it is necessary to increase the flexibility of the boiler control.

15. Successful experience with limestone and other sorbents for combustion of biomass in fluid bed power boilers

Energy Technology Data Exchange (ETDEWEB)

Coe, D.R. [LG& E Power Systems, Inc., Irvine, CA (United States)

1993-12-31

This paper presents the theoretical and practical advantages of utilizing limestone and other sorbents during the combustion of various biomass fuels for the reduction of corrosion and erosion of boiler fireside tubing and refractory. Successful experiences using a small amount of limestone, dolomite, kaolin, or custom blends of aluminum and magnesium compounds in fluid bed boilers fired with biomass fuels will be discussed. Electric power boiler firing experience includes bubbling bed boilers as well as circulating fluid bed boilers in commercial service on biomass fuels. Forest sources of biomass fuels fired include wood chips, brush chips, sawmill waste wood, bark, and hog fuel. Agricultural sources of biomass fuels fired include grape vine prunings, bean straw, almond tree chips, walnut tree chips, and a variety of other agricultural waste fuels. Additionally, some urban sources of wood fuels have been commercially burned with the addition of limestone. Data presented includes qualitative and quantitative analyses of fuel, sorbent, and ash.

16. Structured Mathematical Modeling of Industrial Boiler

OpenAIRE

Aziz, Abdullah Nur; Nazaruddin, Yul Yunazwin; Siregar, Parsaulian; Bindar, Yazid

2014-01-01

As a major utility system in industry, boilers consume a large portion of the total energy and costs. Significant reduction of boiler cost operation can be gained through improvements in efficiency. In accomplishing such a goal, an adequate dynamic model that comprehensively reflects boiler characteristics is required. This paper outlines the idea of developing a mathematical model of a water-tube industrial boiler based on first principles guided by the bond graph method in its derivation. T...

17. Cracking and corrosion recovery boiler

Energy Technology Data Exchange (ETDEWEB)

Suik, H. [Tallinn Technical University, Horizon Pulp and Paper, Tallinn (Estonia)

1998-12-31

The corrosion of heat surfaces and the cracking the drums are the main problems of the recovery boiler. These phenomena have been appeared during long-term operation of boiler `Mitsubishi - 315` erected at 1964. Depth of the crack is depending on the number of shutdowns and on operation time. Corrosion intensity of different heat surfaces is varying depend on the metal temperature and the conditions at place of positioning of tube. The lowest intensity of corrosion is on the bank tubes and the greatest is on the tubes of the second stage superheater and on the tubes at the openings of air ports. (orig.) 5 refs.

18. Cracking and corrosion recovery boiler

Energy Technology Data Exchange (ETDEWEB)

Suik, H [Tallinn Technical University, Horizon Pulp and Paper, Tallinn (Estonia)

1999-12-31

The corrosion of heat surfaces and the cracking the drums are the main problems of the recovery boiler. These phenomena have been appeared during long-term operation of boiler `Mitsubishi - 315` erected at 1964. Depth of the crack is depending on the number of shutdowns and on operation time. Corrosion intensity of different heat surfaces is varying depend on the metal temperature and the conditions at place of positioning of tube. The lowest intensity of corrosion is on the bank tubes and the greatest is on the tubes of the second stage superheater and on the tubes at the openings of air ports. (orig.) 5 refs.

19. Sootblowing optimization for improved boiler performance

Science.gov (United States)

James, John Robert; McDermott, John; Piche, Stephen; Pickard, Fred; Parikh, Neel J.

2012-12-25

A sootblowing control system that uses predictive models to bridge the gap between sootblower operation and boiler performance goals. The system uses predictive modeling and heuristics (rules) associated with different zones in a boiler to determine an optimal sequence of sootblower operations and achieve boiler performance targets. The system performs the sootblower optimization while observing any operational constraints placed on the sootblowers.

20. Optimizing the Integrated Design of Boilers - Simulation

DEFF Research Database (Denmark)

Sørensen, K.; Karstensen, C.; Condra, T.

2004-01-01

Boilers can be considered as consisting of three main components: (i) the pressure part, (ii) the burner and (iii) the control system. To be able to develop the boilers of the future (i.e. the boilers with the lowest emissions, the highest efciency, the best dynamic performance etc.) it is import...

1. MULTIPLE LINEAR REGRESSION ANALYSIS FOR PREDICTION OF BOILER LOSSES AND BOILER EFFICIENCY

OpenAIRE

Chayalakshmi C.L

2018-01-01

MULTIPLE LINEAR REGRESSION ANALYSIS FOR PREDICTION OF BOILER LOSSES AND BOILER EFFICIENCY ABSTRACT Calculation of boiler efficiency is essential if its parameters need to be controlled for either maintaining or enhancing its efficiency. But determination of boiler efficiency using conventional method is time consuming and very expensive. Hence, it is not recommended to find boiler efficiency frequently. The work presented in this paper deals with establishing the statistical mo...

2. Boiler operator's handbook

CERN Document Server

Heselton, Ken

2004-01-01

Containing key information for operators and managers of large and small plants, this is an indispensable guide for those at advanced and early stages of their careers, as well as for managers interested in reducing operating expenses.

3. Construction and commissioning of the Hinkley Point 'B' and Hunterston 'B' boilers

International Nuclear Information System (INIS)

White, D.C.; Holmes, R.L.

1977-01-01

Prior to construction and erection of the reactor boiler units, within the concrete pressure vessel, the units were received from the manufacturing works, and stored in clean and humidity controlled conditions. Because of the loading facilities into the reactor pressure vessel, a very precise erection procedure had to be adhered to. The activities associated with construction of feedwater inlet, superheater steam, and reheated steam inlet and outlet penetrations had to be programmed accordingly. By the very nature of the work load, the time scale involved, and the prime need to maintain the boiler unit materials free of deterioration from atmospheric corrosion after erection, early commissioning of storage systems were implemented; providing wet or dry storage conditions as dictated by the two Generating Boards. Pre-operational commissioning also covered the work of setting up all the steam and water controls, isolating valve systems and the automatic and sequence equipment associated with the feed water controls which are a major design feature of the once through boiler operation. (author)

4. Biomass boilers: towards a higher efficiency

International Nuclear Information System (INIS)

Petitot, Pauline; Signoret, Stephane; Mary, Olivier; Dejeu, Mathieu; Tachet, Jean-Pierre

2014-01-01

A set of articles proposes an overview of the situation and perspectives of biomass fuelled boilers in France. As outlined in an interview, professionals are supported by ADEME and the Heat Fund (Fonds Chaleur) for a continuous development of wood-energy in order to reach national objectives for renewable energies by 2020. The next article discusses issues related to wood supply, with some concerns regarding forest exploitation, and needs to find new management ways and to use other sources than forests. The technical status and perspectives of smoke condensation in wood-fuelled boilers are discussed. The example of a malt-house near Issoudun fuelled by biomass since 2013 is presented. Other examples concern a small town of Burgundy which developed and is still improving a heat network, a wood-fuelled heat network in Saint-Denis, and a biomass wood-fuelled heat production plant for the Toulouse University hospital. Graphs indicate evolutions of prices for different wood-based fuel products. The last article outlines the role of forests and the importance of their protection in the struggle against climate change, and discusses problems faced to support this preservation and its financing

5. Evaluating Environmental, Health and Safety Impacts from Two Nuclear Fuel Cycles: A Comparative Analysis of Once-Through Uranium Use and Plutonium Recycle in Light Water Reactors

Science.gov (United States)

Smith, Bethan L.

this study's comparative impacts of worker collective doses elucidates the dependence of net radiological impacts to workers to fuel-type use. This verification exercise then leads to concluding remarks that fuel-use proportions employed at the end of the hypothetical advanced NFC scenario within the reactor fleet can determine what level of analysis may be required to estimate the net impacts that may be incurred from an advanced NFC. In Chapter 4, a study of potential worker collective doses incurred from carrying out the strategy to manage and dispose of used nuclear fuel outlined by the U.S. Department of Energy (DOE) as part of a comprehensive federal waste management system (FWMS) is discussed. It was estimated that the worker collective dose from repository operations leads to the large part of the radiological impact of the new FWMS. The contribution to worker collective dose was compared to that of the contemporary OTC quantitative model presented in Chapter 2. The additional worker collective dose contributed by FWMS activities is small and when the contributions from each grouped operation of the OTC are renormalized, the FWMS ranges annually from 4-8%. Finally, Chapter 5 offers ideas for future work and provides a summary of the findings of this dissertation.

6. Failure Analysis of 600 MW Supercritical Boiler Water Wall

OpenAIRE

Fu Huilin; Cai Zhengchun; Yan Xiaozhong; He Jinqiao; Zhou Yucai

2013-01-01

Boiler tube often causes abnormal boiler outage, bringing greater economic losses. This thesis mainly comes from the dynamics of boiler water, boiler furnace accident location of wall temperature distribution to explore the cause of the accident boiler. Calculation results show that the deformation will seriously reduce the boiler allowable maximum temperature difference between the screens. And the boiler is not over-temperature, low temperature difference between the screens, which have bur...

7. Experimental investigation on a 0.35 MWth coal-fired horizontal circulating fluidized bed boiler

Energy Technology Data Exchange (ETDEWEB)

Meng, Aihong; Li, Qinghai; Zhang, Yanguo; Wang, Zhaojun; Dang, Wenda [Tsinghua Univ., Beijing (China); Ministry of Education, Beijing (China). Key Lab. for Thermal Science and Power Engineering

2013-07-01

The capacities of industrial coal-fired boilers are normally less than 20-30 MWe. And these coal-fired boilers of low capacity are facing the severe situation of low efficiency and heavy environmental pollution. Hence, an innovative horizontal circulating fluidized bed (HCFB) boiler was developed to enhance heat efficiency and reduce pollutant emission of industrial boilers in China. The chamber in the HCFB boiler consists of primary combustion chamber, secondary combustion chamber and burnout chamber, which were combined horizontally side by side. To verify the conception of horizontal fluidized circulation and to obtain the characteristic data, a 0.35 MWth coal-combustion HCFB boiler was designed and installed to perform some experiments of combustion and mass circulation. In the boiler there were two mass circulating paths, one is inner circulating through the inertia separator and another was external circulating through the cyclone separator. The connection bottom of the secondary chamber and the burnout chamber was designed as an inertia separator, in which separated and collected solid materials were returned to the primary combustion. In fact the secondary separator was a small cyclone separator connecting to the exit of the burnout chamber. Heat efficiency and separating efficiency of the experimental boiler were measured and analyzed. Furthermore, mass and temperature distribution along the chambers height were also investigated. The results showed that the heat efficiency of the bare boiler was 82%. The mass balance based on ash content was measured and analyzed. Separating efficiency of the inertia separator and cyclone separator was 60 and 99.9%, respectively. It showed that the two stage material separation and circulation enhanced coal combustion in the HCFB boiler and help to minimize the height of the furnace.

8. Biomass boiler still best choice

International Nuclear Information System (INIS)

Wallace, Paula

2014-01-01

Full text: The City of Mount Gambier upgraded its boiler in September after analysis showed that biomass was still the optimal energy option. The Mount Gambier Aquatic Centre was built by the local city council in the 1980s as an outdoor pool facility for the public. The complex has three pools — an Olympic-sized, toddler and a learner pool — for a total volume of 1.38ML (including balance tanks). The large pool is heated to 27-28°C, the smaller one 30-32°C. From the very beginning, the pool water was heated by a biomass boiler, and via two heat exchangers whose combined capacity is 520 kW. The original biomass boiler ran on fresh sawdust from a local timber mill. After thirty years of dedicated service the original boiler had become unreliable and difficult to operate. Replacement options were investigated and included a straight gas boiler, a combined solar hot water and gas option, and biomass boilers. The boiler only produces heat, not electricity. All options were subjected to a triple bottom line assessment, which included potential capital costs, operating costs, community and environmental benefits and costs. The project was also assessed using a tool developed by Mount Gambier City Council that considers the holistic benefits — the CHAT Tool, which stands for Comprehensive Holistic Assessment Tool. “Basically it is a survey that covers environmental, social, economic and governance factors,” the council's environmental sustainability officer, Aaron Izzard told WME. In relation to environmental considerations, the kinds of questions explored by the CHAT Tool included: Sustainable use of resources — objective is to reduce council's dependence on non-renewable resources; Greenhouse emissions — objective is to reduce council's contribution of GHG into the atmosphere; Air quality — objective is to improve local air quality. The conclusion of these analyses was that while a biomass boiler would have a higher capital cost than a straight gas

9. A NOx control regulation for electric utility boilers in California

International Nuclear Information System (INIS)

Price, D.R.

1992-01-01

The reduction of oxides of nitrogen emissions is becoming an increasingly important part of ozone attainment plans. As a part of its ozone attainment plan, the Ventura County (California) Air Pollution Control Board adopted in June, 1991, a regulation (Rule 59) to limit oxides of nitrogen emissions from four electrical utility boilers in the county. Rule development took two years and involved considerable public input. The emission limit for each of two 750 megawatt units is set at 0.10 pounds of NO x per megawatt-hour net after June, 1994. The emission limit for each of two 215 megawatt units is 0.20 pounds of NO x per megawatt-hour after June, 1996. Additional limitations are included for fuel oil operation. The rule does not specify an emission control technology. Conventional selective catalytic reduction, urea injection and combustion modifications are considered the technologies most likely to be used to comply. At \$17,613 per ton of NO x reduced for the two large boilers and \$8.992 per ton of NO x reduced for the small boilers, the rule is considered cost effective. The capital cost for conventional selective catalytic reduction systems on all four boilers is expected to be in excess of \$210,000,000

10. CONVERSION OF BOILER-HOUSES IN MINI-THERMAL POWER STATIONS

Directory of Open Access Journals (Sweden)

V. A. Sednin

2005-01-01

Full Text Available One of the methods that makes it possible to increase operational efficiency of heat supply  systems is development of power-and-heat generation on the basis of boiler houses of small and average power. The paper gives main prerequisites for selection of variants and power of power-and-heat generation (cogeneration installations on the basis of gas-piston engines which are to be used at heating boiler houses.

11. 46 CFR 52.25-20 - Exhaust gas boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Exhaust gas boilers. 52.25-20 Section 52.25-20 Shipping COAST GUARD, DEPARTMENT OF HOMELAND SECURITY (CONTINUED) MARINE ENGINEERING POWER BOILERS Other Boiler Types § 52.25-20 Exhaust gas boilers. Exhaust gas boilers with a maximum allowable working pressure...

12. Selective analysis of power plant operation on the Hudson River with emphasis on the Bowline Point Generating Station. Volume 2. [Multiple impact of power plant once-through cooling systems on fish populations

Energy Technology Data Exchange (ETDEWEB)

Barnthouse, L. W.; Cannon, J. B.; Christensen, S. G.

1977-07-01

Because of the location of the Bowline, Roseton, and Indian Point power generating facilities in the low-salinity zone of the Hudson estuary, operation of these plants with the present once-through cooling systems will adversely influence the fish populations that use the area for spawning and initial periods of growth and development. Recruitment rates and standing crops of several fish species may be lowered in response to the increased mortality caused by entrainment of nonscreenable eggs and larvae and by impingement of screenable young of the year. Entrainment and impingement data are particularly relevant for assessing which fish species have the greatest potential for being adversely affected by operation of Bowline, Roseton, and Indian Point with once-through cooling. These data from each of these three plants suggest that the six species that merit the greatest consideration are striped bass, white perch, tomcod, alewife, blueback herring, and bay anchovy. Two points of view are available for assessing the relative importance of the fish species in the Hudson River. From the fisheries point of view, the only two species of major importance are striped bass and shad. From the fish-community and ecosystem point of view, the dominant species, as determined by seasonal and regional standing crops (in numbers and biomass per hectare), are the six species most commonly entrained and impinged, namely, striped bass, white perch, tomcod, alewife, blueback herring, and anchovy.

13. Inception report and gap analysis. Boiler inspection

Energy Technology Data Exchange (ETDEWEB)

NONE

2004-06-01

This inception and gap analysis report on boilers in Latvia, has been prepared in the framework of the 'Implementation of the EU directive on energy performance of buildings: development of the Latvian Scheme for energy auditing of building and inspection of boilers'. The report is the basis for the establishment of training of boiler inspectors; it develops a gap analysis for better understanding and estimating the number of installations in Latvia and develops suggestions for the institutional set up. In particular includes information on existing standard and regulation on boiler, suggestion for the content of the training material of experts for boiler inspections and a syllabus of the training course. A specific section is dedicated to the suggestion for certification system of trained boiler inspectors. (au)

14. Inception report and gap analysis. Boiler inspection

Energy Technology Data Exchange (ETDEWEB)

NONE

2004-06-01

This inception and gap analysis report on boilers in Latvia, has been prepared in the framework of the 'Implementation of the EU directive on energy performance of buildings: development of the Latvian Scheme for energy auditing of building and inspection of boilers'. The report is the basis for the establishment of training of boiler inspectors; it develops a gap analysis for better understanding and estimating the number of installations in Latvia and develops suggestions for the institutional set up. In particular includes information on existing standard and regulation on boiler, suggestion for the content of the training material of experts for boiler inspections and a syllabus of the training course. A specific section is dedicated to the suggestion for certification system of trained boiler inspectors. (au)

15. Further development of recovery boiler; Soodakattilan kehitystyoe

Energy Technology Data Exchange (ETDEWEB)

Janka, K.; Siiskonen, P.; Sundstroem, K. [Tampella Power Oy, Tampere (Finland)] [and others

1996-12-01

The global model of a recovery boiler was further developed. The aim is to be able to model the velocity, temperature and concentration fields in a boiler. At this moment the model includes submodels for: droplet drying, pyrolysis, char burning, gas burning and for droplet trajectory. The preliminary study of NO{sub x} and fly ash behaviour in a boiler was carried out. The study concerning flow field in the superheater area was carried out a 2-dimensional case in which the inflow parameters were taken from global model of a recovery boiler. Further the prediction methods of fouling in a recovery boiler were developed based on theoretical calculations of smelting behaviour of multicomponent mixtures and measurements at operating recovery boilers. (author)

16. Increased combustion stability in modulating biomass boilers for district heating systems

Energy Technology Data Exchange (ETDEWEB)

Eriksson, Gunnar; Hermansson, Roger (eds.) [Lulea Univ. of Technology (Sweden)

2002-09-01

17. Stress-Assisted Corrosion in Boiler Tubes

Energy Technology Data Exchange (ETDEWEB)

Preet M Singh; Steven J Pawel

2006-05-27

A number of industrial boilers, including in the pulp and paper industry, needed to replace their lower furnace tubes or decommission many recovery boilers due to stress-assisted corrosion (SAC) on the waterside of boiler tubes. More than half of the power and recovery boilers that have been inspected reveal SAC damage, which portends significant energy and economic impacts. The goal of this project was to clarify the mechanism of stress-assisted corrosion (SAC) of boiler tubes for the purpose of determining key parameters in its mitigation and control. To accomplish this in-situ strain measurements on boiler tubes were made. Boiler water environment was simulated in the laboratory and effects of water chemistry on SAC initiation and growth were evaluated in terms of industrial operations. Results from this project have shown that the dissolved oxygen is single most important factor in SAC initiation on carbon steel samples. Control of dissolved oxygen can be used to mitigate SAC in industrial boilers. Results have also shown that sharp corrosion fatigue and bulbous SAC cracks have similar mechanism but the morphology is different due to availability of oxygen during boiler shutdown conditions. Results are described in the final technical report.

18. Boiler plants completed in record time

International Nuclear Information System (INIS)

Anon.

2001-01-01

Bubbling fluidised bed (BFB) combustion has steadily increased its share of the boiler market in recent years, particularly in the Nordic region, where it is particularly well-suited to handling the high moisture content biofuels produced and used by the forest products industry. Foster Wheeler is the world's leading supplier of fluidised bed combustion technology. Over 200 of the more than 300 fluidised bed boilers supplied by the company are circulating fluidised bed (CFB) designs, a market in which Foster Wheeler has more than a 40% share. Foster Wheeler Energia Oy supplied the Myllykoski project at Anjalankoski with a fluidised bed boiler, auxiliary steam boilers, and flue gas scrubber systems

19. The Technology Introduction of Chain Boiler Energy Conservation Transformation

Science.gov (United States)

Li, Henan; Liu, Xiwen; Yuan, Hong; Lin, Jiadai; Zhang, Yu

2017-12-01

Introduced the present status of chain boiler efficiency is low, the system analysis of the chain boiler optimization and upgrading of technology, for the whole progress of chain boiler to provide some ideas and reference.

20. Elevated temperature failures in boiler tubes - case studies

International Nuclear Information System (INIS)

1989-01-01

Metallurgical investigation of boiler tube failures enables identification of failure mechanisms and the underlying cause related to boiler conditions. Some case studies in short term overheating, prolonged overheating and low cycle fatigue failures in boiler tubes are discussed. (author)

1. Firetube boiler with high efficiency for producing saturated or superheated steam

Energy Technology Data Exchange (ETDEWEB)

Carosso, V J; Carosso, J Y

1976-10-07

This boiler for producing saturated or super-heated steam is to be manufactured in one piece or in units which can be assembled at site without skilled workers, at the factory. It is to have a high efficiency and dimensions which permit the transport of the completely assembled boiler by road transport. The relatively small water-steam vessel lies across the longitudinal axis of the boiler in the rear boiler space over a battery of preheater tubes. By these measures and by a very detailed and appropriately described rational arrangement of other parts, such as convection bundles, primary and secondary superheater, evaporation tubes, which form an 'evaporation shield', upper and lower longitudinal chambers with vertical connecting pipes of different crossections, the above mentioned condition for space requirement is fulfilled and a high efficiency should be achieved, but with considerable expense.

2. Coal-fired boiler houses in Cracow present state and possibilities to improve their efficiency

Energy Technology Data Exchange (ETDEWEB)

Cyklis, P. [Institute of Industrial Equipment and Power Engineering, Cracow (Poland); Butcher, T.A. [Brookhaven National Lab., Upton, NY (United States)

1995-12-31

A significant amount of heat energy both for heating and process purposes is generated in Cracow, Poland in small-and medium size local boiler houses. The operating procedure of these boiler houses is most often economically and ecologically ineffective because of the bad condition of boilers and lack of funds to install automation, control and measurement equipment. Within the Polish-American Program of Elimination of Low Emission Sources financed by the US Department of Energy, the ENERGOEKSPERT Co., Ltd. investigated chosen boiler houses in Cracow, commissioned by the Cracow Development Office. The results of these investigations were subject of engineering analysis carried out at the Institute of Industrial Equipment and Power Engineering, Technical University, Cracow. The analysis proved that the low-cost improvement of economic efficiency and reduction of air pollutant emission is feasible for combustion of coal fuels.

3. EFFICIENCY IMPROVEMENT IN INDUSTRIAL BOILER BY FLUE GAS DUCT INSULATION

OpenAIRE

Sanjay H. Zala

2017-01-01

Now a days in industry major losses are find out so here we calculate these losses and find out efficiency of boiler. Boiler efficiency and energy losses from boiler are important parameter for any industry using boiler. In this work a detailed analysis was carried out for boiler at Anish Chemicals Bhavnagar. It is a combined water and fire tube boiler using biomass coal as fuel. Boiler efficiency calculated by direct method is in range of (78.5% to 81.6%). Major losses from boiler are heat ...

4. MODELLING, SIMULATING AND OPTIMIZING BOILERS

DEFF Research Database (Denmark)

Sørensen, K.; Condra, T.; Houbak, Niels

2003-01-01

, and the total stress level (i.e. stresses introduced due to internal pressure plus stresses introduced due to temperature gradients) must always be kept below the allowable stress level. In this way, the increased water-/steam space that should allow for better dynamic performance, in the end causes limited...... freedom with respect to dynamic operation of the plant. By means of an objective function including as well the price of the plant as a quantification of the value of dynamic operation of the plant an optimization is carried out. The dynamic model of the boiler plant is applied to define parts...

5. Wood fuelled boiler operating costs

International Nuclear Information System (INIS)

Sandars, D.L.

1995-01-01

This report is a management study into the operating costs of wood-fired boilers. Data obtained from existing wood-fired plant has been analysed and interpreted using the principles of machinery management and the science that underlies the key differences between this fuel and any other. A set of budgeting principles has been developed for the key areas of labour requirement, insurance, maintenance and repair and electricity consumption. Other lesser cost centres such as the provision of shelter and the effects of neglect and accidents have also been considered, and a model constructed. (author)

6. Economic evaluation of a coal fired boiler

International Nuclear Information System (INIS)

Briem, J.J.

1983-01-01

This paper provides basic information on boiler economics which will assist steam users in analyzing the feasibility of using coal to generate steam - in either new or existing facilities. The information presented covers boilers ranging in size from 10,000 to 100,000 pounds per hour steaming capacity

7. 46 CFR 109.555 - Propulsion boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Propulsion boilers. 109.555 Section 109.555 Shipping COAST GUARD, DEPARTMENT OF HOMELAND SECURITY (CONTINUED) A-MOBILE OFFSHORE DRILLING UNITS OPERATIONS Miscellaneous § 109.555 Propulsion boilers. The master or person in charge and the engineer in charge shall...

8. 29 CFR 1915.162 - Ship's boilers.

Science.gov (United States)

2010-07-01

... 29 Labor 7 2010-07-01 2010-07-01 false Ship's boilers. 1915.162 Section 1915.162 Labor Regulations Relating to Labor (Continued) OCCUPATIONAL SAFETY AND HEALTH ADMINISTRATION, DEPARTMENT OF LABOR (CONTINUED) OCCUPATIONAL SAFETY AND HEALTH STANDARDS FOR SHIPYARD EMPLOYMENT Ship's Machinery and Piping Systems § 1915.162 Ship's boilers. (a) Before...

9. Developing Boiler Concepts as Integrated Units

DEFF Research Database (Denmark)

Sørensen, Kim; Condra, Thomas Joseph; Houbak, Niels

2004-01-01

- consisting of pressure part, burner and control system. The Technical University of Denmark, MEK - Energy Engineering Section [12] has participated in the modelling process. The project has included static and dynamic modelling of the boiler concept. For optimization of operation, verication of performance......With the objective to be able to optimize the design and operation of steam boiler concepts Aalborg Industries A/S [1] has together with Aalborg University, Institute of Energy Technology [9] carried out a development project paying special attention to the boiler concept as an integrated unit......, emissions and to obtain long time operation experiences with the boiler concept, a full scale prototype has been built and these tests have been accomplished on the prototype. By applying this integrated unit approach to the boiler concept development it has been possible to optimize the different building...

10. Chemical cleaning of AGR boilers

International Nuclear Information System (INIS)

Moore, S.V.; Moore, W.; Rantell, A.

1978-01-01

AGR boilers are likely to require post service chemical cleaning to remove accumulated oxides at intervals of 15 - 35 kh. The need to clean will be based on an assessment of such factors as the development of flow imbalances through parallel tubes induced by the formation of rough oxide surfaces, an increasing risk of localised corrosion as the growth of porous oxides proceeds and the risk of tube blockage caused by the exfoliation of steam-grown oxides. The study has shown what heterogeneous multilayer oxides possessing a range of physical and chemical properties form on the alloy steels. They include porous and compact magnetites, chromium spinels and sesquioxide. Ammoniated citric acid has been shown to remove deposited and water-grown magnetites from the carbon and alloy steels but will not necessarily remove the substituted spinels grown on the alloy steels or the potentially spalling steam-grown magnetite on the A1SI 316 superheater. Citric acid supplemented with the reducing agent glyoxal completely removes all oxides from the boiler except the protective inner spinel formed on the 316. Removal of the spinels and compact magnetites occurs more by undercutting and physical detachment than by the dissolution. (author)

11. AUTOMATIC BIOMASS BOILER WITH AN EXTERNAL THERMOELECTRIC GENERATOR

OpenAIRE

Marian Brázdil; Ladislav Šnajdárek; Petr Kracík; Jirí Pospíšil

2014-01-01

This paper presents the design and test results of an external thermoelectric generator that utilizes the waste heat from a small-scale domestic biomass boiler with nominal rated heat output of 25 kW. The low-temperature Bi2Te3 generator based on thermoelectric modules has the potential to recover waste heat from gas combustion products as effective energy. The small-scale generator is constructed from independent segments. Measurements have shown that up to 11 W of electricity can be generat...

12. Thermo-hydraulic characteristics of serpentine tubing in the boilers of gas cooled reactors under condition of rapid and slow depressurization

International Nuclear Information System (INIS)

2003-01-01

In nuclear reactors of the magnox or advanced gas cooled type, serpentine tubing is used in some designs to generate steam in a once through arrangement. The calculation of accidents using two phase flow codes requires knowledge of the heat transfer behaviour of the boiler steam side. A series of experiments to study the blowdown characteristics of a typical serpentine boiler section was devised in order to validate the MARTHA section of the MACE code used by nuclear electric . The tests were carried out on the thermal hydraulics experimental research assembly (THERA) loop at manchester university. Depressurization from an initial pressure of 60 bar, with fluid subcooling of 5 k, 50 k, and 100 k was controlled by discharging the test section contents through suitably chosen orifices to produce blowdown to 10% of the initial pressure over a time scale of 30 s to 3600 s. pressures and temperatures in the serpentine were measured at average time intervals of approximately 1 s

13. Biomass boiler energy conversion system analysis with the aid of exergy-based methods

International Nuclear Information System (INIS)

Li, Changchun; Gillum, Craig; Toupin, Kevin; Donaldson, Burl

2015-01-01

Highlights: • Conventional exergy analysis and advanced exergy analysis are performed. • The combustion process dominates the exergy destruction. • Increase excess air will decrease the overall boiler exergy efficiency. • Increase the SH temperatures will increase the overall boiler exergy efficiency. • The avoidable exergy destructions in the air heaters are very small. - Abstract: The objective of this paper is to establish a theoretical framework for the exergy analysis and advanced exergy analysis of a real biomass boiler. These analyses can be used for both the diagnosis and optimization of a biomass boiler as well as for the design of a new biomass boiler. Conventional exergy analysis is performed to recognize the source(s) of inefficiency and irreversibility and identify exergy destruction in different components of the biomass boiler. An advanced exergy analysis is performed to provide comprehensive information about the avoidable exergy destruction and real fuel-saving potential for each component, as well as the overall system. Sensitivity studies of several design parameters including the excess air, biomass moisture and steam parameters were evaluated. The results show that the maximum exergy destruction occurs in the combustion process, followed by the Water Walls (WW) & Radiant Superheater (RSH) and the Low Temperature Superheater (LTSH). The fuel-saving and exergy efficiency improvement strategies for different components are discussed in this paper

14. 46 CFR 61.05-15 - Boiler mountings and attachments.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Boiler mountings and attachments. 61.05-15 Section 61.05... TESTS AND INSPECTIONS Tests and Inspections of Boilers § 61.05-15 Boiler mountings and attachments. (a....05-10. (b) Each stud or bolt for each boiler mounting that paragraph (c) of this section requires to...

15. 46 CFR 63.25-7 - Exhaust gas boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Exhaust gas boilers. 63.25-7 Section 63.25-7 Shipping COAST GUARD, DEPARTMENT OF HOMELAND SECURITY (CONTINUED) MARINE ENGINEERING AUTOMATIC AUXILIARY BOILERS Requirements for Specific Types of Automatic Auxiliary Boilers § 63.25-7 Exhaust gas boilers. (a) Construction...

16. 49 CFR 230.30 - Lap-joint seam boilers.

Science.gov (United States)

2010-10-01

... 49 Transportation 4 2010-10-01 2010-10-01 false Lap-joint seam boilers. 230.30 Section 230.30..., DEPARTMENT OF TRANSPORTATION STEAM LOCOMOTIVE INSPECTION AND MAINTENANCE STANDARDS Boilers and Appurtenances Inspection and Repair § 230.30 Lap-joint seam boilers. Every boiler having lap-joint longitudinal seams...

17. CEGB research on boiler leaks and their detection in service

International Nuclear Information System (INIS)

Hayes, D.J.

1978-01-01

The penalty in loss of output to an electricity generation organisation as a consequence of failure to deal effectively with small LMFBR boiler leaks would be large. There is therefore a considerable incentive for these organisations to satisfy themselves that proper provisions are made to ensure that both the incidence and the severity of boiler leaks are minimised. In the UK, responsibility for the research, development and design work for this and indeed for most aspects of future nuclear power plant rests with the UKAEA and NPC; nevertheless as a consequence of its 'informed operator' policy the Central Electricity Generating Board has devoted some research effort to this field in recent years. o date, research work has been put in hand with the objective of achieving an understanding of the basic behaviour of boiler leaks. In addition, attention has been given to leak detection by monitoring the sodium for increases in oxygen and hydrogen levels. In both cases leaks into liquid sodium rather than into the gas space have been considered. In the course of the work hydrogen and oxygen meters based on the galvanic cell principle have been constructed and evaluated. The former is a new device which is comparable in performance with hydrogen meters based on the ion pump. The present state of the work is briefly described in this paper

18. CEGB research on boiler leaks and their detection in service

Energy Technology Data Exchange (ETDEWEB)

Hayes, D J [Berkeley Nuclear Laboratories, Berkeley, Gloucestershire (United Kingdom)

1978-10-01

The penalty in loss of output to an electricity generation organisation as a consequence of failure to deal effectively with small LMFBR boiler leaks would be large. There is therefore a considerable incentive for these organisations to satisfy themselves that proper provisions are made to ensure that both the incidence and the severity of boiler leaks are minimised. In the UK, responsibility for the research, development and design work for this and indeed for most aspects of future nuclear power plant rests with the UKAEA and NPC; nevertheless as a consequence of its 'informed operator' policy the Central Electricity Generating Board has devoted some research effort to this field in recent years. o date, research work has been put in hand with the objective of achieving an understanding of the basic behaviour of boiler leaks. In addition, attention has been given to leak detection by monitoring the sodium for increases in oxygen and hydrogen levels. In both cases leaks into liquid sodium rather than into the gas space have been considered. In the course of the work hydrogen and oxygen meters based on the galvanic cell principle have been constructed and evaluated. The former is a new device which is comparable in performance with hydrogen meters based on the ion pump. The present state of the work is briefly described in this paper.

19. Electrical design requirements for electrode boilers for nuclear plants

International Nuclear Information System (INIS)

Kempker, M.J.

1979-01-01

Medium-voltage steam electrode boilers, in the 20- to 50-MW range, have become an attractive alternative to comparable fossil-fueled boilers as a source of auxiliary steam during the startup and normal shutdown of nuclear power plants. The electrode boiler represents a favorable option because of environmental, fire protection, and licensing considerations. However, this electrical option brings some difficult design problems for which solutions are required in order to integrate the electrode boiler into the plant low resistance grounded power system. These considerations include the effects of an unbalanced electrode boiler on the performance of polyphase induction motors, boiler grounding for personnel safety, boiler neutral grounding, and ground relaying

20. Environmental performance assessment of utility boiler energy conversion systems

International Nuclear Information System (INIS)

Li, Changchun; Gillum, Craig; Toupin, Kevin; Park, Young Ho; Donaldson, Burl

2016-01-01

Highlights: • Sustainability analyses of utility boilers are performed. • Natural gas fired boilers have the least CO_2 emissions in fossil fueled boilers. • Solar boilers rank last with an emergy yield ratio of 1.2. • Biomass boilers have the best emergy sustainability index. - Abstract: A significant amount of global electric power generation is produced from the combustion of fossil fuels. Steam boilers are one of the most important components for steam and electricity production. The objective of this paper is to establish a theoretical framework for the sustainability analysis of a utility boiler. These analyses can be used by decision-makers to diagnose and optimize the sustainability of a utility boiler. Seven utility boiler systems are analyzed using energy and embodied solar energy (emergy) principles in order to evaluate their environmental efficiencies. They include a subcritical coal fired boiler, a supercritical coal fired boiler, an oil fired boiler, a natural gas fired boiler, a concentrating solar power boiler utilizing a tower configuration, a biomass boiler, and a refuse derived fuel boiler. Their relative environmental impacts were compared. The results show that the natural gas boiler has significantly lower CO_2 emission than an equivalent coal or oil fired boiler. The refuse derived fuel boiler has about the same CO_2 emissions as the natural gas boiler. The emergy sustainability index of a utility boiler system is determined as the measure of its sustainability from an environmental perspective. Our analyses results indicate that the natural gas boiler has a relatively high emergy sustainability index compared to other fossil fuel boilers. Converting existing coal boilers to natural gas boilers is a feasible option to achieve better sustainability. The results also show that the biomass boiler has the best emergy sustainability index and it will remain a means to utilize the renewable energy within the Rankine steam cycle. Before

1. Chemical cleaning of UK AGR boilers

International Nuclear Information System (INIS)

Rudge, A.; Turner, P.; Ghosh, S.; Clary, W.; Tice, D.R.

2002-01-01

For a number of years, the waterside pressure drops across the advanced gas-cooled reactor (AGR) pod boilers have been increasing. The pressure drop increases have accelerated with time, which is the converse behaviour to that expected for rippled magnetite formation (rapid initial increase slowing down with time). Nonetheless, magnetite deposition remains the most likely cause for the increasing boiler resistances. A number of potential countermeasures have been considered in response to the boiler pressure drop increases. However, there was no detectable reduction in the rate of pressure drop increase. Chemical cleaning was therefore considered and a project to substantiate and then implement chemical cleaning was initiated. (authors)

2. Design, construction and operating experience of boilers at Wylfa power station

Energy Technology Data Exchange (ETDEWEB)

Razzell, R N [Wylfa Power Station, Central Electricity Generating Board, Gwynedd (United Kingdom)

1988-07-01

The report will describe the boilers, but will emphasise the problems encountered and the solutions. The boilers are 'once through' with start up drums. Some redundancy was provided but this advantage was lost due to downrating of gas temperature. The boilers are carbon steel suspended plattens (992 per reactor) tightly packed in the annular space between the core shielding and the spherical wall of the pressure vessel. This construction denies access to repair tube leaks. when a leak occurs the faulty platten has to be plugged off. This is done with the reactor at 60% power. The process will be described. Reactor 1 commenced operation in 1971, Reactor 2 in June 1971. Between 1972 and May 1984 21 leaks occurred which resulted in a major shutdown for investigation. This revealed the leaks were caused by gas flow induced vibration resulting in fretting of tubes in clips. Restraints and additional clamps were fitted. This has been successful but the modifications were extensive and in very difficult working conditions, the Reactor being shut down until May 1976. A family of leaks adjacent to personnel access ways commenced in Reactor 1 in 1975 which was later identified as erosion/corrosion on the water/steam side caused by the feed flow instability. This problem is common to both Reactors. Various modifications have been applied. Redistribution of feed flow using orifice plates and ferrules was only temporarily successful. Following extensive rig testing the feed water has been dosed with amino methyl proponal (AMP) since September 1983 with an immediate and sustained reduction in the leak rate. The amine provides protection through the steam/water phase. Rig testing continues to attain a better understanding of the erosion/corrosion. (author)

3. Design, construction and operating experience of boilers at Wylfa power station

International Nuclear Information System (INIS)

Razzell, R.N.

1988-01-01

The report will describe the boilers, but will emphasise the problems encountered and the solutions. The boilers are 'once through' with start up drums. Some redundancy was provided but this advantage was lost due to downrating of gas temperature. The boilers are carbon steel suspended plattens (992 per reactor) tightly packed in the annular space between the core shielding and the spherical wall of the pressure vessel. This construction denies access to repair tube leaks. when a leak occurs the faulty platten has to be plugged off. This is done with the reactor at 60% power. The process will be described. Reactor 1 commenced operation in 1971, Reactor 2 in June 1971. Between 1972 and May 1984 21 leaks occurred which resulted in a major shutdown for investigation. This revealed the leaks were caused by gas flow induced vibration resulting in fretting of tubes in clips. Restraints and additional clamps were fitted. This has been successful but the modifications were extensive and in very difficult working conditions, the Reactor being shut down until May 1976. A family of leaks adjacent to personnel access ways commenced in Reactor 1 in 1975 which was later identified as erosion/corrosion on the water/steam side caused by the feed flow instability. This problem is common to both Reactors. Various modifications have been applied. Redistribution of feed flow using orifice plates and ferrules was only temporarily successful. Following extensive rig testing the feed water has been dosed with amino methyl proponal (AMP) since September 1983 with an immediate and sustained reduction in the leak rate. The amine provides protection through the steam/water phase. Rig testing continues to attain a better understanding of the erosion/corrosion. (author)

4. Treatment of Berkeley boilers in Studsvik. Project description and experiences - Berkeley Boilers Project

International Nuclear Information System (INIS)

Saul, Dave; Davidson, Gavin; Wirendal, Bo

2014-01-01

In November 2011 Studsvik was awarded a contract to transport five decommissioned boilers from the Berkeley Nuclear Licensed Site in the UK to the Studsvik Nuclear Site in Sweden for metal treatment and recycling. A key objective of the project was to remove the boilers from the site by 31 March 2012 and this was successfully achieved with all boilers off site by 22 March and delivered to Studsvik on 6 April. In November 2012 Studsvik was awarded a further contract for the remaining ten Berkeley Boilers with the requirement to remove all boilers from the Berkeley site by 31 March 2013. Again this was successfully achieved ahead of programme with all boilers in Sweden by 1 April 2013. A total of nine boilers have now been processed and all remaining boilers will be completed by end of September 2014. The projects have had many challenges including a very tight timescale and both have been successfully delivered to cost and ahead of the baseline programme. This paper describes the project and the experience gained from treatment of the boilers to date. (authors)

5. Mass spectra features of biomass burning boiler and coal burning boiler emitted particles by single particle aerosol mass spectrometer.

Science.gov (United States)

Xu, Jiao; Li, Mei; Shi, Guoliang; Wang, Haiting; Ma, Xian; Wu, Jianhui; Shi, Xurong; Feng, Yinchang

2017-11-15

In this study, single particle mass spectra signatures of both coal burning boiler and biomass burning boiler emitted particles were studied. Particle samples were suspended in clean Resuspension Chamber, and analyzed by ELPI and SPAMS simultaneously. The size distribution of BBB (biomass burning boiler sample) and CBB (coal burning boiler sample) are different, as BBB peaks at smaller size, and CBB peaks at larger size. Mass spectra signatures of two samples were studied by analyzing the average mass spectrum of each particle cluster extracted by ART-2a in different size ranges. In conclusion, BBB sample mostly consists of OC and EC containing particles, and a small fraction of K-rich particles in the size range of 0.2-0.5μm. In 0.5-1.0μm, BBB sample consists of EC, OC, K-rich and Al_Silicate containing particles; CBB sample consists of EC, ECOC containing particles, while Al_Silicate (including Al_Ca_Ti_Silicate, Al_Ti_Silicate, Al_Silicate) containing particles got higher fractions as size increase. The similarity of single particle mass spectrum signatures between two samples were studied by analyzing the dot product, results indicated that part of the single particle mass spectra of two samples in the same size range are similar, which bring challenge to the future source apportionment activity by using single particle aerosol mass spectrometer. Results of this study will provide physicochemical information of important sources which contribute to particle pollution, and will support source apportionment activities. Copyright © 2017. Published by Elsevier B.V.

6. Multi-pressure boiler thermodynamics analysis code

International Nuclear Information System (INIS)

Lorenzoni, G.

1992-01-01

A new method and the relative FORTRAN program for the thermodynamics design analysis of a multipressure boiler are reported. This method permits the thermodynamics design optimization with regard to total exergy production and a preliminary costs

7. New thinking for the boiler room.

Science.gov (United States)

Rose, Wayne

2008-09-01

Wayne Rose, marketing manager at integrated plant room manufacturer Armstrong Integrated Systems, explains how increasing use of off-site manufacture, the latest 3D modelling technology, and advances in control technology, are revolutionising boiler room design and construction.

8. Modelling and simulating fire tube boiler performance

DEFF Research Database (Denmark)

Sørensen, K.; Condra, T.; Houbak, Niels

2003-01-01

A model for a flue gas boiler covering the flue gas and the water-/steam side has been formulated. The model has been formulated as a number of sub models that are merged into an overall model for the complete boiler. Sub models have been defined for the furnace, the convection zone (split in 2......: a zone submerged in water and a zone covered by steam), a model for the material in the boiler (the steel) and 2 models for resp. the water/steam zone (the boiling) and the steam. The dynamic model has been developed as a number of Differential-Algebraic-Equation system (DAE). Subsequently Mat......Lab/Simulink has been applied for carrying out the simulations. To be able to verify the simulated results experiments has been carried out on a full scale boiler plant....

9. Pirotubular boilers design. Diseno de calderas pirotubulares

Energy Technology Data Exchange (ETDEWEB)

Latre Durso, F. (Geval S.A. (Spain))

1994-01-01

This article describes the conceptual design of Pirotubular boilers from the valuable thermal point of view, to the dimensional. This topic is a very tool valuable for professionals of design and for maintenance and operation equipment.

10. Water side corrosion prevention in boilers

International Nuclear Information System (INIS)

Zeid, A.

1993-01-01

Corrosion may be defined as a naturally occurring physical and chemical deterioration of a material due to reaction with the environment or surrounding atmosphere. In boilers the material is subjected on both sides to two different media which may cause severe corrosion. At the water side the content of O 2 considered one of the principal factors which determine the extent of corrosion in the boiler tubes. This paper deals with certain conditions that result in the increase of O 2 in the boiler water and hence increase the corrosion rate, to minimize the effect of these conditions a chemical treatment was carried out the results obtained indicated the success of the treatment procedure in corrosion prevention and boiler material protection. The treatment is traditional. But the study indicates how a simple mean could be applied to solve a serious problem. 4 tab

11. Catalytic burners in larger boiler appliances

Energy Technology Data Exchange (ETDEWEB)

Silversand, Fredrik; Persson, Mikael (Catator AB, Lund (Sweden))

2009-02-15

This project focuses on the scale up of a Catator's catalytic burner technology to enable retrofit installation in existing boilers and the design of new innovative combinations of catalytic burners and boilers. Different design approaches are discussed and evaluated in the report and suggestions are made concerning scale-up. Preliminary test data, extracted from a large boiler installation are discussed together with an accurate analysis of technical possibilities following an optimization of the boiler design to benefit from the advantages of catalytic combustion. The experimental work was conducted in close collaboration with ICI Caldaie (ICI), located in Verona, Italy. ICI is a leading European boiler manufacturer in the effect segment ranging from about 20 kWt to several MWt. The study shows that it is possibly to scale up the burner technology and to maintain low emissions. The boilers used in the study were designed around conventional combustion and were consequently not optimized for implementation of catalytic burners. From previous experiences it stands clear that the furnace volume can be dramatically decreased when applying catalytic combustion. In flame combustion, this volume is normally dimensioned to avoid flame impingement on cold surfaces and to facilitate completion of the gas-phase reactions. The emissions of nitrogen oxides can be reduced by decreasing the residence time in the furnace. Even with the over-dimensioned furnace used in this study, we easily reached emission values close to 35 mg/kWh. The emissions of carbon monoxide and unburned hydrocarbons were negligible (less than 5 ppmv). It is possible to decrease the emissions of nitrogen oxides further by designing the furnace/boiler around the catalytic burner, as suggested in the report. Simultaneously, the size of the boiler installation can be reduced greatly, which also will result in material savings, i.e. the production cost can be reduced. It is suggested to optimize the

12. Boiler burden reduced at Bedford site.

Science.gov (United States)

Horsley, Chris

2011-10-01

With the NHS aiming to reduce its 2007 carbon footprint by 10% by 2015, Chris Horsley, managing director of Babcock Wanson UK, a provider of industrial boilers and burners, thermal oxidisers, air treatment, water treatment, and associated services, looks at how one NHS Trust has approached the challenge, and considerably reduced its carbon emissions, by refurbishing its boiler house and moving from oil to gas-fired steam generation.

13. Ecological boiler modernization, feasible energy solutions

International Nuclear Information System (INIS)

Krcek, F.; Matev, M.; Sykora, J.; Chladek, J.

2005-01-01

Alstom Power, s.r.o., ALSTOM GROUP in Brno, Czech Republic is a successor of PBS (First Brno Machine Works). PBS was a well-known company in Bulgaria - mainly as Heating Power Plant (HPP) and Industrial Plant supplier of boilers, industrial steam turbines, milling systems, heat exchangers Btc. PBS has been privatised in two stages starting at1993 year. Alstom recently deals with boiler and heat exchanger products. Industrial turbine but has been sold to Siemens in 2004

14. Gas fired boilers and atmospheric pollution

International Nuclear Information System (INIS)

Chiaranello, J.M.

1991-01-01

A general analysis concerning atmospheric pollution is presented: chemical composition and vertical distribution of atmosphere and pollutants, chemical reactions, ozone destruction and production cycles, COx, NOx and SOx pollutions. The gas fired boiler number and repartition in France are presented and the associated pollution is analyzed (CO2, CO, NOx) and quantified. Various pollution control technics concerning gas fired boiler pollutants are described and a pollution criterion for clean gas fired generators is proposed

15. Increasing the thermal efficiency of boiler plant

Directory of Open Access Journals (Sweden)

Uyanchinov Evgeniy

2017-01-01

Full Text Available The thermal efficiency increase of boiler plant is actual task of scientific and technical researches. The optimization of boiler operating conditions is task complex, which determine by most probable average load of boiler, operating time and characteristics of the auxiliary equipment. The work purpose – the determination of thermodynamic efficiency increase ways for boiler plant with a gas-tube boiler. The tasks, solved at the research are the calculation of heat and fuel demand, the exergetic analysis of boilerhouse and heat network equipment, the determination of hydraulic losses and exergy losses due to restriction. The calculation was shown that the exergy destruction can be reduced by 2.39% due to excess air reducing to 10%; in addition the oxygen enrichment of air can be used that leads to reducing of the exergy destruction rate. The processes of carbon deposition from the side of flame and processes of scale formation on the water side leads to about 4.58% losses of fuel energy at gas-tube boiler. It was shown that the exergy losses may be reduced by 2.31% due to stack gases temperature reducing to 148 °C.

16. Development of combined low-emissions burner devices for low-power boilers

Science.gov (United States)

Roslyakov, P. V.; Proskurin, Yu. V.; Khokhlov, D. A.

2017-08-01

Low-power water boilers are widely used for autonomous heat supply in various industries. Firetube and water-tube boilers of domestic and foreign manufacturers are widely represented on the Russian market. However, even Russian boilers are supplied with licensed foreign burner devices, which reduce their competitiveness and complicate operating conditions. A task of developing efficient domestic low-emissions burner devices for low-power boilers is quite acute. A characteristic property of ignition and fuel combustion in such boilers is their flowing in constrained conditions due to small dimensions of combustion chambers and flame tubes. These processes differ significantly from those in open combustion chambers of high-duty power boilers, and they have not been sufficiently studied yet. The goals of this paper are studying the processes of ignition and combustion of gaseous and liquid fuels, heat and mass transfer and NO x emissions in constrained conditions, and the development of a modern combined low-emissions 2.2 MW burner device that provides efficient fuel combustion. A burner device computer model is developed and numerical studies of its operation on different types of fuel in a working load range from 40 to 100% of the nominal are carried out. The main features of ignition and combustion of gaseous and liquid fuels in constrained conditions of the flame tube at nominal and decreased loads are determined, which differ fundamentally from the similar processes in steam boiler furnaces. The influence of the burner devices design and operating conditions on the fuel underburning and NO x formation is determined. Based on the results of the design studies, a design of the new combined low-emissions burner device is proposed, which has several advantages over the prototype.

17. Pelly Crossing wood chip boiler

Energy Technology Data Exchange (ETDEWEB)

1985-03-11

The Pelly wood chip project has demonstrated that wood chips are a successful fuel for space and domestic water heating in a northern climate. Pelly Crossing was chosen as a demonstration site for the following reasons: its extreme temperatures, an abundant local supply of resource material, the high cost of fuel oil heating and a lack of local employment. The major obstacle to the smooth operation of the boiler system was the poor quality of the chip supply. The production of poor quality chips has been caused by inadequate operation and maintenance of the chipper. Dull knives and faulty anvil adjustments produced chips and splinters far in excess of the one centimetre size specified for the system's design. Unanticipated complications have caused costs of the system to be higher than expected by approximately \$15,000. The actual cost of the project was approximately \$165,000. The first year of the system's operation was expected to accrue \$11,600 in heating cost savings. This estimate was impossible to confirm given the system's irregular operation and incremental costs. Consistent operation of the system for a period of at least one year plus the installation of monitoring devices will allow the cost effectiveness to be calculated. The wood chip system's impact on the environment was estimated to be minimal. Wood chip burning was considered cleaner and safer than cordwood burning. 9 refs., 6 figs., 6 tabs.

18. VERIFICATION TESTING OF EMISSIONS FROM THE COMBUSTION OF A-55 CLEAN FUELS IN A FIRETUBE BOILER

Science.gov (United States)

The report gives results of testing three fuels in a small (732 kW) firetube package boiler to determine emissions of carbon monoxide (CO), nitrogen oxide (NO), particulate matter (PM), and total hydrocarbons (THCs). The tests were part of EPA's Environmental Technology Verificat...

19. Combustion and co-combustion of biomass in a bubbling fluidized bed boiler

NARCIS (Netherlands)

Khan, A.A.

2007-01-01

This PhD dissertation concerns the study of different aspects of biomass (co)-combustion in small-scale fluidized bed boilers for heat generation. The most renowned gaseous emissions from fluidized bed combustion, namely, CO and NO, are investigated with the help of experimental and theoretical

20. Market profile of autonomous solar boiler buyers in the period 1995-1998

International Nuclear Information System (INIS)

2000-05-01

The results of a first evaluation of solar water heater users, who decided to purchase or rent a solar boiler independent and autonomous, are presented. The results are compared with customer profiles of small photovoltaic power supplies and (potential) 'green energy' customers. Based on those results public utilities and other interested parties can set up specific activities and send out mailings

1. NOx Control Options and Integration for US Coal Fired Boilers

Energy Technology Data Exchange (ETDEWEB)

Mike Bockelie; Marc Cremer; Kevin Davis; Martin Denison; Adel Sarofim; Connie Senior; Hong-Shig Shim; Dave Swenson; Bob Hurt; Eric Suuberg; Eric Eddings; Kevin Whitty; Larry Baxter; Calvin Bartholomew; William Hecker

2006-06-30

in a pilot scale furnace and soot behavior predicted by the CFD model showed good agreement. Field and laboratory tests were performed for SCR catalysts used for coal and biomass co-firing applications. Fundamental laboratory studies were performed to better understand mechanisms involved with catalyst deactivation. Field tests with a slip stream reactor were used to create catalyst exposed to boiler flue gas for firing coal and for co-firing coal and biomass. The field data suggests the mechanisms leading to catalyst deactivation are, in order of importance, channel plugging, surface fouling, pore plugging and poisoning. Investigations were performed to better understand the mechanisms involved with catalyst regeneration through mechanical or chemical methods. A computer model was developed to predict NOx reduction across the catalyst in a SCR. Experiments were performed to investigate the fundamentals of ammonia/fly ash interactions with relevance to the operation of advanced NOx control technologies such as selective catalytic reduction. Measurements were performed for ammonia adsorption isotherms on commercial fly ash samples subjected to a variety of treatments and on the chemistry of dry and semi-dry ammonia removal processes. This work resulted in the first fundamental ammonia isotherms on carbon-containing fly ash samples. This work confirms industrial reports that aqueous solution chemistry takes place upon the introduction of even very small amounts of water, while the ash remains in a semi-dry state.

2. Thermoelectric Power Generation Utilizing the Waste Heat from a Biomass Boiler

Science.gov (United States)

Brazdil, Marian; Pospisil, Jiri

2013-07-01

The objective of the presented work is to test the possibility of using thermoelectric power to convert flue gas waste heat from a small-scale domestic pellet boiler, and to assess the influence of a thermoelectric generator on its function. A prototype of the generator, able to be connected to an existing device, was designed, constructed, and tested. The performance of the generator as well as the impact of the generator on the operation of the boiler was investigated under various operating conditions. The boiler gained auxiliary power and could become a combined heat and power unit allowing self-sufficient operation. The created unit represents an independent source of electricity with effective use of fuel.

3. The load structure of electro boilers

International Nuclear Information System (INIS)

Feilberg, N.; Livik, K.

1995-01-01

Load measurements have been performed on 24 electro boilers with a time resolution of one hour throughout a period of one year. The boilers are used for space heating and heating of tap water in office buildings, shopping centres and apartment buildings. All boilers have tariffs with disconnection agreements. This report presents load analyses of the measurements from each boiler, and typical load profiles are calculated and presented. It also analyses how boilers are used in relation to the outdoor temperature and the power price on the spot market. All the measurements are performed in Bergen, Norway, in the period August 1993 - August 1994. Typical load profiles are shown, both annual and daily, as well as specific load parameters in addition to key figures used in calculating the total power load on the distribution network. The climate impact on energy and power load is evaluated. The report also shows examples of how the results may be applied in various special fields. 8 figs., 9 tabs

4. Increasing the efficiency of the condensing boiler

Science.gov (United States)

Zaytsev, ON; Lapina, EA

2017-11-01

Analysis of existing designs of boilers with low power consumption showed that the low efficiency of the latter is due to the fact that they work in most cases when the heating period in the power range is significantly less than the nominal power. At the same time, condensing boilers do not work in the most optimal mode (in condensing mode) in the central part of Russia, a significant part of their total operating time during the heating season. This is due to existing methods of equipment selection and joint operation with heating systems with quantitative control of the coolant. It was also revealed that for the efficient operation of the heating system, it is necessary to reduce the inertia of the heat generating equipment. Theoretical patterns of thermal processes in the furnace during combustion gas at different radiating surfaces location schemes considering the influence of the very furnace configuration, characterized in that to reduce the work condensing boiler in conventional gas boiler operation is necessary to maintain a higher temperature in the furnace (in the part where spiral heat exchangers are disposed), which is possible when redistributing heat flow - increase the proportion of radiant heat from the secondary burner emitter allow Perey For the operation of the condensing boiler in the design (condensation) mode practically the entire heating period.

5. Ultrasonic boiler inspection and economic analysis guidelines

International Nuclear Information System (INIS)

Anon.

1987-01-01

Boiler tube failures cause approximately 6% availability loss of large fossil-fired power generating plants. This loss can be reduced by systematic approaches using ultrasonic examination and root cause failure analysis methods. Two projects sponsored by EPRI have provided utility engineers with guidelines for performing ultrasonic examinations and with details on 22 types of tube failure mechanisms. A manual has been published that provides descriptions of typical locations, superficial appearances, damage mechanisms, metallurgy, microstructural changes, likely root causes, and potential corrective actions. Application of the principles in the manual is being demonstrated in an EPRI-funded project at 10 electric utilities over the next two years. Guidelines have been published that prescribe the activities necessary for ultrasonic examinations of boiler tubes. Eight essential elements of a boiler examination should be performed to assure that possible economic benefits are obtained. Work was supported by EPRI under RP 1890 and RP 1865. A software package has been developed for effectively planning inspections for wall thinning in fossil-fired boiler tubing. The software assists in minimizing costs associated with maintenance, such as inspection and repair, while the life of the boiler is maximized

6. AUTOMATIC BIOMASS BOILER WITH AN EXTERNAL THERMOELECTRIC GENERATOR

Directory of Open Access Journals (Sweden)

Marian Brázdil

2014-02-01

Full Text Available This paper presents the design and test results of an external thermoelectric generator that utilizes the waste heat from a small-scale domestic biomass boiler with nominal rated heat output of 25 kW. The low-temperature Bi2Te3 generator based on thermoelectric modules has the potential to recover waste heat from gas combustion products as effective energy. The small-scale generator is constructed from independent segments. Measurements have shown that up to 11 W of electricity can be generated by one segment. Higher output power can be achieved by linking thermoelectric segments. The maximum output power is given by the dew point of the flue gas. The electrical energy that is generated can be used, e.g., for power supply or for charging batteries. In the near future, thermoelectric generators could completely eliminate the dependence an automated domestic boiler system on the power supply from the electricity grid, and could ensure comfortable operation in the event of an unexpected power grid failure.

7. 46 CFR 52.25-5 - Miniature boilers (modifies PMB-1 through PMB-21).

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Miniature boilers (modifies PMB-1 through PMB-21). 52.25... ENGINEERING POWER BOILERS Other Boiler Types § 52.25-5 Miniature boilers (modifies PMB-1 through PMB-21). Miniature boilers must meet the applicable provisions in this part for the boiler type involved and the...

8. Evaluation of thermal overload in boiler operators.

Science.gov (United States)

Braga, Camila Soares; Rodrigues, Valéria Antônia Justino; Campos, Julio César Costa; de Souza, Amaury Paulo; Minette, Luciano José; de Moraes, Angêlo Casali; Sensato, Guilherme Luciano

2012-01-01

The Brazilians educational institutions need a large energy demand for the operation of laundries, restaurants and accommodation of students. Much of that energy comes from steam generated in boilers with wood fuel. The laboral activity in boiler may present problems for the operator's health due to exposure to excessive heat, and its operation has a high degree of risk. This paper describes an analysis made the conditions of thermal environment in the operation of a B category boiler, located at a Higher Education Institution, located in the Zona da Mata Mineira The equipments used to collect data were Meter WBGT of the Heat Index; Meter of Wet Bulb Index and Globe Thermometer (WBGT); Politeste Instruments, an anemometer and an Infrared Thermometer. By the application of questionnaires, the second phase consisted of collecting data on environmental factors (temperature natural environment, globe temperature, relative humidity and air velocity). The study concluded that during the period evaluated, the activity had thermal overload.

9. 46 CFR 61.05-20 - Boiler safety valves.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Boiler safety valves. 61.05-20 Section 61.05-20 Shipping... INSPECTIONS Tests and Inspections of Boilers § 61.05-20 Boiler safety valves. Each safety valve for a drum, superheater, or reheater of a boiler shall be tested at the interval specified by table 61.05-10. [CGD 95-028...

10. Computer simulation of the fire-tube boiler hydrodynamics

Directory of Open Access Journals (Sweden)

Khaustov Sergei A.

2015-01-01

Full Text Available Finite element method was used for simulating the hydrodynamics of fire-tube boiler with the ANSYS Fluent 12.1.4 engineering simulation software. Hydrodynamic structure and volumetric temperature distribution were calculated. The results are presented in graphical form. Complete geometric model of the fire-tube boiler based on boiler drawings was considered. Obtained results are suitable for qualitative analysis of hydrodynamics and singularities identification in fire-tube boiler water shell.

11. Application of GPRS and GIS in Boiler Remote Monitoring System

OpenAIRE

Hongchao Wang; Yifeng Wu

2012-01-01

Application of GPRS and GIS in boiler remote monitoring system was designed in this paper by combining the advantage of GPRS and GIS in remote data transmission with configuration monitoring technology. The detail information of the operating conditions of the industrial boiler can be viewed by marking the location of boiler on the electronic map dynamically which can realize the unified management for industrial boiler of a region or city conveniently. Experimental application show that the ...

12. Condensing boiler applications in the process industry

International Nuclear Information System (INIS)

Chen, Qun; Finney, Karen; Li, Hanning; Zhang, Xiaohui; Zhou, Jue; Sharifi, Vida; Swithenbank, Jim

2012-01-01

Major challenging issues such as climate change, energy prices and fuel security have focussed the attention of process industries on their energy efficiency and opportunities for improvement. The main objective of this research study was to investigate technologies needed to exploit the large amount of low grade heat available from a flue gas condensing system through industrial condensing boilers. The technology and application of industrial condensing boilers in various heating systems were extensively reviewed. As the condensers require site-specific engineering design, a case study was carried out to investigate the feasibility (technically and economically) of applying condensing boilers in a large scale district heating system (40 MW). The study showed that by recovering the latent heat of water vapour in the flue gas through condensing boilers, the whole heating system could achieve significantly higher efficiency levels than conventional boilers. In addition to waste heat recovery, condensing boilers can also be optimised for emission abatement, especially for particle removal. Two technical barriers for the condensing boiler application are corrosion and return water temperatures. Highly corrosion-resistant material is required for condensing boiler manufacture. The thermal design of a 'case study' single pass shell-and-tube condensing heat exchanger/condenser showed that a considerable amount of thermal resistance was on the shell-side. Based on the case study calculations, approximately 4900 m 2 of total heat transfer area was required, if stainless steel was used as a construction material. If the heat transfer area was made of carbon steel, then polypropylene could be used as the corrosion-resistant coating material outside the tubes. The addition of polypropylene coating increased the tube wall thermal resistance, hence the required heat transfer area was approximately 5800 m 2 . Net Present Value (NPV) calculations showed that the choice of a carbon

13. Control Properties of Bottom Fired Marine Boilers

DEFF Research Database (Denmark)

Solberg, Brian; Andersen, Palle; Karstensen, Claus M. S.

2005-01-01

This paper focuses on model analysis of a dynamic model of a bottom fired one-pass smoke tube boiler. Linearised versions of the model are analysed to determine how gain, time constants and right half plane zeros (caused by the shrink-and-swell phenomenon) depend on the steam flow load. Furthermore...... the interactions in the system are inspected to analyse potential benefit from using a multivariable control strategy in favour of the current strategy based on single loop theory. An analysis of the nonlinear model is carried out to further determine the nonlinear characteristics of the boiler system...

14. Developing trends with boiler operation and management

Energy Technology Data Exchange (ETDEWEB)

Stark, J.M. [Occupational Safety and Health Service, Wellington (New Zealand). Dept. of Labour, Engineering Safety Branch

1993-12-31

Over recent years there have been many improvements in boiler control and safety management systems. Technology has made major advances and is now regarded as being well proven in Australia, Europe and the United Kingdom and these changes have been examined by a project committee, convened for the purpose, to establish whether they are equally applicable in New Zealand. The result of the committee`s findings and experience is contained in the `Draft Code of Practice`. This paper explains the development of the `Code of Practice`, the reasoning behind some of the decisions taken and the implications of these changes to boiler owners.

15. Optimal load allocation of multiple fuel boilers.

Science.gov (United States)

Dunn, Alex C; Du, Yan Yi

2009-04-01

This paper presents a new methodology for optimally allocating a set of multiple industrial boilers that each simultaneously consumes multiple fuel types. Unlike recent similar approaches in the utility industry that use soft computing techniques, this approach is based on a second-order gradient search method that is easy to implement without any specialized optimization software. The algorithm converges rapidly and the application yields significant savings benefits, up to 3% of the overall operating cost of industrial boiler systems in the examples given and potentially higher in other cases, depending on the plant circumstances. Given today's energy prices, this can yield significant savings benefits to manufacturers that raise steam for plant operations.

16. Firewood boiler operators and heat exposure

Directory of Open Access Journals (Sweden)

Vilson Bernardo Stollmeier

2017-12-01

Full Text Available This article presents an analysis of heat exposure work in boiler industry wood from a company in the industrial sector, focusing on the analysis of the environmental burden of the activity. Therefore, the methodological procedures consisted of document analysis, interviews, filming, evaluation problems of the effects of the hot environment and its prevention. The results show that the fuel to the boiler operators are exposed to heat and need guidance on their daily activities with prevention of diseases affected by excessive heat. Are also suggested training in technical and health to improve working conditions and the operator's health.

17. Boiler inspection manipulator for Torness Power Station

International Nuclear Information System (INIS)

Carrey, R.T.A.; Yule, I.Y.; Sibson, S.; Playle, M.J.

1996-01-01

The Advanced Gas-cooled Reactors at Torness and Heysham 2 are provided with dedicated access for remote inspection equipment. These in-service inspection (ISI) accesses comprise 12 penetrations above the core for inspection of the above core area and boilers, 12 below core penetrations for inspection of the lower boiler area and access through any of the 8 gas circulator penetrations for inspection of the sub-diagrid area. This paper describes a manipulator which will access the reactor from above the core via any of the 8 peripheral penetrations. (UK)

18. TA-2 Water Boiler Reactor Decommissioning Project

International Nuclear Information System (INIS)

Durbin, M.E.; Montoya, G.M.

1991-06-01

This final report addresses the Phase 2 decommissioning of the Water Boiler Reactor, biological shield, other components within the biological shield, and piping pits in the floor of the reactor building. External structures and underground piping associated with the gaseous effluent (stack) line from Technical Area 2 (TA-2) Water Boiler Reactor were removed in 1985--1986 as Phase 1 of reactor decommissioning. The cost of Phase 2 was approximately \$623K. The decommissioning operation produced 173 m 3 of low-level solid radioactive waste and 35 m 3 of mixed waste. 15 refs., 25 figs., 3 tabs

19. NOx Control Options and Integration for US Coal Fired Boilers

Energy Technology Data Exchange (ETDEWEB)

Mike Bockelie; Kevin Davis; Temi Linjewile; Connie Senior; Eric Eddings; Kevin Whitty; Larry Baxter; Calvin Bartholomew; William Hecker; Stan Harding; Robert Hurt

2003-12-31

This is the fourteenth Quarterly Technical Report for DOE Cooperative Agreement No: DEFC26-00NT40753. The goal of the project is to develop cost effective analysis tools and techniques for demonstrating and evaluating low NOx control strategies and their possible impact on boiler performance for boilers firing US coals. The Electric Power Research Institute (EPRI) is providing co-funding for this program. Using the initial CFD baseline modeling of the Gavin Station and the plant corrosion maps, six boiler locations for the corrosion probes were identified and access ports have been installed. Preliminary corrosion data obtained appear consistent and believable. In situ, spectroscopic experiments at BYU reported in part last quarter were completed. New reactor tubes have been made for BYU's CCR that allow for testing smaller amounts of catalyst and thus increasing space velocity; monolith catalysts have been cut and a small reactor that can accommodate these pieces for testing is in its final stages of construction. A poisoning study on Ca-poisoned catalysts was begun this quarter. A possible site for a biomass co-firing test of the slipstream reactor was visited this quarter. The slipstream reactor at Rockport required repair and refurbishment, and will be re-started in the next quarter. This report describes the final results of an experimental project at Brown University on the fundamentals of ammonia / fly ash interactions with relevance to the operation of advanced NOx control technologies such as selective catalytic reduction. The Brown task focused on the measurement of ammonia adsorption isotherms on commercial fly ash samples subjected to a variety of treatments and on the chemistry of dry and semi-dry ammonia removal processes.

20. 46 CFR 56.50-30 - Boiler feed piping.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Boiler feed piping. 56.50-30 Section 56.50-30 Shipping... APPURTENANCES Design Requirements Pertaining to Specific Systems § 56.50-30 Boiler feed piping. (a) General... least two separate means of supplying feed water for the boilers. All feed pumps shall be fitted with...

1. Biomass boiler conversion potential in the eastern United States

Science.gov (United States)

Charles D. Ray; Li Ma; Thomas Wilson; Daniel Wilson; Lew McCreery; Janice K. Wiedenbeck

2013-01-01

The U.S. is the world's leading consumer of primary energy. A large fraction of this energy is used in boiler installations to generate steam and hot water for heating applications. It is estimated there are total 163,000 industrial and commercial boilers in use in the United States of all sizes. This paper characterizes the commercial and industrial boilers in...

2. New materials for boilers in USC power plants

International Nuclear Information System (INIS)

Hong, Sung Ho; Hong, Seok Joo

2003-01-01

The efficiency of boiler in fossil power plants is a strong function of steam temperature and pressure. Thus, the main technology of increasing boiler efficiency is the development of stronger high temperature materials, capable of operating under high stresses at ever increasing temperature. This paper will presents the new material relating to boiler of USC power plant

3. 46 CFR 176.812 - Pressure vessels and boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 7 2010-10-01 2010-10-01 false Pressure vessels and boilers. 176.812 Section 176.812... TONS) INSPECTION AND CERTIFICATION Material Inspections § 176.812 Pressure vessels and boilers. (a.... (b) Periodic inspection and testing requirements for boilers are contained in § 61.05 in subchapter F...

4. 46 CFR 115.812 - Pressure vessels and boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Pressure vessels and boilers. 115.812 Section 115.812... CERTIFICATION Material Inspections § 115.812 Pressure vessels and boilers. (a) Pressure vessels must be tested... testing requirements for boilers are contained in § 61.05 in subchapter F of this chapter. [CGD 85-080, 61...

5. 46 CFR 109.205 - Inspection of boilers and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Inspection of boilers and machinery. 109.205 Section 109... OPERATIONS Tests, Drills, and Inspections § 109.205 Inspection of boilers and machinery. The chief engineer or engineer in charge, before he assumes charge of the boilers and machinery of a unit shall inspect...

6. 40 CFR 63.988 - Incinerators, boilers, and process heaters.

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 10 2010-07-01 2010-07-01 false Incinerators, boilers, and process... Routing to a Fuel Gas System or a Process § 63.988 Incinerators, boilers, and process heaters. (a) Equipment and operating requirements. (1) Owners or operators using incinerators, boilers, or process...

7. Aspects of new material application for boilers construction

International Nuclear Information System (INIS)

Czerniawski, R.

1996-01-01

Review of steel types commonly used for energetic boilers construction has been done. The worldwide trends in new materials application for improvement of boilers quality have been discussed. The mechanical properties of boiler construction steels have been shown and compared. 3 refs, 5 figs, 1 tab

8. Lower price for solar boilers must improve market penetration

International Nuclear Information System (INIS)

Koevoet, J.B.J.

1999-01-01

The Dutch government aims at 1.7 PJ thermal energy for the year 2007 to be supplied by solar water heaters. For that target the number of installed solar boilers must increase seven times the number of installed solar boilers in 1998. This can be stimulated by a considerable reduction of the market price for such boilers

9. 10 CFR 431.82 - Definitions concerning commercial packaged boilers.

Science.gov (United States)

2010-01-01

... gases. Manufacturer of a commercial packaged boiler means any person who manufactures, produces... 10 Energy 3 2010-01-01 2010-01-01 false Definitions concerning commercial packaged boilers. 431.82... COMMERCIAL AND INDUSTRIAL EQUIPMENT Commercial Packaged Boilers § 431.82 Definitions concerning commercial...

10. 40 CFR 761.71 - High efficiency boilers.

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 30 2010-07-01 2010-07-01 false High efficiency boilers. 761.71... PROHIBITIONS Storage and Disposal § 761.71 High efficiency boilers. (a) To burn mineral oil dielectric fluid containing a PCB concentration of ≥50 ppm, but boiler shall comply with the following...

11. 49 CFR 230.36 - Hydrostatic testing of boilers.

Science.gov (United States)

2010-10-01

... 49 Transportation 4 2010-10-01 2010-10-01 false Hydrostatic testing of boilers. 230.36 Section 230... Appurtenances Pressure Testing of Boilers § 230.36 Hydrostatic testing of boilers. (a) Time of test. The... to any hydrostatic pressure. Hydrostatic testing required by these rules shall be conducted at 25...

12. Optimization of Boiler Heat Load in Water-Heating Boiler-House

Directory of Open Access Journals (Sweden)

B. A. Bayrashevsky

2009-01-01

Full Text Available An analytical method for optimization of water-heating boiler loads has been developed on the basis of approximated semi-empirical dependences pertaining to changes of boiler gross efficiency due to its load. A complex (∂tух/∂ξΔξ is determined on the basis of a systematic analysis (monitoring of experimental data and the Y. P. Pecker’s formula for calculation of balance losses q2. This complex makes it possible to set a corresponding correction to a standard value of the boiler gross efficiency due to contamination of heating surfaces.Software means for optimization of water-heating boilers has been developed and it is recommended to be applied under operational conditions.

13. Selecting Actuator Configuration for a Benson Boiler

DEFF Research Database (Denmark)

Kragelund, Martin Nygaard; Leth, John-Josef; Wisniewski, Rafal

2009-01-01

with particular focus on a boiler in a power plant operated by DONG Energy - a Danish energy supplier. The problem has been reformulated using mathematic notions from economics. The selection of actuator configuration has been limited to the fuel system which in the considered plant consists of three different...

14. Model boiler studies on deposition and corrosion

International Nuclear Information System (INIS)

Balakrishnan, P.V.; McVey, E.G.

1977-09-01

Deposit formation was studied in a model boiler, with sea-water injections to simulate the in-leakage which could occur from sea-water cooled condensers. When All Volatile Treatment (AVT) was used for chemistry control the deposits consisted of the sea-water salts and corrosion products. With sodium phosphate added to the boiler water, the deposits also contained the phosphates derived from the sea-water salts. The deposits were formed in layers of differing compositions. There was no significant corrosion of the Fe-Ni-Cr alloy boiler tube under deposits, either on the open area of the tube or in crevices. However, carbon steel that formed a crevice around the tube was corroded severely when the boiler water did not contain phosphate. The observed corrosion of carbon steel was caused by the presence of acidic, highly concentrated chloride solution produced from the sea-water within the crevice. Results of theoretical calculations of the composition of the concentrated solution are presented. (author)

15. Environmental control during steam boiler washing

Energy Technology Data Exchange (ETDEWEB)

Guimaraes, Marcio A.B.; Abreu Pereira, Vera L. de [Companhia Petroquimica do Nordeste (COPENE), Camacari, BA (Brazil). Div. de Engenharia Ambiental; Ringler, Ulrich E.S. [PROMON Engenharia Ltda., Salvador, BA (Brazil)

1993-12-31

The washing and chemical cleaning of boilers, activities of a high polluting potential, are responsible for the generation of wastewater of high contents of heavy metals, suspended solids and chemical oxygen demand (COD). This paper describes the actions carried out by COPENE - Petroquimica do Nordeste S/A - in order to reduce this problem. (author). 10 refs., 3 figs., 2 tabs.

16. The investigation of the locomotive boiler material

International Nuclear Information System (INIS)

Tucholski, Z.; Wasiak, J.; Bilous, W.; Hajewska, E.

2006-01-01

In the paper, the history of narrow-gauge railway system is described. The other information about the steam locomotive construction, as well as the technical regulations of its construction and exploitation are also done. The results of the studies of the locomotive boiler material are presented. (authors)

17. Coal reburning technology for cyclone boilers

International Nuclear Information System (INIS)

Yagiela, A.S.; Maringo, G.J.; Newell, R.J.; Farzan, H.

1990-01-01

Babcock and Wilcox has obtained encouraging results from engineering feasibility and pilot-scale proof-of-concept studies of coal reburning for cyclone boiler NO x control. Accordingly, B and W completed negotiations for a clean coal cooperative agreement with the Department of Energy to demonstrate coal reburning technology for cyclone boilers. The host site for the demonstration is the Wisconsin Power and Light (WP and L) Company's 100MWe Nelson Dewey Station. Reburning involves the injection of a supplemental fuel (natural gas, oil, or coal) into the main furnace to produce locally reducing stoichiometric conditions which convert the NO x produced therein to molecular nitrogen, thereby reducing overall NO x emissions. There are currently no commercially-demonstrated combustion modification techniques for cyclone boilers which reduce NO x emissions. The emerging reburning technology offers cyclone boiler operators a promising alternative to expensive flue gas cleanup techniques for NO x emission reduction. This paper reviews baseline testing results at the Nelson Dewey Station and pilot-scale results simulating Nelson Dewey operation using pulverized coal (PC) as the reburning fuel. Outcomes of the model studies as well as the full-scale demonstration preliminary design are discussed

18. Environmental control during steam boiler washing

Energy Technology Data Exchange (ETDEWEB)

Guimaraes, Marcio A.B.; Abreu Pereira, Vera L. de [Companhia Petroquimica do Nordeste (COPENE), Camacari, BA (Brazil). Div. de Engenharia Ambiental; Ringler, Ulrich E.S. [PROMON Engenharia Ltda., Salvador, BA (Brazil)

1994-12-31

The washing and chemical cleaning of boilers, activities of a high polluting potential, are responsible for the generation of wastewater of high contents of heavy metals, suspended solids and chemical oxygen demand (COD). This paper describes the actions carried out by COPENE - Petroquimica do Nordeste S/A - in order to reduce this problem. (author). 10 refs., 3 figs., 2 tabs.

19. Decoupled numerical simulation of a solid fuel fired retort boiler

International Nuclear Information System (INIS)

Ryfa, Arkadiusz; Buczynski, Rafal; Chabinski, Michal; Szlek, Andrzej; Bialecki, Ryszard A.

2014-01-01

The paper deals with numerical simulation of the retort boiler fired with solid fuel. Such constructions are very popular for heating systems and their development is mostly based on the designer experience. The simulations have been done in ANSYS/Fluent package and involved two numerical models. The former deals with a fixed-bed combustion of the solid fuel and free-board gas combustion. Solid fuel combustion is based on the coal kinetic parameters. This model encompasses chemical reactions, radiative heat transfer and turbulence. Coal properties have been defined with user defined functions. The latter model describes flow of water inside a water jacked that surrounds the combustion chamber and flue gas ducts. The novelty of the proposed approach is separating of the combustion simulation from the water flow. Such approach allows for reducing the number of degrees of freedom and thus lowering the necessary numerical effort. Decoupling combustion from water flow requires defining interface boundary condition. As this boundary condition is unknown it is adjusted iteratively. The results of the numerical simulation have been successfully validated against measurement data. - Highlights: • New decoupled modelling of small scale boiler is proposed. • Fixed-bed combustion model based on kinetic parameters is introduced. • Decoupling reduced the complexity of the model and computational time. • Simple and computationally inexpensive coupling algorithm is proposed. • Model is successfully validated against measurements

20. FY 1999 report on the potential survey of the environmentally friendly type coal utilization system. Potential survey of the spread of high efficiency coal boiler; 1999 nendo kankyo chowa gata sekitan system kanosei chosa. Kokoritsu sekitan boira fukyu kanosei chosa

Energy Technology Data Exchange (ETDEWEB)

NONE

2000-03-01

For the purpose of reducing the coal consumption amount and reducing the emission amount of environmental pollutants, study of small stoker boilers in China was made in terms of sampling of the data on changes in boiler efficiency caused by combustion conditions and how to improve efficiency. As objects of survey, one boiler use plant in Beijing city and two in Taiyuan city, Shanxi province, were selected to make site survey on the state of installation and operational management of coal boiler. As a result of the actual measurement of boiler efficiency at the plants, the boiler efficiency was the maximum, about 76%, in Beijing city and the minimum, about 51%, in Taiyuan city. In China, the number of boiler with the Beijing city level was extremely small, and most of the boilers were the same as the Taiyuan city level. As a result of studying how to improve efficiency based on the survey results, the following were cited as the main measures for improvement: selection of coal by boiler type and supply of the secondary air, strengthening of the combustion management by controlling furnace pressure and air amount, etc. For the selection of coal, it is necessary to set up a system to be supported by the whole country or the whole department. (NEDO)

1. On-line monitoring system for utility boiler diagnostics

International Nuclear Information System (INIS)

Radovanovic, P.M.; Afgan, N.H.; Caralho, M.G.

1997-01-01

The paper deals with the new developed modular type Monitoring System for Utility Boiler Diagnostics. Each module is intended to assess the specific process and can be used as a stand alone application. Four modules are developed, namely: LTC - module for the on-line monitoring of parameters related to the life-time consumption of selected boiler components; TRD - module for the tube rupture detection by the position and working fluid Ieakage quantity; FAM - module for the boiler surfaces fouling (slagging) assessment and FLAP - module for visualization of the boiler furnace flame position. All four modules are tested on respective pilot plants built oil the 200 and 300 MWe utility boilers. Monitoring System is commercially available and can be realized in any combination of its modules depending on demands induced by the operational problems of specific boiler. Further development of Monitoring System is performed in accordance with the respective EU project on development of Boiler Expert System. (Author)

2. The behavior of ash species in suspension fired biomass boilers

DEFF Research Database (Denmark)

Jensen, Peter Arendt

While fluid bed and grate fired boilers initially was the choice of boilers used for power production from both wood and herbaceous biomass, in recent years suspension fired boilers have been increasingly used for biomass based power production. In Denmark several large pulverized fuel boilers have...... been converted from coal to biomass combustion in the last 15 years. This have included co-firing of coal and straw, up to 100% firing of wood or straw andthe use of coal ash as an additive to remedy problems with wood firing. In parallel to the commercialization of the pulverized biomass firing...... technology a long range of research studies have been conducted, to improve our understanding of the influence and behavior of biomass ash species in suspension fired boilers. The fuel ash plays a key role with respect tooptimal boiler operation and influences phenomena’s as boiler chamber deposit formation...

3. Main boiler feed pump for fast breeder test reactor. Failure analysis and remedial measures

International Nuclear Information System (INIS)

Iyer, M.A.K.; Chande, S.K.; Raghuvir, A.D.; Baskar, S.; Kale, R.D.

1994-01-01

A small capacity ten stage 670 kw feed water pump is used for supplying feed water at a temperature of 190 deg C to a once through steam generator in the Fast Breeder Test Reactor at Kalpakkam. During preparatory heating up stage to commission the steam generator the pump suffered a severe loss of suction which resulted in failure of hydrostatic journal bearings and extensive damage to pump internals. This paper discusses the detailed mechanism of loss of suction, details of damage to the pump and various modifications carried out to prevent recurrence of the problem. (author). 4 refs., 3 figs., 2 tabs

4. Oxy-Combustion Boiler Material Development

Energy Technology Data Exchange (ETDEWEB)

Gagliano, Michael; Seltzer, Andrew; Agarwal, Hans; Robertson, Archie; Wang, Lun

2012-01-31

Under U.S. Department of Energy Cooperative Agreement No. DE-NT0005262 Foster Wheeler North America Corp conducted a laboratory test program to determine the effect of oxy-combustion on boiler tube corrosion. In this program, CFD modeling was used to predict the gas compositions that will exist throughout and along the walls of air-fired and oxy-fired boilers operating with low to high sulfur coals. Test coupons of boiler tube materials were coated with deposits representative of those coals and exposed to the CFD predicted flue gases for up to 1000 hours. The tests were conducted in electric tube furnaces using oxy-combustion and air-fired flue gases synthesized from pressurized cylinders. Following exposure, the test coupons were evaluated to determine the total metal wastage experienced under air and oxy-combustions conditions and materials recommendations were made. Similar to air-fired operation, oxy-combustion corrosion rates were found to vary with the boiler material, test temperature, deposit composition, and gas composition. Despite this, comparison of air-fired and oxy-fired corrosion rates showed that oxy-firing rates were, for the most part, similar to, if not lower than those of air-firing; this finding applied to the seven furnace waterwall materials (wrought and weld overlay) and the ten superheater/reheater materials (wrought and weld overlay) that were tested. The results of the laboratory oxy-combustion tests, which are based on a maximum bulk flue gas SO2 level of 3200 ppmv (wet) / 4050 ppmv (dry), suggest that, from a corrosion standpoint, the materials used in conventional subcritical and supercritical, air-fired boilers should also be suitable for oxy-combustion retrofits. Although the laboratory test results are encouraging, they are only the first step of a material evaluation process and it is recommended that follow-on corrosion tests be conducted in coal-fired boilers operating under oxy-combustion to provide longer term (one to two year

5. Oxy-Combustion Boiler Material Development

Energy Technology Data Exchange (ETDEWEB)

Michael Gagliano; Andrew Seltzer; Hans Agarwal; Archie Robertson; Lun Wang

2012-01-31

Under U.S. Department of Energy Cooperative Agreement No. DE-NT0005262 Foster Wheeler North America Corp conducted a laboratory test program to determine the effect of oxy-combustion on boiler tube corrosion. In this program, CFD modeling was used to predict the gas compositions that will exist throughout and along the walls of air-fired and oxy-fired boilers operating with low to high sulfur coals. Test coupons of boiler tube materials were coated with deposits representative of those coals and exposed to the CFD predicted flue gases for up to 1000 hours. The tests were conducted in electric tube furnaces using oxy-combustion and air-fired flue gases synthesized from pressurized cylinders. Following exposure, the test coupons were evaluated to determine the total metal wastage experienced under air and oxy-combustions conditions and materials recommendations were made. Similar to air-fired operation, oxy-combustion corrosion rates were found to vary with the boiler material, test temperature, deposit composition, and gas composition. Despite this, comparison of air-fired and oxy-fired corrosion rates showed that oxy-firing rates were, for the most part, similar to, if not lower than those of air-firing; this finding applied to the seven furnace waterwall materials (wrought and weld overlay) and the ten superheater/reheater materials (wrought and weld overlay) that were tested. The results of the laboratory oxy-combustion tests, which are based on a maximum bulk flue gas SO{sub 2} level of 3200 ppmv (wet) / 4050 ppmv (dry), suggest that, from a corrosion standpoint, the materials used in conventional subcritical and supercritical, air-fired boilers should also be suitable for oxy-combustion retrofits. Although the laboratory test results are encouraging, they are only the first step of a material evaluation process and it is recommended that follow-on corrosion tests be conducted in coal-fired boilers operating under oxy-combustion to provide longer term (one to

6. MEMS-Based Boiler Operation from Low Temperature Heat Transfer and Thermal Scavenging

Directory of Open Access Journals (Sweden)

Leland Weiss

2012-04-01

Full Text Available Increasing world-wide energy use and growing population growth presents a critical need for enhanced energy efficiency and sustainability. One method to address this issue is via waste heat scavenging. In this approach, thermal energy that is normally expelled to the environment is transferred to a secondary device to produce useful power output. This paper investigates a novel MEMS-based boiler designed to operate as part of a small-scale energy scavenging system. For the first time, fabrication and operation of the boiler is presented. Boiler operation is based on capillary action that drives working fluid from surrounding reservoirs across a heated surface. Pressure is generated as working fluid transitions from liquid to vapor in an integrated steamdome. In a full system application, the steam can be made available to other MEMS-based devices to drive final power output. Capillary channels are formed from silicon substrates with 100 µm widths. Varying depths are studied that range from 57 to 170 µm. Operation of the boiler shows increasing flow-rates with increasing capillary channel depths. Maximum fluid mass transfer rates are 12.26 mg/s from 170 µm channels, an increase of 28% over 57 µm channel devices. Maximum pressures achieved during operation are 229 Pa.

7. Maximising safety in the boiler house.

Science.gov (United States)

Derry, Carr

2013-03-01

Last month's HEJ featured an article, the second in our new series of guidance pieces aimed principally at Technician-level engineers, highlighting some of the key steps that boiler operators can take to maximise system performance and efficiency, and thus reduce running both costs and carbon footprint. In the third such article, Derry Carr, C.Env, I.Eng, BSc (Hons), M.I.Plant.E., M.S.O.E., technical manager & group gas manager at Dalkia, who is vice-chairman of the Combustion Engineering Association, examines the key regulatory and safety obligations for hospital energy managers and boiler technicians, a number of which have seen changes in recent years with revision to guidance and other documentation.

8. Control Properties of Bottom Fired Marine Boilers

DEFF Research Database (Denmark)

Solberg, Brian; Andersen, Palle; Karstensen, Claus M. S.

2005-01-01

This paper focuses on model analysis of a dynamic model of a bottom fired one-pass smoke tube boiler. Linearised versions of the model are analysed to determine how gain, time constants and right half plane zeros (caused by the shrink-and-swell phenomenon) depend on the steam flow load. Furthermore...... the interactions in the system are inspected to analyse potential benefit from using a multivariable control strategy in favour of the current strategy based on single loop theory. An analysis of the nonlinear model is carried out to further determine the nonlinear characteristics of the boiler system...... and to verify whether nonlinear control is needed. Finally a controller based on single loop theory is used to analyse if input constraints become active when rejecting transient behaviour from the disturbance steam flow. The model analysis shows large variations in system gains at steady state as function...

9. Recovery boiler model; Soodakattilan kehitystyoe III

Energy Technology Data Exchange (ETDEWEB)

Janka, K.; Ylitalo, M.; Sundstroem, K.; Helke, R.; Heinola, M. [Kvaerner Pulping Oy, Tampere (Finland)

1997-10-01

The recovery boiler model was further tested and developed. At this moment the model includes submodels for: droplet drying, pyrolysis, char burning, gas burning and for droplet trajectory. During 1996 the formation of CH{sub 4} during pyrolysis and release of sulfur was included to the model. Further the formation of NO from fuel nitrogen and formation of thermal- NO were included to the model using Arrhenius type reaction rate equations. The calculated results are realistic and the model is used as a tool to find out methods to increase the efficiency and availability and decrease the emissions. Analysing the results of the earlier field study of 8 boilers showed that the furnace heat load, fuming rate, find the black liquor composition have influence on the enrichment of the potassium to the fly ash. (orig.)

10. Biomass Cofiring in Coal-Fired Boilers

Energy Technology Data Exchange (ETDEWEB)

2004-06-01

Cofiring biomass-for example, forestry residues such as wood chips-with coal in existing boilers is one of the easiest biomass technologies to implement in a federal facility. The current practice is to substitute biomass for up to 20% of the coal in the boiler. Cofiring has many benefits: it helps to reduce fuel costs as well as the use of landfills, and it curbs emissions of sulfur oxide, nitrogen oxide, and the greenhouse gases associated with burning fossil fuels. This Federal Technology Alert was prepared by the Department of Energy's Federal Energy Management Program to give federal facility managers the information they need to decide whether they should pursue biomass cofiring at their facilities.

11. Soot blowing methods and soot steam consumption in Swedish recovery boilers; Sotningsmetoder och sotaangfoerbrukning i svenska sodapannor

Energy Technology Data Exchange (ETDEWEB)

Svedin, Kristoffer; Wallin, Erik; Ahlroth, Mikael

2008-09-15

The aim with the report was to put together a description of the current state of the sootblowing systems at Swedish recovery boilers, and to explain differences in cleanability and sootblowing efficiency. In chapter 4 a summary of new techniques and alternative soot blowing methods is found. The report is intended for persons working in the pulp industry. To facilitate the benchmarking the recovery boilers have been divided into two groups. Group A comprises recovery boilers which only have one stop per year and the remaining recovery boilers with more than one stop are classified into group B. The following conclusions, based on the recovery boiler design specifications, are of importance to achieve high boiler availability: Low furnace load; High recovery boiler, wide furnace bottom area; Modern air ports; Small or no correlation between cross pitch division in heat surfaces and cleanability could be seen. The expectation was to identify such a relation. However there are doubts on the correctness in reported data. The amount of chlorine and potassium is assumed to affect the cleanability for a few recovery boilers, but for the majority the amounts are low and most likely do not impact the operation. Because of the large impact of the recovery boilers design data (furnace area, load etc.) on the sootblowing, it has been hard to identify the relation cleanability contra sootblowing system. The relations that could be seen are: No distinction between normally designed nozzles and 'high efficiency' nozzles could be identified. The operational conditions for the different models differ a lot and the effect of nozzle type could not be distinguished. Only a minority of the soot blowing sequences are known from the study. In the recovery boilers with problematic areas improvements can be made in the soot blowing sequence. Four recovery boilers are using intelligent soot blowing of some kind. Two of these boilers have low availability and the other two have

12. Stationary Engineers Apprenticeship. Related Training Modules. 12.1-12.9. Boilers.

Science.gov (United States)

Lane Community Coll., Eugene, OR.

This learning module, one in a series of 20 related training modules for apprentice stationary engineers, deals with boilers. Addressed in the individual instructional packages included in the module are the following topics: firetube and watertube boilers; boiler construction; procedures for operating and cleaning boilers; and boiler fittings,…

13. 46 CFR 52.25-7 - Electric boilers (modifies PEB-1 through PEB-19).

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Electric boilers (modifies PEB-1 through PEB-19). 52.25... ENGINEERING POWER BOILERS Other Boiler Types § 52.25-7 Electric boilers (modifies PEB-1 through PEB-19). Electric boilers required to comply with this part must meet the applicable provisions in this part and the...

14. Circulating fluidized bed boilers design and operations

CERN Document Server

Basu, Prabir

1991-01-01

This book provides practicing engineers and students with insight into the design and operation of circulating fluidized bed (CFB) boilers. Through a combination of theoretical concepts and practical experience, this book gives the reader a basic understanding of the many aspects of this subject.Important environmental considerations, including solid waste disposal and predicted emissions, are addressed individually in separate chapters. This book places an emphasis on combustion, hydrodynamics, heat transfer, and material issues, and illustrates these concepts with numerous examples of pres

15. Chromate dermatitis from a boiler lining.

Science.gov (United States)

Rycroft, R J; Calnan, C D

1977-08-01

Chromate dermatitis is described in a mechanical fitter working inside boiler combustion chambers. A source of hexavalent chromate is traced to the action of the heat and alkaline fuel ash on trivalent chrome ore in parts of the refractory lining. Removal of the patient from this contact has resulted in almost complete clearing of his dermatitis, without any relapse, during a 9-month follow-up period.

16. Husk energy for boilers and furnaces

Energy Technology Data Exchange (ETDEWEB)

Deven, M.

1985-10-01

In view of the technical feasibility and economic viability, industries located in rice, coconut, and cotton growing areas, can easily switch over from oil/coal fired furnace/boilers to husk fired ones and thereby effect fuel economy. The banks and financial institutions will readily agree to provide finance as per directions of the governments and in some cases they also offer subsidy for development and utilization of energy saving devices.

17. Particulate emission abatement for Krakow boiler houses

Energy Technology Data Exchange (ETDEWEB)

Wysk, R.

1995-12-31

Among the many strategies for improving air quality in Krakow, one possible method is to adapt new and improved emission control technology. This project focuses on such a strategy. In order to reduce dust emissions from coal-fueled boilers, a new device called a Core Separator has been introduced in several boiler house applications. This advanced technology has been successfully demonstrated in Poland and several commercial units are now in operation. Particulate emissions from the Core Separator are typically 3 to 5 times lower than those from the best cyclone collectors. It can easily meet the new standard for dust emissions which will be in effect in Poland after 1997. The Core Separator is a completely inertial collector and is based on a unique recirculation method. It can effectively remove dust particles below 10 microns in diameter, the so-called PM-10 emissions. Its performance approaches that of fabric filters, but without the attendant cost and maintenance. It is well-suited to the industrial size boilers located in Krakow. Core Separators are now being marketed and sold by EcoInstal, one of the leading environmental firms in Poland, through a cooperative agreement with LSR Technologies.

18. Boiler systems for nuclear powered reactors

International Nuclear Information System (INIS)

Cook, R.K.; George, B.V.

1979-01-01

A power generating plant which comprises a heat source, at least one main steam turbine and at least one main boiler heated by heat from the heat source and providing the steam to drive the turbine, comprises additionally at least one further steam turbine, smaller than the main turbine, and at least one further boiler, of lower capacity than the main boiler, and heated from the same heat source and providing steam for the further turbine. Particularly advantageous in nuclear power stations, where the heat source is a nuclear reactor, the invention enables peak loads, above the normal continuous rating of the main generators driven by the main turbines, to be met by the further turbine(s) and one or more further generators driven thereby. This enables the main turbines to be freed from the thermal stresses of rapid load changes, which stresses are more easily accommodated by the smaller and thus more tolerant further turbine(s). Thus auxiliary diesel-driven or other independent power plant may be made partly or wholly unnecessary. Further, low-load running which would be inefficient if achieved by means of the main turbine(s), can be more efficiently effected by shutting them down and using the smaller further turbine(s) instead. These latter may also be used to provide independent power for servicing the generating plant during normal operation or during emergency or other shutdown, and in this latter case may also serve as a heat sink for the shutdown reactor

19. BOILER MATERIALS FOR ULTRASUPERCRITICAL COAL POWER PLANTS

Energy Technology Data Exchange (ETDEWEB)

R. Viswanathan; K. Coleman; R.W. Swindeman; J. Sarver; J. Blough; W. Mohn; M. Borden; S. Goodstine; I. Perrin

2003-10-20

The principal objective of this project is to develop materials technology for use in ultrasupercritical (USC) plant boilers capable of operating with 760 C (1400 F), 35 MPa (5000 psi) steam. This project has established a government/industry consortium to undertake a five-year effort to evaluate and develop of advanced materials that allow the use of advanced steam cycles in coal-based power plants. These advanced cycles, with steam temperatures up to 760 C, will increase the efficiency of coal-fired boilers from an average of 35% efficiency (current domestic fleet) to 47% (HHV). This efficiency increase will enable coal-fired power plants to generate electricity at competitive rates (irrespective of fuel costs) while reducing CO{sub 2} and other fuel-related emissions by as much as 29%. Success in achieving these objectives will support a number of broader goals. First, from a national prospective, the program will identify advanced materials that will make it possible to maintain a cost-competitive, environmentally acceptable coal-based electric generation option. High sulfur coals will specifically benefit in this respect by having these advanced materials evaluated in high-sulfur coal firing conditions and from the significant reductions in waste generation inherent in the increased operational efficiency. Second, from a national prospective, the results of this program will enable domestic boiler manufacturers to successfully compete in world markets for building high-efficiency coal-fired power plants.

20. Evaluation of dense-phase ultrafine coal (DUC) as a fuel alternative for oil- and gas-designed boilers and heaters. Final report

Energy Technology Data Exchange (ETDEWEB)

1986-12-01

Utility and industrial firms currently using oil- and gas-fired boilers have an interest in substitution of coal for oil and gas as the primary boiler fuel. This interest stems from coal`s two main advantages over oil and gas-lower cost and security of supply. Recent efforts in the area of coal conversion have been directed to converting oil- and gas- fired boilers which were originally designed for coal-firing or were designed with some coal-firing capability. Boilers designed exclusively for oil- or gas-firing have not been considered viable candidates for coal conversion because they generally require a significant capacity derating and extensive and costly modifications. As a result, conversion of boilers in this class to coal-firing has generally been considered unattractive. Renewed interest in the prospects for converting boilers designed exclusively for oil- and gas-firing to coal firing has centered around the concept of using ``ultra fine`` coal as opposed to ``conventional grind`` pulverized coal. The main distinction being the finer particle size to which the former is ground. This fuel type may have characteristics which ameliorate many of the boiler problems normally associated with pulverized coal-firing. The overall concept for ultrafine coal utilization is based on a regional large preparation plant with distribution of a ready to fire fuel directly to many small users. This differs from normal practice in which final coal sizing is performed in pulverizers at the user`s site.

1. Field Test of Boiler Primary Loop Temperature Controller

Energy Technology Data Exchange (ETDEWEB)

Glanville, P. [Partnership for Advanced Residential Retrofit, Des Plaines, IL (United States); Rowley, P. [Partnership for Advanced Residential Retrofit, Des Plaines, IL (United States); Schroeder, D. [Partnership for Advanced Residential Retrofit, Des Plaines, IL (United States); Brand, L. [Partnership for Advanced Residential Retrofit, Des Plaines, IL (United States)

2014-09-01

Beyond these initial system efficiency upgrades are an emerging class of Advanced Load Monitoring (ALM) aftermarket controllers that dynamically respond to the boiler load, with claims of 10% to 30% of fuel savings over a heating season. For hydronic boilers specifically, these devices perform load monitoring, with continuous measurement of supply and, in some cases, return water temperatures. Energy savings from these ALM controllers are derived from dynamic management of the boiler differential, where a microprocessor with memory of past boiler cycles prevents the boiler from firing for a period of time, to limit cycling losses and inefficient operation during perceived low load conditions. These differ from OTR controllers, which vary boiler setpoint temperatures with ambient conditions while maintaining a fixed differential.

2. Modelling, simulating and optimizing boiler heating surfaces and evaporator circuits

DEFF Research Database (Denmark)

Sørensen, K.; Condra, T.; Houbak, Niels

2003-01-01

A model for optimizing the dynamic performance of boiler have been developed. Design variables related to the size of the boiler and its dynamic performance have been defined. The object function to be optimized takes the weight of the boiler and its dynamic capability into account. As constraints...... for the optimization a dynamic model for the boiler is applied. Furthermore a function for the value of the dynamic performance is included in the model. The dynamic models for simulating boiler performance consists of a model for the flue gas side, a model for the evaporator circuit and a model for the drum....... The dynamic model has been developed for the purpose of determining boiler material temperatures and heat transfer from the flue gas side to the water-/steam side in order to simulate the circulation in the evaporator circuit and hereby the water level fluctuations in the drum. The dynamic model has been...

3. Life extension of boilers using weld overlay protection

Energy Technology Data Exchange (ETDEWEB)

Lai, G.; Hulsizer, P. [Welding Services Inc., Norcross, GA (United States); Brooks, R. [Welding Services Inc., Welding Services Europe, Spijkenisse (Netherlands)

1998-12-31

The presentation describes the status of modern weld overlay technology for refurbishment, upgrading and life extension of boilers. The approaches to life extension of boilers include field overlay application, shop-fabricated panels for replacement of the worn, corroded waterwall and shop-fabricated overlay tubing for replacement of individual tubes in superheaters, generating banks and other areas. The characteristics of weld overlay products are briefly described. Also discussed are successful applications of various corrosion-resistant overlays for life extension of boiler tubes in waste-to-energy boilers, coal-fired boilers and chemical recovery boilers. Types of corrosion and selection of weld overlay alloys in these systems are also discussed. (orig.) 14 refs.

4. Life extension of boilers using weld overlay protection

Energy Technology Data Exchange (ETDEWEB)

Lai, G; Hulsizer, P [Welding Services Inc., Norcross, GA (United States); Brooks, R [Welding Services Inc., Welding Services Europe, Spijkenisse (Netherlands)

1999-12-31

The presentation describes the status of modern weld overlay technology for refurbishment, upgrading and life extension of boilers. The approaches to life extension of boilers include field overlay application, shop-fabricated panels for replacement of the worn, corroded waterwall and shop-fabricated overlay tubing for replacement of individual tubes in superheaters, generating banks and other areas. The characteristics of weld overlay products are briefly described. Also discussed are successful applications of various corrosion-resistant overlays for life extension of boiler tubes in waste-to-energy boilers, coal-fired boilers and chemical recovery boilers. Types of corrosion and selection of weld overlay alloys in these systems are also discussed. (orig.) 14 refs.

5. Behavioral study solar boilers 1994. Summary. Part 2 (households)

International Nuclear Information System (INIS)

Visser, J.M.

1995-04-01

The aim of the Dutch national solar boiler campaign of NOVEM and Holland Solar is to realize the installation of 300,000 solar boilers in the Netherlands in the year 2010. In 1995 10,000 boilers were installed. More knowledge of the decision making process and the backgrounds and motives of (potential) buyers is required. From September 1994 to March 1995 a survey has been carried out of the decision making processes in households and housing corporations. The most important results, conclusions and recommendations of the survey are summarized in this report. The parameters that can influence the decision whether to purchase a solar boiler or not are knowledge about the solar boiler, the attitude towards the solar boiler and towards the use of energy and the environment, risk perception, social aspects, information retrieval behavior, constraints, and socio-economic aspects. 44 tabs

6. NOx PREDICTION FOR FBC BOILERS USING EMPIRICAL MODELS

Directory of Open Access Journals (Sweden)

Jiří Štefanica

2014-02-01

Full Text Available Reliable prediction of NOx emissions can provide useful information for boiler design and fuel selection. Recently used kinetic prediction models for FBC boilers are overly complex and require large computing capacity. Even so, there are many uncertainties in the case of FBC boilers. An empirical modeling approach for NOx prediction has been used exclusively for PCC boilers. No reference is available for modifying this method for FBC conditions. This paper presents possible advantages of empirical modeling based prediction of NOx emissions for FBC boilers, together with a discussion of its limitations. Empirical models are reviewed, and are applied to operation data from FBC boilers used for combusting Czech lignite coal or coal-biomass mixtures. Modifications to the model are proposed in accordance with theoretical knowledge and prediction accuracy.

7. A cost-benefit analysis of a pellet boiler with electrostatic precipitator versus conventional biomass technology: A case study of an institutional boiler in Syracuse, New York.

Science.gov (United States)

Levy, Jonathan I; Biton, Leiran; Hopke, Philip K; Zhang, K Max; Rector, Lisa

2017-07-01

patterns of health benefits given non-uniform age distributions and air pollution levels. The incremental investment in a lower-emitting staged combustion pellet boiler with an electrostatic precipitator was well justified by the population health improvements over the conventional wood chip technology with a multicyclone, even given the focus on only primary PM 2.5 within a small spatial domain. Our analytical framework could be generalized to other settings to inform optimal strategies for proposed new facilities or populations. Copyright © 2017. Published by Elsevier Inc.

8. Field Test of Boiler Primary Loop Temperature Controller

Energy Technology Data Exchange (ETDEWEB)

Glanville, P.; Rowley, P.; Schroeder, D.; Brand, L.

2014-09-01

Beyond these initial system efficiency upgrades are an emerging class of Advanced Load Monitoring (ALM) aftermarket controllers that dynamically respond to the boiler load, with claims of 10% to 30% of fuel savings over a heating season. For hydronic boilers specifically, these devices perform load monitoring, with continuous measurement of supply and in some cases return water temperatures. Energy savings from these ALM controllers are derived from dynamic management of the boiler differential, where a microprocessor with memory of past boiler cycles prevents the boiler from firing for a period of time, to limit cycling losses and inefficient operation during perceived low load conditions. These differ from OTR controllers, which vary boiler setpoint temperatures with ambient conditions while maintaining a fixed differential. PARR installed and monitored the performance of one type of ALM controller, the M2G from Greffen Systems, at multifamily sites in the city of Chicago and its suburb Cary, IL, both with existing OTR control. Results show that energy savings depend on the degree to which boilers are over-sized for their load, represented by cycling rates. Also savings vary over the heating season with cycling rates, with greater savings observed in shoulder months. Over the monitoring period, over-sized boilers at one site showed reductions in cycling and energy consumption in line with prior laboratory studies, while less over-sized boilers at another site showed muted savings.

9. Between the boiler and buffer tank; Zwischen Kessel und Speicher

Energy Technology Data Exchange (ETDEWEB)

Ertmer, Katharina

2013-08-06

Some manufacturers offer new heating pump groups for return temperature raising for solid-fuel boilers. [German] Einige Hersteller bieten neue Heizungspumpengruppen zur Ruecklauftemperaturanhebung bei Festbrennstoffkesseln an.

10. Simulation and testing of a new condensing boiler

International Nuclear Information System (INIS)

Rosa, L.; Tosato, R.

1987-01-01

The paper describes a new condensing boiler, characterized by the evacuation of flue-gases by natural draft. The best result is the consequent simplification of manufacturing, hook-up and operation of the boiler. Seasonal efficiency of the boiler, which operates with flue-gases conditioning to assure natural draft, rests about at same levels as for conventional condensing boilers. The authors emphasize the difficulty of simulate natural draft mechanism by mathematics because, in this case, flow of flue-gases and air at the draft diverter is strongly three-dimensional

11. Technical and environmental performance of 10 kW understocker boiler during combustion of biomass and conventional fuels

OpenAIRE

Junga Robert; Wzorek Małgorzata; Kaszubska Mirosława

2017-01-01

This paper treats about the impact fuels from biomass wastes and coal combustion on a small boiler operation and the emission of pollutants in this process. Tests were performed in laboratory conditions on a water boiler with retort furnace and the capacity of 10 kW. Fuels from sewage sludge and agriculture wastes (PBZ fuel) and a blend of coal with laying hens mature (CLHM) were taken into account. The results in emission changes of NOx, CO2, CO and SO2 and operating parameters of the tested...

12. Technical and environmental performance of 10 kW understocker boiler during combustion of biomass and conventional fuels

Directory of Open Access Journals (Sweden)

Junga Robert

2017-01-01

Full Text Available This paper treats about the impact fuels from biomass wastes and coal combustion on a small boiler operation and the emission of pollutants in this process. Tests were performed in laboratory conditions on a water boiler with retort furnace and the capacity of 10 kW. Fuels from sewage sludge and agriculture wastes (PBZ fuel and a blend of coal with laying hens mature (CLHM were taken into account. The results in emission changes of NOx, CO2, CO and SO2 and operating parameters of the tested boiler during combustion were investigated. The obtained results were compared with corresponding results of flame coal (GFC. Combustion of the PBZ fuel turned out to be a stable process in the tested boiler but the thermal output has decreased in about 30% compared to coal combustion, while CO and NOx emission has increased. Similar effect was observed when 15% of the poultry litter was added to the coal. In this case thermal output has also decreased (in about 20% and increase of CO and NOx emission was observed. As a conclusion, it can be stated that more effective control system with an adaptive air regulation and a modified heat exchanger could be useful in order to achieve the nominal power of the tested boiler.

13. Technical and environmental performance of 10 kW understocker boiler during combustion of biomass and conventional fuels

Science.gov (United States)

Junga, Robert; Wzorek, Małgorzata; Kaszubska, Mirosława

2017-10-01

This paper treats about the impact fuels from biomass wastes and coal combustion on a small boiler operation and the emission of pollutants in this process. Tests were performed in laboratory conditions on a water boiler with retort furnace and the capacity of 10 kW. Fuels from sewage sludge and agriculture wastes (PBZ fuel) and a blend of coal with laying hens mature (CLHM) were taken into account. The results in emission changes of NOx, CO2, CO and SO2 and operating parameters of the tested boiler during combustion were investigated. The obtained results were compared with corresponding results of flame coal (GFC). Combustion of the PBZ fuel turned out to be a stable process in the tested boiler but the thermal output has decreased in about 30% compared to coal combustion, while CO and NOx emission has increased. Similar effect was observed when 15% of the poultry litter was added to the coal. In this case thermal output has also decreased (in about 20%) and increase of CO and NOx emission was observed. As a conclusion, it can be stated that more effective control system with an adaptive air regulation and a modified heat exchanger could be useful in order to achieve the nominal power of the tested boiler.

14. Increase of energy efficiency in proportional adjusting of flow rate in the boiler circuit

OpenAIRE

Artamonov Pavel A.; Kurilenko Nikolai I.; Mamontov Gennady Ya.

2017-01-01

The article presents the results of theoretical studies in the field of the boiler circuit operating modes for the boiler rooms operating by the independent heat supply scheme. The 3D model of a boiler circuit for a boiler room with 3 MW rated output was developed, based on which there was made an estimation of the boiler pump performance indicators. There is proposed a method for reducing energy costs for the operation of the pumping equipment of the boiler circuit.

15. Application of 1-hydroxyethylidene-1, 1-diphosphonic acid in boiler water for industrial boilers.

Science.gov (United States)

Zeng, Bin; Li, Mao-Dong; Zhu, Zhi-Ping; Zhao, Jun-Ming; Zhang, Hui

2013-01-01

The primary method used for boiler water treatment is the addition of chemicals to industrial boilers to prevent corrosion and scaling. The static scale inhibition method was used to evaluate the scale inhibition performance of 1-hydroxyethylidene-1, 1-diphosphonic acid (HEDP). Autoclave static experiments were used to study the corrosion inhibition properties of the main material for industrial boilers (20# carbon steel) with an HEDP additive in the industrial boiler water medium. The electrochemical behavior of HEDP on carbon steel corrosion control was investigated using electrochemical impedance spectroscopy and Tafel polarization techniques. Experimental results indicate that HEDP can have a good scale inhibition effect when added at a quantity of 5 to 7 mg/L at a test temperature of not more than 100 °C. To achieve a high scale inhibition rate, the HEDP dosage must be increased when the test temperature exceeds 100 °C. Electrochemical and autoclave static experimental results suggest that HEDP has a good corrosion inhibition effect on 20# carbon steel at a concentration of 25 mg/L. HEDP is an excellent water treatment agent.

16. Deposit Probe Measurements in Large Biomass-Fired Grate Boilers and Pulverized-Fuel Boilers

DEFF Research Database (Denmark)

Hansen, Stine Broholm; Jensen, Peter Arendt; Jappe Frandsen, Flemming

2014-01-01

A number of full-scale deposit probe measuring campaigns conducted in grate-fired and suspension-fired boilers, fired with biomass, have been reviewed and compared. The influence of operational parameters on the chemistry of ash and deposits, on deposit build-up rates, and on shedding behavior has...... of the deposits formed is determined by the fly ash composition and the flue gas temperature; increases in the local flue gas temperature lead to higher contents of Si and Ca and lower contents of Cl in the deposits. The net deposit build-up rates in grate-fired and suspension-fired boilers are at similar levels....../wood-firing in suspension-fired boilers, shedding occurred by debonding with incomplete removal at flue gas temperatures of 600–1000 °C and by debonding with complete removal during wood-firing in suspension-fired boilers at high flue gas temperatures (1300 °C). Shedding events were not observed during wood suspension...

17. CFD modeling of a boiler's tubes rupture

International Nuclear Information System (INIS)

Rahimi, Masoud; Khoshhal, Abbas; Shariati, Seyed Mehdi

2006-01-01

This paper reports the results of a study on the reason for tubes damage in the superheater Platen section of the 320 MW Bisotoun power plant, Iran. The boiler has three types of superheater tubes and the damage occurs in a series of elbows belongs to the long tubes. A three-dimensional modeling was performed using an in-house computational fluid dynamics (CFD) code in order to explore the reason. The code has ability of simultaneous solving of the continuity, the Reynolds-Averaged Navier-Stokes (RANS) equations and employing the turbulence, combustion and radiation models. The whole boiler including; walls, burners, air channels, three types of tubes, etc., was modeled in the real scale. The boiler was meshed into almost 2,000,000 tetrahedral control volumes and the standard k-ε turbulence model and the Rosseland radiation model were used in the model. The theoretical results showed that the inlet 18.9 MPa saturated steam becomes superheated inside the tubes and exit at a pressure of 17.8 MPa. The predicted results showed that the temperature of the steam and tube's wall in the long tubes is higher than the short and medium size tubes. In addition, the predicted steam mass flow rate in the long tube was lower than other ones. Therefore, it was concluded that the main reason for the rupture in the long tubes elbow is changing of the tube's metal microstructure due to working in a temperature higher than the design temperature. In addition, the structural fatigue tension makes the last elbow of the long tube more ready for rupture in comparison with the other places. The concluded result was validated by observations from the photomicrograph of the tube's metal samples taken from the damaged and undamaged sections

18. Boiler inspection manipulator for Torness Power Station

International Nuclear Information System (INIS)

Carrey, R.T.A.; Playle, M.J.

1996-01-01

In-service inspection at Torness Advanced Gas-cooled Reactor is achieved, via penetrations above and below the core area and boilers and through eight circulator penetrations for inspection of the sub-diagrid area. A manipulator is described which can access the area above the reactor core via any of these eight peripheral penetrations. The design and fabrication of the manipulator has led to innovation with a number of possible solutions being tendered. In reactor deployment of the successful design is expected in early 1997. (UK)

19. Multiloop control of a drum boiler

Directory of Open Access Journals (Sweden)

Alena Kozáková

2014-05-01

Full Text Available The Equivalent Subsystems Method (ESM (Kozáková et al., 2011 is methodology of decentralized controller design in the frequency domain which allows designing local controllers using any SISO frequency domain method. The paper deals with the digital ESM version where digital local PID controllers guaranteeing required performance for the full system are designed for individual equivalent subsystems using the practice-oriented Sine-wave method (Bucz et al., 2012. The proposed decentralized controller design procedure was verified on the nonlinear benchmark drum boiler simulation model (Morilla, 2012.

20. Nuclear reactors with auxiliary boiler circuit

International Nuclear Information System (INIS)

George, B.V.; Cook, R.K.

1976-01-01

A gas-cooled nuclear reactor has a main circulatory system for the gaseous coolant incorporating one or more main energy converting units, such as gas turbines, and an auxiliary circulatory system for the gaseous coolant incorporating at least one steam generating boiler arranged to be heated by the coolant after its passage through the reactor core to provide steam for driving an auxiliary steam turbine, such an arrangement providing a simplified start-up procedure also providing emergency duties associated with long term heat removal on reactor shut down

1. A rule-based industrial boiler selection system

NARCIS (Netherlands)

Tan, C.F.; Khalil, S.N.; Karjanto, J.; Tee, B.T.; Wahidin, L.S.; Chen, W.; Rauterberg, G.W.M.; Sivarao, S.; Lim, T.L.

2015-01-01

Boiler is a device used for generating the steam for power generation, process use or heating, and hot water for heating purposes. Steam boiler consists of the containing vessel and convection heating surfaces only, whereas a steam generator covers the whole unit, encompassing water wall tubes,

2. CFD investigation of flow through internally riffled boiler tubes

DEFF Research Database (Denmark)

Rasmussen, Christian; Houbak, Niels; Sørensen, Jens Nørkær

1997-01-01

In this paper we show how to model the swirling flow in an internally riffled boiler tube. The flow field is visualized and the results are compared with measurements.......In this paper we show how to model the swirling flow in an internally riffled boiler tube. The flow field is visualized and the results are compared with measurements....

3. 30 CFR 77.411 - Compressed air and boilers; general.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false Compressed air and boilers; general. 77.411 Section 77.411 Mineral Resources MINE SAFETY AND HEALTH ADMINISTRATION, DEPARTMENT OF LABOR COAL MINE... COAL MINES Safeguards for Mechanical Equipment § 77.411 Compressed air and boilers; general. All...

4. Exergetic Modelling of Oil-Fired Steam Boilers | Ohijeagbon ...

African Journals Online (AJOL)

The performance variables and potential for energy savings in oil-fired industrial steam boilers were studied. Operational parameters of steam boilers using low pour fuel oil (LPFO) and diesel were used to determine thermodynamic properties of material streams and exergetic parameters. Analysis of thermodynamic ...

5. Assessment of Some Performance Characteristics of Refuse Boiler ...

African Journals Online (AJOL)

A pioneer palm oil boiler unit, in an immense power self-contained oil mill, impaired by many years of accumulated depreciation, was rebuilt in the pattern of a design-out scheme aimed primarily at rehabilitating the entire boiler system to a state of functionality. The research work studied the pre-maintenance and post ...

6. DESIGN REPORT: LOW-NOX BURNERS FOR PACKAGE BOILERS

Science.gov (United States)

The report describes a low-NOx burner design, presented for residual-oil-fired industrial boilers and boilers cofiring conventional fuels and nitrated hazardous wastes. The burner offers lower NOx emission levels for these applications than conventional commercial burners. The bu...

7. Thermomechanical finite element analysis of hot water boiler structure

Directory of Open Access Journals (Sweden)

Živković Dragoljub S.

2012-01-01

Full Text Available The paper presents an application of the Finite Elements Method for stress and strain analysis of the hot water boiler structure. The aim of the research was to investigate the influence of the boiler scale on the thermal stresses and strains of the structure of hot water boilers. Results show that maximum thermal stresses appear in the zone of the pipe carrying wall of the first reversing chamber. This indicates that the most critical part of the boiler are weld spots of the smoke pipes and pipe carrying plate, which in the case of significant scale deposits can lead to cracks in the welds and water leakage from the boiler. The nonlinear effects were taken into account by defining the bilinear isotropic hardening model for all boiler elements. Temperature dependency was defined for all relevant material properties, i. e. isotropic coefficient of thermal expansion, Young’s modulus, and isotropic thermal conductivity. The verification of the FEA model was performed by comparing the measured deformations of the hot water boiler with the simulation results. As a reference object, a Viessmann - Vitomax 200 HW boiler was used, with the installed power of 18.2 MW. CAD modeling was done within the Autodesk Inventor, and stress and strain analysis was performed in the ANSYS Software.

8. Hybrid system for fouling control in biomass boilers

Energy Technology Data Exchange (ETDEWEB)

Romeo, Luis M.; Gareta, Raquel [Centro de Investigacin de Recursos y Consumos Energeticos (CIRCE), Universidad de Zaragoza, Centro Politecnico Superior, Mareda de Luna, 3, Zaragoza 50018, (Spain)

2006-12-15

Renewable energy sources are essential paths towards sustainable development and CO{sub 2} emission reduction. For example, the European Union has set the target of achieving 22% of electricity generation from renewable sources by 2010. However, the extensive use of this energy source is being avoided by some technical problems as fouling and slagging in the surfaces of boiler heat exchangers. Although these phenomena were extensively studied in the last decades in order to optimize the behaviour of large coal power boilers, a simple, general and effective method for fouling control has not been developed. For biomass boilers, the feedstock variability and the presence of new components in ash chemistry increase the fouling influence in boiler performance. In particular, heat transfer is widely affected and the boiler capacity becomes dramatically reduced. Unfortunately, the classical approach of regular sootblowing cycles becomes clearly insufficient for them. Artificial Intelligence (AI) provides new means to undertake this problem. This paper illustrates a methodology based on Neural Networks (NNs) and Fuzzy-Logic Expert Systems to select the moment for activating sootblowing in an industrial biomass boiler. The main aim is to minimize the boiler energy and efficiency losses with a proper sootblowing activation. Although the NN type used in this work is well-known and the Hybrid Systems had been extensively used in the last decade, the excellent results obtained in the use of AI in industrial biomass boilers control with regard to previous approaches makes this work a novelty. (Author)

9. Optimization of feed water control for auxiliary boiler

International Nuclear Information System (INIS)

Li Lingmao

2004-01-01

This paper described the feed water control system of the auxiliary boiler steam drum in Qinshan Phase III Nuclear Power Plant, analyzed the deficiency of the original configuration, and proposed the optimized configuration. The optimized feed water control system can ensure the stable and safe operation of the auxiliary boiler, and the normal operation of the users. (author)

10. Assessment of the candidate markets for liquid boiler fuels

Energy Technology Data Exchange (ETDEWEB)

None

1979-12-01

Liquid fuels can be produced from coal in a number of indirect and direct liquefaction processes. While indirect coal liquefaction has been proved commercially outside the United States, most attention in this country has focused on the direct liquefaction processes, which include the processes under examination in this report; namely, the Exxon Donor Solvent (EDS), the H-Coal, and the Solvent Refined Coal (SRC) II processes. The objectives of the study were to: compare the boiler fuels of direct coal liquefaction with residual fuel oil (No. 6 fuel oil) including physical characteristics and environmental hazards, such as carcinogenic characteristics and toxic hazard characteristics; determine whether a boiler fuel market would exist for the coal liquefaction products given their physical characteristics and potential environmental hazards; determine the advantages of utilizing methanol as a boiler fuel on a continuous basis in commercial boilers utilizing existing technology; identify the potential regional candidate markets for direct coal liquefaction products as liquid boiler fuels; determine the distributing and handling costs associated with marketing coal liquefaction products as liquid boiler fuels; determine the current regulatory issues associated with the marketing of coal liquefaction products as boiler fuels; and determine and evaluate other institutional issues associated with the marketing of direct coal liquefaction products as boiler fuels.

11. A theoretical approach for energy saving in industrial steam boilers

International Nuclear Information System (INIS)

Sabry, T.I.; Mohamed, N.H.; Elghonimy, A.M.

1993-01-01

Optimization of the performance characteristics of such a steam boiler has been analyzed theoretically. Suitable thermodynamic relations have been utilized here to construct a computer model that would carry out the boiler performance characteristics at different operating parameters (e.g.; amount of excess air, fuel type, rate of blowdown preheating of combustion air and flow gases temperature). The results demonstrate that this computer model is to be used successfully in selecting the different operating parameters of the steam boiler at variant loads considering the best economical operation. Besides, this model can be used to investigate the sensitivity of the performance characteristics to the deviation of the boiler operating parameters from their optimum values. It was found also that changing the operating parameters beside the type of fuel in a boiler affects its performance characteristics. 3 figs

12. Optimisation of Marine Boilers using Model-based Multivariable Control

DEFF Research Database (Denmark)

Solberg, Brian

Traditionally, marine boilers have been controlled using classical single loop controllers. To optimise marine boiler performance, reduce new installation time and minimise the physical dimensions of these large steel constructions, a more comprehensive and coherent control strategy is needed....... This research deals with the application of advanced control to a specific class of marine boilers combining well-known design methods for multivariable systems. This thesis presents contributions for modelling and control of the one-pass smoke tube marine boilers as well as for hybrid systems control. Much...... of the focus has been directed towards water level control which is complicated by the nature of the disturbances acting on the system as well as by low frequency sensor noise. This focus was motivated by an estimated large potential to minimise the boiler geometry by reducing water level fluctuations...

13. The structure and behavior of salts in kraft recovery boilers

Energy Technology Data Exchange (ETDEWEB)

Backman, R.; Badoi, R.D.; Enestam, S. [Aabo Akademi Univ., Turku (Finland). Combustion Chemistry Research Group

1997-10-01

The melting behavior in the salt system (Na,K)(CO{sub 3},SO{sub 4},S,Cl,OH) is investigated by laboratory methods to enhance and further develop a chemical model for salt mixtures with compositions relevant for recovery boilers. The model, based on both literature data and experimental work can be used as (a) submodel in models for the over-all chemistry in recovery boilers and to estimate (b) deposit formation on heat transfer surfaces (fouling), (c) the melting properties of the fly ash, and (d) the smelt bed in recovery boilers. Experimental techniques used are thermal analysis, high temperature microscopy` and scanning electron microscopy. The model is implemented in a global calculation model which can handle both gas phases and condensed phases in the recovery boiler. The model gives a detailed description of the chemical reactions involved in the fume and dust formation in different locations of the flue gas channel in the boiler. (orig.)

14. Boiling process modelling peculiarities analysis of the vacuum boiler

Science.gov (United States)

Slobodina, E. N.; Mikhailov, A. G.

2017-06-01

The analysis of the low and medium powered boiler equipment development was carried out, boiler units possible development directions with the purpose of energy efficiency improvement were identified. Engineering studies for the vacuum boilers applying are represented. Vacuum boiler heat-exchange processes where boiling water is the working body are considered. Heat-exchange intensification method under boiling at the maximum heat- transfer coefficient is examined. As a result of the conducted calculation studies, heat-transfer coefficients variation curves depending on the pressure, calculated through the analytical and numerical methodologies were obtained. The conclusion about the possibility of numerical computing method application through RPI ANSYS CFX for the boiling process description in boiler vacuum volume was given.

15. Mercury emissions from polish pulverized coalfired boiler

Directory of Open Access Journals (Sweden)

Wichliński Michał

2017-01-01

Full Text Available The current paper presents the research results carried out at one of Polish power plants at a pulverized hard coal-fired 225 MW unit. The research was carried out at full load of the boiler (100% MCR and focused on analysis of mercury content in the input fuel and limestone sorbent for wet flue gas desulfurization (FGD system, as well as investigation of mercury content in the combustion products, i.e. fly ash, slag, FGD product (gypsum and FGD effluents (waste. Within the framework of the present study the concentration of mercury vapor in the exhaust gas was also investigated. The analysis was performed using Lumex RA-915+ spectrometer with an attachment (RP-91C. The measurements were carried out at three locations, i.e. before the electrostatic precipitator (ESP, downstream the ESP, and downstream the wet FGD plant. Design of the measurement system allowed to determine both forms of mercury in the flue gas (Hg0 and Hg2+ at all measurement locations.Based on the measurement results the balance of mercury for a pulverized coal (PC boiler was calculated and the amount of mercury was assessed both in the input solids (fuel and sorbent, as well as the gaseous and solids products (flue gas, slag, ash, gypsum and FGD waste.

16. Code boiler and pressure vessel life assessment

International Nuclear Information System (INIS)

Farr, J.R.

1992-01-01

In the United States of America and in Canada, laws and controls for determining life assessment for continued operation of equipment exist only for those pressure vessels built to Section III and evaluated according to Section XI. In this presentation, some of those considerations which are made in the USA and Canada for deciding on life or condition assessment of boilers and pressure vessels designed and constructed to other sections of the ASME Boiler and Pressure Vessel Code are reviewed. Life assessment or condition assesssment is essential in determining what is necessary for continued operation. With no ASME rules being adopted by laws or regulations, other than OSHA in the USA and similar environmental controls in Canada, to control life assessment for continued operation, the equipment owner must decide if assessment is to be done and how much to do. Some of those considerations are reviewed along with methods and procedures to make an assessment along with a discussion of where the ASME B and PV Code currently stands regarding continued operation. (orig.)

17. Establishing an energy efficiency recommendation for commercial boilers

International Nuclear Information System (INIS)

Ware, Michelle J.

2000-01-01

To assist the federal government in meeting its energy reduction goals, President Clinton's Executive Order 12902 established the Procurement Challenge, which directed all federal agencies to purchase equipment within the top 25th percentile of efficiency. Under the direction of DOE's Federal Energy Management Program (FEMP), the Procurement Challenge's goal is to create efficiency recommendations for all energy-using products that could substantially impact the government's energy reduction goals, like commercial boilers. A typical 5,000,000 Btuh boiler, with a thermal efficiency of 83.2%, can have lifetime energy cost savings of\$40,000 when compared to a boiler with a thermal efficiency of 78%. For the federal market, which makes up 2% of the boiler market, this means lifetime energy cost savings of over\$25,600,000. To establish efficiency recommendations, FEMP uses standardized performance ratings for products sold in the marketplace. Currently, the boiler industry uses combustion efficiency and, sometimes, thermal efficiency performance measures when specifying a commercial boiler. For many years, the industry has used these efficiency measures interchangeably, causing confusion about boiler performance measurements, and making it difficult for FEMP to establish the top 25th percentile of efficiency. This paper will illustrate the method used to establish FEMP's recommendation for boilers. The method involved defining a correlation between thermal and combustion efficiency among boiler classifications; using the correlation to model a data set of all the boiler types available in the market; and identifying how the correlation affected the top 25th percentile analysis. The paper also will discuss the applicability of this method for evaluating other equipment for which there are limited data on performance ratings

18. Size fractionation of waste-to-energy boiler ash enables separation of a coarse fraction with low dioxin concentrations.

Science.gov (United States)

Weidemann, E; Allegrini, E; Fruergaard Astrup, T; Hulgaard, T; Riber, C; Jansson, S

2016-03-01

Polychlorinated dibenzo-p-dioxins and dibenzofurans (PCDD/F) formed in modern Waste-to-Energy plants are primarily found in the generated ashes and air pollution control residues, which are usually disposed of as hazardous waste. The objective of this study was to explore the occurrence of PCDD/F in different grain size fractions in the boiler ash, i.e. ash originating from the convection pass of the boiler. If a correlation between particle size and dioxin concentrations could be found, size fractionation of the ashes could reduce the total amount of hazardous waste. Boiler ash samples from ten sections of a boiler's convective part were collected over three sampling days, sieved into three different size fractions - 0.355 mm - and analysed for PCDD/F. The coarse fraction (>0.355 mm) in the first sections of the horizontal convection pass appeared to be of low toxicity with respect to dioxin content. While the total mass of the coarse fraction in this boiler was relatively small, sieving could reduce the amount of ash containing toxic PCDD/F by around 0.5 kg per tonne input waste or around 15% of the collected boiler ash from the convection pass. The mid-size fraction in this study covered a wide size range (0.09-0.355 mm) and possibly a low toxicity fraction could be identified by splitting this fraction into more narrow size ranges. The ashes exhibited uniform PCDD/F homologue patterns which suggests a stable and continuous generation of PCDD/F. Copyright © 2016 Elsevier Ltd. All rights reserved.

19. BOILER MATERIALS FOR ULTRASUPERCRITICAL COAL POWER PLANTS

Energy Technology Data Exchange (ETDEWEB)

R. Viswanathan; K. Coleman

2003-01-20

The principal objective of this project is to develop materials technology for use in ultrasupercritical (USC) plant boilers capable of operating with 760 C (1400 F), 35 MPa (5000 psi) steam. In the 21st century, the world faces the critical challenge of providing abundant, cheap electricity to meet the needs of a growing global population while at the same time preserving environmental values. Most studies of this issue conclude that a robust portfolio of generation technologies and fuels should be developed to assure that the United States will have adequate electricity supplies in a variety of possible future scenarios. The use of coal for electricity generation poses a unique set of challenges. On the one hand, coal is plentiful and available at low cost in much of the world, notably in the U.S., China, and India. Countries with large coal reserves will want to develop them to foster economic growth and energy security. On the other hand, traditional methods of coal combustion emit pollutants and CO{sub 2} at high levels relative to other generation options. Maintaining coal as a generation option in the 21st century will require methods for addressing these environmental issues. This project has established a government/industry consortium to undertake a five-year effort to evaluate and develop of advanced materials that allow the use of advanced steam cycles in coal-based power plants. These advanced cycles, with steam temperatures up to 760 C, will increase the efficiency of coal-fired boilers from an average of 35% efficiency (current domestic fleet) to 47% (HHV). This efficiency increase will enable coal-fired power plants to generate electricity at competitive rates (irrespective of fuel costs) while reducing CO{sub 2} and other fuel-related emissions by as much as 29%. Success in achieving these objectives will support a number of broader goals. First, from a national prospective, the program will identify advanced materials that will make it possible to

20. A novel direct-fired porous-medium boiler

Science.gov (United States)

Prasartkaew, Boonrit

2018-01-01

Nowadays, power and heat generation systems pay an important role in all economic sectors. These systems are mainly based on combustion reaction and operated under the second law of thermodynamics. A conventional boilers, a main component of heat and power generators, have thermal efficiency in the range of 70 to 85%, mainly owing to they have flue gas heat loss. This paper proposes a novel type of boiler, called a Direct-fired Porous-medium Boiler (DPB). Due to being operated without flue gas heat loss, its thermal efficiency cloud be approximately close to 100%. The steam produced from the proposed boiler; however, is not pure water steam. It is the composite gases of steam and combustion-product-gases. This paper aims at presenting the working concept and reporting the experimental results on the performance of the proposed boiler. The experiments of various operating parameters were performed and collected data were used for the performance analysis. The experimental results demonstrated that the proposed boiler can be operated as well as the conceptual design and then it is promising. It can be possibly further developed to be a high efficiency boiler by means of reducing or suppressing the surface heat loss with better insulator and/or refractory lined.

1. Cross connecting absorber module inlets of multiple boiler units

International Nuclear Information System (INIS)

Cirillo, A.J.; Sperber, P.K.; Belavadi, V.N.; Mukherji, A.

1991-01-01

The retrofitting of scrubbers downstream of existing balanced draft boilers is often accomplished by the addition of induced draft (ID) booster fans. By creating a common plenum between the ID fans and the ID booster fans of two or more boiler-absorber trains, absorber module capacity may be shared among multiple boiler units. At Harrison Power Station, three (3) 4,900,000 lb/hour boilers (640 MWe Gross) will be linked through a common plenum. This sharing capability precludes the need to add standby module capacity, thereby saving capital dollars and keeping project critical path schedules, which typically run through absorber procurement and construction, to a minimum. Through damper placement in the ductwork cross connections, unitized boiler-absorber module operation or common plenum operation may be obtained, thus providing both operational flexibility and reliability. Additionally, open plenum operation allows the removal of an absorber unit from service, while keeping its associated boiler on line, thereby precluding 'cold starts' and maintaining overall unit availabilities. As either unitized or common plenum operation is possible with the cross connection, the furnace draft control systems of each boiler must be examined for varying load operation and trip conditions. This paper addresses the means by which to analyze such cross connection operational scenarios while maintaining compliance with furnace flame out safety guidelines, and will discuss the physical design considerations, ramifications and benefits of same, with select emphasis on what is being implemented at the Harrison Power Station

2. Supercritical boiler material selection using fuzzy analytic network process

Directory of Open Access Journals (Sweden)

Saikat Ranjan Maity

2012-08-01

Full Text Available The recent development of world is being adversely affected by the scarcity of power and energy. To survive in the next generation, it is thus necessary to explore the non-conventional energy sources and efficiently consume the available sources. For efficient exploitation of the existing energy sources, a great scope lies in the use of Rankin cycle-based thermal power plants. Today, the gross efficiency of Rankin cycle-based thermal power plants is less than 28% which has been increased up to 40% with reheating and regenerative cycles. But, it can be further improved up to 47% by using supercritical power plant technology. Supercritical power plants use supercritical boilers which are able to withstand a very high temperature (650-720˚C and pressure (22.1 MPa while producing superheated steam. The thermal efficiency of a supercritical boiler greatly depends on the material of its different components. The supercritical boiler material should possess high creep rupture strength, high thermal conductivity, low thermal expansion, high specific heat and very high temperature withstandability. This paper considers a list of seven supercritical boiler materials whose performance is evaluated based on seven pivotal criteria. Given the intricacy and difficulty of this supercritical boiler material selection problem having interactions and interdependencies between different criteria, this paper applies fuzzy analytic network process to select the most appropriate material for a supercritical boiler. Rene 41 is the best supercritical boiler material, whereas, Haynes 230 is the worst preferred choice.

3. Up-date on cyclone combustion and cyclone boilers

Energy Technology Data Exchange (ETDEWEB)

Carmo, Felipe Alfaia do; Nogueira, Manoel Fernandes Martins; Rocha, Rodrigo Carnera Castro da; Gazel, Hussein Felix; Martins, Diego Henrique dos Reis [Universidade Federal do Para (UFPA), Belem, PA (Brazil). Campus Universitario Jose da Silveira Netto], E-mails: mfmn@ufpa.br, mfmn@ufpa.br

2010-07-01

The boiler concept has been around for more than 70 years, and there are many types available. Boilers provide steam or hot water for industrial and commercial use. The Federal University of Para (UFPA) through the research group EBMA (Energy,Biomass and Environment) has been developing cyclonic furnace with a water wall, a boiler, aiming to use regional timbers (sawdust) and agro-industries residues as fuel to produce steam to be used in industrial processes as well as in power generation,. The use of cyclonic combustion for burning waste instead of burning in a fixed bed is mainly due to two factors efficiency improvement causing a more compact boiler and less risk of explosion, since their process does not generate an accumulation of volatile. Present state-of-art for commercial cyclone boilers has as set up a cyclone combustor with two combustion chambers, in fluid communication, where there ducts for supplying air and fuel directly into the first chamber and for forming a cyclonic flow pattern and a heat exchanger surrounding the second chamber for keeping low combustion temperature in both chambers. This paper shows the results of a literature review about design, construction and operation of cyclonic boilers using solid, liquid or gaseous fuel. This information has been used for the design of a cyclone boiler to be constructed at UFPA for research purposes and its basic concept is presented at the end of this article. (author)

4. 46 CFR 52.20-17 - Opening between boiler and safety valve (modifies PFT-44).

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Opening between boiler and safety valve (modifies PFT-44). 52.20-17 Section 52.20-17 Shipping COAST GUARD, DEPARTMENT OF HOMELAND SECURITY (CONTINUED) MARINE ENGINEERING POWER BOILERS Requirements for Firetube Boilers § 52.20-17 Opening between boiler and safety valve...

5. 40 CFR 266.110 - Waiver of DRE trial burn for boilers.

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 26 2010-07-01 2010-07-01 false Waiver of DRE trial burn for boilers... HAZARDOUS WASTE MANAGEMENT FACILITIES Hazardous Waste Burned in Boilers and Industrial Furnaces § 266.110 Waiver of DRE trial burn for boilers. Boilers that operate under the special requirements of this section...

6. 9 CFR 91.22 - Protection from heat of boilers and engines.

Science.gov (United States)

2010-01-01

... 9 Animals and Animal Products 1 2010-01-01 2010-01-01 false Protection from heat of boilers and... Protection from heat of boilers and engines. No animals shall be stowed along the alleyways leading to the engine or boiler rooms unless the sides of said engine or boiler rooms are covered by a tongue and groove...

7. 46 CFR 91.15-1 - Standards in inspection of hulls, boilers, and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Standards in inspection of hulls, boilers, and machinery... hulls, boilers, and machinery. In the inspection of hulls, boilers, and machinery of vessels, the..., respecting material and inspection of hulls, boilers, and machinery, and the certificate of classification...

8. 30 CFR 57.13001 - General requirements for boilers and pressure vessels.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false General requirements for boilers and pressure... NONMETAL MINES Compressed Air and Boilers § 57.13001 General requirements for boilers and pressure vessels. All boilers and pressure vessels shall be constructed, installed, and maintained in accordance with...

9. 40 CFR 63.7506 - Do any boilers or process heaters have limited requirements?

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 13 2010-07-01 2010-07-01 false Do any boilers or process heaters have..., and Institutional Boilers and Process Heaters General Compliance Requirements § 63.7506 Do any boilers or process heaters have limited requirements? (a) New or reconstructed boilers and process heaters in...

10. 46 CFR 189.15-1 - Standards in inspection of hulls, boilers, and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 7 2010-10-01 2010-10-01 false Standards in inspection of hulls, boilers, and machinery... inspection of hulls, boilers, and machinery. In the inspection of hulls, boilers, and machinery of vessels... chapter, respecting material and construction of hulls, boilers, and machinery, and certificate of...

11. 49 CFR 230.20 - Alteration and repair report for steam locomotive boilers.

Science.gov (United States)

2010-10-01

... boilers. 230.20 Section 230.20 Transportation Other Regulations Relating to Transportation (Continued... boilers. (a) Alterations. When an alteration is made to a steam locomotive boiler, the steam locomotive... maintained for the life of the boiler. (See appendix B of this part.) (b) Welded and riveted repairs to...

12. 46 CFR 61.05-5 - Preparation of boilers for inspection and test.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Preparation of boilers for inspection and test. 61.05-5... PERIODIC TESTS AND INSPECTIONS Tests and Inspections of Boilers § 61.05-5 Preparation of boilers for... preparing the boilers for the hydrostatic test, they shall be filled with water at not less than 70 °F. and...

13. 40 CFR 63.7491 - Are any boilers or process heaters not subject to this subpart?

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 13 2010-07-01 2010-07-01 false Are any boilers or process heaters not..., and Institutional Boilers and Process Heaters What This Subpart Covers § 63.7491 Are any boilers or process heaters not subject to this subpart? The types of boilers and process heaters listed in paragraphs...

14. 40 CFR 63.7499 - What are the subcategories of boilers and process heaters?

Science.gov (United States)

2010-07-01

... 40 Protection of Environment 13 2010-07-01 2010-07-01 false What are the subcategories of boilers..., and Institutional Boilers and Process Heaters Emission Limits and Work Practice Standards § 63.7499 What are the subcategories of boilers and process heaters? The subcategories of boilers and process...

15. 46 CFR 71.15-1 - Standards in inspection of hulls, boilers, and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 3 2010-10-01 2010-10-01 false Standards in inspection of hulls, boilers, and machinery..., boilers, and machinery. In the inspection of hulls, boilers, and machinery of vessels, the standards... and inspection of hulls, boilers, and machinery, and the certificate of classification referring...

16. 30 CFR 56.13001 - General requirements for boilers and pressure vessels.

Science.gov (United States)

2010-07-01

... 30 Mineral Resources 1 2010-07-01 2010-07-01 false General requirements for boilers and pressure... MINES Compressed Air and Boilers § 56.13001 General requirements for boilers and pressure vessels. All boilers and pressure vessels shall be constructed, installed, and maintained in accordance with the...

17. Automating data analysis during the inspection of boiler tubes using line scanning thermography

Science.gov (United States)

Ley, Obdulia; Momeni, Sepand; Ostroff, Jason; Godinez, Valery

2012-05-01

Failures in boiler waterwalls can occur when a relatively small amount of corrosion and loss of metal have been experienced. This study presents our efforts towards the application of Line Scanning Thermography (LST) for the analysis of thinning in boiler waterwall tubing. LST utilizes a line heat source to thermally excite the surface to be inspected and an infrared detector to record the transient surface temperature increase observed due to the presence of voids, thinning or other defects. In waterwall boiler tubes the defects that can be detected using LST correspond to corrosion pitting, hydrogen damage and wall thinning produced by inadequate burner heating or problems with the water chemistry. In this paper we discuss how the LST technique is implemented to determine thickness from the surface temperature data, and we describe our efforts towards developing a semiautomatic analysis tool to speed up the time between scanning, reporting and implementing repairs. We compare the density of data produced by the common techniques used to assess wall thickness and the data produced by LST.

18. Burnout power in once-through tubular steam generators

International Nuclear Information System (INIS)

Campolunghi, F.; Cumo, M.; Ferrari, G.; Leo, R.; Vaccaro, G.

1974-01-01

The present experimental research provides experimental data in a design field where existing burnout correlations are usually extrapolated outside their validity range. Low surface heat fluxes and very long geometries typical of L.M.F.B.R. sodium heated steam generators require full scale water tests. 218 burnout qualities at pressures ranging from 60 to 160 kg/cm 2 and specific mass flowrates from 110 to 260 g/cm 2 s were measured and tested against the most known burnout correlations. Physically it appears that burnout quality is substantially independent from the flowrate, while a sharp subdivision with pressure suggests that for 60 less than p less than 90 kg/cm 2 and 110 less than p less than 160 kg/cm 2 two different burnout mechanisms may set up. (U.S.)

19. Apparatus and method of controlling the thermal performance of an oxygen-fired boiler

Science.gov (United States)

Levasseur, Armand A.; Kang, Shin G.; Kenney, James R.; Edberg, Carl D.

2017-09-05

Disclosed herein is a method of controlling the operation of an oxy-fired boiler; the method comprising combusting a fuel in a boiler; producing a heat absorption pattern in the boiler; discharging flue gases from the boiler; recycling a portion of the flue gases to the boiler; combining a first oxidant stream with the recycled flue gases to form a combined stream; splitting the combined stream into several fractions; and introducing each fraction of the combined stream to the boiler at different points of entry to the boiler.

20. Failure Analysis Of Industrial Boiler Pipe

International Nuclear Information System (INIS)

2000-01-01

Failure analysis of industrial boiler pipe has been done. The tested pipe material is carbon steel SA 178 Grade A refer to specification data which taken from Fertilizer Company. Steps in analysis were ; collection of background operation and material specification, visual inspection, dye penetrant test, radiography test, chemical composition test, hardness test, metallography test. From the test and analysis result, it is shown that the pipe failure caused by erosion and welding was shown porosity and incomplete penetration. The main cause of failure pipe is erosion due to cavitation, which decreases the pipe thickness. Break in pipe thickness can be done due to decreasing in pipe thickness. To anticipate this problem, the ppe will be replaced with new pipe

1. CHP Integrated with Burners for Packaged Boilers

Energy Technology Data Exchange (ETDEWEB)

Castaldini, Carlo; Darby, Eric

2013-09-30

The objective of this project was to engineer, design, fabricate, and field demonstrate a Boiler Burner Energy System Technology (BBEST) that integrates a low-cost, clean burning, gas-fired simple-cycle (unrecuperated) 100 kWe (net) microturbine (SCMT) with a new ultra low-NOx gas-fired burner (ULNB) into one compact Combined Heat and Power (CHP) product that can be retrofit on new and existing industrial and commercial boilers in place of conventional burners. The Scope of Work for this project was segmented into two principal phases: (Phase I) Hardware development, assembly and pre-test and (Phase II) Field installation and demonstration testing. Phase I was divided into five technical tasks (Task 2 to 6). These tasks covered the engineering, design, fabrication, testing and optimization of each key component of the CHP system principally, ULNB, SCMT, assembly BBEST CHP package, and integrated controls. Phase I work culminated with the laboratory testing of the completed BBEST assembly prior to shipment for field installation and demonstration. Phase II consisted of two remaining technical tasks (Task 7 and 8), which focused on the installation, startup, and field verification tests at a pre-selected industrial plant to document performance and attainment of all project objectives. Technical direction and administration was under the management of CMCE, Inc. Altex Technologies Corporation lead the design, assembly and testing of the system. Field demonstration was supported by Leva Energy, the commercialization firm founded by executives at CMCE and Altex. Leva Energy has applied for patent protection on the BBEST process under the trade name of Power Burner and holds the license for the burner currently used in the product. The commercial term Power Burner is used throughout this report to refer to the BBEST technology proposed for this project. The project was co-funded by the California Energy Commission and the Southern California Gas Company (SCG), a

2. Model technique for aerodynamic study of boiler furnace

Energy Technology Data Exchange (ETDEWEB)

1966-02-01

The help of the Division was recently sought to improve the heat transfer and reduce the exit gas temperature in a pulverized-fuel-fired boiler at an Australian power station. One approach adopted was to construct from Perspex a 1:20 scale cold-air model of the boiler furnace and to use a flow-visualization technique to study the aerodynamic patterns established when air was introduced through the p.f. burners of the model. The work established good correlations between the behaviour of the model and of the boiler furnace.

3. Model-based Control of a Bottom Fired Marine Boiler

DEFF Research Database (Denmark)

Solberg, Brian; Karstensen, Claus M. S.; Andersen, Palle

2005-01-01

This paper focuses on applying model based MIMO control to minimize variations in water level for a specific boiler type. A first principles model is put up. The model is linearized and an LQG controller is designed. Furthermore the benefit of using a steam °ow measurement is compared to a strategy...... relying on estimates of the disturbance. Preliminary tests at the boiler system show that the designed controller is able to control the boiler process. Furthermore it can be concluded that relying on estimates of the steam flow in the control strategy does not decrease the controller performance...

4. Numerical modelling of a straw-fired grate boiler

DEFF Research Database (Denmark)

Kær, Søren Knudsen

2004-01-01

The paper presents a computational fluid dynamics (CFD) analysis of a 33 MW straw-fired grate boiler. Combustion on the grate plays akey-role in the analysis of these boilers and in this work a stand-alone code was used to provide inlet conditions for the CFD analysis. Modelpredictions were...... compared with available gas temperature and species concentration measurements showing good agreement. Combustionof biomass in grate-based boilers is often associated with high emission levels and relatively high amounts of unburnt carbon in the fly ash.Based on the CFD analysis, it is suggested that poor...

5. Vacuum boilers developed heating surfaces technic and economic efficiency evaluation

Science.gov (United States)

Slobodina, E. N.; Mikhailov, A. G.; Semenov, B. A.

2018-01-01

The vacuum boilers as manufacturing proto types application analysis was carried out, the possible directions for the heating surfaces development are identified with a view to improving the energy efficiency. Economic characteristics to evaluate the vacuum boilers application efficiency (Net Discounted Income (NDI), Internal Rate of Return (IRR), Profitability Index (PI) and Payback Period) are represented. The given type boilers application technic and economic efficiency criteria were established. NDI changing curves depending on the finning coefficient and operating pressure were obtained as a result of the conducted calculation studies.

6. An optimising controller for Hinkley Point B AGR boilers

International Nuclear Information System (INIS)

Wells, C.

1986-01-01

The improvements to the control system at Hinkley Point 'B' Power Station has as one of its objectives the provision of a half unit valve controller. This will enable the asymmetry between the boiler half units, which is a feature of current operation, to be reduced. The use of an on-line boiler model in conjunction with this facility will allow the risk to the boilers from corrosion, creep, and vibration to be assessed and held at the minimum attainable value, thereby prolonging plant life whilst maximising output and efficiency. (author)

7. Model-based Control of a Bottom Fired Marine Boiler

DEFF Research Database (Denmark)

Solberg, Brian; Karstensen, Claus M. S.; Andersen, Palle

This paper focuses on applying model based MIMO control to minimize variations in water level for a specific boiler type. A first principles model is put up. The model is linearized and an LQG controller is designed. Furthermore the benefit of using a steam °ow measurement is compared to a strategy...... relying on estimates of the disturbance. Preliminary tests at the boiler system show that the designed controller is able to control the boiler process. Furthermore it can be concluded that relying on estimates of the steam flow in the control strategy does not decrease the controller performance...

8. Economical analyses of construction of a biomass boiler house

International Nuclear Information System (INIS)

Normak, A.

2002-01-01

To reduce the energy costs we can use cheaper fuel to fire our boiler. One of the cheapest fuels is wood biomass. It is very actual issue how to use cheaper wood biomass in heat generation to decrease energy costs and to increase biomass share in our energy balance. Before we decide to build biomass boiler house it is recommendable to analyse the economical situation and work out most profitable, efficient, reliable and ecological boiler plant design on particular conditions. The best way to perform the analyses is to use the economical model presented. It saves our time and gives objective evaluation to the project. (author)

9. Maintenance of immersion ultrasonic testing on the water tube boiler

International Nuclear Information System (INIS)

Ishiyama, Toru; Kawasaki, Ichio; Miura, Hirohito

2014-01-01

There are 4-boiler in nuclear fuel cycle engineering laboratories (NCL). These boilers have been operated in the long term over 20 years. One of them, the leakage of boiler water was found at one of the generating tubes, and 2 adjoining generating tubes were corroded in Dec, 2011. These generating tubes were investigated by immersion ultrasonic testing (UT) for measure thickness of the tube. As a result, thinner tube was found in a part of a bend and near the water drum. These parts are covered with sulfide deposit, it seems that the generating tubes were corroded by sulfide. (author)

10. Orion Ammonia Boiler System Preflight Test Preparations

Science.gov (United States)

Levitt, Julia L.

2017-01-01

The Environmental Controls and Life Support Systems (ECLSS) branch at Kennedy Space Center (KSC) is currently undergoing preparations for ground testing of the Orion Multi-Purpose Crew Vehicle (MPCV) to prepare its subsystems for EM-1 (Exploration Mission-1). EM-1, Orions second unmanned flight, is a three-week long lunar mission during which the vehicle will complete a 6-day retrograde lunar orbit before returning to Earth. This paper focuses on the work done during the authors 16-week internship with the Mechanical Engineering Branch of KSCs Engineering Directorate. The authors project involved assisting with the preparations for testing the Orion MPCVs ammonia boiler system. The purpose of the ammonia boiler system is to keep the spacecraft sufficiently cool during the reentry portion of its mission, from service module (SM) separation to post-landing. This system is critical for keeping both the spacecraft (avionics and electronics) and crew alive during reentry, thus a successful test of the system is essential to the success of EM-1. XXXX The author was able to draft a detailed outline of the procedure for the ammonia system functional test. More work will need to be done on the vehicle power-up and power-down portions of the procedure, but the ammonia system testing portion of the procedure is thorough and includes vehicle test configurations, vehicle commands, and GSE. The author was able to compile a substantial list of questions regarding the ammonia system functional test with the help of her mentors. A significant number of these questions were answered in the teleconferences with Lockheed Martin.

11. Smooth Surfaces: A review of current and planned smooth surface technologies for fouling resistance in boiler

Energy Technology Data Exchange (ETDEWEB)

Corkery, Robert; Baefver, Linda; Davidsson, Kent; Feiler, Adam

2012-02-15

Here we have described the basics of boilers, fuels, combustion, flue gas composition and mechanisms of deposition. We have reviewed coating technologies for boiler tubes, including their materials compositions, nano structures and performances. The surface forces in boilers, in particular those relevant to formation of unwanted deposits in boilers have also been reviewed, and some comparative calculations have been included to indicate the procedures needed for further study. Finally practical recommendations on the important considerations in minimizing deposition on boiler surfaces are made

12. Numerical simulation of a biomass fired grate boiler

DEFF Research Database (Denmark)

Yin, Chungen; Rosendahl, Lasse; Kær, Søren Knudsen

2006-01-01

Computational fluid dynamic (CFD) analysis of the thermal flow in the combustion furnace of a biomass-fired grate boiler provides crucial insight into the boiler's performance. Quite a few factors play important roles in a general CFD analysis, such as grid, models, discretization scheme and so on....... For a grate boiler, the modeling the interaction of the fuel bed and the gas phase above the bed is also essential. Much effort can be found in literature on developing bed models whose results are introduced into CFD simulations of freeboard as inlet conditions. This paper presents a CFD analysis...... of the largest biomass-fired grate boiler in Denmark. The focus of this paper is to study how significantly an accurate bed model can affect overall CFD results, i.e., how necessarily it is to develop an accurate bed model in terms of the reliability of CFD results. The ultimate purpose of the study is to obtain...

13. Criteria of choosing building structures for rooftop boiler rooms

Directory of Open Access Journals (Sweden)

Plotnikov Artyom

2018-01-01

Full Text Available The paper investigates parameters of noise and vibration distribution in the territory of residential area depending on the structural materials and power of independent heat supply systems. Rooftop boiler rooms are decentralized heat supply systems in buildings. Today, residential areas are strongly affected by noise and vibrations. Adverse effects are isolated by buildings materials, protective shields and floating floors. Rooftop boiler rooms located in Tyumen city were investigated within this research. Structures of rooftop boiler rooms were analyzed. Acoustic analysis results and the parameters of equivalent continuous sound level are presented. An option for improvement of rooftop boiler rooms structures is suggested. Comparison of capital investments in construction and installation activities is carried out. Conclusion on capital investments required for noise protection is made.

14. Emissions from Power Plant and Industrial Boiler Sector

Data.gov (United States)

U.S. Environmental Protection Agency — This asset provides hourly data on SO2, NOx, and CO2 emissions; gross load, steam load, and heat input; from electricity generation units and industrial boilers from...

15. Knowledge based system for fouling assessment of power plant boiler

International Nuclear Information System (INIS)

Afgan, N.H.; He, X.; Carvalho, M.G.; Azevedo, J.L.T.

1999-01-01

The paper presents the design of an expert system for fouling assessment in power plant boilers. It is an on-line expert system based on selected criteria for the fouling assessment. Using criteria for fouling assessment based on 'clean' and 'not-clean' radiation heat flux measurements, the diagnostic variable are defined for the boiler heat transfer surface. The development of the prototype knowledge-based system for fouling assessment in power plants boiler comprise the integrations of the elements including knowledge base, inference procedure and prototype configuration. Demonstration of the prototype knowledge-based system for fouling assessment was performed on the Sines power plant. It is a 300 MW coal fired power plant. 12 fields are used with 3 on each side of boiler

16. Numerical investigation of ash deposition in straw-fired boilers

DEFF Research Database (Denmark)

Kær, Søren Knudsen

in the design phase of straw-fired boilers. Some of the primary model outputs include improved heat transfer rate predictions and detailed information about local deposit formation rates. This information is essential when boiler availability and efficiency is to be estimated. A stand-alone program has been...... accumulation rates encountered during straw combustion in grate-fired boilers. The sub-models have been based on information about the combustion and deposition properties of straw gathered from the literature and combined into a single Computational Fluid Dynamics (CFD) based analysis tool which can aid...... transfer mechanisms have a pronounced influence on the combustion pattern. The combined set of sub-models has been evaluated using the straw-fired boiler at Masnedø CHP plant as a test case. The predicted grate combustion and KCl release patterns are in qualitative agreement with experimental findings...

17. Boiler for combustion fuel in a fluidized bed

Directory of Open Access Journals (Sweden)

Laković Mirjana S.

2015-01-01

Full Text Available Fuel combustion in fluidized bed combustion is a process that is current and which every day gives more attention and there are many studies that have been closely associated with this technology. This combustion technology is widespread and constantly improving the range of benefits it provides primarily due to reduced emissions. This paper presents the boilers for combustion in a fluidized bed, whit characteristics and advantages. Also is shown the development of this type of boilers in Republic of Serbia. In this paper is explained the concept of fluidized bed combustion. Boilers for this type of combustion can be improved and thereby increase their efficiency level. More detailed characteristics are given for boilers with bubbling and circulating fluidized bed as well as their mutual comparison.

18. Energy efficiency in boilers; Eficiencia energetica em caldeiras

Energy Technology Data Exchange (ETDEWEB)

Ponte, Ricardo Silva The [Universidade Federal do Ceara (UFCE), Fortaleza, CE (Brazil). Dept. de Engenharia Eletrica], email: ricthe@dee.ufc.br; Barbosa, Marcos Antonio Pinheiro; Rufino, Maria da Gracas [Universidade de Fortaleza (UNIFOR), CE (Brazil). Dept. de Engenharia Eletrica], emails: marcos_apb@unifor.br, gsrufino@unifor.br

2010-07-01

The boiler is vapor generator equipment that has been widely used in industrial milieu as in electric energy generation in thermoelectric plants. Since their first conception, the boilers have been changed in order to provide security and energetic efficiency. They can present high losses of energy if they don't be operated according to some criteria. A considerable part of boilers operation cost include fuel expenses. So, the adoption of effective steps in order to reduce fuel consumption is important to industry economy, besides it brings environmental benefits through the reduction of pollution liberation. The present article has the objective of emphasizing the effective steps for the economy of energy in boilers, such as, the regulation of combustion; the control of soot and incrustations; the installation of economizers, air heaters and super heaters; the reduction in purges and reintroduction of condensed steam. (author)

19. Wood-Fired Boiler System Evaluation at Fort Stewart, GA

National Research Council Canada - National Science Library

Potts, Noel

2002-01-01

Part of the plan to modernize the central energy plant (CEP) at Fort Stewart, GA is focused on the installations wood-fired boiler, which provides steam for heating, cooling, and domestic hot water. The U.S...

20. Seismic model of the nuclear boiler SPX2

International Nuclear Information System (INIS)

Christodoulou, K.

1982-01-01

A model of the nuclear boiler SPX2 is proposed in this paper enabling to carry out comparative calculations on the response to seismic effects. The calculations are made in CISE and SEPTEN departments of Electricite de France [fr

1. High gradient magnetic filters for boiler water treatment

International Nuclear Information System (INIS)

Harland, J.R.; Nichols, R.M.

1977-01-01

Heavy metal oxide suspended solids in those steam condensates recycled to the boilers produce buildup within the boiler tubes which can lead to unequal and reduced heat transfer efficiency, and indirectly, to boiler tube failures. Recommended reductions in such suspended solids in feedwater to the economizers of modern high pressure boilers to levels of under 10 ppb have been published. The industrially-available SALA-HGMF magnetic filter has achieved these desired suspended solids levels in treating steam condensates. The high gradient magnetic filter has been shown in pilot tests to achieve and even exceed the recommended low level suspended solids in a practical and efficient industrial system. Such electromagnetic filters, when combined with good system chemistry, have achieved low single number parts per billion levels of several heavy metals with very high single-pass efficiencies

2. Installations of SNCR on bark-fired boilers

International Nuclear Information System (INIS)

1997-01-01

Experience has been collected from the twelve bark-fired boilers in Sweden with selective non catalytic reduction (SNCR) installations to reduce emissions of nitrogen oxides. Most of the boilers have slope grates, but there are also two boilers with cyclone ovens and two fluidized bed boilers. In addition to oil there are also possibilities to burn other fuel types in most boilers, such as sludge from different parts of the pulp and paper mills, saw dust and wood chips. The SNCR installations seems in general to be of simple design. In most installations the injection nozzles are located in existing holes in the boiler walls. The availability is reported to be good from several of the SNCR installations. There has been tube leakage in several boilers. The urea system has resulted in corrosion and in clogging of one oil burner. This incident has resulted in a decision not to use SNCR system with the present design of the system. The fuel has also caused operational problems with the SNCR system in several of the installations due to variations in the moisture content and often high moisture content in bark and sludge, causing temperature variations. The availability is presented to be high for the SNCR system at several of the plants, in two of them about 90 %. The results in NO x reduction vary between the installations depending on boiler, fuel and operation. The emissions are between 45 and 100 mg NO 2 /MJ fuel input and the NO x reduction rates are in most installations between 30 and 40 %, the lowest 20 and the highest 70 %. 13 figs, 3 tabs

3. [Emission characteristics of fine particles from grate firing boilers].

Science.gov (United States)

Wang, Shu-Xiao; Zhao, Xiu-Juan; Li, Xing-Hua; Wei, Wei; Hao, Ji-Ming

2009-04-15

Grate firing boilers are the main type of Chinese industrial boilers, which accounts for 85% of the industrial boilers and is one of the most important emission sources of primary air pollutants in China. In this study, five boilers in three cities were selected and tested to measure the emission characteristics of PM2.5, and gaseous pollutants were applied by a compact dilution sampling system, which was developed for this field study. Results showed that particles mass size distributions for the five industrial boilers presented single peak or double peak, former peaks near 0.14 microm and the later peaks after 1.0 microm; the cyclone dust remover and wet scrubber dust remover had effective removal efficiencies not only to PM2.5, but also to PM1.0; and under the condition of same control techniques, grate firing boiler with high capacity has less PM2.5 emission than the boiler with low capacity. In the PM2.5 collected from flue gases, SO4(2-) was the most abundant ion, accounted for 20%-40% of the PM2.5; and C was the most abundant element (7.5%-31.8%), followed by S (8.4%-18.7%). Carbon balance method was applied to calculate the emission factors of these pollutants. The emission factors of PM2.5, NO, and SO2 were in the range of 0.046-0.486 g x kg(-1), 1.63-2.47 g x kg(-1), 1.35-9.95 g x kg(-1) respectively. The results are useful for the emission inventory development of industrial boilers and the source analysis of PM2.5 in atmospheric environment.

4. AUTOMATIC CONTROL SYSTEM OF THE DRUM BOILER SUPERHEATED STEAM TEMPERATURE.

Directory of Open Access Journals (Sweden)

Juravliov A.A.

2006-04-01

Full Text Available The control system of the temperature of the superheated steam of the drum boiler is examined. Main features of the system are the PI-controller in the external control loop and introduction of the functional component of the error signal of the external control loop with the negative feedback of the error signal between the prescribed value of steam flowrate and the signal of the steam flowrate in the exit of the boiler in the internal control loop.

5. Brief introduction of GEF efficient industrial boiler project in China

Energy Technology Data Exchange (ETDEWEB)

Meijian, T.

1996-12-31

The present situation of installed industrial boilers, their efficiency and environmental impact are assessed. And the factors contribute to the low efficiency and serious pollution are summarized. Based on WB-assisted GEF project, {open_quotes}Efficient Industrial Boiler Project{close_quotes} aimed at CO{sub 2} mitigation in China, a series of effective measures to bring the GHG emission under control are addressed, in technology, system performance, and operation management aspects.

6. The ASME Boiler and Pressure Vessel Code: overview

International Nuclear Information System (INIS)

Farr, J.R.

1987-01-01

To become familiar with the Boiler and Pressure Vessel Code of the American Society of Mechanical Engineers, it is necessary to understand the history, organization, and operation of the Boiler Code Committee as well as to become familiar with the important aspects of each Section of the Code. This chapter will review the background and contents of the Code as well as give a review of the salient contents of most sections. (author)

7. Electric boilers for nuclear power plant in Liebstadt

International Nuclear Information System (INIS)

Anon.

1977-01-01

A type of electric boiler, two of which are to be supplied to the Liebstadt nuclear power plant by Sulzer, is described. They are to be used for start-up and as reserve for the normal steam supply. The mode of operation is that feed water is sprayed into a high tension electrode such that the falling water conducts the current to the earthed electrode. This type of boiler presents advantages in space requrements and enviromental factors. (JIW)

8. Electric boilers for nuclear power plant in Liebstadt

Energy Technology Data Exchange (ETDEWEB)

1977-11-29

A type of electric boiler, two of which are to be supplied to the Liebstadt nuclear power plant by Sulzer, is described. They are to be used for start-up and as reserve for the normal steam supply. The mode of operation is that feedwater is sprayed into a high tension electrode such that the falling water conducts the current to the earthed electrode. This type of boiler presents advantages in space requrements and enviromental factors.

9. Numerical modelling of a straw-fired grate boiler

DEFF Research Database (Denmark)

Kær, Søren Knudsen

2004-01-01

The paper presents a computational fluid dynamics (CFD) analysis of a 33 MW straw-fired grate boiler. Combustion on the grate plays akey-role in the analysis of these boilers and in this work a stand-alone code was used to provide inlet conditions for the CFD analysis. Modelpredictions were compa...... mixing in the furnace is a key issue leading to these problems. q 2003 Elsevier Ltd. All rights reserved....

10. Fracture analysis of tube boiler for physical explosion accident.

Science.gov (United States)

Kim, Eui Soo

2017-09-01

Material and failure analysis techniques are key tools for determining causation in case of explosive and bursting accident result from material and process defect of product in the field of forensic science. The boiler rupture generated by defect of the welding division, corrosion, overheating and degradation of the material have devastating power. If weak division of boiler burner is fractured by internal pressure, saturated vapor and water is vaporized suddenly. At that time, volume of the saturated vapor and water increases up to thousands of volume. This failure of boiler burner can lead to a fatal disaster. In order to prevent an explosion and of the boiler, it is critical to introduce a systematic investigation and prevention measures in advance. In this research, the cause of boiler failure is investigated through forensic engineering method. Specifically, the failure mechanism will be identified by fractography using scanning electron microscopes (SEM) and Optical Microscopes (OM) and mechanical characterizations. This paper presents a failure analysis of household welding joints for the water tank of a household boiler burner. Visual inspection was performed to find out the characteristics of the fracture of the as-received material. Also, the micro-structural changes such as grain growth and carbide coarsening were examined by optical microscope. Detailed studies of fracture surfaces were made to find out the crack propagation on the weld joint of a boiler burner. It was concluded that the rupture may be caused by overheating induced by insufficient water on the boiler, and it could be accelerated by the metal temperature increase. Copyright © 2017 Elsevier B.V. All rights reserved.

11. ANALISA KEHILANGAN ENERGI PADA FIRE TUBE BOILER KAPASITAS 10 TON

Directory of Open Access Journals (Sweden)

2015-06-01

12. Hybrid Intelligent Warning System for Boiler tube Leak Trips

Directory of Open Access Journals (Sweden)

Singh Deshvin

2017-01-01

Full Text Available Repeated boiler tube leak trips in coal fired power plants can increase operating cost significantly. An early detection and diagnosis of boiler trips is essential for continuous safe operations in the plant. In this study two artificial intelligent monitoring systems specialized in boiler tube leak trips have been proposed. The first intelligent warning system (IWS-1 represents the use of pure artificial neural network system whereas the second intelligent warning system (IWS-2 represents merging of genetic algorithms and artificial neural networks as a hybrid intelligent system. The Extreme Learning Machine (ELM methodology was also adopted in IWS-1 and compared with traditional training algorithms. Genetic algorithm (GA was adopted in IWS-2 to optimize the ANN topology and the boiler parameters. An integrated data preparation framework was established for 3 real cases of boiler tube leak trip based on a thermal power plant in Malaysia. Both the IWSs were developed using MATLAB coding for training and validation. The hybrid IWS-2 performed better than IWS-1.The developed system was validated to be able to predict trips before the plant monitoring system. The proposed artificial intelligent system could be adopted as a reliable monitoring system of the thermal power plant boilers.

13. Feasibility of recovery boiler in paper and pulp industry

International Nuclear Information System (INIS)

Rashid, H.

2010-01-01

in this paper feasibility of recovery boiler in terms of economics and environmental impacts in studied. Recovery boilers are employed in the pulp and paper industry where the cooking agent is recovered by burning black liquor. Cooking agent is exhausted due to the absorption of lignin (a burnable component) in cooking agent in the process of straw cooking. The process of recovery boiler is to remove lignin by combustion from black liquor, and heat is produced during the combustion of lignin which is used to produce steam. Recovery boiler is economical as it is recovering valuable chemicals and steam is produced as a byproduct. Steam from recovery boiler is also used for concentrating weak black liquor to concentrated black liquor recovering 50% of the utility water being used at the plant. The regenerated water in the form of foul condensate is reused in the process. The recovery of hazardous chemicals also reduces load of environmental pollution. Which otherwise can pollute the water reservoirs, and regeneration of water makes it environmentally friendly plant. Construction and challenges in operation of recovery boiler such as smelt-water explosion are also discussed in this paper. (author)

14. Failure analysis of boiler tubes in lakhra coal power plant

International Nuclear Information System (INIS)

Shah, A.; Baluch, M.M.; Ali, A.

2010-01-01

Present work deals with the failure analysis of a boiler tube in Lakhra fluidized bed combustion power station. Initially, visual inspection technique was adopted to analyse the fractured surface. Detailed microstructural investigations of the busted boiler tube were carried out using light optical microscope and scanning electron microscope. The hardness tests were also performed. A 50 percent decrease in hardness of intact portion of the tube material and from area adjacent to failure was measured, which was found to be in good agreement with the wall thicknesses measured of the busted boiler tube i.e. 4 mm and 2 mm from unaffected portion and ruptured area respectively. It was concluded that the major cause of failure of boiler tube is erosion of material which occurs due the coal particles strike at the surface of the tube material. Since the temperature of boiler is not maintained uniformly. The variations in boiler temperature can also affect the material and could be another reason for the failure of the tube. (author)

15. 46 CFR 52.01-2 - Adoption of section I of the ASME Boiler and Pressure Vessel Code.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Adoption of section I of the ASME Boiler and Pressure...) MARINE ENGINEERING POWER BOILERS General Requirements § 52.01-2 Adoption of section I of the ASME Boiler and Pressure Vessel Code. (a) Main power boilers and auxiliary boilers shall be designed, constructed...

16. Seasonal performance and energy costs of oil or gas-fired boilers and furnaces

Energy Technology Data Exchange (ETDEWEB)

Berlad, A.L.; Lin, H.C.; Batey, J.; Salzano, F.J.; Yu, W.S.; Hoppe, R.J.; Allen, T.

1977-03-01

The seasonal operating cost of a small oil or gas-fired boiler or furnace depends upon the intrinsic merits of the device itself, the appropriateness of its capacity and cycle characteristics to the imposed load conditions, the weather characteristics and heat loss characteristics of the building being heated, and the control philosophy employed. The current study provides the bases for comparing quantitatively the seasonal operating costs of various specific space heating and/or domestic hot water systems, as influenced by the device specifics and device interaction with the space conditioned system that it serves. The resulting formalism is applied to various space-heating systems. Quantitative cost comparisons are presented.

17. DBSSP - A computer program for simulation of controlled circulation boiler and natural circulation boiler start up behavior

International Nuclear Information System (INIS)

Li Bin; Chen Tingkuan; Yang Dong

2005-01-01

In this paper, a computer program, Drum Boiler Start-up Simulation Program (DBSSP), is developed for simulating the start up behavior of controlled circulation and natural circulation boilers. The mathematical model developed here is based on the first principles of mass, energy and momentum conservations. In the boiler model, heat transfer in the waterwall, the superheater, the reheater and the economizer is simulated by the distributing parameter method, while heat transfer in the drum and the downcomer is simulated by lumped parameter analysis. The program can provide detailed flow and thermodynamic characteristics of the boiler components. The development of this program is based only on design data, so it can be used for any subcritical, controlled or natural circulation boiler. The simulation results were compared with experimental measurements, and good agreements between them were found. This program is expected to be useful for predicting the characteristics and the performance of controlled circulation and natural circulation boilers during the start up process. It also can be used to optimize a start up system for minimum start up time

18. Orion Boiler Plate Airdrop Test System

Science.gov (United States)

Machin, Ricardo A.; Evans, Carol T.

2013-01-01

On the 29th of February 2012 the Orion Capsule Parachute Assembly System (CPAS) project attempted to perform an airdrop test of a boilerplate test article for the second time. The first attempt (Cluster Development Test 2, July 2008) to deliver a similar boilerplate from a C-17 using the Low Velocity Air Drop (LVAD) technique resulted in the programmer parachute failing to properly inflate, the test article failing to achieve the desired test initiation conditions, and the test article a total loss. This paper will pick up where the CDT-2 failure investigation left off, describing the test technique that was adopted, and outline the modeling that was performed to gain confidence that the second attempt would be successful. The second boiler plate test (Cluster Development Test 3-3) was indeed a complete success and has subsequently been repeated several times, allowing the CPAS project to proceed with the full scale system level development testing required to integrate the hardware to the first Entry Flight Test vehicle as well as go into the Critical Design Review with minimum risk and a mature design.

19. Computations of NOx emissions of domestic boilers

Energy Technology Data Exchange (ETDEWEB)

Thevenin, D. [Ecole Centrale de Paris, 92 - Chatenay-Malabry (France). EM2C Lab.; Gicquel, O.; Darabiha, N.

2001-07-01

Due to severe regulations concerning pollutant emissions, practical devices using combustion to release energy must be designed from the start using accurate, predictive numerical tools. A partially premixed methane/air flame in a two-dimensional configuration is investigated in this work. This configuration is close to those used in real domestic gas boilers. The flame structure and flow pattern are calculated using complex chemistry and detailed transport models. A post-processing method is then used to predict NO emission. Computations are performed for two configurations. The two cases have the same primary and secondary mass flow-rates and equivalence ratio. The only difference between them is the introduction of an insert inside the primary injector. Both results have been compared to measurements. Calculations are found to be in good agreement with the flame shapes observed experimentally. The classical burner shows a Bunsen-type flame while the one with an insert has a totally different shape (butterfly-type flame). NO emission levels are also well predicted in both configurations. The butterfly flame induces a reduction in NO emission. This reduction seems to be due to the increased mixing between the burnt gases and the secondary air jet, which homogenizes the temperature distribution and reduces the maximum temperature. (orig.)

20. Steam generators and waste heat boilers for process and plant engineers

CERN Document Server

Ganapathy, V

2014-01-01

Incorporates Worked-Out Real-World ProblemsSteam Generators and Waste Heat Boilers: For Process and Plant Engineers focuses on the thermal design and performance aspects of steam generators, HRSGs and fire tube, water tube waste heat boilers including air heaters, and condensing economizers. Over 120 real-life problems are fully worked out which will help plant engineers in evaluating new boilers or making modifications to existing boiler components without assistance from boiler suppliers. The book examines recent trends and developments in boiler design and technology and presents novel idea

1. Performance of a pellet boiler fired with agricultural fuels

International Nuclear Information System (INIS)

Carvalho, Lara; Wopienka, Elisabeth; Pointner, Christian; Lundgren, Joakim; Verma, Vijay Kumar; Haslinger, Walter; Schmidl, Christoph

2013-01-01

Highlights: ► Performance evaluation of a pellet boiler operated with different agricultural fuels. ► Agricultural fuels could be burn in the tested boiler for a certain period of time. ► All the fuels (except straw and Sorghum) satisfied the European legal requirements. ► Boilers for burning agricultural fuels should have a flexible control system. - Abstract: The increasing demand for woody biomass increases the price of this limited resource, motivating the growing interest in using woody materials of lower quality as well as non-woody biomass fuels for heat production in Europe. The challenges in using non-woody biomass as fuels are related to the variability of the chemical composition and in certain fuel properties that may induce problems during combustion. The objective of this work has been to evaluate the technical and environmental performance of a 15 kW pellet boiler when operated with different pelletized biomass fuels, namely straw (Triticum aestivum), Miscanthus (Miscanthus × giganteus), maize (Zea mays), wheat bran, vineyard pruning (from Vitis vinifera), hay, Sorghum (Sorghum bicolor) and wood (from Picea abies) with 5% rye flour. The gaseous and dust emissions as well as the boiler efficiency were investigated and compared with the legal requirements defined in the FprEN 303-5 (final draft of the European standard 303-5). It was found that the boiler control should be improved to better adapt the combustion conditions to the different properties of the agricultural fuels. Additionally, there is a need for a frequent cleaning of the heat exchangers in boilers operated with agricultural fuels to avoid efficiency drops after short term operation. All the agricultural fuels satisfied the legal requirements defined in the FprEN 303-5, with the exception of dust emissions during combustion of straw and Sorghum. Miscanthus and vineyard pruning were the best fuels tested showing comparable emission values to wood combustion

2. Ultra-Supercritical Pressure CFB Boiler Conceptual Design Study

Energy Technology Data Exchange (ETDEWEB)

Zhen Fan; Steve Goidich; Archie Robertson; Song Wu

2006-06-30

Electric utility interest in supercritical pressure steam cycles has revived in the United States after waning in the 1980s. Since supercritical cycles yield higher plant efficiencies than subcritical plants along with a proportional reduction in traditional stack gas pollutants and CO{sub 2} release rates, the interest is to pursue even more advanced steam conditions. The advantages of supercritical (SC) and ultra supercritical (USC) pressure steam conditions have been demonstrated in the high gas temperature, high heat flux environment of large pulverized coal-fired (PC) boilers. Interest in circulating fluidized bed (CFB) combustion, as an alternative to PC combustion, has been steadily increasing. Although CFB boilers as large as 300 MWe are now in operation, they are drum type, subcritical pressure units. With their sizes being much smaller than and their combustion temperatures much lower than those of PC boilers (300 MWe versus 1,000 MWe and 1600 F versus 3500 F), a conceptual design study was conducted herein to investigate the technical feasibility and economics of USC CFB boilers. The conceptual study was conducted at 400 MWe and 800 MWe nominal plant sizes with high sulfur Illinois No. 6 coal used as the fuel. The USC CFB plants had higher heating value efficiencies of 40.6 and 41.3 percent respectively and their CFB boilers, which reflect conventional design practices, can be built without the need for an R&D effort. Assuming construction at a generic Ohio River Valley site with union labor, total plant costs in January 2006 dollars were estimated to be \$1,551/kW and \$1,244/kW with costs of electricity of \$52.21/MWhr and \$44.08/MWhr, respectively. Based on the above, this study has shown that large USC CFB boilers are feasible and that they can operate with performance and costs that are competitive with comparable USC PC boilers.

3. Research report for fiscal 1988. Researches into energy conservation centering about boiler facilities; 1998 nendo boiler setsubi wo chushin to shita sho energy chosa hokokusho

Energy Technology Data Exchange (ETDEWEB)

NONE

1999-03-01

Boiler facilities in Vietnam were subjected to a feasibility study in a project for making positive use of joint implementation and clean development mechanisms which are prescribed as flexible measures by COP3 (Third Session of the Conference of the Parties to the United Nations Framework Convention on Climate Change). Many were small and old, and found to require improvement in terms of operating efficiency and energy conservation. Measures will be taken to wholly replace 159 boilers and partially modify 160, out of the total of 399 subjected to the study. It is expected that there will be a reduction of 173.8-thousand kiloliters per year when converted into fuel oil and a reduction per year of 599.8 kilotons in terms of CO2 gas. It was also concluded that co-generation plants judged high in energy conservation be introduced into 6 factories subjected to the study. Since energy conservation improvement and co-generation plant introduction will both contribute to the prevention of global warming and since there is commonality between the two in terms of facilities involved, it is preferred that the two be carried out under one and the same project. The enterprise will cost 11,544-million yen in total, and 791.5 kilotons/year of CO2 gas will be reduced. Since Vietnam hopes to be financed by Japan, extension of credit in yen will be the optimum policy. (NEDO)

4. Experimental investigation and mathematical modelling of wood combustion in a moving grate boiler

International Nuclear Information System (INIS)

Zhang, Xiaohui; Chen, Qun; Sharifi, Vida; Swithenbank, Jim; Bradford, Richard

2010-01-01

The use of biomass to generate energy offers significant environmental advantages for the reduction in emissions of greenhouse gases. The main objective of this study was to investigate the performance of a small scale biomass heating plant: i.e. combustion characteristics and emissions. An extensive series of experimental tests was carried out at a small scale residential biomass heating plant i.e. wood chip fired boiler. The concentrations of CO, NO x , particulate matter in the flue gas were measured. In addition, mathematical modelling work using FLIC and FLUENT codes was carried out in order to simulate the overall performance of the wood fired heating system. Results showed that pollutant emissions from the boiler were within the relative emission limits. Mass concentration of CO emission was 550-1600 mg/m 3 (10% O 2 ). NO x concentration in the flue gas from the wood chips combustion varied slightly between 28 and 60 ppmv. Mass concentration of PM 10 in the flue gas was 205 mg/m 3 (10% O 2 ) The modelling results showed that most of the fuel was burnt inside the furnace and little CO was released from the system due to the high flue gas temperature in the furnace. The injection of the secondary air provided adequate mixing and favourable combustion conditions in the over-bed chamber in the wood chips fired boiler. This study has shown that the use of wood heating system result in much lower CO 2 emissions than from a fossil fuel e.g. coal fired heating system. (author)

5. Sodium reflux pool-boiler solar receiver on-sun test results

Energy Technology Data Exchange (ETDEWEB)

Andraka, C E; Moreno, J B; Diver, R B; Moss, T A [Oak Ridge National Lab., TN (United States)

1992-06-01

6. Identification of boiler tube leak in PHWR by measuring short lived radioisotope Iodine-134 in boiler water using gamma spectrometric techniques

International Nuclear Information System (INIS)

Pal, P.K.; Bohra, R.C.

2015-01-01

The boiler tube made up of Monel-400 of RAPS-2 has failed on few occasions. Due to the failure of boiler tube, the active heavy water enters into boiler and feed water leading to contamination of radioactivity in secondary water circuit. The identification of boiler tube failure was done by measuring gamma ray activity of Iodine-134 in the boiler water with sample using gamma spectrometry with high purity germanium detector. In order to increase the sensitivity of the method 5 liters of Boiler water sample was passed through a plastic column containing 40 ml of anion resin and 10 ml of activated charcoal to capture the isotopes of Iodine in the anionic form and molecular form. Samples were collected from all 8 Boilers of RAPS-2. The activity of 134 I was shown only by Boiler - 5. No other boilers showed any activity of 134 I. This indicated that Boiler - 5 had leaky tubes. The leaky hairpin of boiler - 5 was identified by measuring Tritium and IP in the riser and down comer of all 10 HXs. On the basis of Tritium and IP result, HX-7 was identified as leaky hairpin. (author)

7. Process for start-up and slack period operation of fully charged boilers, e. g. of coal pressure gasification plants, and boiler system to carry out the process

Energy Technology Data Exchange (ETDEWEB)

Meyer-Kahrweg, H

1978-10-19

For the start-up and slack period of fully charged boilers hot water of e.g. 180/sup 0/C from a high pressure heater which is fed by a start-up boiler is used. In the first instance the boiler, its preheater and the vaporizer are filled with hot water from the start-up boiler until a medium water level is obtained. Subsequently water from the water separator is recycled through the preheater and the boiler by forced circulation and it is heated up to the hot water temperature by the start-up boiler. After the desired temperature has been reached the pressure combustion is ignited and the circulation through the preheater is interrupted by reversing to direct feed back. A considerable shortening of the start-up time is achieved because no heat is released to the condensation water in the boiler system as is done usually.

8. Active brickworks - phase I[For application in biofuel boilers]; Aktiva murverk - etapp I

Energy Technology Data Exchange (ETDEWEB)

Wrangensten, Lars; Schuster, Robert; Ingman, Rolf; Sendelius, Mikael; Ehleskog, Rickard [AaF-Energikonsult AB, Stockholm (Sweden)

2003-10-01

This report is the first step of the R and D project 'Active brickworks' within the program 'Possibilities to improve the operation conditions in industrial bark boilers by optimised combustion control'. Good high temperature resistance is one of the major characteristics of ceramics. They are based on quartz and aluminium oxide, an attachment component (acid or cement) and also different types of additives which, together with the heating treatment, gives the ceramic materials their features. The brickwork in a boiler has several assignments. First of all resistance to corrosion, erosion and protection against fouling of the water tube walls, but also to significant affect the combustion process by energy saving features and heating radiation. This project has been focused on the last named features, namely to be able to make a more active choice of brickwork in order to utilise the ceramic features and hereby making it possible to lower the combustion process emissions. The material samples received from the manufactures have been tested in a small-scale laboratory rig. Features investigated are emissivity/reflection, heat conductivity and heat capacity. Mathematic simulations have also been performed with a representative type boiler model in order to make conclusions concerning how the results can be transformed to and applied in a real full-scale boiler. The most important designing case for ceramics in bark boilers is when boiler load rapidly increases or during a fast fuel moisture change from dry to wet fuel. It has been concluded in the study that that the ceramic walls in a boiler should be divided into different layers. The outer layer in the ceiling and sidewalls of the drying zone must consist of highly insulating material in order to get a high temperature of heating surfaces close to the furnace. To store heat during load transients the heating surfaces must have high emissivity factor and good heating capacity. From this point of

9. A statistical estimator for the boiler power and its related parameters

International Nuclear Information System (INIS)

Tang, H.

2001-01-01

To determine the boiler power accurately is important for both controlling the plant and maximizing the plant productivity. There are two computed boiler powers for each boiler. They are steam based boiler power and feedwater based boiler power. The steam based boiler power is computed as the enthalpy difference between the feedwater enthalpy and the boiler steam enthalpy. The feedwater based boiler power is computed as enthalpy absorbed by the feedwater. The steam based boiler power is computed in RRS program and used in calibrating the measured reactor power, while the feedwater based boiler power is computed in CSTAT program and used for indication. Since the steam based boiler power is used as feedback in the reactor control, it is chosen to be the one estimated in this work. Because the boiler power employs steam flow, feedwater flow and feedwater temperature measurements, and because any measurement contains constant or drifting noise and bias, the reconciliation and rectification procedures are needed to determine the boiler power more accurately. A statistic estimator is developed to perform the function of data reconciliation, gross error detection and instruments performance monitoring

10. Analysis of a waste-heat boiler by CFD simulation

Energy Technology Data Exchange (ETDEWEB)

Yang, Yongziang; Jokilaakso, A. [Helsinki Univ. of Technology, Otaniemi (Finland)

1996-12-31

Waste-heat boilers play important roles in the continuous operation of a smelter and in the conservation of energy. However, the fluid flow and heat transfer behaviour has not been well studied, concerning the boiler performance and design. This presentation describes simulated gas flow and heat transfer of a waste-heat boiler in the Outokumpu copper flash smelting process. The governing transport equations for the conservation of mass, momentum and enthalpy were solved with a commercial CFD-code PHOENICS. The standard k-{epsilon} turbulence model and a composite-flux radiation model were used in the computations. The computational results show that the flow is strongly recirculating and distinctly three-dimensional in most part of the boiler, particularly in the radiation section. The predicted flow pattern and temperature distribution were in a good agreement with laboratory models and industrial measurements. The results provide detailed information of flow pattern, the temperature distribution and gas cooling efficiency. The CFD proved to be a useful tool in analysing the boiler operation. (author)

11. How much Energy is Embodied in your Central Heating Boiler?

Science.gov (United States)

Koubogiannis, D.; Nouhou, C.

2016-11-01

Life Cycle Analysis (LCA) is an important tool in current research to quantitatively assess energy consumption and environmental impact of a building. In the context of LCA, the Embodied Energy (EE) related to the building and the corresponding Embodied CO2 emissions are valuable data. In such a case, these data concern the constitutive materials of the building and any subsystem, component or equipment in it. Usually, after calculating the mass of these materials, embodied energy values are estimated multiplying them by the corresponding EE coefficients concerning the production of these materials (EEMP). However, apart from transportation energy costs, another part of EE is that consumed for the manufacturing of any item as a finished product. The present work focuses on the manufacturing EE (EEMFG) of central heating boilers in Hellenic dwellings. Six typical boilers of different types are studied. Each of them is analyzed to its constitutive materials and its EEMP is estimated. For four of them, the boiler house where it was constructed in Greece was visited and data were collected. Based on them the corresponding boiler EEMFG values are estimated. The results concerning the EE for material production and manufacturing, as well as the results concerning the corresponding ECO2 values are discussed and assessed. Benchmark values correlating EE and ECO2 with the mass or the heat rate of the boiler are extracted.

12. Slagging in a pulverised-coal-fired boiler

Energy Technology Data Exchange (ETDEWEB)

Devir, G.P.; Pohl, J.H.; Creelman, R.A. [University of Queensland, St. Lucia, Qld. (Australia). Dept. of Chemical Engineering

2000-07-01

This paper describes a technique to evaluate the severity of slagging of a coal in a pulverised-coal-fired boiler. There are few data in the literature on the nature of in-situ boiler slags, their rate of growth and/or their strength properties relevant to sootblowing. The latter is thought to be of more concern to boiler operators and gives rise to the significance of selecting suitable strength tests. As well as standardised methods for characterising pulverised coal performance in a boiler, several novel and less popular techniques are discussed in detail. A suite of three sub-bituminous coals from the Callide Coalfields, Biloela (600 km north of Brisbane), has been selected for slagging tests in the 350 MW{sub e} units of Callide 'B' power station. Disposable air-cooled mild steel slagging probes have been constructed to simulate the conditions for deposit formation in the boiler region. To date, tests for one of these coals has been completed and preliminary results are presented. Once testing for the remaining coals has been completed, it is anticipated that the differences exhibited in deposit growth and strength may be correlated with typical variations in physical and chemical properties of the pulverised coal.

13. Analysis of a waste-heat boiler by CFD simulation

Energy Technology Data Exchange (ETDEWEB)

Yang, Yongziang; Jokilaakso, A [Helsinki Univ. of Technology, Otaniemi (Finland)

1997-12-31

Waste-heat boilers play important roles in the continuous operation of a smelter and in the conservation of energy. However, the fluid flow and heat transfer behaviour has not been well studied, concerning the boiler performance and design. This presentation describes simulated gas flow and heat transfer of a waste-heat boiler in the Outokumpu copper flash smelting process. The governing transport equations for the conservation of mass, momentum and enthalpy were solved with a commercial CFD-code PHOENICS. The standard k-{epsilon} turbulence model and a composite-flux radiation model were used in the computations. The computational results show that the flow is strongly recirculating and distinctly three-dimensional in most part of the boiler, particularly in the radiation section. The predicted flow pattern and temperature distribution were in a good agreement with laboratory models and industrial measurements. The results provide detailed information of flow pattern, the temperature distribution and gas cooling efficiency. The CFD proved to be a useful tool in analysing the boiler operation. (author)

14. Computational Modeling and Assessment Of Nanocoatings for Ultra Supercritical Boilers

Energy Technology Data Exchange (ETDEWEB)

Gandy, David W. [Electric Power Research Institute, Inc., Palo Alto, CA (United States); Shingledecker, John P. [Electric Power Research Institute, Inc., Palo Alto, CA (United States)

2011-05-11

Coal-fired power plants are a significant part of the nation's power generating capacity, currently accounting for more than 55% of the country's total electricity production. Extending the reliable lifetimes of fossil fired boiler components and reducing the maintenance costs are essential for economic operation of power plants. Corrosion and erosion are leading causes of superheater and reheater boiler tube failures leading to unscheduled costly outages. Several types of coatings and weld overlays have been used to extend the service life of boiler tubes; however, the protection afforded by such materials was limited approximately one to eight years. Power companies are more recently focused in achieving greater plant efficiency by increasing steam temperature and pressure into the advanced-ultrasupercritical (A-USC) condition with steam temperatures approaching 760°C (1400°F) and operating pressures in excess of 35MPa (5075 psig). Unfortunately, laboratory and field testing suggests that the resultant fireside environment when operating under A-USC conditions can potentially cause significant corrosion to conventional and advanced boiler materials1-2. In order to improve reliability and availability of fossil fired A-USC boilers, it is essential to develop advanced nanostructured coatings that provide excellent corrosion and erosion resistance without adversely affecting the other properties such as toughness and thermal fatigue strength of the component material.

15. Investing in efficient industrial boiler systems in China and Vietnam

International Nuclear Information System (INIS)

Yang Ming; Dixon, Robert K.

2012-01-01

Energy efficiency in industrial boiler steam systems can be very low due to old technologies, improper design and non-optimal operation of the steam systems. Solutions include efficiency assessments and investments in steam system optimizations, education and training for operators of the systems. This paper presents case studies on assessing and investing in boiler steam systems in China and Vietnam. Methodologies and approaches for data collection and analyses were designed specifically for each of the two countries. This paper concludes: (1) investing in energy efficiency in industrial boiler steam system in China and Vietnam are cost effective; (2) government should not sent national energy efficiency standards lower than that of energy companies or energy equipment manufactures. - Highlights: ► GEF successfully catalyzed investment in industrial energy efficiency boilers in China in 1990s. ► With about \$100 million of investment by the GEF/World Bank/Chinese government, the project will mitigate 40 million tons of CO 2 by 2019. ► This generated lowest unit cost of carbon reduction in the world: about \$2.5 per ton of CO 2 mitigation. ► Investing in energy efficiency in industrial boiler steam system today in Vietnam will be the same cost effective as in China: \$2.1 per ton of CO 2 mitigation.

16. New configurations of a heat recovery absorption heat pump integrated with a natural gas boiler for boiler efficiency improvement

International Nuclear Information System (INIS)

Qu, Ming; Abdelaziz, Omar; Yin, Hongxi

2014-01-01

Highlights: • Thermal and heat transfer models of absorption heat pumps driven by exhaust gas, hot water, or natural gas. • Natural gas boiler combustion model. • Heat exchanger for condensing. • Experimental data of a hot water absorption heat pump. • Economic assessment of heat recovery absorption heat pump for improving natural gas boilers. - Abstract: Conventional natural gas-fired boilers exhaust flue gas direct to the atmosphere at 150–200 °C, which, at such temperatures, contains large amount of energy and results in relatively low thermal efficiency ranging from 70% to 80%. Although condensing boilers for recovering the heat in the flue gas have been developed over the past 40 years, their present market share is still less than 25%. The major reason for this relatively slow acceptance is the limited improvement in the thermal efficiency of condensing boilers. In the condensing boiler, the temperature of the hot water return at the range of 50–60 °C, which is used to cool the flue gas, is very close to the dew point of the water vapor in the flue gas. Therefore, the latent heat, the majority of the waste heat in the flue gas, which is contained in the water vapor, cannot be recovered. This paper presents a new approach to improve boiler thermal efficiency by integrating absorption heat pumps with natural gas boilers for waste heat recovery (HRAHP). Three configurations of HRAHPs are introduced and discussed. The three configurations are modeled in detail to illustrate the significant thermal efficiency improvement they attain. Further, for conceptual proof and validation, an existing hot water-driven absorption chiller is operated as a heat pump at operating conditions similar to one of the devised configurations. An overall system performance and economic analysis are provided for decision-making and as evidence of the potential benefits. These three configurations of HRAHP provide a pathway to achieving realistic high-efficiency natural

17. On synthesis and optimization of steam system networks. 1. Sustained boiler efficiency

CSIR Research Space (South Africa)

Majozi, T

2010-08-01

Full Text Available situations. This paper presents a process integration technique for network synthesis using conceptual and mathematical analysis without compromising boiler efficiency. It was found that the steam flow rate to the HEN could be reduced while maintaining boiler...

18. Lagisza, world's largest CFB boiler, begins commercial operation

Energy Technology Data Exchange (ETDEWEB)

Nuortimo, K. [Foster Wheeler, Varkaus (Finland)

2010-04-15

Early operating experience with the Lagisza circulating fluidised bed (CFB) boiler in Poland - the world's largest such boiler to date, and also the first one with supercritical steam conditions - has been positive. 3 figs., 4 tabs.

19. Evaluation of iron aluminide weld overlays for erosion - corrosion resistant boiler tube coatings in low NO{sub x} boilers

Energy Technology Data Exchange (ETDEWEB)

DuPont, J.N.; Banovic, S.W.; Marder, A.R. [Lehigh Univ., Bethlehem, PA (United States)

1996-08-01

Low NOx burners are being installed in many fossil fired power plants in order to comply with new Clean Air Regulations. Due to the operating characteristics of these burners, boiler tube sulfidation corrosion is often enhanced and premature tube failures can occur. Failures due to oxidation and solid particle erosion are also a concern. A program was initiated in early 1996 to evaluate the use of iron aluminide weld overlays for erosion/corrosion protection of boiler tubes in Low NOx boilers. Composite iron/aluminum wires will be used with the Gas Metal Arc Welding (GMAW) process to prepare overlays on boiler tubes steels with aluminum contents from 8 to 16wt%. The weldability of the composite wires will be evaluated as a function of chemical composition and welding parameters. The effect of overlay composition on corrosion (oxidation and sulfidation) and solid particle erosion will also be evaluated. The laboratory studies will be complemented by field exposures of both iron aluminide weld overlays and co-extruded tubing under actual boiler conditions.

20. DYMEL code for prediction of dynamic stability limits in boilers

International Nuclear Information System (INIS)

Deam, R.T.

1980-01-01

Theoretical and experimental studies of Hydrodynamic Instability in boilers were undertaken to resolve the uncertainties of the existing predictive methods at the time the first Advanced Gas Cooled Reactor (AGR) plant was commissioned. The experiments were conducted on a full scale electrical simulation of an AGR boiler and revealed inadequacies in existing methods. As a result a new computer code called DYMEL was developed based on linearisation and Fourier/Laplace Transformation of the one-dimensional boiler equations in both time and space. Beside giving good agreement with local experimental data, the DYMEL code has since shown agreement with stability data from the plant, sodium heated helical tubes, a gas heated helical tube and an electrically heated U-tube. The code is now used widely within the U.K. (author)

1. Engineering and economic aspects of centalized heating from nuclear boilers

International Nuclear Information System (INIS)

Emel'yanov, I.Ya.; Baturov, B.B.; Korytnikov, V.P.; Koryakin, Yu.I.; Chernyaev, V.A.; Kovylyanskij, Ya.A.; Galaktionov, I.V.

1979-01-01

Some engineering and economic aspects for deployment of centralized nuclear boilers (NB) in the USSR are considered. Engineering, maintenance and economic features of NB as compared to organic-fuelled boilers and nuclear thermal power plants are discussed. Among major factors governing economic efficiency of NB underlined are oraganic fuel costs, reactor unit power, location relative to heat-consuming centres and capacity factor. It is concluded that NB can be economical for heating large consumers (more than 1500 G kal/hr). At the periphery NB can be competitive already at reactor unit power of several MWth. The development of HTGR type reactor-based nuclear-chemical boilers and lines for heat transport in a chemically bound state (e.g., CH 4 → H 2 +CO 2 +CO → CH 4 ) opens the way for a substantial breakthrow in the centralized NB efficiency

2. COAL-FIRED UTILITY BOILERS: SOLVING ASH DEPOSITION PROBLEMS; TOPICAL

International Nuclear Information System (INIS)

Christopher J. Zygarlicke; Donald P. McCollor; Steven A. Benson; Jay R. Gunderson

2001-01-01

The accumulation of slagging and fouling ash deposits in utility boilers has been a source of aggravation for coal-fired boiler operators for over a century. Many new developments in analytical, modeling, and combustion testing methods in the past 20 years have made it possible to identify root causes of ash deposition. A concise and comprehensive guidelines document has been assembled for solving ash deposition as related to coal-fired utility boilers. While this report accurately captures the current state of knowledge in ash deposition, note that substantial research and development is under way to more completely understand and mitigate slagging and fouling. Thus, while comprehensive, this document carries the title ''interim,'' with the idea that future work will provide additional insight. Primary target audiences include utility operators and engineers who face plant inefficiencies and significant operational and maintenance costs that are associated with ash deposition problems. Pulverized and cyclone-fired coal boilers are addressed specifically, although many of the diagnostics and solutions apply to other boiler types. Logic diagrams, ash deposit types, and boiler symptoms of ash deposition are used to aid the user in identifying an ash deposition problem, diagnosing and verifying root causes, determining remedial measures to alleviate or eliminate the problem, and then monitoring the situation to verify that the problem has been solved. In addition to a step-by-step method for identifying and remediating ash deposition problems, this guideline document (Appendix A) provides descriptions of analytical techniques for diagnostic testing and gives extensive fundamental and practical literature references and addresses of organizations that can provide help in alleviating ash deposition problems

3. Mekanisme Proses Pemanasan Air Di Dalam Boiler Dengan Mempergunakan Heater Tambahan Untuk Efisiensi Pembakaran

OpenAIRE

Helmon Sihombing

2010-01-01

Pada proses pemanasan air, air yang berasal dari raw water (air tanah) tidak langsung dibakar didalam boiler. dalam hal ini digunakan peralatan instrumen Deaerator dan economizer yang berfungsi untuk pemanasan awal sebelum dibakar didalam boiler. Fungsi deaerator dan economizer ini adalah sebagai komponen pembantu untuk memanaskan air sebelum dibakar didalam boiler. Apabila pemanasan air langsung dilakukan didalam boiler maka akan membutuhkan waktu yang cukup lama dan menggunakan bahan b...

4. High Efficiency - Reduced Emissions Boiler Systems for Steam, Heat, and Processing

Science.gov (United States)

2012-07-01

enable energy saving necessary for obtaining Energy Star certification for the whole boiler system. Widespread boiler control updates could be possible...adaptability to different boiler and oil/gas burner configurations, and extensibility to operation with nonconventional fuels (e.g., biogas and syngas...typically operating below or slightly above 80%. Higher efficiency improvements can certainly be obtained via boiler replacement and adoption of

5. Modelling of a one pass smoke tube boiler

DEFF Research Database (Denmark)

Karstensen, Claus M. S.; Sørensen, Kim

2004-01-01

A nonlinear state-space model with five states describing a one pass smoke tube boiler has been formulated. By means of mass- and energy-balance the model describes the dynamics of the Furnace, the Convection Zone and the Water/Steam Part and the three sub models are merged into an overall model....... The model is further linearized for use in a linear control design. The simulations have been carried out by means of MATLAB/SIMULINK and the models have been verified with measurements from a full scale boiler plant. Parameters in the model that are difficult to calculate have been estimated and the method...

6. Heat losses in power boilers caused by thermal bridges

Directory of Open Access Journals (Sweden)

Kocot Monika

2017-01-01

Full Text Available In this article the analysis of heat losses caused by thermal bridges that occur in the steam boiler OP-140 is presented. Identification of these bridges were conducted with use of thermographic camera. Heat losses were evaluated based on methodology of VDI 4610 standard, but instead of its simplified equations, criterial equations based on Nusselt number were used. Obtained values of annual heat losses and heat flux density corresponding to the fully insulated boiler surfaces were compared to heat losses generated by thermal bridges located in the same areas. The emphasis is put on the role of industrial insulation in heat losses reduction.

7. High Temperature Corrosion in Biomass-Fired Boilers

DEFF Research Database (Denmark)

Henriksen, Niels; Montgomery, Melanie; Hede Larsen, Ole

2002-01-01

condense on superheater components. This gives rise to specific corrosion problems not previously encountered in coal-fired power plants. The type of corrosion attack can be directly ascribed to the composition of the deposit and the metal surface temperature. To avoid such high corrosion rates, woodchip...... has also been utilised as a fuel. Combustion of woodchip results in a smaller amount of ash, and potassium and chlorine are present in lesser amounts. However, significant corrosion rates were still seen. A case study of a woodchip fired boiler is described. The corrosion mechanisms in both straw-fired...... and woodchip fired boilers are discussed....

8. A METHOD FOR EXERGY ANALYSIS OF SUGARCANE BAGASSE BOILERS

Directory of Open Access Journals (Sweden)

CORTEZ L.A.B.

1998-01-01

Full Text Available This work presents a method to conduct a thermodynamic analysis of sugarcane bagasse boilers. The method is based on the standard and actual reactions which allows the calculation of the enthalpies of each process subequation and the exergies of each of the main flowrates participating in the combustion. The method is presented using an example with real data from a sugarcane bagasse boiler. A summary of the results obtained is also presented together based on the 1st Law of Thermodynamics analysis, the exergetic efficiencies, and the irreversibility rates. The method presented is very rigorous with respect to data consistency, particularly for the flue gas composition.

9. 46 CFR 78.33-1 - Repairs of boiler and pressure vessels.

Science.gov (United States)

2010-10-01

... 46 Shipping 3 2010-10-01 2010-10-01 false Repairs of boiler and pressure vessels. 78.33-1 Section... OPERATIONS Reports of Accidents, Repairs, and Unsafe Equipment § 78.33-1 Repairs of boiler and pressure vessels. (a) Before making any repairs to boilers or unfired pressure vessels, the chief engineer shall...

10. Pencegahan Korosi Dengan Boiler Water Treatment (Bwt) Pada Ketel Uap Kapal.

OpenAIRE

Suleman, Suleman

2007-01-01

This paper explained about a using of Boiler Water Treatment (BWT) as corrosion protection for boiler on ship. BWT used as addition on boiler water, which used destilat water. As experiment results, BWT used on destilat water and destilat - seawater mixed given not koagulan patch on. The simulation given not satisfied results, caused by good not equipment.

11. Aspects of new material application for boilers construction; Aspekty wdrazania nowych materialow w budowie kotlow

Energy Technology Data Exchange (ETDEWEB)

Czerniawski, R. [RAFAKO S.A., Raciborz (Poland)

1996-12-31

Review of steel types commonly used for energetic boilers construction has been done. The worldwide trends in new materials application for improvement of boilers quality have been discussed. The mechanical properties of boiler construction steels have been shown and compared. 3 refs, 5 figs, 1 tab.

12. 46 CFR 97.15-15 - Examination of boilers and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Examination of boilers and machinery. 97.15-15 Section... VESSELS OPERATIONS Tests, Drills, and Inspections § 97.15-15 Examination of boilers and machinery. It shall be the duty of the chief engineer when assuming charge of the boilers and machinery of a vessel to...

13. 46 CFR 32.35-1 - Boilers and machinery-TB/ALL.

Science.gov (United States)

2010-10-01

... 46 Shipping 1 2010-10-01 2010-10-01 false Boilers and machinery-TB/ALL. 32.35-1 Section 32.35-1 Shipping COAST GUARD, DEPARTMENT OF HOMELAND SECURITY TANK VESSELS SPECIAL EQUIPMENT, MACHINERY, AND HULL REQUIREMENTS Main and Auxiliary Machinery § 32.35-1 Boilers and machinery—TB/ALL. Boilers, main and auxiliary...

14. 46 CFR 109.421 - Report of repairs to boilers and pressure vessels.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Report of repairs to boilers and pressure vessels. 109... Report of repairs to boilers and pressure vessels. Before making repairs, except normal repairs and maintenance such as replacement of valves or pressure seals, to boilers or unfired pressure vessels in...

15. 7 CFR 51.2833 - U.S. No. 1 Boilers.

Science.gov (United States)

2010-01-01

... 7 Agriculture 2 2010-01-01 2010-01-01 false U.S. No. 1 Boilers. 51.2833 Section 51.2833 Agriculture Regulations of the Department of Agriculture AGRICULTURAL MARKETING SERVICE (Standards...) Grades § 51.2833 U.S. No. 1 Boilers. U.S. No. 1 Boilers consists of onions which meet all the...

16. 46 CFR 50.05-5 - Existing boilers, pressure vessels or piping systems.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Existing boilers, pressure vessels or piping systems. 50... ENGINEERING GENERAL PROVISIONS Application § 50.05-5 Existing boilers, pressure vessels or piping systems. (a) Whenever doubt exists as to the safety of an existing boiler, pressure vessel, or piping system, the marine...

17. 46 CFR 97.30-1 - Repairs to boilers and pressure vessels.

Science.gov (United States)

2010-10-01

... 46 Shipping 4 2010-10-01 2010-10-01 false Repairs to boilers and pressure vessels. 97.30-1 Section... VESSELS OPERATIONS Reports of Accidents, Repairs, and Unsafe Equipment § 97.30-1 Repairs to boilers and pressure vessels. (a) Before making any repairs to boilers or unfired pressure vessels, the chief engineer...

18. 46 CFR 78.17-30 - Examination of boilers and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 3 2010-10-01 2010-10-01 false Examination of boilers and machinery. 78.17-30 Section... OPERATIONS Tests, Drills, and Inspections § 78.17-30 Examination of boilers and machinery. It shall be the duty of the chief engineer when assuming charge of the boilers and machinery of a vessel to examine...

19. 46 CFR 167.25-1 - Boilers, pressure vessels, piping and appurtenances.

Science.gov (United States)

2010-10-01

... 46 Shipping 7 2010-10-01 2010-10-01 false Boilers, pressure vessels, piping and appurtenances. 167... SCHOOLS PUBLIC NAUTICAL SCHOOL SHIPS Marine Engineering § 167.25-1 Boilers, pressure vessels, piping and... the following standards for boilers, pressure vessels, piping and appurtenances: (1) Marine...

20. 46 CFR 196.15-15 - Examination of boilers and machinery.

Science.gov (United States)

2010-10-01

... 46 Shipping 7 2010-10-01 2010-10-01 false Examination of boilers and machinery. 196.15-15 Section... VESSELS OPERATIONS Test, Drills, and Inspections § 196.15-15 Examination of boilers and machinery. (a) It shall be the duty of the chief engineer when he assumes charge of the boilers and machinery of a vessel...

1. 46 CFR 62.35-20 - Oil-fired main boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Oil-fired main boilers. 62.35-20 Section 62.35-20... AUTOMATION Requirements for Specific Types of Automated Vital Systems § 62.35-20 Oil-fired main boilers. (a) General. (1) All main boilers, regardless of intended mode of operation, must be provided with the...

2. 46 CFR 196.30-1 - Repairs to boilers and pressure vessels.

Science.gov (United States)

2010-10-01

... 46 Shipping 7 2010-10-01 2010-10-01 false Repairs to boilers and pressure vessels. 196.30-1... VESSELS OPERATIONS Reports of Accidents, Repairs, and Unsafe Equipment § 196.30-1 Repairs to boilers and pressure vessels. (a) Before making any repairs to boilers or unfired pressure vessels, the Chief Engineer...

3. 46 CFR 35.25-1 - Examination of boilers and machinery by engineer-T/ALL.

Science.gov (United States)

2010-10-01

... 46 Shipping 1 2010-10-01 2010-10-01 false Examination of boilers and machinery by engineer-T/ALL... Engine Department § 35.25-1 Examination of boilers and machinery by engineer—T/ALL. It shall be the duty of an engineer when assuming charge of the boilers to examine the same forthwith and thoroughly. If...

4. Boiler corrosion (citations from the NTIS data base). Report for 1964-Jul 76

International Nuclear Information System (INIS)

Smith, M.F.

1976-07-01

Research on design, improved efficiency, materials, cathodic protection, corrosion inhibiting additives and combustion in coal and fuel oil fired boilers are cited. Corrosion from limestone injection for pollution control, magnetohydrodynamics, ship boilers, and nuclear power plant boilers are included. (This updated bibliography contains 86 abstracts, 9 of which are new entries to the previous edition.)

5. 46 CFR 167.25-5 - Inspection of boilers, pressure vessels, piping and appurtenances.

Science.gov (United States)

2010-10-01

...) NAUTICAL SCHOOLS PUBLIC NAUTICAL SCHOOL SHIPS Marine Engineering § 167.25-5 Inspection of boilers, pressure vessels, piping and appurtenances. The inspection of boilers, pressure vessels, piping and appurtenances... 46 Shipping 7 2010-10-01 2010-10-01 false Inspection of boilers, pressure vessels, piping and...

6. 46 CFR 52.01-35 - Auxiliary, donkey, fired thermal fluid heater, and heating boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Auxiliary, donkey, fired thermal fluid heater, and... (CONTINUED) MARINE ENGINEERING POWER BOILERS General Requirements § 52.01-35 Auxiliary, donkey, fired thermal... requirements for miscellaneous boiler types, such as donkey, fired thermal fluid heater, heating boiler, etc...

7. Real-time monitoring energy efficiency and performance degradation of condensing boilers

NARCIS (Netherlands)

Baldi, S.; Le, Q.T.; Holub, O.; Endel, P

2017-01-01

Condensing boilers achieve higher efficiency than traditional boilers by using waste heat in flue gases to preheat cold return water entering the boiler. Water vapor produced during combustion is condensed into liquid form, thus recovering its latent heat of vaporization, leading to around 10–12%

8. 46 CFR 63.25-3 - Electric hot water supply boilers.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Electric hot water supply boilers. 63.25-3 Section 63.25... water supply boilers. (a) Electric hot water supply boilers that have a capacity not greater than 454... section except the periodic testing required by paragraph (j) of this section. Electric hot water supply...

9. SRC burn test in 700-hp oil-designed boiler. Annex Volume C. Boiler emission report. Final technical report

Energy Technology Data Exchange (ETDEWEB)

1983-09-01

The Solvent-Refined Coal (SRC) test burn program was conducted at the Pittsburgh Energy Technology Center (PETC) located in Bruceton, Pa. One of the objectives of the study was to determine the feasibility of burning SRC fuels in boilers set up for fuel oil firing and to characterize emissions. Testing was conducted on the 700-hp oil-fired boiler used for research projects. No. 6 fuel oil was used for baseline data comparison, and the following SRC fuels were tested: SRC Fuel (pulverized SRC), SRC Residual Oil, and SRC-Water Slurry. Uncontrolled particulate emission rates averaged 0.9243 lb/10/sup 6/ Btu for SRC Fuel, 0.1970 lb/10/sup 6/ Btu for SRC Residual Oil, and 0.9085 lb/10/sup 6/ Btu for SRC-Water Slurry. On a lb/10/sup 6/ Btu basis, emissions from SRC Residual Oil averaged 79 and 78%, respectively, lower than the SRC Fuel and SRC-Water Slurry. The lower SRC Residual Oil emissions were due, in part, to the lower ash content of the oil and more efficient combustion. The SRC Fuel had the highest emission rate, but only 2% higher than the SRC-Water Slurry. Each fuel type was tested under variable boiler operating parameters to determine its effect on boiler emissions. The program successfully demonstrated that the SRC fuels could be burned in fuel oil boilers modified to handle SRC fuels. This report details the particulate emission program and results from testing conducted at the boiler outlet located before the mobile precipitator take-off duct. The sampling method was EPA Method 17, which uses an in-stack filter.

10. Efficiency of using direct-flow burners and nozzles in implementation of dry-bottom ash removal at the TPP-210A boiler furnace

Science.gov (United States)

Arkhipov, A. M.; Kanunnikov, A. A.; Kirichkov, V. S.; Prokhorov, V. B.; Fomenko, M. V.; Chernov, S. L.

2017-02-01

In reconstruction of operating pulverized coal-fired boilers, one of the main factors is the choice of a method for slag removal: dry bottom ash removal (DBAR) or slag-tap removal (STR). In this case, ecological and economic aspects should be taken into account, and also the early ignition of pulverized coal fuel, the reliability of operation of the furnace walls in the mode without slagging, and the stability of slag removal should be provided. In this work, issues of changeover of the pulverized coal-fired boilers of the TPP-210A type from the STR mode to the DBAR mode are considered. As of today, the main problems during the operation of these boilers are the high emissions of nitrogen oxides together with flue gases into the atmosphere and the appropriated payoffs, a small range of loads available, the necessity of stabilization of the pulverizedcoal flame sustainability by using the highly reactive fuel, large mechanical fuel underburning, etc. Results of studying aerodynamics of a furnace with DBAR obtained in the process of physical simulation are given; technical solutions and preliminary design (configuration of burners and nozzles in the boiler furnace, conceptual design of the pulverized coal burner, configuration of TPP-210A boiler with the low heat liberation of furnace cross-section and volumetric heat release) are set forth, which are associated with the optimization of aerodynamics of furnace volume, when the direct-flow burners and nozzles are used, and with organization of the efficient staged combustion of solid fuel. Two versions of possible modernization of a boiler unit are considered. Under conditions of the planned increase in the steam production capacity, the most promising measures are as follows: the DBAR implementation with reducing heat releases of the cross-section and volume of the furnace approximately by half, the installation of the direct-flow burners and nozzles with injection of recirculation gases into the active combustion

11. SOURCE SAMPLING FINE PARTICULATE MATTER: WOOD-FIRED INDUSTRIAL BOILER

Science.gov (United States)

The report provides a profile for a wood-fired industrial boiler equipped with a multistage electrostatic precipitator control device. Along with the profile of emissions of fine particulate matter of aerodynamic diameter of 2.5 micrometers or less (PM-2.5), data are also provide...

12. Integrated boiler, superheater, and decomposer for sulfuric acid decomposition

Science.gov (United States)

Moore, Robert [Edgewood, NM; Pickard, Paul S [Albuquerque, NM; Parma, Jr., Edward J.; Vernon, Milton E [Albuquerque, NM; Gelbard, Fred [Albuquerque, NM; Lenard, Roger X [Edgewood, NM

2010-01-12

A method and apparatus, constructed of ceramics and other corrosion resistant materials, for decomposing sulfuric acid into sulfur dioxide, oxygen and water using an integrated boiler, superheater, and decomposer unit comprising a bayonet-type, dual-tube, counter-flow heat exchanger with a catalytic insert and a central baffle to increase recuperation efficiency.

13. Wylfa nuclear boiler repair. How a major problem was solved

International Nuclear Information System (INIS)

1977-09-01

The CEGB has published a booklet, with coloured illustrations, that describes in detail the story of an unusually difficult boiler repair on a Magnox reactor at Wylfa nuclear power station. Boiler leaks affected the operation of No. 2 reactor in 1972, and persisted during 1973. A special procedure was developed for plugging the leaks using a remote welding machine but with the incidence of leaks continuing attempts were made to obtain a specimen of leaking tube by cutting through the boiler support tank to gain access. Eventually the fault was then traced to excessive relative motion between the tubes and support clips. Remedial work took seven months and was completed in December 1975. The start of the problem and the method of plugging the leaks is described. Details are given of the investigation leading to the obtaining and examination of a sample of leaking tube and the determination of the fault. Establishment of the cause as an unusual form of resonant vibration causing wear and fretting in clip-to-tube positions in the economiser region of the boiler is described in detail. The difficulties and accomplishments of the repair work are detailed. Finally the operation is looked at in retrospect and the experiences gained are summarised. (UK)

14. Hardware and software techniques for boiler operation and management

Energy Technology Data Exchange (ETDEWEB)

Kobayashi, Hiroshi (Hirakawa Iron Works, Ltd., Osaka (Japan))

1989-04-01

A study was conducted on the requirements for easy-operable boiler from the view points of hardware and software technologies. Relation among efficiency, energy-saving, and economics, and control of total emission regarding low NOx operation, were explained, with suggestion of orientation to developed necessary hard- and soft- ware for the realization. 8 figs.

15. Creep analysis of boiler tubes by fem | Taye | Zede Journal

African Journals Online (AJOL)

In this paper an analysis is developed for the determination of creep deformation of an axisymmetric boiler tubes subjected to axisymmetric loads. The stresses and the permanent strains at a particular time and at the steady state condition, resulting from loading of the tube under constant internal pressure and elevated ...

16. assessment of some performance characteristics of refuse boiler ...

African Journals Online (AJOL)

TIMZY

2013-07-02

Jul 2, 2013 ... A pioneer palm oil boiler unit, in an immense power self-contained oil mill, impaired by many years of accumulated ... revealed that under a single shift operating mode (8 hours), a time saving of 72 minutes arising from the effectiveness of ... electric power generation and for other processing equipment and ...

17. Oxygen pitting failure of a bagasse boiler tube

CSIR Research Space (South Africa)

Heyes, AM

2001-04-01

Full Text Available Examination of a failed roof tube from a bagasse boiler showed transverse through-cracks and extensive pitting. The pitting was typically oxygen induced pitting and numerous fatigue cracks had started within these pits. It is highly probable...

18. Log-fueled boilers; Les chaudieres a buches

Energy Technology Data Exchange (ETDEWEB)

NONE

2002-07-01

This document describes the different technologies of wood boilers fueled with logs (ascending combustion and natural draught, horizontal combustion and natural draught, reverse combustion and natural draught, reverse combustion and forced draught), their advantages and drawbacks, selection criteria and installation rules. (J.S.)

19. 40 CFR 65.149 - Boilers and process heaters.

Science.gov (United States)

2010-07-01

... stream is not introduced as or with the primary fuel, a temperature monitoring device in the fire box...-throughput transfer racks, as applicable, shall meet the requirements of this section. (2) The vent stream... thermal units per hour) or greater. (ii) A boiler or process heater into which the vent stream is...

20. SEM Investigation of Superheater Deposits from Biomass-Fired Boilers

DEFF Research Database (Denmark)

Jensen, Peter Arendt; Frandsen, Flemming; Hansen, Jørn

2004-01-01

, mature superheater deposit samples were extracted from two straw-fired boilers, Masnedø and Ensted, with fuel inputs of 33 MWth and 100 MWth, respectively. SEM (scanning electron microscopy) images and EDX (energy dispersive X-ray) analyses were performed on the deposit samples. Different strategies...

1. AUTOMATIC CONTROL SYSTEM ОF REGIONAL BOILER HOUSE

Directory of Open Access Journals (Sweden)

V. A. Sednin

2005-01-01

Full Text Available Implementation of an automatic control system is one of directions that promotes to increase an operational efficiency of a heat supply system. A heating boiler house in Surgut (Russia is taken as an example to demonstrate an actual realization of such system.

2. A risk approach to the management of boiler tube thinning

International Nuclear Information System (INIS)

Noori, Soudabeh A.; Price, John W.H.

2006-01-01

A large set of industrial thickness inspection data covering four boiler units of a power station over a period of five years was made available to the authors. The measurements were made in regions of the boiler where corrosion/erosion was the major cause of failure of the boiler tubes. There were over 40,000 separately measured data points in the data and all were collected with some care and expense. In the development of maintenance strategies for equipment, this type of data is typical of the data that must be collected and assessed. This data thus represents an opportunity to evaluate the ability to generate a useful risk approach to the management of the tubing. An important example of a risk-based approach is the American Petroleum Institute (API) Risk Based Inspection ('RBI'), API 581. A variety of problems were encountered applying this to boiler tubes. The problems include irrelevant API 581 corrosion rate tables, lack of information on how to analyse inspection data, difficulty of dealing with multiple inspection categories and lack of suitable direction for programming inspection intervals

3. Reliability of non-heated tube bends of boilers

International Nuclear Information System (INIS)

Bugaj, N.V.; Akhremenko, V.L.; Zamotaev, V.S.

1984-01-01

Bend failures are described for non-heated boiler tubes of 12Kh1MF and 20 steels. Methods of reliability evaluations are presented which permit revealing and replacing the bends with inadequate resources. Influences of operation conditions on bend durability is shown as well as the factors which are dominating at bend failures

4. Static stability characteristics of the boilers at Oldbury nuclear power station

International Nuclear Information System (INIS)

Paynter, R.J.; Rea, J.

1986-01-01

The cause of an intermittent load loss at Oldbury Nuclear Power Station is shown to be the high sensitivity of boiler performance to the imposed spatial distribution of boiler gas inlet temperature. This high sensitivity is demonstrated to be a function of the inherent static stability characteristics of the boilers. The installation of orifice plates with a high flow resistance into the feed pipework to the half boilers has greatly reduced the boiler sensitivity and eliminated the intermittent load loss so that, on average, higher electrical generation is obtained from the station. (author)

5. Fuel quality and its effect on the design of power boilers in the USA

Energy Technology Data Exchange (ETDEWEB)

Kotler, V.R.

1984-05-01

Statistical data, taken from Power, Proceedings of the American Power Conference and others, on developments since the 1950s in boiler design caused by the increasing use of lower quality fuel (subbituminous and lignite coals) are presented. The effect of pollution regulations in the USA on boiler design is discussed. The results of a 16 year study by the TVA on the decrease in coal quality fired in its boilers and its effect on boiler efficiency are presented. Methods of transport are surveyed. Descriptions and characteristics of several modern boilers designed by Babcock and Wilcox, Combustion Engineering, Foster-Wheeler and Riley Stoker are given. 13 references.

6. Multi-objective Optimization of Coal-fired Boiler Combustion Based on NSGA-II

OpenAIRE

Tingfang Yu; Hongzhen Zhu; Chunhua Peng

2013-01-01

NOx emission characteristics and overall heat loss model for a 300MW coal-fired boiler were established by Back Propagation (BP) neural network, by which the the functional relationship between outputs (NOx emissions & overall heat loss of the boiler) and inputs (operational parameters of the boiler) of a coal-fired boiler can be predicted. A number of field test data from a full-scale operating 300MWe boiler were used to train and verify the BP model. The NOx emissions & heat loss pr...

7. Control of the Bed Temperature of a Circulating Fluidized Bed Boiler by using Particle Swarm Optimization

Directory of Open Access Journals (Sweden)

AYGUN, H.

2012-05-01

Full Text Available Circulating fluidized bed boilers are increasingly used in the power generation due to their higher combustion efficiency and lower pollutant emissions. Such boilers require an effective control of the bed temperature, because it influences the boiler combustion efficiency and the rate of harmful emissions. A Particle-Swarm-Optimization-Proportional-Integrative-Derivative (PSO-PID controller for the bed temperature of a circulating fluidized bed boiler is presented. In order to prove the capability of the proposed controller, its performances are compared at different boiler loads with those of a Fuzzy Logic (FL controller. The simulation results demonstrate some advantages of the proposed controller.

8. Effect of Water Quality on the Performance of Boiler in Nigerian Petroleum Industry

Directory of Open Access Journals (Sweden)

J. O. ODIGURE

2005-06-01

Full Text Available This work investigates quality of water used in boilers of Refinery Company in Nigeria. The results shows that the quality of water fed to boilers are off specification. Low water quality used in boilers led to frequent failure of the boilers as a result of tube rupture. This has resulted into low capacity utilization and loss of processing fees. The poor performance of the boiler feed treatment plant is attributable to the deplorable condition of water intake plant, raw water treatment, demineralization plant, change in raw water quality and non-functioning of the polisher unit.

9. Chlorine in solid fuels fired in pulverized fuel boilers sources, forms, reactions, and consequences: a literature review

Energy Technology Data Exchange (ETDEWEB)

David A. Tillman; Dao Duong; Bruce Miller [Foster Wheeler North America Corp. (United States)

2009-07-15

Chlorine is a significant source of corrosion and deposition, both from coal and from biomass, and in PF boilers. This investigation was designed to highlight the potential for corrosion risks associated with once-through units and advanced cycles. The research took the form of a detailed literature investigation to evaluate chlorine in solid fuels: coals of various ranks and origins, biomass fuels of a variety of types, petroleum cokes, and blends of the above. The investigation focused upon an extensive literature review of documents dating back to 1991. The focus is strictly corrosion and deposition. To address the deposition and corrosion issues, this review evaluates the following considerations: concentrations of chlorine in available solid fuels including various coals and biomass fuels, forms of chlorine in those fuels, and reactions - including reactivities - of chlorine in such fuels. The assessment includes consideration of alkali metals and alkali earth elements as they react with, and to, the chlorine and other elements (e.g., sulfur) in the fuel and in the gaseous products of combustion. The assessment also includes other factors of combustion: for example, combustion conditions including excess O{sub 2} and combustion temperatures. It also considers analyses conducted at all levels: theoretical calculations, bench scale laboratory data and experiments, pilot plant experiments, and full scale plant experience. Case studies and plant surveys form a significant consideration in this review. The result of this investigation focuses upon the concentrations of chlorine acceptable in coals burned exclusively, in coals burned with biomass, and in biomass cofired with coal. Values are posited based upon type of fuel and combustion technology. Values are also posited based upon both first principles and field experience. 86 refs., 8 figs., 7 tabs.

10. Dynamic behavior of tobacco waste in the coal-fired fluidized-bed boiler

Energy Technology Data Exchange (ETDEWEB)

Zhang, Kai; Chang, Jian; Chen, Honggang; Yang, Yongping [North China Electric Power Univ., Beijing (China). National Eng Lab for Biomass Power Generation Equipment; Yu, Bangting [China Univ. of Petroleum, Beijing (China). State Key Lab. of Heavy Oil Processing

2013-07-01

Circulating fluidized bed (CFB) technology is an advanced method for utilizing coal and other solid fuels in an environmentally acceptable manner. During the processing procedure in the nicotiana tabacum plants, lots of tobacco stem wastes are produced, which are normally being dumped to the landfill field. If this kind of waste can be used as a part of the fuel to be added into the coal in a CFB combustor, it will reduce the use of coal and then cut the net carbon emissions. To understand the complicated fluid dynamics of nicotiana tabacum wastes in the coal-fired CFB boiler, the mixing and segregation behavior of tobacco stalk are preliminary measured in a cylindrical fluidized bed. Obvious segregation behavior is found due to distinct differences in density and shape between tobacco stem and coal, which results in poor fluidization quality and bad combustion efficiency. To overcome this disadvantage, a jet with high gas velocity is introduced through the air distributor and a detailed experimental study is conducted in a fluidized bed made up of stem-sand mixture with different solid components at various jet velocities, which greatly improve the mixing performance of stem in the fluidized bed. The above findings are helpful for the technological upgrading of small- or middle-sized CFB boiler with adding tobacco stem into coal.

11. Homogenous and heterogeneous combustion in the secondary chamber of a straw-fired batch boiler

Directory of Open Access Journals (Sweden)

Szubel Mateusz

2017-01-01

Full Text Available Currently, the attention of the producers of biomass batch boilers is mostly focused on the problem of the total efficiency of energy conversion, CO emissions as well as particulate matter emissions. Due to the regulations of the European Union, the emissions referred to above have to be kept at certain levels because of health considerations, but also because of the necessity to increase the efficiency of the devices. The paper presents the process of analysis of a straw-fired small-scale boiler. In this study, the early stage CFD model presented in a previous paper [1] has been improved and evaluated. Based on [2], an additional set of specimens participating in homogeneous gas reactions was assumed to describe the combustion process sufficiently. Associated Arrhenius parameters have been applied for the description of these reactions. ANSYS Fluent 16 has been used to perform the analysis and the analysis was focused on the CO emissions level as well as on the impact of the modelling approach on the result of the computing. Moreover, losses related to incomplete combustion have been calculated for each of the considered cases.

12. Wood Pellet-Fired Biomass Boiler Project at the Ketchikan Federal Building

Energy Technology Data Exchange (ETDEWEB)

Tomberlin, Gregg [National Renewable Energy Lab. (NREL), Golden, CO (United States)

2014-06-01

Biomass boiler systems have existed for many years, but the technology has advanced in recent decades and can now provide automated and efficient operation for a relatively modest investment. Key advances in system monitoring and control allow for lower operating costs, since the control systems run all aspects of the boiler, including feed, load reduction and even tube cleaning. These advances have made such systems economical on a small scale in situations where inexpensive fuels like natural gas are not available. This creates an opportunity for building operators in remote, cold-climate locations to reduce the use of expensive fuels for heating buildings. GSA Region 10 installed the system at the federal building in Ketchikan, Alaska and submitted the project to the Green Proving Ground (GPG) program. GSA's GPG program contracted with the National Renewable Energy Laboratory (NREL) to assess the installation and the technology. The system serves as a demonstration to assess actual system efficiencies, as well as operating characteristics and financial benefits. In addition to installation and operational issues, the project team/researchers examined other issues, including fuel transportation costs, building energy savings, and overall economics.

13. 46 CFR 53.01-3 - Adoption of section IV of the ASME Boiler and Pressure Vessel Code.

Science.gov (United States)

2010-10-01

... 46 Shipping 2 2010-10-01 2010-10-01 false Adoption of section IV of the ASME Boiler and Pressure...) MARINE ENGINEERING HEATING BOILERS General Requirements § 53.01-3 Adoption of section IV of the ASME Boiler and Pressure Vessel Code. (a) Heating boilers shall be designed, constructed, inspected, tested...

14. Operator's Manual, Boiler Room Operations and Maintenance. Supplement A, Air Pollution Training Institute Self-Instructional Course SI-466.

Science.gov (United States)

Environmental Protection Agency, Research Triangle Park, NC. Air Pollution Training Inst.

This Operator's Manual is a supplement to a self-instructional course prepared for the United States Environmental Protection Agency. This publication is the Boiler Room Handbook for operating and maintaining the boiler and the boiler room. As the student completes this handbook, he is putting together a manual for running his own boiler. The…

15. 40 CFR 270.22 - Specific part B information requirements for boilers and industrial furnaces burning hazardous...

Science.gov (United States)

2010-07-01

... requirements for boilers and industrial furnaces burning hazardous waste. 270.22 Section 270.22 Protection of... requirements for boilers and industrial furnaces burning hazardous waste. When an owner or operator of a cement kiln, lightweight aggregate kiln, solid fuel boiler, liquid fuel boiler, or hydrochloric acid...

16. Multi-unit shutdown due to boiler feedwater chemical excursion

International Nuclear Information System (INIS)

Diebel, M.E.

1991-01-01

Ontario Hydro's Bruce Nuclear Generating Station 'B' consists of four 935 W CANDU units located on the east shore of Lake Huron in the province of Ontario, Canada. On July 25 and 26, 1989 three of the four operating units were shutdown due to boiler feedwater chemical excursions initiated by a process upset in the Water Treatment Plant that provides demineralized make-up water to all four units. The chemicals that escaped from an ion exchange vessel during a routine regeneration very quickly spread through the condensate make-up system and into the boiler feedwater systems. This resulted in boiler sulfate levels exceeding shutdown limits. A total of 260 GWH of electrical generation was unexpectedly made unavailable to the grid at a time of peak seasonal demand. This event exposed several unforeseen deficiencies and vulnerabilities in the automatic demineralized water make-up quality protection scheme, system designs, operating procedures and the ability of operating personnel to recognize and appropriately respond to such an event. The combination of these factors contributed towards turning a minor system upset into a major multi-unit shutdown. This paper provides the details of the actual event initiation in the Water Treatment Plant and describes the sequence of events that led to the eventual shutdown of three units and near shutdown of the fourth. The design inadequacies, procedural deficiencies and operating personnel responses and difficulties are described. The process of recovering from this event, the flushing out of system piping, boilers and the feedwater train is covered as well as our experiences with setting up supplemental demineralized water supplies including trucking in water and the use of rental trailer mounted demineralizing systems. System design, procedural and operational changes that have been made and that are still being worked on in response to this event are described. The latest evidence of the effect of this event on boiler tube

17. Staged fluidized-bed coal combustor for boiler retrofit

International Nuclear Information System (INIS)

Rehmat, A.; Dorfman, L.; Shibayama, G.; Waibel, R.

1991-01-01

The Advanced Staged Fluidized-Bed Coal Combustion System (ASC) is a novel clean coal technology for either coal-fired repowering of existing boilers or for incremental power generation using combined-cycle gas turbines. This new technology combines staged combustion for gaseous emission control, in-situ sulfur capture, and an ash agglomeration/vitrification process for the agglomeration/vitrification of ash and spent sorbent, thus rendering solid waste environmentally benign. The market for ASC is expected to be for clean coal-fired repowering of generating units up to 250 MW, especially for units where space is limited. The expected tightening of the environmental requirements on leachable solids residue by-products could considerably increase the marketability for ASC. ASC consists of modular low-pressure vessels in which coal is partially combusted and gasified using stacked fluidized-bed processes to produce low-to-medium-Btu, high-temperature gas. This relatively clean fuel gas is used to repower/refuel existing pulverized-coal, natural gas, or oil-fired boilers using bottom firing and reburning techniques. The benefits of ASC coal-fired repowering include the ability to repower boilers without obtaining additional space while meeting the more stringent environmental requirements of the future. Low NO x , SO x , and particulate levels are expected while a nonleachable solid residue with trace metal encapsulation is produced. ASC also minimizes boiler modification and life-extension expenditures. Repowered efficiencies can be restored to the initial operating plant efficiency, and the existing boiler capacity can be increased by 10%. Preliminary cost estimates indicate that ASC will have up to a \$250/kW capital cost advantage over existing coal-fired repowering options. 4 figs., 4 tabs

18. To Selection of Small-Capacity Turbine Type and Rated Conditions

Directory of Open Access Journals (Sweden)

N. B. Karnitsky

2010-01-01

Full Text Available Profitability of industrial-heating boiler transition to mini-TPP is revealed in the paper. The paper presents a comparative analysis of high- and low-speed turbines of small capacity.

19. Deposit Probe Measurements in Danish Grate and Pulverized Fuel Biomass Power Boilers

DEFF Research Database (Denmark)

Hansen, Stine Broholm; Jensen, Peter Arendt; Jappe Frandsen, Flemming

2012-01-01

. Corresponding samples of fuels, ash deposits and fly ash have provided information on the transformation of inorganics in the boiler. Generally, grate fired boilers provide a fly ash containing high contents of K, Cl and S compared to the fuel ash, while suspension fired boilers fly ash has a composition nearly...... similar to the fuel ash. Inner most biomass deposits are always salt-rich, while thicker deposit layers also contain some Si and Ca. Deposit probe formation rate measurements have been performed in different ways on several boilers. Grate and suspension fired boilers seems to cause similar deposit...... formation rates. Suspension fired boilers generate more fly ash, while grate boilers form a fly ash with a higher fraction of melt formation (and thereby a higher sticking probability) at similar temperatures. For suspension fired units it is observed that wood with a lower ash content than straw gives rise...

20. Recovery Act: Oxy-Combustion Technology Development for Industrial-Scale Boiler Applications

Energy Technology Data Exchange (ETDEWEB)

Levasseur, Armand

2014-01-01

This Topical Report outlines guidelines and key considerations for design and operation of pulverized coal-fired boilers for oxy-combustion. The scope addressed includes only the boiler island, not the entire oxy-fired CO{sub 2} capture plant. These guidelines are primarily developed for tangential-fired boilers and focus on designs capable of dual air and oxy-fired operation. The guidelines and considerations discussed are applicable to both new units and existing boiler retrofits. These guidelines are largely based on the findings from the extensive 15 MW{sub th} pilot testing and design efforts conducted under this project. A summary level description is provided for each major aspect of boiler design impacted by oxy-combustion, and key considerations are discussed for broader application to different utility and industrial designs. Guidelines address the boiler system arrangement, firing system, boiler thermal design, ducting, materials, control system, and other key systems.