A single phase photovoltaic inverter control for grid connected system
Indian Academy of Sciences (India)
This paper presents a control scheme for single phase grid connected photovoltaic (PV) system operating under both grid connected and isolated grid mode. The control techniques include voltage and current control of grid-tie PV inverter. During grid connected mode, grid controls the amplitude and frequency of the PV ...
Current Harmonics from Single-Phase Grid-Connected Inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Zhou, Keliang; Blaabjerg, Frede
2016-01-01
Environmental conditions and operational modes may significantly impact the distortion level of the injected current from single-phase grid-connected inverter systems, such as photovoltaic (PV) inverters, which may operate in cloudy days with a maximum power point tracking, in a non-unity power...... factor, or in the low voltage ride through mode with reactive current injection. In this paper, the mechanism of the harmonic current injection from grid-connected single-phase inverter systems is thus explored, and the analysis is conducted on single-phase PV systems. In particular, the analysis...... is focused on the impacts of the power factor and the feed-in grid current level on the quality of the feed-in grid current from single-phase inverters. As a consequence, an internal model principle based high performance current control solution is tailor-made and developed for single-phase grid-connected...
A grid-connected single-phase photovoltaic micro inverter
Wen, X. Y.; Lin, P. J.; Chen, Z. C.; Wu, L. J.; Cheng, S. Y.
2017-11-01
In this paper, the topology of a single-phase grid-connected photovoltaic (PV) micro-inverter is proposed. The PV micro-inverter consists of DC-DC stage with high voltage gain boost and DC-AC conversion stage. In the first stage, we apply the active clamp circuit and two voltage multipliers to achieve soft switching technology and high voltage gain. In addition, the flower pollination algorithm (FPA) is employed for the maximum power point tracking (MPPT) in the PV module in this stage. The second stage cascades a H-bridge inverter and LCL filter. To feed high quality sinusoidal power into the grid, the software phase lock, outer voltage loop and inner current loop control method are adopted as the control strategy. The performance of the proposed topology is tested by Matlab/Simulink. A PV module with maximum power 300W and maximum power point voltage 40V is applied as the input source. The simulation results indicate that the proposed topology and the control strategy are feasible.
A Novel Model Predictive Control for Single-Phase Grid-Connected Photovoltaic Inverters
DEFF Research Database (Denmark)
Zangeneh Bighash, Esmaeil; Sadeghzadeh, Seyed Mohammad; Ebrahimzadeh, Esmaeil
2017-01-01
Single-phase grid-connected inverters with LCL filter are widely used to connect photovoltaic systems to the utility grid. Among the existing control schemes, predictive control methods are faster and more accurate but also more complicated to implement. Recently, the Model Predictive Control (MPC......) algorithm for single-phase inverter has been presented, where the algorithm implementation is straightforward. In the MPC approach, all switching states are considered in each switching period to achieve the control objectives. However, since the number of switching states in single-phase inverters is small......, the inverter output current has a high Total Harmonic Distortions (THD). In order to reduce this, this paper presents an improved MPC for single-phase grid-connected inverters. In the proposed approach, the switching algorithm is changed and the number of the switching states is increased by means of virtual...
High Quality Model Predictive Control for Single Phase Grid Connected Photovoltaic Inverters
DEFF Research Database (Denmark)
Zangeneh Bighash, Esmaeil; Sadeghzadeh, Seyed Mohammad; Ebrahimzadeh, Esmaeil
2018-01-01
Single phase grid-connected inverters with LCL filter are widely used to connect the photovoltaic systems to the utility grid. Among the presented control schemes, predictive control methods are faster and more accurate but are more complex to implement. Recently, the model-predictive control...... algorithm for single-phase inverter has been presented, where the algorithm implementation is straightforward. In the proposed approach, all switching states are tested in each switching period to achieve the control objectives. However, since the number of the switching states in single-phase inverter...... is low, the inverter output current has a high total harmonic distortions. In order to reduce the total harmonic distortions of the injected current, this paper presents a high-quality model-predictive control for one of the newest structure of the grid connected photovoltaic inverter, i.e., HERIC...
A single phase photovoltaic inverter control for grid connected system
Indian Academy of Sciences (India)
operation the PV inverter operates in voltage-controlled mode to maintain a constant amplitude and frequency of the voltage ..... 10W i.e. less than 8% of the maximum power, a step size of k2 is ...... ply/demand side management system.
Lyapunov-Based Control Scheme for Single-Phase Grid-Connected PV Central Inverters
Meza, C.; Biel, D.; Jeltsema, D.; Scherpen, J. M. A.
A Lyapunov-based control scheme for single-phase single-stage grid-connected photovoltaic central inverters is presented. Besides rendering the closed-loop system globally stable, the designed controller is able to deal with the system uncertainty that depends on the solar irradiance. A laboratory
A Direct Maximum Power Point Tracking Method for Single-Phase Grid Connected PV Inverters
DEFF Research Database (Denmark)
EL Aamri, Faicel; Maker, Hattab; Sera, Dezso
2018-01-01
in dynamic conditions, especially in low irradiance when the measurement of signals becomes more sensitive to noise. The proposed MPPT is designed for single-phase single-stage grid-connected PV inverters, and is based on estimating the instantaneous PV power and voltage ripples, using second...
S4 Grid-Connected Single-Phase Transformerless Inverter for PV Application
DEFF Research Database (Denmark)
Ardashir, Jaber Fallah; Siwakoti, Yam Prasad; Sabahi, Mehran
2016-01-01
This paper introduces a new single-phase transformerless inverter for grid-connected photovoltaic systems with low leakage current. It consists of four power switches, two diodes, two capacitors and a filter at the output stage. The neutral of the grid is directly connected to the negative terminal...... size, low cost, flexible grounding configuration and higher efficiency. The operating principle and analysis of the proposed circuit are presented in details. Experimental results of a 500 W prototype are demonstrated to validate the proposed topology and the overall concept. The results obtained...... clearly verify the performance of the proposed inverter and its practical application for grid-connected PV systems....
Adaptive fuzzy sliding control of single-phase PV grid-connected inverter.
Fei, Juntao; Zhu, Yunkai
2017-01-01
In this paper, an adaptive fuzzy sliding mode controller is proposed to control a two-stage single-phase photovoltaic (PV) grid-connected inverter. Two key technologies are discussed in the presented PV system. An incremental conductance method with adaptive step is adopted to track the maximum power point (MPP) by controlling the duty cycle of the controllable power switch of the boost DC-DC converter. An adaptive fuzzy sliding mode controller with an integral sliding surface is developed for the grid-connected inverter where a fuzzy system is used to approach the upper bound of the system nonlinearities. The proposed strategy has strong robustness for the sliding mode control can be designed independently and disturbances can be adaptively compensated. Simulation results of a PV grid-connected system verify the effectiveness of the proposed method, demonstrating the satisfactory robustness and performance.
A PWM strategy for acoustic noise reduction for grid-connected single-phase inverters
Energy Technology Data Exchange (ETDEWEB)
Shao, R.; Guo, Z.; Chang, L. [New Brunswick Univ., Fredericton, NB (Canada). Dept. of Electrical and Computer Engineering
2006-07-01
This paper presented a newly proposed and improved pulse width modulation (PWM) strategy for grid-connected single-phase inverters. Small distributed generators using energy from renewable resources such as PV and wind systems typically use grid-connected single-phase inverters as voltage source inverters for good acoustic performance. PWM is generally applied in these inverters in order to achieve good waveforms of output current as required by interconnection standards. In routine simultaneous switching PWM methods, the current ripples through the inverter output filter inductor are at the carrier switching frequency, which is one of the major causes for inverter acoustic noise. The new PWM strategy effectively alleviates acoustic noise and improves output power quality. It is based on the principle of evenly splitting the switching of Insulated Gate Bipolar Transistors (IGBT) in each switching cycle among all IGBTs of the full bridge, thereby using a non-simultaneous mode of PWM which doubles the output current ripple frequency. This increases the inductor current ripple frequency to twice the carrier frequency. It is therefore possible to increase the current ripple frequency, or noise frequency into the range of ultrasonic which is inaudible to the human ear, without increasing the inverter's switching frequency to which the inverter's switching loss is proportional. In addition, this new PWM scheme can reduce the output current harmonics distortion and dc link current ripples. As such, lower capacitance in dc link capacitors and lower inductance of output inductor are needed. The improved PWM scheme was verified in a 3 kW grid-connected single-phase inverter. It was shown that the PWM strategy can be readily implemented with a digital signal processing microcontroller. 8 refs., 11 figs.
A review of single-phase grid-connected inverters for photovoltaic modules
DEFF Research Database (Denmark)
Kjaer, Soren Baekhoej; Pedersen, John Kim; Blaabjerg, Frede
2005-01-01
-phase grid; 3) whether they utilizes a transformer (either line or high frequency) or not; and 4) the type of grid-connected power stage. Various inverter topologies are presented, compared, and evaluated against demands, lifetime, component ratings, and cost. Finally, some of the topologies are pointed out......This review focuses on inverter technologies for connecting photovoltaic (PV) modules to a single-phase grid. The inverters are categorized into four classifications: 1) the number of power processing stages in cascade; 2) the type of power decoupling between the PV module(s) and the single...
DEFF Research Database (Denmark)
Siwakoti, Yam Prasad; Blaabjerg, Frede
2016-01-01
This paper proposes a new single-phase flying capacitor transformerless PV inverter for grid-connected photovoltaic (PV) systems. The neutral of the grid can be directly connected to the negative terminal of the source (PV). It consists of four power switches, one diode, one capacitor and a small...... and some topologies, which requires two times of the peak ac-voltage magnitude) and, (5) the flying capacitor charges every switching cycle, which reduces the size of the required capacitor with switching frequency. In addition, industry standard half bridge module can be used in the new inverter without...
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Guerrero, Josep M.
2016-01-01
Current regulation is crucial for operating single-phase grid-connected inverters. The challenge of the current controller is how to fast and precisely tracks the current with zero steady-state error. This paper proposes a novel feedback mechanism for the conventional PI controller. It allows...... done indicates that the widely used PR (P+Resonant) control is just a special case of the proposed control solution. The time-domain simulation in Matlab/Simulink and experimental results from a TMS320F2812 DSP based laboratory prototypes are in good agreement, which verify the effectiveness...
Directory of Open Access Journals (Sweden)
Borkowski Dariusz
2016-01-01
Full Text Available Single-phase grid connected inverters are nowadays broadly developed and tested in various types of applications especially in photovoltaic systems. The main aim of the inverter control strategy is to extract the maximum energy from the PV system which corresponds to the maximum power at certain conditions. However, the MPPT methods are also important in other renewable energy conversion systems. This paper analyses the performance of a commercially available photovoltaic inverter in water and wind systems. Presented models are implemented in a laboratory test bench in the form of torque characteristics realised by an induction motor fed by the inverter with vector control. The parameters are scaled into relative variables to provide a proper performance comparison. Presented tests include step response to assess the performance of a system dynamic. The dynamic tests showed a fast response of the investigated systems. The MPPT tracking accuracy tested under realistic profiles is similar for both cases: 98% and 96% respectively for the wind and water systems. These results prove the satisfactory performance of the MPPT of the PV microinverter in these applications.
Leakage current analysis of single-phase transformer-less grid-connected PV inverters
DEFF Research Database (Denmark)
Ma, Lin; Kerekes, Tamas; Teodorescu, Remus
2016-01-01
Transformer-less string PV inverter is getting more and more widely utilized due to its higher efficiency, smaller volume and weight. However, without the galvanic isolation, the leakage current limitation and operation safety became the key issues of transformer-less inverters. This paper...... simplifies the leakage current generation circuit model and presents a leakage current estimation method both in real time and frequency domain. It shows that the leakage current is related to the circuit stray parameters, output filter and common mode voltage. Furthermore, with the proposed analysis method......, the leakage current generation of H-bridge with different modulation methods and HERIC inverter are discussed individually. At last, the presented method has been verified via simulation....
DEFF Research Database (Denmark)
Zhang, Zhen; Yang, Yongheng; Blaabjerg, Frede
2016-01-01
With the fast development in Photovoltaic (PV) technology, the relevant grid-connection requirements/standards are continuously being updated, and more challenges have been imposed on both single-phase and three-phase grid-connected PV systems. For instance, PV systems are currently required...... to remain connected under grid voltage sags (even zero voltage condition). In this case, much attention should be paid to the grid synchronization in such a way to properly ride-through grid faults. Thus, in this paper, the most commonly-used and recently-developed Phase Locked Loop (PLL) synchronization...... methods have been evaluated for single-phase grid-connected PV systems in the case of Zero-Voltage Ride-Through (ZVRT) operation. The performances of the prior-art PLL methods in response to zero voltage faults in terms of detection precision and dynamic response are assessed in this paper. Simulation...
DEFF Research Database (Denmark)
Dai, Ning-Yi; Zhang, Wen-Chen; Wong, Man-Chung
2015-01-01
with the conventional inductive-coupling grid-connected inverter (IGCI), this structure provides an alternative interface for use between a low-voltage DC microgrid and an AC grid. A comparison between the CGCI and the IGCI is performed. It is concluded that the CGCI is able to transfer active power and provide lagging...... of the CGCI remains at approximately of 50% of the peak grid voltage. In addition, a P-unit current controller is proposed for use with the CGCI, as a proportional-integral controller is not suitable. Finally, simulation and experiments show the effectiveness of the proposed approach....
DEFF Research Database (Denmark)
Zangeneh Bighash, Esmaeil; Sadeghzadeh, Seyed Mohammad; Ebrahimzadeh, Esmaeil
2017-01-01
Nowadays capacity of the photovoltaic systems in the grid is remarkable and provides a major part of energy in the grid. Therefore, an abruption of these systems from the grid can create a damage to the grid. Unlike in the past that PV systems disconnected from the grid when a voltage drop occurred......, nowadays these systems should have Low Voltage Ride-Through (LVRT) capability. The PV system should stay connected to the grid at fault time and help to recover the grid voltage by injecting the reactive power like in a power plant or a custom power device. There are two important factors for single phase...... grid connected PV inverters. The first one is the structure of the inverter and the second one is the control part. In this regard, the HERIC inverter can be a good selection among the transformerless inverters for a PV system due to its high efficiency. For the control part, this paper presents a look...
DEFF Research Database (Denmark)
Ko, Youngjong; Park, Kiwoo; Lee, Kyo-Beum
2011-01-01
In a grid connected power conversion system, the phase angle information of a grid voltage is very essential for supplying power to the grid since it is used for active and reactive power control. A Phase Locked Loop (PLL) system is used and should be robust because often the actual grid voltages...
The Influence of phase-locked loop on the stability of single-phase grid-connected inverter
DEFF Research Database (Denmark)
Zhang, Chong; Wang, Xiongfei; Blaabjerg, Frede
2015-01-01
. Moreover, the Second Order Generalized Integrator PLL (SOGI-PLL) and the inverse Park transformation PLL (Park-PLL) are also modeled. It is found that the quadrature signal generators of SOGI-PLL and Park-PLL play a stabilizing role in grid-inverter interactions, which thus provide promising candidates...
Directory of Open Access Journals (Sweden)
Jianke Li
2014-01-01
Full Text Available Compared with L-type filter, LCL-type filter is more suitable for high-power low-switching frequency applications with reducing the inductance, improving dynamic performance. However, the parameter design for the LCL filter is more complex due to the influence of the controller response performance of the converter. If the harmonic current around switching frequency can be fully suppressed, it is possible for inverter to decrease the total inductance as well as the size and the cost. In this paper, the model of the LCL filter is analyzed and numerical algorithms are adopted to analyze the stability of the closed-loop control system and stable regions are deduced with different parameters of LCL filter. Then, the minimum sampling frequencies are deduced with different conditions. Simulation and experimental results are provided to validate the research on the generating mechanism for the unstable region of sampling frequency.
Overview of Single-Phase Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2017-01-01
A continuous booming installation of solar photovoltaic (PV) systems has been witnessed worldwide. It is mainly driven by the imperative demand of “clean” power generation from renewables. Grid-connected PV systems will thus become an even more active player in the future mixed power systems, which...... systems. This chapter thus gives an overview of the advancement of power electronics converters in single-phase grid-connected PV systems, being commonly used in residential applications. Demands to single-phase grid-connected PV systems and the general control strategies are also addressed...... are linked together by a vast of power electronics converters and the power grid. In order to achieve a reliable and efficient power generation from PV systems, more stringent demands have been imposed on the entire PV system. It, in return, advances the development of the power converter technology in PV...
Chaves, Eric N; Coelho, Ernane A A; Carvalho, Henrique T M; Freitas, Luiz C G; Júnior, João B V; Freitas, Luiz C
2016-09-01
This paper presents the design of a controller based on Internal Model Control (IMC) applied to a grid-connected single-phase PWM inverter. The mathematical modeling of the inverter and the LCL output filter, used to project the 1-DOF IMC controller, is presented and the decoupling of grid voltage by a Feedforward strategy is analyzed. A Proportional - Resonant Controller (P+Res) was used for the control of the same plant in the running of experimental results, thus moving towards the discussion of differences regarding IMC and P+Res performances, which arrived at the evaluation of the proposed control strategy. The results are presented for typical conditions, for weak-grid and for non-linear local load, in order to verify the behavior of the controller against such situations. Copyright © 2016 ISA. Published by Elsevier Ltd. All rights reserved.
Analysis and Design of Solar Photo voltaic Grid Connected Inverter
Directory of Open Access Journals (Sweden)
Muddasani Satyanarayana
2015-08-01
Full Text Available This paper presents common mode voltage analysis of single phase grid connected photovoltaic inverter. Many researchers proposed different grid tie inverters for applications like domestic powering, street lighting, water pumping, cooling and heating applications, however traditional grid tie PV inverter uses either a line frequency or a high frequency transformer between the inverter and grid but losses will increase in the network leading to reduced efficiency of the system. In order to increase the efficiency, with reduced size and cost of the system, the effective solution is to remove the isolation transformer. But common mode (CM ground leakage current due to parasitic capacitance between the PV panels and the ground making the system unreliable. The common mode current reduces the efficiency of power conversion stage, affects the quality of grid current, deteriorate the electric magnetic compatibility and give rise to the safety threats. In order to eliminate the common mode leakage current in Transformerless PV systm two control algorithms of multi-carrier pwm are implemented and compared for performance analysis.The shoot-through issue that is encountered by traditional voltage source inverter is analyzed for enhanced system reliability. These control algorithms are compared for common mode voltage and THD comparisons. The proposed system is designed using MATLAB/SIMULINK software for analysis.
Overview of Single-Phase Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2015-01-01
A still booming installation of solar photovoltaic (PV) systems has been witnessed worldwide. It is mainly driven by the demand of “clean” power generation. Grid-connected PV systems will become an even active player in the future mixed power systems, which are linked by a vast of power electronics...
Passive P-control of a grid-connected photovoltaic inverter
Meza, C.; Jeltsema, D.; Scherpen, J. M. A.; Biel, D.
2008-01-01
A passive P-controller for a single-phase single-stage grid-connected photovoltaic inverter is presented. Explicit dependance of the PV array parameters on external unpredictable variables such as temperature and solar irradiance is avoided by extending the control scheme with a reference estimator.
Overview of Single-Phase Grid-Connected Photovoltaic Systems
Yang, Yongheng; Blaabjerg, Frede
2015-01-01
A still booming installation of solar photovoltaic (PV) systems has been witnessed worldwide. It is mainly driven by the demand of “clean” power generation. Grid-connected PV systems will become an even active player in the future mixed power systems, which are linked by a vast of power electronics converters. In order to achieve a reliable and efficient power generation from PV systems, stringent demands have been imposed on the entire PV system. It in return advances the development of powe...
Online Variable Topology-Type Photovoltaic Grid-Connected Inverter
DEFF Research Database (Denmark)
Wu, Fengjiang; Sun, Bo; Duan, Jiandong
2015-01-01
In photovoltaic (PV) grid-connected generation system, the key focus is how to expand the generation range of the PV array and enhance the total efficiency of the system. This paper originally derived expressions of the total loss and grid current total harmonics distortions of cascaded inverter...... and H-bridge inverter under the conditions of variable output voltage and power of the PV array. It is proved that, compared with the H-bridge inverter, the operation range of the cascaded inverter is wider, whereas the total loss is larger. Furthermore, a novel online variable topology-type grid......-connected inverter is proposed. A bidirectional power switch is introduced into the conventional cascaded inverter to connect the negative terminals of the PV arrays. When the output voltages of the PV arrays are lower, the proposed inverter works under cascaded inverter mode to obtain wider generation range. When...
DEFF Research Database (Denmark)
Yang, Yongheng; Zhou, Keliang; Blaabjerg, Frede
2013-01-01
-connected PV inverters may be severely affected in different operation modes. In this paper, a detailed analysis is conducted to reveal the relationship between the harmonics level with the power factor and the current level in the PV systems. A current control solution which employs an Internal Model...... Principle (IMP) is proposed to suppress the harmonic currents injected into the grid. Experiments are carried out to verify the analysis and the performance of the proposed control method. It is demonstrated that the proposed method presents an effective solution to harmonics suppression for single......-phase grid-connected PV systems in different operation modes. Especially, it can remove higher order harmonics effectively leading to a better power quality compared to the Proportional plus Multi-Resonant Controller, and it has less computational burden....
Study on unitized inverter with photovoltaic grid-connected and stand-alone functions
Energy Technology Data Exchange (ETDEWEB)
Wang, Haining; Su, Jianhui; Ding, Ming [Hefei University of Technology, Hefei (China)
2008-07-01
The main circuit and algorithm of unitized single phase inverter are presented, in which photovoltaic (PV) grid-connected algorithm, independency sine inverter algorithm and storage battery charge administer are all integrated basing on DSP (Digital Signal Processor). The control system identifies utility failure initiatively and then switches to independency power supply automatically. The methods of charging battery are multiform. Basing on material term to use utility or solar array to charge can optimize charge efficiency, assure the capacitance of battery and prolong life-span of battery. In addition, some results are offered basing on the prototype of a 2.5kW single phase inverter. (orig.)
Harmonic currents Compensator Grid-Connected Inverter at the Microgrid
DEFF Research Database (Denmark)
Asuhaimi Mohd Zin, A.; Naderipour, A.; Habibuddin, M.H.
2016-01-01
The main challenge associated with the grid-connected inverter in distributed generation (DG) systems is to maintain the harmonic contents in output current below the specified values and compensates for unbalanced loads even when the grid is subject to disturbances such as harmonic distortion...... and unbalanced loads. To overcome these challenges, a current control strategy for a three-phase grid-connected inverter under unbalanced and nonlinear load conditions is presented. It enables grid-connected inverter by the proposed control method to inject balanced clean currents to the grid even when the local...... loads are unbalanced and/or nonlinear and also compensate of the harmonic currents and control the active and reactive power. The main advantage and objective of this method is to effectively compensate for the harmonic currents content of the grid current and microgrid without using any compensation...
Grid-connected inverter for wind power generation system
Institute of Scientific and Technical Information of China (English)
YANG Yong; RUAN Yi; SHEN Huan-qing; TANG Yan-yan; YANG Ying
2009-01-01
In wind power generation system the grid-connected inverter is an important section for energy conversion and transmission, of which the performance has a direct influence on the entire wind power generation system. The mathematical model of the grid-connected inverter is deduced firstly. Then, the space vector pulse width modulation (SVPWM) is analyzed. The power factor can be controlled close to unity, leading or lagging, which is realized based on PI-type current controller and grid voltage vector-oriented control. The control strategy is verified by the simulation and experimental results with a good sinusoidal current, a small harmonic component and a fast dynamic response.
Grid-Connected Inverter for Distributed Generation in Microgrid
DEFF Research Database (Denmark)
Naderipour, Amirreza; Miveh, Mohammad Reza; Guerrero, Josep M.
for power generation. DGS units can operate in parallel to the main grid or in a Microgrid (MG) mode. An MG is a discrete energy system consisting of DGSs and loads capable of operating in parallel with, or independently from, the main grid. Meanwhile, Grid-Connected Inverters (GCIs) are typically used...
Design optimization of grid-connected PV inverters
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2011-01-01
The DC/AC inverters are the key elements in grid-connected PV energy production systems. In this paper, new design optimization techniques focused on transformerless (very high efficiency) PV inverters are proposed. They have been developed based on an analysis of the deficiencies of the current......, state-of-the-art PV inverters design technology, which limits the amount of PV energy supplied into the electric grid. The influences of the electric grid regulations and standards and the PV array operational characteristics on the design of grid-connected PV inverters have also been considered....... The simulation results verify that the proposed optimization techniques enable the maximization of the PV energy injected into the electric grid by the optimized PV installation....
Synchronization in single-phase grid-connected photovoltaic systems under grid faults
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2012-01-01
The highly increasing penetration of single-phase photovoltaic (PV) systems pushes the grid requirements related to the integration of PV power systems to be updated. These upcoming regulations are expected to direct the grid-connected renewable generators to support the grid operation and stabil......The highly increasing penetration of single-phase photovoltaic (PV) systems pushes the grid requirements related to the integration of PV power systems to be updated. These upcoming regulations are expected to direct the grid-connected renewable generators to support the grid operation...
Directory of Open Access Journals (Sweden)
J. Fallah Ardashir
2017-06-01
Full Text Available This paper proposes a new single phase transformerless Photovoltaic (PV inverter for grid connected systems. It consists of six power switches, two diodes, one capacitor and filter at the output stage. The neutral of the grid is directly connected to the negative terminal of the source. This results in constant common mode voltage and zero leakage current. Model Predictive Controller (MPC technique is used to modulate the converter to reduce the output current ripple and filter requirements. The main advantages of this inverter are compact size, low cost, flexible grounding configuration. Due to brevity, the operating principle and analysis of the proposed circuit are presented in brief. Simulation and experimental results of 200W prototype are shown at the end to validate the proposed topology and concept. The results obtained clearly verifies the performance of the proposed inverter and its practical application for grid connected PV systems.
Delta Power Control Strategy for Multi-String Grid-Connected PV Inverters
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2016-01-01
With a still increasing penetration level of grid-connected PV systems, more advanced active power control functionalities have been introduced in certain grid regulations. A delta power constraint, where a portion of the active power from the PV panels is reserved during operation, is required...... for grid support (e.g., during frequency deviation). In this paper, a cost-effective solution to realize delta power control for grid-connected PV systems is presented, where the residential/commercial multi-string PV inverter configuration is adopted. This control strategy is a combination of Maximum...... for the entire PV system is achieved. Simulations and experiments have been performed on a 3-kW single-phase grid-connected PV system. The results have confirmed the effectiveness of the delta power control strategy, where the power reserve according to the delta power constraint is achieved under several...
DEFF Research Database (Denmark)
Li, Zhongyu; Zhao, Rende; Xin, Zhen
2016-01-01
The Inrush Transient Current (ITC) in the output of the photovoltaic grid-connected inverters is usually generated when grid voltage sag occurs, which can trigger the protection of the grid-connected inverters, and even destroy the semiconductor switches. Then, the grid-connected inverters...
A New Power Calculation Method for Single-Phase Grid-Connected Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2013-01-01
A new method to calculate average active power and reactive power for single-phase systems is proposed in this paper. It can be used in different applications where the output active power and reactive power need to be calculated accurately and fast. For example, a grid-connected photovoltaic...... system in low voltage ride through operation mode requires a power feedback for the power control loop. Commonly, a Discrete Fourier Transform (DFT) based power calculation method can be adopted in such systems. However, the DFT method introduces at least a one-cycle time delay. The new power calculation...... method, which is based on the adaptive filtering technique, can achieve a faster response. The performance of the proposed method is verified by experiments and demonstrated in a 1 kW single-phase grid-connected system operating under different conditions.Experimental results show the effectiveness...
Robust Droop Control of Grid-Connected Inverters
DEFF Research Database (Denmark)
Elkayam, Moria; Kuperman, Alon; Guerrero, Josep M.
2016-01-01
The use of distributed generation in microgrid systems is becoming a popular way to provide a reliable source of electricity to critical loads. Droop control techniques are used in power systems for the synchronization of grid-connected inverters by local measurements of active and reactive powers....... Despite the benefits of distributed generation, the drawback is that large grid-side impedance steps can cause a system to become unstable. A robust control method based on disturbance observer is proposed in this paper. When the proposed robust controller is utilized, closed loop performance remains...
Zero-Voltage Ride-Through Capability of Single-Phase Grid-Connected Photovoltaic Systems
Directory of Open Access Journals (Sweden)
Zhen Zhang
2017-03-01
Full Text Available Distributed renewable energy systems play an increasing role in today’s energy paradigm. Thus, intensive research activities have been centered on improving the performance of renewable energy systems, including photovoltaic (PV systems, which should be of multiple-functionality. That is, the PV systems should be more intelligent in the consideration of grid stability, reliability, and fault protection. Therefore, in this paper, the performance of single-phase grid-connected PV systems under an extreme grid fault (i.e., when the grid voltage dips to zero is explored. It has been revealed that combining a fast and accurate synchronization mechanism with appropriate control strategies for the zero-voltage ride-through (ZVRT operation is mandatory. Accordingly, the representative synchronization techniques (i.e., the phase-locked loop (PLL methods in the ZVRT operation are compared in terms of detection precision and dynamic response. It shows that the second-order generalized integrator (SOGI-PLL is a promising solution for single-phase systems in the case of fault ride-through. A control strategy by modifying the SOGI-PLL scheme is then introduced to single-phase grid-connected PV systems for ZVRT operation. Simulations are performed to verify the discussions. The results have demonstrated that the proposed method can help single-phase PV systems to temporarily ride through zero-voltage faults with good dynamics.
Current control loop of 3-phase grid-connected inverter
International Nuclear Information System (INIS)
Jabbar, A F; Mansor, M
2013-01-01
This paper presents a comparative study of current control loop in 3-phase inverter which is used to control the active and reactive output power. Generally, current control loop, power control loop and phase lock-loop are the conventional parameters that can be found in an inverter system controlled by the conventional linear control type, for instance proportional (P), integral (I) and derivative (D). If the grid remains stable throughout the day, PID control can be use. However variation of magnitude, frequency, voltage dips, transient, and other related power quality issues occur in a 3-phase grid often affects the control loop. This paper aims to provide an overall review on the available current control techniques used in grid connected system.
Improved Droop Control Strategy for Grid-Connected Inverters
DEFF Research Database (Denmark)
Abusara, Mohammad; Sharkh, Suleiman; Guerrero, Josep M.
2015-01-01
An improved control strategy for grid-connected inverters within microgrids is presented in this paper. The strategy is based on the classical P-ω and Q-V droop method. The improvement in the proposed control strategy is twofold: Firstly, the transient response of the droop controller is improved...... by replacing the traditional method of measuring average power, which is based on using a first order low pass filter, by a real time integration filter. This is shown to reduce the imported transient energy when connecting to the grid. Secondly, the steady state output current quality is improved by utilising...... a virtual inductance, which is shown to reject grid voltage harmonics disturbance and thus improve the output current THD. A small signal model of the inverter based on the transfer function approach is developed to analyse is stability and determine droop gains. Simulation and experimental results...
Model Building of Photovoltaic Array with MPPT Function and Research on Single Phase Grid Connected
Directory of Open Access Journals (Sweden)
Li Zhengzhou
2016-01-01
Full Text Available With the continued development of solar photovoltaic technology, research on distributed grid connected photovoltaic system has become a research focus in the field of photovoltaic grid power plant and the computer simulation technology is an effective technology means in the study. On the basis of the photovoltaic array output characteristic equation, the photovoltaic array maximum power control simulation model based on M function is established by using MATLAB/Simulink and the simulation model of single phase grid connected photovoltaic array is proposed. It overcomes the shortcomings of the process of building the model of the PV array by using Simulink component library and provides the basic guarantee for the realization of system simulation, guiding theory research and system design.
Delta Power Control Strategy for Multistring Grid-Connected PV Inverters
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2017-01-01
, is required for grid support (e.g., during frequency deviation). In this paper, a cost-effective solution to realize delta power control (DPC) for grid-connected PV systems is presented, where the multistring PV inverter configuration is adopted. This control strategy is a combination of maximum power point...... tracking (MPPT) and constant power generation (CPG) modes. In this control scheme, one PV string operating in the MPPT mode estimates the available power, whereas the other PV strings regulate the total PV power by the CPG control strategy in such a way that the delta power constraint for the entire PV...... system is achieved. Simulations and experiments have been performed on a 3-kW single-phase grid-connected PV system. The results have confirmed the effectiveness of the proposed DPC strategy, where the power reserve according to the delta power constraint is achieved under several operating conditions....
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2018-01-01
strategies based on: 1) a power control method (P-CPG), 2) a current limit method (I-CPG) and 3) the Perturb and Observe algorithm (P&O-CPG). However, the operational mode changes (e.g., from the maximum power point tracking to a CPG operation) will affect the entire system performance. Thus, a benchmarking...... of the presented CPG strategies is also conducted on a 3-kW single-phase grid-connected PV system. Comparisons reveal that either the P-CPG or I-CPG strategies can achieve fast dynamics and satisfactory steady-state performance. In contrast, the P&O-CPG algorithm is the most suitable solution in terms of high...
Zero-voltage ride-through capability of single-phase grid-connected photovoltaic systems
DEFF Research Database (Denmark)
Zhang, Zhen; Yang, Yongheng; Ma, Ruiqing
2017-01-01
Distributed renewable energy systems play an increasing role in today’s energy paradigm. Thus, intensive research activities have been centered on improving the performance of renewable energy systems, including photovoltaic (PV) systems, which should be of multiple-functionality. That is, the PV...... systems should be more intelligent in the consideration of grid stability, reliability, and fault protection. Therefore, in this paper, the performance of single-phase grid-connected PV systems under an extreme grid fault (i.e., when the grid voltage dips to zero) is explored. It has been revealed...... that combining a fast and accurate synchronization mechanism with appropriate control strategies for the zero-voltage ride-through (ZVRT) operation is mandatory. Accordingly, the representative synchronization techniques (i.e., the phase-locked loop (PLL) methods) in the ZVRT operation are compared in terms...
Two-stage single-phase grid-connected photovoltaic system with reduced complexity
da Silva, Cintia S.; Motta, Filipe R.; Tofoli, Fernando L.
2011-06-01
This article presents a grid-connected photovoltaic (PV) system using the classical DC-DC buck converter, which is responsible for stepping down the resulting voltage from several series-connected panels. Besides, the structure provides high power factor operation by injecting a quasi-sinusoidal current into the grid, with near no displacement in relation to the line voltage at the point of common coupling among the PV system and the loads. A CSI employing thyristors is cascaded with the DC-DC stage so that AC voltage results. The inverter output voltage level is adjusted by using a low-frequency transformer, which also provides galvanic isolation. The proposed system is described as mathematical approach and design guidelines are presented, providing an overview of the topology. An experimental prototype is also implemented, and relevant results to validate the proposal are discussed.
Disturbance estimator based predictive current control of grid-connected inverters
Al-Khafaji, Ahmed Samawi Ghthwan
2013-01-01
ABSTRACT: The work presented in my thesis considers one of the modern discrete-time control approaches based on digital signal processing methods, that have been developed to improve the performance control of grid-connected three-phase inverters. Disturbance estimator based predictive current control of grid-connected inverters is proposed. For inverter modeling with respect to the design of current controllers, we choose the d-q synchronous reference frame to make it easier to understand an...
Directory of Open Access Journals (Sweden)
Wenzhou Lu
2016-01-01
Full Text Available This paper analyzes the general properties of IMP-based controller and presents an internal-model-principle-based (IMP-based specific harmonics repetitive control (SHRC scheme. The proposed SHRC is effective for specific nk±m order harmonics, with n>m≥0 and k=0,1,2,…. Using the properties of exponential function, SHRC can also be rewritten into the format of multiple resonant controllers in parallel, where the control gain of SHRC is n/2 multiple of that of conventional RC (CRC. Therefore, including SHRC in a stable closed-loop feedback control system, asymptotic disturbance eliminating, or reference tracking for any periodic signal only including these specific harmonic components at n/2 times faster error convergence rate compared with CRC can be achieved. Application examples of SHRC controlled three-phase/single-phase grid-connected PWM inverters demonstrate the effectiveness and advantages of the proposed SHRC scheme.
Grid Connection of Wave Power Farm Using an N-Level Cascaded H-Bridge Multilevel Inverter
Directory of Open Access Journals (Sweden)
Rickard Ekström
2013-01-01
Full Text Available An N-level cascaded H-bridge multilevel inverter is proposed for grid connection of large wave power farms. The point-absorber wave energy converters are individually rectified and used as isolated DC-sources. The variable power characteristics of the wave energy converters are discussed, and a method of mitigating this issue is demonstrated. The complete power control system is given in detail and has been experimentally verified for a single-phase setup of the 9-level inverter. Theoretical expressions of the power sharing between multilevel cells are derived and show good correspondence with the experimental results.
Directory of Open Access Journals (Sweden)
Abdelmajid Abouloifa
2018-01-01
Full Text Available This paper addresses the problem of controlling the single-phase grid connected to the photovoltaic system through a full bridge inverter with LCL-filter. The control aims are threefold: (i imposing the voltage in the output of PV panel to track a reference provided by the MPPT block; (ii regulating the DC-link voltage to guarantee the power exchange between the source and AC grid; (iii ensuring a satisfactory power factor correction (PFC. The problem is dealt with using a cascade nonlinear adaptive controller that is developed making use of sliding-mode technique and observers in order to estimate the state variables and grid parameters, by measuring only the grid current, PV voltage, and the DC bus voltage. The control problem addressed by this work involves several difficulties, including the uncertainty of some parameters of the system and the numerous state variables are inaccessible to measurements. The results are confirmed by simulation under MATLAB∖Simulink∖SimPowerSystems, which show that the proposed regulator is robust with respect to climate changes.
Frequency Adaptive Repetitive Control of Grid-Tied Single-Phase PV Inverters
DEFF Research Database (Denmark)
Zhou, Keliang; Yang, Yongheng; Blaabjerg, Frede
2015-01-01
. This paper thus explores a frequency adaptive repetitive control strategy for grid converters, which employs fractional delay filters in order to adapt to the change of the grid frequency. Case studies with experimental results of a single-phase grid-connected PV inverter system are provided to verify...
State-space-based harmonic stability analysis for paralleled grid-connected inverters
DEFF Research Database (Denmark)
Wang, Yanbo; Wang, Xiongfei; Chen, Zhe
2016-01-01
This paper addresses a state-space-based harmonic stability analysis of paralleled grid-connected inverters system. A small signal model of individual inverter is developed, where LCL filter, the equivalent delay of control system, and current controller are modeled. Then, the overall small signal...... model of paralleled grid-connected inverters is built. Finally, the state space-based stability analysis approach is developed to explain the harmonic resonance phenomenon. The eigenvalue traces associated with time delay and coupled grid impedance are obtained, which accounts for how the unstable...... inverter produces the harmonic resonance and leads to the instability of whole paralleled system. The proposed approach reveals the contributions of the grid impedance as well as the coupled effect on other grid-connected inverters under different grid conditions. Simulation and experimental results...
DEFF Research Database (Denmark)
Zare, Mohammad Hadi; Mohamadian, Mustafa; Wang, Huai
2017-01-01
Microinverters usually connect a PV panel to a Single-phase power grid. In such system, the input power is constant while the output power oscillates twice the line frequency. Thus, the input and output power differences should be stored in a storage component, which is typically an electrolytic ...... irritation of two different places on the micro inverter lifetime is studied....... capacitor. However, electrolytic capacitors are usually blamed for their short lifetime. Recently, some active power decoupling methods are introduced in the literature which can takes advantage of high reliable film capacitors. However, some extra switches and diodes are added to the microinverter which...... can influence the microinverter lifetime. This paper investigates the microinverter reliability according to mission profile where it is installed. To get more accurate results, uncertainties in both lifetime model and manufacturing process are considered. The effect of ambient temperature and solar...
Resonance Interaction of Multi-Parallel Grid-Connected Inverters with LCL Filter
DEFF Research Database (Denmark)
Lu, Minghui; Wang, Xiongfei; Loh, Poh Chiang
2017-01-01
This letter investigates the resonance characteristics and stability problem caused by the interactions of multiparallel LCL-filtered inverters. Compared to single grid-connected inverter, the multiinverter system presents a more challenging resonance issue, where the inverter interactions may...... excite multiple resonances at various frequencies. This letter proposes a modeling and analysis method based on the current separation scheme. It reveals that an interactive resonant current that circulates between the paralleled three-phase inverters may arise, depending on the current distribution...
Grid-Voltage-Feedforward Active Damping for Grid-Connected Inverter with LCL Filter
DEFF Research Database (Denmark)
Lu, Minghui; Wang, Xiongfei; Blaabjerg, Frede
2016-01-01
For the grid-connected voltage source inverters, the feedforward scheme of grid voltage is commonly adopted to mitigate the current distortion caused by grid background voltages harmonics. This paper investigates the grid-voltage-feedforward active damping for grid connected inverter with LCL...... filter. It reveals that proportional feedforward control can not only fulfill the mitigation of grid disturbance, but also offer damping effects on the LCL filter resonance. Digital delays are intrinsic to digital controlled inverters; with these delays, the feedforward control can be equivalent...
Directory of Open Access Journals (Sweden)
Bingzhang Li
2017-03-01
Full Text Available Two-stage single-phase grid-connected converters are widely used in renewable energy applications. Due to the presence of a second harmonic ripple across the DC bus voltage, it is very challenging to design the DC bus voltage control scheme in single-phase grid-connected inverters. The DC bus voltage controller must filter the ripple and balance a tradeoff between low harmonic distortion and high bandwidth. This paper presents a fast DC bus voltage controller, which uses a second order digital finite impulse response (FIR notch filter in conjunction with input power feedforward scheme to ensure the steady-state and dynamic performance. To gain the input power without extra hardware, a Kalman filter is incorporated to estimate the DC bus input current. At the same time, a modulation compensation strategy is implemented to eliminate the nonlinearity of the grid current control loop, which is caused by the DC bus voltage ripple. Moreover, a novel synchronous frame current controller for single-phase systems is also introduced, and its equivalent model in stationary frame has been derived. Simulation and experimental results are provided to verify the effective of the proposed control scheme.
Co-design of the LCL Filter and Control for Grid-Connected Inverters
DEFF Research Database (Denmark)
Zhang, Yu; Xue, Mingyu; Li, Minying
2014-01-01
In most grid-connected inverters (GCI) with an LCL filter, since the design of both the LCL filter and the controller is done separately, considerable tuning efforts have to be exerted when compared to inverters using an L filter. Consequently, an integrated co-design of the filter and the contro...
Application of Fuzzy Control in a Photovoltaic Grid-Connected Inverter
Directory of Open Access Journals (Sweden)
Zhaohong Zheng
2018-01-01
Full Text Available To realize the maximum power output of a grid-connected inverter, the MPPT (maximum power point tracking control method is needed. The perturbation and observation (P&O method can cause the inverter operating point to oscillate near the maximum power. In this paper, the fuzzy control P&O method is proposed, and the fuzzy control algorithm is applied to the disturbance observation method. The simulation results of the P&O method with fuzzy control and the traditional P&O method prove that not only can the new method reduce the power loss caused by inverter oscillation during maximum power point tracking, but also it has the advantage of speed. Inductive loads in the post-grid-connected stage cause grid-connected current distortion. A fuzzy control algorithm is added to the traditional deadbeat grid-connected control method to improve the quality of the system’s grid-connected operation. The fuzzy deadbeat control method is verified by experiments, and the harmonic current of the grid-connected current is less than 3%.
Low voltage ride-through of single-phase transformerless photovoltaic inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Wang, Huai
2013-01-01
Transformerless photovoltaic (PV) inverters are going to be more widely adopted in order to achieve high efficiency, as the penetration level of PV systems is continuously booming. However, problems may arise in highly PV-integrated distribution systems. For example, a sudden stoppage of all PV...... discussed. The selected inverters are the full-bridge inverter with bipolar modulation, full-bridge inverter with DC bypass and the Highly Efficient and Reliable Inverter Concept (HERIC). A 1 kW single-phase grid-connected PV system is analyzed to verify the discussions. The tests confirmed that, although...
Improved control strategy for the three-phase grid-connected inverter
DEFF Research Database (Denmark)
Yao, Zhilei; Xiao, Lan; Guerrero, Josep M.
2015-01-01
An improved control strategy for the three-phase grid-connected inverter with space vector pulse width modulation (SVPWM) is proposed. When the grid current contains harmonics, the d- and q-axis grid currents will be interacted, and then the waveform quality of the grid current will be poorer....... As the reference output voltage cannot directly reflect the change of the reference grid current, the dynamic response of the grid-connected inverter is slow. In order to solve the aforementioned problems, the d- and q-axis grid currents in the decoupled components of the grid current controller can be substituted...... by the d- and q-axis reference grid currents, respectively. The operating principles of the traditional and proposed control methods are illustrated. Experimental results for a 15-kVA three-phase grid-connected inverter with SVPWM verify the theoretical analysis. Compared with the traditional control...
A New Family of Multilevel Grid Connected Inverters Based on Packed U Cell Topology.
Pakdel, Majid; Jalilzadeh, Saeid
2017-09-29
In this paper a novel packed U cell (PUC) based multilevel grid connected inverter is proposed. Unlike the U cell arrangement which consists of two power switches and one capacitor, in the proposed converter topology a lower DC power supply from renewable energy resources such as photovoltaic arrays (PV) is used as a base power source. The proposed topology offers higher efficiency and lower cost using a small number of power switches and a lower DC power source which is supplied from renewable energy resources. Other capacitor voltages are extracted from the base lower DC power source using isolated DC-DC power converters. The operation principle of proposed transformerless multilevel grid connected inverter is analyzed theoretically. Operation of the proposed multilevel grid connected inverter is verified through simulation studies. An experimental prototype using STM32F407 discovery controller board is performed to verify the simulation results.
Grid-connected to/from off-grid transference for micro-grid inverters
Heredero Peris, Daniel; Chillón Antón, Cristian; Pages Gimenez, Marc; Gross, Gabriel Igor; Montesinos Miracle, Daniel
2013-01-01
This paper compares two methods for controlling the on-line transference from connected to stand-alone mode and vice versa in converters for micro-grids. The first proposes a method where the converter changes from CSI (Current Source Inverter) in grid-connected mode to VSI (Voltage Source Inverter) in off-grid. In the second method, the inverter always works as a non-ideal voltage source, acting as VSI, using AC droop control strategy.
Design Optimization of Transformerless Grid-Connected PV Inverters Including Reliability
Koutroulis, Eftichios; Blaabjerg, Frede
2013-01-01
This paper presents a new methodology for optimal design of transformerless photovoltaic (PV) inverters targeting a cost-effective deployment of grid-connected PV systems. The optimal switching frequency as well as the optimal values and types of the PV inverter components is calculated such that the PV inverter LCOE generated during the PV system lifetime period is minimized. The LCOE is also calculated considering the failure rates of the components, which affect the reliability performance...
Directory of Open Access Journals (Sweden)
Xingang Fu
2016-04-01
Full Text Available This paper investigates a novel recurrent neural network (NN-based vector control approach for single-phase grid-connected converters (GCCs with L (inductor, LC (inductor-capacitor and LCL (inductor-capacitor-inductor filters and provides their comparison study with the conventional standard vector control method. A single neural network controller replaces two current-loop PI controllers, and the NN training approximates the optimal control for the single-phase GCC system. The Levenberg–Marquardt (LM algorithm was used to train the NN controller based on the complete system equations without any decoupling policies. The proposed NN approach can solve the decoupling problem associated with the conventional vector control methods for L, LC and LCL-filter-based single-phase GCCs. Both simulation study and hardware experiments demonstrate that the neural network vector controller shows much more improved performance than that of conventional vector controllers, including faster response speed and lower overshoot. Especially, NN vector control could achieve very good performance using low switch frequency. More importantly, the neural network vector controller is a damping free controller, which is generally required by a conventional vector controller for an LCL-filter-based single-phase grid-connected converter and, therefore, can overcome the inefficiency problem caused by damping policies.
Online grid impedance estimation for single-phase grid-connected systems using PQ variations
DEFF Research Database (Denmark)
Ciobotaru, Mihai; Teodorescu, Remus; Rodriguez, Pedro
2007-01-01
algorithms are used in order to estimate the value of the grid impedance. The online grid impedance estimation method can be used for compliance with the anti-islanding standard requirements (IEEE1574, IEEE929 and VDE0126) and for adaptive control of the grid-connected converters. The proposed method...
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2016-01-01
With a still increase of grid-connected Photovoltaic (PV) systems, challenges have been imposed on the grid due to the continuous injection of a large amount of fluctuating PV power, like overloading the grid infrastructure (e.g., transformers) during peak power production periods. Hence, advanced...
Real Time Photovoltaic Array Simulator for Testing Grid-Connected PV Inverters
DEFF Research Database (Denmark)
Sera, Dezso; Valentini, Massimo; Raducu, Alin
2008-01-01
In this paper a real time flexible PV array simulator is presented. It is a system that can simulate different PV panel arrays in specific environmental conditions. To evaluate performance of the Maximum Power Point Tracking (MPPT) of grid-connected Photovoltaic (PV) inverters only measurements...... undertaken with an appropriate PV array simulator provide accurate and reproducible results. Thus the PV array simulator has been developed and implemented. MPPT efficiency tests on a commercial grid-connected PV inverter have been performed to validate the PV array simulator....
Harmonic resonance assessment of multiple paralleled grid-connected inverters system
DEFF Research Database (Denmark)
Wang, Yanbo; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
This paper presents an eigenvalue-based impedance stability analytical method of multiple paralleled grid-connected inverter system. Different from the conventional impedance-based stability criterion, this work first built the state-space model of paralleled grid-connected inverters. On the basis...... of this, a bridge between the state-space-based modelling and impedance-based stability criterion is presented. The proposed method is able to perform stability assessment locally at the connection points of the component. Meanwhile, the eigenvalue-based sensitivity analysis is adopted to identify...
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Bak, Claus Leth
2015-01-01
The increasing number of renewable energy sources at the distribution grid is becoming a major issue for utility companies, since the grid connected converters are operating at different operating points due to the probabilistic characteristics of renewable energy. Besides, typically, the harmonics...... proposes a new model of a single phase grid connected renewable energy source using the Harmonic State Space modeling approach, which is able to identify such problems and the model can be extended to be applied in the multiple connected converter analysis. The modeling results show the different harmonic...... and impedance from other renewable energy sources are not taken carefully into account in the installation and design. However, this may bring an unknown harmonic instability into the multiple power sourced system and also make the analysis difficult due to the complexity of the grid network. This paper...
Frequency scanning-based stability analysis method for grid-connected inverter system
DEFF Research Database (Denmark)
Wang, Yanbo; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
This paper proposes a frequency scanning-based impedance analysis for stability assessment of grid-connected inverter system, which is able to perform stability assessment without using system mathematical models and inherit the superior feature of impedance-based stability criterion with conside......This paper proposes a frequency scanning-based impedance analysis for stability assessment of grid-connected inverter system, which is able to perform stability assessment without using system mathematical models and inherit the superior feature of impedance-based stability criterion...... with consideration of the inverter nonlinearities. Small current disturbance is injected into grid-connected inverter system in a particular frequency range, and the impedance is computed according to the harmonic-frequency response using Fourier analysis, and then the stability is predicted on the basis...... of the impedance stability criterion. The stability issues of grid-connected inverters with grid-current feedback and the converter-current feedback are addressed using the proposed method. The results obtained from simulation and experiments validate the effectiveness of the method. The frequency scanning...
Algaddafi, Ali; Altuwayjiri, Saud A; Ahmed, Oday A; Daho, Ibrahim
2017-01-01
Grid connected inverters play a crucial role in generating energy to be fed to the grid. A filter is commonly used to suppress the switching frequency harmonics produced by the inverter, this being passive, and either an L- or LCL-filter. The latter is smaller in size compared to the L-filter. But choosing the optimal values of the LCL-filter is challenging due to resonance, which can affect stability. This paper presents a simple inverter controller design with an L-filter. The control topology is simple and applied easily using traditional control theory. Fast Fourier Transform analysis is used to compare different grid connected inverter control topologies. The modelled grid connected inverter with the proposed controller complies with the IEEE-1547 standard, and total harmonic distortion of the output current of the modelled inverter has been just 0.25% with an improved output waveform. Experimental work on a commercial PV inverter is then presented, including the effect of strong and weak grid connection. Inverter effects on the resistive load connected at the point of common coupling are presented. Results show that the voltage and current of resistive load, when the grid is interrupted, are increased, which may cause failure or damage for connecting appliances.
Three-level grid-connected photovoltaic inverter with maximum power point tracking
International Nuclear Information System (INIS)
Tsang, K.M.; Chan, W.L.
2013-01-01
Highlight: ► This paper reports a novel 3-level grid connected photovoltaic inverter. ► The inverter features maximum power point tracking and grid current shaping. ► The inverter can be acted as an active filter and a renewable power source. - Abstract: This paper presents a systematic way of designing control scheme for a grid-connected photovoltaic (PV) inverter featuring maximum power point tracking (MPPT) and grid current shaping. Unlike conventional design, only four power switches are required to achieve three output levels and it is not necessary to use any phase-locked-loop circuitry. For the proposed scheme, a simple integral controller has been designed for the tracking of the maximum power point of a PV array based on an improved extremum seeking control method. For the grid-connected inverter, a current loop controller and a voltage loop controller have been designed. The current loop controller is designed to shape the inverter output current while the voltage loop controller can maintain the capacitor voltage at a certain level and provide a reference inverter output current for the PV inverter without affecting the maximum power point of the PV array. Experimental results are included to demonstrate the effectiveness of the tracking and control scheme.
H-Bridge Transformerless Inverter with Common Ground for Single-Phase Solar-Photovoltaic System
DEFF Research Database (Denmark)
Siwakoti, Yam Prasad; Blaabjerg, Frede
2017-01-01
This paper proposes a new single-phase H-Bridge transformerless inverter with common ground for grid-connected photovoltaic systems (hereafter it is called ‘Siwakoti-H’ inverter). The inverter works on the principle of flying capacitor and consists of only four power switches (two reverse blocking...... IGBT's (RB-IGBT) and two MOSFET's), a capacitor and a small filter at the output stage. The proposed topology share a common ground with the grid and the PV source. A Unipolar Sinusoidal Pulse-Width Modulation (SPWM) technique is used to modulate the inverter to minimize switching loss, output current...
Directory of Open Access Journals (Sweden)
Jiao Jiao
2016-11-01
Full Text Available Explored in this paper is the grid impedance effect on the stability of a single-phase grid connected inverter with an LC filter based on an analysis of the inverter output impedance. For a single-phase grid connected inverter, a PI controller is often used to regulate the current injected into the grid. However, the control performance can be influenced when the inverter is connected to a weak grid. Also, the utility grid has background harmonic noise, which can make the injected current distorted. Therefore, analysis of the output impedance of a single-phase grid connected inverter is important for the robustness and stability of the system. By modeling the output impedance of inverter, it can be determined that the proportional gain and integral gain of the controller have an effect on the output impedance. Analytical results show that by adjusting the PI controller parameters, the ability for harmonic reduction and stability of the system can be improved. Simulation and experiments using a 1 kW single-phase grid connected inverter verify the effectiveness of the theoretical analysis.
Small-Signal Modeling and Analysis of Grid-Connected Inverter with Power Differential Droop Control
Directory of Open Access Journals (Sweden)
Xin Chen
2016-01-01
Full Text Available The conventional voltage and frequency droop control strategy in grid-connected inverter suffers a major setback in the presence of disturbance by producing oscillations. Adding a power differential term in droop controller is an effective way to address such drawback. In this paper, grid-connected inverter’s small-signal models of the conventional droop control and the power differential droop control are established. The eigenvalues of the models are then determined by system matrix. The eigenvalues analysis is presented which helps in identifying the relationship between the system stability and controller parameters. It is concluded that the damping ratio of dominant low-frequency eigenvalues increased and the oscillation caused by the disturbance is suppressed when a power differential term is added to the droop control method. The MATLAB/Simulink models of grid-connected inverter with both control strategies are also established to validate the results of small-signal analysis.
Model Building of Photovoltaic Array with MPPT Function and Research on Single Phase Grid Connected
Li Zhengzhou
2016-01-01
With the continued development of solar photovoltaic technology, research on distributed grid connected photovoltaic system has become a research focus in the field of photovoltaic grid power plant and the computer simulation technology is an effective technology means in the study. On the basis of the photovoltaic array output characteristic equation, the photovoltaic array maximum power control simulation model based on M function is established by using MATLAB/Simulink and the simulation m...
Directory of Open Access Journals (Sweden)
Mahmoud Salem
2015-12-01
Full Text Available Achieving high reliable grid-connected photovoltaic (PV systems with high power quality and high operation efficiency is highly required for distributed generation units. A double grid-frequency voltage ripple is found on the dc-link voltage in single-phase photovoltaic grid-connected systems due to the unbalance of the instantaneous dc input and ac output powers. This voltage ripple has undesirable effects on the power quality and operational efficiency of the whole system. Harmonic distortion in the injected current to the grid is one of the problems caused by this double grid-frequency voltage ripple. The double grid frequency ripple propagates to the PV voltage and current which disturb the extracted maximum power from the PV array. This paper introduces intelligent solutions towards mitigate the side effects of the double grid-frequency voltage ripple on the transferred power quality and the operational efficiency of single-phase two-stage grid-connected PV system. The proposed system has three control loops: MPPT control loop, dc-link voltage control loop and inverter current control loop. Solutions are introduced for all the three control loops in the system. The current controller cancels the dc-link voltage effect on the total harmonic distortion of the output current. The dc-link voltage controller is designed to generate a ripple free reference current signal that leads to enhance the quality of the output power. Also a modified MPPT controller is proposed to optimize the extracted power from the PV array. Simulation results show that higher injected power quality is achieved and higher efficiency of the overall system is realized.
Adaptive Synchronization of Grid-Connected Threephase Inverters by Using Virtual Oscillator Control
DEFF Research Database (Denmark)
Li, Mingshen; Gui, Yonghao; Guerrero, Josep M.
2018-01-01
This paper presents an adaptive synchronization for current-controlled grid-connected inverter based on a time domain virtual oscillator controller (VOC). Inspired by the phenomenon of dynamics of adaptive oscillator under the perturbation effect. Firstly, the fast learning rule of the oscillator...
Reliability Oriented Design Tool For the New Generation of Grid Connected PV-Inverters
DEFF Research Database (Denmark)
Sintamarean, Nicolae Cristian; Blaabjerg, Frede; Wang, Huai
2015-01-01
is achieved and is further used as an input to the lifetime model. The proposed reliability-oriented design tool is used to study the impact of mission profile (MP) variation and device degradation (aging) in the PV inverter lifetime. The obtained results indicate that the MP of the field where the PV...... inverter is operating has an important impact (up to 70%) on the converter lifetime expectation, and it should be considered in the design stage to better optimize the converter design margin. In order to have correct lifetime estimation, it is crucial to consider also the device degradation feedback (in......This paper introduces a reliability-oriented design tool for a new generation of grid-connected photovoltaic (PV) inverters. The proposed design tool consists of a real field mission profile (RFMP) model (for two operating regions: USA and Denmark), a PV panel model, a grid-connected PV inverter...
DEFF Research Database (Denmark)
Han, Yang; Li, Zipeng; Guerrero, Josep M.
2015-01-01
typical current feedback control schemes in LCL grid-connected system are analyzed and compared systematically. Analysis in s-domain take the effect of the digital computation and modulation delay into account. The stability analysis is presented by root locus in the discrete domain, the optimal values......Proportional-resonant (PR) compensator and LCL filter becomes a better choice in grid-connected inverter system with high performance and low costs. However, the resonance phenomenon caused by LCL filter affect the system stability significantly. In this paper, the stability problem of three...
Energy Technology Data Exchange (ETDEWEB)
Rampinelli, Giuliano Arns
2010-12-15
Grid-connected photovoltaic systems directly convert solar energy into electrical energy delivering to the distribution grid a clean and renewable energy. These systems are basically formed by an array of photovoltaic modules and inverters. The inverters are responsible for converting direct current to alternating current. A study of electrical and thermal characteristics of inverters used in grid-connected photovoltaic systems from a theoretical and experimental analysis. The inverters tests were carried out in two stages: the first stage was performed at Solar Energy Lab. of the Federal University of Rio Grande do Sul (UFRGS), Brazil, where it was used a 4,8 kW{sub p} grid-connected photovoltaic system and ten inverters of different manufacturers. The inverters electrical characteristics measured and analyzed were: direct current to alternating current conversion efficiency, maximum power point tracker efficiency, power factor and harmonic distortion in current and voltage. Inverters thermal testing was also conducted and its results are presented ana analyzed. The second stage of the experimental tests was performed at Photovoltaic Solar Energy Lab. at CIEMAT in Spain. It was used 3 kW{sub p} photovoltaic system and seven inverters of different manufacturers. The inverters are single-phase, up to 5 kW and different topologies (high frequency transformer, low frequency transformer and transformerless). The influence of DC voltage input in the behavior of DC to AC conversion efficiency and power factor was analyzed. The results of the tests allowed the development of mathematical models that describe the electrical and thermal behavior of the inverters. The proposed mathematical models were inserted into computer simulation software developed at UFRGS named FVConect. The evolution of the simulation results compared to the experimental results validates the proposed models. The analysis of the behavior of the inverters improves the understanding of the operating os
Benchmarking of Grid Fault Modes in Single-Phase Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Zou, Zhixiang
2013-01-01
Pushed by the booming installations of singlephase photovoltaic (PV) systems, the grid demands regarding the integration of PV systems are expected to be modified. Hence, the future PV systems should become more active with functionalities of Low Voltage Ride-Through (LVRT) and grid support...... phase systems under grid faults. The intent of this paper is to present a benchmarking of grid fault modes that might come in future single-phase PV systems. In order to map future challenges, the relevant synchronization and control strategies are discussed. Some faulty modes are studied experimentally...... and provided at the end of this paper. It is concluded that there are extensive control possibilities in single-phase PV systems under grid faults. The Second Order General Integral based PLL technique might be the most promising candidate for future single-phase PV systems because of its fast adaptive...
DEFF Research Database (Denmark)
Wang, Huai; Yang, Yongheng; Blaabjerg, Frede
2013-01-01
While 99% efficiency has been reported, the target of 20 years of service time imposes new challenge to cost-effective solutions for grid-connected photovoltaic (PV) inverters. Aluminum electrolytic capacitors are the weak-link in terms of reliability and lifetime in single-phase PV systems....... A reliability-oriented design guideline is proposed in this paper for the input capacitors in single-phase transformer-less PV inverters. The guideline ensures that the service time requirement is to be accomplished under different power levels and ambient temperature profiles. The theoretical analysis has been...... demonstrated by a 1 kW single-phase PV inverter....
Methods for the Optimal Design of Grid-Connected PV Inverters
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2011-01-01
and the efficient processing of this power by the DC/AC inverter. In this paper two new methods are presented for the optimal design of a PV inverter power section, output filter and MPPT control strategy. The influences of the electric grid regulations and standards as well as the PV array operational......The DC/AC inverters are used in grid-connected PV energy production systems as the power processing interface between the PV energy source and the electric grid. The energy injected into the electric grid by the PV installation depends on the amount of power extracted from the PV power source...
Droop-Controlled Inverters with Seamless Transition between Islanding and Grid-Connected Operations
DEFF Research Database (Denmark)
Hu, Shang-Hung; Kuo, Chun-Yi; Lee, Tzung-Lin
2011-01-01
This paper presents a seamless transition method for droop-controlled inverters to operate in both islanding and grid-connected modes. A local PLL and a virtual inductance are designed to ride through transient when the inverter switches between two modes with no synchronization. The proposed...... method can cooperatively work with well-developed droop controls so that the inverters are able to share load among them as well as subsist under transient events of the utility. Theoretical analysis and experimental results validate effectiveness of the proposed method....
Dynamics Assessment of Grid-Synchronization Algorithms for Single-Phase Grid-Connected Converters
DEFF Research Database (Denmark)
Han, Yang; Luo, Mingyu; Guerrero, Josep M.
2015-01-01
Several advanced phase-lock-loop (PLL) algorithms have been proposed for single-phase power electronic systems. Among these algorithms, the orthogonal signal generators (OSGs) are widely utilized to generate a set of in-quadrature signals, owing to its benefit of simple digital implementation and...
Benchmarking of grid fault modes in single-phase grid-connected photovoltaic systems
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Zou, Zhixiang
2012-01-01
Pushed by the booming installations of single-phase photovoltaic (PV) systems, the grid demands regarding the integration of PV systems are expected to be modified. Hence, the future PV systems should become more active with functionalities of low voltage ride-through (LVRT) and the grid support...
Design optimization of transformerless grid-connected PV inverters including reliability
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2012-01-01
Of the Electricity (LCOE) generated during the PV system lifetime period is minimized. The LCOE is calculated also considering the failure rates of the components, which affect the reliability performance and lifetime maintenance cost of the PV inverter. A design example is presented, demonstrating that compared...... to the non-optimized PV inverter structures, the PV inverters designed using the proposed optimization methodology exhibit lower total manufacturing and lifetime maintenance cost and inject more energy into the electric-grid and by that minimizing LCOE.......This paper presents a new methodology for optimal design of transformerless Photovoltaic (PV) inverters targeting a cost-effective deployment of grid-connected PV systems. The optimal values and types of the PV inverter components are calculated such that the PV inverter Levelized Cost...
Design Optimization of Transformerless Grid-Connected PV Inverters Including Reliability
DEFF Research Database (Denmark)
Koutroulis, Eftichios; Blaabjerg, Frede
2013-01-01
such that the PV inverter LCOE generated during the PV system lifetime period is minimized. The LCOE is also calculated considering the failure rates of the components, which affect the reliability performance and lifetime maintenance cost of the PV inverter. A design example is presented, demonstrating...... that compared to the nonoptimized PV inverter structures, the PV inverters designed using the proposed optimization methodology exhibit lower total manufacturing and lifetime maintenance cost and inject more energy into the electric-grid and by that minimizing LCOE.......This paper presents a new methodology for optimal design of transformerless photovoltaic (PV) inverters targeting a cost-effective deployment of grid-connected PV systems. The optimal switching frequency as well as the optimal values and types of the PV inverter components is calculated...
DEFF Research Database (Denmark)
Akhavan, Ali; Mohammadi, Hamid Reza; Guerrero, Josep M.
2018-01-01
The quality of injected current in multi-paralleled grid-connected inverters is a matter of concern. The current controlled grid-connected inverters with LCL filter are widely used in the distributed generation (DG) systems due to their fast dynamic response and better power features. However...... with resonances in the system, damping methods such as passive or active damping is necessary. Secondly and perhaps more importantly, paralleled grid-connected inverters in a microgrid are coupled due to grid impedance. Generally, the coupling effect is not taken into account when designing the control systems...
Jin, N.; Yang, F.; Shang, S. Y.; Tao, T.; Liu, J. S.
2016-08-01
According to the limitations of the LVRT technology of traditional photovoltaic inverter existed, this paper proposes a low voltage ride through (LVRT) control method based on model current predictive control (MCPC). This method can effectively improve the photovoltaic inverter output characteristics and response speed. The MCPC method of photovoltaic grid-connected inverter designed, the sum of the absolute value of the predictive current and the given current error is adopted as the cost function with the model predictive control method. According to the MCPC, the optimal space voltage vector is selected. Photovoltaic inverter has achieved automatically switches of priority active or reactive power control of two control modes according to the different operating states, which effectively improve the inverter capability of LVRT. The simulation and experimental results proves that the proposed method is correct and effective.
Flexible Control Strategy for Grid-Connected Inverter under Unbalanced Grid Faults without PLL
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Liu, W.; Zhang, X.
2015-01-01
Power oscillation and current quality are the important performance targets for the grid-connected inverter under unbalanced grid faults. Firstly, the inherent reason for the current harmonic and power oscillation of the inverter is discussed with a quantitative analysis. Secondly, a new control...... strategy is proposed to achieve the coordinate control of power and current quality without the need for a phase-locked loop or voltage/current positive/negative sequence extraction calculation. Finally, the experimental tests are conducted under unbalanced grid faults, and the results verify...
Directory of Open Access Journals (Sweden)
M. Pakdel
2017-04-01
Full Text Available This paper presents a novel neutral point clamped full-bridge topology for transformerless photovoltaic grid-tied inverters. Transformerless grid-connected inverters have been used widely in recent years since they offer higher efficiency and lower costs. Ground leakage current suppression is the main issue which should be considered carefully in transformerless photovoltaic grid-connected inverters. Among different methods used to decline ground leakage current, neutral point clamped (NPC topologies are considered more useful and effective. In NPC topologies, the short-circuited output voltage at the freewheeling period is clamped to the middle of the DC bus voltage. Therefore, the common-mode voltage (CM will be constant at the whole switching period. Various NPC topologies such as H6 [1], HB-ZVR [2], oH5 [3], and PN-NPC [4] have been proposed. In this paper, a novel NPC topology is proposed which has lower power losses and higher efficiency over previous topologies. Furthermore, the proposed NPC topology exhibits a similar ground leakage current with the PN-NPC topology. The proposed NPC topology is analyzed theoretically using simulation studies and an experimental prototype is provided to verify theoretical analysis and simulation studies.
DEFF Research Database (Denmark)
Lu, Minghui; Blaabjerg, Frede
2017-01-01
This paper identifies stable resonance frequency range for grid-connected inverter with Grid-Voltage Feedforward Regulator (GVFR). Beginning with the current loop stability analysis without GVFR, system poles distribution is analytically studied in z-domain, the critical frequency is therefore...... calculated as well as the control gain limit. Then, this paper reveals the GVFR would change the system stability in the weak power system, two frequency boundaries and three typical resonance frequency ranges are identified and compared. System poles distribution shows that GVFR can offer damping effects...
DEFF Research Database (Denmark)
Li, Mingshen; Gui, Yonghao; Quintero, Juan Carlos Vasquez
2017-01-01
In this paper, an improved grid voltage modulated control (GVM) with power compensation is proposed for grid-connected voltage inverters when the grid voltage is unbalanced. The objective of the proposed control is to remove the power ripple and to improve current quality. Three power compensation...... objectives are selected to eliminate the negative sequence components of currents. The modified GVM method is designed to obtain two separate second-order systems for not only the fast convergence rate of the instantaneous active and reactive powers but also the robust performance. In addition, this method...
Directory of Open Access Journals (Sweden)
Gianluca Brando
2016-09-01
Full Text Available In the context of grid connected photovoitaic (PV generation systems, there are two paramount aspects regarding the Maximum Power Point Tracking (MPPT of the photovoltaic units and the continuity of the service. The most diffused MPPT algorithms are based on either perturb and observe, or on an incremental conductance approach and need both PV current and voltage measurements. Several topology reconfigurable converters are also associated with the PV plants, guaranteeing fault-tolerant features. The generation continuity can also be assured by interleaved inverters, which keep the system operating at reduced maximum power in case of failure. In this paper, an evolution of a hysteresis based MPPT algorithm is presented, based on the measurement of only one voltage, together with a novel space vector modulation suitable for a two-channel three-phase grid connected interleaved inverter. The proposed MMPT algorithm and modulation technique are tested by means of several numerical analyses on a PV generation system of about 200 kW maximum power. The results testify the validity of the proposed strategies, showing good performance, even during a fault occurrence and in the presence of deep shading conditions.
Research on LLCL Filtering Grid - Connected inverter under the Control of PFI
Li, Ren-qing; Zong, Ke-yong; Wang, Yan-ping; Li, Yang; Zhang, Jing
2018-03-01
This passage puts forward a kind of LLCL inverter which is based on the proportional feedback integral(PFI) control so as so satisfy the request of the grid-current outputed by the renewable energy generation system. The passage builds the topological graph of grid-connected inverter and makes an analysis of principle of linear superposition aims to reveal the essence of the problem of steady-state error that exists in proportional integral control. We use LLCL filter and the method of passive damping to solve the problem of resonant peak. We make simulation of the grid system with the software named MATLAB/Simulink. The result shows that the grid current enters steady state quickly and in the same time, which has the identical phase and frequency of grid-voltage. The harmonic content in grid current satisfies the request of grid standard.
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2016-01-01
In the case of a wide-scale adoption of grid-connected Photovoltaic (PV) systems, more fluctuated power will be injected into the grid due to the intermittency of solar PV energy. A sudden change in the PV power can potentially induce grid voltage fluctuations, and thus challenge the stability......-point. Experiments conducted on a 3-kW single-phase two-stage grid-connected PV system have verified that the proposed solution can accomplish fast dynamics, high accuracy, and high robustness in the power ramp-rate control for PV systems....
Grid-connected photovoltaic power systems: survey of inverter and related protection equipments
Energy Technology Data Exchange (ETDEWEB)
Ishikawa, T
2002-12-15
This report for the International Energy Agency (IEA) made by Task 5 of the Photovoltaic Power Systems (PVPS) programme reports on a survey made on inverter and related protection equipment. The mission of the Photovoltaic Power Systems Programme is to enhance the international collaboration efforts which accelerate the development and deployment of photovoltaic solar energy. Task 5 deals with issues concerning grid-interconnection and distributed PV power systems. This report summarises the data obtained from survey of recent inverter technology and inverter protection equipment for grid interconnected PV systems. The results are based on the surveys using a questionnaire to identify the current status of grid-interconnection inverters. This report is to serve as a reference for those interested in installing grid-connected PV systems, electric utility company personnel, manufacturers and researchers. The results of the survey are presented and discussed. Technical and financial data is reviewed and two appendices provide details on the results obtained and those institutions involved in the survey.
DEFF Research Database (Denmark)
Han, Yang; Li, Zipeng; Yang, Ping
2017-01-01
The LCL grid-connected inverter has the ability to attenuate the high-frequency current harmonics. However, the inherent resonance of the LCL filter affects the system stability significantly. To damp the resonance effect, the dual-loop current control can be used to stabilize the system. The grid...... Control Strategy for LCL-Type Grid-Connected Inverters. Available from: https://www.researchgate.net/publication/313734269_Analysis_and_Design_of_Improved_Weighted_Average_Current_Control_Strategy_for_LCL-Type_Grid-Connected_Inverters [accessed Apr 20, 2017]....... current plus capacitor current feedback system is widely used for its better transient response and high robustness against the grid impedance variations. While the weighted average current (WAC) feedback scheme is capable to provide a wider bandwidth at higher frequencies but show poor stability...
Mani, venkatesan; Ramachandran, Rajeswari; N, Deverajan
2016-01-01
A fuzzy based three phase inverter with single DC source for grid connected photo voltaic (PV) system employing three phase transformer is presented in this paper. Space Vector Pulse Width Modulation (SVPWM) control scheme is effectively used to generate the appropriate switching sequences to the inverter switches. The intend of the fuzzy logic approach is to meet high quality output, fast response and high robustness. Finally Total Harmonics Distortion (THD) generated by the inverter is comp...
The Frequency Fluctuation Impact Analysis for Droop Controlled Grid-connecting Inverter in Microgrid
DEFF Research Database (Denmark)
Wei, Feng; Sun, Kai; Guan, Yajuan
2016-01-01
No matter with PV or batteries as DC source, the droop controlled grid-connecting inverter (DC-GCI) has been widely used in microgrid. As the bandwidth of the outer active and reactive power control loop is designed to be much slower when comparing to the inner voltage/current loop of the DCGCI......, and the low equivalent impedance presented by the system, the power disturbance resulting from grid’s frequency fluctuation of DC-GCI may not be compensated by the outer power controller in time. Therefore, the frequency stability of the system mainly depends on its voltage tracking performance dominated...... by the inner loop’s voltage control strategy. In this paper, three widely used inner voltage/current control schemes, including PI controller in the synchronous rotating reference frame, and the PR controller with fixed and dynamic resonant frequency in the stationary frame have been discussed. The small...
Stability Analysis and Active Damping for LLCL-filter-Based Grid-Connected Inverters
DEFF Research Database (Denmark)
Huang, Min; Wang, Xiongfei; Loh, Poh Chiang
2015-01-01
to use either passive or active damping methods. This paper analyzes the stability of the LLCL-filter based grid-connected inverter and identifies a critical resonant frequency for the LLCL-filter when sampling and transport delays are considered. In a high resonant frequency region the active damping...... is not required but in a low resonant frequency region the active damping is necessary. The basic LLCL resonance damping properties of different feedback states based on a notch filter concept are also studied. Then an active damping method which is using the capacitor current feedback for LLCL......-filter is introduced. Based on this active damping method, a design procedure for the controller is given. Last, both simulation and experimental results are provided to validate the theoretical analysis of this paper....
A Transformer-less Single Phase Inverter For photovoltaic Systems
DEFF Research Database (Denmark)
Mostaan, Ali; Alizadeh, Ebrahim; Qu, Ying
2017-01-01
A single phase transformer-less inverter is introduced in this paper. The negative polarities of the input voltage and output terminal have common ground. Therefore, the leakage current problem that is common in PV systems is eliminated naturally. In addition, the proposed inverter has fewer comp...
Solar-Based Boost Differential Single Phase Inverter | Eya | Nigerian ...
African Journals Online (AJOL)
Solar-Based Boost Differential Single Phase Inverter. ... Solar-based boost differential inverter is reduced down to 22.37% in closed loop system with the aid of Proportional –integral-Differential (PID) ... The dc power source is photovoltaic cell.
Cheng, Yuhua; Chen, Kai; Bai, Libing; Yang, Jing
2014-02-01
Precise control of the grid-connected current is a challenge in photovoltaic inverter research. Traditional Proportional-Integral (PI) control technology cannot eliminate steady-state error when tracking the sinusoidal signal from the grid, which results in a very high total harmonic distortion in the grid-connected current. A novel PI controller has been developed in this paper, in which the sinusoidal wave is discretized into an N-step input signal that is decided by the control frequency to eliminate the steady state error of the system. The effect of periodical error caused by the dead zone of the power switch and conduction voltage drop can be avoided; the current tracking accuracy and current harmonic content can also be improved. Based on the proposed PI controller, a 700 W photovoltaic grid-connected inverter is developed and validated. The improvement has been demonstrated through experimental results.
Power Control Flexibilities for Grid-Connected Multi-Functional Photovoltaic Inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Wang, Huai
2016-01-01
and intelligent services, such as fault ride-through and reactive power compensation, is the key to attain higher utilisation of solar PV energy. Such functionalities for the future PV inverters can contribute to reduced cost of energy, and thus enable more cost-effective PV installations. To implement...... the advanced features, a flexible power controller is developed in this study, which can be configured in the PV inverter and flexibly change from one to another mode during operation. Based on the single-phase PQ theory, the control strategy offers the possibilities to generate appropriate references...... for the inner current control loop. The references depend on system conditions and also specific demands from both system operators and prosumers. Besides, this power control strategy can be implemented in commercial PV inverters as a standardised function, and also the operation modes can be achieved online...
Power control flexibilities for grid-connected multi-functional photovoltaic inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Wang, Huai
2014-01-01
to reduced cost of energy. To implement the advanced features, a flexible power controller is developed in this paper, which can be configured in the PV inverter and flexibly be changed from one to another. This power control strategy is based on the single-phase PQ theory, and it offers the possibilities...... of ancillary and intelligent services, like Low Voltage Ride-Through (LVRT), reactive power compensation, and reliability-oriented thermal management/control by PV systems is a key to attain higher utilization of solar energy. Those essential functionalities for the future PV inverters can contribute...... to generate appropriate references for the inner current control loop. The references depend on the system conditions and also specific demands from both system operators and customers. Besides, this power control strategy can be implemented in a commercial PV inverter as standardized functions, and also...
DEFF Research Database (Denmark)
Mousazadeh, Seyyed Yousef; Jalilian, Alireza; Savaghebi, Mehdi
2018-01-01
In this paper, a coordinated harmonic compensation and voltage support scheme is presented for distributed generations’ (DGs’) interface inverters in a resistive grid-connected microgrid. Voltage support is performed by reactive power compensation which can mitigate the over/under voltage problem...
DEFF Research Database (Denmark)
Kwon, JunBum; Wang, Xiongfei; Bak, Claus Leth
2014-01-01
This paper addresses the harmonic compensation error problem existing with parallel connected inverter in the same grid interface conditions by means of impedance-based analysis and modeling. Unlike the single grid connected inverter, it is found that multiple parallel connected inverters and grid...... impedance can make influence to each other if they each have a harmonic compensation function. The analysis method proposed in this paper is based on the relationship between the overall output impedance and input impedance of parallel connected inverter, where controller gain design method, which can...
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2017-01-01
As the penetration level of grid-connected PV systems increases, more advanced control functionality is demanded. In order to ensure smooth and friendly grid integration as well as enable more PV installations, the power generated by PV systems needs to be flexible and capable of: 1) limiting...... strategies for grid-connected PV inverters by modifying maximum power point tracking algorithms, where the PV power is regulated by changing the operating point of the PV system. In this way, no extra equipment is needed, being a cost-effective solution. Experiments on a 3-kW grid-connected PV system have...... the maximum feed-in power, 2) ensuring a smooth change rate, and 3) providing a power reserve. Besides, such flexible power control functionalities have to be achieved in a cost-effective way in order to ensure the competitiveness of solar energy. Therefore, this paper explores flexible active power control...
Online Optimal Switching Frequency Selection for Grid-Connected Voltage Source Inverters
Directory of Open Access Journals (Sweden)
Saher Albatran
2017-12-01
Full Text Available Enhancing the performance of the voltage source inverters (VSIs without changing the hardware structure has recently acquired an increased amount of interest. In this study, an optimization algorithm, enhancing the quality of the output power and the efficiency of three-phase grid connected VSIs is proposed. Towards that end, the proposed algorithm varies the switching frequency (fsw to maintain the best balance between switching losses of the insulated-gate-bipolar-transistor (IGBT power module as well as the output power quality under all loading conditions, including the ambient temperature effect. Since there is a contradiction with these two measures in relation to the switching frequency, the theory of multi-objective optimization is employed. The proposed algorithm is executed on the platform of Altera® DE2-115 field-programmable-gate-array (FPGA in which the optimal value of the switching frequency is determined online without the need for heavy offline calculations and/or lookup tables. With adopting the proposed algorithm, there is an improvement in the VSI efficiency without degrading the output power quality. Therefore, the proposed algorithm enhances the lifetime of the IGBT power module because of reduced variations in the module’s junction temperature. An experimental prototype is built, and experimental tests are conducted for the verification of the viability of the proposed algorithm.
Zero-Axis Virtual Synchronous Coordinate Based Current Control Strategy for Grid-Connected Inverter
Directory of Open Access Journals (Sweden)
Longyue Yang
2018-05-01
Full Text Available Unbalanced power has a great influence on the safe and stable operation of the distribution network system. The static power compensator, which is essentially a grid-connected inverter, is an effective solution to the three-phase power imbalance problem. In order to solve the tracking error problem of zero-sequence AC current signals, a novel control strategy based on zero-axis virtual synchronous coordinates is proposed in this paper. By configuring the operation of filter transmission matrices, a specific orthogonal signal is obtained for zero-axis reconstruction. In addition, a controller design scheme based on this method is proposed. Compared with the traditional zero-axis direct control, this control strategy is equivalent to adding a frequency tuning module by the orthogonal signal generator. The control gain of an open loop system can be equivalently promoted through linear transformation. With its clear mathematical meaning, zero- sequence current control can be controlled with only a first-order linear controller. Through reasonable parameter design, zero steady-state error, fast response and strong stability can be achieved. Finally, the performance of the proposed control strategy is verified by both simulations and experiments.
Passivity Enhancement in RES Based Power Plant with Paralleled Grid-Connected Inverters
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Blaabjerg, Frede
2016-01-01
Harmonic instability is threatening the operation of power plants with multiple grid connected converters in parallel. To analyze and improve the stability of the grid connected converters, the passivity of the output admittance converters is first analyzed in this paper. It is shown that the non-passivity...
International Nuclear Information System (INIS)
García-Triviño, Pablo; Gil-Mena, Antonio José; Llorens-Iborra, Francisco; García-Vázquez, Carlos Andrés; Fernández-Ramírez, Luis M.; Jurado, Francisco
2015-01-01
Highlights: • Three PSO-based PI controllers for a grid-connected inverter were presented. • Two online PSO-based PI controllers were compared with an offline PSO-tuned PI. • The HRES and the inverter were evaluated under power changes and grid voltage sags. • Online ITAE-based PSO reduced ITAE (current THD) by 15.24% (5.32%) versus offline one. - Abstract: This paper is focused on the study of particle swarm optimization (PSO)-based PI controllers for the power control of a grid-connected inverter supplied from a hybrid renewable energy system. It is composed of two renewable energy sources (wind turbine and photovoltaic – PV – solar panels) and two energy storage systems (battery and hydrogen system, integrated by fuel cell and electrolyzer). Three PSO-based PI controllers are implemented: (1) conventional PI controller with offline tuning by PSO algorithm based on the integral time absolute error (ITAE) index; (2) PI controllers with online self-tuning by PSO algorithm based on the error; and (3) PI controllers with online self-tuning by PSO algorithm based on the ITAE index. To evaluate and compare the three controllers, the hybrid renewable energy system and the grid-connected inverter are simulated under changes in the active and reactive power values, as well as under a grid voltage sag. The results show that the online PSO-based PI controllers that optimize the ITAE index achieves the best response
DEFF Research Database (Denmark)
Yang, Yongheng; Wang, Huai; Blaabjerg, Frede
2013-01-01
years) has been set as a main target and an emerging demand from the customers, which imposes a new challenge on grid-connected transformerless inverters. In order to reduce maintenance cost, it is essential to predict the lifetime of the transformerless PV inverter and its components based......The popularity of transformerless photovoltaic (PV) inverters in Europe proves that these topologies can achieve higher efficiency (e.g., ≥ 98% has been reported). Along with the advanced power electronics technology and the booming development of PV power systems, a long service time (e.g. 25...... on the mission profiles — solar irradiance and ambient temperature. In this paper, a mission profile based analysis approach is proposed and it is demonstrated by three main single-phase transformerless PV inverters — Full-Bridge (FB) with bipolar modulation scheme, the FB inverter with DC bypass (FB...
DEFF Research Database (Denmark)
Afshari, Ehsan; Moradi, Gholam Reza; Rahimi, Ramin
2017-01-01
Power quality and voltage control are among the most important aspects of the grid-connected power converter operation under faults. Non-sinusoidal current is injected during unbalanced voltage sag and active or/and reactive power includes double frequency content. This paper introduces a novel...... control strategy to mitigate the double grid frequency oscillations in the active power and dc-link voltage of the two-stage three-phase grid-connected Photovoltaic (PV) inverters during unbalanced faults. With the proposed control method, PV inverter injects sinusoidal currents under unbalanced grid...... faults. In addition, an efficient and easy-to-implement current limitation method is introduced, which can effectively limit the injected currents to the rated value during faults. In this case, the fault-ride-through operation is ensured and it will not trigger the overcurrent protection. A non...
Gu, Herong; Guan, Yajuan; Wang, Huaibao; Wei, Baoze; Guo, Xiaoqiang
2014-01-01
Microgrid is an effective way to integrate the distributed energy resources into the utility networks. One of the most important issues is the power flow control of grid-connected voltage-source inverter in microgrid. In this paper, the small-signal model of the power flow control for the grid-connected inverter is established, from which it can be observed that the conventional power flow control may suffer from the poor damping and slow transient response. While the new power flow control can mitigate these problems without affecting the steady-state power flow regulation. Results of continuous-domain simulations in MATLAB and digital control experiments based on a 32-bit fixed-point TMS320F2812 DSP are in good agreement, which verify the small signal model analysis and effectiveness of the proposed method. PMID:24672304
Gu, Herong; Guan, Yajuan; Wang, Huaibao; Wei, Baoze; Guo, Xiaoqiang
2014-01-01
Microgrid is an effective way to integrate the distributed energy resources into the utility networks. One of the most important issues is the power flow control of grid-connected voltage-source inverter in microgrid. In this paper, the small-signal model of the power flow control for the grid-connected inverter is established, from which it can be observed that the conventional power flow control may suffer from the poor damping and slow transient response. While the new power flow control can mitigate these problems without affecting the steady-state power flow regulation. Results of continuous-domain simulations in MATLAB and digital control experiments based on a 32-bit fixed-point TMS320F2812 DSP are in good agreement, which verify the small signal model analysis and effectiveness of the proposed method.
Citro, Costantino; Gavriluta, Catalin; Nizak Md, H. K.; Beltran, H.
2012-01-01
This paper presents a design procedure for linear current controllers of three-phase grid-connected inverters. The proposed method consists in deriving a numerical model of the converter by using software simulations and applying the pole placement technique to design the controller with the desired performances. A clear example on how to apply the technique is provided. The effectiveness of the proposed design procedure has been verified through the experimental results obtained with ...
DEFF Research Database (Denmark)
Yang, Dongsheng; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
The LCL-type grid connected inverter has been widely used as the intelligent power interface between the distributed generation unit and the power grid. To reduce the cost and volume of the filter, it is desirable to design the LCL filter with higher resonance frequency provided that the quality...... of injected grid current is not compromised. Actually, it is the typical case for the T-type or NPC three-level inverter to design its LCL resonance frequency close to half of the switching frequency. In this case, however, the sideband effect of SPWM modulation can impose a significant impact on the system...
Control of Single-Stage Single-Phase PV inverter
DEFF Research Database (Denmark)
Ciobotaru, Mihai; Teodorescu, Remus; Blaabjerg, Frede
2005-01-01
In this paper the issue of control strategies for single-stage photovoltaic (PV) inverter is addressed. Two different current controllers have been implemented and an experimental comparison between them has been made. A complete control structure for the single-phase PV system is also presented......-forward; - and the grid current controller implemented in two different ways, using the classical proportional integral (PI) and the novel proportional resonant (PR) controllers. The control strategy was tested experimentally on 1.5 kW PV inverter....
DEFF Research Database (Denmark)
Kerekes, Tamas; Liserre, Marco; Mastromauro, R. A.
2009-01-01
Future ancillary services provided by photovoltaic (PV) systems could facilitate their penetration in power systems. Also low power PV systems can be designed to improve the power quality. This paper presents a single-phase photovoltaic system that provides grid voltage support and compensation o...
DEFF Research Database (Denmark)
Golestan, Saeed; Monfared, Mohammad; D. Freijedo, Francisco
2012-01-01
One of the most important aspects for the proper operation of the single-phase grid-tied power-conditioning systems is the synchronization with the utility grid. Among various synchronization techniques, phase locked loop (PLL) based algorithms have found a lot of interest for the advantages...
International Nuclear Information System (INIS)
Himour, Kamal; Ghedamsi, Kaci; Berkouk, El Madjid
2014-01-01
Highlights: • Use of battery bank in grid connection photovoltaic system to ensure the energetic autonomy of the system. • Improve the quality of energy by the use of five-level inverter in a grid connection PV generation system. • Control of inverter by fast and simplified space vector pulse width modulation. • Control and supervision of active and reactive power in the grid. - Abstract: This paper aimed to evaluate the use of photovoltaic-battery storage systems to supply electric power in the distribution grid through a multilevel inverter. The proposed system is composed by four PV generators with MPPT (P and O) control, four battery storage systems connected to each capacitor of the DC link and a five level diode clamped inverter connected to the grid by a traditional three phase transformer. The proposed control has a hierarchical structure with both a grid side control level to regulate the power and the current injected to the grid and four input side regulation units. The system operator controls the power production of the four PV generators by sending out reference power signals to each input side regulation unit, the input side regulation units regulate the voltage of each capacitor of the DC link, regulate the voltage and the state of charge of each battery storage system
DEFF Research Database (Denmark)
Yang, Yongheng; Hadjidemetriou, Lenos; Blaabjerg, Frede
2015-01-01
Grid-connected renewables are increasingly developed in recent years, e.g. wind turbine systems and photovoltaic systems. Synchronization of the injected current with the grid is mandatory. However, grid disturbances like voltage sags, harmonics, and frequency deviations may occur during operatio...
DEFF Research Database (Denmark)
Qu, Hao; Yang, Xijun; Guo, Yougui
2014-01-01
Single-phase voltage source converter (VSC) is an important power electronic converter (PEC), including single-phase voltage source inverter (VSI), single-phase voltage source rectifier (VSR), single-phase active power filter (APF) and single-phase grid-connection inverter (GCI). Single-phase VSC...
Baygi, Mahdi Oloumi; Ghazi, Reza; Monfared, Mohammad
2014-07-01
Applying the min-projection strategy (MPS) to a three-phase grid-connected inverter to improve its transient performance is the main objective of this paper. For this purpose, the inverter is first modeled as a switched linear system. Then, the feasibility of the MPS technique is investigated and the stability criterion is derived. Hereafter, the fundamental equations of the MPS for the control of the inverter are obtained. The proposed scheme is simulated in PSCAD/EMTDC environment. The validity of the MPS approach is confirmed by comparing the obtained results with those of VOC method. The results demonstrate that the proposed method despite its simplicity provides an excellent transient performance, fully decoupled control of active and reactive powers, acceptable THD level and a reasonable switching frequency. Copyright © 2014 ISA. Published by Elsevier Ltd. All rights reserved.
DEFF Research Database (Denmark)
Hu, Shang-hung; Lee, Tzung-Lin; Kuo, Chun-Yi
2016-01-01
This paper presents a seamless transition method for a droop-controlled inverter. The droop control is suitable to make the inverter work as a voltage source in both islanded and grid-connected modes, however, the transfer between theses modes can result in a big inrush current that may damage...... a smooth transition between them, requiring neither synchronization signals nor grid-side information. The control algorithm and design procedure are presented. Experimental results from a laboratory prototype validate the effectiveness of the proposed method....... the system. The proposed method allows the droop-controlled inverter to improve the transient response when transferring between modes, by detecting the inrush current, activating a current control loop during transients, and then transferring back to droop-controlled mode smoothly by using a virtual...
DEFF Research Database (Denmark)
Vernica, Ionut; Ma, Ke; Blaabjerg, Frede
2017-01-01
provide valuable reliability information based on given mission profiles and system specification is first developed and its main concept is presented. In order to facilitate the test and access to the loading and lifetime information of the power devices, a novel mission profile based stress emulator...... experimental setup is proposed and designed. The link between the stress emulator setup and the reliability tool software is highlighted. Finally, the reliability assessment platform is demonstrated on a 3-phase grid-connected inverter application study case....
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Liu, Wenzhao; Lu, Zhigang
2017-01-01
The grid-connected inverters may experience excessive current stress in case of unbalanced grid voltage Fault Ride Through (FRT), which significantly affects the reliability of the power supply system. In order to solve the problem, the inherent mechanisms of the excessive current phenomenon...... with the conventional FRT solutions are discussed. The quantitative analysis of three phase current peak values are conducted and a novel current-limited control strategy is proposed to achieve the flexible active and reactive power regulation and successful FRT in a safe current operation area with the aim...
A Unified Current Loop Tuning Approach for Grid-Connected Photovoltaic Inverters
Directory of Open Access Journals (Sweden)
Weiyi Zhang
2016-09-01
Full Text Available High level penetration of renewable energy sources has reshaped modern electrical grids. For the future grid, distributed renewable power generation plants can be integrated in a larger scale. Control of grid-connected converters is required to achieve fast power reference tracking and further to present grid-supporting and fault ride-through performance. Among all of the aspects for converter control, the inner current loop for grid-connected converters characterizes the system performance considerably. This paper proposes a unified current loop tuning approach for grid-connected converters that is generally applicable in different cases. A direct discrete-time domain tuning procedure is used, and particularly, the selection of the phase margin and crossover frequency is analyzed, which acts as the main difference compared with the existing studies. As a general method, the approximation in the modeling of the controller and grid filter is avoided. The effectiveness of the tuning approach is validated in both simulation and experimental results with respect to power reference tracking, frequency and voltage supporting.
Direct-current vector control of three-phase grid-connected rectifier-inverter
Energy Technology Data Exchange (ETDEWEB)
Li, Shuhui; Haskew, Timothy A.; Hong, Yang-Ki; Xu, Ling [Department of Electrical and Computer Engineering, University of Alabama, Tuscaloosa, AL 35475 (United States)
2011-02-15
The three-phase grid-connected converter is widely used in renewable and electric power system applications. Traditionally, control of the three-phase grid-connected converter is based on the standard decoupled d-q vector control mechanism. Nevertheless, the study of this paper shows that there is a limitation in the conventional standard vector control method. Some of the limitations have also been found recently by other researchers. To overcome the shortage of the conventional vector control technique, this paper proposes a new direct-current d-q vector control mechanism in a nested-loop control structure, based on which an optimal control strategy is developed in a nonlinear programming formulation. The behaviors of both the conventional and proposed control methods are compared and evaluated in simulation and laboratory hardware experiment environments, both of which demonstrates that the proposed approach is effective for grid-connected power converter control in a wide system conditions while the conventional standard vector control approach may behave improperly especially when the converter operates beyond its PWM saturation limit. (author)
DEFF Research Database (Denmark)
Pan, Donghua; Ruan, Xinbo; Wang, Xiongfei
2018-01-01
Single-loop current control is an attractive scheme for the LCL-type grid-connected inverter due to its simplicity and low cost. However, conventional single-loop control schemes, which command either the inverter current or the grid current, are subject to the specific resonance frequency regions....... The weighted average current control, which splits the filter capacitor into two parts (in form of an LCCL filter) and commands the current flowing between these two parts, is independent of the resonance frequency, but on the other hand, it is limited by the poor sensitivity to the grid impedance variation...... and weak stability in the grid current. These limitations are comprehensively explained in this paper and then addressed by identifying that the single-loop weighted average current control is equivalent to the dual-loop grid current control with an inherent capacitor current active damping. By tuning...
Energy Technology Data Exchange (ETDEWEB)
Burger, Bruno [Fraunhofer-Institute for Solar Energy Systems ISE, Department of Electrical Energy Systems, Heidenhofstr. 2, 79110 Freiburg (Germany); Ruether, Ricardo [LABSOLAR-Laboratorio de Energia Solar, LabEEE-Laboratorio de Eficiencia Energetica em Edificacoes, Universidade Federal de Santa Catarina/UFSC, Caixa Postal 476, Florianopolis-SC 88040-900 (Brazil)
2006-01-15
Inverter sizing strategies for grid-connected photovoltaic (PV) systems often do not take into account site-dependent peculiarities of ambient temperature, inverter operating temperature and solar irradiation distribution characteristics. The operating temperature affects PV modules and inverters in different ways and PV systems will hardly ever have a DC output equal to or above their STC-rated nominal power. Inverters are usually sized with a nominal AC output power some 30% (sometimes even more) below the PV array nominal power. In this paper, we show that this practice might lead to considerable energy losses, especially in the case of PV technologies with high temperature coefficients of power operating at sites with cold climates and of PV technologies with low temperature coefficients of power operating at sites with warm climates and an energy distribution of sunlight shifted to higher irradiation levels. In energy markets where PV kWh are paid premium tariffs, like in Germany, energy yield optimization might result in a favorable payback of the extra capital invested in a larger inverter. This paper discusses how the time resolution of solar radiation data influences the correct sizing of PV plants. We demonstrate that using instant (10s) irradiation values instead of average hourly irradiation values leads to considerable differences in optimum inverter sizing. When calculating inverter yearly efficiency values using both, hourly averages and 1-min averages, we can show that with increased time resolution of solar irradiation data there are higher calculated losses due to inverter undersizing. This reveals that hourly averages hide important irradiation peaks that need to be considered. We performed these calculations for data sets from pyranometer readings from Freiburg (48{sup o}N, Germany) and Florianopolis (27{sup o}S, Brazil) to further show the peculiarities of the site-dependent distribution of irradiation levels and its effects on inverter sizing
Study of LCL filter performance for inverter fed grid connected system
Thamizh Thentral, T. M.; Geetha, A.; Subramani, C.
2018-04-01
The abandoned use of power electronic converters in the application of grid connected system paves a way for critical injected harmonics. Hence the use of filter becomes a significant play among the present scenario. Higher order passive filter is mostly preferred in this application because of its reduced cost and size. This paper focuses on the design of LCL filter for the reduction of injected harmonics. The reason behind choosing LCL filter is inductor sizing and good ripple component attenuation over the other conventional filters. This work is simulated in MATLAB platform and the results are prominent to the objectives mentioned above. Also, the simulation results are verified with the implemented hardware model.
DEFF Research Database (Denmark)
Ye, Tao; Dai, Ning-Yi; Lam, Chi-Seng
2016-01-01
to compensate reactive power and transfer active power simultaneously. It is a promising solution for micro-grid and building-integrated distributed generator systems. A quasiproportional- resonant (quasi-PR) controller is applied to reduce steady-state current tracking errors of the CGCI in this paper......The capacitive-coupling grid-connected inverter (CGCI) is coupled to the point of common coupling via a second-order LC branch. Its operational voltage is much lower than that of a conventional inductive-coupling grid-connected inverter (IGCI) when it serves as a multifunctional inverter...... tracking errors are greatly reduced when the quasi-PR controller rather than the proportional-integration controller is applied. Experimental results are also provided to validate the CGCI as a multifunctional grid-connected inverter....
Nonlinear adaptive control of grid-connected three-phase inverters for renewable energy applications
Mahdian-Dehkordi, N.; Namvar, M.; Karimi, H.; Piya, P.; Karimi-Ghartemani, M.
2017-01-01
Distributed generation (DG) units are often interfaced to the main grid using power electronic converters including voltage-source converters (VSCs). A VSC offers dc/ac power conversion, high controllability, and fast dynamic response. Because of nonlinearities, uncertainties, and system parameters' changes involved in the nature of a grid-connected renewable DG system, conventional linear control methods cannot completely and efficiently address all control objectives. In this paper, a nonlinear adaptive control scheme based on adaptive backstepping strategy is presented to control the operation of a grid-connected renewable DG unit. As compared to the popular vector control technique, the proposed controller offers smoother transient responses, and lower level of current distortions. The Lyapunov approach is used to establish global asymptotic stability of the proposed control system. Linearisation technique is employed to develop guidelines for parameters tuning of the controller. Extensive time-domain digital simulations are performed and presented to verify the performance of the proposed controller when employed in a VSC to control the operation of a two-stage DG unit and also that of a single-stage solar photovoltaic system. Desirable and superior performance of the proposed controller is observed.
Sangwongwanich, Ariya; Yang, Yongheng; Sera, Dezso; Blaabjerg, Frede
2018-01-01
Lifetime of PV inverters is affected by the installation sites related to different solar irradiance and ambient temperature profiles (also referred to as mission profiles). In fact, the installation site also affects the degradation rate of the PV panels, and thus long-term energy production and reliability. Prior-art lifetime analysis in PV inverters has not yet investigated the impact of PV panel degradations. This paper thus evaluates the lifetime of PV inverters considering panel degrada...
Control Aspects of a LCL Grid-Connected Green Power Inverter
DEFF Research Database (Denmark)
Kjær, Søren Bækhøj; Andersen, Gert Karmisholt; Klumpner, Christian
2002-01-01
A full-bridge inverter for interfacing the utility grid is developed for using in a Green Power Inverter application. The inverter is feed from an arbitrary green power source (fuel cell, photovoltaic, small wind turbine etc.) through a rectifier into the dc-link. In order to maintain a sinusoidal...... grid current with low harmonic distortion and a high power factor, the inverter is controlled to emulate a negative resistance towards the grid. The size of the emulated resistor is determined by the dc-link voltage controller, which tries to maintain a constant dc-link voltage. This is however...
Fault Ride-Through of a Grid-connected Photovoltaic System with Quasi Z Source Inverter
DEFF Research Database (Denmark)
Al-Durra, Ahmed; Fayyad, Yara; Muyeen, S.M.
2016-01-01
This article presents fault ride-through schemes for a three-phase quasi Z source single-stage photovoltaic (PV) inverter that is connected to the grid after the distribution network. The quasi Z source inverter employs a unique LC network to couple the inverter main circuit to the input of the PV...... the grid side so that the grid fault ride-through requirements can be fulfilled. Scheme A involves control modification in the system; Schemes B and C involve hardware modification in the circuit topology by adding a chopper circuit across the DC link in Scheme B and across the quasi Z source inverter...
Grid-Connected Control Strategy of Five-level Inverter Based on Passive E-L Model
Directory of Open Access Journals (Sweden)
Tao Li
2017-10-01
Full Text Available At present, the research on five-level inverters mainly involves the modulation algorithm and topology, and few articles study the five-level inverter from the control strategy. In this paper, the nonlinear passivity-based control (PBC method is proposed for single-phase uninterruptible power supply inverters. The proposed PBC method is based on an energy shaping and damping injection idea, which is performed to regulate the energy flow of an inverter to a desired level and to assure global asymptotic stability, respectively. Furthermore, this paper presents a control algorithm based on the theory of passivity that gives an inverter in a photovoltaic system additional functions: power factor correction, harmonic currents compensation, and the ability to stabilize the system under varying injection damping. Finally, the effectiveness of the PBC method in terms of both stability and harmonic distortion is verified by the simulation and experiments under resistive and inductive loads.
Isolated high-efficiency grid-connected de-central inverter for photovoltaic modules
Vermulst, B.J.D.
2012-01-01
While an increasing number of photovoltaic (PV) systems is installed, those systems typically use central inverters. In practical cases, output-power differences between PV modules will cause these central-inverter-based systems not to achieve Maximum Power Point (MPP) for each PV module.
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Sera, Dezso
2018-01-01
Lifetime of PV inverters is affected by the installation sites related to different solar irradiance and ambient temperature profiles (also referred to as mission profiles). In fact, the installation site also affects the degradation rate of the PV panels, and thus long-term energy production...... and reliability. Prior-art lifetime analysis in PV inverters has not yet investigated the impact of PV panel degradations. This paper thus evaluates the lifetime of PV inverters considering panel degradation rates and mission profiles. Evaluations have been carried out on PV systems installed in Denmark...... and Arizona. The results reveal that the PV panel degradation rate has a considerable impact on the PV inverter lifetime, especially in the hot climate (e.g., Arizona), where the panel degrades at a faster rate. In that case, the PV inverter lifetime prediction can be deviated by 54%, if the impact of PV...
Directory of Open Access Journals (Sweden)
Yang Yu
2013-01-01
Full Text Available Based on a brief review on current harmonics generation mechanism for grid-connected inverter under distorted grid voltage, the harmonic disturbances and uncertain items are immersed into the original state-space differential equation of grid-connected inverter. A new algorithm of global current harmonic rejection based on nonlinear backstepping control with multivariable internal model principle is proposed for grid-connected inverter with exogenous disturbances and uncertainties. A type of multivariable internal model for a class of nonlinear harmonic disturbances is constructed. Based on application of backstepping control law of the nominal system, a multivariable adaptive state feedback controller combined with multivariable internal model and adaptive control law is designed to guarantee the closed-loop system globally uniformly bounded, which is proved by a constructed Lyapunov function. The presented algorithm extends rejection of nonlinear single-input systems to multivariable globally defined normal form, the correctness and effectiveness of which are verified by the simulation results.
Control strategy based on SPWM switching patterns for grid connected photovoltaic inverter
Hassaine, L.; Mraoui, A.
2017-02-01
Generally, for lower installation of photovoltaic systems connected to the grid, pulse width modulation (PWM) is a widely used technique for controlling the voltage source inverters injects currents into the grid. The current injected must be sinusoidal with reduced harmonic distortion. In this paper, a digital implementation of a control strategy based on PWM switching patterns for an inverter for photovoltaic system connected to the grid is presented. This strategy synchronize a sinusoidal inverter output current with a grid voltage The digital implementation of the proposed PWM switching pattern when is compared with the conventional one exhibit the advantage: Simplicity, reduction of the memory requirements and power calculation for the control
Interaction Admittance Based Modeling of Multi-Paralleled Grid-Connected Inverter with LCL-Filter
DEFF Research Database (Denmark)
Lu, Minghui; Blaabjerg, Frede; Wang, Xiongfei
2016-01-01
This paper investigates the mutual interaction and stability issues of multi-parallel LCL-filtered inverters. The stability and power quality of multiple grid-tied inverters are gaining more and more research attention as the penetration of renewables increases. In this paper, interactions...... and coupling effects among the multi-paralleled inverters and power grid are explicitly revealed. An Interaction Admittance concept is introduced to express and model the interaction through the physical admittances of the network. Compared to the existing modeling methods, the proposed analysis provides...
DEFF Research Database (Denmark)
Zhou, Xiaoping; Zhou, Leming; Chen, Yandong
2018-01-01
In this paper, a robust grid-current-feedback reso-nance suppression (GCFRS) method for LCL-type grid-connected inverter is proposed to enhance the system damping without introducing the switching noise and eliminate the impact of control delay on system robustness against grid-impedance variation....... It is composed of GCFRS method, the full duty-ratio and zero-beat-lag PWM method, and the lead-grid-current-feedback-resonance-suppression (LGCFRS) method. Firstly, the GCFRS is used to suppress the LCL-resonant peak well and avoid introducing the switching noise. Secondly, the proposed full duty-ratio and zero......-beat-lag PWM method is used to elimi-nate the one-beat-lag computation delay without introducing duty cycle limitations. Moreover, it can also realize the smooth switching from positive to negative half-wave of the grid current and improve the waveform quality. Thirdly, the proposed LGCFRS is used to further...
Control of Grid Connected Photovoltaic System Using Three-Level T-Type Inverter
Zorig, Abdelmalik; Belkeiri, Mohammed; Barkat, Said; Rabhi, Abdelhamid
2016-08-01
Three-level T-Type inverter (3LT2I) topology has numerous advantageous compared to three-level neutral-point-clamped (NPC) inverter. The main benefits of 3LT2I inverter are the efficiency, inverter cost, switching losses, and the quality of output voltage waveforms. In this paper, a photovoltaic distributed generation system based on dual-stage topology of DC-DC boost converter and 3LT2I is introduced. To that end, a decoupling control strategy of 3LT2I is proposed to control the current injected into the grid, reactive power compensation, and DC-link voltage. The resulting system is able to extract the maximum power from photovoltaic generator, to achieve sinusoidal grid currents, and to ensure reactive power compensation. The voltage-balancing control of two split DC capacitors of the 3LT2I is achieved using three-level space vector modulation with balancing strategy based on the effective use of the redundant switching states of the inverter voltage vectors. The proposed system performance is investigated at different operating conditions.
Directory of Open Access Journals (Sweden)
A. Abbas Elserougi
2013-09-01
Full Text Available Voltage boosting is very essential issue in renewable-energy fed applications. The classical two-stage power conversion process is typically used to interface the renewable energy sources to the grid. For better efficiency, single-stage inverters are recommended. In this paper, the performance of single-stage three-phase grid-connected boost inverter is investigated when its gain is extended by employing over-modulation technique. Using of over-modulation is compared with the employment of third order harmonic injection. The latter method can increase the inverter gain by 15% without distorting the inverter output voltage. The performance of extended gain grid-connected boost inverter is also tested during normal operation as well as in the presence of grid side disturbances. Simulation and experimental results are satisfactory.
Low-voltage grid-connection of photovoltaic power systems
Energy Technology Data Exchange (ETDEWEB)
Collinson, A.; Thornycroft, J.
1999-07-01
This report summarises the results of a project aimed at developing technical guidelines concerning grid connected photovoltaic (PV) inverter generators which are to be published in draft form as the {sup U}K Technical Guidelines for Inverter Connected Single Phase Photovoltaic (PV) Generators up to 5kVA{sup .} The background to the use of PV in the UK is traced, and the technical criteria for electrical integration of PV systems, and UK guidelines for grid connected PV systems are examined. The findings of the working group of the International Energy Agency (IEA) Implementing Agreement on Photovoltaic Power Systems are also presented in this report. Appendices discuss the UK technical guidelines, the IEA Task V activities,, utility aspects of grid-connected PV systems, and demonstration tests on grid-connected PV systems, and lists Task V reports.
Low Voltage Ride-Through of Single-Phase Transformerless Photovoltaic Inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede; Wang, Huai
2014-01-01
Transformerless photovoltaic (PV) inverters are going to be more widely adopted in order to achieve high efficiency, as the penetration level of PV systems is continuously booming. However, problems may arise in highly PV-integrated distribution systems. For example, a sudden stoppage of all PV...... are also discussed. The selected inverters are the full-bridge inverter with bipolar modulation, full-bridge inverter with DC bypass and the Highly Efficient and Reliable Inverter Concept (HERIC). A 1 kW singlephase grid-connected PV system is analyzed to verify the discussions. The tests confirmed that...
Grid-connected Photovoltaic Micro-inverter with New Hybrid Control LLC Resonant Converter
DEFF Research Database (Denmark)
Xingkui, Mao; Qisheng, Huang; Qingbo, Ke
2016-01-01
A high-efficiency photovoltaic (PV) micro-inverter consisting of two power stages i.e. a LLC resonant converter with a new hybrid control scheme and a dc-ac inverter is proposed, studied and designed in this paper. In the first power stage, the new hybrid control combining pulse-frequency modulat......A high-efficiency photovoltaic (PV) micro-inverter consisting of two power stages i.e. a LLC resonant converter with a new hybrid control scheme and a dc-ac inverter is proposed, studied and designed in this paper. In the first power stage, the new hybrid control combining pulse......-frequency modulation (PFM) and phase-shift pulse-width modulation (PS-PWM) is employed on a full-bridge LLC dc-dc converter, in order to achieve high efficiency when PV output voltage varies in a wide range. Moreover, a maximum power point tracking (MPPT) method based on power perturbation is implemented in the dc...
Impact of grid impedance variations on harmonic emission of grid-connected inverters
DEFF Research Database (Denmark)
Hoseinzadeh, Bakhtyar; Bak, Claus Leth; Blaabjerg, Frede
2017-01-01
This paper addresses harmonic magnification due to resonance circuits resulting from interaction between uncertain grid impedance and converter. The source of harmonic may be either the grid or inverter. It is demonstrated that unknown and unpredictable grid impedance may result in variable...
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Zhang, Xue; Wang, Baocheng
2014-01-01
This letter presents a new control strategy of threephase grid-connected inverter for the positive sequence voltage recovery and negative sequence voltage reduction under asymmetrical grid faults. Unlike the conventional control strategy based on an assumption that the network impedance is mainly...... of the proposed solution for the flexible voltage support in a low-voltage grid, where thenetwork impedance is mainly resistive.......This letter presents a new control strategy of threephase grid-connected inverter for the positive sequence voltage recovery and negative sequence voltage reduction under asymmetrical grid faults. Unlike the conventional control strategy based on an assumption that the network impedance is mainly...... inductive, the proposed control strategy is more flexible and effective by considering the network impedance impact, which is of great importance for the high penetration of grid-connected renewable energy systems into low-voltage grids. The experimental tests are carried out to validate the effectiveness...
Application of interleaved flyback micro inverter in a grid connected system
Brindha, R.; Ananthichristy, A.; Poornima, P. U.; Madhana, M.; Ashok Rathish, S.; Ragavi, Selvam
2018-04-01
The two control strategies CCM and DCM have various effects on the loss distribution and efficiency and thus were studied for the interleaved flyback micro inverter concentrating on the loss analysis under different load conditions. The dominant losses with heavy load include the conduction loss and the transformer loss in case of the interleaved flyback micro inverter; whereas driving of gate loss, the turn-off loss in the transformer core loss and in the powermosfets are included in the dominant losses with light load. A new hybrid control strategy which has the one-phase DCM and two-phase DCM control reduces the dominant losses in order to improving the efficiency based on the load in wide load range is proposed here.
DEFF Research Database (Denmark)
Chen, Zhiyong; Chen, Yandong; Guerrero, Josep M.
2016-01-01
This paper firstly presents an equivalent coupling circuit modeling of multi-parallel inverters in microgrid operating in grid-connected mode. By using the model, the coupling resonance phenomena are explicitly investigated through the mathematical approach, and the intrinsic and extrinsic...
Directory of Open Access Journals (Sweden)
Yanxue Yu
2017-01-01
Full Text Available As a basic building block in power systems, the three-phase voltage-source inverter (VSI connects the distributed energy to the grid. For the inductor-capacitor-inductor (LCL-filter three-phase VSI, according to different current sampling position and different reference frame, there mainly exist four control schemes. Different control schemes present different impedance characteristics in their corresponding determined frequency range. To analyze the existing resonance phenomena due to the variation of grid impedances, the sequence impedance models of LCL-type grid-connected three-phase inverters under different control schemes are presented using the harmonic linearization method. The impedance-based stability analysis approach is then applied to compare the relative stability issues due to the impedance differences at some frequencies and to choose the best control scheme and the better controller parameters regulating method for the LCL-type three-phase VSI. The simulation and experiments both validate the resonance analysis results.
The PWM strategies of grid-connected distributed generation active NPC inverters
DEFF Research Database (Denmark)
Ma, Lin; Xinmin, Jin; Kerekes, Tamas
2009-01-01
The Neutral Point Clamped topology due to high efficiency, low leakage current and EMI, its integration is widely used in the distributed generation (DG) systems. However the main disadvantage of the NPC inverter is given by an unequal distribution of the losses in the semiconductor devices, which...... leads to an unequal distribution of temperature. By using the Active NPC topology, the power losses distribution problem is alleviated. The modulation strategy is a key issue for losses distribution in this topology. In this paper two known strategies are discussed and a new proposed PWM strategy......, namely the Adjustable Losses Distribution (ALD) PWM strategy is proposed for better losses distribution in the Active NPC (ANPC) topology. Simulations using Simulink and the PLECS toolbox have been done for evaluating efficiency of different NPC topologies and some experimental results are presented...
Stability of Grid-Connected PV Inverters with Large Grid Impedance Variation
DEFF Research Database (Denmark)
Liserre, Marco; Teodorescu, Remus; Blaabjerg, Frede
2004-01-01
Photovoltaic (PV) inverters used in dispersed power generation of houses in the range of 1-5 kW are currently available from several manufactures. However, large grid impedance variation is challenging the control and the grid filter design in terms of stability. In fact the PV systems are well...... suited for loads connected in a great distance to the transformer (long wires) and the situation becomes even more difficult in low-developed remote areas characterized by low power transformers and long distribution wires with high grid impedance. Hence a theoretical analysis is needed because the grid...... impedance variation leads to dynamic and stability problems both in the low frequency range (around the current controller bandwidth frequency) as well as in the high frequency range (around the LCL-filter resonance frequency). In the low frequency range the possible variation of the impedance challenges...
Stability analysis and active damping for LLCL-filter based grid-connected inverters
DEFF Research Database (Denmark)
Huang, Min; Blaabjerg, Frede; Loh, Poh Chiang
2014-01-01
A higher order passive power filter (LLCL-filter) for the grid-tied inverter is becoming attractive for the industrial applications due to the possibility to reduce the cost of the copper and the magnetic material. To avoid the well-known stability problems of the LLCL-filter it is requested to use...... either passive or active damping methods. This paper analyzes the stability when damping is required and when damping is not necessary considering sampling and transport delay. Basic LLCL resonance damping properties of different feedback states are also studied. Then an active damping method which...... is using the capacitor current feedback for LLCL-filter is introduced. Based on this method, a design procedure for the control method is given. Last, both simulation and experimental results are provided to validate the theoretical analysis of this paper....
Directory of Open Access Journals (Sweden)
Meenakshi Jayaraman
2017-11-01
Full Text Available Recently, multilevel inverters are more researched due to the advantages they offer over conventional voltage source inverters in grid connected applications. Passive filters are connected at the output of these inverters to produce sinusoidal waveforms with reduced harmonics and to satisfy grid interconnection standard requirements. This work proposes a new passive filter topology for a pulse width modulated five-level cascaded inverter interfaced grid connected system. The proposed passive filter inserts an additional resistance-capacitance branch in parallel to the filter capacitor of the traditional inductive–capacitive–inductive filter in addition to a resistance in series with it to reduce damping power loss. It can attenuate the switching frequency harmonic current components much better than the traditional filter while maintaining the same overall inductance, reduced capacitance and resistance values. The basic parameter design procedure and an approach to discover the parameters of the proposed filter is introduced. Further, a novel methodology using Particle Swarm Optimization (PSO is recommended to guarantee minimum damping loss while ensuring reduced peak during resonance. In addition, PSO algorithm is newly employed in this work to maximize harmonic attenuation in and around the switching frequency on the premise of allowable values of filter inductance and capacitance. A comparative discussion considering traditional passive filters and the proposed filter is presented and evaluated through experiments conducted on a 110 V, 1 kW five-level grid connected inverter. The modulation algorithm for the multilevel inverter is implemented using a SPARTAN 6-XC6SLX25 Field Programmable Gate Array (FPGA processor. The analysis shows that the proposed filter not only provides decreased damping power loss but also is capable of providing considerable harmonic ripple reduction in the high frequency band, improved output waveforms and lesser
Directory of Open Access Journals (Sweden)
Seung-Jin Yoon
2018-02-01
Full Text Available Inductive-capacitive-inductive (LCL-type filters are currently preferred as a replacement for L-type filters in distributed generation (DG power systems, due to their superior harmonic attenuation capability. However, the third-order dynamics introduced by LCL filters pose a challenge to design a satisfactory controller for such a system. Conventionally, an LCL-filtered grid-connected inverter can be effectively controlled by using a full-state feedback control. However, this control approach requires the measurement of all system state variables, which brings about more complexity for the inverter system. To address this issue, this paper presents a systematic procedure to design an observer-based integral state feedback control for a LCL-filtered grid-connected inverter in the discrete-time domain. The proposed control scheme consists of an integral state feedback controller and a full-state observer which uses the control input, grid-side currents, and grid voltages to predict all the system state variables. Therefore, only the grid-side current sensors and grid voltage sensors are required to implement the proposed control scheme. Due to the discrete-time integrator incorporated in the state feedback controller, the proposed control scheme ensures both the reference tracking and disturbance rejection performance of the inverter system in a practical and simple way. As a result, superior control performance can be achieved by using the reduced number of sensors, which significantly reduces the cost and complexity of the LCL-filtered grid-connected inverter system in DG applications. To verify the practical usefulness of the proposed control scheme, a 2 kW three-phase prototype grid-connected inverter has been constructed, and the proposed control system has been implemented based on 32-bit floating-point digital signal processor (DSP TMS320F28335. The effectiveness of the proposed scheme is demonstrated through the comprehensive simulation
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Jia, X.; Lu, Z.
2016-01-01
Leakage current reduction is one of the important issues for the transformelress PV systems. In this paper, the transformerless single-phase cascaded H-bridge PV inverter is investigated. The common mode model for the cascaded H4 inverter is analyzed. And the reason why the conventional cascade H4...... inverter fails to reduce the leakage current is clarified. In order to solve the problem, a new cascaded H5 inverter is proposed to solve the leakage current issue. Finally, the experimental results are presented to verify the effectiveness of the proposed topology with the leakage current reduction...... for the single-phase transformerless PV systems....
DEFF Research Database (Denmark)
Guo, Xiaoqiang; Guerrero, Josep M.
2016-01-01
Current quality is one of the most important issues for operating three-phase grid-connected inverter in distributed generation systems. In practice, the grid current quality is degraded in case of non-ideal utility voltage. A new control strategy is proposed for the three-phase gridconnected...... inverter. Different from the traditional method, our proposal utilizes the unique abc-frame complex-coefficient filter and controller to achieve the balanced, sinusoidal grid current. The main feature of the proposed method is simple and easy to implement without any frame transformation. The theoretical...
Single Phase Transformer-less Buck-Boost Inverter with Zero Leakage Current for PV Systems
DEFF Research Database (Denmark)
Mostaan, Ali; Abdelhakim, Ahmed; N. Soltani, Mohsen
2017-01-01
In this paper, a novel single-stage single-phase transformer-less buck-boost inverter is proposed, in which a reduced number of passive components is used. The proposed inverter combines the conventional buck, boost, and buck-boost converters in one converter in order to obtain a sinusoidal output...
Single phase inverter for a three phase power generation and distribution system
Lindena, S. J.
1976-01-01
A breadboard design of a single-phase inverter with sinusoidal output voltage for a three-phase power generation and distribution system was developed. The three-phase system consists of three single-phase inverters, whose output voltages are connected in a delta configuration. Upon failure of one inverter the two remaining inverters will continue to deliver three-phase power. Parallel redundancy as offered by two three-phase inverters is substituted by one three-phase inverter assembly with high savings in volume, weight, components count and complexity, and a considerable increase in reliability. The following requirements must be met: (1) Each single-phase, current-fed inverter must be capable of being synchronized to a three-phase reference system such that its output voltage remains phaselocked to its respective reference voltage. (2) Each single-phase, current-fed inverter must be capable of accepting leading and lagging power factors over a range from -0.7 through 1 to +0.7.
Pati, Akshaya K; Sahoo, N C
2017-07-01
This paper presents an adaptive super-twisting sliding mode control (STC) along with double-loop control for voltage tracking performance of three-phase differential boost inverter and DC-link capacitor voltage regulation in grid-connected PV system. The effectiveness of the proposed control strategies are demonstrated under realistic scenarios such as variations in solar insolation, load power demand, grid voltage, and transition from grid-connected to standalone mode etc. Additional supplementary power quality control functions such as harmonic compensation, and reactive power management are also investigated with the proposed control strategy. The results are compared with conventional proportional-integral controller, and PWM sliding mode controller. The system performance is evaluated in simulation and in real-time. Copyright © 2017 ISA. Published by Elsevier Ltd. All rights reserved.
DEFF Research Database (Denmark)
Tang, Yi; Yao, Wenli; Loh, Poh Chiang
2015-01-01
, and this observation is so far not discussed in the literature. In this case, very cost-effective LCL-filter design can be achieved for grid-connected converters whose dominant switching harmonics may appear at double of the switching frequency, e.g. in unipolar modulated three-level full bridge converters and 12...
Microcontroller Based SPWM Single-Phase Inverter For Wind Power Application
Directory of Open Access Journals (Sweden)
Khin Ohmar Lin
2017-04-01
Full Text Available In this paper microcontroller based sinusoidal pulse width modulation SPWM single-phase inverter is emphasized to constant frequency conversion scheme for wind power application. The wind-power generator output voltage and frequency are fluctuated due to the variation of wind velocity. Therefore the AC output voltage of wind-generator is converted into DC voltage by using rectifier circuit and this DC voltage is converted back to AC voltage by using inverter circuit. SPWM technique is used in inverter to get nearly sine wave and reduce harmonic content. The rating of inverter is 500W single-phase 220V 50 Hz. The required SPWM timing pulses for the inverter are generated from the PIC16F877A microcontroller. Circuit simulation was done by using Proteus 7 Professional and MATLABR 2008 software. The software for microcontroller is implemented by using MPASM assembler.
Directory of Open Access Journals (Sweden)
Iman Lorzadeh
2016-08-01
Full Text Available Inductive-capacitive-inductive (LCL-type line filters are widely used in grid-connected voltage source inverters (VSIs, since they can provide substantially improved attenuation of switching harmonics in currents injected into the grid with lower cost, weight and power losses than their L-type counterparts. However, the inclusion of third order LCL network complicates the current control design regarding the system stability issues because of an inherent resonance peak which appears in the open-loop transfer function of the inverter control system near the control stability boundary. To avoid passive (resistive resonance damping solutions, due to their additional power losses, active damping (AD techniques are often applied with proper control algorithms in order to damp the LCL filter resonance and stabilize the system. Among these techniques, the capacitor current feedback (CCF AD has attracted considerable attention due to its effective damping performance and simple implementation. This paper thus presents a state-of-the-art review of resonance and stability characteristics of CCF-based AD approaches for a digitally-controlled LCL filter-based grid-connected inverter taking into account the effect of computation and pulse width modulation (PWM delays along with a detailed analysis on proper design and implementation.
Li, Shuhui; Fairbank, Michael; Johnson, Cameron; Wunsch, Donald C; Alonso, Eduardo; Proaño, Julio L
2014-04-01
Three-phase grid-connected converters are widely used in renewable and electric power system applications. Traditionally, grid-connected converters are controlled with standard decoupled d-q vector control mechanisms. However, recent studies indicate that such mechanisms show limitations in their applicability to dynamic systems. This paper investigates how to mitigate such restrictions using a neural network to control a grid-connected rectifier/inverter. The neural network implements a dynamic programming algorithm and is trained by using back-propagation through time. To enhance performance and stability under disturbance, additional strategies are adopted, including the use of integrals of error signals to the network inputs and the introduction of grid disturbance voltage to the outputs of a well-trained network. The performance of the neural-network controller is studied under typical vector control conditions and compared against conventional vector control methods, which demonstrates that the neural vector control strategy proposed in this paper is effective. Even in dynamic and power converter switching environments, the neural vector controller shows strong ability to trace rapidly changing reference commands, tolerate system disturbances, and satisfy control requirements for a faulted power system.
DEFF Research Database (Denmark)
Han, Yang; Shen, Pan; Guerrero, Josep M.
2016-01-01
Grid-connected inverters (GCIs) with LCL output filter have the ability of attenuating high-frequency (HF) switching ripples. However, by using only grid-current control, the system is prone to resonances if it is not properly damped, and the current distortion would be amplified significantly...... method is adopted. Furthermore, the grid voltage feed-forward and multiple PR controllers are integrated in the current loop to mitigate the current distortion introduced by the grid background distortion. Besides, the parameters design guidelines are presented to show the feasibility and effectiveness...
Directory of Open Access Journals (Sweden)
Mechouma Rabiaa
2014-01-01
Full Text Available In recent years, power demand of industrial applications has increased significantly reaching some megawatts. The use of multilevel converters for applications of medium and high powers is proposed as a solution to drawback semiconductor technology. A multilevel converter not only achieves high power ratings, but also enables the use of renewable energy sources. Renewable energy sources such as photovoltaic can be easily interfaced to a multilevel converter system for a high power application. This paper presents the simulation study in Matlab/Simulink of a grid connected photovoltaic three phase Neutral Point Clamped (NPC inverter with DC/DC boost converter for constant and variable solar radiation.
Modelling of the modified-LLCL-filter-based single-phase grid-tied Aalborg inverter
DEFF Research Database (Denmark)
Liu, Zifa; Wu, Huiyun; Liu, Yuan
2017-01-01
Owing to less conduction and switching power losses, the recently proposed Aalborg inverter has high efficiency within a wide range of input DC voltage for single-phase DC/AC power conversion. In theory, the conduction power losses can be further decreased, if an LLCL-filter is adopted instead...... of an LCL-filter for a voltage source inverter, mainly due to the reduced inductance. The Aalborg inverter shows the characteristic of a current source inverter, when working in the `boost' state. Whether the LLCL-filter can meet the control requirement of this type inverter needs to be further explored....... In this study, the small signal analysis for the modified-LLCL-filter-based Aalborg inverter is addressed. Through the modelling, it can be proven that compared with the LCL-filter, the modified-LLCL-filter causes no extra control challenge for the Aalborg inverter, and therefore more inductance in the power...
Reducing Electromagnetic Interference in a Grid Tied Single Phase Power Inverter
2016-09-01
With the growing demand for a reliable electrical grid, backup power supplies and energy management systems are a necessity. Systems such as server...ELECTROMAGNETIC INTERFERENCE IN A GRID TIED SINGLE PHASE POWER INVERTER by Jason Hassan Valiani September 2016 Thesis Advisor: Giovanna Oriti...3. REPORT TYPE AND DATES COVERED Master’s thesis 4. TITLE AND SUBTITLE REDUCING ELECTROMAGNETIC INTERFERENCE IN A GRID TIED SINGLE PHASE POWER
Challenges in thermal design of industrial single-phase power inverter
Directory of Open Access Journals (Sweden)
Ninković Predrag
2016-01-01
Full Text Available This paper presents the influence of thermal aspects in design process of an industrial single-phase inverter, choice of its topology and components. Stringent design inputs like very high overload level, demand for natural cooling and very wide input voltage range have made conventional circuit topology inappropriate therefore asking for alternative solution. Different power losses calculations in semiconductors are performed and compared, outlining the guidelines how to choose the final topology. Some recommendations in power magnetic components design are given. Based on the final project, a 20kVA single-phase inverter for thermal power plant supervisory and control system is designed and commissioned.
DEFF Research Database (Denmark)
Lorzadeh, Iman; Askarian Abyaneh, Hossein; Savaghebi, Mehdi
2016-01-01
Inductive-capacitive-inductive (LCL)-type line filters are widely used in grid-connected voltage source inverters (VSIs), since they can provide substantially improved attenuation of switching harmonics in currents injected into the grid with lower cost, weight and power losses than their L......-type counterparts. However, the inclusion of third order LCL network complicates the current control design regarding the system stability issues because of an inherent resonance peak which appears in the open-loop transfer function of the inverter control system near the control stability boundary. To avoid...... passive (resistive) resonance damping solutions, due to their additional power losses, active damping (AD) techniques are often applied with proper control algorithms in order to damp the LCL filter resonance and stabilize the system. Among these techniques, the capacitor current feedback (CCF) AD has...
Single-Phase 3L PR Controlled qZS Inverter Connected to the Distorted Grid
DEFF Research Database (Denmark)
Makovenko, Elena; Husev, Oleksandr; Roncero-Clemente, Carlos
2016-01-01
This paper presents a single-phase three-level NPC qZS inverter connected to a distorted grid using PID and PR regulators. A case study system along with the control strategy are described. Tuning approaches for PID and PR regulators are addressed and validated by means of simulation results...
PI and repetitive control for single phase inverter based on virtual rotating coordinate system
Li, Mengqi; Tong, Yibin; Jiang, Jiuchun; Liang, Jiangang
2018-03-01
Microgrid technology developed rapidly and nonlinear loads were connected increasingly. A new control strategy was proposed for single phase inverter when connected nonlinear loads under island condition. PI and repetitive compound controller was realized under synchronous rotating coordinate system and acquired high quality sinusoidal voltage output without voltage spike when loads step changed. Validity and correctness were verified by simulation using MATLAB/Simulink.
Reliability Evaluation of a Single-phase H-bridge Inverter with Integrated Active Power Decoupling
DEFF Research Database (Denmark)
Tang, Junchaojie; Wang, Haoran; Ma, Siyuan
2016-01-01
it with the traditional passive DC-link solution. The converter level reliability is obtained by component level electro-thermal stress modeling, lifetime model, Weibull distribution, and Reliability Block Diagram (RBD) method. The results are demonstrated by a 2 kW single-phase inverter application.......Various power decoupling methods have been proposed recently to replace the DC-link Electrolytic Capacitors (E-caps) in single-phase conversion system, in order to extend the lifetime and improve the reliability of the DC-link. However, it is still an open question whether the converter level...... reliability becomes better or not, since additional components are introduced and the loading of the existing components may be changed. This paper aims to study the converter level reliability of a single-phase full-bridge inverter with two kinds of active power decoupling module and to compare...
DEFF Research Database (Denmark)
Wang, Huai; Yang, Yongheng; Blaabjerg, Frede
2013-01-01
The efficiency of 98% has been reported on transformer-less photovoltaic (PV) inverters and the penetration of grid-connected PV systems is booming as well. In the future, the PV systems are expected to contribute to the grid stability by means of low voltage ride-through operation and grid suppo...
A Synchronization Method for Single-Phase Grid-Tied Inverters
DEFF Research Database (Denmark)
Hadjidemetriou, Lenos; Kyriakides, Elias; Yang, Yongheng
2016-01-01
The controllers of single-phase grid-tied inverters require improvements to enable distribution generation systems to meet the grid codes/standards with respect to power quality and the fault ride through capability. In that case, the response of the selected synchronization technique is crucial...... for the performance of the entire grid-tied inverter. In this paper, a new synchronization method with good dynamics and high accuracy under a highly distorted voltage is proposed. This method uses a Multi-Harmonic Decoupling Cell (MHDC), which thus can cancel out the oscillations on the synchronization signals due...... to the harmonic voltage distortion while maintaining the dynamic response of the synchronization. Therefore, the accurate and dynamic response of the proposed MHDC-PLL can be beneficial for the performance of the whole single-phase grid-tied inverter....
DEFF Research Database (Denmark)
Li, Zipeng; Jiang, Aiting; Shen, Pan
2016-01-01
, this paper presents a systematic design method for the LCL-LC filtered grid-connected photovoltaic (PV) system. With this method, controller parameters and the active damping feedback coefficient are easily obtained by specifying the system stability and dynamic performance indices, and it is more convenient......-frequency harmonics attenuation ability, but the resonant problem affects the system stability remarkably. In this paper, active damping based on the capacitor voltage feedback is proposed using the concept of the equivalent virtual impedance in parallel with the capacitor. With the consideration of system delay...... to optimize the system performance according to the predefined satisfactory region. Finally, the simulation results are presented to validate the proposed design method and control scheme....
DEFF Research Database (Denmark)
Naderipour, Amirreza; Asuhaimi Mohd Zin, Abdullah; Bin Habibuddin, Mohd Hafiz
2017-01-01
In recent years, renewable energy sources have been considered the most encouraging resources for grid and off-grid power generation. This paper presents an improved current control strategy for a three-phase photovoltaic grid-connected inverter (GCI) under unbalanced and nonlinear load conditions....... It is challenging to suppress the harmonic content in the output current below a pre-set value in the GCI. It is also difficult to compensate for unbalanced loads even when the grid is under disruption due to total harmonic distortion (THD) and unbalanced loads. The primary advantage and objective of this method...... is to effectively compensate for the harmonic current content of the grid current and microgrid without the use of any compensation devices, such as active and passive filters. This method leads to a very low THD in both the GCI currents and the current exchanged with the grid. The control approach is designed...
DEFF Research Database (Denmark)
Al-Shetwi, Ali Q.; Sujod, Muhamad Zahim; Blaabjerg, Frede
2018-01-01
to enhance the LVRT capability based on the Malaysian standards and modern grid codes connection requirements. The proposed control overcomes the problems of dc-link over-voltage and ac over-current that may cause disconnection or damage to the inverter. For this purpose, dc-chopper brake controller...... to improve the capability of ride-through fault safely and keep the inverter connected, but also to provide grid support through active and reactive power control at different type of faults....
A single-phase embedded Z-source DC-AC inverter.
Kim, Se-Jin; Lim, Young-Cheol
2014-01-01
In the conventional DC-AC inverter consisting of two DC-DC converters with unipolar output capacitors, the output capacitor voltages of the DC-DC converters must be higher than the DC input voltage. To overcome this weakness, this paper proposes a single-phase DC-AC inverter consisting of two embedded Z-source converters with bipolar output capacitors. The proposed inverter is composed of two embedded Z-source converters with a common DC source and output AC load. Though the output capacitor voltages of the converters are relatively low compared to those of a conventional inverter, an equivalent level of AC output voltages can be obtained. Moreover, by controlling the output capacitor voltages asymmetrically, the AC output voltage of the proposed inverter can be higher than the DC input voltage. To verify the validity of the proposed inverter, experiments were performed with a DC source voltage of 38 V. By controlling the output capacitor voltages of the converters symmetrically or asymmetrically, the proposed inverter can produce sinusoidal AC output voltages. The experiments show that efficiencies of up to 95% and 97% can be achieved with the proposed inverter using symmetric and asymmetric control, respectively.
An LLCL Power Filter for Single-Phase Grid-Tied Inverter
DEFF Research Database (Denmark)
Wu, Weimin; He, Yuanbin; Blaabjerg, Frede
2012-01-01
This paper presents a new topology of higher order power filter for grid-tied voltage-source inverters, named the LLCL filter, which inserts a small inductor in the branch loop of the capacitor in the traditional LCL filter to compose a series resonant circuit at the switching frequency. Particul......This paper presents a new topology of higher order power filter for grid-tied voltage-source inverters, named the LLCL filter, which inserts a small inductor in the branch loop of the capacitor in the traditional LCL filter to compose a series resonant circuit at the switching frequency...... to the inverter system control. The parameter design criteria of the proposed LLCL filter is also introduced. The comparative analysis and discussions regarding the traditional LCL filter and the proposed LLCL filter have been presented and evaluated through experiment on a 1.8-kW-single-phase grid-tied inverter...
2016-09-01
Khaligh, “Optimization of sizing and battery cycle life in battery/ultracapacitor hybrid energy storage systems for electric vehicle applications...depth cycling operation in photovoltaic system ,” in 22nd International Conference “Mixed Design of Integrated Circuits and Systems ,” Toruń, Poland...CURRENT LINK HARMONIC RIPPLE IN SINGLE-PHASE VOLTAGE SOURCE INVERTER SYSTEMS USING SUPERCAPACITORS by Gabriel D. Hernandez September 2016
Implementation of grid-connected to/from off-grid transference for micro-grid inverters
Heredero Peris, Daniel; Chillón Antón, Cristian; Pages Gimenez, Marc; Gross, Gabriel Igor; Montesinos Miracle, Daniel
2013-01-01
This paper presents the transfer of a microgrid converter from/to on-grid to/from off-grid when the converter is working in two different modes. In the first transfer presented method, the converter operates as a Current Source Inverter (CSI) when on-grid and as a Voltage Source Inverter (VSI) when off-grid. In the second transfer method, the converter is operated as a VSI both, when operated on-grid and off-grid. The two methods are implemented successfully in a real pla...
DEFF Research Database (Denmark)
Vasquez, J. C.; Guerrero, J. M.; Luna, A.
2009-01-01
This paper proposes a novel control for voltagesource inverters with the capability to flexibly operate in gridconnected and islanded modes. The control scheme is based on the droop method, which uses some estimated grid parameters such as the voltage and frequency and the magnitude and angle of ...
Common-Ground-Type Transformerless Inverters for Single-Phase Solar Photovoltaic Systems
DEFF Research Database (Denmark)
Siwakoti, Yam Prasad; Blaabjerg, Frede
2018-01-01
This paper proposes a family of novel flying capacitor transformerless inverters for single-phase photovoltaic (PV) systems. Each of the new topologies proposed is based on a flying capacitor principle and requires only four power switches and/or diodes, one capacitor, and a small filter at the o......This paper proposes a family of novel flying capacitor transformerless inverters for single-phase photovoltaic (PV) systems. Each of the new topologies proposed is based on a flying capacitor principle and requires only four power switches and/or diodes, one capacitor, and a small filter...... at the output stage. A simple unipolar sinusoidal pulse width modulation technique is used to modulate the inverter to minimize the switching loss, output current ripple, and the filter requirements. In general, the main advantages of the new inverter topologies are: 1) the negative polarity of the PV...... description of the operating principle with modulation techniques, design guidelines, and comprehensive comparisons is presented to reveal the properties and limitations of each topology in detail. Finally, experimental results of 1-kVA prototypes are presented to prove the concept and theoretical analysis...
DEFF Research Database (Denmark)
Al-Shetwi, Ali Q.; Sujod, Muhamad Zahim; Blaabjerg, Frede
2018-01-01
and current limiter are used to absorb the excessive dc-voltage and limits excessive ac current, respectively. This control strategy can also ensure the reactive power support through the injection of reactive current according to the standard requirements as soon as the voltage sag is detected. Furthermore...... to improve the capability of ride-through fault safely and keep the inverter connected, but also to provide grid support through active and reactive power control at different type of faults....
Improved Reliability of Single-Phase PV Inverters by Limiting the Maximum Feed-in Power
DEFF Research Database (Denmark)
Yang, Yongheng; Wang, Huai; Blaabjerg, Frede
2014-01-01
Grid operation experiences have revealed the necessity to limit the maximum feed-in power from PV inverter systems under a high penetration scenario in order to avoid voltage and frequency instability issues. A Constant Power Generation (CPG) control method has been proposed at the inverter level...... devices, allowing a quantitative prediction of the power device lifetime. A study case on a 3 kW single-phase PV inverter has demonstrated the advantages of the CPG control in terms of improved reliability.......Grid operation experiences have revealed the necessity to limit the maximum feed-in power from PV inverter systems under a high penetration scenario in order to avoid voltage and frequency instability issues. A Constant Power Generation (CPG) control method has been proposed at the inverter level....... The CPG control strategy is activated only when the DC input power from PV panels exceeds a specific power limit. It enables to limit the maximum feed-in power to the electric grids and also to improve the utilization of PV inverters. As a further study, this paper investigates the reliability performance...
DEFF Research Database (Denmark)
Lu, Minghui; Xin, Zhen; Wang, Xiongfei
2016-01-01
should be designed under one-sixth of sampling frequency. However, the low resonance frequency leads to a comparatively large filter inductance or/and capacitance. To extend the stable boundary to the region above fs/6, this paper proposes a novel voltage feedforward scheme for the LCL-filtered inverter....... Theoretical analysis is then provided to validate its feasibility and stability. Compared to other widely used active damping strategies, no extra sensors are needed because the filter capacitor voltage, which is used for voltage feedforward control, is also sampled for phase-locked loop in this paper...
DEFF Research Database (Denmark)
Ciobotaru, Mihai; Agelidis, Vassilios; Teodorescu, Remus
2008-01-01
Islanding prediction is a necessary feature of inverter-based photovoltaic (PV) system in order to meet stringent standard requirements for interconnection with the electrical grid. Both passive and active anti-islanding methods exist. Typically, active methods modify a given parameter, which also...... extracted from the voltage at PCC moves outside of a preset threshold value. This new active anti-islanding method meets both standard requirements IEEE 929-2000, IEEE 1547.1 and VDE 0126.1.1. The disturbance used by this method is small compared to other active anti-islanding methods, such as active...
DEFF Research Database (Denmark)
Liu, Wenzhao; Guo, Xiaoqiang; Savaghebi, Mehdi
2016-01-01
The photovoltaic (PV) inverter installed on board experiences the excessive current stress in case of the offshore unbalanced voltage fault ride through (FRT), which significantly affects the operation reliability of the power supply system. In order to solve the problem, the inherent mechanism...... of the excessive current phenomenon with the conventional fault ride through control is discussed. The quantitative analysis of the current peak value is conducted and a new current-limiting control strategy is proposed to achieve the flexible power control and successful fault ride through in a safe current...
Grid-Connection Half-Bridge PV Inverter System for Power Flow Controlling and Active Power Filtering
Directory of Open Access Journals (Sweden)
Chih-Lung Shen
2012-01-01
Full Text Available A half-bridge photovoltaic (PV system is proposed, which can not only deal with bidirectional power flowing but also improve power quality. According to varying insolation, the system conditions real power for dc and ac loads to accommodate different amounts of PV power. Furthermore, the system eliminates current harmonics and improves power factor simultaneously. As compared with conventional PV inverter, the total number of active switches and current sensors can be reduced so that its cost is lower significantly. For current command determination, a linear-approximation method (LAM is applied to avoid the complicated calculation and achieve the maximum power point tracking (MPPT feature. For current controlling, a direct-source-current-shaping (DSCS algorithm is presented to shape the waveform of line current. Simulation results and practical measurements also demonstrate the feasibility of the proposed half-bridge PV system.
Control of Grid Connected Photovoltaic Systems with Microinverters
DEFF Research Database (Denmark)
Yahya, Abdelhafid; El Fadil, Hassan; Oulcaid, Mustapha
2018-01-01
This paper addresses the problem of controlling grid connected photovoltaic (PV) systems that are driven with microinverters. The systems to be controlled consist of a solar panel, a boost dc–dc converter, a DC link capacitor, a single-phase full-bridge inverter, a filter inductor, and an isolation...... transformer. We seek controllers that are able to simultaneously achieve four control objectives, namely: (i) asymptotic stability of the closed loop control system; (ii) maximum power point tracking (MPPT) of the PV module; (iii) tight regulation of the DC bus voltage; and (iv) unity power factor (PF...
Control Method of Single-phase Inverter Based Grounding System in Distribution Networks
DEFF Research Database (Denmark)
Wang, Wen; Yan, L.; Zeng, X.
2016-01-01
of neutral-to-ground voltage is critical for the safety of distribution networks. An active grounding system based on single-phase inverter is proposed to achieve this objective. Relationship between output current of the system and neutral-to-ground voltage is derived to explain the principle of neutral......The asymmetry of the inherent distributed capacitances causes the rise of neutral-to-ground voltage in ungrounded system or high resistance grounded system. Overvoltage may occur in resonant grounded system if Petersen coil is resonant with the distributed capacitances. Thus, the restraint...
DEFF Research Database (Denmark)
Teodorescu, Remus; Blaabjerg, Frede; Borup, Uffe
2004-01-01
disturbance rejection capability leads to the need of grid feed-forward compensation. However the imperfect compensation action of the feed-forward control results in high harmonic distortion of the current and consequently non-compliance with international standards. In this paper a new control strategy...... aimed to mitigate these problems is proposed. Stationary-frame generalized integrators are used to control the fundamental current and to compensate the grid harmonics providing disturbance rejection capability without the need of feed-forward grid compensation. Moreover the use of a grid LCL......The PI current control of a single-phase inverter has well known drawbacks: steady-state magnitude and phase-error and limited disturbance rejection capability. When the current controlled inverter is connected to the grid, the phase error results in a power factor decrement and the limited...
Naderipour, Amirreza; Asuhaimi Mohd Zin, Abdullah; Bin Habibuddin, Mohd Hafiz; Miveh, Mohammad Reza; Guerrero, Josep M.
2017-01-01
In recent years, renewable energy sources have been considered the most encouraging resources for grid and off-grid power generation. This paper presents an improved current control strategy for a three-phase photovoltaic grid-connected inverter (GCI) under unbalanced and nonlinear load conditions. It is challenging to suppress the harmonic content in the output current below a pre-set value in the GCI. It is also difficult to compensate for unbalanced loads even when the grid is under disruption due to total harmonic distortion (THD) and unbalanced loads. The primary advantage and objective of this method is to effectively compensate for the harmonic current content of the grid current and microgrid without the use of any compensation devices, such as active and passive filters. This method leads to a very low THD in both the GCI currents and the current exchanged with the grid. The control approach is designed to control the active and reactive power and harmonic current compensation, and it also corrects the system unbalance. The proposed control method features the synchronous reference frame (SRF) method. Simulation results are presented to demonstrate the effective performance of the proposed method. PMID:28192436
Naderipour, Amirreza; Asuhaimi Mohd Zin, Abdullah; Bin Habibuddin, Mohd Hafiz; Miveh, Mohammad Reza; Guerrero, Josep M
2017-01-01
In recent years, renewable energy sources have been considered the most encouraging resources for grid and off-grid power generation. This paper presents an improved current control strategy for a three-phase photovoltaic grid-connected inverter (GCI) under unbalanced and nonlinear load conditions. It is challenging to suppress the harmonic content in the output current below a pre-set value in the GCI. It is also difficult to compensate for unbalanced loads even when the grid is under disruption due to total harmonic distortion (THD) and unbalanced loads. The primary advantage and objective of this method is to effectively compensate for the harmonic current content of the grid current and microgrid without the use of any compensation devices, such as active and passive filters. This method leads to a very low THD in both the GCI currents and the current exchanged with the grid. The control approach is designed to control the active and reactive power and harmonic current compensation, and it also corrects the system unbalance. The proposed control method features the synchronous reference frame (SRF) method. Simulation results are presented to demonstrate the effective performance of the proposed method.
Modified Dual Three-Pulse Modulation technique for single-phase inverter topology
Sree Harsha, N. R.; Anitha, G. S.; Sreedevi, A.
2016-01-01
In a recent paper, a new modulation technique called Dual Three Pulse Modulation (DTPM) was proposed to improve the efficiency of the power converters of the Electric/Hybrid/Fuel-cell vehicles. It was simulated in PSIM 9.0.4 and uses analog multiplexers to generate the modulating signals for the DC/DC converter and inverter. The circuit used is complex and many other simulation softwares do not support the analog multiplexers as well. Also, the DTPM technique produces modulating signals for the converter, which are essentially needed to produce the modulating signals for the inverter. Hence, it cannot be used efficiently to switch the valves of a stand-alone inverter. We propose a new method to generate the modulating signals to switch MOSFETs of a single phase Dual-Three pulse Modulation based stand-alone inverter. The circuits proposed are simulated in Multisim 12.0. We also show an alternate way to switch a DC/DC converter in a way depicted by DTPM technique both in simulation (MATLAB/Simulink) and hardware. The circuitry is relatively simple and can be used for the further investigations of DTPM technique.
DEFF Research Database (Denmark)
Anurag, Anup; Yang, Yongheng; Blaabjerg, Frede
2015-01-01
loading, considering the operation outside active feed-in hours. An analytical lifetime model is then employed for lifetime quantization based on the Palgrem Miner rule. Thereafter, considering the lifetime reduction of the PV inverter under different mission profiles with reactive power injection......The widespread adoption of mixed renewables urgently require reactive power exchange at various feed-in points of the utility grid. Photovoltaic (PV) inverters are able to provide reactive power in a decentralized manner at the grid-connection points even outside active power feed-in operation......, especially at night when there is no solar irradiance. This serves as a motivation for utilizing the PV inverters at night for reactive power compensation. Thus, an analysis on the impact of reactive power injection by PV inverters outside feed-in operation on the thermal performance and the reliability has...
DEFF Research Database (Denmark)
Zhang, Zhen; Yang, Yongheng; Blaabjerg, Frede
2017-01-01
With the fast development of distributed power generations, stability and security have attracted extensive attention in the recent years. As a representative of clean energies, Photovoltaic (PV) systems have been installed extensively worldwide. This drives grid-connected requirements...... to be continuously updated. In current active grid requirements/codes, PV systems should be more intelligent in the considerations of the grid stability, reliability and fault protection. In this paper, two control strategies (i.e., the single-phase PQ control and power phase-angle control) are evaluated for grid...
Nouaiti, Ayoub; Saad, Abdallah; Mesbahi, Abdelouahed; Khafallah, Mohamed
2018-01-01
This paper presents the design and the implementation of a low-cost single phase five-level inverter for photovoltaic applications. The proposed multilevel inverter is composed of a simple boost converter, a switched-capacitor converter, and an H-bridge converter. An efficient control method which associates a closed-loop regulation method with a simple maximum power point tracking (MPPT) method is applied in order to allow the proposed multilevel inverter to transfer power energy from solar ...
DEFF Research Database (Denmark)
Xin, Zhen; Mattavelli, Paolo; Yao, WenLi
2017-01-01
Due to the low inductance of an LCL-filter, the grid current generated by an LCL-filtered Voltage Source Inverter (VSI) is sensitive to low-order grid-voltage harmonics. This issue is especially tough for the control system with Inverter Current Feedback (ICF), because the grid-current harmonics...... can freely flow into the filter capacitor without control. To cope with this issue, this paper develops an approach for the ICF control system to suppress the grid-current harmonics without adding extra sensors. The proposed method applies harmonic controllers and feedforward scheme simultaneously...
Experimental grid connected PV system power analysis
Semaoui, Smail; Abdeladim, Kamel; Arab, Amar Hadj; Boulahchich, Saliha; Amrouche, Said Ould; Yassaa, Noureddine
2018-05-01
Almost 80 % of Algerian territory is appropriate for the exploitation of solar energy. The Algerian energetic strategy provides a substantial injection of PV electricity to the national grid. Currently, about 344 MWp of PV arrays which corresponds approximately to 2,34 km2 of module surfaces, are connected on electricity grid over the national territory. The Algerian Northern regions are characterized by strong pollution and high humidity. These phenomena affect the energetic productivity of PV generator. The objective of our study is to analyze experimental grid connected PV system power in coastal locations. Hence, experiments have been conducted on three identical PV systems to determine the electrical performances. Transformer-less inverters are the most attractive for the ground-based photovoltaic (PV) system due to their efficiencies, reduced cost and weight. Besides, the absence of the galvanic isolation generates problems of capacitive leakage current on the AC side and the degradation of the insulation resistance on the DC side of the inverter. In this work, experimental study of the behavior of single-phase inverters without transformers is presented. The main objective of this work is to study the degradation of the insulation resistance at the input of the inverter, and the capacitive leakage current at the output of the inverter. This study was achieved at the CDER on a rainy day of 15/03/2017, on the first PV plant connected to the low voltage network in Algeria. This investigation can help forecasting the PV array energetic production by taking into account natural conditions.
Space Vector Pulse Width Modulation Strategy for Single-Phase Three-Level CIC T-source Inverter
DEFF Research Database (Denmark)
Shults, Tatiana E.; Husev, Oleksandr O.; Blaabjerg, Frede
2016-01-01
This paper presents a novel space vector pulse-width modulation strategy for a single-phase three-level buck-boost inverter based on an impedance-source network. The case study system is based on T-source inverter with continuous input current. To demonstrate the improved performance of the inver......This paper presents a novel space vector pulse-width modulation strategy for a single-phase three-level buck-boost inverter based on an impedance-source network. The case study system is based on T-source inverter with continuous input current. To demonstrate the improved performance...... of the inverter, the strategy was compared the traditional pulse-width modulation. It is shown that the approach proposed has fewer switching states and does not suffer from neutral point misbalance....
Adaptive Hysteresis Band Current Control for Transformerless Single-Phase PV Inverters
DEFF Research Database (Denmark)
Vázquez, Gerardo; Rodriguez, Pedro; Ordoñez, Rafael
2009-01-01
Current control based on hysteresis algorithms are widely used in different applications, such as motion control, active filtering or active/reactive power delivery control in distributed generation systems. The hysteresis current control provides to the system a fast and robust dynamic response......, and requires a simple implementation in standard digital signal platforms. On the other hand, the main drawback of classical hysteresis current control lies in the fact that the switching frequency is variable, as the hysteresis band is fixed. In this paper a variable band hysteresis control algorithm...... different single-phase PV inverter topologies, by means of simulations performed with PSIM. In addition, the behavior of the thermal losses when using each control structure in such converters has been studied as well....
A Standalone Solar Photovoltaic Power Generation using Cuk Converter and Single Phase Inverter
Verma, A. K.; Singh, B.; Kaushika, S. C.
2013-03-01
In this paper, a standalone solar photovoltaic (SPV) power generating system is designed and modeled using a Cuk dc-dc converter and a single phase voltage source inverter (VSI). In this system, a dc-dc boost converter boosts a low voltage of a PV array to charge a battery at 24 V using a maximum power point tracking control algorithm. To step up a 24 V battery voltage to 360 V dc, a high frequency transformer based isolated dc-dc Cuk converter is used to reduce size, weight and losses. The dc voltage of 360 V is fed to a single phase VSI with unipolar switching to achieve a 230 Vrms, 50 Hz ac. The main objectives of this investigation are on efficiency improvement, reduction in cost, weight and size of the system and to provide an uninterruptible power to remotely located consumers. The complete SPV system is designed and it is modeled in MATLAB/Simulink. The simulated results are presented to demonstrate its satisfactory performance for validating the proposed design and control algorithm.
DEFF Research Database (Denmark)
Husev, Oleksandr; Strzelecki, Ryszard; Blaabjerg, Frede
2016-01-01
This paper describes novel single-phase solutions with increased inverter voltage levels derived by means of a nonstandard inverter configuration and impedance source networks. Operation principles based on special modulation techniques are presented. Detailed component design guidelines along wi...... with simulation and experimental verification are also provided. Possible application fields are discussed, as well as advantages and disadvantages. Finally, future studies are addressed for the new solutions....
DEFF Research Database (Denmark)
Abdelhakim, Ahmed; Mattavelli, Paolo; Davari, Pooya
2018-01-01
This paper investigates and evaluates the performance of a single-phase split-source inverter (SSI), where an alternative unidirectional dc-ac configuration is used. Such configuration is utilized in order to use two common-cathode diodes in a single-device instead of using two separate diodes, r...
DEFF Research Database (Denmark)
Hadjidemetriou, Lenos; Kyriakides, Elias; Yang, Yongheng
2016-01-01
Synchronization is a crucial aspect in grid-tied systems, including single-phase photovoltaic inverters, and it can affect the overall performance of the system. Among prior-art synchronization schemes, the Multi Harmonic Decoupling Cell Phase-Locked Loop (MHDC-PLL) presents a fast response under...
Leakage current analysis of a single-phase transformer-less PV inverter connected to the grid
DEFF Research Database (Denmark)
Ma, Lin; Tang, F.; Zhou, F.
2009-01-01
Due to the large surface of the PV generator, its stray capacity with respect to the ground reaches values that can be quite high. When no transformer is used in a grid-connected PV system, common-mode current, which caused by the common mode voltage, can flow through the stray capacitance between...... the PV array and the ground. It is quite harmful to the body safety and PV system. In order to avoid leakage current, different inverter topologies that generate no varying common-mode voltages, such as bipolar pulse-width modulation (PWM) full-bridge topology, NPC topology have been proposed. From...... the safety and energy saving viewpoint, it is necessary to develop a higher efficiency topology. In this paper, the generation mechanism of common mode current is discussed. Then different methods used to eliminate the leakage current are compared. Finally, the full-bridge which generates no varying common...
DEFF Research Database (Denmark)
Ardashir, Jaber Fallah; Sabahi, Mehran; Hosseini, Seyed Hossein
2017-01-01
This paper proposes a new single-phase transformerless photovoltaic (PV) inverter for grid-tied PV systems. The topology is derived from the concept of a charge pump circuit in order to eliminate the leakage current. It is composed of four power switches, two diodes, two capacitors, and an LCL...... resonant control strategy is used to control the injected current. The main benefits of the proposed inverter are: the neutral of the grid is directly connected to the negative terminal of the PV panel, so the leakage current is eliminated; its compact size; low cost; the used dc voltage of the proposed...... are presented. Experimental results are presented to confirm both the theoretical analysis and the concept of the proposed inverter. The obtained results clearly validate the performance of the proposed inverter and its practical application in grid-tied PV systems....
Directory of Open Access Journals (Sweden)
A. Nouaiti
2018-02-01
Full Text Available This paper presents the design and the implementation of a low-cost single phase five-level inverter for photovoltaic applications. The proposed multilevel inverter is composed of a simple boost converter, a switched-capacitor converter, and an H-bridge converter. An efficient control method which associates a closed-loop regulation method with a simple maximum power point tracking (MPPT method is applied in order to allow the proposed multilevel inverter to transfer power energy from solar panels to autonomous load with no storage batteries. An experimental prototype of this inverter is fabricated at the laboratory and tested with a digital control system. Obtained results confirm the simplicity and the performance of the proposed photovoltaic system.
International Nuclear Information System (INIS)
Hamid, Muhammad Imran; Jusoh, Awang
2014-01-01
Highlights: • A reduction scheme for harmonics from utility interactive PV-inverter is proposed. • Single-phase conditioner with 3-phase expandability structure is used. • The single-phase conditioner in 3-phase structure work independently. • The scheme works effectively within overall operation range of the PV-inverter. • Conditioner in the scheme also improves the PV-inverter and plant’s utility factor. - Abstract: As the natural behavior of energy source and design characteristic, the current generated by a grid-interactive PV-inverter may contain harmonics. This distortion component will be carried on from the PV-inverter during injection power into the grid. Excessive harmonics in a grid will lead to a variety of power quality problems. This paper presents a distortion reduction scheme, utilizing a fed forward single-phase, generation-side power conditioner with a structure that can be expanded for use in a three-phase system and can work independently under imbalanced condition. Conditioner is placed in parallel with the photovoltaic plant and it functions to compensate the plant’s output current distortion, so that the total current flow to the grid is sinusoidal. This method also includes the implementation of a simpler control system for the conditioner, which consists of a combination of distortion current extraction, synchronization and a current control system, and realized through a TMS320F28335: a 150 MHz floating point DSP controller. Testing of the conditioner prototype, which was conducted on a real operation of a PV plant, showed that the scheme worked effectively within the overall operation range of the PV plant. This paper also discusses the potential of utility factor improvement of the PV-inverter and plant due to implementation of conditioner in the scheme
Almasoudi, Fahad M.; Alatawi, Khaled S.; Matin, Mohammad
2017-08-01
Implementation of transformerless inverters in PV grid-tied system offer great benefits such as high efficiency, light weight, low cost, etc. Most of the proposed transformerless inverters in literature are verified for only real power application. Currently, international standards such as VDE-AR-N 4105 has demanded that PV grid-tied inverters should have the ability of controlling a specific amount of reactive power. Generation of reactive power cannot be accomplished in single phase transformerless inverter topologies because the existing modulation techniques are not adopted for a freewheeling path in the negative power region. This paper enhances a previous high efficiency proposed H6 trnasformerless inverter with SiC MOSFETs and demonstrates new operating modes for the generation of reactive power. A proposed pulse width modulation (PWM) technique is applied to achieve bidirectional current flow through freewheeling state. A comparison of the proposed H6 transformerless inverter using SiC MOSFETs and Si MOSFTEs is presented in terms of power losses and efficiency. The results show that reactive power control is attained without adding any additional active devices or modification to the inverter structure. Also, the proposed modulation maintains a constant common mode voltage (CM) during every operating mode and has low leakage current. The performance of the proposed system verifies its effectiveness in the next generation PV system.
DEFF Research Database (Denmark)
Huang, Min; Blaabjerg, Frede; Yang, Yongheng
2013-01-01
-tied system, the output current harmonics of inverter are directly affected by the output line to line voltage. Hence, this paper proposes a new method to analyze the inverter output current harmonics by using the equivalent phase voltage of the three phase inverter. Based on this, a step by step design...
Directory of Open Access Journals (Sweden)
Tofael Ahmed
2014-06-01
Full Text Available In this paper, a single phase doubly grounded semi-Z-source inverter with maximum power point tracking (MPPT is proposed for photovoltaic (PV systems. This proposed system utilizes a single-ended primary inductor (SEPIC converter as DC-DC converter to implement the MPPT algorithm for tracking the maximum power from a PV array and a single phase semi-Z-source inverter for integrating the PV with AC power utilities. The MPPT controller utilizes a fast-converging algorithm to track the maximum power point (MPP and the semi-Z-source inverter utilizes a nonlinear SPWM to produce sinusoidal voltage at the output. The proposed system is able to track the MPP of PV arrays and produce an AC voltage at its output by utilizing only three switches. Experimental results show that the fast-converging MPPT algorithm has fast tracking response with appreciable MPP efficiency. In addition, the inverter shows the minimization of common mode leakage current with its ground sharing feature and reduction of the THD as well as DC current components at the output during DC-AC conversion.
LLCL-Filter Based Single-Phase Grid-Tied Aalborg Inverter
DEFF Research Database (Denmark)
Wu, Weimin; Feng, Shuangshuang; Ji, Junhao
2014-01-01
The Aalborg Inverter is a new type of high efficient DC/AC grid-tied inverter, where the input DC voltage can vary in a wide range. Compared with the LCL-filter, the LLCL-filter can save the total inductance for the conventional voltage source inverter. In this paper, an LLCL-filter based Aalborg...... Inverter is proposed and its character is illustrated through the small signal analysis in both “Buck” and “Buck-Boost” mode. From the modeling, it can be seen that the resonant inductor in the capacitor loop has not brought extra control difficulties, whereas more inductance in the power loop can be saved...
DEFF Research Database (Denmark)
Yang, Yongheng; Zhou, Keliang; Blaabjerg, Frede
2015-01-01
It is mandatory for grid-connected power converters to synchronize the feed-in currents with the grid. Moreover, the power converters should produce feed-in currents with low total harmonic distortions according to the demands, by employing advanced current controllers, e.g., Proportional Resonant...... deviations. Experiments on a single-phase grid-connected inverter system are presented, which have verified the proposals and also the effectiveness of the frequency adaptive current controllers....... (PR) and Repetitive Controllers (RC). The synchronization is actually to detect the instantaneous grid information (e.g., frequency and phase of the grid voltage) for the current control, which is commonly performed by a Phase-Locked-Loop (PLL) system. As a consequence, harmonics and deviations...
Modeling Single-Phase PV HB-ZVR Inverter Connected to Grid
DEFF Research Database (Denmark)
Guo, Yougui; Zeng, Ping; Zhu, Jieqiong
2011-01-01
PLECS is used to model the PV H-bridge zero voltage rectifier (HB-ZVR) inverter connected to grid and good results are obtained. First, several common topologies of PV inverters are introduced. Then the unipolar PWM control strategy is described for PV HB-ZVR inverter. Third, PLECS is briefly...... introduced. Fourth, the modeling of PV HB-ZVR inverter is presented with PLECS. Finally, a series of simulations are carried out. The simulation results tell us PLECS is very powerful tool to real power circuits and it is very easy to simulate LCL filter. They have also verified that the unipolar PWM control...... strategy is feasible to control the PV HB-ZVR inverter....
DEFF Research Database (Denmark)
Zangeneh Bighash, Esmaeil; Sadeghzadeh, Seyed Mohammad; Ebrahimzadeh, Esmaeil
2018-01-01
dynamic response and stability. To fill in this gap, this paper presents a fast and robust current controller based on a Model-Predictive Control (MPC) for single-phase PV inverters in other to deal with the LVRT operation. In order to confirm the effectiveness of the proposed controller, results...... the voltage sag period is short, a fast dynamic performance along with a soft behavior of the controller is the most important issue in the LVRT duration. Recently, some methods like Proportional Resonant (PR) controllers, have been presented to control the single phase PV systems in LVRT mode. However......, these methods have had uncertainties in respect their contribution in LVRT mode. In PR controllers, a fast dynamic response can be obtained by tuning the gains of PR controllers for a high bandwidth, but typically the phase margin is decreased. Therefore, the design of PR controllers needs a tradeoff between...
DEFF Research Database (Denmark)
Monfared, Mohammad; Golestan, Saeed; Guerrero, Josep M.
2014-01-01
Control of three-phase power converters in the synchronous reference frame is now a mature and well developed research topic. However, for single-phase converters, it is not as well-established as three-phase applications. This paper deals with the design of a synchronous reference frame multi-lo...... on a frequency response approach is presented. Finally, the theoretical achievements are supported by experimental results.......-loop control strategy for single phase inverter-based islanded distributed generation (DG) systems. The proposed controller uses a synchronous reference frame PI (SRFPI) controller to regulate the instantaneous output voltage, a capacitor current shaping loop in the stationary reference frame to provide active...
DEFF Research Database (Denmark)
Blaabjerg, Frede; Nami, A.; Zare, F.
2008-01-01
In this paper, a different configuration based on different DC bus voltage for a diode-clamped multilevel inverter has been presented. Two different symmetrical and asymmetrical arrangements of a four-level diode clamped inverters have been compared, in order to find an optimum arrangement...... compared with the conventional four-level inverter and this will lead to the reduction of harmonic content of output voltage. A predictive current control technique has been carried out to verify the viability of new configuration. The advantages of this control method are simplicity and applicability...
DEFF Research Database (Denmark)
Boora, Arash A.; Nami, Alireza; Zare, Firuz
2010-01-01
The output voltage quality of some of the single-phase multilevel inverters can be improved when their dc-link voltages are regulated asymmetrically. Symmetrical and asymmetrical multilevel diode-clamped inverters have the problem of dc-link capacitor voltage balancing, especially when power factor...... that the proposed combination of introduced multioutput dc–dc converter and single-phase ADCI is a good candidate for power conversion in residential photovoltaic (PV) utilization....
Photovoltaic power system tests on an 8-kilowatt single-phase line-commutated inverter
Stover, J. B.
1978-01-01
Efficiency and power factor were measured as functions of solar array voltage and current. The effects of input shunt capacitance and series inductance were determined. Tests were conducted from 15 to 75 percent of the 8 kW rated inverter input power. Measured efficiencies ranged from 76 percent to 88 percent at about 50 percent of rated inverter input power. Power factor ranged from 36 percent to 72 percent.
DEFF Research Database (Denmark)
Micallef, Alexander; Apap, Maurice; Spiteri-Staines, Cyril
2017-01-01
Optimization of the islanded and grid-connected operation of microgrids is important to achieve a high degree of reliability. In this paper, the authors consider the effect of current harmonics in single phase microgrids during both modes of operation. A detailed analysis of the effect of the out......Optimization of the islanded and grid-connected operation of microgrids is important to achieve a high degree of reliability. In this paper, the authors consider the effect of current harmonics in single phase microgrids during both modes of operation. A detailed analysis of the effect...... of the output impedance of the considered primary control loops on the harmonic output of the considered voltage source inverters is initially carried out. A virtual admittance loop is proposed to attenuate the current harmonic output in grid-connected operation that is generated due to the grid voltage...... distortion present at the point of common coupling (PCC) and due to local non-linear loads. This paper also considers the harmonic current sharing and resulting voltage harmonics at the PCC during islanded operation of the microgrid. A capacitive virtual impedance loop was implemented to improve the harmonic...
Directory of Open Access Journals (Sweden)
Renke Han
2014-01-01
Full Text Available It is a very crucial problem to make a microgrid operated reasonably and stably. Considering the nonlinear mathematics model of inverter established in this paper, the input-output feedback linearization method is used to transform the nonlinear mathematics model of inverters to a linear tracking synchronization and consensus regulation control problem. Based on the linear mathematics model and multiagent consensus algorithm, a decentralized coordinated controller is proposed to make amplitudes and angles of voltages from inverters be consensus and active and reactive power shared in the desired ratio. The proposed control is totally distributed because each inverter only requires local and one neighbor’s information with sparse communication structure based on multiagent system. The hybrid consensus algorithm is used to keep the amplitude of the output voltages following the leader and the angles of output voltage as consensus. Then the microgrid can be operated more efficiently and the circulating current between DGs can be effectively suppressed. The effectiveness of the proposed method is proved through simulation results of a typical microgrid system.
A new high-efficiency single-phase transformerless PV inverter topology
DEFF Research Database (Denmark)
Kerekes, Tamas; Teodorescu, Remus; Rodriguez, Pedro
2011-01-01
There is a strong trend in the photovoltaic (PV) inverter technology to use transformerless topologies in order to acquire higher efficiencies combining with very low ground leakage current. In this paper a new topology, based on the H-Bridge with a new AC bypass circuit consisting in a diode...
Neba, Yasuhiko
This paper deals with a maximum power point tracking (MPPT) control of the photovoltaic generation with the single-phase utility interactive inverter. The photovoltaic arrays are connected by employing the PWM current source inverter to the utility. The use of the pulsating dc current and voltage allows the maximum power point to be searched. The inverter can regulate the array voltage and keep the arrays to the maximum power. This paper gives the control method and the experimental results.
System and method for single-phase, single-stage grid-interactive inverter
Liu, Liming; Li, Hui
2015-09-01
The present invention provides for the integration of distributed renewable energy sources/storages utilizing a cascaded DC-AC inverter, thereby eliminating the need for a DC-DC converter. The ability to segment the energy sources and energy storages improves the maintenance capability and system reliability of the distributed generation system, as well as achieve wide range reactive power compensation. In the absence of a DC-DC converter, single stage energy conversion can be achieved to enhance energy conversion efficiency.
High Performance ZVT with Bus Clamping Modulation Technique for Single Phase Full Bridge Inverters
Energy Technology Data Exchange (ETDEWEB)
Xia, Yinglai; Ayyanar, Raja
2016-03-20
This paper proposes a topology based on bus clamping modulation and zero-voltage-transition (ZVT) technique to realize zero-voltage-switching (ZVS) for all the main switches of the full bridge inverters, and inherent ZVS and/or ZCS for the auxiliary switches. The advantages of the strategy include significant reduction in the turn-on loss of the ZVT auxiliary switches which typically account for a major part of the total loss in other ZVT circuits, and reduction in the voltage ratings of auxiliary switches. The modulation scheme and the commutation stages are analyzed in detail. Finally, a 1kW, 500 kHz switching frequency inverter of the proposed topology using SiC MOSFETs has been built to validate the theoretical analysis. The ZVT with bus clamping modulation technique of fixed timing and adaptive timing schemes are implemented in DSP TMS320F28335 resulting in full ZVS for the main switches in the full bridge inverter. The proposed scheme can save up to 33 % of the switching loss compared with no ZVT case.
Stability of single-phase natural circulation with inverted U-tube steam generators
Energy Technology Data Exchange (ETDEWEB)
Sanders, J.
1988-08-01
For natural circulation it is shown that parallel flow in the tubes of an inverted U-tube stream generator can be, at certain power levels, unstable. A mathematical model, based on one-dimensional Oberbeck-Boussinesq equations, shows that stability can be attained if in some tubes the water flows backward, opposite to the normal flow direction. The results are compared to measurements obtained from the natural circulation test A2-77A in the LOBI-MOD2 integral system test facility.
DEFF Research Database (Denmark)
Ji, Junhao; Wu, Weimin; He, Yuanbin
2015-01-01
The single-phase power converter topologies evolving of photovoltaic applications are still including passive filters, like the LCLor LLCL-filter. Compared with the LCL-filter, the total inductance of the LLCL-filter can be reduced a lot. However, due to the resonant inductor in series...... with the bypass capacitor, the differential mode (DM) electromagnetic interference (EMI) noise attenuation of an LLCL-filter-based grid-tied inverter declines. Conventionally, a capacitor was inserted in parallel with the LC resonant circuit branch of the LLCL-filter to suppress the DM EMI noise. In order...... to achieve a small value of capacitor as well as to minimize the additional reactive power, a novel simple DM EMI suppressor for the LLCL-filter-based system is proposed. The characters of two kinds of DM EMI suppressor are analyzed and compared in detail. Simulations and experiments on a 0.5-kW 110-V/50-Hz...
Ghanbarian, Mohammad Mehdi; Nayeripour, Majid; Rajaei, Amirhossein; Mansouri, Mohammad Mahdi
2016-03-01
As the output power of a microgrid with renewable energy sources should be regulated based on the grid conditions, using robust controllers to share and balance the power in order to regulate the voltage and frequency of microgrid is critical. Therefore a proper control system is necessary for updating the reference signals and determining the proportion of each inverter in the microgrid control. This paper proposes a new adaptive method which is robust while the conditions are changing. This controller is based on a modified sliding mode controller which provides adapting conditions in linear and nonlinear loads. The performance of the proposed method is validated by representing the simulation results and experimental lab results. Copyright © 2015 ISA. Published by Elsevier Ltd. All rights reserved.
Grid-connected of photovoltaic module using nonlinear control
DEFF Research Database (Denmark)
El Fadil, H.; Giri, F.; Guerrero, Josep M.
2012-01-01
The problem of controlling single-phase grid connected photovoltaic (PV) system is considered. The control objective is fourfold: (i) asymptotic stability of the closed loop system, (ii) maximum power point tracking (MPPT) of PV module (iii) tight regulation of the DC bus voltage, and (iv) unity...
Comparative Analysis of Inversors for Small PV Systems Grid Connected
International Nuclear Information System (INIS)
Sidrach de Cardona, M.; Ramirez, L.
2001-01-01
The energy produced by a grid connected photovoltaic system is a function of weather conditions, mainly available radiation and temperature, photovoltaic array efficiency and inverter characteristics. The results obtained in experimental measurements with four small grid-connected inverters are described in this work. The main goal is to know the inverter performance in real operation conditions. For this purpose a 2 kW photovoltaic system has been used. These results allow us to know both the inverter efficiency and its output power quality. The following parameters have been evaluated as a function of output inverter power: efficiency, point of maximum power tracking, intensity and voltage waveform, total harmonic distortion and harmonic values to 31 order, frequency, power factor and reactive power. Other interesting parameters like stand-by energy consumption and daily losses due to the inverter threshold have also been analyzed. The results allow us to know the inverter features as a function of its real work point. In our comparative study it is possible to observe remarkable differences between the inverters; these results show how important it is to have a unique standard for inverters to photovoltaic grid-connected systems. (Author) 10 refs
Grid-Connected Photovoltaic System with Active Power Filtering Functionality
Directory of Open Access Journals (Sweden)
Joaquín Vaquero
2018-01-01
Full Text Available Solar panels are an attractive and growing source of renewable energy in commercial and residential applications. Its use connected to the grid by means of a power converter results in a grid-connected photovoltaic system. In order to optimize this system, it is interesting to integrate several functionalities into the power converter, such as active power filtering and power factor correction. Nonlinear loads connected to the grid generate current harmonics, which deteriorates the mains power quality. Active power filters can compensate these current harmonics. A photovoltaic system with added harmonic compensation and power factor correction capabilities is proposed in this paper. A sliding mode controller is employed to control the power converter, implemented on the CompactRIO digital platform from National Instruments Corporation, allowing user friendly operation and easy tuning. The power system consists of two stages, a DC/DC boost converter and a single-phase inverter, and it is able to inject active power into the grid while compensating the current harmonics generated by nonlinear loads at the point of common coupling. The operation, design, simulation, and experimental results for the proposed system are discussed.
Interharmonics from Grid-Connected PV Systems
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Sera, Dezso
2017-01-01
As the penetration level of grid-connected Photovoltaic (PV) systems increases, the power quality is one of the major concerns for system operators and the demands are becoming even stricter. The impact of interharmonics on the grid has been acknowledged in recent research when considering a large......-scale adoption of PV inverters. However, the origins of interharmonics remain unclear. Thus, this paper performs tests on a commercial PV inverter to explore interharmonic generation and more important investigates the mechanism of interharmonic emission. The investigation reveals that the perturbation...... of the solutions. Simulation results indicate that the constant-voltage MPPT method is the most suitable solution to the mitigation of interharmonics introduced by the MPPT operation, as it avoids the perturbation in the PV voltage during operation....
DEFF Research Database (Denmark)
Qin, Zian; Tang, Yi; Loh, Poh Chiang
2015-01-01
studied, where the commercially available film capacitors, circuit topologies, and control strategies for active power decoupling are all taken into account. Then, an adaptive decoupling voltage control method is proposed to further improve the performance of dc decoupling in terms of efficiency...... and reliability. The feasibility and superiority of the identified solution for active power decoupling together with the proposed adaptive decoupling voltage control method are finally verified by both the experimental results obtained on a 2 kW single-phase inverter.......This paper presents the benchmark study of ac and dc active power decoupling circuits for second-order harmonic mitigation in kW-scale single-phase inverters. First of all, the best solutions of active power decoupling to achieve high efficiency and power density are identified and comprehensively...
Control of Power and Voltage of Solar Grid Connected
Allah, Boucetta Abd; Djamel, Labed
2016-01-01
Renewable energy is high on International agendas. Currently, grid-connected photovoltaic systems are a popular technology to convert solar energy into electricity. Control of power injected into the grid, maximum power point, high efficiency, and low total harmonic distortion of the currents injected into the grid are the requirements for inverter connection into the grid. Consequently, the performance of the inverters connected to the grid depends largely on the control strategy applied. In...
Flexible Mode Control of Grid Connected Wind Energy Conversion System Using Wavelet
Directory of Open Access Journals (Sweden)
Bhavna Jain
2015-01-01
Full Text Available Small wind turbine systems offer services to critical loads during grid faults and also connected back to grid in normal condition. The connection of a wind energy conversion system to the grid requires a robust phase locked loop (PLL and continuous monitoring of the grid conditions such as overvoltage, undervoltage, overfrequency, underfrequency, and grid outages. This paper describes a flexible control operation to operate a small wind turbine in both stand-alone mode via planned islanding and grid connected mode as well. In particular, a proper monitoring and control algorithm is required for transition between the modes. A wavelet based energy function is used for detection of grid disturbances as well as recovery of grid so that transition between the modes is made. To obtain good power quality LCL filter is used to reduce ripples. PLL is used for synchronization whenever mode changes from stand-alone to grid connected. Simulation results from a 10 kW wind energy conversion system are included to show the usefulness of the proposed methods. The control method is tested by generated gate pulses for single phase bridge inverter using field programmable gate array (FPGA.
Battery impedance spectroscopy using bidirectional grid connected
Indian Academy of Sciences (India)
Keywords. Impedance spectroscopy; grid connection; battery converter; state of charge; health monitoring ... The converter is grid connected and controlled to operate at unity power factor. Additional ... Sadhana. Current Issue : Vol. 43, Issue 6.
Bush, Craig R.
This dissertation presents a novel current source converter topology that is primarily intended for single-phase photovoltaic (PV) applications. In comparison with the existing PV inverter technology, the salient features of the proposed topology are: a) the low frequency (double of line frequency) ripple that is common to single-phase inverters is greatly reduced; b) the absence of low frequency ripple enables significantly reduced size pass components to achieve necessary DC-link stiffness and c) improved maximum power point tracking (MPPT) performance is readily achieved due to the tightened current ripple even with reduced-size passive components. The proposed topology does not utilize any electrolytic capacitors. Instead an inductor is used as the DC-link filter and reliable AC film capacitors are utilized for the filter and auxiliary capacitor. The proposed topology has a life expectancy on par with PV panels. The proposed modulation technique can be used for any current source inverter where an unbalanced three-phase operation is desires such as active filters and power controllers. The proposed topology is ready for the next phase of microgrid and power system controllers in that it accepts reactive power commands. This work presents the proposed topology and its working principle supported by with numerical verifications and hardware results. Conclusions and future work are also presented.
DEFF Research Database (Denmark)
Wang, Wen; Yan, Lingjie; Zeng, Xiangjun
2017-01-01
Neutral-to-ground overvoltage may occur in non-effectively grounded power systems because of the distributed parameters asymmetry and resonance between Petersen coil and distributed capacitances. Thus, the constraint of neutral-to-ground voltage is critical for the safety of distribution networks....... In this paper, an active grounding system based on single-phase inverter and its control parameter design method is proposed to achieve this objective. Relationship between its output current and neutral-to-ground voltage is derived to explain the principle of neutral-to-ground voltage compensation. Then...
A PWM Controller of a Full Bridge Single-Phase Synchronous Inverter for Micro-Grid System
Rahman, Tawfikur; Motakabber, S. M. A.; Ibrahimy, M. I.; Raghib, Aliza ‘Aini Binti Md Ralib@ Md
2017-12-01
Nowadays, microgrid system technology is becoming popular for small area power management systems. It is essential to be less harmonic-distortion and high efficiency of the inverter for microgrid applications. Pulse width modulation (PWM) controller is a conventional switching control technique which is suitable to use in the microgrid connected power inverter system. The control method and algorithm of this technique are challenging, and different approaches are required to avoid the complexity for a customized solution of the microgrid application. This paper proposes a comparative analysis of different controller and their operational methods. A PWM controller is used to reduce the ripple voltage noise while a continuous current mode provides a small output ripple which gives steady-state error as zero on fundamental and cutoff frequency. To reduce the ripple current, higher frequency harmonic distortion, switching loss and phase noise, LC low pass filter is used on either side of input and output terminals. The proposed inverter is designed by MATLAB 2016a simulation software. A balanced load resistance (RL = 20.5 Ω) of star configuration and a dual input DC voltage of ± 35V are considered. In this design, the circuit parameters, the fundamental frequency of 50 Hz, the PWM duty cycle of 95%, the cutoff frequency of the switching controller of 33 kHz are considered. The inverter in this paper exhibits THD of 0.44% and overall efficiency approximately of 98%. The proposed inverter is expected to be suitable for microgrid applications.
Energy Technology Data Exchange (ETDEWEB)
NONE
1997-03-01
Discussions and evaluations have been performed on the safety and durability of the device installed with inverter to protect grid connection being an important device in the photovoltaic power generation system. This paper summarizes the achievements in fiscal 1996. The current fiscal year performed data collection and long-term continuous operation according to the durability test program for the device installed with inverter to protect grid connection, as the continuation from the previous fiscal year. In the electrical characteristics, although no large changes have been found in AC overvoltage and AC undervoltage, instability was observed in the detection level. With regard to temperatures in different components, the temperature rise has become nearly the same as in the maximum output continuous operation as a result of the repetition of the operation and shutdown, whereas the influence on the electrical and thermal stresses have increased. Particularly, when temperature rise in the AC side noise filter was given observation, the measurement of conductive high-frequency terminal voltage showed a value higher by several ten dB than in the previous fiscal year. The current fiscal year has gone farther to starting the measurement of noise electric field intensity as the base of electromagnetic interference. (NEDO)
DEFF Research Database (Denmark)
Li, Kerui; Shen, Yanfeng; Yang, Yongheng
2018-01-01
and thus low leakage currents in PV applications. The symmetric Z-source HERIC inverter requires two extra active switches. Nevertheless, the operation frequency of the two switches is the line frequency, leading to negligible losses. More importantly, the performance in terms of low leakage currents...... and harmonics is improved. Experimental tests are performed to validate the analysis and performance of the proposed system....
DEFF Research Database (Denmark)
Gautam, Aditya R.; Fulwani, Deepak; Guerrero, Josep M.
2016-01-01
The paper presents a detailed analysis of second order harmonic ripple in a DC microgrid. A boost converter feeding PWM inverter load is considered and equivalent circuit is proposed. The effect of the size of input capacitor, output capacitor and inductor of boost converter, on this ripple has...
DEFF Research Database (Denmark)
Wickramasinghe Abeywardana, Damith Buddika; Acuna, Pablo; Hredzak, Branislav
2018-01-01
Vehicle to grid (V2G) reactive power compensation using electric vehicle (EV) onboard chargers helps to ensure grid power quality by achieving unity power factor operation. However, the use of EVs for V2G reactive power compensation increases the second-order harmonic ripple current component...... from the grid, exposes the EV battery to these undesirable ripple current components for a longer period and discharges the battery due to power conversion losses. This paper presents a way to provide V2G reactive power compensation through a boost inverter-based single stage EV charger and a DC...
Mission Profile Translation to Capacitor Stresses in Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Ma, Ke; Wang, Huai
2014-01-01
DC capacitors are widely adopted in grid-connected PhotoVoltaic(PV) systems for power stabilization and control decoupling. They have become one of the critical components in grid-connected PV inverters in terms of cost, reliability and volume. The electrical and thermal stresses of the DC...... stresses of the DC capacitors under both normal and abnormal grid conditions. As a consequence, this investigation provides new insights into the sizing and reliability prediction of those capacitors with respect to priorart studies. Two study cases on a single-stage PV inverter and a two-stage PV inverter...
Grid-connected wind and photovoltaic system
Devabakthuni, Sindhuja
The objective of this thesis is to design a grid connected wind and photovoltaic system. A new model of converter control was designed which maintains the voltage of the bus to grid as constant when combined system of solar and wind is connected to AC bus. The model is designed to track maximum power at each point irrespective of changes in irradiance, temperature and wind speed which affects the power supplied to grid. Solar power from the sun is not constant as it is affected by changes in irradiances and temperature. Even the wind power is affected by wind speed. A MPPT controller was designed for both systems. A boost converter is designed which uses the pulses from MPPT controller to boost the output. Wind system consists of wind turbine block from the MATLAB with a pitch angle controller to maintain optimum pitch angle. The output from wind turbine is connected to a permanent magnet synchronous generator. The unregulated DC output from the photovoltaic system is directly given to boost converter. The AC output from the wind system is given to an uncontrolled rectifier to get a unregulated DC output. The unregulated DC output goes to the boost converter. A voltage source inverter was designed which converts the rectified DC output from the boost converter to AC power. The inverter is designed to maintain constant AC bus voltage irrespective of the disturbances in the power supply. Photovoltaic and wind systems are individually designed for 5KW each in MATLAB-Simulink environment. In this thesis, the models were subjected to changes in irradiance, temperature and wind speed and the results were interpreted. The model was successful in tracking maximum at every instant and the AC bus voltage was maintained constant throughout the simulation.
Voltage Quality of Grid Connected Wind Turbines
DEFF Research Database (Denmark)
Chen, Zhe; Blaabjerg, Frede; Sun, Tao
2004-01-01
Grid connected wind turbines may cause quality problems, such as voltage variation and flicker. This paper discusses the voltage variation and flicker emission of grid connected wind turbines with doubly-fed induction generators. A method to compensate flicker by using a voltage source converter...
DEFF Research Database (Denmark)
Qin, Zian; Tang, Yi; Loh, Poh Chiang
2016-01-01
efficiency and high power density is identified and comprehensively studied, and the commercially available film capacitors, the circuit topologies, and the control strategies adopted for active power decoupling are all taken into account. Then, an adaptive decoupling voltage control method is proposed...... to further improve the performance of dc decoupling in terms of efficiency and reliability. The feasibility and superiority of the identified solution for active power decoupling together with the proposed adaptive decoupling voltage control method are finally verified by both the simulation and experimental......This paper presents the benchmark study of ac and dc active power decoupling circuits for second order harmonic mitigation in kW scale single-phase inverters. First of all, a brief comparison of recently reported active power decoupling circuits is given, and the best solution that can achieve high...
Cao, Dong
Due the energy crisis and increased oil price, renewable energy sources such as photovoltaic panel, wind turbine, or thermoelectric generation module, are used more and more widely for vehicle and grid-connected applications. However, the output of these renewable energy sources varies according to different solar radiation, wind speed, or temperature difference, a power converter interface is required for the vehicle or grid-connected applications. Thermoelectric generation (TEG) module as a renewable energy source for automotive industry is becoming very popular recently. Because of the inherent characteristics of TEG modules, a low input voltage, high input current and high voltage gain dc-dc converters are needed for the automotive load. Traditional high voltage gain dc-dc converters are not suitable for automotive application in terms of size and high temperature operation. Switched-capacitor dc-dc converters have to be used for this application. However, high voltage spike and EMI problems exist in traditional switched-capacitor dc-dc converters. Huge capacitor banks have to be utilized to reduce the voltage ripple and achieve high efficiency. A series of zero current switching (ZCS) or zero voltage switching switched-capacitor dc-dc converters have been proposed to overcome the aforementioned problems of the traditional switched-capacitor dc-dc converters. By using the proposed soft-switching strategy, high voltage spike is reduced, high EMI noise is restricted, and the huge capacitor bank is eliminated. High efficiency, high power density and high temperature switched-capacitor dc-dc converters could be made for the TEG interface in vehicle applications. Several prototypes have been made to validate the proposed circuit and confirm the circuit operation. In order to apply PV panel for grid-connected application, a low cost dc-ac inverter interface is required. From the use of transformer and safety concern, two different solutions can be implemented, non
DEFF Research Database (Denmark)
Guan, Yajuan; Quintero, Juan Carlos Vasquez; Guerrero, Josep M.
2015-01-01
In this paper, a hierarchical control system based on a novel autonomous current sharing controller for grid-connected microgrids (MGs) is presented. A three-level hierarchical control system is implemented to guarantee the power sharing performance among voltage controlled parallel inverters......, while providing the required active and reactive power to the utility grid. A communication link is used to transmit the control signal from the tertiary and secondary control levels to the primary control. Simulation results from a MG based on two grid-connected parallel inverters are shown in order...
Optimising the economic viability of grid-connected photovoltaic systems
International Nuclear Information System (INIS)
Mondol, Jayanta Deb; Yohanis, Yigzaw G; Norton, Brian
2009-01-01
The impact of photovoltaic (PV) array size, orientation, inclination, load profile, electricity buying price, feed-in tariffs, PV/inverter sizing ratio ('sizing ratio') and PV/inverter cost ratio ('cost ratio') on the economic viability of a grid-connected PV system was investigated using a validated TRNSYS simulation model. The results showed that the fractional load met directly by a PV system depends on matching between PV supply and building load profile, sizing ratio and PV inclination. The profitability of a grid-connected PV system increases if the PV system is sized to reduce excess PV electrical energy fed to the grid when the feed-in tariff is lower than electricity buying price. The effect of feed-in tariffs on PV saving for selected European countries has been shown. The cost of the PV electricity depends on sizing ratio, PV and inverter lifetimes, cost ratio, PV inclination and financial parameters. The effect of cost ratio on the optimum PV/inverter sizing ratio is less significant when the cost ratio lies within 7-11. The minimum PV electricity cost at low and high insolation conditions were obtained for sizing ratios of 1.6 and 1.2, respectively. The lowest PV electricity cost was found for surface slopes within 30-40 for the selected European locations. The PV electricity cost for cost ratio of 5 and 13 varied from 0.44-0.85 EURkWh -1 to 0.38-0.76 EURkWh -1 , respectively within high to low insolation conditions when the PV module unit cost, market discount rate, PV size, PV lifetime and inverter lifetime were assumed to be 6.5 EURW p -1 , 3%, 13 kW p , 20 years and 10 years, respectively. (author)
Directory of Open Access Journals (Sweden)
ARUN, K.
2016-05-01
Full Text Available A modified digital signal processing procedure is described for the on-line estimation of DC, fundamental and harmonics of periodic signal. A frequency locked loop (FLL incorporated within the parallel structure of observers is proposed to accommodate a wide range of frequency drift. The error in frequency generated under drifting frequencies has been used for changing the sampling frequency of the composite observer, so that the number of samples per cycle of the periodic waveform remains constant. A standard coupled oscillator with automatic gain control is used as numerically controlled oscillator (NCO to generate the enabling pulses for the digital observer. The NCO gives an integer multiple of the fundamental frequency making it suitable for power quality applications. Another observer with DC and second harmonic blocks in the feedback path act as filter and reduces the double frequency content. A systematic study of the FLL is done and a method has been proposed to design the controller. The performance of FLL is validated through simulation and experimental studies. To illustrate applications of the new FLL, estimation of individual harmonics from nonlinear load and the design of a variable sampling resonant controller, for a single phase grid-connected inverter have been presented.
Reliability analysis of grid connected small wind turbine power electronics
International Nuclear Information System (INIS)
Arifujjaman, Md.; Iqbal, M.T.; Quaicoe, J.E.
2009-01-01
Grid connection of small permanent magnet generator (PMG) based wind turbines requires a power conditioning system comprising a bridge rectifier, a dc-dc converter and a grid-tie inverter. This work presents a reliability analysis and an identification of the least reliable component of the power conditioning system of such grid connection arrangements. Reliability of the configuration is analyzed for the worst case scenario of maximum conversion losses at a particular wind speed. The analysis reveals that the reliability of the power conditioning system of such PMG based wind turbines is fairly low and it reduces to 84% of initial value within one year. The investigation is further enhanced by identifying the least reliable component within the power conditioning system and found that the inverter has the dominant effect on the system reliability, while the dc-dc converter has the least significant effect. The reliability analysis demonstrates that a permanent magnet generator based wind energy conversion system is not the best option from the point of view of power conditioning system reliability. The analysis also reveals that new research is required to determine a robust power electronics configuration for small wind turbine conversion systems.
MPPT algorithm for voltage controlled PV inverters
DEFF Research Database (Denmark)
Kerekes, Tamas; Teodorescu, Remus; Liserre, Marco
2008-01-01
This paper presents a novel concept for an MPPT that can be used in case of a voltage controlled grid connected PV inverters. In case of single-phase systems, the 100 Hz ripple in the AC power is also present on the DC side. Depending on the DC link capacitor, this power fluctuation can be used t...... to track the MPP of the PV array, using the information that at MPP the power oscillations are very small. In this way the algorithm can detect the fact that the current working point is at the MPP, for the current atmospheric conditions....
EXPERIMENTAL STUDY AND PERFORMANCE OF SOLAR ENERGY SYSTEM WITH GRID CONNECTED POWER SUPPLY
Pradeep Bharti; Dr. A.K.Sharma
2017-01-01
In this paper , we are analyzed about the solar power with grid connection using of various component such as PV Cells battery inverter, and grid power connection , in this way we are connected the grid power and solar power , after that finally we are analyzed the power quality of output with the help of various devices.
DEFF Research Database (Denmark)
Abdeldjabar, Benrabah; Xu, Dianguo; Wang, Xiongfei
2016-01-01
This paper deals with the problem of LCL filter resonance in grid connected inverter control. The system equations are reformulated to allow the application of the active disturbance rejection control (ADRC). The resonance, assumed unknown, is treated as a disturbance, then estimated and mitigated...
Three-Phase Grid-Connected of Photovoltaic Generator Using Nonlinear Control
DEFF Research Database (Denmark)
Yahya, A.; El Fadil, H.; Guerrero, Josep M.
2014-01-01
This paper proposes a nonlinear control methodology for three phase grid connected of PV generator. It consists of a PV arrays; a voltage source inverter, a grid filter and an electric grid. The controller objectives are threefold: i) ensuring the Maximum power point tracking (MPPT) in the side...... stability analysis and simulation results that the proposed controller meets all the objectives....
A Sensorless Power Reserve Control Strategy for Two-Stage Grid-Connected PV Systems
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2017-01-01
Due to the still increasing penetration of grid-connected Photovoltaic (PV) systems, advanced active power control functionalities have been introduced in grid regulations. A power reserve control, where namely the active power from the PV panels is reserved during operation, is required for grid...... support. In this paper, a cost-effective solution to realize the power reserve for two-stage grid-connected PV systems is proposed. The proposed solution routinely employs a Maximum Power Point Tracking (MPPT) control to estimate the available PV power and a Constant Power Generation (CPG) control...... performed on a 3-kW two-stage single-phase grid-connected PV system, where the power reserve control is achieved upon demands....
Battery impedance spectroscopy using bidirectional grid connected ...
Indian Academy of Sciences (India)
Shimul Kumar Dam
Keywords. Impedance spectroscopy; grid connection; battery converter; state of charge; health monitoring. 1. Introduction .... the load should be within the safe range of operation specified by the ... A split capacitor damping scheme is adopted here as shown in ...... spectroscopy testing on the Advanced Technology Devel-.
Energy Technology Data Exchange (ETDEWEB)
NONE
1996-03-01
Discussions and evaluations have been performed on the safety and durability of the device installed with inverter to protect grid connection being an important device in the photovoltaic power generation system. In discussing the durability test items, electrical property changes were observed on AC overvoltage, AC undervoltage, frequency rise, and frequency fall, as the continuation from the previous fiscal year, in order to evaluate temperature rise in different parts due to lapse of operation time and the effects of thermal stress in each component on the stress of the entire product. Furthermore, verification of single operation detecting function, tests on sudden input power change, sudden grid voltage change, and measurement of conductive high frequency terminal voltage were conducted in addition to the above observations. In discussing the durability test methods, repetition of operation and shutdown during the rated operation was adopted in place of the simulated operation using variation in the insolation having been discussed in the previous year. As a result of the tests, no noticeable changes were recognized from the evaluation result after a lapse of 5,000 hours from the start of the operation, as compared to those after the aging operation. (NEDO)
Energy Technology Data Exchange (ETDEWEB)
NONE
1998-03-01
Tests and discussions have been performed on the safety and durability of the device installed with inverter to protect grid connection, being an important device in the photovoltaic power generation system. The particularly important requirements demanded in the device were specified as maintenance of electric power quality, coordination with the protection system in the grid side, and assurance of safety of personnel and facilities. The current fiscal year has performed operation corresponding to that in the actual field for 20 years in total, and the evaluation tests on electrical characteristics and electric power quality. This paper summarizes the achievements in four years including the results available up to the previous fiscal year. Although no large change has been identified in the electrical characteristics, variance has been found in the detection time of overvoltage in the grid side. With regard to the electric power quality, the value has exceeded 89 dB as the determining condition for the certification test in the conduction interfering waves of 5 kHz to 10 kHz. In addition, it was confirmed that the conductive high-frequency noise terminal voltage in the grid side after the repetition of operations and shutdowns tends to increase according to the operation lapse time. (NEDO)
Novel deadbeat power control strategy for grid connected systems
Directory of Open Access Journals (Sweden)
Yousry Atia
2015-09-01
Full Text Available This paper introduces a novel approach for power control of three phase voltage source inverter (VSI in grid connected distribution generation system. In this approach, the control of active and reactive power is based on deadbeat control strategy. First, the difference between the reference and actual currents are introduced in different approach. Then current to power substitutions are carried out to obtain direct relationship between the required inverter voltage and instantaneous power errors. There is no need for coordinate transformation or PLL, where the required inverter voltage vector calculations carried out in α–β stationary reference frame. The proposed technique introduces two cross coupling components in the control function. Including these two components, the controller can achieve nearly zero steady-state tracking error of the controlled variables. To obtain fixed switching frequency operations, space vector modulation (SVM is used to synthesize the required inverter voltage vector and to generate the switching pulses for the VSI. The proposed strategy has the simplicity of the direct power control (DPC technique and doesn’t require any current control loops. The proposed strategy is experimentally implemented using fixed-point microcontroller. Simulation and experimental results are presented to confirm the superiority of the proposed strategy.
Research on simulated devices for Solar photovoltaic grid-connected generation system
Directory of Open Access Journals (Sweden)
quan-zhu Zhang
2017-01-01
Full Text Available On the standpoint of energy conservation and emission reduction, one device simulated photovoltaic grid-connected generation system based on SPWM was designed in the paper. And DC/AC inverter could transduce efficiently direct current to alternating current. The MCU(Micro-Control-Unit, in this system could achieve the control method for maximum-power-point and tracking for frequency and phase. Moreover, the MCU could implement PWM (Plus-Width Modulating through programming. The system showed clearly the whole photovoltaic grid-connected generation system using simulated methods and ways.
Bosco Raj, T. Ajith; Ramesh, R.; Maglin, J. R.; Vaigundamoorthi, M.; William Christopher, I.; Gopinath, C.; Yaashuwanth, C.
2014-01-01
The main objective of this work is to study the behaviour of the solar PV systems and model the efficient Grid-connected solar power system. The DC-DC MPPT circuit using chaotic pulse width modulation has been designed to track maximum power from solar PV module. The conversion efficiency of the proposed MPPT system is increased when CPWM is used as a control scheme. This paper also proposes a simplified multilevel (seven level) inverter for a grid-connected photovoltaic system. The primary g...
Experimental evaluation of 8kW grid-connected photovoltaic system in Egypt
Elkholy, A.; Fahmy, F.H.; Abou El-Ela, A.A.; Nafeh, Abd El-Shafy A.; Spea, S.R.
2016-01-01
An experimental observation study of 8 kW grid-connected photovoltaic (PV) system that is installed at Electronics Research Institute (ERI), Giza, Egypt (Latitude 30.04°N, Longitude 31.21°E), is presented. This study includes the quality of the electrical power generated and injected into the network. The considered system consists of 28 × 295 Wp multicrystalline PV modules, StecaGrid three-phase 8 kW grid-connected inverter and a Solar-Log 300 PM+ for data acquisition and remote monitoring. ...
A Review on Direct Power Control for Applications to Grid Connected PWM Converters
Directory of Open Access Journals (Sweden)
T. A. Trivedi
2015-08-01
Full Text Available The Direct Power Control strategy has become popular as an alternative to the conventional vector oriented control strategy for grid connected PWM converters. In this paper, Direct Power Control as applied to various applications of grid connected converters is reviewed. The Direct Power Control for PWM rectifiers, Grid Connected DC/AC inverters applications such as renewable energy sources interface, Active Power Filters, Doubly Fed Induction Generators and AC-DC-AC converters are discussed. Control strategies such as Look-Up table based control, predictive control, Virtual Flux DPC, Model based DPC and DPC-Space Vector Modulation are critically reviewed. The effects of various key parameters such as selection of switching vector, sampling time, hysteresis band and grid interfacing on performance of direct power controlled converters are presented.
Zhou, Ning; Yang, Jia; Cheng, Zheng; Chen, Bo; Su, Yong Chun; Shu, Zhan; Zou, Jin
2017-06-01
Solar photovoltaic power generation is the power generation using solar cell module converting sunlight into DC electric energy. In the paper an equivalent model of solar photovoltaic power generation system is built in RTDS. The main circuit structure of the two-stage PV grid-connected system consists of the DC-DC, DC-AC circuit. The MPPT (Maximum Power Point Tracking) control of the PV array is controlled by adjusting the duty ratio of the DC-DC circuit. The proposed control strategy of constant voltage/constant reactive power (V/Q) control is successfully implemented grid-connected control of the inverter when grid-connected operation. The closed-loop experiment of islanding protection device of photovoltaic power plant on RTDS, verifies the correctness of the simulation model, and the experimental verification can be applied to this type of device.
Grid-connected solar electricity going mainstream
Energy Technology Data Exchange (ETDEWEB)
MacLellan, I. [Arise Technologies Corp., Kitchener, ON (Canada)
2004-06-01
In 20 days, the sun provides the equivalent amount of energy found in all known fossil fuel reserves. This paper provides an outline of solar energy industry activities from the perspective of Arise Technologies, a Canadian-based solar energy company. An overview of the company's vision and marketing strategy was presented, including annual sales. Details of the company's commercial projects were reviewed, with specific reference to the first Canadian grid-connected solar electric subdivision. An introduction to photovoltaic electricity (PV) as an environmentally positive energy source was presented. Statistics included information on the current solar market worldwide as well as government and industry investment. Portable solar energy applications were provided, as well as grid-tied products in relation to private dwelling and commercial, industrial and institutional buildings. Details of an Arise solar home were presented. An outline of the Technology Early Action Measures (TEAM) was presented, with reference to the federal government's Climate Change Action Plan. The benefits of solar economics were given. PV factory production was overviewed, with a presentation of the experience curve and the number of grid-connected solar electric homes globally. Top global PV manufacturers were listed as well as a chart of world energy transitions underlining the emergence of renewable energy programs and systems. A summary of solar energy in Japan was provided, along with details of mid and long term solar energy planning, as well as other projects around the world. Canadian investment in PV was compared with other countries and details of past government spending on other energy sources were also presented. It was concluded that Canada was far behind other G-8 countries with reference to grid-connected PV, but that off-grid PV was a real business in Canada. It was also concluded that Japan would represent the first real mainstream grid-connected market
Grid-connected solar electricity going mainstream
International Nuclear Information System (INIS)
MacLellan, I.
2004-01-01
In 20 days, the sun provides the equivalent amount of energy found in all known fossil fuel reserves. This paper provides an outline of solar energy industry activities from the perspective of Arise Technologies, a Canadian-based solar energy company. An overview of the company's vision and marketing strategy was presented, including annual sales. Details of the company's commercial projects were reviewed, with specific reference to the first Canadian grid-connected solar electric subdivision. An introduction to photovoltaic electricity (PV) as an environmentally positive energy source was presented. Statistics included information on the current solar market worldwide as well as government and industry investment. Portable solar energy applications were provided, as well as grid-tied products in relation to private dwelling and commercial, industrial and institutional buildings. Details of an Arise solar home were presented. An outline of the Technology Early Action Measures (TEAM) was presented, with reference to the federal government's Climate Change Action Plan. The benefits of solar economics were given. PV factory production was overviewed, with a presentation of the experience curve and the number of grid-connected solar electric homes globally. Top global PV manufacturers were listed as well as a chart of world energy transitions underlining the emergence of renewable energy programs and systems. A summary of solar energy in Japan was provided, along with details of mid and long term solar energy planning, as well as other projects around the world. Canadian investment in PV was compared with other countries and details of past government spending on other energy sources were also presented. It was concluded that Canada was far behind other G-8 countries with reference to grid-connected PV, but that off-grid PV was a real business in Canada. It was also concluded that Japan would represent the first real mainstream grid-connected market, followed by Europe
DEFF Research Database (Denmark)
Yang, Yongheng; Blaabjerg, Frede
2013-01-01
The progressively growing of single-phase photovoltaic (PV) systems makes the Distribution System Operators (DSO) to update or revise the existing grid codes in order to guarantee the availability, quality and reliability of the electrical system. It is expected that the future PV systems connected...... to the low-voltage grid will be more active with functionalities of low voltage ride-through (LVRT) and the grid support capability, which is not the case today. In this paper, the operation principle is demonstrated for a single-phase grid-connected PV system in low voltage ride through operation in order...... to map future challenges. The system is verified by simulations and experiments. Test results show that the proposed power control method is effective and the single-phase PV inverters connected to low-voltage networks are ready to provide grid support and ride-through voltage fault capability...
Frequency Adaptive Selective Harmonic Control for Grid-Connected Inverters
DEFF Research Database (Denmark)
Yang, Yongheng; Zhou, Keliang; Wang, Huai
2015-01-01
SHC scheme consists of multiple parallel recursive (nk±m)-order (k = 0, 1, 2, . . ., and m ≤ n/2) harmonic control modules with independent control gains, which can be optimally weighted in accordance with the harmonic distribution. The hybrid SHC thus offers an optimal trade-off among cost...
A New Design Method for the Passive Damped LCL and LLCL Filter-Based Single-Phase Grid-Tied Inverter
DEFF Research Database (Denmark)
Wu, Weimin; He, Yuanbin; Tang, Tianhao
2013-01-01
A higher order passive power filter (LLCL filter) for the grid-tied inverter is becoming attractive for industrial applications due to the possibility to reduce the cost of the copper and the magnetic material. However, similar to the conventional LCL filter, the grid-tied inverter is facing...
Sotoodeh, Pedram
This dissertation presents the design of a novel multi-level inverter with FACTS capability for small to mid-size (10-20kW) permanent-magnet wind installations using modular multi-level converter (MMC) topology. The aim of the work is to design a new type of inverter with D-STATCOM option to provide utilities with more control on active and reactive power transfer of distribution lines. The inverter is placed between the renewable energy source, specifically a wind turbine, and the distribution grid in order to fix the power factor of the grid at a target value, regardless of wind speed, by regulating active and reactive power required by the grid. The inverter is capable of controlling active and reactive power by controlling the phase angle and modulation index, respectively. The unique contribution of the proposed work is to combine the two concepts of inverter and D-STATCOM using a novel voltage source converter (VSC) multi-level topology in a single unit without additional cost. Simulations of the proposed inverter, with 5 and 11 levels, have been conducted in MATLAB/Simulink for two systems including 20 kW/kVAR and 250 W/VAR. To validate the simulation results, a scaled version (250 kW/kVAR) of the proposed inverter with 5 and 11 levels has been built and tested in the laboratory. Experimental results show that the reduced-scale 5- and 11-level inverter is able to fix PF of the grid as well as being compatible with IEEE standards. Furthermore, total cost of the prototype models, which is one of the major objectives of this research, is comparable with market prices.
Promotional drivers for grid-connected PV
Energy Technology Data Exchange (ETDEWEB)
Lopez Polo, A.; Hass, R.; Suna, D.
2009-03-15
This report for the International Energy Agency (IEA) made by Task 10 of the Photovoltaic Power Systems (PVPS) programme takes a look at promotional measures for grid-connected photovoltaic systems. The mission of the Photovoltaic Power Systems Programme is to enhance the international collaboration efforts which accelerate the development and deployment of photovoltaic solar energy. The objective of Task 10 is stated as being to enhance the opportunities for wide-scale, solution-oriented application of photovoltaics in the urban environment. The paper discusses the core objective of this study which was to analyse the success of various governmental regulatory programs and governmental and non-governmental marketing programs for grid-connected PV systems. To meet this objective, a review of the most important past and current programs around the world was conducted. The theoretical bases of supply and demand are explained and the types of existing strategies are documented in a second Section. In Chapter 3, various programs around the world are described. Chapter 4 focuses on defining success criteria which will be used for the analysis of the programs. Finally, the major conclusions drawn complete this analysis.
DEFF Research Database (Denmark)
Liu, Yuan; Wu, Weimin; Li, Yun
2016-01-01
The capacitor-current-feedback active damping method is attractive for high-order-filter-based high power grid-tied inverter when the grid impedance varies within a wide range. In order to improve the system control bandwidth and attenuate the high order grid background harmonics by using the quasi....... In this paper, a low pass filter is proposed to be inserted in the capacitor current feedback loop op LLCL-filter based grid-tied inverter together with a digital proportional and differential compensator. The detailed theoretical analysis is given. For verification, simulations on a 2kW/220V/10kHz LLCL...
Interim Report by Asia International Grid Connection Study Group
Omatsu, Ryo
2018-01-01
The Asia International Grid Connection Study Group Interim Report examines the feasibility of developing an international grid connection in Japan. The Group has investigated different cases of grid connections in Europe and conducted research on electricity markets in Northeast Asia, and identifies the barriers and challenges for developing an international grid network including Japan. This presentation introduces basic contents of the interim report by the Study Group.
DEFF Research Database (Denmark)
Tang, Y.; Yao, W.; Blaabjerg, Frede
2015-01-01
In single-phase uninterruptible power supply (UPS) applications, it is well known that the AC side instantaneous power is not constant by nature. The resulting input current from the DC source side will inevitably contain low frequency ripple components that may largely deteriorate the system...... as active power conversion, while its CM operation is controlled in such a way that the low frequency ripple current on the DC side can be maintained in a minimum level. The proposed ripple current reduction method may not only work with linear loads, but also nonlinear loads, where more sophisticated...
Review international standards for grid connected photovoltaic systems in Malaysia
International Nuclear Information System (INIS)
Mekhilef, S.; Rahim, N.A.
2006-01-01
Grid connected PV is being applied on variety application including large centralised stations, commercial building and individual houses. There is a need for specific standard to address distinctive new issue created by grid connected PV power system. Internationally many countries are attempting to develop standards for building integration, Dc side issues and grid connection issues. This paper surveys the current development state of the major countries standards in this area, comparing and contrasting, standards and guideline under development, also addressing the need of standards for grid connected in Malaysia
Flicker Mitigation of Grid Connected Wind Turbines Using STATCOM
DEFF Research Database (Denmark)
Sun, Tao; Chen, Zhe; Blaabjerg, Frede
2004-01-01
to the point of common coupling (PCC) to relieve the flicker produced by grid connected wind turbines and the corresponding control scheme is described in detail. Simulation results show that STATCOM is an effective measure to mitigate the flicker level during continuous operation of grid connected wind......Grid connected wind turbines may produce flicker during continuous operation. In this paper flicker emission of grid connected wind turbines with doubly fed induction generators is investigated during continuous operation. A STATCOM using PWM voltage source converter (VSC) is connected in shunt...
International Nuclear Information System (INIS)
Lau, K.Y.; Muhamad, N.A.; Arief, Y.Z.; Tan, C.W.; Yatim, A.H.M.
2016-01-01
Blessed with abundant solar radiation, Malaysia has a huge potential for grid-connected PV (photovoltaic) installations, particularly for its fast-growing residential sector. Nevertheless, Malaysia's PV installation capacity is relatively small compared with the global PV capacity. Significantly, the pricing mechanisms for grid-connected PV projects need to be appropriately assessed to build up the public's confidence to invest in PV projects. In this paper, we analyze the effects of component costs, FiTs (feed-in tariffs), and carbon taxes on grid-connected PV systems in Malaysian residential sector using the HOMER (Hybrid Optimization of Multiple Energy Resources) software. Results demonstrate that the implementation of grid-connected PV systems is highly feasible with PV array costs of $ 1120/kW or lower. For higher PV array costs up to $ 2320/kW, introducing an FiT rate three times higher ($ 0.30/kWh) than the grid tariff for a 100 kW grid sale capacity will, NPC-wise, prioritize grid-connected PV systems over the utility grid. By implementing the FiT ($ 0.50/kWh) and the carbon tax ($ 36/metric ton) schemes simultaneously, grid-connected PV systems will remain as the optimal systems even for costly PV arrays (up to $ 4000/kW). The findings are of paramount importance as far as PV pricing variability is concerned. - Highlights: • Grid-connected PV for Malaysian residential sector has been analyzed using HOMER. • Component costs, feed-in tariffs, and carbon taxes affect optimal system types. • Grid-connected PV projects are feasible for low PV array costs ($ 1120/kW or lower). • For higher PV array and inverter costs, feed-in tariffs should be implemented. • Combining feed-in tariffs with carbon taxes are effective for further lowering NPCs.
DEFF Research Database (Denmark)
Anurag, Anup; Yang, Yongheng; Blaabjerg, Frede
2015-01-01
Reactive power support by photovoltaic (PV) systems is of increasingly interest, when compared to the conventional reactive power compensation devices. PV inverters can exchange reactive power with the utility grid in a decentralized manner even outside feed-in operation, especially at nights when...... there is no solar irradiance. However, reactive power injection causes additional power losses in the switching components leading to a temperature rise in the devices. Thus, this paper analyses the impact of reactive power injection by PV inverters outside feed-in operation on the thermal performance...... of their power switching components. A thermal analysis based on the mission profile (i.e., solar irradiance and ambient temperature) has been incorporated, so as to determine the additional temperature rise in the components induced by the operation outside feed-in hours. An analytical lifetime model has been...
Active and reactive power neurocontroller for grid-connected photovoltaic generation system
Directory of Open Access Journals (Sweden)
I. Abadlia
2016-03-01
Full Text Available Many researchers have contributed to the development of a firm foundation for analysis and design of control applications in grid-connected renewable energy sources. This paper presents an intelligent control algorithm fond on artificial neural networks for active and reactive power controller in grid-connected photovoltaic generation system. The system is devices into two parts in which each part contains an inverter with control algorithm. A DC/DC converter in output voltage established by control magnitude besides maximum power point tracker algorithm always finds optimal power of the PV array in use. A DC/AC hysteresis inverter designed can synchronize a sinusoidal current output with the grid voltage and accurate an independent active and reactive power control. Simulation results confirm the validation of the purpose. Neurocontroller based active and reactive power presents an efficiency control that guarantees good response to the steps changing in active and reactive power with an acceptable current/voltage synchronism. In this paper the power circuit and the control system of the presented grid-connected photovoltaic generation system is simulated and tested by MatLab/Simulink.
Research on Frequency Control of Grid Connected Sodium-Sulfur Battery
Directory of Open Access Journals (Sweden)
Zhang Fenglin
2018-01-01
Full Text Available Sodium sulfur battery is the only energy storage battery with large capacity and high energy density. It has a great application prospect in the peak load shifting of power grid, due to the lack of domestic research on it, it is urgent to evaluate the effect of grid-connection of sodium sulfur battery scientifically. According to the experimental data of the sodium sulfur battery project, the battery model is built. Compared with the real discharge curve, the error of the model simulation curve is small, so the battery model is effective. The AC / DC power grid model is built, and the rectifier and inverter control circuits are designed to simulate the scenario that the wind turbine and the battery are supplied to the passive load. The simulation results show that the grid-connected model of the sodium sulfur battery under the two control strategies can stabilize the larger frequency fluctuation.
DEFF Research Database (Denmark)
Blaabjerg, Frede; Aquila, A. Dell; Liserre, Marco
2004-01-01
of dc/dc converters via a 50 Hz frequency-shift. The input admittance is calculated and measured for two study examples (a three-phase active rectifier and a single-phase photovoltaic inverter). These examples show that the purpose of a well designed controller for grid-connected converters......A systematic approach to study dc/ac and ac/dc converters without the use of synchronous transformation is proposed. The use of a frequency-shift technique allows a straightforward analysis of single-phase and three-phase systems. The study of dc/ac and of ac/dc converters is reported to the study...... is to minimize the input admittance in order to make the grid converter more robust to grid disturbance....
Modeling of Step-up Grid-Connected Photovoltaic Systems for Control Purposes
Directory of Open Access Journals (Sweden)
Daniel Gonzalez
2012-06-01
Full Text Available This paper presents modeling approaches for step-up grid-connected photovoltaic systems intended to provide analytical tools for control design. The first approach is based on a voltage source representation of the bulk capacitor interacting with the grid-connected inverter, which is a common model for large DC buses and closed-loop inverters. The second approach considers the inverter of a double-stage PV system as a Norton equivalent, which is widely accepted for open-loop inverters. In addition, the paper considers both ideal and realistic models for the DC/DC converter that interacts with the PV module, providing four mathematical models to cover a wide range of applications. The models are expressed in state space representation to simplify its use in analysis and control design, and also to be easily implemented in simulation software, e.g., Matlab. The PV system was analyzed to demonstrate the non-minimum phase condition for all the models, which is an important aspect to select the control technique. Moreover, the system observability and controllability were studied to define design criteria. Finally, the analytical results are illustrated by means of detailed simulations, and the paper results are validated in an experimental test bench.
Autonomous economic operation of grid connected DC microgrid
DEFF Research Database (Denmark)
Nutkani, Inam Ullah; Wang, Peng; Loh, Poh Chiang
2014-01-01
This paper presents an autonomous power sharing scheme for economic operation of grid-connected DC microgrid. Autonomous economic operation approach has already been tested for standalone AC microgrids to reduce the overall generation cost and proven a simple and easier to realize compared...... with the centralized management approach. In this paper, the same concept has been extended to grid-connected DC microgrid. The proposed economic droop scheme takes into consideration the power generation cost of Distributed Generators (DGs) and utility grid tariff and adaptively tunes their respective droop curves...... secondary control. The performance of the proposed scheme has been verified for the example grid-connected DC microgrid....
International Nuclear Information System (INIS)
Rey-Boué, Alexis B.; García-Valverde, Rafael; Ruz-Vila, Francisco de A.; Torrelo-Ponce, José M.
2012-01-01
Highlights: ► A design methodology for Photovoltaic grid-connected systems is presented. ► Models of the Photovoltaic Generator and the 3-phase Inverter are described. ► The power factor and the power quality are regulated with vector control. ► Simulation and experimental results validate the design methodology. ► The proposed methodology can be extended to any Renewable or Industrial System. - Abstract: A novel methodology is presented in this paper, for the design of the Power and Control Subsystems of a 3-phase Photovoltaic Grid-Connected system in an easy and comprehensive way, as an integrative approach. At the DC side of the Power Subsystem, the Photovoltaic Generator modeling is revised and a simple model is proposed, whereas at the AC side, a vector analysis is done to deal with the instantaneous 3-phase variables of the grid-connected Voltage Source Inverter. A d–q control approach is established in the Control Subsystem, along with its specific tuned parameters, as a vector control alternative which will allow the decoupled control of the instantaneous active and reactive powers. A particular Case of Study is presented to illustrate the behavior of the design methodology regarding the fulfillment of the Photovoltaic plant specifications. Some simulations are run to study the performance of the Photovoltaic Generator together with the exerted d–q control to the grid-connected 3-phase inverter, and some experimental results, obtained from a built flexible platform, are also shown. The simulations and the experimental results validate the overall performance of the 3-phase Photovoltaic Grid-Connected system due to the attained unitary power factor operation together with good power quality. The final validation of the proposed design methodology is also achieved.
Grid-connected photovoltaic system design for local government ...
African Journals Online (AJOL)
Grid-connected photovoltaic system design for local government offices in Nigeria. ... Nigerian Journal of Technology. Journal Home ... It is neat, silent and elegant process of generating electric power in environmentally friendly manner. In this ...
International Review of Grid Connection Requirements for Wind Turbines
Energy Technology Data Exchange (ETDEWEB)
Jauch, Clemens; Soerensen, Poul [Risoe National Laboratory, Roskilde (Denmark). Wind Energy Dept.; Bak-Jensen, Birgitte [Aalborg Univ. (Denmark). Inst. of Energy Technology
2004-07-01
Some of the latest and most relevant grid connection requirements for wind turbines of different countries are summarized and discussed. The inherent implications of these requirements for current wind turbine technology are outlined and discussed.
PLL strategies of grid connected converters under distorted input voltages
Czech Academy of Sciences Publication Activity Database
Šimek, Petr; Škramlík, Jiří; Valouch, Viktor
2014-01-01
Roč. 59, č. 1 (2014), s. 1-12 ISSN 0001-7043 Institutional support: RVO:61388998 Keywords : voltage source converter * grid - connected applications * phase locked loop Subject RIV: JA - Electronics ; Optoelectronics, Electrical Engineering
International Nuclear Information System (INIS)
Jou, Hurng-Liahng; Chang, Yi-Hao; Wu, Jinn-Chang; Wu, Kuen-Der
2015-01-01
Highlights: • The operation strategy for grid-connected PV generation system integrated with battery energy storage is proposed. • The PV system is composed of an inverter and two DC-DC converter. • The negative impact of grid-connected PV generation systems on the grid can be alleviated by integrating a battery. • The operation of the developed system can be divided into nine modes. - Abstract: The operation strategy for a lab-scale grid-connected photovoltaic generation system integrated with battery energy storage is proposed in this paper. The photovoltaic generation system is composed of a full-bridge inverter, a DC–DC boost converter, an isolated bidirectional DC–DC converter, a solar cell array and a battery set. Since the battery set acts as an energy buffer to adjust the power generation of the solar cell array, the negative impact on power quality caused by the intermittent and unstable output power from a solar cell array is alleviated, so the penetration rate of the grid-connected photovoltaic generation system is increased. A lab-scale prototype is developed to verify the performance of the system. The experimental results show that it achieves the expected performance
Simulation and Analysis of a Grid Connected Multi-level Converter Topologies and their Comparison
Directory of Open Access Journals (Sweden)
Mohammad Shadab Mirza
2014-09-01
Full Text Available This paper presents simulation and analysis of a grid connected multi-level converter topologies. In this paper, converter circuit works as an inverter by controlling the switching angle (α. This paper, presents a MATLAB/SIMULINK model of multi-level converter topologies (topology1 & topology2. Topology1 is without transformer while topology2 with transformer. Both the topologies are simulated and analyzed for three level converters in order to reduce the total harmonic distortion (THD. A comparative study of topology1 and topology2 is also presented in this paper for different switching angles (α and battery voltages. The results have been tabulated and discussed.
Energy Technology Data Exchange (ETDEWEB)
Sidrach de Cardona, M.; Ramirez, L.
2001-07-01
The energy produced by a grid connected photovoltaic system is a function of weather conditions, mainly available radiation and temperature, photovoltaic array efficiency and inverter characteristics. The results obtained in experimental measurements with four small grid-connected inverters are described in this work. The main goal is to know the inverter performance in real operation conditions. For this purpose a 2 kW{sub p} photovoltaic system has been used. These results allow us to know both the inverter efficiency and its output power quality. The following parameters have been evaluated as a function of but put inverter power efficiency, point of maximum power tracking, intensity and voltage waveform, total harmonic distortion and harmonic values to 31 order, frequency, power factor and reactive power. Other interesting parameters like stand-by energy consumption and daily losses due to the inverter threshold have also been analyzed. the results allow us to know the inverter features as a function of its real work point. In our comparative study it is possible to observe remarkable differences between the inverters; these results show how important it is to have a unique standard for inverters to photovoltaic grid-connected systems. (Author)
REVIEW ON GRID INTERFACING OF MULTIMEGAWATT PHOTOVOLTAIC INVERTERS
Mr. Vilas S. Solanke*; Mr. Naveen Kumar
2016-01-01
This paper presents review on the latest development of control of grid connected photovoltaic energy conversion system. Also this paper present existing systems control algorithm for three-phase and single phase grid-connected photovoltaic (PV) system. This paper focuses on one aspect of solar energy, namely grid interfacing of large-scale PV farms. This Grid-connected photovoltaic i.e. PV systems can provide a number of benefits to electric utilities, such as power loss reduction, improve...
A Hybrid Power Control Concept for PV Inverters with Reduced Thermal Loading
DEFF Research Database (Denmark)
Yang, Yongheng; Wang, Huai; Blaabjerg, Frede
2014-01-01
on a single-phase PV inverter under yearly operation is presented with analyses of the thermal loading, lifetime, and annual energy yield. It has revealed the trade-off factors to select the power limit and also verified the feasibility and the effectiveness of the proposed control concept.......This letter proposes a hybrid power control concept for grid-connected Photovoltaic (PV) inverters. The control strategy is based on either a Maximum Power Point Tracking (MPPT) control or a Constant Power Generation (CPG) control depending on the instantaneous available power from the PV panels....... The essence of the proposed concept lies in the selection of an appropriate power limit for the CPG control to achieve an improved thermal performance and an increased utilization factor of PV inverters,and thus to cater for a higher penetration level of PV systems with intermittent nature. A case study...
Experimental evaluation of 8 kW grid-connected photovoltaic system in Egypt
Directory of Open Access Journals (Sweden)
A. Elkholy
2016-09-01
Full Text Available An experimental observation study of 8 kW grid-connected photovoltaic (PV system that is installed at Electronics Research Institute (ERI, Giza, Egypt (Latitude 30.04°N, Longitude 31.21°E, is presented. This study includes the quality of the electrical power generated and injected into the network. The considered system consists of 28 × 295 Wp multicrystalline PV modules, StecaGrid three-phase 8 kW grid-connected inverter and a Solar-Log 300 PM+ for data acquisition and remote monitoring. The power quality parameters at the inverter output side have been measured using CA8335 power quality analyzer. The system has been installed in August 2014 and generated 5.7 MWh till February 2015. The produced electricity by the system is injected directly into the grid without storage device. The purpose of this paper is to present and evaluate the measurements of the power quality parameters obtained from the PV site. Also, this paper presents a comprehensive evaluation of the performance of the system over a period of one week. The observation and analyses exploitation of the collected data can help to evaluate the performance of the PV system connected to the network.
DEFF Research Database (Denmark)
Yang, Yongheng; Zhou, Keliang; Blaabjerg, Frede
2016-01-01
Grid-connected power converters should employ advanced current controllers, e.g., Proportional Resonant (PR) and Repetitive Controllers (RC), in order to produce high-quality feed-in currents that are required to be synchronized with the grid. The synchronization is actually to detect...... of the resonant controllers and by approximating the fractional delay using a Lagrange interpolating polynomial for the RC, respectively, the frequency-variation-immunity of these periodic current controllers with a fixed sampling rate is improved. Experiments on a single-phase grid-connected system are presented...... the instantaneous grid information (e.g., frequency and phase of the grid voltage) for the current control, which is commonly performed by a Phase-Locked-Loop (PLL) system. Hence, harmonics and deviations in the estimated frequency by the PLL could lead to current tracking performance degradation, especially...
DEFF Research Database (Denmark)
Tang, Yi; Yao, Wenli; Loh, Poh Chiang
2016-01-01
This paper presents a transformerless inverter topology, which is capable of simultaneously solving leakage current and pulsating power issues in grid-connected photovoltaic (PV) systems. Without adding any additional components to the system, the leakage current caused by the PV-to-ground parasi......This paper presents a transformerless inverter topology, which is capable of simultaneously solving leakage current and pulsating power issues in grid-connected photovoltaic (PV) systems. Without adding any additional components to the system, the leakage current caused by the PV......-to-ground parasitic capacitance can be bypassed by introducing a common-mode (CM) conducting path to the inverter. The resulting ground leakage current is therefore well controlled to be below the regulation limit. Furthermore, the proposed inverter can also eliminate the well-known double-line-frequency pulsating...... power that is inherent in single-phase PV systems. By properly injecting CM voltages to the output filter capacitors, the pulsating power can be decoupled from the dc-link. Therefore, it is possible to use long-lifetime film capacitors instead of electrolytic capacitors to improve the reliability...
DEFF Research Database (Denmark)
Golestan, Saeed; Guerrero, Josep M.; Quintero, Juan Carlos Vasquez
2017-01-01
Single-phase phase-locked loops (PLLs) are popular for the synchronization and control of single-phase gridconnected converters. They are also widely used for monitoring and diagnostic purposes in the power and energy areas. In recent years, a large number of single-phase PLLs with different stru......-PLLs). The members of each category are then described and their pros and cons are discussed. This work provides a deep insight into characteristics of different single-phase PLLs and, therefore, can be considered as a reference for researchers and engineers....
Directory of Open Access Journals (Sweden)
Ayetül Gelen
2015-05-01
Full Text Available This paper presents a thermal based modified dynamic model of a Solid Oxide Fuel Cell (SOFC for grid-connected systems. The proposed fuel cell model involves ohmic, activation and concentration voltage losses, thermal dynamics, methanol reformer, fuel utilization factor and power limiting module. A power conditioning unit (PCU, which consists of a DC-DC boost converter and a DC-AC voltage-source inverter (VSI, their controller, transformer and filter, is designed for grid-connected systems. The voltage-source inverter with six Insulated Gate Bipolar Transistor (IGBT switches inverts the DC voltage that comes from the converter into a sinusoidal voltage synchronized with the grid. The simulations and modeling of the system are developed on Matlab/Simulink environment. The performance of SOFC with converter is examined under step and random load conditions. The simulation results show that the designed boost converter for the proposed thermal based modified SOFC model has fairly followed different DC load variations. Finally, the AC bus of 400 Volt and 50 Hz is connected to a single-machine infinite bus (SMIB through a transmission line. The real and reactive power managements of the inverter are analyzed by an infinite bus system. Thus, the desired nominal values are properly obtained by means of the inverter controller.
Selective compensation of voltage harmonics in grid-connected microgrids
DEFF Research Database (Denmark)
Savaghebi, Mehdi; Vasquez, Juan Carlos; Jalilian, Alireza
2013-01-01
In this paper, a novel approach is proposed for selective compensation of main voltage harmonics in a grid-connected microgrid. The aim of compensation is to provide a high voltage quality at the point of common coupling (PCC). PCC voltage quality is of great importance due to sensitive loads tha...... to an acceptable level....
Reliability Oriented Design of a Grid-Connected Photovoltaic Microinverter
DEFF Research Database (Denmark)
Shen, Yanfeng; Wang, Huai; Blaabjerg, Frede
2017-01-01
High reliability performance of microinverters in Photovoltaic (PV) systems is a merit to match lifetime with PV panels, and to reduce the required maintenance efforts and costs. This digest applies a reliability oriented design method for a grid-connected PV microinverter to achieve specific...
Repetitive controller for improving grid-connected photovoltaic systems
Almeida, de P.M.; Duarte, J.L.; Ribeiro, P.F.; Barbosa, P.G.
2014-01-01
This study presents the modelling and design steps of a discrete time recursive repetitive controller (RC) to be used in a grid-connected photovoltaic (PV) system. It is shown that the linear synchronous reference frame proportional-integral controller, originally designed to control the converter's
grid-connected photovoltaic system design for local government
African Journals Online (AJOL)
user
wind power and has durability of more than twenty five years with a very minimal .... enhance energy yield of grid connected PV power plant by naturally catching .... cause it to operate at maximum power point irrespective of changing weather ...
A GRID-CONNECTED HYBRID WIND-SOLAR POWER SYSTEM
Directory of Open Access Journals (Sweden)
MAAMAR TALEB
2017-06-01
Full Text Available A hybrid renewable energy system consisting of a photovoltaic generator and a wind driven DC machine is interconnected with the power utilities grid. The interconnection is done through the use of two separate single phase full wave controlled bridge converters. The bridge converters are operated in the “inverter mode of operation”. That is to guaranty the extraction of the real powers from the wind driven generator as well as from the photovoltaic generator and inject them into the power utilities grid. At any pretended surrounding weather conditions, maximum extraction of powers from both renewable energy sources is targeted. This is done through the realization of self-adjusted firing angle controllers responsible of triggering the semiconductor elements of the controlled converters. An active power filter is shunted with the proposed setup to guaranty the sinusoid quality of the power utilities line current. The overall performance of the proposed system has been simulated in MATLAB/SIMULINK environment. Quite satisfactory and encouraging results have been obtained.
Long term performance analysis of a grid connected photovoltaic system in Northern Ireland
International Nuclear Information System (INIS)
Mondol, Jayanta Deb; Yohanis, Yigzaw; Smyth, Mervyn; Norton, Brian
2006-01-01
The performance of a 13 kW p roof mounted, grid connected photovoltaic system in Northern Ireland over a period of three years has been analysed on hourly, daily and monthly bases. The derived parameters included reference yield, array yield, final yield, array capture losses, system losses, PV and inverter efficiencies and performance ratio. The effects of insolation and inverter operation on the system performance were investigated. The monthly average daily PV, system and inverter efficiencies varied from 4.5% to 9.2%, 3.6% to 7.8% and 50% to 87%, respectively. The annual average PV, system and inverter efficiencies were 7.6%, 6.4% and 75%, respectively. The monthly average daily DC and AC performance ratios ranged from 0.35 to 0.74 and 0.29 to 0.66, respectively. The annual average monthly AC performance ratios for the three years were 0.60, 0.61 and 0.62, respectively. The performance of this system is compared with that of other representative systems internationally
DEFF Research Database (Denmark)
Teodorescu, Remus; Blaabjerg, Frede
2004-01-01
This paper is describing the recently introduced proportional-resonant (PR) controllers and their suitability for grid-connected converters current control. It is shown that the known shortcomings associated with PI controllers like steady - state error for single-phase converters and the need...... of decoupling for three-phase converters can be alleviated. Additionally, selective harmonic compensation is also possible with PR controllers. Suggested control-diagrams for three-phase grid converters and active filters are also presented. A practical application of PR current control for a photovoltaic (PV...
DEFF Research Database (Denmark)
Afshari, Ehsan; Moradi, Gholam Reza; Yang, Yongheng
2017-01-01
Unbalanced grid voltage dips may lead to unbalanced non-sinusoidal current injections, dc-link voltage oscillations, and active and/or reactive power oscillations with twice the grid fundamental frequency in three-phase grid-connected Photovoltaic (PV) systems. Double grid frequency oscillations...... of the most important issues that should be coped with for a reliable operation of grid-connected converters under unbalanced grid faults. Accordingly, this paper reviews the existing CRC methods and presents a current reference generation method, which can have 16 unique modes. Issues are also investigated...... at the dc-link of the conventional two-stage PV inverters can further deteriorate the dc-link capacitor, which is one of the most life-limiting components in the system. Proper controls of these converters may efficiently address this problem. In those solutions, Current Reference Calculation (CRC) is one...
Modeling and Simulation for an 8 kW Three-Phase Grid-Connected Photo-Voltaic Power System
Cen, Zhaohui
2017-09-01
Gird-connected Photo-Voltaic (PV) systems rated as 5-10 kW level have advantages of scalability and energy-saving, so they are very typical for small-scale household solar applications. In this paper, an 8 kW three-phase grid-connected PV system model is proposed and studied. In this high-fidelity model, some basic PV system components such as solar panels, DC-DC converters, DC-AC inverters and three-phase utility grids are mathematically modelled and organized as a complete simulation model. Also, an overall power controller with Maximum Power Point Control (MPPT) is proposed to achieve both high-efficiency for solar energy harvesting and grid-connection stability. Finally, simulation results demonstrate the effectiveness of the PV system model and the proposed controller, and power quality issues are discussed.
Design of Current-Controller with PR-regulator for LCL-Filter Based Grid-Connected Converter
DEFF Research Database (Denmark)
Zeng, Guohong; Rasmussen, Tonny Wederberg
2010-01-01
In the application of LCL-filter based converters, the structure and parameters of current-controller is very important for the system stability and output current quality. This paper presents a filter-capacitor current feedback control scheme for grid-connected converter. The controller...... is consisted of a proportional-resonance regulator and a proportional regulator. Unlike the existing control strategy with unit capacitor current feedback, the proposed method applies the proportional regulator to the feedback path, which can decouple these two regulators, and simplify the tuning process...... of the control strategy and the proposed current controller design method are verified by the simulation results of a 50kVA grid-connected inverter....
Modeling and Simulation for an 8 kW Three-Phase Grid-Connected Photo-Voltaic Power System
Directory of Open Access Journals (Sweden)
Cen Zhaohui
2017-09-01
Full Text Available Gird-connected Photo-Voltaic (PV systems rated as 5-10 kW level have advantages of scalability and energy-saving, so they are very typical for small-scale household solar applications. In this paper, an 8 kW three-phase grid-connected PV system model is proposed and studied. In this high-fidelity model, some basic PV system components such as solar panels, DC-DC converters, DC-AC inverters and three-phase utility grids are mathematically modelled and organized as a complete simulation model. Also, an overall power controller with Maximum Power Point Control (MPPT is proposed to achieve both high-efficiency for solar energy harvesting and grid-connection stability. Finally, simulation results demonstrate the effectiveness of the PV system model and the proposed controller, and power quality issues are discussed.
Evaluation of Harmonic Content from a Tap Transformer Based Grid Connection System for Wind Power
Directory of Open Access Journals (Sweden)
S. Apelfröjd
2013-01-01
Full Text Available Simulations done in MATLAB/Simulink together with experiments conducted at the Ångströms laboratory are used to evaluate and discuss the total harmonic distortion (THD and total demand distortion (TDD of a tap transformer based grid connection system. The grid connection topology can be used with different turbine and generator topologies and is here applied on a vertical axis wind turbine (VAWT with a permanent magnet synchronous generator (PMSG and its operational scheme. The full variable-speed wind conversion system consists of a diode rectifier, DC link, IGBT inverter, LCL-filter, and tap transformer. The full variable-speed operation is enabled by the use of the different step-up ratios of the tap transformer. In the laboratory study, a full experimental setup of the system was used, a clone of the on-site PMSG driven by a motor was used, and the grid was replaced with a resistive load. With a resistive load, grid harmonics and possible unbalances are removed. The results show a TDD and THD below 5% for the full operating range and harmonic values within the limits set up by IEEE-519. Furthermore, a change in tap, going to a lower step-up ratio, results in a reduction in both THD and TDD for the same output power.
New current control based MPPT technique for single stage grid connected PV systems
International Nuclear Information System (INIS)
Jain, Sachin; Agarwal, Vivek
2007-01-01
This paper presents a new maximum power point tracking algorithm based on current control for a single stage grid connected photovoltaic system. The main advantage of this algorithm comes from its ability to predict the approximate amplitude of the reference current waveform or power that can be derived from the PV array with the help of an intermediate variable β. A variable step size for the change in reference amplitude during initial tracking helps in fast tracking. It is observed that if the reference current amplitude is greater than the array capacity, the system gets unstable (i.e. moves into the positive slope region of the p-v characteristics of the array). The proposed algorithm prevents the PV system from entering the positive slope region of the p-v characteristics. It is also capable of restoring stability if the system goes unstable due to a sudden environmental change. The proposed algorithm has been tested on a new single stage grid connected PV configuration recently developed by the authors to feed sinusoidal current into the grid. The system is operated in a continuous conduction mode to realize advantages such as low device current stress, high efficiency and low EMI. A fast MPPT tracker with single stage inverter topology operating in CCM makes the overall system highly efficient. Specific cases of the system, operating in just discontinuous current mode and discontinuous current mode and their relative merits and demerits are also discussed
Directory of Open Access Journals (Sweden)
T. Ajith Bosco Raj
2014-01-01
Full Text Available The main objective of this work is to study the behaviour of the solar PV systems and model the efficient Grid-connected solar power system. The DC-DC MPPT circuit using chaotic pulse width modulation has been designed to track maximum power from solar PV module. The conversion efficiency of the proposed MPPT system is increased when CPWM is used as a control scheme. This paper also proposes a simplified multilevel (seven level inverter for a grid-connected photovoltaic system. The primary goal of these systems is to increase the energy injected to the grid by keeping track of the maximum power point of the panel, by reducing the switching frequency, and by providing high reliability. The maximum power has been tracked experimentally. It is compared with parallel boost converter. Also this model is based on mathematical equations and is described through an equivalent circuit including a PV source with MPPT, a diode, a series resistor, a shunt resistor, and dual boost converter with active snubber circuit. This model can extract PV power and boost by using dual boost converter with active snubber. By using this method the overall system efficiency is improved thereby reducing the switching losses and cost.
International Nuclear Information System (INIS)
Khatib, Tamer; Sopian, Kamaruzzaman; Kazem, Hussein A.
2013-01-01
Highlights: • We analyzed an actual performance of grid connected PV system. • We derived accurate models for the system based on the actual performance. • We assist the electricity productively of the proposed system. - Abstract: This paper presents a field operation experience for a grid connected PV system under tropical climate. The system is consisted of a 5 kWp photovoltaic (PV) array and a 6 kW DC/AC inverter. The operation performance data are recorded in order to develop accurate mathematical models for the system as well as to evaluate the productivity of the system. The experiment results show that, the average PV performance (the ratio of the theoretical performance to the actual performance) is 73.12% while the average inverter performance (the ratio of the theoretical inverter efficiency to the actual inverter efficiency) is 98.56%. Moreover, it is found that the daily yield factor of the PV system is 2.51 kW h/kWp day while, the capacity factor is 10.47%. However, it is concluded that the productivity of the system is below the prospected rate and thus, an inspection of the system must be done in order to diagnose the problem of the system’s low productivity. This paper presents worthwhile information for those who are interested in PV system installation in Malaysia and nearby country
new topology for single-phase, three-level, spwm vsi with lc filter
African Journals Online (AJOL)
level PWM inverter. However, this is not the case with single-phase PWM inverters. In these days, the popular single-phase inverters adopt the full-bridge type using approximate sinusoidal modulation technique. The output voltage in them has two values: zero and pos- itive supply dc voltage levels in the positive half cycle.
Grid-Connected Distributed Generation: Compensation Mechanism Basics
Energy Technology Data Exchange (ETDEWEB)
Aznar, Alexandra Y [National Renewable Energy Laboratory (NREL), Golden, CO (United States);
2017-10-02
This short report defines compensation mechanisms for grid-connected, behind-the-meter distributed generation (DG) systems as instruments that comprise three core elements: (1) metering and billing arrangements, (2) sell rate design, and (3) retail rate design. This report describes metering and billing arrangements, with some limited discussion of sell rate design. We detail the three possible arrangements for metering and billing of DG: net energy metering (NEM); buy all, sell all; and net billing.
Global distribution of grid connected electrical energy storage systems
Directory of Open Access Journals (Sweden)
Katja Buss
2016-06-01
Full Text Available This article gives an overview of grid connected electrical energy storage systems worldwide, based on public available data. Technologies considered in this study are pumped hydroelectric energy storage (PHES, compressed air energy storage (CAES, sodium-sulfur batteries (NaS, lead-acid batteries, redox-flow batteries, nickel-cadmium batteries (NiCd and lithium-ion batteries. As the research indicates, the worldwide installed capacity of grid connected electrical energy storage systems is approximately 154 GW. This corresponds to a share of 5.5 % of the worldwide installed generation capacity. Furthermore, the article gives an overview of the historical development of installed and used storage systems worldwide. Subsequently, the focus is on each considered technology concerning the current storage size, number of plants and location. In summary it can be stated, PHES is the most commonly used technology worldwide, whereas electrochemical technologies are increasingly gaining in importance. Regarding the distribution of grid connected storage systems reveals the share of installed storage capacity is in Europe and Eastern Asia twice as high as in North America.
The German experience with grid-connected PV-systems
International Nuclear Information System (INIS)
Erge, T.; Hoffmann, V.U.; Kiefer, K.
2001-01-01
Grid-connected photovoltaics experienced increasing attention in Germany in recent years and are expected to face a major boost at the beginning of the new millennium. Highlights like the German 100,000-Roofs-Solar-Programme, PV programmes at schools financed by utilities and governments (e.g. 'SONNEonline' by PreussenElektra, 'Sonne in der Schule' by BMWi and 'Sonne in der Schule' by Bayernwerk) and large centralised installations of MW size ('Neue Messe Munchen' by Bayernwerk and 'Energiepark Mont-Cenis' by state Nordrhein-Westfalen, Stadtwerke Herne and European Union) count for the potential of grid-connected PV. Today in Germany a typical grid-connected PV installation of 1 kW nominal power produces average annual energy yields of 700 kWh (dependent on location and system components) and shows a high operating availability. The price per kWh from PV installations is still significantly higher than the price for conventional energy, but new funding schemes and cost models (like the large increase of feed-in tariff in Germany due to the Act on Granting Priority to Renewable Energy Sources in 2000) give optimism about the future. (Author)
Modelling and Simulation of Grid Connected SPV System with Active Power Filtering Features
Saroha, Jaipal; Pandove, Gitanjali; Singh, Mukhtiar
2017-09-01
In this paper, the detailed simulation studies for a grid connected solar photovoltaic system (SPV) have been presented. The power electronics devices like DC-DC boost converter and grid interfacing inverter are most important components of proposed system. Here, the DC-DC boost converter is controlled to extract maximum power out of SPV under different irradiation levels, while the grid interfacing inverter is utilized to evacuate the active power and feed it into grid at synchronized voltage and frequency. Moreover, the grid interfacing inverter is also controlled to sort out the issues related to power quality by compensating the reactive power and harmonics current component of nearby load at point of common coupling. Besides, detailed modeling of various component utilized in proposed system is also presented. Finally, extensive simulations have been performed under different irradiation levels with various kinds of load to validate the aforementioned claims. The overall system design and simulation have been performed by using Sim Power System toolbox available in the library of MATLAB.
Performance evaluation of 10 MW grid connected solar photovoltaic power plant in India
B. Shiva Kumar; K. Sudhakar
2015-01-01
The growing energy demand in developing nations has triggered the issue of energy security. This has made essential to utilize the untapped potential of renewable resources. Grid connected PV systems have become the best alternatives in renewable energy at large scale. Performance analysis of these grid connected plants could help in designing, operating and maintenance of new grid connected systems. A 10 MW photovoltaic grid connected power plant commissioned at Ramagundam is one of the larg...
Transient stability with grid connection and wind turbine drive-train effects
DEFF Research Database (Denmark)
Fajardo-R, Luis A.; Medina, Aurelio; Iov, Florin
2009-01-01
This paper assesses transient stability of grid-connected wind turbines, combining grid-connection, wind turbine flexibility, and induction generator stability features. Through a grid-connected 2 MW wind turbine cage-generator, the investigation is conducted to identify the critical clearing time...
Grid-connected photovoltaic power systems. Technical and potential problems. A review
International Nuclear Information System (INIS)
Eltawil, Mohamed A.; Zhao, Zhengming
2010-01-01
Traditional electric power systems are designed in large part to utilize large baseload power plants, with limited ability to rapidly ramp output or reduce output below a certain level. The increase in demand variability created by intermittent sources such as photovoltaic (PV) presents new challenges to increase system flexibility. This paper aims to investigate and emphasize the importance of the grid-connected PV system regarding the intermittent nature of renewable generation, and the characterization of PV generation with regard to grid code compliance. The investigation was conducted to critically review the literature on expected potential problems associated with high penetration levels and islanding prevention methods of grid tied PV. According to the survey, PV grid connection inverters have fairly good performance. They have high conversion efficiency and power factor exceeding 90% for wide operating range, while maintaining current harmonics THD less than 5%. Numerous large-scale projects are currently being commissioned, with more planned for the near future. Prices of both PV and balance of system components (BOS) are decreasing which will lead to further increase in use. The technical requirements from the utility power system side need to be satisfied to ensure the safety of the PV installer and the reliability of the utility grid. Identifying the technical requirements for grid interconnection and solving the interconnect problems such as islanding detection, harmonic distortion requirements and electromagnetic interference are therefore very important issues for widespread application of PV systems. The control circuit also provides sufficient control and protection functions like maximum power tracking, inverter current control and power factor control. Reliability, life span and maintenance needs should be certified through the long-term operation of PV system. Further reduction of cost, size and weight is required for more utilization of PV
Energy Technology Data Exchange (ETDEWEB)
Kim, Jong-Soo; Choe, Gyu-Yeong; Lee, Byoung-Kuk [School of Information and Communication Engineering, Sungkyunkwan University, 300 Cheoncheon-dong, Jangan-gu, Suwon, Gyeonggi-do 440-746 (Korea, Republic of); Kang, Hyun-Soo [R and D Center, Advanced Drive Technology (ADT) Company, 689-26 Geumjeong-dong, Gunpo-si, Gyeonggi-do 435-862 (Korea, Republic of)
2011-05-15
The low frequency current ripple in grid-connected fuel cell systems is generated from dc-ac inverter operation, which generates 60 Hz fundamental component, and gives harmful effects on fuel cell stack itself, such as making cathode surface responses slower, causing an increase of more than 10% in the fuel consumption, creating oxygen starvation, causing a reduction in the operating lifetime, and incurring a nuisance tripping such as overload situation. With these reasons, low frequency current ripple makes fuel cell system unstable and lifetime of fuel cell stack itself short. This paper presents a fast and robust control algorithm to eliminate low frequency current ripple in grid-connected fuel cell systems. Compared with the conventional methods, in the proposed control algorithm, dc link voltage controller is shifted from dc-dc converter to dc-ac inverter, resulting that dc-ac inverter handles dc link voltage control and output current control simultaneously with help of power balancing technique. The results indicate that the proposed algorithm can not only completely eliminate current ripple but also significantly reduce the overshoot or undershoot during transient states without any extra hardware. The validity of the proposed algorithm is verified by computer simulations and also by experiments with a 1 kW laboratory prototype. (author)
Modeling and Simulation for an 8 kW Three-Phase Grid-Connected Photo-Voltaic Power System
Cen Zhaohui
2017-01-01
Gird-connected Photo-Voltaic (PV) systems rated as 5-10 kW level have advantages of scalability and energy-saving, so they are very typical for small-scale household solar applications. In this paper, an 8 kW three-phase grid-connected PV system model is proposed and studied. In this high-fidelity model, some basic PV system components such as solar panels, DC-DC converters, DC-AC inverters and three-phase utility grids are mathematically modelled and organized as a complete simulation model....
A New Green Power Inverter for Fuel Cells
DEFF Research Database (Denmark)
Andersen, Gert Karmisholt; Klumpner, Christian; Kjær, Søren Bækhøj
2002-01-01
This paper presents a new grid connected inverter for fuel cells. It consists of a two stage power conversion topology. Since the fuel cell operates with a low voltage in a wide voltage range (25 V-45 V) this volt- age must be transformed to around 350-400 V in order to invert this dc power into ac...... power to the grid. The proposed converter consists of an isolated dc-dc converter cascaded with a single phase H-bridge inverter. The dc-dc converter is a current-fed push-pull converter. A new dedicated voltage mode startup procedure has been developed in order to limit the inrush current during...... startup. The inverter is controlled as a power factor controller with resistor emulation.Experimental results of converter efficiency, grid performance and fuel cell response are shown for a 1 kW prototype. The proposed converter exhibits a high efficiency in a wide power range (higher than 92...
experimental implementation of single-phase, three-level, sinusoidal
African Journals Online (AJOL)
Page 1 ... of many multilevel inverter configurations. This paper presents an experimental report of a simplified topology for single-phase, SPWM, three-level voltage source inverter wit R-L load. To keep the power circuit ... employed in many industrial applications such as variable speed drives, uninterruptible power sup-.
International Nuclear Information System (INIS)
Trillo-Montero, D.; Santiago, I.; Luna-Rodriguez, J.J.; Real-Calvo, R.
2014-01-01
Highlights: • Software application to perform an automated analysis of grid-connected PV systems. • It integrates data from all devices registering data on typical PV installations. • Flexible to analyze installations with different configurations and components. • An analysis of two grid-connected PV systems located in Andalusia, was performed. • Temperature losses in summer months varying between 15% and 25% of energy production. - Abstract: The aim of this paper was to design and develop a software application that enables users to perform an automated analysis of data from the monitoring of grid-connected photovoltaic (PV) systems. This application integrates data from all devices already in operation such as environmental sensors, inverters and meters, which record information on typical PV installations. This required the development of a Relational Database Management System (RDBMS), consisting of a series of linked databases, enabling all PV system information to be stored; and a software, called S·lar, which enables all information from the monitoring to be automatically migrated to the database as well as determining some standard magnitudes related to performances and losses of PV installation components at different time scales. A visualization tool, which is both graphical and numerical, makes access to all of the information be a simple task. Moreover, the application enables relationships between parameters and/or magnitudes to be easily established. Furthermore, it can perform a preliminary analysis of the influence of PV installations on the distribution grids where the produced electricity is injected. The operation of such a software application was implemented by performing the analysis of two grid-connected PV installations located in Andalusia, Spain, via data monitoring therein. The monitoring took place from January 2011 to May 2012
Costs of the grid connection of wind turbines
International Nuclear Information System (INIS)
Siden, G.
1995-01-01
The costs of the grid connection of wind turbines in Sweden have until now been about 5 % of the total investments, provided that the distance of the connection cable is limited. Now the grid will soon be filled locally and it will be necessary to strengthen it. The costs for this can also be about 5 %, and the total cost about 10 %. Improvements in the electrical systems of the wind turbines and the connection technique can give less disturbance in the grid and diminish the costs. It is important to agree on how to share the costs for strengthening the grid. Otherwise, it can become an obstacle when building new wind turbines. (author)
Costs of the grid connection of wind turbines
Energy Technology Data Exchange (ETDEWEB)
Siden, G [Halmstad Univ. (Sweden)
1996-12-31
The costs of the grid connection of wind turbines in Sweden have until now been about 5 % of the total investments, provided that the distance of the connection cable is limited. Now the grid will soon be filled locally and it will be necessary to strengthen it. The costs for this can also be about 5 %, and the total cost about 10 %. Improvements in the electrical systems of the wind turbines and the connection technique can give less disturbance in the grid and diminish the costs. It is important to agree on how to share the costs for strengthening the grid. Otherwise, it can become an obstacle when building new wind turbines. (author)
Costs of the grid connection of wind turbines
Energy Technology Data Exchange (ETDEWEB)
Siden, G. [Halmstad Univ. (Sweden)
1995-12-31
The costs of the grid connection of wind turbines in Sweden have until now been about 5 % of the total investments, provided that the distance of the connection cable is limited. Now the grid will soon be filled locally and it will be necessary to strengthen it. The costs for this can also be about 5 %, and the total cost about 10 %. Improvements in the electrical systems of the wind turbines and the connection technique can give less disturbance in the grid and diminish the costs. It is important to agree on how to share the costs for strengthening the grid. Otherwise, it can become an obstacle when building new wind turbines. (author)
Performance Parameters for Grid-Connected PV Systems
Energy Technology Data Exchange (ETDEWEB)
Marion, B.; Adelstein, J.; Boyle, K.; Hayden, H.; Hammond, B.; Fletcher, T.; Canada, B.; Narang, D.; Shugar, D.; Wenger, H.; Kimber, A.; Mitchell, L.; Rich, G.; Townsend, T.
2005-02-01
The use of appropriate performance parameters facilitates the comparison of grid-connected photovoltaic (PV) systems that may differ with respect to design, technology, or geographic location. Four performance parameters that define the overall system performance with respect to the energy production, solar resource, and overall effect of system losses are the following: final PV system yield, reference yield, performance ratio, and PVUSA rating. These performance parameters are discussed for their suitability in providing desired information for PV system design and performance evaluation and are demonstrated for a variety of technologies, designs, and geographic locations. Also discussed are methodologies for determining system a.c. power ratings in the design phase using multipliers developed from measured performance parameters.The use of appropriate performance parameters facilitates the comparison of grid-connected photovoltaic (PV) systems that may differ with respect to design, technology, or geographic location. Four performance parameters that define the overall system performance with respect to the energy production, solar resource, and overall effect of system losses are the following: final PV system yield, reference yield, performance ratio, and PVUSA rating. These performance parameters are discussed for their suitability in providing desired information for PV system design and performance evaluation and are demonstrated for a variety of technologies, designs, and geographic locations. Also discussed are methodologies for determining system a.c. power ratings in the design phase using multipliers developed from measured performance parameters.
Lightning Surge Analysis on a Large Scale Grid-Connected Solar Photovoltaic System
Directory of Open Access Journals (Sweden)
Nur Hazirah Zaini
2017-12-01
Full Text Available Solar photovoltaic (PV farms currently play a vital role in the generation of electrical power in different countries, such as Malaysia, which is moving toward the use of renewable energy. Malaysia is one of the countries with abundant sunlight and thus can use solar PV farms as alternative sources for electricity generation. However, lightning strikes frequently occur in the country. Being installed in open and flat areas, solar PV farms, especially their electronic components, are at great risk of damage caused by lightning. In this paper, the effects of lightning currents with different peak currents and waveshapes on grid-connected solar PV farms were determined to approximate the level of transient effect that can damage solar PV modules, inverters and transformers. Depending on the location of the solar PV farm, engineer can obtain information on the peak current and median current of the site from the lightning location system (LLS and utilise the results obtained in this study to appropriately assign an SPD to protect the solar panel, inverter and the main panel that connected to the grid. Therefore, the simulation results serve as the basis for controlling the effects of lightning strikes on electrical equipment and power grids where it provides proper justification on the ‘where to be installed’ and ‘what is the rating’ of the SPD. This judgment and decision will surely reduce the expensive cost of repair and replacement of electrical equipment damages due to the lightning.
Energy Technology Data Exchange (ETDEWEB)
Xue Yijing [Vestas China, Beijing (China); Akhmatov, Vladislav [Technical Univ. of Denmark, Lyngby (Denmark). Centre for Electric Technology
2009-07-01
Utilization of Voltage Source Converter (VSC) - High Voltage Direct Current (HVDC) systems for grid-connection of large offshore windfarms becomes relevant as installed power capacities as well as distances to the connection points of on-land transmission systems increase. At the same time, the grid code requirements of the Transmission System Operators (TSO), including ancillary system services and Low-Voltage Fault-Ride-Through (LVFRT) capability of large offshore windfarms, become more demanding. This paper presents a general-level model of and a LVFRT solution for a VSC-HVDC system for grid-connection of large offshore windfarms. The VSC-HVDC model is implemented using a general approach of independent control of active and reactive power in normal operations. The on-land VSC inverter, i.e. a grid-side inverter, provides voltage support to the transmission system and comprises a LVFRT solution in short-circuit faults. The presented model, LVFRT solution and impact on the system stability are investigated as a case study of a 1,000 MW offshore windfarm grid-connected through a VSC-HVDC system. The investigation is carried out on a model of the west Danish, with some elements of the north German, 400 kV, 220 kV and 150 kV transmission systems stage 2005-2006 using the DIgSILENT PowerFactory simulation program. In the investigation, a thermal power plant just south to the Danish border has been substituted by this 1,000 MW offshore windfarm utilizing the VSC-HVDC system. The investigation has shown that the substitution of a thermal power plant by a VSC-HVDC connected offshore windfarm should not have any negative impact on the short-term stability of the west Danish transmission system. The investigation should be repeated applying updated system model stages and offshore wind power commissioning schedules in the North and Baltic Seas. (orig.)
Performance analysis of a 11.2 kWp roof top grid-connected PV system in Eastern India
Directory of Open Access Journals (Sweden)
Renu Sharma
2017-11-01
Full Text Available Barren land and roof tops of buildings are being increasingly used worldwide to install solar panels for generating electricity. One such step has been taken by Siksha ‘O’Anusandhan University, Bhubaneswar (Latitude 20.24° N and Longitude 80.85° E by installing a 11.2 kWp grid connected solar power system during February, 2014. This PV system is tilted at an angle of 21° on the top floor of a 25 metre height building. This system was installed This paper presents the results of this grid connected photovoltaic system which was monitored between September 2014 to August 2015. The entire electricity generated by the system was fed into the state grid. The different parameters of the system studied include PV module efficiency, array yield, final yield, inverter efficiency and performance ratio of the system. The total energy generated during this period was found to be 14.960 MWh and the PV module efficiency, inverter efficiency and performance ratio were found to be 13.42%, 89.83% and 0.78 respectively.
Low-voltage ride-through of a droop-based three-phase four-wire grid-connected microgrid
DEFF Research Database (Denmark)
Sadeghkhani, Iman; Golshan, Mohamad Esmail Hamedani; Mehrizi-Sani, Ali
2018-01-01
system operations during abnormal grid conditions. The objective of this paper is to propose an LVRT scheme that improves the power quality of the entire microgrid. The developed method is implemented as the controller of the interface voltage-sourced converter (VSC) of a distributed energy resource...... control of each phase and does not require calculation of symmetrical components. Moreover, it can be employed in the VSC control systems with various reference frames and is effective for droop-based grid-connected microgrids with both single-phase and three-phase four-wire configurations. The proposed......The ability of riding through the grid disturbances can increase the integration of microgrids into the distribution system. Consequently, a grid-connected microgrid should provide ancillary services such as low voltage ride-through (LVRT) capability and reactive power support to sustain the power...
Performance Analysis of 14 MW Grid-Connected Photovoltaic System
International Nuclear Information System (INIS)
Kagilik, Ahmed S.; Tawel, Abduraouf M.
2015-01-01
Many Libyan authorities proposed to investigate the possibility of utilizing a suitable terrain in Libya to add generation capacity of large-scale photovoltaic power plants. In this paper, the first grid-connected PV plant of 14 MWp which will be executed in Hoon city and supported by the Renewable Energy Authority of Libya (REAOL) is presented. To understand and improve the operational behavior of PV system, a comprehensive study including the plant design and detailed performance analysis under a local climate conditions is performed. Using polycrystalline silicon technology, the first year energy yield is estimated and the monthly system output for this plant is calculated. The performance ratio and various power losses (temperature, irradiance, power electronics, interconnection, etc.) are determined. The PV system supplied 24964 MWh to the grid during the first year giving an average annual overall yield factor 1783 kWh/kWp and average annual performance ratio of the system of 76.9%.(author)
Prospects for investment in large-scale, grid-connected solar power in Africa
DEFF Research Database (Denmark)
Hansen, Ulrich Elmer; Nygaard, Ivan; Pedersen, Mathilde Brix
since the 1990s have changed the competiveness of solar PV in all markets, ranging from individual households via institutions to mini-grids and grid-connected installations. In volume and investment, the market for large-scale grid-connected solar power plants is by far the most important......-scale investments in grid-connected solar power plants and local assembly facilities for PV panels, have exceeded even optimistic scenarios. Finally, therefore, there seem to be bright prospects for investment in large-scale grid-connected solar power in Africa....
Phase-lock loop of Grid-connected Voltage Source Converter under non-ideal grid condition
DEFF Research Database (Denmark)
Wang, Haojie; Sun, Hai; Han, Minxiao
2015-01-01
It is a normal practice that the DC micro-grid is connected to AC main grid through Grid-connected Voltage Source Converter (G-VSC) for voltage support. Accurate control of DC micro-grid voltage is difficult for G-VSC under unbalanced grid condition as the fundamental positive-sequence component...... and distorted system voltage the proposed PLL can accurately detect the fundamental positive-sequence component of grid voltage thus accurate control of DC micro-grid voltage can be realized....... phase information cannot be accurately tracked. Based on analysis of the cause of double-frequency ripple when unbalance exists in main grid, a phase-locked loop (PLL) detection technique is proposed. Under the conditions of unsymmetrical system voltage, varying system frequency, single-phase system...
Directory of Open Access Journals (Sweden)
S.Z.Mohammad Noor
2016-06-01
Full Text Available This paper presents an implementation of Single-phase Single stage String inverter for Grid connected Photovoltaic (PV system. The proposed system uses Modified Perturb and Observe (P&O algorithm implemented using Fuzzy Logic Control (FLC as Maximum Power Point Tracking (MPPT. The inverter is designed for 340W system using two series of STP170s24/Ac PV modules. The MPPT unit keeps tracking the maximum power from the PV array by changing the modulation index and the phase angle of inverter’s output voltage. The simulation model is developed using Matlab/Simulink to evaluate the performance of the converter. Selected experimental results are also presented in this paper.
Performance analysis and investigation of a grid-connected photovoltaic installation in Morocco
Directory of Open Access Journals (Sweden)
Kamal Attari
2016-11-01
Full Text Available The paper present an evaluation of a grid-connected photovoltaic (PV system installed on the roof of a government building located in Tangier, Morocco. The experimental data was recorded from 1st January 2015 to December 2015 based on real time observation. The aim is to encourage the use of solar PV system for government, commercial and residence building in Morocco based on the obtained results. The system is made up of 20 modules of 250 Wp and one inverter of 5 kW. The assessed parameters of the PV installation includes energy output, final yield, modules temperature, efficiency module, performance ratio (PR and others. The PV park supplied the grid with 6411.3 kWh during the year 2015. The final yield (Yf ranged from 1.96 to 6.42 kWh/kWp, the performance ratio (PR ranged from 58% to 98% and the annual capacity factor was found to be 14.84%. The final yield of PV installation is compared with other final yields of solar PV systems located at other places. Finally various power losses are given through a diagram loss.
Directory of Open Access Journals (Sweden)
SINGH Alka
2012-10-01
Full Text Available Use of distributed resources is growing in developing countries like India and in developed nations too. The increased acceptance of suchresources is mainly due to their modularity, increased reliability, good power quality and environment friendly operation. These are currently being interfaced to the existing systems using voltage source inverters (VSC’s. The control of such distributed resources is significantly different than the conventional power systems mainly because the VSC’s have no inertia unlike the synchronous generators.This paper deals with the Matlab modeling and design of control aspects of one such distributed source feeding a common load. A grid connected supply is also available. The control algorithm is developed for real and reactive power sharing of the load between thedistributed source and the grid. The developed control scheme is tested for linear (R-L load as well as nonlinear loads. With suitable modifications, the control algorithm can be extended for several distributed resources connected in parallel.
ASEAN grid-connected biomass residues fired cogeneration plants
International Nuclear Information System (INIS)
Adnan, M.F.; Alias, R.
2006-01-01
Energy supply is one of the major concerns in the world. With uncertainty in the main oil suppliers, the oil price is expected to remain high due to continuous demand from the world. Since oil is mostly used for electricity and transportation, its shortage would cause major disruptions in our daily activities. Thus to counter this scenario and faster depletion of fossil fuel resources, various measures have been taken to find alternative source of energy such as renewable energy. One of the renewable energy sources is from biomass residues which is aplenty particularly in ASEAN. Through one of the collaboration programme between ASEAN and EC which is The EC-ASEAN Cogeneration Programme, a number of Full-Scale Demonstration Projects (FSDP) using biomass residues have been commissioned and implemented successfully. Four of the FSDPs in Thailand and Malaysia are connected to the grid. These projects have been operating very well and since the fuel is commonly available in this ASEAN region, duplication should not be a problem. Thus, this paper would highlight the success stories in implementing biomass residues grid connected project while enhancing cooperation between ASEAN and EC. (Author)
A Grid Connected Photovoltaic Inverter with Battery-Supercapacitor Hybrid Energy Storage.
Miñambres-Marcos, Víctor Manuel; Guerrero-Martínez, Miguel Ángel; Barrero-González, Fermín; Milanés-Montero, María Isabel
2017-08-11
The power generation from renewable power sources is variable in nature, and may contain unacceptable fluctuations, which can be alleviated by using energy storage systems. However, the cost of batteries and their limited lifetime are serious disadvantages. To solve these problems, an improvement consisting in the collaborative association of batteries and supercapacitors has been studied. Nevertheless, these studies don't address in detail the case of residential and large-scale photovoltaic systems. In this paper, a selected combined topology and a new control scheme are proposed to control the power sharing between batteries and supercapacitors. Also, a method for sizing the energy storage system together with the hybrid distribution based on the photovoltaic power curves is introduced. This innovative contribution not only reduces the stress levels on the battery, and hence increases its life span, but also provides constant power injection to the grid during a defined time interval. The proposed scheme is validated through detailed simulation and experimental tests.
Leakage Current Suppression with A Novel Six-Switch Photovoltaic Grid-Connected Inverter
DEFF Research Database (Denmark)
Wei, Baoze; Guo, Xiaoqiang; Guerrero, Josep M.
2015-01-01
In order to solve the problem of the leakage current in non-isolated photovoltaic (PV) systems, a novel six-switch topology and control strategy are proposed in this paper. The inductor-bypass strategy solves the common-mode voltage limitation of the conventional six-switch topology in case...... of unmatched inductances. And the stray capacitor voltage of the non-isolated photovoltaic system is free of high frequency ripples. Theoretical analysis and simulation are carried out to verify the proposed topology and its control strategy. Results indicate that the leakage current suppression can...
New control strategy for grid connecting of wind turbine inverter without converter reactor
DEFF Research Database (Denmark)
Rasmussen, Tonny Wederberg; Sørensen, Kasper B.; Bjørneboe, Daniel
2013-01-01
Wind turbines and the belonging converters increase in size and price. A reduction in the number of main components is desirable while it reduces need of space, investments and increases the efficiency. A wind turbine contains both a converter reactor and a step up transformer. The paper presents...... theory and laboratory measurements for a new control strategy which make it possibly to connect a wind turbine converter to the utility grid without using the converter reactor or make measurements at the high voltage side of the transformer. The capability to control the DC voltage and reactive power...
Research on control strategy based on fuzzy PR for grid-connected inverter
Zhang, Qian; Guan, Weiguo; Miao, Wen
2018-04-01
In the traditional PI controller, there is static error in tracking ac signals. To solve the problem, the control strategy of a fuzzy PR and the grid voltage feed-forward is proposed. The fuzzy PR controller is to eliminate the static error of the system. It also adjusts parameters of PR controller in real time, which avoids the defect of fixed parameter fixed. The grid voltage feed-forward control can ensure the quality of current and improve the system's anti-interference ability when the grid voltage is distorted. Finally, the simulation results show that the system can output grid current with good quality and also has good dynamic and steady state performance.
Leakage Current Suppression with A Novel Six-Switch Photovoltaic Grid-Connected Inverter
Wei, Baoze; Guo, Xiaoqiang; Guerrero, Josep M.; Savaghebi, Mehdi
2015-01-01
In order to solve the problem of the leakage current in non-isolated photovoltaic (PV) systems, a novel six-switch topology and control strategy are proposed in this paper. The inductor-bypass strategy solves the common-mode voltage limitation of the conventional six-switch topology in case of unmatched inductances. And the stray capacitor voltage of the non-isolated photovoltaic system is free of high frequency ripples. Theoretical analysis and simulation are carried out to verify the propos...
On-line grid impedance estimation based on harmonic injection for grid-connected PV inverter
DEFF Research Database (Denmark)
Ciobotaru, Mihai; Teodorescu, Remus; Blaabjerg, Frede
2007-01-01
two different signal processing algorithms. The DFT technique is used for the single harmonic injection and the statistic technique is used for the double harmonic injection. The grid impedance estimation is used for compliance with the anti-islanding requirements of the German standard (VDE0126...
A Grid Connected Photovoltaic Inverter with Battery-Supercapacitor Hybrid Energy Storage
Guerrero-Martínez, Miguel Ángel; Barrero-González, Fermín
2017-01-01
The power generation from renewable power sources is variable in nature, and may contain unacceptable fluctuations, which can be alleviated by using energy storage systems. However, the cost of batteries and their limited lifetime are serious disadvantages. To solve these problems, an improvement consisting in the collaborative association of batteries and supercapacitors has been studied. Nevertheless, these studies don’t address in detail the case of residential and large-scale photovoltaic systems. In this paper, a selected combined topology and a new control scheme are proposed to control the power sharing between batteries and supercapacitors. Also, a method for sizing the energy storage system together with the hybrid distribution based on the photovoltaic power curves is introduced. This innovative contribution not only reduces the stress levels on the battery, and hence increases its life span, but also provides constant power injection to the grid during a defined time interval. The proposed scheme is validated through detailed simulation and experimental tests. PMID:28800102
Grid Voltage Modulated Direct Power Control for Grid Connected Voltage Source Inverters
DEFF Research Database (Denmark)
Gui, Yonghao; Kim, Chunghun; Chung, Chung Choo
2017-01-01
-loop system is exponentially stable in the whole operating range. The proposed method is verified by using MATLAB/Simulink with PLECS blockset. The simulation results show that the proposed method has not only good tracking performances in both active and reactive powers but also a lower current total...
A simple output voltage control scheme for single phase wavelet ...
African Journals Online (AJOL)
DR OKE
of the wavelet modulated (WM) scheme is that a single synthesis function, derived ... a single-phase H-bridge voltage-source (VS) inverter using MATLAB simulations. ... reconstruction process has been suggested to device a new class of ...
International Nuclear Information System (INIS)
Sundaram, Sivasankari; Babu, Jakka Sarat Chandra
2015-01-01
Highlights: • A real time performance analysis with validation of the system is carried out for 5 MW p plant. • Dependence or interactions of input factors over performance responses are identified. • The topology of the PV system and the inverter technology is suggested for improved realization. • The average PV module, inverter and system efficiency are found to be 6.08%, 88.2% and 5.08%. • Average energy and exergy efficiency of the system is found to be 6.08% and 3.54%. - Abstract: The main objective of this paper is to present the validated annual performance analysis with the monitored results from a 5 MW p grid connected photovoltaic plant located in India at Sivagangai district in Tamilnadu. The total annual energy generated was 8495296.4 kW h which averages around 707941.4 kW h/month. In addition to the above, real time performance of the plant is validated through system software called RETscreen plus which employs regression analysis for validation. The measured annual average energy generated by the 5 MW p system is 24116.61 kW h/day which is appropriately close to the predicted annual average which was found to be 24055.25 kW h/day by RETscreen. The predicted responses are further justified by the value of statistical indicators such as mean bias error, root mean square error and mean percentage error. The annual average daily array yield, corrected reference yield, final yield, module efficiency, inverter efficiency and system efficiency were found to be 5.46 h/day, 5.128 h/day 4.810 h/day, 6.08%, 88.20% and 5.08% respectively. The overall absolute average daily capture loss and system loss of the particular system under study is 0.384 h/day and 0.65 h/day respectively. A comparison is also made between the performance indices of solar photovoltaic system situated at other locations from the literature’s published. Furthermore the effect of input factors over the output of the system is emphasized by regression coefficients obtained
Policy incentives and grid-connected photovoltaics system development in China
Energy Technology Data Exchange (ETDEWEB)
Wang Jing; Xu Yugao
2007-07-01
China has made considerable progress in solar PV generation technology. However, compared with conventional generation technologies or even other renewables such as wind and biomass, grid-connected PV technology is in its early stage and has not reached an adequate level of economic performance. Therefore, policy incentives will play important roles in attracting more social investments to facilitate the development of grid-connected PV generation. This paper is focused on analyzing the role of incentive policies in enhancing the market competitiveness of grid-connected solar PV systems in the context of China with an economic model and some policy suggestions are given based on simulation modeling efforts. (auth)
Optimal system sizing in grid-connected photovoltaic applications
Simoens, H. M.; Baert, D. H.; de Mey, G.
A costs/benefits analysis for optimizing the combination of photovoltaic (PV) panels, batteries and an inverter for grid interconnected systems at a 500 W/day Belgian residence is presented. It is assumed that some power purchases from the grid will always be necessary, and that excess PV power can be fed into the grid. A minimal value for the cost divided by the performance is defined for economic optimization. Shortages and excesses are calculated for PV panels of 0.5-10 kWp output, with consideration given to the advantages of a battery back-up. The minimal economic value is found to increase with the magnitude of PV output, and an inverter should never be rated at more than half the array maximum output. A maximum panel size for the Belgian residence is projected to be 6 kWp.
A controller design method for 3 phase 4 wire grid connected VSI ...
Indian Academy of Sciences (India)
and grid connected VSI with LCL filter is a higher order system. ... as LCL filter is used as an interface between VSI and electric grid to meet ... chronous reference frame (SRF) theory where independent control of active and reactive power.
Establishment of key grid-connected performance index system for integrated PV-ES system
Li, Q.; Yuan, X. D.; Qi, Q.; Liu, H. M.
2016-08-01
In order to further promote integrated optimization operation of distributed new energy/ energy storage/ active load, this paper studies the integrated photovoltaic-energy storage (PV-ES) system which is connected with the distribution network, and analyzes typical structure and configuration selection for integrated PV-ES generation system. By combining practical grid- connected characteristics requirements and technology standard specification of photovoltaic generation system, this paper takes full account of energy storage system, and then proposes several new grid-connected performance indexes such as paralleled current sharing characteristic, parallel response consistency, adjusting characteristic, virtual moment of inertia characteristic, on- grid/off-grid switch characteristic, and so on. A comprehensive and feasible grid-connected performance index system is then established to support grid-connected performance testing on integrated PV-ES system.
Power Quality of Grid-Connected Wind Turbines with DFIG and Their Interaction with the Grid
DEFF Research Database (Denmark)
Sun, Tao
quality issues of grid-connected wind turbines and the interaction between wind turbines and the grid. The specific goal of the research has been to investigate flicker emission and mitigation of grid-connected wind turbines with doubly fed induction generators (DFIG) during continuous operation...... measures are proposed to mitigate the flicker levels produced by grid-connected wind turbines with DFIG, respectively by wind turbine output reactive power control and using STATCOM. Simulation results demonstrate that these two measures are effective for flicker mitigation regardless of mean wind speed....... To evaluate the flicker levels produced by grid-connected wind turbines with DFIG, a flickermeter model is developed according to the IEC standard IEC 61000-4-15, which simulates the response of the lamp-eye-brain chain and provides on-line statistical analysis ofthe flicker signal and the final results...
Fundamentals of Grid Connected Photo-Voltaic Power Electronic Converter Design
Evju, Svein Erik
2007-01-01
In this master thesis the basic theory of grid connected photo-voltaic systems is explained, giving an introduction to the different aspects of system design. Starting with a look at the standards concerning grid connection of distributed resources, and working its way through how the photo-voltaic cells work, to how photo-voltaic modules with electrical converters can be arranged. Some different converter topologies suitable for use with photo-voltaics are found, and based on these topologie...
A Sensorless Power Reserve Control Strategy for Two-Stage Grid-Connected PV Systems
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2017-01-01
Due to the still increasing penetration of grid-connected Photovoltaic (PV) systems, advanced active power control functionalities have been introduced in grid regulations. A power reserve control, where namely the active power from the PV panels is reserved during operation, is required for grid support. In this paper, a cost-effective solution to realize the power reserve for two-stage grid-connected PV systems is proposed. The proposed solution routinely employs a Maximum Power Point Track...
Review of 2 kW grid connected LOPF tests in Nissum Bredning
DEFF Research Database (Denmark)
Margheritini, Lucia
This report has been prepared by Per Resen and Aalborg University for the ForskVE project 10878: 2 kW grid connected LOPF test buoy. AAU has the role of reviewing and advise on the data analysis, besides compiling this report. The purpose of this project was to document the mechanical power...... production against a target power curve of a 2kW grid connected wave energy buoy in Nissum Bredning at Helligsø....
Stability analysis of grid inverter LCL-filter resonance in wind or photovoltaic parks
DEFF Research Database (Denmark)
Arcuri, S.; Liserre, M.; Ricchiuto, D.
2011-01-01
Typically the resonance problems related to the use of LCL-filters in grid connected inverters are analyzed assuming the operation of a single inverter. Wind and photovoltaic parks may experience propagation of resonance from a poorly damped inverter to other systems connected in parallel....... The paper focuses on the study of the resonance at a park system level with simulations and experimental results....
Arafat, Md Nayeem
Distributed generation systems (DGs) have been penetrating into our energy networks with the advancement in the renewable energy sources and energy storage elements. These systems can operate in synchronism with the utility grid referred to as the grid connected (GC) mode of operation, or work independently, referred to as the standalone (SA) mode of operation. There is a need to ensure continuous power flow during transition between GC and SA modes, referred to as the transition mode, in operating DGs. In this dissertation, efficient and effective transition control algorithms are developed for DGs operating either independently or collectively with other units. Three techniques are proposed in this dissertation to manage the proper transition operations. In the first technique, a new control algorithm is proposed for an independent DG which can operate in SA and GC modes. The proposed transition control algorithm ensures low total harmonic distortion (THD) and less voltage fluctuation during mode transitions compared to the other techniques. In the second technique, a transition control is suggested for a collective of DGs operating in a microgrid system architecture to improve the reliability of the system, reduce the cost, and provide better performance. In this technique, one of the DGs in a microgrid system, referred to as a dispatch unit , takes the additional responsibility of mode transitioning to ensure smooth transition and supply/demand balance in the microgrid. In the third technique, an alternative transition technique is proposed through hybridizing the current and droop controllers. The proposed hybrid transition control technique has higher reliability compared to the dispatch unit concept. During the GC mode, the proposed hybrid controller uses current control. During the SA mode, the hybrid controller uses droop control. During the transition mode, both of the controllers participate in formulating the inverter output voltage but with different
International Nuclear Information System (INIS)
Tina, G.M.; Scandura, P.F.
2012-01-01
Highlights: ► PV systems with sun tracking and concentrators (CPVS) can reduce the cost of energy per kWh produced. ► The V-trough low-concentration system solution is compatible with flat PV module technologies. ► Optical, thermal and electrical models are needed to forecast real power production. ► The description of a PV grid connected system with batteries, a one-axis tracker and CPV photovoltaic system is presented. ► Outdoor measurements of the generating system are provided and discussed. - Abstract: Photovoltaic systems (PVSs) combined with either some form of storage, such as a battery energy storage system (BESS), or direct load control, can play a crucial role in achieving a more economical operation of the electric utility system while enhancing its reliability with additional energy sources. At the same time, it is also important to use cost-effective PV solutions. In this context, a low-concentration PVS (CPVS) is analysed as a feasible alternative. This paper, present a case study of a complex PVS, composed of two PVSs, a storage system (BEES) and an inverter that allows the system to operate in both the island and grid-connected modes. The first PVS, is a 2.76-kWp single-axis tracking system (azimuth) with modules facing south and tilted 30°, while the second PVS is a dual-axis tracking system, rated 860 Wp, consisting of a concentrator at the flat mirrors (DoubleSun® Four). The system is installed on the roof of the main building of the “ITIS Marconi” school (Italy). A detailed description of the system is provided, and preliminary operating data are presented and discussed. The efficiencies of the PV systems are calculated and measured to evaluate the cost effectiveness of a low-concentration system.
International Nuclear Information System (INIS)
Hernandez, J.; Gordillo, G.; Vallejo, W.
2013-01-01
Highlights: ► A model to predict in a reliable way the behavior of a GCPV system is presented. ► Radiation and temperature behavior were shaped with probability density functions. ► This probability density functions were made from real measurements. ► This model was verified for comparing their behavior with real measurements. ► It can be used in any electrical systems language which have programming routines. - Abstract: This paper presents a methodology to predict in a statistically reliable way the behavior of a grid-connected photovoltaic system. The methodology developed can be implemented either in common programming software or through an off-the-shelf simulation of electrical systems. Initially, the atmospheric parameters that influence the behavior of PV generators (radiation and temperature) are characterized in a probabilistic manner. In parallel, a model compound by various PV generator components is defined: the modules (and their electrical and physical characteristics), their connection to form the generator, and the inverter type. This model was verified for comparing their behavior with output measured on a real installed system of 3.6 kWp. The solar resource characterized and the photovoltaic system model are integrated in a non-deterministic approach using the stochastic Monte Carlo method, developed in the programming language DPL of the electrical-systems simulation software DIGSILENT®. It is done to estimate the steady-state electrical parameters describing the influence of the grid-connected photovoltaic system. Specifically, we estimated the nominal peak power of the PV generator to minimize network losses, subject to constraints on nodes voltages and conductor currents
Borni, A.; Abdelkrim, T.; Zaghba, L.; Bouchakour, A.; Lakhdari, A.; Zarour, L.
2017-02-01
In this paper the model of a grid connected hybrid system is presented. The hybrid system includes a variable speed wind turbine controlled by aFuzzy MPPT control, and a photovoltaic generator controlled with PSO Fuzzy MPPT control to compensate the power fluctuations caused by the wind in a short and long term, the inverter currents injected to the grid is controlled by a decoupled PI current control. In the first phase, we start by modeling of the conversion system components; the wind system is consisted of a turbine coupled to a gearless permanent magnet generator (PMG), the AC/DC and DC-DC (Boost) converter are responsible to feed the electric energy produced by the PMG to the DC-link. The solar system consists of a photovoltaic generator (GPV) connected to a DC/DC boost converter controlled by a PSO fuzzy MPPT control to extract at any moment the maximum available power at the GPV terminals, the system is based on maximum utilization of both of sources because of their complementary. At the end. The active power reached to the DC-link is injected to the grid through a DC/AC inverter, this function is achieved by controlling the DC bus voltage to keep it constant and close to its reference value, The simulation studies have been performed using Matlab/Simulink. It can be concluded that a good control system performance can be achieved.
Optimization of Renewable Energy Hybrid System for Grid Connected Application
Directory of Open Access Journals (Sweden)
Mustaqimah Mustaqimah
2012-10-01
Full Text Available ABSTRACT. Hybrid energy systems are pollution free, takes low cost and less gestation period, user and social friendly. Such systems are important sources of energy for shops, schools, and clinics in village communities especially in remote areas. Hybrid systems can provide electricity at a comparatively economic price in many remote areas. This paper presents a method to jointly determine the sizing and operation control of hybrid energy systems. The model, PV wind hydro and biomass hybrid system connects to grid. The system configuration of the hybrid is derived based on a theoretical domestic load at a typical location and local solar radiation, wind and water flow rate data and biomass availability. The hybrid energy system is proposed for 10 of teacher’s houses of Industrial Training Institute, Mersing. It is predicted 10 kW load consumption per house. The hybrid energy system consists of wind, solar, biomass, hydro, and grid power. Approximately energy consumption is 860 kWh/day with a 105 kW peak demand load. The proposed hybrid renewable consists of solar photovoltaic (PV panels, wind turbine, hydro turbine and biomass. Battery and inverter are included as part of back-up and storage system. It provides the economic sensitivity of hybridization and the economic and environmental benefits of using a blend of technologies. It also presents the trade off that is involved in optimizing a hybrid energy system to harness and utilize the available renewable energy resources efficiently.
Performance evaluation of 10 MW grid connected solar photovoltaic power plant in India
Directory of Open Access Journals (Sweden)
B. Shiva Kumar
2015-11-01
Full Text Available The growing energy demand in developing nations has triggered the issue of energy security. This has made essential to utilize the untapped potential of renewable resources. Grid connected PV systems have become the best alternatives in renewable energy at large scale. Performance analysis of these grid connected plants could help in designing, operating and maintenance of new grid connected systems. A 10 MW photovoltaic grid connected power plant commissioned at Ramagundam is one of the largest solar power plants with the site receiving a good average solar radiation of 4.97 kW h/m2/day and annual average temperature of about 27.3 degrees centigrade. The plant is designed to operate with a seasonal tilt. In this study the solar PV plant design aspects along with its annual performance is elaborated. The various types of power losses (temperature, internal network, power electronics, grid connected etc. and performance ratio are also calculated. The performance results of the plant are also compared with the simulation values obtained from PV syst and PV-GIS software. The final yield (Y F of plant ranged from 1.96 to 5.07 h/d, and annual performance ratio (PR of 86.12%. It has 17.68% CUF with annual energy generation of 15798.192 MW h/Annum.
DEFF Research Database (Denmark)
Yang, Yongheng; Sangwongwanich, Ariya; Liu, Hongpeng
2017-01-01
In this paper, a cost-effective control scheme for two-stage grid-connected PhotoVoltaic (PV) systems in Low Voltage Ride-Through (LVRT) operation is proposed. In the case of LVRT, the active power injection by PV panels should be limited to prevent from inverter over-current and also energy...... aggregation at the dc-link, which will challenge the dc-link capacitor lifetime if remains uncontrolled. At the same time, reactive currents should be injected upon any demand imposed by the system operators. In the proposed scheme, the two objectives can be feasibly achieved. The active power is regulated...... point tracking controller without significant hardware or software modifications. In this way, the PV system will not operate at the maximum power point, whereas the inverter will not face any over-current challenge but can provide reactive power support in response to the grid voltage fault...
Directory of Open Access Journals (Sweden)
Manel Hlaili
2016-01-01
Full Text Available Photovoltaic (PV energy is one of the most important energy sources since it is clean and inexhaustible. It is important to operate PV energy conversion systems in the maximum power point (MPP to maximize the output energy of PV arrays. An MPPT control is necessary to extract maximum power from the PV arrays. In recent years, a large number of techniques have been proposed for tracking the maximum power point. This paper presents a comparison of different MPPT methods and proposes one which used a power estimator and also analyses their suitability for systems which experience a wide range of operating conditions. The classic analysed methods, the incremental conductance (IncCond, perturbation and observation (P&O, ripple correlation (RC algorithms, are suitable and practical. Simulation results of a single phase NPC grid connected PV system operating with the aforementioned methods are presented to confirm effectiveness of the scheme and algorithms. Simulation results verify the correct operation of the different MPPT and the proposed algorithm.
Conditions and costs for renewables electricity grid connection: Examples in Europe
International Nuclear Information System (INIS)
Swider, Derk J.; Beurskens, Luuk; Davidson, Sarah; Twidell, John; Pyrko, Jurek; Prueggler, Wolfgang; Auer, Hans; Vertin, Katarina; Skema, Romualdas
2008-01-01
This paper compares conditions and costs for RES-E grid connection in selected European countries. These are Germany, the Netherlands, the United Kingdom, Sweden, Austria, Lithuania and Slovenia. Country specific case studies are presented for wind onshore and offshore, biomass and photovoltaic power systems, as based on literature reviews and stakeholder interviews. It is shown that, especially for wind offshore, the allocation of grid connection costs can form a significant barrier for the installation of new RES-E generation if the developer has to bear all such costs. If energy policy makers want to reduce the barriers for new large-scale RES-E deployment, then it is concluded that the grid connection costs should be covered by the respective grid operator. These costs may then be recouped by increasing consumer tariffs for the use of the grid. (author)
Analysis of turbine-grid interaction of grid-connected wind turbine using HHT
Chen, A.; Wu, W.; Miao, J.; Xie, D.
2018-05-01
This paper processes the output power of the grid-connected wind turbine with the denoising and extracting method based on Hilbert Huang transform (HHT) to discuss the turbine-grid interaction. At first, the detailed Empirical Mode Decomposition (EMD) and the Hilbert Transform (HT) are introduced. Then, on the premise of decomposing the output power of the grid-connected wind turbine into a series of Intrinsic Mode Functions (IMFs), energy ratio and power volatility are calculated to detect the unessential components. Meanwhile, combined with vibration function of turbine-grid interaction, data fitting of instantaneous amplitude and phase of each IMF is implemented to extract characteristic parameters of different interactions. Finally, utilizing measured data of actual parallel-operated wind turbines in China, this work accurately obtains the characteristic parameters of turbine-grid interaction of grid-connected wind turbine.
Harmonic Interaction Analysis in Grid Connected Converter using Harmonic State Space (HSS) Modeling
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Bak, Claus Leth
2015-01-01
-model, are introduced to analyze these problems. However, it is found that Linear Time Invariant (LTI) base model analysis makes it difficult to analyze these phenomenon because of time varying system operation trajectories, varying output impedance seen by grid connected systems and neglected switching component......An increasing number of power electronics based Distributed Generation (DG) systems and loads generate coupled harmonic as well as non-characteristic harmonic with each other. Several methods like impedance based analysis, which is derived from conventional small signal- and average...... during the modeling process. This paper investigates grid connected converter by means of Harmonic State Space (HSS) small signal model, which is modeled from Linear Time varying Periodically (LTP) system. Further, a grid connected converter harmonic matrix is investigated to analyze the harmonic...
Directory of Open Access Journals (Sweden)
Zheng Li
2017-11-01
Full Text Available A centralized grid-connected photovoltaic (PV station is a widely adopted method of neutral grounding using resistance, which can potentially make pre-existing protection systems invalid and threaten the safety of power grids. Therefore, studying the fault characteristics of grid-connected PV systems and their impact on power-grid protection is of great importance. Based on an analysis of the grid structure of a grid-connected PV system and of the low-voltage ride-through control characteristics of a photovoltaic power supply, this paper proposes a short-circuit calculation model and a fault-calculation method for this kind of system. With respect to the change of system parameters, particularly the resistance connected to the neutral point, and the possible impact on protective actions, this paper achieves the general rule of short-circuit current characteristics through a simulation, which provides a reference for devising protection configurations.
Experiences of a grid connected solar array energy production
Hagymássy, Zoltán; Vántus, András
2015-04-01
Solar energy possibilities of Hungary are higher than in Central Europe generally. The Institute for Land Utilisation, Technology and Regional Development of the University of Debrecen installed a photovoltaic (PV) system. The PV system is structured into 3 subsystems (fields). The first subsystem has 24 pieces of Kyocera KC 120 W type modules, the second subsystem has 72 pieces of Siemens ST 40W, and the remaining has 72 pieces of Dunasolar DS 40W In order to be operable independently of each other three inverter modules (SB 2500) had been installed. The recorder can be connected directly to a desktop PC. Operating and meteorological dates are recorded by MS Excel every 15 minutes. The power plant is connected to a weather station, which contents a PT 100 type temperature and humidity combined measuring instrument, a CM 11 pyranometer, and a wind speed measuring instrument. The produced DC, and AC power, together with the produced energy are as well, and the efficiency can be determined for each used PV technology. The measured operating and meteorological dates are collected by Sunny Boy Control, produced by the SMA. The energy productions of the subsystems are measured continually and the subsystems are measured separately. As an expected, the produced energy of polycrystalline -Si PV module and monocrystalline -Si PV was higher than amorphous-Si PV module. It is well known that energy analysis is more suitable for energy balance when we design a system. The air temperature and the temperature of the panels and the global irradiation conditions were measured. In summertime the panel temperature reaches 60-80 degrees in a sunny day. The panel temperatures are in a spring sunny day approximately 30-40 degrees. It can be concluded that the global irradiation is a major impact feature to influence the amount of energy produced. The efficiency depends on several parameters (spectral distribution of the incoming light, temperature values, etc.). The energy efficiency
Single-Phase Phase-Locked Loop Based on Derivative Elements
DEFF Research Database (Denmark)
Guan, Qingxin; Zhang, Yu; Kang, Yong
2017-01-01
High-performance phase-locked loops (PLLs) are critical for power control in grid-connected systems. This paper presents a new method of designing a PLL for single-phase systems based on derivative elements (DEs). The quadrature signal generator (QSG) is constructed by two DEs with the same...... PLL to achieve high performance when the grid frequency changes rapidly. This paper presents the model of the PLL and a theoretical performance analysis with respect to both the frequency-domain and time-domain behavior. The error arising from the discretization process is also compensated, ensuring...
Benchmarking of small-signal dynamics of single-phase PLLs
DEFF Research Database (Denmark)
Zhang, Chong; Wang, Xiongfei; Blaabjerg, Frede
2015-01-01
Phase-looked Loop (PLL) is a critical component for the control and grid synchronization of grid-connected power converters. This paper presents a benchmarking study on the small-signal dynamics of three commonly used PLLs for single-phase converters, including enhanced PLL, second......-order generalized integrator based PLL, and the inverse-PLL. First, a unified small-signal model of those PLLs is established for comparing their dynamics. Then, a systematic design guideline for parameters tuning of the PLLs is formulated. To confirm the validity of theoretical analysis, nonlinear time...
High frequency three-phase PWM grid connected drive using silicon-carbide switches
DEFF Research Database (Denmark)
Kouchaki, Alireza; Pedersen, Jacob Lykke; Nymand, Morten
2016-01-01
This paper presents controller design procedure for a fully silicon-carbide (SiC) based three-phase grid-connected PWM drive. The influence of the feedforward compensation for the presented setup is studied and the transfer function of the system with feedforward is derived and compared with the ......This paper presents controller design procedure for a fully silicon-carbide (SiC) based three-phase grid-connected PWM drive. The influence of the feedforward compensation for the presented setup is studied and the transfer function of the system with feedforward is derived and compared...
Power control of a wind farm with active stall wind turbines and AC grid connection
DEFF Research Database (Denmark)
Hansen, Anca Daniela; Sørensen, Poul; Iov, Florin
both the control on wind turbine level as well as the central control on the wind farm level. The ability of active stall wind farms with AC grid connection to regulate the power production to the reference power ordered by the operators is assessed and discussed by means of simulations.......This paper describes the design of a centralised wind farm controller for a wind farm made-up exclusively of active stall wind turbines with AC grid connection. The overall aim of such controller is to enable the wind farms to provide the best grid support. The designed wind farm control involves...
Passivity-Based Stability Assessment of Grid-Connected VSCs - An Overview
DEFF Research Database (Denmark)
Harnefors, Lennart; Wang, Xiongfei; Yepes, Alejandro G.
2016-01-01
The interconnection stability of a grid-connected voltage-source converter (VSC) can be assessed by the passivity properties of the VSC input admittance. If critical grid resonances fall within regions where the input admittance acts passively, i.e., has nonnegative real part, then their destabil......The interconnection stability of a grid-connected voltage-source converter (VSC) can be assessed by the passivity properties of the VSC input admittance. If critical grid resonances fall within regions where the input admittance acts passively, i.e., has nonnegative real part...
Performance evaluation of a 2-mode PV grid connected system in Thailand -- Case study
Energy Technology Data Exchange (ETDEWEB)
Jivacate, C.; Mongconvorawan, S.; Sinratanapukdee, E.; Limsawatt, W. [Electricity Generating Authority of Thailand, Nontha Buri (Thailand)
1994-12-31
A PV grid connected system with small battery bank has been set up in a rural district, North Thailand in order to demonstrate a 2-mode operation concept. The objective is to gain experience on the PV grid connected concept without battery storage. However, due to the evening peak demand and a rather weak distribution grid which is typical in rural areas, small battery bank is still required to enable the maximum energy transfer to grid for the time being before moving fully to the no battery mode. The analyzed data seems to indicate possible performance improvement by re-arranging the number of PV modules and battery in the string.
Solar photovoltaic systems and their use as grid-connected generators in the United Kingdom
Energy Technology Data Exchange (ETDEWEB)
Munro, D K; Hacker, R J; Thornycroft, J M [Halcrow Gilbert Associates Ltd., Swindon (United Kingdom)
1995-10-01
There is an increasing interest in the use of building-integrated solar photovoltaic generators as grid-connected generators. This paper discusses the experience with this technology in Europe. Typical systems and their integration into domestic and non-domestic buildings are described. Information is provided on the energy output that can be expected from the systems and the economics of their use. The paper provides an overview of the requirements for photovoltaic systems as grid-connected generation plant in the United Kingdom. (Author)
Flexible operation of parallel grid-connecting converters under unbalanced grid voltage
DEFF Research Database (Denmark)
Lu, Jinghang; Savaghebi, Mehdi; Guerrero, Josep M.
2017-01-01
-link voltage ripple, and overloading. Moreover, under grid voltage unbalance, the active power delivery ability is decreased due to the converter's current rating limitation. In this paper, a thorough study on the current limitation of the grid-connecting converter under grid voltage unbalance is conducted....... In addition, based on the principle that total output active power should be oscillation free, a coordinated control strategy is proposed for the parallel grid-connecting converters. The case study has been conducted to demonstrate the effectiveness of this proposed control strategy....
A novel optimized LCL-filter designing method for grid connected converter
DEFF Research Database (Denmark)
Guohong, Zeng; Rasmussen, Tonny Wederberg; Teodorescu, Remus
2010-01-01
This paper presents a new LCL-filters optimized designing method for grid connected voltage source converter. This method is based on the analysis of converter output voltage components and inherent relations among LCL-filter parameters. By introducing an optimizing index of equivalent total capa...
Grid connection rules for electric cars integrated as virtual power plant in smart grids
DEFF Research Database (Denmark)
Leban, Krisztina Monika; Ritchie, Ewen; Thøgersen, Paul Bach
2013-01-01
This paper reviews the situation of V2G and proposes a solution involving a consolidating fleet manager, and a decision making process for the individual V2G electric car owner. A grid connection routine for electric vehicles is proposed. The algorithm dealing with decisions to be taken in foreseen...
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
Harmonic instability is threatening the operation of renewable energy based power plants where multiple gridconnected VSIs are connected in parallel. To analyze and improve the stability of the grid-connected VSIs, the real part of the output admittance of the VSIs is first investigated......-connected VSIs can improve the stability of the renewable power plant....
Dynamics of voltage source converter in a grid connected solar photovoltaic system
DEFF Research Database (Denmark)
Haribabu, Divyanagalakshmi; Vangari, Adithya; Sakamuri, Jayachandra N.
2015-01-01
This paper emphasises the modelling and control of a voltage source converter (VSC) for three phase grid connected PV system. The transfer functions for inner current control and outer DC link voltage control for VSC are derived. The controllers for VSC are designed based on PI and K factor contr...
Planning and development of wind farms: Environmental impact and grid connection
DEFF Research Database (Denmark)
Clausen, Niels-Erik
These course notes are intended for the three-week course 46200 Planning and Development of Wind Farms given by DTUWind Energy, Technical University of Denmark. The purpose of the course notes is to give an introduction to planning procedures, environmental impact assessments, and grid connection....
Model Predictive Current Control for High-Power Grid-Connected Converters with Output LCL Filter
DEFF Research Database (Denmark)
Delpino, Hernan Anres Miranda; Teodorescu, Remus; Rodriguez, Pedro
2009-01-01
A model predictive control strategy for a highpower, grid connected 3-level neutral clamped point converter is presented. Power losses constraints set a limit on commutation losses so reduced switching frequency is required, thus producing low frequency current harmonics. To reduce these harmonics...
Control strategies for gas turbine generators for grid connected and islanding operations
DEFF Research Database (Denmark)
Mahat, Pukar; Chen, Zhe; Bak-Jensen, Birgitte
2010-01-01
fine while a DG is connected to a grid, might not work as desired while it is islanded and vise versa. This paper presents a strategy to operate distribution systems with a small gas turbine generator (GTG), which is capable of supplying local loads, in both islanding and grid connected conditions...
An offshore wind farm with dc grid connection and its performance under power system transients
DEFF Research Database (Denmark)
Deng, Fujin; Chen, Zhe
2011-01-01
by disconnections. This paper presents a transient performance study of an offshore wind farm with HVDC transmission for grid connection, where the wind turbines in the offshore wind farm are also connected with dc collection network. A power-reduction control strategy (PRCS) for transient performance improvement...
Online Energy Management System for Distributed Generators in a Grid-Connected Microgrid
DEFF Research Database (Denmark)
Hernández, Adriana Carolina Luna; Aldana, Nelson Leonardo Diaz; Graells, Moises
2015-01-01
A microgrid is an energy subsystem composed of generation units, energy storage, and loads that requires power management in order to supply the load properly according to defined objectives. This paper proposes an online energy management system for a storage based grid-connected microgrid...
Economic Power Dispatch of Distributed Generators in a Grid-Connected Microgrid
DEFF Research Database (Denmark)
Hernández, Adriana Carolina Luna; Aldana, Nelson Leonardo Diaz; Andrade, Fabio
2015-01-01
Grid-connected microgrids with storage systems are reliable configurations for critical loads which can not tolerate interruptions of energy supply. In such cases, some of the energy resources should be scheduled in order to coordinate optimally the power generation according to a defined objective...
Almeida, de P.M.; Barbosa, P.G.; Oliveira, J.G.; Duarte, J.L.; Ribeiro, P.F.
2015-01-01
This paper presents the modelling and design steps of a digital proportional multi-resonant controller used in a grid-connected photovoltaic (PV) system. It is shown that the use of only one Proportional-Resonant (PR) compensator, tuned to the system fundamental frequency, may have its effectiveness
Input-Admittance Passivity Compliance for Grid-Connected Converters with LCL Filter
DEFF Research Database (Denmark)
Diaz, Enrique Rodriguez; Freijedo, Francisco D.; Guerrero, Josep M.
2018-01-01
This work presents a design methodology and its experimental validation for the input-admittance passivity compliance of LCL grid-connected converters. The designs of the LCL filter parameters and discrete controller are addressed systematically, and suitable design guidelines are provided......-admittance passivity compliance....
Analysis of the influences of grid-connected PV power system on distribution grids
Directory of Open Access Journals (Sweden)
Dumitru Popandron
2013-12-01
Full Text Available This paper presents the analysis of producing an electric power of 2.8 MW using a solar photovoltaic plant. The PV will be grid connected to the distribution network. The study is focused on the influences of connecting to the grid of a photovoltaic system, using modern software for analysis, modeling and simulation in power systems.
Optimizing electrical load pattern in Kuwait using grid connected photovoltaic systems
International Nuclear Information System (INIS)
Al-Hasan, A.Y.; Ghoneim, A.A.; Abdullah, A.H.
2004-01-01
Grid connected photovoltaic systems is one of the most promising applications of photovoltaic systems. These systems are employed in applications where utility service is already available. In this case, there is no need for battery storage because grid power may be used to supplement photovoltaic systems (PV) when the load exceeds available PV generation. The load receives electricity from both the photovoltaic array and the utility grid. In this system, the load is the total electrical energy consumption. The main objective of the present work is to optimize the electrical load pattern in Kuwait using grid connected PV systems. In this situation, the electric load demand can be satisfied from both the photovoltaic array and the utility grid. The performance of grid connected photovoltaic systems in the Kuwait climate has been evaluated. It was found that the peak load matches the maximum incident solar radiation in Kuwait, which would emphasize the role of using the PV station to minimize the electrical load demand. In addition, a significant reduction in peak load can be achieved with grid connected PV systems
Quantitative Analysis Method of Output Loss due to Restriction for Grid-connected PV Systems
Ueda, Yuzuru; Oozeki, Takashi; Kurokawa, Kosuke; Itou, Takamitsu; Kitamura, Kiyoyuki; Miyamoto, Yusuke; Yokota, Masaharu; Sugihara, Hiroyuki
Voltage of power distribution line will be increased due to reverse power flow from grid-connected PV systems. In the case of high density grid connection, amount of voltage increasing will be higher than the stand-alone grid connection system. To prevent the over voltage of power distribution line, PV system's output will be restricted if the voltage of power distribution line is close to the upper limit of the control range. Because of this interaction, amount of output loss will be larger in high density case. This research developed a quantitative analysis method for PV systems output and losses to clarify the behavior of grid connected PV systems. All the measured data are classified into the loss factors using 1 minute average of 1 second data instead of typical 1 hour average. Operation point on the I-V curve is estimated to quantify the loss due to the output restriction using module temperature, array output voltage, array output current and solar irradiance. As a result, loss due to output restriction is successfully quantified and behavior of output restriction is clarified.
Design of LLCL-filter for grid-connected converter to improve stability and robustness
DEFF Research Database (Denmark)
Huang, Min; Wang, Xiongfei; Loh, Poh Chiang
2015-01-01
of the switching frequency range. The resonance frequencies of the LLCL-filters based grid-connected converters are sensitive to the grid impedance as well as cable capacitance, which may influence the stability of the overall system. This paper proposes a new parameter design method for LLCL-filter from the point...
Directory of Open Access Journals (Sweden)
Senad Apelfröjd
2014-01-01
Full Text Available Results from experiments on a tap transformer based grid connection system for a variable speed vertical axis wind turbine are presented. The tap transformer based system topology consists of a passive diode rectifier, DC-link, IGBT inverter, LCL-filter, and tap transformer. Full range variable speed operation is enabled by using the different step-up ratios of a tap transformer. Simulations using MATLAB/Simulink have been performed in order to study the behavior of the system. A full experimental set up of the system has been used in the laboratory study, where a clone of the on-site generator was driven by an induction motor and the system was connected to a resistive load to better evaluate the performance. Furthermore, the system is run and evaluated for realistic wind speeds and variable speed operation. For a more complete picture of the system performance, a case study using real site Weibull parameters is done, comparing different tap selection options. The results show high system efficiency at nominal power and an increase in overall power output for full tap operation in comparison with the base case, a standard transformer. In addition, the loss distribution at different wind speeds is shown, which highlights the dominant losses at low and high wind speeds. Finally, means for further increasing the overall system efficiency are proposed.
Apelfröjd, Senad; Eriksson, Sandra
2014-01-01
Results from experiments on a tap transformer based grid connection system for a variable speed vertical axis wind turbine are presented. The tap transformer based system topology consists of a passive diode rectifier, DC-link, IGBT inverter, LCL-filter, and tap transformer. Full range variable speed operation is enabled by using the different step-up ratios of a tap transformer. Simulations using MATLAB/Simulink have been performed in order to study the behavior of the system. A full experimental set up of the system has been used in the laboratory study, where a clone of the on-site generator was driven by an induction motor and the system was connected to a resistive load to better evaluate the performance. Furthermore, the system is run and evaluated for realistic wind speeds and variable speed operation. For a more complete picture of the system performance, a case study using real site Weibull parameters is done, comparing different tap selection options. The results show high system efficiency at nominal power and an increase in overall power output for full tap operation in comparison with the base case, a standard transformer. In addition, the loss distribution at different wind speeds is shown, which highlights the dominant losses at low and high wind speeds. Finally, means for further increasing the overall system efficiency are proposed.
2014-01-01
Results from experiments on a tap transformer based grid connection system for a variable speed vertical axis wind turbine are presented. The tap transformer based system topology consists of a passive diode rectifier, DC-link, IGBT inverter, LCL-filter, and tap transformer. Full range variable speed operation is enabled by using the different step-up ratios of a tap transformer. Simulations using MATLAB/Simulink have been performed in order to study the behavior of the system. A full experimental set up of the system has been used in the laboratory study, where a clone of the on-site generator was driven by an induction motor and the system was connected to a resistive load to better evaluate the performance. Furthermore, the system is run and evaluated for realistic wind speeds and variable speed operation. For a more complete picture of the system performance, a case study using real site Weibull parameters is done, comparing different tap selection options. The results show high system efficiency at nominal power and an increase in overall power output for full tap operation in comparison with the base case, a standard transformer. In addition, the loss distribution at different wind speeds is shown, which highlights the dominant losses at low and high wind speeds. Finally, means for further increasing the overall system efficiency are proposed. PMID:25258733
Directory of Open Access Journals (Sweden)
Layachi ZAGHBA
2017-12-01
Full Text Available In this study, is to investigate the effect of real climatic conditions on the performance parameters of a 9 kWp grid connected photovoltaic plant during one-year using typical days installed in the desert environment in south of Algeria (Ghardaia site. The PV plant contain the following components: solar PV array, with a DC/DC boost converter, neural MPPT, that allow maximal power conversion into the grid, have been included. These methods can extract maximum power from each of the independent PV arrays connected to DC link voltage level, a DC/AC inverter and a PI current control system. The PV array is divides in two parallel PV technology types; the first includes 100 PV modules mono-crystalline silicon (mc-Si arranged in 20 parallel groups of 5 modules in series, and the second of composed of 24 amorphous modules (Inventux X series, arranged in 6 parallel groups of 4 modules in series. The proposed system tested using MATLAB/SIMULINK platform in which a maximum power tracked under constant and real varying solar irradiance. The study concluded that output power and energy from two PV technology types (mc-Si and Amorphous-Si increases linearly with increase of solar irradiance.
International Nuclear Information System (INIS)
Fernández, Eduardo F.; Almonacid, Florencia
2015-01-01
Highlights: • Concentrating grid-connected systems are working at maximum power point. • The operating cell temperature is inherently lower than at open circuit. • Two novel methods for estimating the cell temperature are proposed. • Both predict the operating cell temperature from atmospheric parameters. • Experimental results show that both methods perform effectively. - Abstract: The working cell temperature of high concentrator photovoltaic systems is a crucial parameter when analysing their performance and reliability. At the same time, due to the special features of this technology, the direct measurement of the cell temperature is very complex and is usually obtained by using different indirect methods. High concentrator photovoltaic modules in a system are operating at maximum power since they are connected to an inverter. So that, their cell temperature is lower than the cell temperature of a module at open-circuit voltage since an important part of the light power density is converted into electricity. In this paper, a procedure for indirectly estimating the cell temperature of a high concentrator photovoltaic system from atmospheric parameters is addressed. Therefore, this new procedure has the advantage that is valid for estimating the cell temperature of a system at any location of interest if the atmospheric parameters are available. To achieve this goal, two different methods are proposed: one based on simple mathematical relationships and another based on artificial intelligent techniques. Results show that both methods predicts the cell temperature of a module connected to an inverter with a low margin of error with a normalised root mean square error lower or equal than 3.3%, an absolute root mean square error lower or equal than 2 °C, a mean absolute error lower or equal then 1.5 °C, and a mean bias error and a mean relative error almost equal to 0%
An analysis method for harmonic resonance and stability of multi-paralleled LCL-filtered inverters
DEFF Research Database (Denmark)
Lu, Minghui; Wang, Xiongfei; Blaabjerg, Frede
2015-01-01
Paralleled grid-connected inverters with LCL-filters are coupled through the non-negligible grid impedance. However, the coupling effects among inverters and grid are usually ignored during the design, which may lead to unexpected system resonance and even instability. This paper thus investigates...
Reliability Assessment of Transformerless PV Inverters considering Mission Profiles
Directory of Open Access Journals (Sweden)
Yongheng Yang
2015-01-01
Full Text Available Due to the small volume and high efficiency, transformerless inverters have gained much popularity in grid-connected PV applications, where minimizing leakage current injection is mandatory. This can be achieved by either modifying the modulation schemes or adding extra power switching devices, resulting in an uneven distribution of the power losses on the switching devices. Consequently, the device thermal loading is redistributed and thus may alter the entire inverter reliability performance, especially under a long-term operation. In this consideration, this paper assesses the device reliability of three transformerless inverters under a yearly mission profile (i.e., solar irradiance and ambient temperature. The mission profile is translated to device thermal loading, which is used for lifetime prediction. Comparison results reveal the lifetime mismatches among the power switching devices operating under the same condition, which offers new thoughts for a robust design and a reliable operation of grid-connected transformerless PV inverters with high efficiency.
Transformerless PV inverters. Final report
Energy Technology Data Exchange (ETDEWEB)
Borup, U.
2009-12-15
Since the start of the project the market for grid connected PV inverters have developed further. When the project started three - phase inverter were only available in high power systems. The technology developed within this project will enable three phase technology also to be implemented in string inverters for system down to 10 kW. We expect this to be very attractive due to the increased demand for symmetrical feed-in to the grid. The project relevance is therefore high and the sector continues to develop very much driven by technology. Especially the inverter technology is getting a lot of focus. The inverter systems are expected to take a much larger role in supporting the electrical grid in the future. The technology platform developed within the project is prepared to be extended with these utility functionalities. The main results of the project were: 1) A new technology concept for transformer-less inverters has been demonstrated with a number of prototypes. 2) Efficiency above 97,7% has been proven. 3) Efficiency and Maximum power point tracking has been optimized to ensure that almost all energy produced of the panels is transferred to the grid. 4) The platform is developed with a very fast control board, which enables extended functionality as demanding grid supporting functions in the future. Details about cost price and details about the control loop implementation is excluded from the report due to the competitive situation for Danfoss Solar Inverters A/S. (LN)
Highlight of Grid-connected PV systems in administrative buildings in Egypt
Directory of Open Access Journals (Sweden)
Dina Said
2017-03-01
Full Text Available Solar energy applications are becoming increasingly common in Egypt. The abundant sunshine in Egypt, as well as the increasing competitiveness of solar energy systems including- but not limited to photovoltaic (PV, – predicts that these technologies could be weighed to be raised in Egypt.PV systems are installed on roof tiles or other parts of building structures to supplement grid utility, reduce electric bills, and provide emergency back–up energy. Moreover, they simultaneously reduce significant amounts of CO2 emissions. It is foreseen, a number of residential and public buildings in Egypt are using solar power to cut electric utility bills significantly. The approximately payback period to recover the investment costs for PV systems is up to about 5 years. In addition, it is more economical to use PV system than grid utility systems. The two components that determine the total initial price of a grid- connected PV system are the modules and the balance of systems (BOS. The BOS includes different components such as mounting frames, inverters and site- specific installation hardware.The Government of Egypt (GOE has endorsed the deployment of PV systems through three approaches. It started with a prime minister decree to install PV projects on one-thousand of the governmental buildings. This was followed by as an initiative called "Shamsk ya Masr", and finally the Feed-in Tariff (FiT projects.Following the prime minster decree the Egyptian Electricity Holding Company (EEHC and its affiliated companies took the lead to install PV systems at the top roof of their administrative buildings and interconnect these systems to the electricity network where the suitable locations have been selected for mounting them. About 90 PV systems have been already mounted with about a capacity of 9 MW. On the other hand, "Shamsk ya Masr" has considered energy efficiency (EE so as to complement the PV systems, which will be installed on administrative
Discontinuous interleaving of parallel inverters for efficiency improvement
DEFF Research Database (Denmark)
Rannestad, Bjørn; Munk-Nielsen, Stig; Gadgaard, Kristian
2017-01-01
Interleaved switching of parallel inverters has previously been proposed for efficiency/size improvements of grid connected three-phase inverters. This paper proposes a novel interleaving method which practically eliminates insulated gate bipolar transistor (IGBT) turn-on losses and drastically...... overall power module losses are reduced. The modulation strategy is suited for converters with doubly fed induction generators (DFIG) for wind turbines, but are not limited hereto. Improvement of switching performance are measured and operational efficiency improvements are calculated and verified...
Photovoltaic Grid-Connected Modeling and Characterization Based on Experimental Results
Humada, Ali M.; Hojabri, Mojgan; Sulaiman, Mohd Herwan Bin; Hamada, Hussein M.; Ahmed, Mushtaq N.
2016-01-01
A grid-connected photovoltaic (PV) system operates under fluctuated weather condition has been modeled and characterized based on specific test bed. A mathematical model of a small-scale PV system has been developed mainly for residential usage, and the potential results have been simulated. The proposed PV model based on three PV parameters, which are the photocurrent, IL, the reverse diode saturation current, Io, the ideality factor of diode, n. Accuracy of the proposed model and its parameters evaluated based on different benchmarks. The results showed that the proposed model fitting the experimental results with high accuracy compare to the other models, as well as the I-V characteristic curve. The results of this study can be considered valuable in terms of the installation of a grid-connected PV system in fluctuated climatic conditions. PMID:27035575
Wind Power Grid Connected Capacity Prediction Using LSSVM Optimized by the Bat Algorithm
Directory of Open Access Journals (Sweden)
Qunli Wu
2015-12-01
Full Text Available Given the stochastic nature of wind, wind power grid-connected capacity prediction plays an essential role in coping with the challenge of balancing supply and demand. Accurate forecasting methods make enormous contribution to mapping wind power strategy, power dispatching and sustainable development of wind power industry. This study proposes a bat algorithm (BA–least squares support vector machine (LSSVM hybrid model to improve prediction performance. In order to select input of LSSVM effectively, Stationarity, Cointegration and Granger causality tests are conducted to examine the influence of installed capacity with different lags, and partial autocorrelation analysis is employed to investigate the inner relationship of grid-connected capacity. The parameters in LSSVM are optimized by BA to validate the learning ability and generalization of LSSVM. Multiple model sufficiency evaluation methods are utilized. The research results reveal that the accuracy improvement of the present approach can reach about 20% compared to other single or hybrid models.
Sensorless Reserved Power Control Strategy for Two-Stage Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Sangwongwanich, Ariya; Yang, Yongheng; Blaabjerg, Frede
2016-01-01
Due to still increasing penetration level of grid-connected Photovoltaic (PV) systems, advanced active power control functionalities have been introduced in grid regulations. A reserved power control, where the active power from the PV panels is reserved during operation, is required for grid...... support. In this paper, a cost-effective solution to realize the reserved power control for grid-connected PV systems is proposed. The proposed solution routinely employs a Maximum Power Point Tracking (MPPT) control to estimate the available PV power and a Constant Power Generation (CPG) control...... to achieve the power reserve. In this method, the irradiance measurements that have been used in conventional control schemes to estimate the available PV power are not required, and thereby being a sensorless solution. Simulations and experimental tests have been performed on a 3-kW two-stage single...
Grid support of a wind farm with active stall wind turbines and AC grid connection
DEFF Research Database (Denmark)
Hansen, Anca Daniela; Sørensen, Poul Ejnar; Iov, F.
2006-01-01
grid connection. The designed control system has the task of enabling such a wind farm to provide the best grid support. It is based on two control levels: a supervisory control level, which controls the power production of the whole farm by sending out reference signals to each individual wind turbine......One of the main concerns in the grid integration of large wind farms is their ability to behave as active controllable components in the power system. This article presents the design of a new integrated power control system for a wind farm made up exclusively of active stall wind turbines with AC......, and a local control level, which ensures that the reference power signals at the wind turbine level are reached. The ability of active stall wind farms with AC grid connection to control the power production to the reference power ordered by the operators is assessed and discussed by means of simulations....
Photovoltaic Grid-Connected Modeling and Characterization Based on Experimental Results.
Humada, Ali M; Hojabri, Mojgan; Sulaiman, Mohd Herwan Bin; Hamada, Hussein M; Ahmed, Mushtaq N
2016-01-01
A grid-connected photovoltaic (PV) system operates under fluctuated weather condition has been modeled and characterized based on specific test bed. A mathematical model of a small-scale PV system has been developed mainly for residential usage, and the potential results have been simulated. The proposed PV model based on three PV parameters, which are the photocurrent, IL, the reverse diode saturation current, Io, the ideality factor of diode, n. Accuracy of the proposed model and its parameters evaluated based on different benchmarks. The results showed that the proposed model fitting the experimental results with high accuracy compare to the other models, as well as the I-V characteristic curve. The results of this study can be considered valuable in terms of the installation of a grid-connected PV system in fluctuated climatic conditions.
A techno-economic assessment of grid connected photovoltaic system for hospital building in Malaysia
Mat Isa, Normazlina; Tan, Chee Wei; Yatim, AHM
2017-07-01
Conventionally, electricity in hospital building are supplied by the utility grid which uses mix fuel including coal and gas. Due to enhancement in renewable technology, many building shall moving forward to install their own PV panel along with the grid to employ the advantages of the renewable energy. This paper present an analysis of grid connected photovoltaic (GCPV) system for hospital building in Malaysia. A discussion is emphasized on the economic analysis based on Levelized Cost of Energy (LCOE) and total Net Present Post (TNPC) in regards with the annual interest rate. The analysis is performed using Hybrid Optimization Model for Electric Renewables (HOMER) software which give optimization and sensitivity analysis result. An optimization result followed by the sensitivity analysis also being discuss in this article thus the impact of the grid connected PV system has be evaluated. In addition, the benefit from Net Metering (NeM) mechanism also discussed.
Progress in markets for grid-connected PV systems in the built environment
International Nuclear Information System (INIS)
Haas, R.
2004-01-01
In the last decade of the twentieth century a wide variety of promotion strategies increased the market penetration of small grid-connected PV systems world-wide. The objective of this paper is to assess the impact of these promotion strategies on the market for and on the economic performance of small grid-connected PV systems. The most important conclusions of this analysis are: Pure cost-effectiveness is not crucial for private customers. Affordability is rather what counts. Non-monetary issues play an important role for a substantial increase in market deployment. Comprehensive accompanied information and education activities are also important along with financial incentives. There are still considerable barriers in the market: on the one hand transparent and competitive markets exist in only a few countries; on the other hand non-monetary transaction costs still represent a major barrier. Progress with respect to cost reduction has been achieved, but mainly for non-module components. (author)
Distributed Power System Virtual Inertia Implemented by Grid-Connected Power Converters
DEFF Research Database (Denmark)
Fang, Jingyang; Li, Hongchang; Tang, Yi
2018-01-01
Renewable energy sources (RESs), e.g. wind and solar photovoltaics, have been increasingly used to meet worldwide growing energy demands and reduce greenhouse gas emissions. However, RESs are normally coupled to the power grid through fast-response power converters without any inertia, leading...... to decreased power system inertia. As a result, the grid frequency may easily go beyond the acceptable range under severe frequency events, resulting in undesirable load-shedding, cascading failures, or even large-scale blackouts. To address the ever-decreasing inertia issue, this paper proposes the concept...... of distributed power system virtual inertia, which can be implemented by grid-connected power converters. Without modifications of system hardware, power system inertia can be emulated by the energy stored in the dc-link capacitors of grid-connected power converters. By regulating the dc-link voltages...
Active Power Quality Improvement Strategy for Grid-connected Microgrid Based on Hierarchical Control
DEFF Research Database (Denmark)
Wei, Feng; Sun, Kai; Guan, Yajuan
2018-01-01
proposes an active, unbalanced, and harmonic GCC suppression strategy based on hierarchical theory. The voltage error between the bus of the DCGC-MG and the grid’s PCC was transformed to the dq frame. On the basis of the grid, an additional compensator, which consists of multiple resonant voltage......When connected to a distorted grid utility, droop-controlled grid-connected microgrids (DCGC-MG) exhibit low equivalent impedance. The harmonic and unbalanced voltage at the point of common coupling (PCC) deteriorates the power quality of the grid-connected current (GCC) of DCGC-MG. This work...... regulators, was then added to the original secondary control to generate the negative fundamental and unbalanced harmonic voltage reference. Proportional integral and multiple resonant controllers were adopted as voltage controller at the original primary level to improve the voltage tracking performance...
The research of SSR which can be restrained by photovoltaic grid connected
Li, Kuan; Liu, Meng; Zheng, Wei; Li, Yudun; Wang, Xin
2018-02-01
Utilization of photovoltaic power generation has attracted considerable attention, and it is growing rapidly due to its environmental benefits. The series capacitive compensation is needed to be introduced into the lines which could improve the transmission capacity. However, the series capacitive compensation may lead to sub-synchronous resonance(SSR). This paper proposes a method to restrain the SSR based on photovoltaic grid connected which is caused by series capacitive compensation. Sub-synchronous oscillation damping controller (SSDC) is designed based on complex torque coefficient approach, and the SSDC is added to the PV power station’s main controller to damp SSR. IEEE Second benchmark model is used as simulation model based on PSCAD/EMTDC. The results show that the designed SSDC could restrain SSR and improve stability in PV grid connected effectively.
Control System interaction in the VSC-HVDC Grid Connected Offshore Wind Power Plant
DEFF Research Database (Denmark)
Glasdam, Jakob Bærholm; Kocewiak, Łukasz Hubert; Hjerrild, Jesper
2015-01-01
the source of the instability has been identified and mitigation methods have been designed and implemented. This procedure is not straightforward and can have a long lead time. The harmonic instability can have severe economic consequences for the OWPP owner due to the large investment. Harmonic stability...... the procedure of the stability study and its application for the HVDC grid connected OWPPs. The purpose of this paper is to investigate the harmonic instability phenomena in HVDC grid connected OWPPs using both frequency and time domain simulations. A good correlation at lower frequencies between the two......Conventional offshore wind power plants (OWPPs) are due to the combination of the extensive sub-marine cabling and possible low available short-circuit power at the point of common connection (PCC) susceptible to the harmonic instability phenomena. The instability is caused by the resonances...
Marketing residential grid-connected PV systems using a balanced scorecard as a marketing tool
International Nuclear Information System (INIS)
Bach, N.; Calais, P.; Calais, M.
2001-01-01
A strategic analysis of the electricity market in Western Australia yields a market potential for renewable energy in Western Australia. However, from a purely financial viewpoint the installation of grid-connected pv-systems still is not economically viable. In this paper a balanced scorecard (BSC) is developed to capture and visualize other than financial benefits. Therefore, the BSC can be used as a marketing tool to communicate the benefits of a privately owned GCPV system to potential customers. (author)
System modelling and energy management for grid connected PV systems associated with storage
Riffonneau , Yann; DELAILLE , Arnaud; Barruel , Franck; Bacha , Seddik
2008-01-01
International audience; This paper presents the modelling and energy management of a grid connected PV system associatedwith storage. Within the economic, energetic and environmental context, objective of the system is to ensure loadssupply at the least cost by optimising the use of solar power. Therefore, due to the complicated operating patterns, anenergy management system which decides on energy flow for any moment is necessary. First, we present the systemstudied. Based on an AC bus typol...
Application of synchronous grid-connected controller in the wind-solar-storage micro grid
Li, Hua; Ren, Yongfeng; Li, Le; Luo, Zhenpeng
2016-01-01
Recently, there has been an increasing interest in using distributed generators (DG) not only to inject power into the grid, but also to enhance the power quality. In this study, a space voltage pulse width modulation (SVPWM) control method is proposed for a synchronous grid-connected controller in a wind-solar-storage micro grid. This method is based on the appropriate topology of the synchronous controller. The wind-solar-storage micro grid is controlled to reconnect to the grid synchronous...
Methodology for the optimal design of tansformerless grid-connected PV interters
DEFF Research Database (Denmark)
Koutroulis, E.; Blaabjerg, Frede
2012-01-01
inverter, such that the PV inverter levelised cost of the generated electricity is minimised. The proposed method constitutes a systematic design process, which is capable to explore the impact of the PV inverter configuration on the trade-off between the PV inverter manufacturing cost and the power losses...
Study on optimal configuration of the grid-connected wind-solar-battery hybrid power system
Ma, Gang; Xu, Guchao; Ju, Rong; Wu, Tiantian
2017-08-01
The capacity allocation of each energy unit in the grid-connected wind-solar-battery hybrid power system is a significant segment in system design. In this paper, taking power grid dispatching into account, the research priorities are as follows: (1) We establish the mathematic models of each energy unit in the hybrid power system. (2) Based on dispatching of the power grid, energy surplus rate, system energy volatility and total cost, we establish the evaluation system for the wind-solar-battery power system and use a number of different devices as the constraint condition. (3) Based on an improved Genetic algorithm, we put forward a multi-objective optimisation algorithm to solve the optimal configuration problem in the hybrid power system, so we can achieve the high efficiency and economy of the grid-connected hybrid power system. The simulation result shows that the grid-connected wind-solar-battery hybrid power system has a higher comprehensive performance; the method of optimal configuration in this paper is useful and reasonable.
Performance of Grid-Connected Photovoltaic System in Two Sites in Kuwait
Directory of Open Access Journals (Sweden)
Ali Hajiah
2012-01-01
Full Text Available This paper presents an assessment of the electricity generated by photovoltaic (PV grid-connected systems in Kuwait. Three years of meteorological data are provided for two main sites in Kuwait, namely, Al-Wafra and Mutla. These data and a PV grid-connected system mathematical model are used to assist a 100 kWp grid-connected PV system proposed for both sites. The proposed systems show high energy productivity whereas the annual capacity factors for Mutla and Al-Wafra are 22.25% and 21.6%, respectively. Meanwhile the annual yield factors for Mutla and Al-Wafra are 1861 kWh/kWp/year and 1922.7 kWh/kWp/year, respectively. On the other hand the cost of the energy generated by both systems is about 0.1 USD/kWh which is very close to the price of the energy sold by the Ministry of Electricity and Water (MEW. Furthermore the invested money is recovered during the assumed life cycle time whereas the payback period for both sites is about 15 years. This work contains worthwhile technical information for those who are interested in PV technology investment in Kuwait.
Energy-efficient three-phase bidirectional converter for grid-connected storage applications
International Nuclear Information System (INIS)
Colmenar-Santos, Antonio; Linares-Mena, Ana-Rosa; Velázquez, Jesús Fernández; Borge-Diez, David
2016-01-01
Highlights: • Storage control system developed based on AC DC three phase bidirectional converter. • Bidirectional AC DC converter for storage integration into distribution grids. • Efficiencies over 98% for values over 30% of the bidirectional converter rated power. • Sensitivity analysis of the parameters set by the transmission system operator. • Low-cost option for control and integration of new grid-connected storage systems. - Abstract: Grid connected energy storage systems are expected to play an essential role in the development of Smart Grids, providing, among other benefits, ancillary services to power grids. It is therefore crucial to design and develop control and conversion systems that represent the key instrument where intelligence for decision-making is applied, in order to validate and ensure its optimal operation as part and parcel of the electrical system. The present research describes the design and development of a battery energy storage system based on an AC-DC three-phase bidirectional converter capable of operating either in charge mode to store electrical energy, or in discharge mode to supply load demands. The design is modelled with MATLAB® Simulink® environment in order to evaluate the performance during load variations. Moreover, the assessment is complemented by a global sensitivity analysis for variations in the operating parameters set by the transmission system operator. The effectiveness of the simulation is confirmed by implementing the system and carrying out grid connection tests, obtaining efficiencies over 98% for values over the 30% of the bidirectional converter rated power.
Values and potentials of grid-connected solar photovoltaic applications in Malaysia
International Nuclear Information System (INIS)
Ahmad Hadri Haris; Iszuan Shah Syed Ismail
2006-01-01
Since early 1998, TNB Research Sdn Bhd has been conducting a pilot project to evaluate the performance and economics of grid-connected solar photovoltaic (PV) applications in Malaysia. The project is co-funded by Tenaga Nasional Berhad (TNB) and Malaysia Electricity Supply Industry Trust Account (MESITA). Currently, research project is being concluded with many valuable findings that would be able to provide the direction for the next solar PV development in Malaysia. In total, six pilot grid-connected solar PV systems were installed, where five are located within Klang Valley area and one in Port Dickson. The systems installation and commissioning were staggered between August 1998 to November 2001. A variety of building type was also selected for the system installation. In addition, various PV systems technologies and configurations were applied with average PV power capacity of 3 kW. These variances provide a good opportunity to assess the actual performances and economics of the solar PV applications under the Malaysian environment. This paper would discuss some of the findings, but with a focus on the values and potentials of the grid-connected solar PV applications in Malaysia
Cost reduction in PV manufacturing. Impact on grid-connected and building-integrated markets
International Nuclear Information System (INIS)
Maycock, Paul D.
1997-01-01
In the past three years there have been several key events or changes that can lead to fully economic, massive deployment to the grid-connected and central PV markets. The factors discussed in this report include: (1) significant cost reduction in single crystal and polycrystal silicon so that modules profitably priced at $3.10-$3.30 per peak watt and installed grid-connected systems with installed cost of $5.50 per watt are being offered; (2) several new thin film plants - amorphous silicon, cadmium telluride, and copper indium diselenide are being built for 1996, 1997 production with greatly reduced costs; (3) government subsidized volume orders for PV in grid-connected houses (Japan, Germany, Switzerland, Italy, and the United States) provide volume (2000+ units per year) that lead to reduced costs; (4) environmental benefits for PV are being applied in Europe and Japan permitting 'early adopters' to enter the market; and (5) government and commercial acceptance of PV building integrated products, especially in Europe, are expanding PV markets. The combination of these forces lead to the prediction that an 'accelerated' market mode could start in the year 2000
Microgrid energy management in grid-connected and islanding modes based on SVC
International Nuclear Information System (INIS)
Gabbar, Hossam A.; Abdelsalam, Abdelazeem A.
2014-01-01
Highlights: • SVC is used to enhance the performance of a microgrid (MG). • MG performance is measured by some key performance indicators (KPIs). • KPIs comprise power loss, voltage deviation, power factor, THD and v/f deviation. • The microgrid is simulated in grid-connected and islanded modes. • Results show SVC stabilizes voltage, reduce losses and THD and enhance power factor. - Abstract: Microgrids are small scale energy grids that can provide adequate energy supply to cover regional demand by integrating renewable energy generation and storage technologies. This paper develops a high performance dynamic model of a microgrid system comprising a wind turbine, a PV, a fuel cell, a micro gas turbine generator, an energy storage, electric loads with variable load profile and flexible AC transmission system (FACTS) devices. The FACTS devices based on static VAR compensators have been employed as a supervisory controller. Key performance indicators such as microgrid power losses, buses voltage deviations, buses power factor, buses voltage total harmonic distortion and voltage-frequency deviation are used to evaluate the performance of this microgrid in grid-connected and islanding modes. The results obtained from the Matlab/Simulink environment show that the proposed microgrid design with SVC has the ability to meet its special requirements such as bus voltages stabilization, reduction of feeder losses, power factor enhancement and mitigation of total harmonic distortion using SVC in grid-connected and islanding modes
Energy Technology Data Exchange (ETDEWEB)
Hedstroem, Jonas; Svensson, Stefan
2006-09-15
A performance database containing all grid-connected PV-systems in Sweden has been in operation since March 2002. The systems in the database are described in detail and energy production is continuously added in the form of monthly values. The energy production and the system descriptions are published on www.elforsk.se/solenergi. In august 2006 31 active systems were present in the database. As result of the Swedish subsidy program this number is expected to increase to over 100 systems in the next years. The new owners of PV-systems are obliged to report the produced electricity to the authorities at least once a year. In this work we have studied different means to simplify the collection of data. Four different methods are defined. 1. The conversion of readings from energy meters made at arbitrary distance in time into monthly values. 2. Methods to handle data obtained with the monitoring systems provided by different inverter manufactures. 3. Methods to acquire data from PV-systems with energy meters reporting to the green certificate system. 4. Commercial GSM/GPRS monitoring systems. The first method is the minimum level required by the authorities. The second and third methods are the use of equipments that are expected to be used by some PV-systems for other reasons. Method 4 gives a possibility to create a fully automatic collection method. The described GPRS-systems are expected to have an initial cost of roughly 4000 SEK and a yearly fee of 200 SEK (1 SEK {approx} 0.14 USD)
International Nuclear Information System (INIS)
Mitscher, Martin; Rüther, Ricardo
2012-01-01
We analyze the economic competitiveness of grid-connected, distributed solar photovoltaic generation through small-scale rooftop installations in five Brazilian state-capitals. The locations represent a comprehensive set of the two essential parameters for the economic viability of PV—solar irradiation and local electricity tariffs. Levelized electricity costs (LEC) for PV generation and net present values (NPV) for a specific PV system are presented. The analysis comprises three different interest rate scenarios reflecting different conditions for capital acquisition to finance the generators; subsidized, mature market and country-specific risk-adjusted interest. In the NPV analysis, revenue flow is modeled by the sale of PV electricity at current residential tariffs assuming net metering. Using subsidized interest rates, the analysis shows that solar PV electricity is already competitive in Brazil, while in the country-specific risk-adjusted rate, the declining, but still high capital costs of PV make it economically unfeasible. At a mature market interest rate, PV competitiveness is largely dependent on the residential tariff. Economic competitiveness in this scenario is given for locations with high residential tariffs. We demonstrate the high potential of distributed generation with photovoltaic installations in Brazil, and show that under certain conditions, grid-connected PV can be economically competitive in a developing country. - Highlights: ► Debt financed grid-connected PV on Brazilian rooftops can be economically feasible since 2011. ► The cost of capital in Brazil is the decisive parameter in PV competitiveness with conventional generation sources. ► Low-cost, long-term financing is an essential requirement for PV to become an economically justifiable generation alternative. ► The Brazilian market holds huge potential for distributed, residential rooftop PV systems of small size.
Grid-connected integrated community energy system. Volume II. Final report
Energy Technology Data Exchange (ETDEWEB)
1977-07-01
A preliminary feasibility analysis of a grid-connected ICES in the City of Independence, Missouri, is presented. It is found that the ICES concept can be made feasible in Independence by employing a 20-MW coal-fired boiler and turbine and using waste heat to provide the energy for heating and cooling commercial facilities with over 3 million square feet of floor space. When fully loaded thermally, the ICES results in favorable fuel utilization and energy conservation in comparison to conventional energy systems. The City of Independence is experienced with all of the institutional factors that may impact the ICES Demonstration Project.
RMS Current of a Photovoltaic Generator in Grid-Connected PV Systems: Definition and Application
Directory of Open Access Journals (Sweden)
P. J. Pérez
2008-01-01
Full Text Available This paper includes a definition of a new and original concept in the photovoltaic field, RMS current of a photovoltaic generator for grid-connected systems. The RMS current is very useful for calculating energy losses in cables used in a PV generator. As well, a current factor has been defined in order to simplify RMS current calculation. This factor provides an immediate (quick and easy calculation method for the RMS current that does not depend on the case particular conditions (orientation, location, etc.. RMS current and current factor values have been calculated for different locations and modules.
Grid-connected ICES: preliminary feasibility analysis and evaluation. Volume 3. Final report
Energy Technology Data Exchange (ETDEWEB)
None
1977-06-30
Maps, charts, and drawings of the Demonstration Community for the grid-connected ICES project composed of the medical complex in New Orleans (HEAL) are presented in Appendix A. The physical profile of the existing buildings and site plans is included. Demand profiles for steam, electric, gas, etc. are presented in Appendix B with extensive tables and graphs. Air quality and noise pollution data are presented in Appendix C. Data on financing in Appendix D are presented and also texts and information on revenue bonds are given. The final appendix gives qualifications for personnel for HEAL; NOSPI; de Laureal Engineers, Inc.; and Orr-Schelen-Mayeron and Associates, Inc.
The implantation of a grid-connected PV system at CEPEL
Energy Technology Data Exchange (ETDEWEB)
Galdino, Marco Antonio, E-mail: marcoag@cepel.br
2003-07-01
This technical report presents the experience undertaken by CEPEL for implantation of a grid connected PV system at its headquarters, located in Rio de Janeiro, RJ, Brazil. This technology, although considered far from Brazilian reach, is expected to grow significantly in the near future. The paper describes briefly several aspects concerning the PV system and the DAS (data acquisition system) implemented in order to allow the continuous evaluation of its performance and operational conditions. The system was installed in December, 2002, and the data are still preliminary. (author)
LCL-Filter Design for Robust Active Damping in Grid-Connected Converters
DEFF Research Database (Denmark)
Pena-Alzola, Rafael; Liserre, Marco; Blaabjerg, Frede
2014-01-01
in the grid inductance may compromise system stability, and this problem is more severe for parallel converters. This situation, typical of rural areas with solar and wind resources, calls for robust LCL-filter design. This paper proposes a design procedure with remarkable results under severe grid inductance......Grid-connected converters employ LCL-filters, instead of simple inductors, because they allow lower inductances while reducing cost and size. Active damping, without dissipative elements, is preferred to passive damping for solving the associated stability problems. However, large variations...
Research on grid connection control technology of double fed wind generator
Ling, Li
2017-01-01
The composition and working principle of variable speed constant frequency doubly fed wind power generation system is discussed in this thesis. On the basis of theoretical analysis and control on the modeling, the doubly fed wind power generation simulation control system is designed based on a TMS320F2407 digital signal processor (DSP), and has done a large amount of experimental research, which mainly include, variable speed constant frequency, constant pressure, Grid connected control experiment. The running results show that the design of simulation control system is reasonable and can meet the need of experimental research.
Generation-Side Power Scheduling in a Grid-Connected DC Microgrid
DEFF Research Database (Denmark)
Hernández, Adriana Carolina Luna; Aldana, Nelson Leonardo Diaz; Meng, Lexuan
2015-01-01
In this paper, a constrained mixed-integer programming model for scheduling the active power supplied by the generation units in storage-based DC microgrids is presented. The optimization problem minimizes operating costs taking into account a two-stage mode operation of the energy storage system...... so that a more accurate model for optimization of the microgrid operation can be obtained. The model is used in a particular grid-connected DC microgrid that includes two renewable energy sources and an energy storage system which supply a critical load. The results of the scheduling process...
DEFF Research Database (Denmark)
Török, Lajos; Mathe, Laszlo; Munk-Nielsen, Stig
2014-01-01
The purpose of this work was to investigate a three-phase-grid connected power supply using small DC link capacitor for electrolyser application. The hydrogen generation system requires low voltage and high current power supply. Thus the structure of the 3-phase power supply is defined as follows......: a three phase rectification, a small DC-link capacitor and a phase-shifted full-bridge converter with current doubler rectification. Design constraints and control problems are investigated. The advantages and problems caused by the use of small DC link capacitor are presented. The control of the system...
Selective Compensation of Voltage Harmonics in a Grid-Connected Microgrid
DEFF Research Database (Denmark)
Savaghebi, M.; Guerrero, Josep M.; Jalilian, A.
2011-01-01
In this paper, a method for selective voltage harmonic compensation in a grid-connected microgrid is presented. Harmonic compensation is done through proper control of distributed generators (DGs) interface converters. In order to achieve proper sharing of compensation effort among the DGs, a power...... named “Harmonic Distortion Power (HDP)” is defined. In the proposed method, active and reactive power control loops are considered to control the powers injected by the DGs. Also, a virtual impedance loop and voltage and current proportional-resonant controllers are included. Simulation results show...
DEFF Research Database (Denmark)
Zhang, Chi; Dragicevic, Tomislav; Vasquez, Juan Carlos
2014-01-01
LCL filters play an important role in grid-connected converters when trying to reduce switching-frequency ripple currents injected into the grid. Besides, their small size and low cost make them attractive for many practical applications. However, the LCL filter is a third-order system, which...... presents a resonance peak frequency. Oscillation will occur in the control loop in high frequency ranges, especially in current loop in double-loops controlled converters. In order to solve this, many strategies have been proposed to damp resonance, including passive and active methods. This paper makes...
Islanding detection technique using wavelet energy in grid-connected PV system
Kim, Il Song
2016-08-01
This paper proposes a new islanding detection method using wavelet energy in a grid-connected photovoltaic system. The method detects spectral changes in the higher-frequency components of the point of common coupling voltage and obtains wavelet coefficients by multilevel wavelet analysis. The autocorrelation of the wavelet coefficients can clearly identify islanding detection, even in the variations of the grid voltage harmonics during normal operating conditions. The advantage of the proposed method is that it can detect islanding condition the conventional under voltage/over voltage/under frequency/over frequency methods fail to detect. The theoretical method to obtain wavelet energies is evolved and verified by the experimental result.
DEFF Research Database (Denmark)
Hajizadeh, Amin; Shahirinia, Amir
2017-01-01
Investigation of an advanced control structure for integration of Photovoltaic Power Systems through Grid Connected-Modular Multilevel Converter (GC-MMC) is proposed in this paper. To achieve this goal, a non-linear model of MMC regarding considering of negative and positive sequence components has...... been presented. Then, due to existence of unbalance voltage faults in distribution grid, non-linarites and uncertainties in model, model predictive controller which is developed for GC-MMC. They are implemented based upon positive and negative components of voltage and current to mitigate the power...
Unified Impedance Model of Grid-Connected Voltage-Source Converters
DEFF Research Database (Denmark)
Wang, Xiongfei; Harnefors, Lennart; Blaabjerg, Frede
2018-01-01
This paper proposes a unified impedance model of grid-connected voltage-source converters for analyzing dynamic influences of the Phase-Locked Loop (PLL) and current control. The mathematical relations between the impedance models in the different domains are first explicitly revealed by means...... of complex transfer functions and complex space vectors. A stationary (αβ-) frame impedance model is then proposed, which not only predicts the stability impact of the PLL, but reveals also its frequency coupling effect explicitly. Furthermore, the impedance shaping effect of the PLL on the current control...... results and theoretical analysis confirm the effectiveness of the stationary-frame impedance model....
A Combined Two-Method MPPT Control Scheme for Grid-Connected Photovoltaic Systems
DEFF Research Database (Denmark)
Dorofte, Christinel; Borup, Uffe; Blaabjerg, Frede
2005-01-01
In order to increase the output efficiency of a grid-connected photovoltaic (PV) system it is important to have an efficient Maximum Power Point Tracker (MPPT). In the case of low irradiation, the Perturb and Observe (PO) and Incremental Conductance (IC) methods have a poor efficiency, because...... of the poor resolution in the acquired signals, when a fixed point implementation is done. A cost-effective two-method MPPT control scheme is proposed in this paper to track the maximum power point (MPP) at both low and high irradiation, by combining a Constant Voltage (CV) method and modified PO algorithm...
Energy Technology Data Exchange (ETDEWEB)
Larsson, Aake; Larsson, Richard [Vattenfall Power Consultants, Stockholm (Sweden)
2006-12-15
Grid connections of large power generating units normally require more detailed studies compared to small single units. The required R and D-level depends on the specific characteristics of the production units and the connecting grid. An inquiry for a grid connection will raise questions for the grid owner regarding transmission capability, losses, fault currents, relay protection, dynamic stability etc. Then only a few larger wind farms have been built, the experiences from these types of grid connections are limited and for that reason it can be difficult to identify issues appropriate for further studies. To ensure that electric power generating units do not have unacceptable impact on the grid, directions from the Swedish TSO (Svenska Kraftnaet) have been stated. The directions deal, for example, with power generation in specific ranges of voltage level and frequency and the possibility to remain connected to the grid when different faults occur. The requirements and the consequences of these directions are illustrated. There are three main issues that should be considered: Influence on the power flow from generating units regarding voltage level, currents, losses etc.; Different types of electric systems in generating units contribute to different levels of fault currents. For that reason the resulting fault current levels have to be studied; It is required that generating units should remain connected to the grid at different modes of operation and faults. These modes have to be verified. Load flow and dynamic studies normally demand computer models. Comprehensive models, for instance of wind farms, can bee difficult to design and normally large computer capacity is required. Therefore simplified methods to perform relevant studies are described. How to model an electric power generating unit regarding fault currents and dynamic stability is described. An inquiry for a grid connection normally brings about a discussion concerning administration. To make it
Investigation of Grid-connected Voltage Source Converter Performance under Unbalanced Faults
DEFF Research Database (Denmark)
Jia, Jundi; Yang, Guangya; Nielsen, Arne Hejde
2016-01-01
Renewable energy sources (RES) and HVDC links are typically interfaced with the grid by power converters, whose performance during grid faults is significantly different from that of traditional synchronous generators. This paper investigates the performance of grid-connected voltage source...... that the performance of VSCs varies with their control strategies. Negative-sequence current control is necessary to restrict converter current in each phase under unbalanced faults. Among presented control strategies, the balanced current control strategy complies with the present voltage support requirement best...
Harmonic Interaction Analysis in Grid-connected Converter using Harmonic State Space (HSS) Modeling
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
research about the harmonic interaction. However, it is found that the Linear Time Invariant (LTI) based model analysis makes it difficult to analyze these phenomena because of the time-varying properties of the power electronic based systems. This paper investigates grid-connected converter by using......An increasing number of power electronic based Distributed Generation (DG) systems and loads generate not only characteristic harmonics but also unexpected harmonics. Several methods like impedance based analysis, which are derived from the conventional average model, are introduced to perform...
Raji, Atanda K; Kahn, Mohamed T E
2015-01-01
The problems of increasing electricity demand by the unabated population and economy growth can be solved by employing sustainable distributed generation technologies. Convectional primary energy sources such as coal, liquid hydrocarbons' and natural gasses create environmental degradation and energy security problems. Even though the cost of solar energy is zero, the same cannot be said of a solar energy system. The system cost especially the initial capital investment has been hindering the...
DEFF Research Database (Denmark)
Ye, Tao; Dai, Ning-Yi; Lam, Chi-Seng
2015-01-01
. A Quasi-proportional-resonant (Quasi-PR) current controller is designed for the CGCI in this paper. Its modeling and parameter selection are studied in detail. In contrast with proportional-integration (PI) current controller, the Quasi-PR controller reduces steady-state error. It also generates a voltage...
DEFF Research Database (Denmark)
Huang, Min; Wang, Xiongfei; Loh, Poh Chiang
2014-01-01
damping method with an extra feedback provides a high rejection of the resonance so that the dynamic is improved. In this paper, taking a Proportional-Resonant (PR) together with a harmonic compensator (HC), resonant-inductor-voltage-feedback active damping is applied on an LLCL-filter based three...... of the proposed method is investigated in simulation and by experimental results....
Modelling and simulation of multiple single - phase induction motor in parallel connection
Directory of Open Access Journals (Sweden)
Sujitjorn, S.
2006-11-01
Full Text Available A mathematical model for parallel connected n-multiple single-phase induction motors in generalized state-space form is proposed in this paper. The motor group draws electric power from one inverter. The model is developed by the dq-frame theory and was tested against four loading scenarios in which satisfactory results were obtained.
Grid connectivity issues and the importance of GCC. [GCC - Grid Code Compliance
Energy Technology Data Exchange (ETDEWEB)
Das, A.; Schwartz, M.-K. [GL Renewable Certification, Malleswaram, Bangalore (India)
2012-07-01
In India, the wind energy is concentrated in rural areas with a very high penetration. In these cases, the wind power has an increasing influence on the power quality on the grids. Another aspect is the influence of weak grids on the operation of wind turbines. Hence it becomes very much essential to introduce such a strong grid code which is particularly applicable to wind sector and suitable for Indian environmental grid conditions. This paper focuses on different international grid codes and their requirement with regard to the connection of wind farms to the electric power systems to mitigate the grid connectivity issues. The requirements include the ways to achieve voltage and frequency stability in the grid-tied wind power system. In this paper, comparative overview and analysis of the main grid connecting requirements will be conducted, comprising several national and regional codes from many countries where high wind penetration levels have been achieved or are expected in the future. The objective of these requirements is to provide wind farms with the control and regulation capabilities encountered in conventional power plants and are necessary for the safe, reliable and economic operation of the power system. This paper also provides a brief idea on the Grid Code Compliance (GCC) certification procedure implemented by the leading accredited certifying body like Germanischer Lloyd Renewables Certification (GL RC), who checks the conformity of the wind turbines as per region specific grid codes. (Author)
Analysis of grid connected solar PV system in the Southeastern Part of Bangladesh
International Nuclear Information System (INIS)
Ariful Islam; Fatema Akther Shima; Akhera Khanam
2013-01-01
Bangladesh is a potential site of implementing renewable energy system to reduce the severe power crisis throughout the year. According to this, Chittagong is the southeastern part of Bangladesh is also a potential site for implementing renewable energy system such as grid-connected photovoltaic (PV) system. Financial viability and green-house gas emission reduction of solar PV as an electricity generation source are assessed for 500 kW grid connected solar PV system at University of Chittagong, Chittagong. Homer simulation soft-ware and monthly average solar radiation data from NASA is used for this task. In the proposed system monthly electricity generation varies between 82.65 MW h and 60.3 MW h throughout the year with a mean value of 68.25 MW h depending on the monthly highest and lowest solar radiation data. It is found that per unit electricity production cost is US$ 0.20 based on project lifetime 25 years. The IRR, equity payback and benefit-cost ratio shows favorable condition for development of the proposed solar PV system in this site. A minimum 664 tones of green-house gas emissions can be reduced annually utilizing the proposed system. (authors)
Intelligent Scheduling of a Grid-Connected Heat Pump in a Danish Detached House
DEFF Research Database (Denmark)
Gianniou, Panagiota; Foteinaki, Kyriaki; Heller, Alfred
This study proposes a methodology for intelligent scheduling of a heat pump installed in a refurbished grid-connected detached house in Denmark. This scheduling is conducted through the coupling of a dynamic building simulation tool with an optimization tool. The optimization of the operation of ...... thermal comfort conditions. The proposed methodology bridges dynamic building modelling with optimization of real-time operation of HVAC systems offering a detailed model for building physics, especially regarding thermal mass and a stochastic price-based control....... of the system is based on a price-signal considering a three-day period for different weather cases. The results show that the optimal scheduling of the system is successful in terms of reducing the peak load during times when electricity prices are high, thus achieving cost savings as well as maintaining good......This study proposes a methodology for intelligent scheduling of a heat pump installed in a refurbished grid-connected detached house in Denmark. This scheduling is conducted through the coupling of a dynamic building simulation tool with an optimization tool. The optimization of the operation...
Feasibility Study of Grid Connected PV-Biomass Integrated Energy System in Egypt
Barakat, Shimaa; Samy, M. M.; Eteiba, Magdy B.; Wahba, Wael Ismael
2016-10-01
The aim of this paper is to present a feasibility study of a grid connected photovoltaic (PV) and biomass Integrated renewable energy (IRE) system providing electricity to rural areas in the Beni Suef governorate, Egypt. The system load of the village is analyzed through the environmental and economic aspects. The model has been designed to provide an optimal system configuration based on daily data for energy availability and demands. A case study area, Monshaet Taher village (29° 1' 17.0718"N, 30° 52' 17.04"E) is identified for economic feasibility in this paper. HOMER optimization model plan imputed from total daily load demand, 2,340 kWh/day for current energy consuming of 223 households with Annual Average Insolation Incident on a Horizontal Surface of 5.79 (kWh/m2/day) and average biomass supplying 25 tons / day. It is found that a grid connected PV-biomass IRE system is an effective way of emissions reduction and it does not increase the investment of the energy system.
Grid-connected solar electricity in France : the example of Martinique, a French overseas department
Energy Technology Data Exchange (ETDEWEB)
Melle, Y. [Tenesol (France)
2006-07-01
Tenesol has specialized in photovoltaic (PV) solar energy since 1983 with experience in grid connections, professional applications, decentralized rural electrification and solar pumping. The company's operations include the manufacture of solar panels, system design and turnkey installations backed by a comprehensive after sales service through a global network of subsidiaries. Half of Tenesol's group shareholdings belong to Electricite de France and half belong to Total. The 2 specialized subsidiaries of Tenesol are Tenesa Manufacturing and Tenesol Technologies. This presentation focused Tenesol's operations in Martinique and its financial environment of grid-connected photovoltaics. It presented Tenesol's approach for technical and economic validation of roof suitability in terms of the disc orientation of PV panels. The key figures of installing a 300 square metre 40 kWp PV system were presented along with photographs of installations in Martinique. The installations have a total installed capacity of 2.5 MWp and an annual solar electricity production of 3,375,000 kWhs, resulting in a reduction of 3,000 tons of carbon dioxide annually. figs.
Distributed Optimisation Algorithm for Demand Side Management in a Grid-Connected Smart Microgrid
Directory of Open Access Journals (Sweden)
Omowunmi Mary Longe
2017-06-01
Full Text Available The contributions of Distributed Energy Generation (DEG and Distributed Energy Storage (DES for Demand Side Management (DSM purposes in a smart macrogrid or microgrid cannot be over-emphasised. However, standalone DEG and DES can lead to under-utilisation of energy generation by consumers and financial investments; in grid-connection mode, though, DEG and DES can offer arbitrage opportunities for consumers and utility provider(s. A grid-connected smart microgrid comprising heterogeneous (active and passive smart consumers, electric vehicles and a large-scale centralised energy storage is considered in this paper. Efficient energy management by each smart entity is carried out by the proposed Microgrid Energy Management Distributed Optimisation Algorithm (MEM-DOA installed distributively within the network according to consumer type. Each smart consumer optimises its energy consumption and trading for comfort (demand satisfaction and profit. The proposed model was observed to yield better consumer satisfaction, higher financial savings, and reduced Peak-to-Average-Ratio (PAR demand on the utility grid. Other associated benefits of the model include reduced investment on peaker plants, grid reliability and environmental benefits. The MEM-DOA also offered participating smart consumers energy and tariff incentives so that passive smart consumers do not benefit more than active smart consumers, as was the case with some previous energy management algorithms.
Probability of islanding in utility networks due to grid connected photovoltaic power systems
Energy Technology Data Exchange (ETDEWEB)
Verhoeven, B.
2002-09-15
This report for the International Energy Agency (IEA) made by Task 5 of the Photovoltaic Power Systems (PVPS) programme takes a look at the probability of islanding in utility networks due to grid-connected photovoltaic power systems. The mission of the Photovoltaic Power Systems Programme is to enhance the international collaboration efforts which accelerate the development and deployment of photovoltaic solar energy. Task 5 deals with issues concerning grid-interconnection and distributed PV power systems. This report summarises the results on a study on the probability of islanding in power networks with a high penetration level of grid connected PV-systems. The results are based on measurements performed during one year in a Dutch utility network. The measurements of active and reactive power were taken every second for two years and stored in a computer for off-line analysis. The area examined and its characteristics are described, as are the test set-up and the equipment used. The ratios between load and PV-power are discussed. The general conclusion is that the probability of islanding is virtually zero for low, medium and high penetration levels of PV-systems.
Implementation of MRAC controller of a DFIG based variable speed grid connected wind turbine
International Nuclear Information System (INIS)
Abdeddaim, Sabrina; Betka, Achour; Drid, Said; Becherif, Mohamed
2014-01-01
Highlights: • Set-up of an experimental test emulating a wind turbine, driving a grid-connected conventional DFIG. • An optimal operation below rated speed is achieved by means of an appropriate maximum power-point tracking algorithm. • Design and implementation of an adaptive model reference controller (MRAC) of the active and reactive power regulation. - Abstract: This paper presents the design and the implementation of a model reference adaptive control of the active and reactive power regulation of a grid connected wind turbine based on a doubly fed induction generator. This regulation is achieved below the synchronous speed, by means of a maximum power-point tracking algorithm. The experiment was conducted on a 1 kW didactic wound rotor induction machine in association with a wind turbine emulator. This implementation is realized using a dSPACE 1104 single-board control and acquisition interface. The obtained results show a permanent track of the available maximum wind power, under a chosen wind speed profile. Furthermore the proposed controller exhibits a smooth regulation of the stator active and reactive power amounts exchanged between the machine and the grid
A report on the performance of a grid connected photovoltaic power generation system
International Nuclear Information System (INIS)
Mohd Azhar Abdul Rahman; Mohd Surif Abdul Wahab; Azmi Omar
2000-01-01
Malaysia is located almost on the equator and is blessed with an abundance of sunlight almost all year round. So obviously, with the right planning and strategies that are coupled to the right technology and development in the market, the potential for photovoltaic system as an alternative source of power in this country looks promising and is constantly gaining ground and popularity. Sunlight is free and the photovoltaic system is also emission and pollution free which is a guest boost to the current worldwide effort to reduce the global environmental problems. Utility giant Tenaga Nasional Berhad is in line with the Government aspiration to promote the development of solar photovoltaic in the country, who believe in the success and acceptance potential of the photovoltaic system as an alternative source of power generation for long term energy option. In March 1998, a contract was awarded by Tenaga Nasional Berhad to its research subsidiary, Tenaga Nasional Research and Development Sdn. Bhd. to undertake a pilot research project on the development of a grid connected photovoltaic system. This research project is co-funded by the Electric Supply Industry Trust fund. One of the main objective of this research project is to seek the best approach to popularize the Grid Connected Photovoltaic System for domestic as well as suitable commercial premises in this country. This paper will report the initial findings of the project in terms of technical capability and commercial liability. (Author)
Energy Technology Data Exchange (ETDEWEB)
Suomalainen, Kiti
2006-01-15
An environmental life cycle assessment has been conducted for a 62 MW grid-connected photovoltaic installation to study the role of BOS components in the total environmental load. Also the influence of the current electricity supply has been investigated. For an alternative approach a net output approach has been used, where all electricity requirements are supplied by the photovoltaic installation itself. The components taken into account are monocrystalline silicon cells in frameless modules, steel support structures in concrete foundations, inverters, transformers, cables, transports and construction of roads and buildings. For stationary inert products without intrinsic energy requirements, such as cables, inverters, support structures etc., only raw material acquisition and processing are taken into account, since they are considered the most dominant stages in the life cycle. The results confirm a minor environmental load from BOS components compared to the module life cycle, showing approximately ten to twenty percent impact of the total. Uncertainties lie in the approximations for electronic devices as well as in the emissions from silicon processing. Concerning the electricity supply, the results differ considerably depending on which system perspective is used. In the net output approach the impacts decrease with approximately ninety percent from the traditional approach. Some increases are also shown in toxicity categories due to the increased module production needed for the enlargement of the installation.
Smart Energy Management and Control for Fuel Cell Based Micro-Grid Connected Neighborhoods
Energy Technology Data Exchange (ETDEWEB)
Dr. Mohammad S. Alam
2006-03-15
Fuel cell power generation promises to be an efficient, pollution-free, reliable power source in both large scale and small scale, remote applications. DOE formed the Solid State Energy Conversion Alliance with the intention of breaking one of the last barriers remaining for cost effective fuel cell power generation. The Alliance’s goal is to produce a core solid-state fuel cell module at a cost of no more than $400 per kilowatt and ready for commercial application by 2010. With their inherently high, 60-70% conversion efficiencies, significantly reduced carbon dioxide emissions, and negligible emissions of other pollutants, fuel cells will be the obvious choice for a broad variety of commercial and residential applications when their cost effectiveness is improved. In a research program funded by the Department of Energy, the research team has been investigating smart fuel cell-operated residential micro-grid communities. This research has focused on using smart control systems in conjunction with fuel cell power plants, with the goal to reduce energy consumption, reduce demand peaks and still meet the energy requirements of any household in a micro-grid community environment. In Phases I and II, a SEMaC was developed and extended to a micro-grid community. In addition, an optimal configuration was determined for a single fuel cell power plant supplying power to a ten-home micro-grid community. In Phase III, the plan is to expand this work to fuel cell based micro-grid connected neighborhoods (mini-grid). The economic implications of hydrogen cogeneration will be investigated. These efforts are consistent with DOE’s mission to decentralize domestic electric power generation and to accelerate the onset of the hydrogen economy. A major challenge facing the routine implementation and use of a fuel cell based mini-grid is the varying electrical demand of the individual micro-grids, and, therefore, analyzing these issues is vital. Efforts are needed to determine
Robustness analysis of the efficiency in PV inverters
DEFF Research Database (Denmark)
Pigazo, Alberto; Liserre, Marco; Blaabjerg, Frede
2013-01-01
topology and control strategy but also on the characteristics of the employed components. The aim of this paper is evaluate the effect of physical variations associated to the main components on the overall efficiency of PV inverters. It is concluded that a statistical evaluation of the power converter......During last years an increasing attention has been paid to the efficiency of grid-connected PV inverters. They are manufactured from a number of discrete components and by using a certain topology and control strategy. Hence, the performance of a certain PV inverter not only depends on the selected...
DEFF Research Database (Denmark)
Yang, Yongheng; Wang, Huai; Blaabjerg, Frede
2014-01-01
.g. Germany and Italy. Those advanced features can be provided by next generation PV systems, and will be enhanced in the future to ensure an even efficient and reliable utilization of PV systems. In light of this, Reactive Power Injection (RPI) strategies for single-phase PV systems are explored...... in this paper. The RPI possibilities are: a) constant average active power control, b) constant active current control, c) constant peak current control and d) thermal optimized control strategy. All those strategies comply with the currently active grid codes, but are with different objectives. The proposed...... RPI strategies are demonstrated firstly by simulations and also tested experimentally on a 1 kW singe-phase grid-connected system in LVRT operation mode. Those results show the effectiveness and feasibilities of the proposed strategies with reactive power control during LVRT operation. The design...
Reliable Grid Condition Detection and Control of Single-Phase Distributed Power Generation Systems
DEFF Research Database (Denmark)
Ciobotaru, Mihai
standards addressed to the grid-connected systems will harmonize the combination of the DPGS and the classical power plants. Consequently, the major tasks of this thesis were to develop new grid condition detection techniques and intelligent control in order to allow the DPGS not only to deliver power...... to the utility grid but also to sustain it. This thesis was divided into two main parts, namely "Grid Condition Detection" and "Control of Single-Phase DPGS". In the first part, the main focus was on reliable Phase Locked Loop (PLL) techniques for monitoring the grid voltage and on grid impedance estimation...... techniques. Additionally, a new technique for detecting the islanding mode has been developed and successfully tested. In the second part, the main reported research was concentrated around adaptive current controllers based on the information provided by the grid condition detection techniques. To guarantee...
Directory of Open Access Journals (Sweden)
Menxi Xie
2017-06-01
Full Text Available High performance synchronization methord is citical for grid connected power converter. For single-phase system, power based phase-locked loop(pPLL uses a multiplier as phase detector(PD. As single-phase grid voltage is distorted, the phase error information contains ac disturbances oscillating at integer multiples of fundamental frequency which lead to detection error. This paper presents a new scheme based on moving average filter(MAF applied in-loop of pPLL. The signal characteristic of phase error is dissussed in detail. A predictive rule is adopted to compensate the delay induced by MAF, thus achieving fast dynamic response. In the case of frequency deviate from nomimal, estimated frequency is fed back to adjust the filter window length of MAF and buffer size of predictive rule. Simulation and experimental results show that proposed PLL achieves good performance under adverse grid conditions.
International Nuclear Information System (INIS)
Abdoulaye, D; Koalaga, Z; Zougmore, F
2012-01-01
This paper deals with a key solution for power outages problem experienced by many African countries and this through grid-connected photovoltaic (PV) systems with batteries storage. African grids are characterized by an insufficient power supply and frequent interruptions. Due to this fact, users who especially use classical grid-connected photovoltaic systems are unable to profit from their installation even if there is sun. In this study, we suggest the using of a grid-connected photovoltaic system with batteries storage as a solution to these problems. This photovoltaic system works by injecting the surplus of electricity production into grid and can also deliver electricity as a stand-alone system with all security needed. To achieve our study objectives, firstly we conducted a survey of a real situation of one African electrical grid, the case of Burkina Faso (SONABEL: National Electricity Company of Burkina). Secondly, as study case, we undertake a sizing, a modeling and a simulation of a grid-connected PV system with batteries storage for the LAME laboratory at the University of Ouagadougou. The simulation shows that the proposed grid-connected system allows users to profit from their photovoltaic installation at any time even if the public electrical grid has some failures either during the day or at night.
Optimal sizing of a hybrid grid-connected photovoltaic and wind power system
International Nuclear Information System (INIS)
González, Arnau; Riba, Jordi-Roger; Rius, Antoni; Puig, Rita
2015-01-01
Highlights: • Hybrid renewable energy systems are efficient mechanisms to generate electrical power. • This work optimally sizes hybrid grid-connected photovoltaic–wind power systems. • It deals with hourly wind, solar irradiation and electricity demand data. • The system cost is minimized while matching the electricity supply with the demand. • A sensitivity analysis to detect the most critical design variables has been done. - Abstract: Hybrid renewable energy systems (HRES) have been widely identified as an efficient mechanism to generate electrical power based on renewable energy sources (RES). This kind of energy generation systems are based on the combination of one or more RES allowing to complement the weaknesses of one with strengths of another and, therefore, reducing installation costs with an optimized installation. To do so, optimization methodologies are a trendy mechanism because they allow attaining optimal solutions given a certain set of input parameters and variables. This work is focused on the optimal sizing of hybrid grid-connected photovoltaic–wind power systems from real hourly wind and solar irradiation data and electricity demand from a certain location. The proposed methodology is capable of finding the sizing that leads to a minimum life cycle cost of the system while matching the electricity supply with the local demand. In the present article, the methodology is tested by means of a case study in which the actual hourly electricity retail and market prices have been implemented to obtain realistic estimations of life cycle costs and benefits. A sensitivity analysis that allows detecting to which variables the system is more sensitive has also been performed. Results presented show that the model responds well to changes in the input parameters and variables while providing trustworthy sizing solutions. According to these results, a grid-connected HRES consisting of photovoltaic (PV) and wind power technologies would be
DEFF Research Database (Denmark)
Tan, Jin; Wang, Xiao Ru; Chen, Zhe
2013-01-01
In order to study the stability of a grid-connected direct-drive permanent magnet synchronous generator (PMSG) wind turbine systems, this paper presents the modal analysis of a PMSG wind turbine system. A PMSG model suitable for small signal stability analysis is presented. The modal properties...... of a grid-connected PMSG wind turbine system are studied. Then the comprehensive impacts of the shaft model, shaft parameters, operation points and lengths of the transmission line on the modal characteristic of the system are investigated by the eigenvalue analysis method. Meanwhile, the corresponding...... analysis. It offers a better understanding about the essence of the stability of grid-connected PMSG wind turbine system....
Energy Technology Data Exchange (ETDEWEB)
Arifujjaman, Md.
2011-07-01
In order to recover the maximum energy from small scale wind turbine systems many parameters have to be controlled. The aim of this paper is to propose a control strategy for the grid connected PMG-based small wind turbine systems. A mathematical model of small wind turbine systems was developed and the system simulated. Results show demonstrated that the control strategy is highly efficient. Sure enough it reduces the dependence on system variables, diminishes the system complexity, its furling and maximum power point controllers are efficient and it provides a stable operation for multiple wind speeds. This study developed a modeling and control strategy which was proved to be feasible by simulation results.
Directory of Open Access Journals (Sweden)
Yavuz Ates
2016-05-01
Full Text Available The renewable energy-based distributed generation (DG implementation in power systems has been an active research area during the last few decades due to several environmental, economic and political factors. Although the integration of DG offers many advantages, several concerns, including protection schemes in systems with the possibility of bi-directional power flow, are raised. Thus, new protection schemes are strongly required in power systems with a significant presence of DG. In this study, an adaptive protection strategy for a distribution system with DG integration is proposed. The proposed strategy considers both grid-connected and islanded operating modes, while the adaptive operation of the protection is dynamically realized considering the availability of DG power production (related to faults or meteorological conditions in each time step. Besides, the modular structure and fast response of the proposed strategy is validated via simulations conducted on the IEEE 13-node test system.
Control Strategies for Trap Filter Interfaced Three-Phase Grid Connected Converters
DEFF Research Database (Denmark)
Min, Huang
In order to utilize renewable energy systems power electronics are needed to convert the energy to grid. The AC-DC and DC-AC power conversion are dominant in wind power system and photovoltaic system. However, the use of PWM scheme introduces undesirable harmonics. In order to enhance the grid...... damping in order to stabilize the whole system with resonance issue. LC trap filter application for current source converters to reduce the size of the filter and get a higher power factor....... integration of the renewable energy systems, the filter plays an important role. Even though this topic has already been widely studied, there are many optimizations and problems should be solved. How to design a filter for grid-connected converters in distributed generation system to get a lower loss...
Performance analysis of a grid connected photovoltaic park on the island of Crete
International Nuclear Information System (INIS)
Kymakis, Emmanuel; Kalykakis, Sofoklis; Papazoglou, Thales M.
2009-01-01
The favorable climate conditions of the island of Crete and the recent legislation for utilization of renewable energy sources provide a substantial incentive for installation of photovoltaic power plants. In this paper, the grid connected photovoltaic park of C. Rokas SA in Sitia, Crete, is presented, and its performance is evaluated. The photovoltaic park has a peak power of 171.36 kW p and has been in operation since 2002. The park is suitably monitored during 1 year, and the performance ratio and the various power losses (temperature, soiling, internal, network, power electronics, grid availability and interconnection) are calculated. The PV park supplied 229 MW h to the grid during 2007, ranging from 335.48 to 869.68 kW h. The final yield (Y F ) ranged from 1.96 to 5.07 h/d, and the performance ratio (PR) ranged from 58 to 73%, giving an annual PR of 67.36%
Online model-based fault detection for grid connected PV systems monitoring
Harrou, Fouzi
2017-12-14
This paper presents an efficient fault detection approach to monitor the direct current (DC) side of photovoltaic (PV) systems. The key contribution of this work is combining both single diode model (SDM) flexibility and the cumulative sum (CUSUM) chart efficiency to detect incipient faults. In fact, unknown electrical parameters of SDM are firstly identified using an efficient heuristic algorithm, named Artificial Bee Colony algorithm. Then, based on the identified parameters, a simulation model is built and validated using a co-simulation between Matlab/Simulink and PSIM. Next, the peak power (Pmpp) residuals of the entire PV array are generated based on both real measured and simulated Pmpp values. Residuals are used as the input for the CUSUM scheme to detect potential faults. We validate the effectiveness of this approach using practical data from an actual 20 MWp grid-connected PV system located in the province of Adrar, Algeria.
Grid connection of active stall wind farms using a VSC based DC transmission system
DEFF Research Database (Denmark)
Iov, F.; Sørensen, Poul Ejnar; Hansen, A.D.
2005-01-01
Currently, there is an increasing trend to connect large MW wind farms to the transmission system. Requirements that focus on the influence of the farms on the grid stability and power quality, and on the control capabilities of wind farms have already been established. The main trends of modern...... wind turbines/farms are clearly the variable speed operation and a grid connection through a power electronic interface, especially using doubly fed induction generators. Using power electronics the control capabilities of these wind turbines/farms are extended and thus the grid requirements...... are fulfilled. However, the traditional squirrel-cage generators based wind turbines/wind farms directly connected to the grid have less control capabilities. These wind turbines/farms cannot regulate their production and contribute to power system stability. A DC transmission system for connection...
Hysteresis current control technique of VSI for compensation of grid-connected unbalanced loads
DEFF Research Database (Denmark)
Pouresmaeil, Edris; Akorede, Mudathir Funsho; Montesinos-Miracle, Daniel
2014-01-01
interconnection issues that usually arise as DG units connect to the electric grid. The proposed strategy, implemented in Matlab/Simulink environment in different operating scenarios, provides compensation for active, reactive, unbalanced, and harmonic current components of grid-connected nonlinear unbalanced...... resources as they connect to the exiting power grid could provoke many power quality problems on the grid side. For this reason, due considerations must be given to power generation and safe running before DG units is actually integrated into the power grid. The main aim of this paper is to address the grid...... loads. The simulation results obtained in this study demonstrate the level of accuracy of the proposed technique, which ensure a balance in the overall grid phase currents, injection of maximum available power from DG resources to the grid, improvement of the utility grid power factor, and a reduction...
Mitigation of Voltage and Current Harmonics in Grid-Connected Microgrids
DEFF Research Database (Denmark)
Savaghebi, Mehdi; Guerrero, Josep M.; Jalilian, Alireza
2012-01-01
In this paper, a control approach is proposed for selective compensation of main voltage and current harmonics in grid-connected microgrids. Two modes of compensation are considered, i.e. voltage and current compensation modes. In the case that sensitive loads are connected to the point of common...... coupling (PCC), voltage compensation mode is activated in order to provide a high voltage quality at PCC. Otherwise, grid current harmonics are mitigated (current compensation mode) in order to avoid excessive harmonic supply by the grid. In both modes, harmonic compensation is achieved through proper...... control of distributed generators (DGs) interface converters. The compensation effort of each harmonic is shared considering the corresponding current harmonic supplied by the DGs. The control system of each DG comprises harmonic compensator, power controllers, voltage and current controllers and virtual...
DEFF Research Database (Denmark)
Li, H.; Zhao, B.; Yang, C.
2011-01-01
based on normal form theory is proposed. The transient models of the wind turbine generation system including the flexible drive train model are derived based on the direct transient stability estimation method. A method of critical clearing time (CCT) calculation is developed for the transient......Increasing levels of wind energy in modern electrical power system is initiating a need for accurate analysis and estimation of transient stability of wind turbine generation systems. This paper investigates the transient behaviors and possible direct methods for transient stability evaluation...... of a grid-connected wind turbine with squirrel cage induction generator (SCIG). Firstly, by using an equivalent lump mass method, a three-mass wind turbine equivalent model is proposed considering both the blades and the shaft flexibility of the wind turbine drive train system. Combined with the detailed...
Online model-based fault detection for grid connected PV systems monitoring
Harrou, Fouzi; Sun, Ying; Saidi, Ahmed
2017-01-01
This paper presents an efficient fault detection approach to monitor the direct current (DC) side of photovoltaic (PV) systems. The key contribution of this work is combining both single diode model (SDM) flexibility and the cumulative sum (CUSUM) chart efficiency to detect incipient faults. In fact, unknown electrical parameters of SDM are firstly identified using an efficient heuristic algorithm, named Artificial Bee Colony algorithm. Then, based on the identified parameters, a simulation model is built and validated using a co-simulation between Matlab/Simulink and PSIM. Next, the peak power (Pmpp) residuals of the entire PV array are generated based on both real measured and simulated Pmpp values. Residuals are used as the input for the CUSUM scheme to detect potential faults. We validate the effectiveness of this approach using practical data from an actual 20 MWp grid-connected PV system located in the province of Adrar, Algeria.
Grid-connected polymer solar panels: initial considerations of cost, lifetime, and practicality
DEFF Research Database (Denmark)
Medford, Andrew James; Lilliedal, Mathilde Raad; Jørgensen, Mikkel
2010-01-01
Large solar panels were constructed from polymer solar cell modules prepared using full roll-to-roll (R2R) manufacture based on the previously published ProcessOne. The individual flexible polymer solar modules comprising multiple serially connected single cell stripes were joined electrically...... and laminated between a 4 mm tempered glass window and black Tetlar foil using two sheets of 0.5 mm thick ethylene vinyl acetate (EVA). The panels produced up to 8 W with solar irradiance of ~960 Wm−2, and had outer dimensions of 1 m x 1.7 m with active areas up to 9180 cm2. Panels were mounted on a tracking...... station and their output was grid connected between testing. Several generations of polymer solar cells and panel constructions were tested in this context to optimize the production of polymer solar panels. Cells lacking a R2R barrier layer were found to degrade due to diffusion of oxygen after less than...
International Nuclear Information System (INIS)
Joergensen, Claus; Ropenus, Stephanie
2008-01-01
In liberalized power markets, there are significant power price fluctuations due to independently varying changes in demand and supply, the latter being substantial in systems with high wind power penetration. In such systems, hydrogen production by grid connected electrolysis can be cost optimized by operating an electrolyzer part time. This paper presents a study on the minimization of the hydrogen production price and its dependence on estimated power price fluctuations. The calculation of power price fluctuations is based on a parameterization of existing data on wind power production, power consumption and power price evolution in the West Danish power market area. The price for hydrogen is derived as a function of the optimal electrolyzer operation hours per year for four different wind penetration scenarios. It is found to amount to 0.41-0.45 EUR/Nm 3 . The study further discusses the hydrogen price sensitivity towards investment costs and the contribution from non-wind power sources. (author)
Microgrid Restraining Strategy Based on Improved DC Grid Connected DFIG Torque Ripple
Fei, Xia; Yang, Zhixiong; Zongze, Xia
2017-05-01
Aiming to the voltage of the stator side is generated by the modulation of the SSC in the improved topology, especially under the circumstance with the asymmTeric fault of stator side, DFIG’s electromagnTeic torque, amplifies ripple of grid-connected power for the grid side. The novel control mTehod suitable to stator side converter and rotor side converter based on reduced-order resonant controller (RORC) is proposed in this thesis, DFIG’s torque and output power performance are improved. Under the RORC control conditions the transfer functions of stator current and torque control system are established, the amplitude characteristic and the system stability of RORC control are analysed. The simulation results in Matlab/Simulink verify the correctness and validity of the proposed mTehod.
Lv, Z. H.; Li, Q.; Huang, R. W.; Liu, H. M.; Liu, D.
2016-08-01
Based on the discussion about topology structure of integrated distributed photovoltaic (PV) power generation system and energy storage (ES) in single or mixed type, this paper focuses on analyzing grid-connected performance of integrated distributed photovoltaic and energy storage (PV-ES) systems, and proposes a comprehensive evaluation index system. Then a multi-level fuzzy comprehensive evaluation method based on grey correlation degree is proposed, and the calculations for weight matrix and fuzzy matrix are presented step by step. Finally, a distributed integrated PV-ES power generation system connected to a 380 V low voltage distribution network is taken as the example, and some suggestions are made based on the evaluation results.
Energy Technology Data Exchange (ETDEWEB)
Meier, Ch.; Frei, R.
2001-07-01
This final report for the Swiss Federal Office of Energy describes the development of a performance guarantee for the power delivered by grid-connected photovoltaic (PV) power plant. This is important for investors, who need to be able to calculate the price of the energy produced by the PV plant. The report examines the results of various case studies and experience gained with GRS contracts developed in different countries including Switzerland, the Netherlands, France and Germany. The problems encountered, which provided feedback for the further development of the contract presented in the report, are discussed. The model contract, which proposes a framework which provides many possible variations and adaptations, is presented in detail. Various problem areas such as guaranteed energy yield, meteorological references, correction methods, failure detection, dispute settlement and many other points are covered.
Performance Ratios of Grid Connected Photovoltaic Systems and Theory of Errors
Directory of Open Access Journals (Sweden)
Javier Vilariño-García
2016-07-01
Full Text Available A detailed analysis of the different levels of dynamic performance of grid connected photovoltaic systems and its interface based on the development of a block diagram explaining the course of energy transformation from solar radiation incident on the solar modules until it becomes useful energy available in the mains. Indexes defined by the Spanish standard UNE-EN 61724: Monitoring photovoltaic systems: Guidelines for measurement, data exchange and analysis, are explained from the basics fundaments of block algebra and the transfer function of linear systems. The accuracy requirements demanded by the aforementioned standard for measuring these parameters are discussed in the theory of errors and the real limits of the results obtained.