Stochastic seismic floor response analysis method for various damping systems
International Nuclear Information System (INIS)
Kitada, Y.; Hattori, K.; Ogata, M.; Kanda, J.
1991-01-01
A study using the stochastic seismic response analysis method which is applicable for the estimation of floor response spectra is carried out. It is pointed out as a shortcoming in this stochastic seismic response analysis method, that the method tends to overestimate floor response spectra for low damping systems, e.g. 1% of the critical damping ratio. An investigation on the cause of the shortcoming is carried out and a number of improvements in this method were also made to the original method by taking correlation of successive peaks in a response time history into account. The application of the improved method to a typical BWR reactor building is carried out. The resultant floor response spectra are compared with those obtained by deterministic time history analysis. Floor response spectra estimated by the improved method consistently cover the response spectra obtained by the time history analysis for various damping ratios. (orig.)
The seismic response and floor spectra of OL3 NPP buildings in Finland
International Nuclear Information System (INIS)
Pentti Varpasuo
2005-01-01
The purpose of the present work is the computation of seismic response and floor spectra of the nuclear power plant OL3 buildings in Olkiluoto. The following OL3 plant buildings were included in the analysis: 1. the Reactor Building UJA/UJB; 2. the Safeguard Buildings UJH/UJK 1-4; 3. and the Fuel Building UFA The in-structure spectra were generated using the ground motion response spectra documented in YVL GUIDE 2.6 'Seismic events at nuclear power plants' issued by Finnish Centre of Radiation Protection. The floor spectra were computed for the following equipment damping values: 2%, 4%, 7%, and 10%. The joint model for the plant buildings was generated. All analyses were linear and the direct time integration method was used with time step of 0.001 sec. All response runs were carried out with MSC/Nastran general purpose structural analysis program. The development of floor spectra has been carried out in accordance with the US NRC -Regulatory Guide 1.122: 'Development of Floor Design Response Spectra for Seismic Design of Floor-Supported Equipment or Components'. The response results show that the dominant frequencies of the reactor building are located around 5 Hz in frequency space and that the typical amplification of spectral peaks for 4% damping is from 8 -10 times when compared to peak ground acceleration. (authors)
Seismic response of free standing fuel rack construction to 3-D floor motion
International Nuclear Information System (INIS)
Soler, A.I.; Singh, K.
1983-01-01
Seismic analysis of free standing submerged racks is complicated by the presence of water and structural non-linearities such as fuel assembly cell impact and floor interface friction. A direct time integration technique has been proposed to analyze this class of structures. Application of the time integration technique on a fourteen degree of freedom lumped mass model of the rack reveals some heretofore unpublished quirks in the structure's behavior. The method of analysis is utilized to compare the seismic response of some representative rack designs. Results show wide differences in the structural response, depending on the fabrication details of racks
International Nuclear Information System (INIS)
Anon.
1979-01-01
This guide presents an acceptable method for developing two horizontal and one vertical floor design response spectra at various floor or other equipment-support locations from the time-history motions resulting from the dynamic analysis of the supporting structure. These floor design response spectra are used in the dynamic analysis of systems or equipment supported at various locations of the supporting structure. Consulation has been provided by the Advisory Committee on Reactor Safeguards
Tool for generation of seismic floor response spectra for secondary system design
International Nuclear Information System (INIS)
Cardoso, Tarcisio F.; Almeida, Andreia A. Diniz de
2009-01-01
The spectral analysis is still a valuable method to the seismic structure design, especially when one focalizes the topics of secondary systems in large industrial installations, as nuclear power plants. Two aspects of this situation add their arguments to recommend the use of this kind of analysis: the random character of the excitation and the multiplicity and the variability of the secondary systems. The first aspect can be managed if one assumes the site seismicity represented by a power spectrum density function of the ground acceleration, and then, by the systematic resolution of a first passage problem, to develop a uniformly probable response spectrum. The second one suggests also a probabilistic approach to the response spectrum in order to be representative all over the extensive group of systems with different characteristics, which can be enrolled in a plant. The present paper proposes a computational tool to achieve in-structure floor response spectra for secondary system design, which includes a probabilistic approach and considers coupling effects between primary and inelastic secondary systems. The analysis is performed in the frequency domain, with SASSI2000 system. A set of auxiliary programs are developed to consider three-dimensional models and their responses to a generic base excitation, acting in 3 orthogonal directions. The ground excitation is transferred to a secondary system SDOF model conveniently attached to the primary system. Then, a uniformly probable coupled response spectrum is obtained using a first passage analysis. In this work, the ExeSASSI program is created to manage SASSI2000 several modules and a set of auxiliary programs created to perform the probabilistic analyses. (author)
Floor response spectra of WWER-1000, NPP Kozloduy generated from local seismic excitation
International Nuclear Information System (INIS)
Bojadziev, Z.; Kostov, M.
1996-01-01
The seismic review level characteristics for the Kozloduy NPP site were set to 0.2 g and a respective free field acceleration response spectra were derived after a profound site conformation project. Accordingly a separate investigation is recommended for local seismic excitation. The goals of the analyses are: to define the seismic motion characteristics from local seismic sources; to perform structural analyses and in-structure spectra generation for local seismic excitation; and to compare the forces (spectra) from local events with those generated as seismic design review basis
International Nuclear Information System (INIS)
Anon.
1993-01-01
''Reactor Site Criteria,'' requires, in part, that safety-related structures, systems, and components remain functional in the event of a Safe Shutdown Earthquake (SSE). It specifies the use of a suitable dynamic analysis as one method of ensuring that the structures, systems, and components can withstand the seismic loads. Similarly, paragraph (a)(2) of Section VI of the same appendix requires, in part, that the structures, systems, and components necessary for continued operation without undue risk to the health and safety of the public remain functional in the event of an Operating Basis Earthquake (OBE). Again, the use of suitable dynamic analysis is specified as one method of ensuring that the structures, systems, and components can withstand the seismic loads. This guide describes methods acceptable to the NRC staff for developing two horizontal and one vertical floor design response spectra at various floors or other equipment-support locations of interest from the time-history motions resulting from the dynamic analysis of the supporting structure. These floor design response spectra are needed for the dynamic analysis of the systems or equipment supported at various locations of the supporting structure
Floor response spectra for seismic qualification of Kozloduy VVER 440-230 NPP
Energy Technology Data Exchange (ETDEWEB)
Kostov, M.K. [Bulgarian Academy of Sciences, Sofia (BG). Central Lab. for Seismic Mechanics and Earthquake Engineering; Ma, D.C. [Argonne National Lab., IL (United States); Prato, C.A. [Univ. of Cordoba (AR); Stevenson, J.D. [Stevenson and Associates, Cleveland, OH (US)
1993-08-01
In this paper the floor response spectra generation methodology for Kozloduy NPP, Unit 1-2 of VVER 440-230 is presented. The 2D coupled soil-structure interaction models are used combined with a simplified correction of the final results for accounting of torsional effects. Both time history and direct approach for in-structure spectra generation are used and discussion of results is made.
Floor response spectra for seismic qualification of Kozloduy VVER 440-230 NPP
International Nuclear Information System (INIS)
Kostov, M.K.; Prato, C.A.; Stevenson, J.D.
1993-01-01
In this paper the floor response spectra generation methodology for Kozloduy NPP, Unit 1-2 of VVER 440-230 is presented. The 2D coupled soil-structure interaction models are used combined with a simplified correction of the final results for accounting of torsional effects. Both time history and direct approach for in-structure spectra generation are used and discussion of results is made
Development of generic floor response spectra for equipment qualification for seismic loads
International Nuclear Information System (INIS)
Curren, J.R.; Costantino, C.J.
1984-01-01
A generic floor response spectra has been developed for use in the qualification of electrical and mechanical equipment in operating nuclear power plants. Actual PWR and BWR - Mark I structural models were used as representative of a class of structures. For each model, the stiffness properties were varied, with the same mass, so as to extend the fundamental base structure natural frequency from 2 cps to 36 cps. This resulted in fundamental mode coupled natural frequencies as low as 0.86 cps and as high as 30 cps. The characteristics of 1000 floor response spectra were studied to determine the generic spectra. A procedure for its application to any operating plant has been established. The procedure uses as much or as little information that currently exists at the plant relating to the question of equipment qualification. A generic floor response spectra is proposed for the top level of a generic structure. Reduction factors are applied to the peak acceleration for equipment at lower levels
Development of generic floor response spectra for equipment qualification for seismic loads
International Nuclear Information System (INIS)
Curreri, J.R.; Costantino, C.J.
1984-10-01
A generic floor response spectra has been developed for use in the qualification of electrical and mechanical equipment in operating nuclear power plants. Actual PWR and BWR - Mark I structural models were used as representative of a class of structures. For each model, the stiffness properties were varied, with the same mass, so as to extend the fundamental base structure natural frequency from 2 cps to 36 cps. This resulted in fundamental mode coupled natural frequencies as low as 0.86 cps and as high as 30 cps. The characteristics of 1000 floor response spectra were studied to determine the generic spectra. A procedure for its application to any operating plant has been established. The procedure uses as much or as little information that currently exists at the plant relating to the question of equipment qualification. A generic floor response spectra is proposed for the top level of a generic structure. Reduction factors are applied to the peak acceleration for equipment at lower levels
International Nuclear Information System (INIS)
Sakurai, A.; Shiojiri, H.; Aoyagi, S.; Matsuda, T.; Fujimoto, S.; Sasaki, Y.; Hirayama, H.
1987-01-01
The NSSS isolation floor vibration characteristics were made clear. Especially, the side support bearing (rubber bearing) is effective for horizontal floor motion restraint and rocking motion control. Seismic isolation effects for responses of the reactor components can be sufficiently expected, using the vertical seismic isolation floor. From the analytical and experimental studies, the following has been concluded: (1) Seismic isolation structure, which is suitable for large pool-type LMFBR, were proposed. (2) Seismic response characteristics of the seismic isolation structure were investigated. It was made clear that the proposed seismic isolation (Combination of the isolated building and the isolated NSSS floor) was effective. (orig./HP)
An alternative procedure for direct generation of seismic floor spectra
International Nuclear Information System (INIS)
Singh, M.P.; Sharma, A.M.
1983-01-01
Several approaches have been developed for generation of floor spectra which do not require seismic inputs in the form of acceleration time histories but can use a prescribed set of ground response spectra directly. These approaches are often referred to as direct approaches. Most of these approaches are based on the method of mode displacement of structural dynamics. Some problems can, however, occur with these approaches if the response of a system is affected by the high frequency modes and if these modes are omitted from the analyses. Herein an alternative approach based on the method of mode acceleration is proposed wherein the effect of high frequency modes is correctly included without their explicit evaluation. The seismic inputs in this approach are required to be prescribed in terms of relative acceleration and velocity spectra. The approach is very effective for the calculation of floor spectra for structural systems which have significant contribution from high frequency modes, and also for floors close to the base which are usually affected by the higher modes. In other cases too, this approach has been shown to provide better results than the mode displacement approach for a given number of modes used in the analysis. Thus, a general use of this approach in lieu of the mode displacement approach is advocated. (orig.)
Development of a 3-dimensional seismic isolation floor for computer systems
International Nuclear Information System (INIS)
Kurihara, M.; Shigeta, M.; Nino, T.; Matsuki, T.
1991-01-01
In this paper, we investigated the applicability of a seismic isolation floor as a method for protecting computer systems from strong earthquakes, such as computer systems in nuclear power plants. Assuming that the computer system is guaranteed for 250 cm/s 2 of input acceleration in the horizontal and vertical directions as the seismic performance, the basic design specification of the seismic isolation floor is considered as follows. Against S 1 level earthquakes, the maximum acceleration response of the seismic isolation floor in the horizontal and vertical directions is kept less than 250 cm/s 2 to maintain continuous computer operation. Against S 2 level earthquakes, the isolation floor allows large horizontal movement and large displacement of the isolation devices to reduce the acceleration response, although it is not guaranteed to be less than 250 cm/s 2 . By reducing the acceleration response, however, serious damage to the computer systems is reduced, so that they can be restarted after an earthquake. Usually, seismic isolation floor systems permit 2-dimensional (horizontal) isolation. However, in the case of just-under-seated earthquakes, which have large vertical components, the vertical acceleration response of this system is amplified by the lateral vibration of the frame of the isolation floor. Therefore, in this study a 3-dimensional seismic isolation floor, including vertical isolation, was developed. This paper describes 1) the experimental results of the response characteristics of the 3-dimensional seismic isolation floor built as a trial using a 3-dimensional shaking table, and 2) comparison of a 2-dimensional analytical model, for motion in one horizontal direction and the vertical direction, to experimental results. (J.P.N.)
Seismic proving test of process computer systems with a seismic floor isolation system
International Nuclear Information System (INIS)
Fujimoto, S.; Niwa, H.; Kondo, H.
1995-01-01
The authors have carried out seismic proving tests for process computer systems as a Nuclear Power Engineering Corporation (NUPEC) project sponsored by the Ministry of International Trade and Industry (MITI). This paper presents the seismic test results for evaluating functional capabilities of process computer systems with a seismic floor isolation system. The seismic floor isolation system to isolate the horizontal motion was composed of a floor frame (13 m x 13 m), ball bearing units, and spring-damper units. A series of seismic excitation tests was carried out using a large-scale shaking table of NUPEC. From the test results, the functional capabilities during large earthquakes of computer systems with a seismic floor isolation system were verified
Energy Technology Data Exchange (ETDEWEB)
Jussila, Vilho [VTT Technical Research Centre of Finland Ltd, Kemistintie 3, 02230 Espoo (Finland); Li, Yue [Dept. of Civil Engineering, Case Western Reserve University, Cleveland, OH 44106 (United States); Fülöp, Ludovic, E-mail: ludovic.fulop@vtt.fi [VTT Technical Research Centre of Finland Ltd, Kemistintie 3, 02230 Espoo (Finland)
2016-12-01
Highlights: • Floor flexibility plays a non-negligible role in amplifying horizontal vibrations. • COV of in-floor horizontal and vertical acceleration are 0.15–0.25 and 0.25–0.55. • In-floor variation of vibrations is higher in lower floors. • Floor spectra from limited nodes underestimates vibrations by a factor of 1.5–1.75. - Abstract: Floor vibration of a reactor building subjected to seismic loads was investigated, with the aim of quantifying the variability of vibrations on each floor. A detailed 3D building model founded on the bedrock was excited simultaneously in three directions by artificial accelerograms compatible with Finnish ground response spectra. Dynamic simulation for 21 s was carried out using explicit time integration. The extracted results of the simulation were acceleration in several floor locations, transformed to pseudo-acceleration (PSA) spectra in the next stage. At first, the monitored locations on the floors were estimated by engineering judgement in order to arrive at a feasible number of floor nodes for post processing of the data. It became apparent that engineering judgment was insufficient to depict the key locations with high floor vibrations, which resulted in un-conservative vibration estimates. For this reason, a more systematic approach was later considered, in which nodes of the floors were selected with a more refined grid of 2 m. With this method, in addition to the highest PSA peaks in all directions, the full vibration distribution in each floor can be determined. A statistical evaluation of the floor responses was also carried out in order to define floor accelerations and PSAs with high confidence of non-exceedance. The conclusion was that in-floor variability can be as high as 50–60% and models with sufficiently dense node grids should be used in order to achieve a realistic estimate of floor vibration under seismic action. The effects of the shape of the input spectra, damping, and flexibility of the
International Nuclear Information System (INIS)
Jussila, Vilho; Li, Yue; Fülöp, Ludovic
2016-01-01
Highlights: • Floor flexibility plays a non-negligible role in amplifying horizontal vibrations. • COV of in-floor horizontal and vertical acceleration are 0.15–0.25 and 0.25–0.55. • In-floor variation of vibrations is higher in lower floors. • Floor spectra from limited nodes underestimates vibrations by a factor of 1.5–1.75. - Abstract: Floor vibration of a reactor building subjected to seismic loads was investigated, with the aim of quantifying the variability of vibrations on each floor. A detailed 3D building model founded on the bedrock was excited simultaneously in three directions by artificial accelerograms compatible with Finnish ground response spectra. Dynamic simulation for 21 s was carried out using explicit time integration. The extracted results of the simulation were acceleration in several floor locations, transformed to pseudo-acceleration (PSA) spectra in the next stage. At first, the monitored locations on the floors were estimated by engineering judgement in order to arrive at a feasible number of floor nodes for post processing of the data. It became apparent that engineering judgment was insufficient to depict the key locations with high floor vibrations, which resulted in un-conservative vibration estimates. For this reason, a more systematic approach was later considered, in which nodes of the floors were selected with a more refined grid of 2 m. With this method, in addition to the highest PSA peaks in all directions, the full vibration distribution in each floor can be determined. A statistical evaluation of the floor responses was also carried out in order to define floor accelerations and PSAs with high confidence of non-exceedance. The conclusion was that in-floor variability can be as high as 50–60% and models with sufficiently dense node grids should be used in order to achieve a realistic estimate of floor vibration under seismic action. The effects of the shape of the input spectra, damping, and flexibility of the
Vulnerability and floor spectra of seismically isolated structures
International Nuclear Information System (INIS)
Pham, K.H.
2010-09-01
This thesis was motivated by issues that arise regarding the use of the method of seismic isolation in the nuclear industry. Despite the research conducted during the last decades in the field of seismic isolation, many questions about the behavior of isolated structures remain. These questions concern, on the one hand, the vulnerability of these structures, due to an excursion (unexpected) in the post-linear domain, and on the other hand, phenomena that can lead to a significant excitation of none isolated modes. Furthermore, unlike previous work studying the seismic behavior of buildings, an important part of this thesis is devoted to the behavior of equipment through the study of floor spectra. Firstly, the probability of failure, in the case of nonlinear response of the superstructure, was studied with simple models, for different laws of nonlinear behavior and different types of support. Then, the effects of heavy damping were investigated and the mechanism of amplification of the response of non-isolated modes has been explained. To resolve the amplification problem of none isolated modes, the mixed isolated systems, combining passive isolation with semi-active devices, have been considered. The numerical analyses confirm the effectiveness of this approach. Finally, a series of shaking table tests on a simple model with two degrees of freedom was conducted. The model is equipped with a magneto-rheological damper which is controlled as a semi-active device. The comparison of the experimental results with those of numerical simulations shows that the models developed are able to represent satisfactorily the essential physical phenomena. (author)
International Nuclear Information System (INIS)
Curreri, J.; Costantino, C.; Subudhi, M.; Reich, M.
1983-09-01
Generic floor response spectra were developed for use in the qualification of electrical and mechanical equipment in operating nuclear power plants. The characteristics of 1000 floor response spectra were studied to determine the generic spectra. The procedure developed uses as much or as little information that currently exists at the plant relating to the question of equipment qualification. The general approach was to study the effects on the dynamic characteristics of each of the elements in the chain of events that goes between the loads and the responses. This includes the loads, the soils and the structures. A free-field earthquake response spectra was used to generate horizontal earthquake time histories. The excitation was applied through the soil and into the various structures to produce responses in equipment. An entire range of soil conditions was used with each structure. Actual PWR and BWR - Mark I structural models were used. For each model, the stiffness properties were varied, with the same mass, so as to extend the fundamental base structure natural frequency from 2 cps to 36 cps. The natural frequencies of the structures were varied to obtain maximum response conditions. The actual properties were first used to locate the natural frequencies. The stiffness properties were than varied, with the same mass, to extend the range of the fundamental base structure natural frequency. The intention was to have the coupled structural material frequencies in the vicinity of the peak amplitude frequency content of the excitation spectrum. Particular attention was therefore given to the frequency band between 2 Hz and 4 Hz. A horizontal generic floor response spectra is proposed for the top level of a generic structure. Reduction factors are applied to the peak acceleration for equipment at lower levels
Seismic analysis and design of steel beam - thick slab floor systems
International Nuclear Information System (INIS)
Reed, P.W.
1981-01-01
This paper presents a method for seismic analysis and design of floor systems composed of thick reinforced concrete slabs supported by steel beams. The response spectrum modal analysis is used to determine the dynamic response of an orthotropic finite element model. An approximate approach to find the fundamental frequency is explained, allowing an actual acceleration to be determined. The fundamental mode is found to be a major portion of the overall response, whereas the secondary modes are shown to result in a very small portion of the overall response. Dynamic multipliers for the fundamental mode and significant secondary modes are given for several typical floor layouts. These would be used to find equivalent static stress resultants which are used to design the floor. (orig.)
Floor response spectra of buildings with uncertain structural properties
International Nuclear Information System (INIS)
Chen, P.C.
1975-01-01
All Category I equipment, such as reactors, vessels, and major piping systems of nuclear power plants, is required to withstand earthquake loadings in order to minimize risk of seismic damage. The equipment is designed by using response spectra of the floor on which the equipment is mounted. The floor response spectra are constructed usually from the floor response time histories which are obtained through a deterministic dynamic analysis. This analysis assumes that all structural parameters, such as mass, stiffness, and damping have been calculated precisely, and that the earthquakes are known. However, structural parameters are usually difficult to determine precisely if the structures are massive and/or irregular, such as nuclear containments and its internal structures with foundation soil incorporated into the analysis. Faced with these uncertainties, it has been the practice to broaden the floor response spectra peaks by +-10 percent of the peak frequencies on the basis of conservatism. This approach is based on engineering judgement and does not have an analytical basis to provide a sufficient level of confidence in using these spectra for equipment design. To insure reliable design, it is necessary to know structural response variations due to variations in structural properties. This consideration leads to the treatment of structural properties as random variables and the use of probabilistic methods to predict structural response more accurately. New results on floor response spectra of buildings with uncertain structural properties obtained by determining the probabilistic dynamic response from the deterministic dynamic response and its standard deviation are presented. The resulting probabilistic floor response spectra are compared with those obtained deterministically, and are shown to provide a more reliable method for determining seismic forces
Generation of floor response spectra for PFBR RCB
International Nuclear Information System (INIS)
Sajish, S.D.; Ramakrishna, V.; Chellapandi, P.; Chetal, S.C.
2003-01-01
This paper describes the generation of floor time histories and corresponding floor response spectrums at various locations in reactor containment building (RCB) for 500 MWe Prototype Fast Breeder Reactor (PFBR). The RCB and its internal structures are modeled with equivalent 3D-beam elements (stick model), which have got the essential global stiffness and inertial properties of the corresponding building. The main aspect in the simulation of beam model is derivation of equivalent cross sectional properties such as bending, torsional and shear rigidities including shear centers. These properties have been obtained through 3D plate/shell element models with appropriate kinematic constraints, for the zones between floors of corresponding buildings. The stick model includes a set of springs and dampers to simulate soil effects, on which base raft and various sticks are mounted. The soil stiffness and damping values are derived based on equations given in ASCE-98. Time history analysis has been done using three uncorrelated time histories, which are derived from the site dependent design response spectra. Floor time histories (FTH) are extracted at important locations from which the corresponding floor response spectrums (FRS) have been generated for various damping values. Peak broadening of the response spectrums has been done according ASCE criteria. Floor response spectrum corresponds to reactor assembly support shows amplification 2.5 for SSE and 3 for OBE. CASTEM 3M is used for seismic analysis and generation of FRS. (author)
International Nuclear Information System (INIS)
Rong Feng; Wang Jiachun; He Shuyan
2006-01-01
Analysis of Soil-Structure Interaction (SSI) and calculation of Floor Response Spectrum (FRS) is substantial for anti-seismic design for China Advanced Research Reactor (CARR) project. The article uses direct method to analyze the seismic reaction of the reactor building in considering soil-structure interaction by establishing two-dimensional soil-structure co-acting model for analyzing and inputting of seismic waves from three directions respectively. The seismic response and floor response spectrum of foundation and floors of the building under different cases have been calculated. (authors)
International Nuclear Information System (INIS)
Gantenbein, F.; Aguilar, J.
1983-08-01
The purpose of this paper is the evaluation of seismic response and floor spectra for a typical PWR 900 reactor building with respect to soil-structure interaction for soil stiffness). The typical PWR 900 reactor building consists of a concrete cylindrical external building and roof dome, a concrete internal structure (internals) on a common foundation mat as illustrated. The seismic response is obtained by SRSS method and floor spectra directly from ground spectrum and modal properties of the structure. Seismic responses and floor spectra computation is performed in the case of two different ground spectra: EDF spectrum (mean of oscillator spectra obtained from 8 californian records) normalized to 0.2 g, and DSN spectrum (typical of shallow seism) normalized to 0.3 g. The first section is devoted to internals' modelisation, the second one to the axisymmetric model of the reactor, the third one to the seismic response, the fourth one to floor spectra
Evaluation of Floor Response Spectrum considering Ductility of Structure
International Nuclear Information System (INIS)
Park, Junhee; Choi, In-Kil
2014-01-01
The FRS (floor response spectrum) is directly influenced by the behavior of structure under the seismic load. If the structure is nonlinear range, the energy dissipation will be occurred by the damage of structure and the maximum force will be reduced. In Zion method, the inelastic energy abortion factor has been used to consider the nonlinearity of structure. This factor was used for the seismic fragility of structure. For the seismic fragility of equipment, the uncertainty of this factor was used differently according to the story level. But this method is not warranted under the strong earthquake leads to the structural damage. Therefore it is needed to evaluate the FRS considering the nonlinear behavior of structure and to assessment the conservatism related to nonlinear behavior of structure in FRS. In this study, the nonlinear analysis was performed for the conservatism of FRS under the damage of structure. The conservatism of FRS by the nonlinear analysis was compared by that proposed by the Zion method. The conservatism of floor acceleration response for the equipment was evaluated by performing the nonlinear analysis. From the nonlinear analysis results, it was showed that the median and β c of FRSR was increased with the ductility of structure and the response of equipment had the resonance effect between the frequency of equipment and structure. The seismic capacity of equipment by the Zion method can be different from the real seismic capacity of equipment because the inelastic structure response factor has nothing to do with the ductility of structure. Therefore the median and COV for FRSR should be defined considering the ductility of structure and the frequency of equipment for more exactly evaluating the seismic capacity of equipment
Evaluation of Floor Response Spectrum considering Ductility of Structure
Energy Technology Data Exchange (ETDEWEB)
Park, Junhee; Choi, In-Kil [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2014-10-15
The FRS (floor response spectrum) is directly influenced by the behavior of structure under the seismic load. If the structure is nonlinear range, the energy dissipation will be occurred by the damage of structure and the maximum force will be reduced. In Zion method, the inelastic energy abortion factor has been used to consider the nonlinearity of structure. This factor was used for the seismic fragility of structure. For the seismic fragility of equipment, the uncertainty of this factor was used differently according to the story level. But this method is not warranted under the strong earthquake leads to the structural damage. Therefore it is needed to evaluate the FRS considering the nonlinear behavior of structure and to assessment the conservatism related to nonlinear behavior of structure in FRS. In this study, the nonlinear analysis was performed for the conservatism of FRS under the damage of structure. The conservatism of FRS by the nonlinear analysis was compared by that proposed by the Zion method. The conservatism of floor acceleration response for the equipment was evaluated by performing the nonlinear analysis. From the nonlinear analysis results, it was showed that the median and β{sub c} of FRSR was increased with the ductility of structure and the response of equipment had the resonance effect between the frequency of equipment and structure. The seismic capacity of equipment by the Zion method can be different from the real seismic capacity of equipment because the inelastic structure response factor has nothing to do with the ductility of structure. Therefore the median and COV for FRSR should be defined considering the ductility of structure and the frequency of equipment for more exactly evaluating the seismic capacity of equipment.
Seismic isolation floor and vibration control equipment for nuclear power plant
International Nuclear Information System (INIS)
Niwa, H.; Fujimoto, S.; Aida, Y.; Miyano, H.
1996-01-01
We have developed a seismic isolation floor to improve protection against earthquakes for process computer systems, and a magnetic dynamic damper to reduce the mechanical vibrations of piping systems and pumps in nuclear power plants. Seismic excitation tests of the seismic isolation floor, on which process computer systems were installed, were performed using large earthquake simulators. The test results proved that the seismic isolation floor significantly reduced seismic forces. To control mechanical vibrations, a magnetic dynamic damper was designed using permanent magnets. This magnetic dynamic damper does not require mechanical springs, dampers and supports in the floors and walls of the building. Vibration tests using a rotating machine model confirmed that the magnetic dynamic damper effectively controlled vibrations in such a rotating machine model. (author)
Analysis of design floor response spectra and testing of the electrical systems
International Nuclear Information System (INIS)
Ambriashvili, Y.
1996-01-01
This report covers the following activities as foreseen according to the working plan of 'Atmoenergoproject': analysis of calculated floor response spectra used during the design of Kozloduy NPP and comparison with other spectra recommended for this NPP; analysis of floor response spectrum for the most important systems (reactor, main coolant loop, electrical systems); tests of main electrical systems and analysis of the results on seismic stability of those systems. Results of the response spectra analysis are given, some of the electrical systems are identified by the Kozloduy authorities to be analyzed in future according to the results of the test on seismicity
A comparison of floor response spectra techniques
International Nuclear Information System (INIS)
Yan, M.J.; Galford, J.E.
1983-01-01
Floor response spectra (FRS) conventionally have been generated using a time-history method. Babcock and Wilcox has developed a new technique, the Fast Floor Response Spectra (FFRS) method, in which dynamic analyses are done entirely in the frequency domain. This paper compares the two techniques and demonstrates that the FFRS method complies with the 'equivalency' and 'conservatism' requirements of the US NRC's Standard Review Plan. The upper end of a once-through steam generator in the B and W 205 nuclear steam supply system (NSSS) was used to demonstrate that the FFRS method is equivalent to the time-history technique. The two techniques were compared with respect to frequency content and magnitude of response for a given point on the structure. First, the specified forcing function was described in terms of an acceleration time history and an acceleration spectra enveloping that time history. The time-history forcing function was then used in a direct transient analysis to determine the response at the specified point on the NSSS. The resultant response was subsequently converted to a floor response spectra for that point. To show that the FFRS method gave equivalent and conservative results, the FFRS technique was used to determine the modal response directly from the spectral description of the forcing function. The FFRS- and time-history-generated data agreed to within 13 (worst case on conservative side) of each other with the former cutting analytical costs by 99%. (orig./HP)
Seismic responses of unanchored electrode storage fixtures
International Nuclear Information System (INIS)
Ting-shu Wu; Blomquist, C.A.; Haupt, H.J.; Herceg, J.E.
1993-01-01
Two anchored electrode storage fixtures will be installed in the process cell of the Integral Fast Reactor's Fuel Cycle Facility at ANL-W in Idaho. In addition to the concerns for structural integrity, the potential for uplifting and tipping of the fixtures during the design basis earthquake must also be examined. In the analysis, a response-spectrum method was employed to investigate tipping, while a static approach was used for the structural-integrity evaluations. The results show that the combined stresses from seismic and other loads are within the allowables permitted by the design codes. The overall vertical seismic reaction forces at the leveling pads are compressive, implying that the fixtures will remain in contact with the floor. No uplifting or tipping of the fixture will occur during the design basis earthquake
International Nuclear Information System (INIS)
Shyu, Y.-S.; Luh, Gary G.; Blum, Arie
2004-01-01
This paper proposes a procedure for generating floor response spectra compatible time histories used for equipment seismic qualification in nuclear power plants. From the 84th percentile power spectrum density function of an earthquake ensemble of four randomly generated time history motions, a statistically equivalent time history can be obtained by converting the power spectrum density function from the frequency domain into the time domain. With minor modification, if needed, the converted time history will satisfy both the spectral and the power spectrum density enveloping criteria, as required by the USNRC per Revision 2 of the Standard Review Plan, Section 3.7.1. Step-by-step generating procedures and two numerical examples are presented to illustrate the applications of the methodology. (author)
Seismic isolation - efficient procedure for seismic response assessement
International Nuclear Information System (INIS)
Zamfir, M. A.; Androne, M.
2016-01-01
The aim of this analysis is to reduce the dynamic response of a structure. The seismic isolation solution must take into consideration the specific site ground motion. In this paper will be presented results obtained by applying the seismic isolation method. Based on the obtained results, important conclusions can be outlined: the seismic isolation device has the ability to reduce seismic acceleration of the seismic isolated structure to values that no longer present a danger to people and environment; the seismic isolation solution is limiting devices deformations to safety values for ensuring structural integrity and stability of the entire system; the effective seismic energy dissipation and with no side effects both for the seismic isolated building and for the devices used, and the return to the initial position before earthquake occurence are obtained with acceptable permanent displacement. (authors)
Analysis of Bi-directional Effects on the Response of a Seismic Base Isolation System
International Nuclear Information System (INIS)
Park, Hyung-Kui; Kim, Jung-Han; Kim, Min Kyu; Choi, In-Kil
2014-01-01
The floor response spectrum depends on the height of the floor of the structure. Also FRS depends on the characteristics of the seismic base isolation system such as the natural frequency, damping ratio. In the previous study, the floor response spectrum of the base isolated structure was calculated for each axis without considering bi-directional effect. However, the shear behavior of the seismic base isolation system of two horizontal directions are correlated each other by the bi-directional effects. If the shear behavior of the seismic isolation system changes, it can influence the floor response spectrum and displacement response of isolators. In this study, the analysis of a bi-directional effect on the floor response spectrum was performed. In this study, the response of the seismic base isolation system based on the bi-directional effects was analyzed. By analyzing the time history result, while there is no alteration in the maximum shear force of seismic base isolation system, it is confirmed that the shear force is generally more decreased in a one-directional that in a two-directional in most parts. Due to the overall decreased shear force, the floor response spectrum is more reduced in a two-directional than in a one-directional
Seismic response of base isolated auxiliary building with age related degradation
International Nuclear Information System (INIS)
Park, Jun Hee; Choun, Young Sun; Choi, In Kil
2012-01-01
The aging of an isolator affects not only the mechanical properties of the isolator but also the dynamic properties of the upper structure, such as the change in stiffness, deformation capacity, load bearing capacity, creep, and damping. Therefore, the seismic response of base isolated structures will change with time. The floor response in the base isolated nuclear power plants (NPPs) can be particularly changed because of the change in stiffness and damping for the isolator. The increased seismic response due to the aging of isolator can cause mechanical problems for many equipment located in the NPPs. Therefore, it is necessary to evaluate the seismic response of base isolated NPPs with age related degradation. In this study, the seismic responses for a base isolated auxiliary building of SHIN KORI 3 and 4 with age related degradation were investigated using a nonlinear time history analysis. Floor response spectrums (FRS) were presented with time for identifying the change in seismic demand under the aging of isolator
Use and generation of floor response spectra
International Nuclear Information System (INIS)
Ordonez Villalobos, A.
1983-01-01
One of the main objectives of the dynamic analysis of the structures of a nuclear power plant is the determination of the dynamic input that these structures transmit to the equipment and substructures they support, usually given as Floor Response Spectra (FRS). A close collaboration and feedback between the different groups that use and develop the FRS, is considered to be a very important factor in order to adapt the scope and content of the FRS to the precision required for a proper analysis or testing of the equipment; not only for the action of simple events but also for multiple combined actions. These aspects should be evaluated not only in the final stages of qualification of the equipment users schedules do not coincide with the schedules of the analysis group that develops the FRS. Different mechanisms of interchange of information and colaboration are suggested in order to optimize the availability, use and production of FRS. In the aspect of FRS generation, different procedures are reviewed including the direct procedures, not only for FRS but also for secondary FRS that are needed for the evaluation of equipment supported on other equipment or subsystems. It is concluded that in many cases, the direct procedures can be developed economically with the advantage that is easy to take into account the variability not only of the transfer function (including damping, stiffness and modal mass ratio). Different probabilities of excedence levels can be stabilized in order to obtain a more realistic dynamic response of the equipment. These last aspects can contribute to a more flexible procedure for the availability and generation of the FRS. (orig./HP)
Floor Response Spectra of a Base Isolated Auxiliary Building in Different Temperature Environments
International Nuclear Information System (INIS)
Park, Junhee; Choun, Youngsun; Choi, Inkil
2013-01-01
It is necessary to investigate the aging effect of degradation factors and to evaluate the seismic response of base isolated NPPs with age-related degradation. In this study, the seismic responses for NPPs using high damping rubber bearing with age-related degradation in different temperature were investigated by performing a nonlinear time history analysis. The floor response spectrums (FRS) were presented with time in different temperature environments. The degradation of HRB is found to be particularly sensitive to the ambient temperature. The increase of HRB stiffness leads to the increase of FRS it was observed that the seismic demand for equipment located in the AUX was changed. Therefore it is required that the seismic evaluation for the isolation system (e. g. isolators, equipment located in isolated structure) is performed considering the temperature environments. From the seismic fragility analysis, the seismic capacity of cabinet was affected by the degradation of HRB. Therefore the isolators in the isolated buildings should be carefully designed and manufactured considering the degradation during the life time
Determination of the NPP Cernavoda reactor building seismic response
International Nuclear Information System (INIS)
Krutzik, N.J.; Rotaru, I.; Bobei, M.; Mingiuc, C.; Serban, V.
1997-01-01
Seismic input for systems and equipment installed in buildings depends on: - the seismic movement in free field on site; - the building movement in the soil; - the building deflection. The percentage of the 3 movements for the system and equipment input, depends on the position of the systems and equipment inside the building as well on the type of the foundation soil. The type of the foundation soil is important because if it is stiff it transfers a lot of energy to the building, energy which amplify the movement of the building on the top. If the foundation soil is soft, it accommodates the overall movement of the building in the soil, amplifying the movement to lower levels and the building response is attenuated if a resonance phenomenon between the whole building movement and the seismic excitation does not exist. This input is given with the design floor response spectra (FRS), in the logarithmic scale and seismic anchor movement (SAM). The design floor response spectra for NPP Cernavoda U1 Nuclear Building were determined in several stages starting with simple models (STICK type) without twisting movement and ending with detailed 3-dimensional models. From the point of view of dynamic behavior, the Reactor Building can be considered to be made up of 4 sub-structures: the containment building, internal structures containing separate elements such as the reactor vault, the fuel transfer structure and itself. Each sub-structure has its own movement (some of the structures present also some local effects) which combines with the overall movement of the building in the soil and the seismic excitation produce the total movement so that the response spectrum for each point of the sub-structure is specific. One should note that for structures which also show the twisting effect, the selection of the points on the floor, for the determination on the response spectra, is an engineering decision so that the response should be relevant for the equipment installed on the
Generation of floor response spectra for mixed-oxide fuel fabrication plants
International Nuclear Information System (INIS)
Arthur, D.F.; Murray, R.C.; Tokarz, F.J.
1975-01-01
Floor or amplified response spectra are generally used as input motion for seismic analysis of critical equipment and piping in nuclear power plants and related facilities. The floor spectra are normally the result of a time-history calculation of building response to ground shaking. However, alternate approximate methods have been suggested by both Kapur and Biggs. As part of a study for the Nuclear Regulatory Commission horizontal floor response spectra were generated and compared by all three methods. The dynamic analyses were performed on a model of the Westinghouse Recycle Fuels Plant Manufacturing Building (MOFFP). Input to the time-history calculations was a synthesized accelerogram whose response spectrum is similar to that in Regulatory Guide 1.60. The response spectrum of the synthetic ground motion was used as input to the Kapur and Biggs methods. Calculations were performed for both hard (3500 fps) and soft (1500 fps) foundation soils. Results of comparison of the three methods indicate that although the approximate methods could easily be made acceptable from a safety standpoint, they would be overly conservative. The time-history method will yield floor spectra which are less uncertain and less conservative for a relatively modest additional effort. (auth)
Site response assessment using borehole seismic records
Energy Technology Data Exchange (ETDEWEB)
Park, Donghee; Chang, Chunjoong; Choi, Weonhack [KHNP Central Research Institute, Daejeon (Korea, Republic of)
2014-05-15
In regions with high seismic activity, such as Japan, the Western United States and Taiwan, borehole seismometers installed deep underground are used to monitor seismic activity during the course of seismic wave propagation at various depths and to study the stress changes due to earthquakes and analyze the connection to fault movements. The Korea Meteorological Administration (KMA) and the Korea Institute of Geology and Mining (KIGAM) have installed and are operating borehole seismometers at a depth of 70∼100 meters for the precise determination of epicenters. Also, Korea Hydro and Nuclear Power Co., Ltd. (KHNP) has installed and is operating 2 borehole seismic stations near Weolseong area to observe at a depth of 140 meters seismic activities connected to fault activity. KHNP plans to operate in the second half of 2014 a borehole seismic station for depths less than 300 and 600 meters in order to study the seismic response characteristics in deep strata. As a basic study for analyzing ground motion response characteristics at depths of about 300 to 600 meters in connection with the deep geological disposal of spent nuclear fuel, the present study examined the background noise response characteristics of the borehole seismic station operated by KHNP. In order to analyze the depth-dependent impact of seismic waves at deeper depths than in Korea, seismic data collected by Japan's KIK-net seismic stations were used and the seismic wave characteristics analyzed by size and depth. In order to analyze the borehole seismic observation data from the seismic station operated by KHNP, this study analyzed the background noise characteristics by using a probability density function.
Site response assessment using borehole seismic records
International Nuclear Information System (INIS)
Park, Donghee; Chang, Chunjoong; Choi, Weonhack
2014-01-01
In regions with high seismic activity, such as Japan, the Western United States and Taiwan, borehole seismometers installed deep underground are used to monitor seismic activity during the course of seismic wave propagation at various depths and to study the stress changes due to earthquakes and analyze the connection to fault movements. The Korea Meteorological Administration (KMA) and the Korea Institute of Geology and Mining (KIGAM) have installed and are operating borehole seismometers at a depth of 70∼100 meters for the precise determination of epicenters. Also, Korea Hydro and Nuclear Power Co., Ltd. (KHNP) has installed and is operating 2 borehole seismic stations near Weolseong area to observe at a depth of 140 meters seismic activities connected to fault activity. KHNP plans to operate in the second half of 2014 a borehole seismic station for depths less than 300 and 600 meters in order to study the seismic response characteristics in deep strata. As a basic study for analyzing ground motion response characteristics at depths of about 300 to 600 meters in connection with the deep geological disposal of spent nuclear fuel, the present study examined the background noise response characteristics of the borehole seismic station operated by KHNP. In order to analyze the depth-dependent impact of seismic waves at deeper depths than in Korea, seismic data collected by Japan's KIK-net seismic stations were used and the seismic wave characteristics analyzed by size and depth. In order to analyze the borehole seismic observation data from the seismic station operated by KHNP, this study analyzed the background noise characteristics by using a probability density function
Seismic Responses of an Added-Story Frame Structure with Viscous Dampers
Cheng, Xuansheng; Jia, Chuansheng; Zhang, Yue
2014-01-01
The damping ratio of an added-story frame structure is established based on complex damping theory to determine the structure seismic response. The viscous dampers are selected and arranged through target function method. A significant damping effect is obtained when a small velocity index is selected. The seismic responses of a five-floor reinforced concrete frame structure with directly added light steel layers and light steel layers with viscous dampers are compared with the finite element...
Seismic response analyses for reactor facilities at Savannah River
International Nuclear Information System (INIS)
Miller, C.A.; Costantino, C.J.; Xu, J.
1991-01-01
The reactor facilities at the Savannah River Plant (SRP) were designed during the 1950's. The original seismic criteria defining the input ground motion was 0.1 G with UBC [uniform building code] provisions used to evaluate structural seismic loads. Later ground motion criteria have defined the free field seismic motion with a 0.2 G ZPA [free field acceleration] and various spectral shapes. The spectral shapes have included the Housner spectra, a site specific spectra, and the US NRC [Nuclear Regulatory Commission] Reg. Guide 1.60 shape. The development of these free field seismic criteria are discussed in the paper. The more recent seismic analyses have been of the following type: fixed base response spectra, frequency independent lumped parameter soil/structure interaction (SSI), frequency dependent lumped parameter SSI, and current state of the art analyses using computer codes such as SASSI. The results from these computations consist of structural loads and floor response spectra (used for piping and equipment qualification). These results are compared in the paper and the methods used to validate the results are discussed. 14 refs., 11 figs
Seismic response of uplifting concrete gravity dams
International Nuclear Information System (INIS)
Leger, P.; Sauve, G.; Bhattacharjee, S.
1992-01-01
The foundation interaction effects on the seismic response of dam-foundation systems have generally been studied using the linear elastic finite element models. In reality, the foundation can not develop effective tensile stresses to a significant degree along the interface. A two-dimensional finite element model, in which nonlinear gap elements are used at the dam-foundation interface to determine the uplift response of concrete gravity dams subjected to seismic loads, is presented. Time domain analyses were performed for a wide range of modelling assumptions such as dam height, interface uplift pressure, interface mesh density, and earthquake input motions, that were systematically varied to find their influence on the seismic response. The nonlinear interface behavior generally reduces the seismic response of dam-foundation systems acting as a seismic isolation mechanism, and may increase the safety against sliding by reducing the base shear transmitted to the foundation. 4 refs., 5 figs., 6 tabs
Consideration of vertical seismic response spectrum in nuclear safety review
International Nuclear Information System (INIS)
Sun Zaozhan; Huang Bingchen
2011-01-01
The basic requirements for civil nuclear installation are introduced in the article. Starting from the basic concept of seismic response spectrum, the authors analyze the site seismic response spectrum and the design seismic response spectrum that desire much consideration. By distinguishing the absolute seismic response spectrum and relative seismic response spectrum, the authors analyze the difference and relationship between the vertical seismic response spectrum and horizontal seismic response spectrum. The authors also bring forward some suggestions for determining the site vertical seismic response spectrum by considering the fact in our country. (authors)
Seismic Responses of an Added-Story Frame Structure with Viscous Dampers
Directory of Open Access Journals (Sweden)
Xuansheng Cheng
2014-01-01
Full Text Available The damping ratio of an added-story frame structure is established based on complex damping theory to determine the structure seismic response. The viscous dampers are selected and arranged through target function method. A significant damping effect is obtained when a small velocity index is selected. The seismic responses of a five-floor reinforced concrete frame structure with directly added light steel layers and light steel layers with viscous dampers are compared with the finite element software SAP2000. Calculation results show that, after adding the layers, the structure becomes flexible and the shear in the bottom layer decreases. However, the interlaminar shear of the other layers increases. The seismic response of the added layers is very significant and exhibits obvious whiplash effect. The interstory displacement angles of some layers do not meet the requirements. The seismic response of the structure decreases after the adoption of viscous dampers; thereby seismic requirements are satisfied.
Systematic evaluations of probabilistic floor response spectrum generation
International Nuclear Information System (INIS)
Lilhanand, K.; Wing, D.W.; Tseng, W.S.
1985-01-01
The relative merits of the current methods for direct generation of probabilistic floor response spectra (FRS) from the prescribed design response spectra (DRS) are evaluated. The explicit probabilistic methods, which explicitly use the relationship between the power spectral density function (PSDF) and response spectra (RS), i.e., the PSDF-RS relationship, are found to have advantages for practical applications over the implicit methods. To evaluate the accuracy of the explicit methods, the root-mean-square (rms) response and the peak factor contained in the PSDF-RS relationship are systematically evaluated, especially for the narrow-band floor spectral response, by comparing the analytical results with simulation results. Based on the evaluation results, a method is recommended for practical use for the direct generation of probabilistic FRS. (orig.)
Influence of soil-structure interaction on floor response spectra
International Nuclear Information System (INIS)
Costantino, C.J.; Miller, C.A.; Curreri, J.R.
1985-01-01
A study was undertaken to investigate the influence of soil-structure interaction on floor response spectra developed in typical nuclear power plant structures. A horizontal earthquake time history, whose spectra envelops the Reg. Guide 1.60 criteria and is scaled to a 1 g peak acceleration, was used as input to structural models. Two different structural stick models were used, representing typical BWR and PWR facilities. By varying the structural and soil stiffness parameters, a wide range of system behaviors were investigated. Floor response spectra, required to assess equipment qualification, were of primary interest. It was found from a variation of parameter study that the interaction soil parameters, particularly radiation damping, greatly affect the nature of the calculated responses. (orig.)
Influence of soil-structure interaction on floor response spectra
International Nuclear Information System (INIS)
Costantino, C.J.; Miller, C.A.; Curreri, J.R.
1985-01-01
A study was undertaken to investigate the influence of soil-structure interaction on floor response spectra developed in typical nuclear power plant structures. A horizontal earthquake time history, whose spectra envelops the Regulatory Guide 1.60 criteria and is scaled to a log peak acceleration, was used as input to structural models. Two different structural stick models were used, representing typical BWR and PWR facilities. By varying the structural and soil stiffness parameters, a wide range of system behaviors were investigated. Floor response spectra, required to assess equipment qualification, were of primary interest. It was found from a variation of parameter study that the interaction soil parameters, particularly radiation damping, greatly affect the nature of the calculated responses. 2 refs., 2 figs., 2 tabs
Generation of floor response spectra for a model structure of nuclear power plant
International Nuclear Information System (INIS)
Vaidyanathan, C.V.; Kamatchi, P.; Ravichandran, R.; Lakshmanan, N.
2003-01-01
The importance of Nuclear power plants and the consequences of a nuclear accident require that the nuclear structures be designed for the most severe environmental conditions. Earthquakes constitutes major design consideration for the system, structures and equipment of a nuclear power plant. The design of structures on ground is based on the ground response spectra. Many important parts of a nuclear power plant facility are attached to the principal parts of the structure and respond in a manner determined by the structural response rather than by the general ground motion to which the structure is supported. Hence the seismic response of equipment is generally based on the response spectrum of the floor on which it is mounted. In this paper such floor response spectra have been generated at different nodes of a chosen model structure of a nuclear power plant. In the present study a detailed nonlinear time history analysis has been carried out on the mathematical model of the chosen Nuclear Power Plant model structure with the spectrum compatible time history. The acceleration response results of the time history analysis has been used in the spectral analysis and the response spectra are generated. Further peak broadening has been done to account for uncertainties in the material properties and soil characteristics. (author)
Floor Response Spectra of Nuclear Containment Building with Soil-Structure Interaction
Energy Technology Data Exchange (ETDEWEB)
Seo, Choon Gyo; Ryu, Jeong Soo [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2008-10-15
This paper presents a seismic analysis technique for a 3D soil-structure interaction(SSI) system in frequency domain, based on the finite element formulation incorporating frequency-dependent dynamic infinite elements for the far field soil region. Earthquake input motions are regarded as traveling SV-wave which is vertically incident from a far-field soil region. In which, the equivalent earthquake forces in the frequency domain are calculated using the exterior rigid boundary method and the free field response analysis. For the application, floor response spectra analyses for nuclear containment building on a soil medium is carried out, the obtained results are compared with the free field response by other solution.
Reduction of seismic response in breeder plants
International Nuclear Information System (INIS)
Tajirian, F.F.; Somes, N.F.; Todeschini, R.A.
1984-01-01
Thin-walled vessels to be used in the Nuclear Steam Supply Systems (NSSS) of future LMFBR's will be more sensitive to seismic excitation than their equivalents used in conventional LWR plants. Optimization studies of building arrangement have indicated that embedment of future plants may be one feasible strategy for reducing seismic response. This paper presents the results of a three-dimensional soil-structure interaction analysis using the computer program SASSI. Two types of embedded buildings are considered: full embedment of the nuclear island, and embedment of the reactor cavity alone. A comparison, between the response of the embedded structure with that of a plant supported on the surface, indicates that the seismic response at the reactor vessel support ledge can be lowered by embedment of either the entire nuclear island or the reactor cavity alone. This reduction is larger when the plant is embedded in a softer site due to the increased effect of soil-structure interaction
Seismic response of LMFBR tanks with imperfections
International Nuclear Information System (INIS)
Gvildys, J.; Ma, D.C.; Chang, Y.W.
1985-01-01
This paper deals with seismic responses of imperfect circular tanks. Physical imperfection due to manufacturing tolerances and numerical imperfection due to finite element spatial discretization are described. Numerical imperfections produced by 4-node and 9-node Lagrangian shell elements are examined. A convergence study is performed in which the number of the shell elements required to capture the dominant ''out-of-roundness'' modes under seismic excitations is determined. The response of a shell with a cos4theta imperfection due to manufacturing tolerances is compared with that of a perfect circular shell to demonstrate the effects of imperfection on the axial stresses of the shell under seismic conditions. 3 refs., 4 figs., 2 tabs
International Nuclear Information System (INIS)
Kostarev, V.V.; Petrenko, A.V.; Vasilyev, P.S.; Reinsch, K.-H.
2005-01-01
This paper concerns a further development of High Viscous Damper (HVD) approach for essential decreasing of structure's floor response spectra. Usually restraining of components and pipelines by HVD is used for significant decreasing of operational vibration and seismic loads. A new approach consists of dampers installation for essential upgrading of a whole system's damping that is much more efficient in both technical and economical points of view than restraining of each component of the system. In that way using of HVD means high energy dissipation for whole dynamic system 'Building-Components' subjected to the base seismic or other extreme load excitation. The specific feature of each NPP site is an existing of a few closely spaced buildings: reactor building, turbine hall and so on. As the rule such buildings play sufficiently different roles in NPP operation and therefore have sufficiently different design, natural frequencies (periods) and distortion of floors and different rocking modes on a soil. The main idea explained in the paper is an interconnection of buildings by HVD. Then differences in their mechanical properties provide their out-of-phase relative motions during an earthquake and therefore effective dissipative work provided by HVD devices. At the same time implementation of HVD approach allows to eliminate possible interactions and collisions in the gaps between building structures that wears potential threat of building failure. The detailed 3D finite element models of reactor building, turbine hall and special building were developed for NPP with VVER-1000 MWt reactor type. Performed analysis has shown high efficiency of suggested approach for protection of buildings, structures, systems and components against seismic and other impacts. (authors)
Cardiorespiratory Responses to Pool Floor Walking in People Poststroke.
Jeng, Brenda; Fujii, Takuto; Lim, Hyosok; Vrongistinos, Konstantinos; Jung, Taeyou
2018-03-01
To compare cardiorespiratory responses between pool floor walking and overground walking (OW) in people poststroke. Cross-sectional study. University-based therapeutic exercise facility. Participants (N=28) were comprised of 14 community-dwelling individuals poststroke (5.57±3.57y poststroke) and 14 age- and sex-matched healthy adults (mean age, 58.00±15.51y; male/female ratio, 9:5). Not applicable. A telemetric metabolic system was used to collect cardiorespiratory variables, including oxygen consumption (V˙o 2 ), energy expenditure (EE), and expired volume per unit time (V˙e), during 6-minute walking sessions in chest-depth water and on land at a matched speed, determined by average of maximum walking speed in water. Individuals poststroke elicited no significant differences in cardiorespiratory responses between pool floor walking and OW. However, healthy controls showed significant increases in mean V˙o 2 values by 94%, EE values by 109%, and V˙e values by 94% (all Pstroke group did not. Our results indicate that people poststroke, unlike healthy adults, do not increase EE while walking in water compared with on land. Unlike stationary walking on an aquatic treadmill, forward locomotion during pool floor walking at faster speeds may have increased drag force, which requires greater EE from healthy adults. Without demanding excessive EE, walking in water may offer a naturally supportive environment for gait training in the early stages of rehabilitation. Copyright © 2017 American Congress of Rehabilitation Medicine. All rights reserved.
Peak-Broadening of Floor Response Spectra for Base Isolated Nuclear Structures
International Nuclear Information System (INIS)
Ju, Heekun; Choun, Young-Sun; Kim, Min-Kyu
2015-01-01
In this paper, uncertainties in developing FRS are explained first. Then FDRS of a fixed structure is computed using a conventional method as an example. Lastly FRS of a base-isolated structure is computed and suitability of current peak-broadening method is examined. Uncertainties in the material property of structure influence FRS of fixed structures significantly, but their effect on FRS of base-isolated structures is negligible. Nuclear structures should be designed to ensure the safety of equipment and components mounted on their floors. However, coupled analysis of a structure and components is complex, so equipment is separately analyzed using floor response spectra (FRS). FRS calculated from dynamic analysis of structural model should be modified to create floor design response spectra (FDRS), the input for seismic design of equipment. For nuclear structures, smoothing and broadening peaks of FRS is required to account for uncertainties owing to material properties of structures, soil, modeling techniques, and others. The peak broadening method proposed for fixed based structures may not be appropriate for base-isolated structures because of additional uncertainties in the property of isolation bearings. For base-isolated structures, mechanical property of isolator plays a dominant role on the change of FRS. As base-isolated nuclear plants should meet the ASCE provisions, uncertainty in the isolation system would be around 10%. For the base isolated 3-storied beam model with 2.5-sec isolation period, 6.9% of broadening ratio was enough for development of FDRS at the required variation condition. Also for the models with various isolation periods, less than 10% of broadening ratio was sufficient
Factors affecting seismic response of submarine slopes
Directory of Open Access Journals (Sweden)
G. Biscontin
2006-01-01
Full Text Available The response of submerged slopes on the continental shelf to seismic or storm loading has become an important element in the risk assessment for offshore structures and 'local' tsunami hazards worldwide. The geological profile of these slopes typically includes normally consolidated to lightly overconsolidated soft cohesive soils with layer thickness ranging from a few meters to hundreds of meters. The factor of safety obtained from pseudo-static analyses is not always a useful measure for evaluating the slope response, since values less than one do not necessarily imply slope failure with large movements of the soil mass. This paper addresses the relative importance of different factors affecting the response of submerged slopes during seismic loading. The analyses use a dynamic finite element code which includes a constitutive law describing the anisotropic stress-strain-strength behavior of normally consolidated to lightly overconsolidated clays. The model also incorporates anisotropic hardening to describe the effect of different shear strain and stress histories as well as bounding surface principles to provide realistic descriptions of the accumulation of the plastic strains and excess pore pressure during successive loading cycles. The paper presents results from parametric site response analyses on slope geometry and layering, soil material parameters, and input ground motion characteristics. The predicted maximum shear strains, permanent deformations, displacement time histories and maximum excess pore pressure development provide insight of slope performance during a seismic event.
Seismic response of reinforced soil slopes
DEFF Research Database (Denmark)
Tzavara, Ioanna; Zania, Varvara; Tsompanakis, Yiannis
2010-01-01
The main aim of the current study is to assess the dynamic response of reinforced soil structures taking into account the most important aspects of the problem and to compare the available design methods. For this purpose, initially the most commonly used pseudostatic approach is implemented via...... a parametric investigation to illustrate the impact of the crucial parameters of this approach. Subsequently, Newmark’s sliding block model is modified to account for the reinforcement forces in the calculation of seismic displacements. Finally, finite element analyses were performed and the numerical results...
Seismic response of reactor building on alluvial soil by direct implicit integration
International Nuclear Information System (INIS)
Thakkar, S.K.; Dinkar, A.K.
1983-01-01
The evaluation of seismic response of a reactor building is a complex problem. A study has been made in this paper of seismic response of a reactor building by direct implicit integration method. The direct implicit integration methods besides being unconditionally stable have the merit of including response of higher modes without much effort. A reactor building consisting of external shell, internal shell, internals and raft is considered to be resting on alluvium. The complete building including the foundation is idealized by axisymmetric finite elements. The structure is analyzed separately for horizontal and vertical components of ground motion using harmonic analysis. Total response is found by superposition of two responses. The variation of several parameters, such as soil stiffness, embedment depth, inertia of foundation, viscous boundary and damping on seismic response is studied. The structural response is seen to depend significantly on the soil stiffness and damping. The seismic response is observed to be less sensitive to embedment depth and inertia of foundation. The vertical accelerations on the raft, boiler room floor slab and dome due to vertical ground motions are quite appreciable. The viscous boundary is seen to alter structural response in significantly compared to rigid boundaries in a larger mesh and its use appears to be promising in absorbing energy of body waves when used with direct implicit integration method. (orig.)
MOBB: a permanent ocean floor broadband seismic observatory in Monterey Bay, California
Uhrhammer, R.; Romanowicz, B.; Stakes, D.; Neuhauser, D.; McGill, P.; Ramirez, T.
2003-04-01
The Monterey ocean bottom broadband station (MOBB) was installed on the seafloor in Monterey Bay, 40 km offshore, and at a depth of 1000m from the sea surface, on April 9-11, 2002. Its success capitalizes on the experience gained in the 1997 International MOISE experiment, conducted under similar conditions. The deployment took place during 3 dives on consecutive days and made use of MBARI's Point Lobos ship and ROV Ventana. The station is currently recording data autonomously. Eventually, it will be linked to the planned (and recently funded) MARS (Monterey Accelerated Research System; \\url {http://www.mbari.org/mars/}) cable and provide real-time, continuous seismic data to be merged with the rest of the northern California real-time seismic system. The data are archived at the NCEDC for on-line availability, as part of the Berkeley Digital Seismic Network (BDSN). The ocean-bottom MOBB station currently comprises a three-component seismometer package, a current-meter, a DPG, and recording and battery packages. The seismic package contains a low-power (2.2W), three-component CMG-1T broadband seismometer system, built by Guralp, Inc., with a three-component 24-bit digitizer, a leveling system, and a precision clock. The seismometer package is mounted on a cylindrical titanium pressure vessel 54cm in height and 41 cm in diameter, custom built by the MBARI team and outfitted for underwater connection. Data recovery dives, during which the recording and battery package will be exchanged are planned every three months for the next 3 years. Three such dives have already taken place, on 06/27/02, 09/20/02 and on 01/07/03. Due to a software problem, data were lost during the time period 07/01/02 and 09/20/02. Many regional and teleseismic earthquakes have been well recorded and the mass position signals indicate that the instruments have progressively settled. Preliminary analysis of data retrieved during the 2002 summer and winter dives will be presented. In particular
Wave processes and geologic responses on the floor of the Yellow Sea
Booth, James S.; Winters, William J.
1991-01-01
The floor of the Yellow Sea is a geologically mundane surface: it is nearly horizontal, lacks relief, and, with few exceptions, is devoid of conspicuous geomorphologic features. However, it is the principal repository for the prodigious sediment load of the Huanghe (Yellow River); and, due to its inherent shallowness (average depth is 40 m), it is frequently stressed by waves generated by winter storms and typhoons. Analyses of mass physical properties of cores representing the upper few meters of sediment in the central and north-central Yellow Sea (near the Shandong Peninsula), in conjunction with analyses of slope stability, failure modes, and erodibility, permit an assessment of the likelihood and effect of dynamic, transient geologic events on the seabed.Vane shear-strength profiles along with consolidation test data indicate that the present surface of the seabed is in a depositional mode and is compacting normally. in addition, liquid-limit profiles imply that in the study area these neritic sediments have been accumulating in an environment that probably has not been modified significantly since sea level reached its current level. There is no geotechnical evidence in the nine cores recovered that slope failures have occurred, and clasts, sand lenses or other manifestations of mass movements, including flows, also are absent. These observations support previous interpretations of seismic records. Moreover, slope stability analysis for static conditions shows that the sea floor is quite stable.Regardless, shear-stress levels generated by cyclic loading during major storms may approach the sediment shear strengths, and, when coupled with concomitant excess pore pressures, could cause slope failure. Unless the failed beds collapsed or flowed, however, there probably would be little conspicuous evidence of such a failure. in fact, evaluation of the potential of these sediments for disintegrative behavior suggests that they are not prone to either collapse or
Seismic shear wall ISP NUPEC's seismic ultimate dynamic response test. Comparison report
International Nuclear Information System (INIS)
1996-01-01
In the seismic design of a nuclear power plant, evaluation of the ultimate strength of the nuclear reactor building is an important subject for assessment of seismic reliability of the plant. In order to carry out the evaluation, the response characteristics of reinforced concrete seismic shear walls up to their ultimate state have to be understood. For this purpose, there is a need to develop reliable non-linear response analysis methods which enables the reliable ultimate strength evaluation of nuclear reactor buildings. Along with this need, many computer codes have been developed. These computer codes are compared. (K.A.)
Critical seismic response of nuclear reactors
International Nuclear Information System (INIS)
Drenick, R.F.; Wang, P.C.; Yun, C.B.; Philappacopoulos, A.J.
1980-01-01
This paper deals with the problem of how to assess the seismic resistance of important structures, particularly of nuclear reactor structures. Most of the design procedures presently in use or under investigation are based on design response spectra obtained by statistical evaluation of past ground excitations assuming certain probability distributions (e.g., normal or lognormal) of response peaks. Artificial time histories generated from these spectra are also used. However, it is not clear whether these approaches lead to designs that can be relied upon on the confidence levels that are presumably desired for structures such as nuclear reactors whose integrity during an earthquake is of considerable importance. The trouble lies with the fact that the analysis of structural integrity seems highly sensitive to the assumptions regarding the nature of those probability distributions: small variations, especially in the tails of the distributions, can induce large changes in the desired results. This greatly weakens the reliance that can be placed in many assessments of earthquake resistance. In this paper, a new method is developed which has the potential of avoiding those weaknesses. It is more specifically based on assumptions that seem well supported by seismological observations but side-steps others, especially those regarding probability distribution of ground motions, which are more conjectural. (orig./RW)
Assessment of seismic design response factors of concrete wall buildings
Mwafy, Aman
2011-03-01
To verify the seismic design response factors of high-rise buildings, five reference structures, varying in height from 20- to 60-stories, were selected and designed according to modern design codes to represent a wide range of concrete wall structures. Verified fiber-based analytical models for inelastic simulation were developed, considering the geometric nonlinearity and material inelasticity of the structural members. The ground motion uncertainty was accounted for by employing 20 earthquake records representing two seismic scenarios, consistent with the latest understanding of the tectonic setting and seismicity of the selected reference region (UAE). A large number of Inelastic Pushover Analyses (IPAs) and Incremental Dynamic Collapse Analyses (IDCAs) were deployed for the reference structures to estimate the seismic design response factors. It is concluded that the factors adopted by the design code are adequately conservative. The results of this systematic assessment of seismic design response factors apply to a wide variety of contemporary concrete wall buildings with various characteristics.
Response spectrum analysis of coupled structural response to a three component seismic disturbance
International Nuclear Information System (INIS)
Boulet, J.A.M.; Carley, T.G.
1977-01-01
The work discussed herein is a comparison and evaluation of several response spectrum analysis (RSA) techniques as applied to the same structural model with seismic excitation having three spatial components. The structural model includes five lumped masses (floors) connected by four elastic members. The base is supported by three translational springs and two horizontal torsional springs. In general, the mass center and shear center of a building floor are distinct locations. Hence, inertia forces, which act at the mass center, induce twisting in the structure. Through this induced torsion, the lateral (x and y) displacements of the mass elements are coupled. The ground motion components used for this study are artificial earthquake records generated from recorded accelerograms by a spectrum modification technique. The accelerograms have response spectra which are compatible with U.S. NRC Regulatory Guide 1.60. Lagrange's equations of motion for the system were written in matrix form and uncoupled with the modal matrix. Numerical integration (fourth order Runge-Kutta) of the resulting modal equations produced time histories of system displacements in response to simultaneous application of three orthogonal components of ground motion, and displacement response spectra for each modal coordinate in response to each of the three ground motion components. Five different RSA techniques were used to combine the spectral displacements and the modal matrix to give approximations of maximum system displacements. These approximations were then compared with the maximum system displacements taken from the time histories. The RSA techniques used are the method of absolute sums, the square root of the sum of the sum of the squares, the double sum approach, the method of closely spaced modes, and Lin's method
Sunarti, D; Haryono, H; Soedarsono, S
2010-01-01
The purpose of this research was to study the effect of density and floor types on performance,physiological state and immune response of broilers. The research involved 368 male broilers of theNew Lohman strain aged 8 days which were raised up to 35 days at different densities and floor types.Floor types consisted of rice hull litter and bamboo slat were used as the main plot; while densities of 7,10, 13 and 16 birds/m2 applied as the sub-plot. The results showed that the final body weight g...
International Nuclear Information System (INIS)
Ghiocel, Dan M.; Wilson, Paul R.; Thomas, Gary G.; Stevenson, John D.
1998-01-01
The paper discusses methodological aspects involved in a probabilistic seismic soil-structure interaction (SSI) analysis for a Seismic Probabilistic Risk Assessment (SPRA) review. An example of an Eastern US nuclear power plant (NPP) is presented. The approach presented herein follows the current practice of the Individual Plant Examination for External Events (IPEEE) program in the US. The NPP is founded on a relatively soft soil deposit, and thus the SSI effects on seismic responses are significant. Probabilistic models used for the idealization of the seismic excitation and the surrounding soil deposit are described. Using a lognormal format, computed random variability effects were combined with those proposed in the SPRA methodology guidelines. Probabilistic floor response spectra and structural fragilities for different NPP buildings were computed. Structural capacities were determined following the current practice which assumes independent median safety factors for strength and inelastic absorption. Limitations of the IPEEE practice for performing SPRA are discussed and alternate procedures, more rigorous and simple to implement, are suggested
Seismic analysis response factors and design margins of piping systems
International Nuclear Information System (INIS)
Shieh, L.C.; Tsai, N.C.; Yang, M.S.; Wong, W.L.
1985-01-01
The objective of the simplified methods project of the Seismic Safety Margins Research Program is to develop a simplified seismic risk methodology for general use. The goal is to reduce seismic PRA costs to roughly 60 man-months over a 6 to 8 month period, without compromising the quality of the product. To achieve the goal, it is necessary to simplify the calculational procedure of the seismic response. The response factor approach serves this purpose. The response factor relates the median level response to the design data. Through a literature survey, we identified the various seismic analysis methods adopted in the U.S. nuclear industry for the piping system. A series of seismic response calculations was performed. The response factors and their variabilities for each method of analysis were computed. A sensitivity study of the effect of piping damping, in-structure response spectra envelop method, and analysis method was conducted. In addition, design margins, which relate the best-estimate response to the design data, are also presented
Seismic response of a block-type nuclear reactor core
International Nuclear Information System (INIS)
Dove, R.C.; Bennett, J.G.; Merson, J.L.
1976-05-01
An analytical model is developed to predict seismic response of large gas-cooled reactor cores. The model is used to investigate scaling laws involved in the design of physical models of such cores, and to make parameter studies
Seismic response of flexible cylindrical tanks
Energy Technology Data Exchange (ETDEWEB)
Jaeger, T A; Boley, B A [comps.
1977-01-01
An experimental study of the seismic behavior of thin shell circular cylindrical liquid storage tanks is described. The investigation was planned to evaluate the adequacy of present methods of tank design, and was conducted using the Earthquake Simulator Facility of the University of California, Berkeley. The model tank considered in this paper was 6 ft high by 12 ft in diameter, and was welded from thin sheet aluminum to simulate a steel tank 36 feet in diameter. During testing the tank had an open top, held 60 inches of water, and was subjected to a time scaled El Centro (1940) earthquake, amplified to a peak acceleration of 0.5 g. Both base free and base fixed conditions were studied. Results of the experiments demonstrate that fluid pressures included both impulsive and convective components, and that the wave sloshing followed basic theory quite closely. But it also was apparent that the tank flexibility influenced the hydrodynamic pressures, as indicated by pressure amplification in the clamped tank, and by a total change of pressure history in the unclamped case. Significant out of round distortions of the tank were developed, of a three lobe form or the free base case and with four lobes in the fixed base case. Uplift of the tank base was closely related to the out-of-round deformation of the unanchored tank, whereas initial eccentricities apparently caused the section distortions in the anchored system. Stresses in the tank wall do not follow the expected pattern of response to overturning moment; instead they seem to be mainly associated with the section distortions. At present there is no analytical procedure for predicting these distortions .
Seismic Response Analysis of Continuous Multispan Bridges with Partial Isolation
Directory of Open Access Journals (Sweden)
E. Tubaldi
2015-01-01
Full Text Available Partially isolated bridges are a particular class of bridges in which isolation bearings are placed only between the piers top and the deck whereas seismic stoppers restrain the transverse motion of the deck at the abutments. This paper proposes an analytical formulation for the seismic analysis of these bridges, modelled as beams with intermediate viscoelastic restraints whose properties describe the pier-isolator behaviour. Different techniques are developed for solving the seismic problem. The first technique employs the complex mode superposition method and provides an exact benchmark solution to the problem at hand. The two other simplified techniques are based on an approximation of the displacement field and are useful for preliminary assessment and design purposes. A realistic bridge is considered as case study and its seismic response under a set of ground motion records is analyzed. First, the complex mode superposition method is applied to study the characteristic features of the dynamic and seismic response of the system. A parametric analysis is carried out to evaluate the influence of support stiffness and damping on the seismic performance. Then, a comparison is made between the exact solution and the approximate solutions in order to evaluate the accuracy and suitability of the simplified analysis techniques for evaluating the seismic response of partially isolated bridges.
Energy Technology Data Exchange (ETDEWEB)
Lee, J. H.; Yoo, B.; Koo, K. H. [KAERI, Taejon (Korea, Republic of)
2001-05-01
The seismic response time history analyses for the lumped mass models of KALIMER reactor building with a horizontal and vertical seismic isolation are performed for Artificial Time History and Kobe earthquake. The vertical amplification by the horizontal isolation is reduced by a vertical isolation for both earthquakes. The 3% viscous damping and the vertical isolation frequency of 1.5Hz gives a reduced vertical response compared to the fixed base condition at reactor support, and the 9% viscous damping to Kobe earthquake is required to get an equivalent vertical response with a fixed base condition.
International Nuclear Information System (INIS)
Lee, J. H.; Yoo, B.; Koo, K. H.
2001-01-01
The seismic response time history analyses for the lumped mass models of KALIMER reactor building with a horizontal and vertical seismic isolation are performed for Artificial Time History and Kobe earthquake. The vertical amplification by the horizontal isolation is reduced by a vertical isolation for both earthquakes. The 3% viscous damping and the vertical isolation frequency of 1.5Hz gives a reduced vertical response compared to the fixed base condition at reactor support, and the 9% viscous damping to Kobe earthquake is required to get an equivalent vertical response with a fixed base condition
Preliminary Seismic Response and Fragility Analysis for DACS Cabinet
Energy Technology Data Exchange (ETDEWEB)
Oh, Jinho; Kwag, Shinyoung; Lee, Jongmin; Kim, Youngki [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2013-05-15
A DACS cabinet is installed in the main control room. The objective of this paper is to perform seismic analyses and evaluate the preliminary structural integrity and seismic capacity of the DACS cabinet. For this purpose, a 3-D finite element model of the DACS cabinet was developed and its modal analyses are carried out to analyze the dynamic characteristics. The response spectrum analyses and the related safety evaluation are then performed for the DACS cabinet subject to seismic loads. Finally, the seismic margin and seismic fragility of the DACS cabinet are investigated. A seismic analysis and preliminary structural integrity of the DACS cabinet under self weight and SSE load have been evaluated. For this purpose, 3-D finite element models of the DACS cabinet were developed. A modal analysis, response spectrum analysis, and seismic fragility analysis were then performed. From the structural analysis results, the DACS cabinet is below the structural design limit of under SSE 0.3g, and can structurally withstand until less than SSE 3g based on an evaluation of the maximum effective stresses. The HCLPF capacity for the DGRS of the SSE 0.3g is 0.55g. A modal analysis, response spectrum analysis, and seismic fragility analysis were then performed. From the structural analysis results, the DACS cabinet is below the structural design limit of under SSE 0.3g, and can structurally withstand until less than SSE 3g based on an evaluation of the maximum effective stresses. The HCLPF capacity for the DGRS of the SSE 0.3g is 0.55g. Therefore, it is concluded that the DACS cabinet was safely designed in that no damage to the preliminary structural integrity and sufficient seismic margin is expected.
Preliminary Seismic Response and Fragility Analysis for DACS Cabinet
International Nuclear Information System (INIS)
Oh, Jinho; Kwag, Shinyoung; Lee, Jongmin; Kim, Youngki
2013-01-01
A DACS cabinet is installed in the main control room. The objective of this paper is to perform seismic analyses and evaluate the preliminary structural integrity and seismic capacity of the DACS cabinet. For this purpose, a 3-D finite element model of the DACS cabinet was developed and its modal analyses are carried out to analyze the dynamic characteristics. The response spectrum analyses and the related safety evaluation are then performed for the DACS cabinet subject to seismic loads. Finally, the seismic margin and seismic fragility of the DACS cabinet are investigated. A seismic analysis and preliminary structural integrity of the DACS cabinet under self weight and SSE load have been evaluated. For this purpose, 3-D finite element models of the DACS cabinet were developed. A modal analysis, response spectrum analysis, and seismic fragility analysis were then performed. From the structural analysis results, the DACS cabinet is below the structural design limit of under SSE 0.3g, and can structurally withstand until less than SSE 3g based on an evaluation of the maximum effective stresses. The HCLPF capacity for the DGRS of the SSE 0.3g is 0.55g. A modal analysis, response spectrum analysis, and seismic fragility analysis were then performed. From the structural analysis results, the DACS cabinet is below the structural design limit of under SSE 0.3g, and can structurally withstand until less than SSE 3g based on an evaluation of the maximum effective stresses. The HCLPF capacity for the DGRS of the SSE 0.3g is 0.55g. Therefore, it is concluded that the DACS cabinet was safely designed in that no damage to the preliminary structural integrity and sufficient seismic margin is expected
Study of peak broadening effect in floor time histories
International Nuclear Information System (INIS)
Soni, R.S.; Kushwaha, H.S.; Mahajan, S.C.; Kakodkar, A.
1996-01-01
Seismic design of secondary systems such components and piping is usually carried out by using the floor motions at their support points. These floor motions can be in the form of Floor Response Spectra (FRS) or the Floor Time Histories (FTH). In order to account for the various uncertainties in generating these floor motions, these motions should be peak broadened and smoothened as per the regulatory codes. Presented here in this paper is the methodology to account for such peak broadening effect in the FTH. Results of this study have been compared with the FRS approach and various important conclusions have been arrived at based on the study
Seismic response analysis for a deeply embedded nuclear power plant
International Nuclear Information System (INIS)
Chen, W.W.H.; Chatterjee, M.; Day, S.M.
1979-01-01
One of the important aspect of the aseimic design of nuclear power plants is the evaluation of the seismic soil-structure interaction effect due to design earthquakes. The soil-structure interaction effect can initiate rocking and result in different soil motions compared to the free field motions, thus significantly affecting the structural response. Two methods are generally used to solve the seismic soil-structure interaction problems: the direct finite element method (FLUSH) and the substructure or impedance approach. This paper presents the results of the horizontal seismic soil-structure interaction analysis using the impedance aproach and the direct finite element method for a deeply embedded nuclear power plant. (orig.)
Influence of plastic deformation on seismic response of piping
International Nuclear Information System (INIS)
Yao Yanping; Chen Yong; Lu Mingwan
2000-01-01
On the basis of a brief summary of linear elastic seismic analysis methods, the importance for consideration of plastic deformation during the dynamic response analysis of piping system is indicated. The present methods of considering plasticity and the disadvantages of these methods are discussed. And the authors point out that in order to reduce the conservatism of present codes and to put forward appropriate and realistic piping seismic design methods, the key is to understand the plastic dynamic failure mode for piping under seismic excitation and to calculate the inelastic energy dissipation. The analysis and evaluation are applicable to nuclear piping systems
Seismic Response Analysis and Design of Structure with Base Isolation
International Nuclear Information System (INIS)
Rosko, Peter
2010-01-01
The paper reports the study on seismic response and energy distribution of a multi-story civil structure. The nonlinear analysis used the 2003 Bam earthquake acceleration record as the excitation input to the structural model. The displacement response was analyzed in time domain and in frequency domain. The displacement and its derivatives result energy components. The energy distribution in each story provides useful information for the structural upgrade with help of added devices. The objective is the structural displacement response minimization. The application of the structural seismic response research is presented in base-isolation example.
Directory of Open Access Journals (Sweden)
D. Sunarti
2014-10-01
Full Text Available The purpose of this research was to study the effect of density and floor types on performance,physiological state and immune response of broilers. The research involved 368 male broilers of theNew Lohman strain aged 8 days which were raised up to 35 days at different densities and floor types.Floor types consisted of rice hull litter and bamboo slat were used as the main plot; while densities of 7,10, 13 and 16 birds/m2 applied as the sub-plot. The results showed that the final body weight gain of the35-day Lohmann broilers at densities of 7, 10 and 13 birds/m2 were 28.22, 24.43 and 19.27 kgrespectively, compared to 16 birds/m2 at 13.53 kg (P>0.05. Broilers in the bamboo slats floor hadlymph weight at 3.73 g compared to the litter floor at 2.55 g (P<0.05. Also, broilers in the bambooslats had average RHL (0.65 lower than broilers in the litter floor (0.79. It could be concluded thatbamboo slats best being used for broilers up to a density of 13 broilers/m2.
Generate floor response spectra, Part 2: Response spectra for equipment-structure resonance
International Nuclear Information System (INIS)
Li, Bo; Jiang, Wei; Xie, Wei-Chau; Pandey, Mahesh D.
2015-01-01
Highlights: • The concept of tRS is proposed to deal with tuning of equipment and structures. • Established statistical approaches for estimating tRS corresponding to given GRS. • Derived a new modal combination rule from the theory of random vibration. • Developed efficient and accurate direct method for generating floor response spectra. - Abstract: When generating floor response spectra (FRS) using the direct spectra-to-spectra method developed in the companion paper, probability distribution of t-response spectrum (tRS), which deals with equipment-structure resonance or tuning, corresponding to a specified ground response spectrum (GRS) is required. In this paper, simulation results using a large number of horizontal and vertical ground motions are employed to establish statistical relationships between tRS and GRS. It is observed that the influence of site conditions on horizontal statistical relationships is negligible, whereas the effect of site conditions on vertical statistical relationships cannot be ignored. Considering the influence of site conditions, horizontal statistical relationship suitable for all site conditions and vertical statistical relationships suitable for hard sites and soft sites, respectively, are established. The horizontal and vertical statistical relationships are suitable to estimate tRS for design spectra in USNRC R.G. 1.60 and NUREG/CR-0098, Uniform Hazard Spectra (UHS) in Western North America (WNA), or any GRS falling inside the valid coverage of the statistical relationship. For UHS with significant high frequency spectral accelerations, such as UHS in Central and Eastern North America (CENA), an amplification ratio method is proposed to estimate tRS. Numerical examples demonstrate that the statistical relationships and the amplification ratio method are acceptable to estimate tRS for given GRS and to generate FRS using the direct method in different practical situations.
Generate floor response spectra, Part 2: Response spectra for equipment-structure resonance
Energy Technology Data Exchange (ETDEWEB)
Li, Bo, E-mail: b68li@uwaterloo.ca; Jiang, Wei, E-mail: w46jiang@uwaterloo.ca; Xie, Wei-Chau, E-mail: xie@uwaterloo.ca; Pandey, Mahesh D., E-mail: mdpandey@uwaterloo.ca
2015-11-15
Highlights: • The concept of tRS is proposed to deal with tuning of equipment and structures. • Established statistical approaches for estimating tRS corresponding to given GRS. • Derived a new modal combination rule from the theory of random vibration. • Developed efficient and accurate direct method for generating floor response spectra. - Abstract: When generating floor response spectra (FRS) using the direct spectra-to-spectra method developed in the companion paper, probability distribution of t-response spectrum (tRS), which deals with equipment-structure resonance or tuning, corresponding to a specified ground response spectrum (GRS) is required. In this paper, simulation results using a large number of horizontal and vertical ground motions are employed to establish statistical relationships between tRS and GRS. It is observed that the influence of site conditions on horizontal statistical relationships is negligible, whereas the effect of site conditions on vertical statistical relationships cannot be ignored. Considering the influence of site conditions, horizontal statistical relationship suitable for all site conditions and vertical statistical relationships suitable for hard sites and soft sites, respectively, are established. The horizontal and vertical statistical relationships are suitable to estimate tRS for design spectra in USNRC R.G. 1.60 and NUREG/CR-0098, Uniform Hazard Spectra (UHS) in Western North America (WNA), or any GRS falling inside the valid coverage of the statistical relationship. For UHS with significant high frequency spectral accelerations, such as UHS in Central and Eastern North America (CENA), an amplification ratio method is proposed to estimate tRS. Numerical examples demonstrate that the statistical relationships and the amplification ratio method are acceptable to estimate tRS for given GRS and to generate FRS using the direct method in different practical situations.
Subsystem response review. Seismic safety margins research program
International Nuclear Information System (INIS)
Kennedy, R.P.; Campbell, R.D.; Wesley, D.A.; Kamil, H.; Gantayat, A.; Vasudevan, R.
1981-07-01
A study was conducted to document the state of the art in seismic qualification of nuclear power plant components and subsystems by analysis and testing and to identify the sources and magnitude of the uncertainties associated with analysis and testing methods. The uncertainties are defined in probabilistic terms for use in probabilistic seismic risk studies. Recommendations are made for the most appropriate subsystem response analysis methods to minimize response uncertainties. Additional studies, to further quantify testing uncertainties, are identified. Although the general effect of non-linearities on subsystem response is discussed, recommendations and conclusions are based principally on linear elastic analysis and testing models. (author)
Response of cylindrical steel shell under seismic loading
International Nuclear Information System (INIS)
Tariq, M.; Amin, K.M.
2003-01-01
The seismic response of a cylindrical shell is simulated using the finite element method, and by spectral analysis. For this purpose the fundamental frequency of the cylinder is first calculated and compared with a published result. The mode shapes are also calculated which are later used for spectral analysis. The boundary nodes of the shell are displaced periodically according to a predetermined function of time by employing the acceleration time history of the El Centro earthquake to simulate the seismic loading. However, to conduct spectral analysis, the displacements are first transformed from the time domain to frequency domain using the Fast Fourier transformation. This spectral data is then used to obtain the actual displacement in the first mode under the given seismic loading. The techniques employed here can be used for cylindrical shell structures like rotor of a gas centrifuge, besides other structures that are subjected to seismic loading, besides in other time dependent loading conditions, for example rocket motor vibrations. (author)
Analysis of large concrete storage tank under seismic response
Energy Technology Data Exchange (ETDEWEB)
Le, Jingyuan; Cui, Hongcheng; He, Qiang; Ju, Jinsan [China Agricultural University, Beijing (China); You, Xiaochuan [Tsinghua University, Beijing (China)
2015-01-15
This study adopted the finite element software ABAQUS to trace the dynamic response history of large reinforced concrete storage tank during different seismic excitations. The dynamic characteristics and failure modes of the tank's structure were investigated by considering the rebar's effect. Calculation results show that the large concrete storage tank remains in safe working conditions under a seismic acceleration of 55 cm/s{sup 2}. The joint of the concrete wall and dome begins to crack when seismic acceleration reaches 250 cm/s{sup 2}. As the earthquake continues, cracks spread until the top of the wall completely fails and stops working. The maximum displacement of the concrete tank and seismic acceleration are in proportion. Peak displacement and stress of the tank always appear behind the maximum acceleration.
Seismic response analysis of floating nuclear power plant
International Nuclear Information System (INIS)
Hagiwara, Yutaka; Nakamura, Hideharu; Shiojiri, Hiroo
1988-01-01
Since Floating Nuclear Power Plants (FNPs) are considered to be isolated from horizontal seismic motion, it is anticipated to reduce seismic load for plant components and buildings on the barge. On the other hand, barge oscillation and sloshing in the closed basin might be excited by earthquakes, because natural periods of those motions correspond to relatively-long period component (between 2 and 20 seconds) of seismic motion. Therefore, it is necessary to evaluate seismic isolation effects and barge oscillation, for the rational design of FNPs. However, there do not exist any reasonable analytical tools which can evaluate seismic response of floating structures in closed basin. The purpose of the present report is to develop a seismic analysis method for FNPs. The proposed method is based on the finite element method, and the formulation includes fluid-structure interaction, water surface wave, buoyancy effect, and non-linear characteristics of mooring system. Response analysis can be executed in both time-domain and frequency-domain. Shaking table tests were conducted to validate the proposed method of analysis. The test results showed significant isolation effect of floating structure, and apparent interaction between the barge and the basin. And 2-D and 3-D frequency domain analyses and the 2-D linear and non-linear time-domain analyses were done and those analyses could simulate the test results well. (author)
Impact of mesh and DEM resolutions in SEM simulation of 3D seismic response
Khan, Saad; van der Meijde, M.; van der Werff, H.M.A.; Shafique, Muhammad
2017-01-01
This study shows that the resolution of a digital elevation model (DEM) and model mesh strongly influences 3D simulations of seismic response. Topographic heterogeneity scatters seismic waves and causes variation in seismic response (am-plification and deamplification of seismic amplitudes) at the
Polackwich, Alan Scott; Li, Jianbo; Shoskes, Daniel A
2015-10-01
Chronic prostatitis/chronic pelvic pain syndrome is a common condition that often requires multimodal therapy. Patients with chronic pelvic pain syndrome have a high incidence of pelvic floor spasm, which can be treated with pelvic floor physical therapy. However, this is a specialized skill. We compared outcomes of pelvic floor physical therapy as part of multimodal therapy in patients with chronic pelvic pain syndrome between those treated at our institution and elsewhere. We identified patients from our chronic pelvic pain syndrome registry with pelvic floor spasm who were seen between 2010 and 2014 for more than 1 visit. Patient phenotype was assessed with the UPOINT system and symptom severity was determined by the National Institutes of Health CPSI. A 6-point decrease in CPSI was used to define patient improvement. A total of 82 patients fit the study criteria. Mean age was 41.6 years (range 19 to 75) and median symptom duration was 24 months (range 3 to 240). Mean CPSI was 26.8 (range 10 to 41), the median number of positive UPOINT domains was 3 (range 1 to 6) and 27 patients (32.9%) were treated locally. At followup 9 patients had refused pelvic floor physical therapy, and 24 and 48 had undergone pelvic floor physical therapy elsewhere and at CCF, respectively. The mean change in CPSI was 1.11 ± 4.1 in patients who refused, -3.46 ± 6.7 in those treated elsewhere and -11.3 ± 7.0 in those treated at CCF (p physical therapy at CCF (OR 4.23, p = 0.002) and symptom duration (OR 0.52, p = 0.03) predicted improvement. Pelvic floor physical therapy can be effective for chronic pelvic pain syndrome in patients with pelvic floor spasm. However, the outcome depends on specialty training and experience of therapists. Copyright © 2015 American Urological Association Education and Research, Inc. Published by Elsevier Inc. All rights reserved.
Seismic responses of an unanchored generic fixture with different simulated boundary conditions
International Nuclear Information System (INIS)
Wu, T.S.; Blomquist, C.A.; Herceg, J.E.
1994-01-01
In the design of equipment for seismic loadings, it is common to anchor the equipment to prevent tipping or sliding. However, there are situations where the equipment should not be anchored. An unanchored piece of equipment is held to the floor only by the gravitational effect and, in the absence of friction, it could move freely. In the analytical investigation of an unanchored item during a seismic event, there is uncertainty on the proper simulation of the boundary conditions so that the analysis model will have no rigid-body motion. Seismic responses of a simple analytical model that is representative of a group of unanchored equipment have been investigated with different sets of simulated boundary conditions. The results show that, when the main interest of investigation is to assess the potential for tipping during an earthquake, the case with one of the four supporting pads simply supported, its two neighboring pads constrained against twisting motion, and all pads without vertical displacements yields the most conservative prediction. The analysis is applied to the fuel processing cell of the Integral Fast Reactor project. In order not to breach the liner of the existing facility and to keep operational flexibility of the fixtures, all new equipment to be installed within the fuel processing cell are required to be unanchored
International Nuclear Information System (INIS)
Tai, Koichi; Sasajima, Keisuke; Fukushima, Shunsuke; Takamura, Noriyuki; Onishi, Shigenobu
2014-01-01
This paper provides seismic design analysis methods suitable for crossover piping system, which connects between seismic isolated building and non-isolated building in the seismic isolated nuclear power plant. Through the numerical study focused on the main steam crossover piping system, seismic response spectrum analysis applying ISM (Independent Support Motion) method with SRSS combination or CCFS (Cross-oscillator, Cross-Floor response Spectrum) method has found to be quite effective for the seismic design of multiply supported crossover piping system. (author)
Seismic response of rock joints and jointed rock mass
International Nuclear Information System (INIS)
Ghosh, A.; Hsiung, S.M.; Chowdhury, A.H.
1996-06-01
Long-term stability of emplacement drifts and potential near-field fluid flow resulting from coupled effects are among the concerns for safe disposal of high-level nuclear waste (HLW). A number of factors can induce drift instability or change the near-field flow patterns. Repetitive seismic loads from earthquakes and thermal loads generated by the decay of emplaced waste are two significant factors. One of two key technical uncertainties (KTU) that can potentially pose a high risk of noncompliance with the performance objectives of 10 CFR Part 60 is the prediction of thermal-mechanical (including repetitive seismic load) effects on stability of emplacement drifts and the engineered barrier system. The second KTU of concern is the prediction of thermal-mechanical-hydrological (including repetitive seismic load) effects on the host rock surrounding the engineered barrier system. The Rock Mechanics research project being conducted at the Center for Nuclear Waste Regulatory Analyses (CNWRA) is intended to address certain specific technical issues associated with these two KTUs. This research project has two major components: (i) seismic response of rock joints and a jointed rock mass and (ii) coupled thermal-mechanical-hydrological (TMH) response of a jointed rock mass surrounding the engineered barrier system (EBS). This final report summarizes the research activities concerned with the repetitive seismic load aspect of both these KTUs
Seismic response analysis of a 13-story steel moment-framed building in Alhambra, California
Rodgers, Janise E.; Sanli, Ahmet K.; Çelebi, Mehmet
2004-01-01
The seismic performance of steel moment-framed buildings has been of particular interest since brittle fractures were discovered at the beam-column connections of some frames following the M6.7 1994 Northridge earthquake. This report presents an investigation of the seismic behavior of an instrumented 13-story steel moment frame building located in the greater Los Angeles area of California. An extensive strong motion dataset, ambient vibration data, engineering drawings and earthquake damage reports are available for this building. The data are described and subsequently analyzed. The results of the analyses show that the building response is more complex than would be expected from its highly symmetrical geometry. The building's response is characterized by low damping in the fundamental mode, larger peak accelerations in the intermediate stories than at the roof, extended periods of vibration after the cessation of strong input shaking, beating in the response, and significant torsion during strong shaking at the top of the concrete piers which extend from the basement to the second floor. The analyses of the data and all damage detection methods employed except one method based on system identification indicate that the response of the structure was elastic in all recorded earthquakes. These findings are in general agreement with the results of intrusive inspections (meaning fireproofing and architectural finishes were removed) conducted on approximately 5 percent of the moment connections following the Northridge earthquake, which found no earthquake damage.
Seismic analyses of structures. 1st draft
International Nuclear Information System (INIS)
David, M.
1995-01-01
The dynamic analysis presented in this paper refers to the seismic analysis of the main building of Paks NPP. The aim of the analysis was to determine the floor response spectra as response to seismic input. This analysis was performed by the 3-dimensional calculation model and the floor response spectra were determined for a number levels from the floor response time histories and no other adjustments were applied. The following results of seismic analysis are presented: 3-dimensional finite element model; basic assumptions of dynamic analyses; table of frequencies and included factors; modal masses for all modes; floor response spectra in all the selected nodes with figures of indicated nodes and important nodes of free vibration
Seismic response analysis of an instrumented building structure
Li, H.-J.; Zhu, S.-Y.; Celebi, M.
2003-01-01
The Sheraton - Universal hotel, an instrumented building lying in North Hollywood, USA is selected for case study in this paper. The finite element method is used to produce a linear time - invariant structural model, and the SAP2000 program is employed for the time history analysis of the instrumented structure under the base excitation of strong motions recorded in the basement during the Northridge, California earthquake of 17 January 1994. The calculated structural responses are compared with the recorded data in both time domain and frequency domain, and the effects of structural parameters evaluation and indeterminate factors are discussed. Some features of structural response, such as the reason why the peak responses of acceleration in the ninth floor are larger than those in the sixteenth floor, are also explained.
Seismic response of buried pipelines: a state-of-the-art review
International Nuclear Information System (INIS)
Datta, T.K.
1999-01-01
A state-of-the-art review of the seismic response of buried pipelines is presented. The review includes modeling of soil-pipe system and seismic excitation, methods of response analysis of buried pipelines, seismic behavior of buried pipelines under different parametric variations, seismic stresses at the bends and intersections of network of pipelines. pipe damage in earthquakes and seismic risk analysis of buried pipelines. Based on the review, the future scope of work on the subject is outlined. (orig.)
A method to generate generic floor response spectra for operating nuclear power plants
International Nuclear Information System (INIS)
Curreri, J.; Costantino, C.; Subudhi, M.; Reich, M.
1985-01-01
A free-field earthquake response spectra was used to generate horizontal earthquake time histories. The excitation was applied through the soil and into the various structures to produce responses in equipment. An entire range of soil conditions was used with each structure, from soft soil to solid rock. Actual PWR and BWR - Mark I structural models were used as representative of a class of structures. For each model, the stiffness properties were varied, with the same mass, so as to extend the fundamental base structure natural frequency from 2 cps to 36 cps. This resulted in fundamental mode coupled natural frequencies as low as 0.86 cps and as high as 30 cps. From all of these models of soils and structures, floor response spectra were generated at each floor level. The natural frequencies of the structures were varied to obtain maximum response conditions. The actual properties were first used to locate the natural frequencies. The stiffness properties were than varied, with the same mass, to extend the range of the fundamental base structure natural frequency. The intention was to have the coupled structural material frequencies in the vicinity of the peak amplitude frequency content of the excitation spectrum. Particular attention was therefore given to the frequency band between 2 Hz and 4 Hz. A horizontal generic floor response spectra is proposed for the top level of a generic structure. Reduction factors are applied to the peak acceleration for equipment at lower levels. (orig./HP)
Seismic analyses of structures. 1st draft
Energy Technology Data Exchange (ETDEWEB)
David, M [David Consulting, Engineering and Design Office (Czech Republic)
1995-07-01
The dynamic analysis presented in this paper refers to the seismic analysis of the main building of Paks NPP. The aim of the analysis was to determine the floor response spectra as responseto seismic input. This analysis was performed by the 3-dimensional calculation model and the floor response spectra were determined for a number levels from the floor response time histories and no other adjustments were applied. The following results of seismic analysis are presented: 3-dimensional finite element model; basic assumptions of dynamic analyses; table of frequencies and included factors; modal masses for all modes; floor response spectra in all the selected nodes with figures of indicated nodes and important nodes of free vibration.
Seismic response and rehabilitation of critical substation equipment
Energy Technology Data Exchange (ETDEWEB)
Saadeghvaziri, M.A.; Allaverdi, N.H. [New Jersey Inst. of Technology, Newark, NJ (United States); Ashrafi, A. [Columbia Univ., New York, NY (United States); Ersoy, S. [Greenman-Pedersen Inc., Babylon, NY (United States)
2004-07-01
Substations are one of the most important components of an electrical power system. They provide protection to transmission and distribution lines and transfer power between different voltage levels. Transformers and bushings within the substation are vulnerable to earthquake ground motion. It is extremely important that electric power systems remain functional following seismic damage. This study assessed the seismic response of critical substation equipment and described advanced technologies for rehabilitation measures such as the Friction Pendulum System (FPS). It presents the results of an extensive finite element analysis on response of transformers and bushings. The objective was to determine the seismic behaviour of transformers and bushings during an earthquake and to determine the probability of different failure modes. The response of an FPS isolated transformer to different earthquakes was also examined along with FPS radii, ground motion intensity and vertical excitations. A finite element model was developed for FPS. The study showed that seismic isolation is a viable mitigation strategy, but a modest increase in slack must be provided. 15 refs., 1 tab., 12 figs.
Seismic structural response analysis for multiple support excitation
International Nuclear Information System (INIS)
Shaw, D.E.
1975-01-01
In the seismic analysis of nuclear power plant equipment such as piping systems situations often arise in which piping systems span between adjacent structures or between different elevations in the same structure. Owing to the differences in the seismic time history response of different structures or different elevations of the same structure, the input support motion will differ for different supports. The concept of a frequency dependent participation factor and rotational response spectra accounting for phase differences between support excitations is developed by using classical equations of motion to formulate the seismic response of a structure subjected to multiple support excitation. The essence of the method lies in describing the seismic excitation of a multiply excited structure in terms of translational and rotational spectra used at every support and a frequency dependent spatial distribution function derived from the phase relationships of the different support time histories. In this manner it is shown that frequency dependent participation factors can be derived from the frequency dependent distribution functions. Examples are shown and discussed relative to closed form solutions and the state-of-the-art techniques presently being used for the solution of problems of multiply excited structures
International Nuclear Information System (INIS)
Takanashi, Koichi; Ohi, Kenichi
1988-01-01
A group of steel and reinforced concrete scaled structures with intentionally reduced seismic strength to 1/3 to 1/2 were constructed in 1983 for long term observation in order to collect precise data of earthquake response and grasp failure mechanisms during earthquakes. A monitoring system was installed in the structures as well as in the surrounding soil. Some reliable data have been successfully recorded since then, which can be available for verification of analytical models. (author)
Floor Response Evaluation for Auxiliary Building Subjected to Aircraft Impact Loading
International Nuclear Information System (INIS)
Shin, Sang Shup; Hahm, Daegi; Choi, Inkil
2014-01-01
These studies have been aimed to verify and ensure the safety of the targeted walls and structures especially in the viewpoint of the deterministic approach. However, a probabilistic safety assessment as well as deterministic approach for the damage of the internal component in the nuclear power plants (NPPs) subjected to aircraft crash is also needed. A probabilistic safety assessment for aircraft crash includes many uncertainties such as impact velocity, mass, impact location, shape, size, material etc. of aircraft. In this paper, an impact location was selected among the various parameters. This paper found the acceleration floor response spectra at specified locations (safety related components) on the target structure that assumed to be impact velocity 150m/s and maximum fuel for the specified aircraft model. In order to obtain the floor response in case of the crash with a various locations, the analyses for the auxiliary building subjected to aircraft impact were performed using Riera force history method and missile-target interaction method. The difference between responses in case of the building floor subjected to impact was occurred. Thus, in order to obtain the more accurate results, missile-target interaction method was used. This paper found the response at the selected point (node point No. 51). In order to probabilistic assessment for the safety related components, the assessment for a various parameters (velocity, mass, materials etc.) as well as impact locations should be needed
Seismic interferometry : Reconstructing the earth's reflection response
Draganov, D.S.; Wapenaar, C.P.A.; Thorbecke, J.W.
2006-01-01
In 1968, Jon Claerbout showed that the reflection response of a 1D acoustic medium can be reconstructed by autocorrelating the transmission response. Since then, several authors have derived relationships for reconstructing Green's functions at the surface, using crosscorrelations of (noise)
Zaidan,Patrícia; Silva,Elirez Bezerra da
2014-01-01
Objective to investigate the response of the pelvic floor muscles (PFM), and urinary incontinence (UI), in patients having undergone a prostatectomy, after treatment using electrical stimulation. Materials and methods this observational study was conducted in an outpatient urogynecologic physical therapy clinic of Hospital dos Servidores in Rio de Janeiro, Brazil from August to September 2012. Ten patients (aged, 64 ± 7 years) with urinary incontinence resulting from radical prostatectom...
International Nuclear Information System (INIS)
Ikushima, Takeshi
1995-11-01
The computer program ROCKING has been developed for seismic response analysis, which includes rocking and sliding behavior, of radioactive materials transport and/or storage casks. Main features of ROCKING are as follows; (1) Cask is treated as a rigid body. (2) Rocking and sliding behavior are considered. (3) Impact forces are represented by the spring dashpot model located at impact points. (4) Friction force is calculated at interface between a cask and a floor. (5) Forces of wire ropes against tip-over work only as tensile loads. In the paper, the calculation model, the calculation equations, validity calculations and user's manual are shown. (author)
International Nuclear Information System (INIS)
Byun, Y.J.; Kim, J.G.; Sung, K.K.; Lee, D.H.
2015-01-01
This paper deals with 3 topics concerning the APR1400 reactor vessel internals (RVI) seismic analysis: nonlinear problems, approaches to account for uncertainties of seismic model, and dynamic responses to various seismic excitations. First, the noticeable nonlinear characteristics of the RVI seismic model are discussed, and the modeling methods for properly simulating the nonlinear behaviors of RVI under seismic loads are presented. By applying these methods to the seismic model, the seismic analysis can correctly predict the dynamic response of RVI. Next, two approaches to account for the uncertainties of seismic model are evaluated: the time history broadening method, and the sensitivity analysis based on NUREG-0800, Section 4.2, Appendix A. From the evaluation results, it is confirmed that the time history broadening method employed in the seismic analysis of APR1400 RVI sufficiently accounts for the uncertainty of seismic model. Finally, the response characteristics of APR1400 RVI to various seismic excitations are investigated. The seismic excitations corresponding to various soil profiles, including the effects of cracked and un-cracked concrete stiffness on the reactor containment building structure, are used as forcing functions. From this study, the effects of various site conditions on the dynamic response of APR1400 RVI are identified. As a result, the enveloped seismic responses obtained from this study will contribute to the development of RVI seismic design that covers a wide range of potential site conditions. (authors)
Effects of Moat Wall Impact on the Seismic Response of Base Isolated Nuclear Power Plants
International Nuclear Information System (INIS)
Kim, Min Kyu; Kim, Jung Han; Mosqueda, Gilberto; Sarebanhab, Alireza
2015-01-01
The objectives of this study are to examine the effects of impact on the response of seismically isolated NPPs and identify characteristics of the isolation hardware and hard stop that minimize these effects. Considering variable distances to the hard stop and properties of the moat wall, the amplification in response is reported for acceleration and floor spectral accelerations at different points along the height of a NPP containment structure. Base isolation can be an effective strategy to protect critical facilities such as Nuclear Power Plants (NPPs) from the damaging effects of horizontal earthquake ground shaking. To be effective in reducing accelerations and deformations of the structure above, the seismic isolation bearings can be subjected to large displacements. In the case of an extreme earthquake, bearing displacements need to be limited by a hard stop in order to prevent failure of the bearings. Impact to the hard stop, which is often the moat wall at the basement level, is also of significant concern due to the potential for increased transfer of forces and amplification in response of the structural system, piping and other contents. However, the consequences of impact or factors important to mitigate its effects are not very well understood. The main findings of this study are related to modeling of NPP with moat wall in OpenSees and LSDyna as well as observations resulting from the parametric study of the performance of the NPP under different intensity levels of seismic excitations for different properties of the moat wall and bearings. • Variation in the isolator properties should be considered when examining seismic pounding. For BDBE even, 58.5 % cases result to the impact for lower bound properties while this value was 5.5 % for upper bound properties. Since the impact results are dependent to the assumed bearing properties, a better range of properties can be obtained from experimental testing of the bearing under large shear strains.
Method to generate generic floor response spectra for operating nuclear power plant
International Nuclear Information System (INIS)
Curreri, J.; Costantino, C.; Subudhi, M.; Reich, M.
1985-01-01
The general approach in the development of the response spectra was to study the effects on the dynamic characteristics of each of the elements in the chain of events that goes between the loads and the responses. This includes the loads, the soils and the structures. A free-field earthquake response spectra was used to generate horizontal earthquake time histories. The excitation was applied through the soil and into the various structures to produce responses in equipment. An entire range of soil conditions was used with each structure, from soft soil to solid rock. Actual PWR and BWR - Mark I structural models were used as representative of a class of structures. For each model, the stiffness properties were varied, with the same mass, so as to extend the fundamental base structure natural frequency from 2 cps to 36 cps. This resulted in fundamental mode coupled natural frequencies as low as 0.86 cps and as high as 30 cps. From all of these models of soils and structures, floor response spectra were generated at each floor level. The natural frequencies of the structures were varied to obtain maximum response conditions. The actual properties were first used to locate the natural frequencies. The stiffness properties were then varied, with the same mass, to extend the range of the fundamental base structure natural frequency. The intention was to have the coupled structural material frequencies in the vicinity of the peak amplitude frequency content of the excitation spectrum. Particular attention was therefore given to the frequency band between 2 Hz and 4 Hz. A horizontal generic floor response spectra is proposed for the top level of a generic structure. Reduction factors are applied to the peak acceleration for equipment at lower levels
Seismic response of cable stayed bridges under multi support excitation
Directory of Open Access Journals (Sweden)
Mahmoud Reza ُُShiravand
2017-07-01
Full Text Available In this Study, the seismic response of cable stayed bridges have been evaluated under multi-support excitations. There are three sources that cause the earthquake wave characteristics change during its propagation path. Local site effect, loss of coherency and wave passage effect are three sources of spatial variation of seismic ground motions. In long span structures, such as cable supported bridges, this phenomenon is more evident and traditional analyzing (uniform excitation may not be valid and be conservative. Thus, it is necessary to investigate the response of cable stayed bridges under non-uniform excitations. For this purpose, the non-uniform time histories were artificially generated using Kriging method based on a set of known time history in the west support of bridge. Nonlinear time history analysis was performed and cables axial force, deck moment, pylons moment and finally drift ratio of bridge have been examined in order to investigate how non-uniform excitation change the seismic response of bridge compared with uniform excitations. Results show non-uniform excitation in some bridge components increase responses and decreases in the others. In non-uniform excitation, although total time history energy is lesser than uniform excitation, it can significantly change the distribution of the forces and makes differential displacement between cables supports and increase the possibility of failure.
Celebi, M.
2006-01-01
An integrated seismic monitoring system with a total of 53 channels of accelerometers is now operating in and at the nearby free-field site of the 20-story steel-framed Atwood Building in highly seismic Anchorage, Alaska. The building has a single-story basement and a reinforced concrete foundation without piles. The monitoring system comprises a 32-channel structural array and a 21-channel site array. Accelerometers are deployed on 10 levels of the building to assess translational, torsional, and rocking motions, interstory drift (displacement) between selected pairs of adjacent floors, and average drift between floors. The site array, located approximately a city block from the building, comprises seven triaxial accelerometers, one at the surface and six in boreholes ranging in depths from 15 to 200 feet (???5-60 meters). The arrays have already recorded low-amplitude shaking responses of the building and the site caused by numerous earthquakes at distances ranging from tens to a couple of hundred kilometers. Data from an earthquake that occurred 186 km away traces the propagation of waves from the deepest borehole to the roof of the building in approximately 0.5 seconds. Fundamental structural frequencies [0.58 Hz (NS) and 0.47 Hz (EW)], low damping percentages (2-4%), mode coupling, and beating effects are identified. The fundamental site frequency at approximately 1.5 Hz is close to the second modal frequencies (1.83 Hz NS and 1.43 EW) of the building, which may cause resonance of the building. Additional earthquakes prove repeatability of these characteristics; however, stronger shaking may alter these conclusions. ?? 2006, Earthquake Engineering Research Institute.
International Nuclear Information System (INIS)
Healey, J.J.; Wu, S.T.; Murga, M.
1980-02-01
As part of the Phase I effort of the Seismic Safety Margins Research Program (SSMRP) being performed by the University of California Lawrence Livermore Laboratory for the US Nuclear Regulatory Commission, the basic objective of Subtask IV.1 (Structural Building Response Review) is to review and summarize current methods and data pertaining to seismic response calculations particularly as they relate to the objectives of the SSMRP. This material forms one component in the development of the overall computational methodology involving state of the art computations including explicit consideration of uncertainty and aimed at ultimately deriving estimates of the probability of radioactive releases due to seismic effects on nuclear power plant facilities
Response of sliding structures to seismic excitation: bibliographical study
International Nuclear Information System (INIS)
Sarh, K.; Duval, C.
1992-11-01
Calculation of the seismic response of structures on sliding supports involves the dual problem of ''non-linear'' and ''random'' dynamic behaviour. After a review of the non-linearities common in dynamics, slipping is compared with a hysteresis phenomenon. Simple examples are then used to present the Fokker-Planck equation and the equivalent linearization method. Finally, the methods for modification of the excitation spectrum intended for the engineering calculations are recalled. (authors). 21 figs., 23 refs
International Nuclear Information System (INIS)
Hagiwara, Yutaka; Yamamoto, Kohsuke; Kawamoto, Yoji; Nakagawa, Masaki; Akiyama, Hiroshi
1998-01-01
Plastic shear-bending buckling under seismic loadings is one of the major problems in the structural design of FBR main vessels. Pseudo-dynamic and dynamic buckling tests of cylinders were performed in order to study the effects of nonlinear seismic response on buckling strength, ductility, and plastic response reduction. The buckling strength formulae and the rule for ductility factors both derived from static tests were confirmed to be valid for the tests under dynamic loads. The displacement-constant rule for response reduction effect was modified by acceleration amplification factor in order to maintain applicability for various spectral profiles of seismic excitations. The response reduction estimated by the proposed rule was reasonably conservative for all cases of the pseudo-dynamic and the dynamic tests. Finally, a seismic safety assessment rule was proposed for plastic shear-bending buckling of cylinders, which include the proposed response reduction rule. (author)
Evaluation of the Reduction of Seismic Response of Adjacent Structures Using Viscous Damper Joint
Directory of Open Access Journals (Sweden)
Hamed Karbalay Malek
2017-09-01
Full Text Available This study examines the effect of common viscose damper on the behavior of adjacent reinforced concrete structures. For this purpose, three reinforced concrete 3, 5 and 7 floors buildings with a regular plan were selected and were compared in two cases without and with viscous dampers at the seams. They are designed based on discussions of Buildings Regulations 2800 and the 6 and 9 issues of Iranian National Building Regulations. Those buildings face under accelerograms of Bam, Mangil and El Centro, and then they are analyzed with nonlinear modal time history. This Accelerograms before applying to the structures, they are scaled based on the 2800 Regulations. Those buildings were modeled by SAP2000 finite element modeling software. Linear behavior of structural components of the structure and the non-linear behavior viscous damper were modeled. Finally, the seismic response of buildings includes the base shear force, up to a maximum lateral acceleration of seismic classes and classes for both with and without the viscous damper have been extracted and compared. The results showed the reduction in relative lateral displacement, maximum acceleration and base cut applied to structure in the presence of viscous dampers between two structures. This decline is not even in the direction that the viscous damper is viewed as significant.
Seismic response and damage detection analyses of an instrumented steel moment-framed building
Rodgers, J.E.; Celebi, M.
2006-01-01
The seismic performance of steel moment-framed buildings has been of particular interest since brittle fractures were discovered at the beam-column connections in a number of buildings following the M 6.7 Northridge earthquake of January 17, 1994. A case study of the seismic behavior of an extensively instrumented 13-story steel moment frame building located in the greater Los Angeles area of California is described herein. Response studies using frequency domain, joint time-frequency, system identification, and simple damage detection analyses are performed using an extensive strong motion dataset dating from 1971 to the present, supported by engineering drawings and results of postearthquake inspections. These studies show that the building's response is more complex than would be expected from its highly symmetrical geometry. The response is characterized by low damping in the fundamental mode, larger accelerations in the middle and lower stories than at the roof and base, extended periods of vibration after the cessation of strong input shaking, beating in the response, elliptical particle motion, and significant torsion during strong shaking at the top of the concrete piers which extend from the basement to the second floor. The analyses conducted indicate that the response of the structure was elastic in all recorded earthquakes to date, including Northridge. Also, several simple damage detection methods employed did not indicate any structural damage or connection fractures. The combination of a large, real structure and low instrumentation density precluded the application of many recently proposed advanced damage detection methods in this case study. Overall, however, the findings of this study are consistent with the limited code-compliant postearthquake intrusive inspections conducted after the Northridge earthquake, which found no connection fractures or other structural damage. ?? ASCE.
Hashiguchi, Nobuko; Tochihara, Yutaka; Ohnaka, Tadakatsu; Tsuchida, Chiaki; Otsuki, Tamio
2004-11-01
The purpose of this study was to investigate the effects of a floor heating and air conditioning system on thermal responses of the elderly. Eight elderly men and eight university students sat for 90 minutes in a chair under the following 3 conditions: air conditioning system (A), floor heating system (F) and no heating system (C). The air temperature of sitting head height for condition A was 25 degrees C, and the maximum difference in vertical air temperature was 4 degrees C. The air and floor temperature for condition F were 21 and 29 degrees C, respectively. The air temperature for condition C was 15 degrees C. There were no significant differences in rectal temperature and mean skin temperature between condition A and F. Systolic blood pressure of the elderly men in condition C significantly increased compared to those in condition A and F. No significant differences in systolic blood pressure between condition A and F were found. The percentage of subjects who felt comfortable under condition F was higher than that of those under condition A in both age groups, though the differences between condition F and A was not significant. Relationships between thermal comfort and peripheral (e.g., instep, calf, hand) skin temperature, and the relationship between thermal comfort and leg thermal sensation were significant for both age groups. However, the back and chest skin temperature and back thermal sensation for the elderly, in contrast to that for the young, was not significantly related to thermal comfort. These findings suggested that thermal responses and physiological strain using the floor heating system did not significantly differ from that using the air conditioning system, regardless of the subject age and despite the fact that the air temperature with the floor heating system was lower. An increase in BP for elderly was observed under the condition in which the air temperature was 15 degrees C, and it was suggested that it was necessary for the elderly
Dynamic response of Belene WWER-1000 to seismic loading conditions
International Nuclear Information System (INIS)
Krutzik, N.J.; Petrovski, D.; Sachanski, S.
1993-01-01
Within the framework of investigating of the capacity of the WWER-100 at the Belene site, an analysis was performed using revised seismic input data as well as two alternative foundation concepts (natural soil and soil exchange). The starting point for the analysis was the development of a suitable model of the coupled structures (base building, external building, containment, internal structure) and soil taking into account the real properties of the originally layered as well as the exchanged soil. The soil-structure effects were considered according to the analytical method employed, either through soil impedance (substructure method) or explicitly by a complex (direct method). On the basis of the results obtained by the two methods (substructure and direct method) the seismic safety of the complex structures for different foundation concepts was evaluated. By comparing the calculated structural response with the design spectra originally used for the design of components and systems the available safety margin was estimated
Subsystem response analysis for the Seismic Safety Margins Research Program
International Nuclear Information System (INIS)
Chuang, T.Y.
1981-01-01
A review of the state-of-the-art of seismic qualification methods of subsystem has been completed. This task assesses the accuracy of seismic analysis techniques to predict dynamic response, and also identifies and quantifies sources of random and modeling undertainty in subsystem response determination. The subsystem has been classified as two categories according to the nature of support: multiply supported subsystems (e.g., piping systems) and singly supported subsystems (e.g., pumps, turbines, electrical control panels, etc.). The mutliply supported piping systems are analyzed by multisupport input time history method. The input motions are the responses of major structures. The dynamic models of the subsystems identified by the event/fault tree are created. The responses calculated by multisupport input time history method are consistent with the fragility parameters. These responses are also coordinated with the event/fault tree description. The subsystem responses are then evaluated against the fragility curves of components and systems and incorporated in the event/fault tree analysis. (orig./HP)
International Nuclear Information System (INIS)
Benda, B.J.; Johnson, J.J.; Lo, T.Y.
1981-08-01
The primary task of the Major Structure Response Project within the Seismic Safety Margins Research Program (SSMRP) was to develop detailed finite element models of the Zion Nuclear Power Plant's containment building and auxiliary-fuel-turbine (AFT) complex. The resulting models served as input to the seismic methodology analysis chain. The containment shell was modeled as a series of beam elements with the shear and bending characteristics of a circular cylindrical shell. Masses and rotary inertias were lumped at nodal points; thirteen modes were included in the analysis. The internal structure was modeled with three-dimensional finite elements, with masses again lumped at selected nodes; sixty modes were included in the analysis. The model of the AFT complex employed thin plate and shell elements to represent the concrete shear walls and floor diaphragms, and beam and truss elements to model the braced frames. Because of the size and complexity of the model, and the potentially large number of degrees of freedom, masses were lumped at a limited number of node points. These points were selected so as to minimize the effect of the discrete mass distribution on structural response. One hundred and thirteen modes were extracted. A second objective of Project IV was to investigate the effects of uncertainty and variability on structural response. To this end, four side studies were conducted. Three of them, briefly summarized in this volume, addressed themselves respectively to an investigation of sources of random variability in the dynamic response of nuclear power plant structures; formulation of a methodology for modeling and evaluating the effects of structural uncertainty on predicted modal characteristics of major nuclear power plant structures and substructures; and a preliminary evaluation of nonlinear responses in shear-wall structures. A fourth side study, reported in detail in this volume, quantified variations in dynamic characteristics and seismic
Seismic analyses of Paks RB. Progress report 1993-1994
Energy Technology Data Exchange (ETDEWEB)
David, M [David Consulting, Engineering and Design Office (Czech Republic)
1995-07-01
The dynamic analysis presented in this report refers to the seismic analysis of the main building of Paks NPP. The following tasks which have been completed are described: design of 3-dimensional model of the main building; calculation of frequencies and modes of free vibrations; determination of modal masses for all modes of vibrations; floor response spectra as response to seismic excitation assumed for the Paks site; relative response of seismic acceleration at the top of the condensing tower.
Seismic Safety Program: Ground motion and structural response
Energy Technology Data Exchange (ETDEWEB)
1993-05-01
In 1964, John A. Blume & Associates Research Division (Blume) began a broad-range structural response program to assist the Nevada Operations Office of the US Atomic Energy Commission (AEC) in ensuring the continued safe conduct of underground nuclear detonation testing at the Nevada Test Site (NTS) and elsewhere. Blume`s long experience in earthquake engineering provided a general basis for the program, but much more specialized knowledge was required for the AEC`s purposes. Over the next 24 years Blume conducted a major research program to provide essential understanding of the detailed nature of the response of structures to dynamic loads such as those imposed by seismic wave propagation. The program`s results have been embodied in a prediction technology which has served to provide reliable advanced knowledge of the probable effects of seismic ground motion on all kinds of structures, for use in earthquake engineering and in building codes as well as for the continuing needs of the US Department of Energy`s Nevada Operations Office (DOE/NV). This report is primarily an accounting of the Blume work, beginning with the setting in 1964 and the perception of the program needs as envisioned by Dr. John A. Blume. Subsequent chapters describe the structural response program in detail and the structural prediction procedures which resulted; the intensive data acquisition program which, as is discussed at some length, relied heavily on the contributions of other consultant-contractors in the DOE/NV Seismic Safety Support Program; laboratory and field studies to provide data on building elements and structures subjected to dynamic loads from sources ranging from testing machines to earthquakes; structural response activities undertaken for testing at the NTS and for off-NTS underground nuclear detonations; and concluding with an account of corollary studies including effects of natural forces and of related studies on building response.
Floor response spectra for multi-degree-of-freedom systems by Fourier transform
International Nuclear Information System (INIS)
Scanlan, R.H.; Sachs, K.
1975-01-01
A method of generating floor response spectra from a given ground response spectrum is given. This time-saving approach makes use of Fourier spectrum techniques and the randomness of phase angles. In matrix form a structure having many degrees-of-freedom is described by the equation of motion with M, C, K as the mass-, damping-, and stiffness matrices and Z being the acceleration time history of the earthquake and I a direction vector. If the Fourier spectrum FZ of the ground motion is known, then by standard methods the Fourier spectrum of the equipment response can be obtained. The assumption of random phase angles for the synthetic time history Z seems reasonable. The response is then also a superposition of cosine waves. Good agreement with time history methods is obtained. This method is much faster than time history methods, which are being used in most applications
Reanalysis and evaluation of seismic response of reactor building
International Nuclear Information System (INIS)
Li Zhongcheng; Li Zhongxian
2005-01-01
For the Ling Ao phase-I (LA-I) Nuclear Power Plant (NPP), its' seismic analysis of nuclear island was in accordance with the approaches in RCC-G standard for the model M310 in France, in which the Simplified impedance method was employed for the consideration of SSI. Thanks to the rapid progress being made in upgrading the evaluation technology and the capability of data processing systems, methods and software tools for the SSI analysis have experienced significant development all over the world. Focused on the model of reactor building of the LA-I NPP, in this paper the more sophisticated 3D half-space continuum impedance method based on the Green functions is used to analyze the functions of the soil, and then the seismic responses of the coupled SSI system are calculated and compared with the corresponding design values. It demonstrates that the design method provides a set of conservatively safe results. The conclusions from the study are hopefully to provide some important references to the assessment of seismic safety margin for LA-I NPP. (authors)
Full scale testing for investigation of wind turbine seismic response
Energy Technology Data Exchange (ETDEWEB)
Prowell, I.; Veletzos, M.; Elgamal, A. [California Univ., San Diego, CA (United States). Dept. of Structural Engineering
2008-07-01
In 2007, much of the growth in wind energy development was concentrated in North America and Asia, two regions which periodically experience strong earthquakes that may impact the final turbine design. As such, rational prediction of seismic hazards must be considered in order to maintain and enhance the ability of wind power to compete economically with other energy sources. In response to this challenge, researchers at the University of California, San Diego (UCSD) have experimentally investigated wind turbines to gain an understanding of expected earthquake forces. This paper described the experimental setup for a full scale shake table test of a 65 kW wind turbine. The turbine was excited perpendicular to the axis of the rotor with a seismic base shaking record scaled to various levels. The data was analyzed using simple but effective procedures to provide insight into the observed structural damping of the wind turbine. The experimental investigation showed that full scale seismic testing of wind turbines is possible and can provide valuable insight into dynamic behaviour of wind turbines. The results can be used to develop a more accurate picture of how wind turbines are impacted by earthquakes. The data regarding the low observed super-structure damping provides a basis for calibration and further development of verified design procedures. 20 refs., 3 tabs.
Analysis of the seismic response of a fast reactor core
International Nuclear Information System (INIS)
Martelli, A.; Maresca, G.
1984-01-01
This report deals with the methods to apply for a correct evaluation of the reactor core seismic response. Reference is made to up-to-date design data concerning the PEC core, taking into account the presence of the core-restraint plate located close to the PEC core elements top and applying the optimized iterative procedure between the vessel linear calculation and the non-linear ones limited to the core, which had been described in a previous report. It is demonstrated that the convergence of this procedure is very fast, similar to what obtained in the calculations of the cited report, carried out with preliminary data, and it is shown that the cited methods allow a reliable evaluation of the excitation time histories for the experimental tests in support of the seismic verification of the shutdown system and the core of a fast reactor, as well as relevant data for the experimental, structural and functional, verification of the core elements in the case of seismic loads
Directory of Open Access Journals (Sweden)
Ahmer Ali
2017-06-01
Full Text Available Due to the severe impacts of recent earthquakes, the use of seismic isolation is paramount for the safety of nuclear structures. The diversity observed in seismic events demands ongoing research to analyze the devastating attributes involved, and hence to enhance the sustainability of base-isolated nuclear power plants. This study reports the seismic performance of a seismically-isolated nuclear reactor containment building (NRCB under strong short-period ground motions (SPGMs and long-period ground motions (LPGMs. The United States Nuclear Regulatory Commission-based design response spectrum for the seismic design of nuclear power plants is stipulated as the reference spectrum for ground motion selection. Within the period range(s of interest, the spectral matching of selected records with the target spectrum is ensured using the spectral-compatibility approach. NRC-compliant SPGMs and LPGMs from the mega-thrust Tohoku earthquake are used to obtain the structural response of the base-isolated NRCB. To account for the lack of earthquakes in low-to-moderate seismicity zones and the gap in the artificial synthesis of long-period records, wavelet-decomposition based autoregressive moving average modeling for artificial generation of real ground motions is performed. Based on analysis results from real and simulated SPGMs versus LPGMs, the performance of NRCBs is discussed with suggestions for future research and seismic provisions.
Energy Technology Data Exchange (ETDEWEB)
Ali, Ahmer [ENVICO Consultants Co. Ltd., Seoul (Korea, Republic of); Abu-Hayah, Nadin; Kim, Doo Kie [Civil and Environmental Engineering, Kunsan National University, Gunsan (Korea, Republic of); Cho, Sung Gook [Innose Tech Co., Ltd., Incheon (Korea, Republic of)
2017-06-15
Due to the severe impacts of recent earthquakes, the use of seismic isolation is paramount for the safety of nuclear structures. The diversity observed in seismic events demands ongoing research to analyze the devastating attributes involved, and hence to enhance the sustainability of base-isolated nuclear power plants. This study reports the seismic performance of a seismically-isolated nuclear reactor containment building (NRCB) under strong short-period ground motions (SPGMs) and long-period ground motions (LPGMs). The United States Nuclear Regulatory Commission-based design response spectrum for the seismic design of nuclear power plants is stipulated as the reference spectrum for ground motion selection. Within the period range(s) of interest, the spectral matching of selected records with the target spectrum is ensured using the spectral-compatibility approach. NRC-compliant SPGMs and LPGMs from the mega-thrust Tohoku earthquake are used to obtain the structural response of the base-isolated NRCB. To account for the lack of earthquakes in low-to-moderate seismicity zones and the gap in the artificial synthesis of long-period records, wavelet-decomposition based autoregressive moving average modeling for artificial generation of real ground motions is performed. Based on analysis results from real and simulated SPGMs versus LPGMs, the performance of NRCBs is discussed with suggestions for future research and seismic provisions.
International Nuclear Information System (INIS)
Ryu, Jeong-Soo; Seo, Choon-Gyo; Kim, Jae-Min; Yun, Chung-Bang
2010-01-01
This paper proposes a slightly new three-dimensional radial-shaped dynamic infinite elements fully coupled to finite elements for an analysis of soil-structure interaction system in a horizontally layered medium. We then deal with a seismic analysis technique for a three-dimensional soil-structure interactive system, based on the coupled finite-infinite method in frequency domain. The dynamic infinite elements are simulated for the unbounded domain with wave functions propagating multi-generated wave components. The accuracy of the dynamic infinite element and effectiveness of the seismic analysis technique may be demonstrated through a typical compliance analysis of square surface footing, an L-shaped mat concrete footing on layered soil medium and two kinds of practical seismic analysis tests. The practical analyses are (1) a site response analysis of the well-known Hualien site excited by all travelling wave components (primary, shear, Rayleigh waves) and (2) a generation of a floor response spectrum of a nuclear power plant. The obtained dynamic results show good agreement compared with the measured response data and numerical values of other soil-structure interaction analysis package.
On the response of large dams to incoherent seismic excitation
International Nuclear Information System (INIS)
Ramadan, O.; Novak, M.
1993-01-01
An intensive parametric study was conducted to investigate the response of concrete gravity dams to horizontal, spatially variable seismic ground motions. Both segmented dams consisting of separate blocks, or monoliths, and continuous monolithic dams are considered. The study includes the effects of various parameters on system natural frequencies, vibration modes, modal displacement ratios, as well as dam displacements and internal stresses due to spatially variable ground motions. The dam analytical model, and dam response to incoherent ground motions are described. The results show that the dam vibrates almost as a rigid body under the fully correlated waves, but bends and twists significantly under the spatially correlated motions. Dam-foundation interaction magnifies the low frequency components of the dam response, more so for a full reservoir, but decreases the high frequency components. For long dams, the effects of spatially incoherent ground motions are qualitatively different and can be much greater than those due to surface travelling waves. 3 refs., 3 figs
Kinematic seismic response of piles in layered soil profile
International Nuclear Information System (INIS)
Ahmad, I.; Khan, A.N.
2006-01-01
This paper is aimed at highlighting the importance of Kinematic Seismic Response of Piles, a phenomenon often ignored in dynamic analysis. A case study is presented where the end bearing pile is embedded in two layer soil system of highly contrasting stiffnesses; a typical case where kinematic loading plays important role. The pile soil system is modeled as continuous system and as discrete parameter system; both are based on BDWF (Beam on Dynamic Winkler Foundation) formulation. For discrete parameter system, a finite element software SAP2000 is used and the modeling technique of kinematic interaction in finite element software is discussed. For pile soil system modeled as continuous system, a general MATLAB code is developed capable of performing elastic site response analysis in two layer soil system, solving differential equation governing kinematic interaction, and giving as output the maximum ground displacement, maximum pile displacement, rotation, moment and shear distribution along pile length. The paper concludes that kinematic seismic actions must be evaluated particularly at the interface of soil layers of significantly differing soil stiffnesses. (author)
Seismic response Analyses of Hanaro in-chimney bracket structures
International Nuclear Information System (INIS)
Lee, Jae Han; Ryu, J.S.; Cho, Y.G.; Lee, H.Y.; Kim, J.B.
1999-05-01
The in-chimney bracket will be installed in the upper part of chimney, which holds the capsule extension pipes in upper one-third of length. For evaluating the effects on the capsules and related reactor structures, ANSYS finite element analysis model is developed and the dynamic characteristics are analyzed. The seismic response anlayses of in-chimney bracket and related reactor structures of HANARO under the design earthquake response spectrum loads of OBE (0.1 g) and SSE (0.2 g) are performed. The maximum horizontal displacements of the flow tubes are within the minimum half gaps between close flow tubes, it is expected that these displacement will not produce any contact between neighbor flow tubes. The stress values in main points of reactor structures and in-chimney bracket for the seismic loads are also within the ASME Code limits. It is also confirmed that the fatigue usage factor is much less than 1.0. So, any damage on structural integrity is not expected when an in-chimney bracket is installed to upper part of the reactor chimney. (author). 12 refs., 24 tabs., 37 figs
Stochastic seismic response of building with super-elastic damper
Gur, Sourav; Mishra, Sudib Kumar; Roy, Koushik
2016-05-01
Hysteretic yield dampers are widely employed for seismic vibration control of buildings. An improved version of such damper has been proposed recently by exploiting the superelastic force-deformation characteristics of the Shape-Memory-Alloy (SMA). Although a number of studies have illustrated the performance of such damper, precise estimate of the optimal parameters and performances, along with the comparison with the conventional yield damper is lacking. Presently, the optimal parameters for the superelastic damper are proposed by conducting systematic design optimization, in which, the stochastic response serves as the objective function, evaluated through nonlinear random vibration analysis. These optimal parameters can be employed to establish an initial design for the SMA-damper. Further, a comparison among the optimal responses is also presented in order to assess the improvement that can be achieved by the superelastic damper over the yield damper. The consistency of the improvements is also checked by considering the anticipated variation in the system parameters as well as seismic loading condition. In spite of the improved performance of super-elastic damper, the available variant of SMA(s) is quite expensive to limit their applicability. However, recently developed ferrous SMA are expected to offer even superior performance along with improved cost effectiveness, that can be studied through a life cycle cost analysis in future work.
Seismic Response Analysis of Assembled Reactor Vessel Internals
International Nuclear Information System (INIS)
Je, Sang-Yun; Chang, Yoon-Suk; Kang, Sung-Sik
2015-01-01
RVIs (Reactor Vessel Internals) perform important safe-related functions such as upholding the nuclear fuel assembly as well as providing the coolant passage of the reactor core and supporting the control rod drive mechanism. Therefore, the components including RVIs have to be designed and constructed taking into account the structural integrity under various accident scenarios. The reliable seismic analysis is essentially demanded to maintain the safe-related functions of RVIs. In this study, a modal analysis was performed based on the previous researches to examine values of frequencies, mode shapes and participation factors. Subsequently, the structural integrity respecting to the earthquake was evaluated through a response spectrum analysis by using the output variables of modal analysis. In this study, the structural integrity of the assembled RVIs was carried out against the seismic event via the modal and response spectrum analyses. Even though 287MPa of the maximum stress value occurred at the connected region between UGS and CSA, which was lower than its allowable value. At present, fluid-structure interaction effects are being examined for further realistic simulation, which will be reported in the near future
Seismic Responses of Shot Span Bridge under Three Different Patterns of Earthquake Excitations
International Nuclear Information System (INIS)
Zhou Daochuan; Chen Guorong; Lu Yan
2010-01-01
This paper presents a study of the influence of three different types of seismic input methods on the longitudinal seismic response of a short, three-span, variable cross-section, reinforced concrete bridge. Research progress of the seismic model is introduced briefly. Finite element model is created for the bridge and time history analysis conducted. Three different types of illustrative excitations are considered: 1) the EI-Centro seismic wave is used as uniform excitations at all bridge supports; 2) fixed apparent wave velocity is used for response analysis of traveling wave excitations on the bridge; 3) conforming to a selected coherency model, the multiple seismic excitation time histories considering spatially variable effects are generated. The contrast study of the response analysis result under the three different seismic excitations is conducted and the influence of different seismic input methods is studied. The comparative analysis of the bridge model shows that the uniform ground motion input can not provide conservative seismic demands-in a number of cases it results in lower response than that predicted by multiple seismic excitations. The result of uniform excitation and traveling wave excitation shows very small difference. Consequently, multiple seismic excitations needs to be applied at the bridge supports for response analysis of short span bridge.
Bertalanffy, Helmut; Tissira, Nadir; Krayenbühl, Niklaus; Bozinov, Oliver; Sarnthein, Johannes
2011-03-01
Surgical exposure of intrinsic brainstem lesions through the floor of the 4th ventricle requires precise identification of facial nerve (CN VII) fibers to avoid damage. To assess the shape, size, and variability of the area where the facial nerve can be stimulated electrophysiologically on the surface of the rhomboid fossa. Over a period of 18 months, 20 patients were operated on for various brainstem and/or cerebellar lesions. Facial nerve fibers were stimulated to yield compound muscle action potentials (CMAP) in the target muscles. Using the sites of CMAP yield, a detailed functional map of the rhomboid fossa was constructed for each patient. Lesions resected included 14 gliomas, 5 cavernomas, and 1 epidermoid cyst. Of 40 response areas mapped, 19 reached the median sulcus. The distance from the obex to the caudal border of the response area ranged from 8 to 27 mm (median, 17 mm). The rostrocaudal length of the response area ranged from 2 to 15 mm (median, 5 mm). Facial nerve response areas showed large variability in size and position, even in patients with significant distance between the facial colliculus and underlying pathological lesion. Lesions located close to the facial colliculus markedly distorted the response area. This is the first documentation of variability in the CN VII response area in the rhomboid fossa. Knowledge of this remarkable variability may facilitate the assessment of safe entry zones to the brainstem and may contribute to improved outcome following neurosurgical interventions within this sensitive area of the brain.
Influence of fabric anisotropy on seismic responses of foundations
Directory of Open Access Journals (Sweden)
Jin Qin
2015-04-01
Full Text Available Earthquakes, as one of the well-known natural disasters, are highly destructive and unpredictable. Foundation failure due to liquefaction induced by earthquakes can cause casualties as well as significant damage to the building itself. Fabric anisotropy of soil grains is considered to be an important factor in dynamic soil response based on previous researches and laboratory tests. However, the limited availability of real physical data makes it less persuasive. In this study, a shake table installed on a geotechnical centrifuge is used to provide the designed seismic motions, and therefore, to simulate the realistic earthquake motion to foundations. Important parameters in the responses such as acceleration, excess pore pressure and deformation are evaluated to investigate the influence. Implications for design are also discussed.
DEFF Research Database (Denmark)
Petersen, Marianne Graves; Krogh, Peter; Ludvigsen, Martin
2005-01-01
Within architecture, there is a long tradition of careful design of floors. The design has been concerned with both decorating floors and designing floors to carry information. Ubiquitous computing technology offers new opportunities for designing interactive floors. This paper presents three...... different interactive floor concepts. Through an urban perspective it draws upon the experiences of floors in architecture, and provides a set of design issues for designing interactive floors....
Seismic response of structures by the response spectrum method
International Nuclear Information System (INIS)
Hadjian, A.H.
1981-01-01
The problems of the acceleration profile at the lower elevations of cantilever structures and the response of relatively rigid structures are explored. It is shown that the use of the conventional methods for the above problems provide very approximate results. An alternate combination of the modal responses is proposed that not only resolves the above problems but also provides better estimates of response for the complete range of structure frequencies. The procedure treats the relative and rigid body responses separately and then appropriately combines the two results. For the rigid range of frequencies (fundamental frequencies greater than about 2 Hz), the proposed procedure does not encounter any numerical difficulties because of the additive nature of the component responses; however, the application of the proposed procedure for very flexible structures causes accuracy problems since the rigid body effects tend to be subtractive from the flexural response of about equal magnitude. For this latter class of problems, the conventional approach of modal combination provides adequate results and avoids the above mentioned numerical difficulties. (orig.)
Effects of different SSI parameters on the floor response spectra of a nuclear reactor building
International Nuclear Information System (INIS)
Kabir, A.F.; Bolourchi, S.; Maryak, M.E.
1991-01-01
The effects of several critical soil-structure interaction (SSI) parameters on the floor response spectra (FRS) of a typical nuclear reactor building have been examined. These parameters are computation of soil impedance functions using different approaches, scattering effects (reductions in ground motion due to embedment and rigidity of building foundation) and strain dependency of soil dynamic properties. This paper reports that the significant conclusions of the study, which are applicable to a deeply embedded very rigid nuclear reactor building, are as follows: FRS generated without considering scattering effects are highly conservative; differences between FRS, generated considering strain-dependency of soil dynamic properties, and those generated suing low-strain values, are not significant; and the lumped-parameter approach of SSI calculations, which only uses a single value of soil shear modulus in impedance calculations, may not be able to properly compute the soil impedances for a soil deposit with irregularly varying properties with depth
International Nuclear Information System (INIS)
Fogelquist, J.; Kaul, M.K.; Koppe, R.; Tagart, S.W. Jr.; Thailer, H.; Uffer, R.
1980-03-01
This project is directed toward a portion of the Seismic Safety Margins Research Program which includes one link in the seismic methodology chain. The link addressed here is the structural subsystem dynamic response which consists of those components and systems whose behavior is often determined decoupled from the major structural response. Typically the mathematical model utilized for the major structural response will include only the mass effects of the subsystem and the main model is used to produce the support motion inputs for subsystem seismic qualification. The main questions addressed in this report have to do with the seismic response uncertainty of safety-related components or equipment whose seismic qualification is performed by (a) analysis, (b) tests, or (c) combinations of analysis and tests, and where the seismic input is assumed to have no uncertainty
Boyle, Sarah A.; Roberts, Beth; Pope, Brittany M.; Blake, Margaret R.; Leavelle, Stephen E.; Marshall, Jennifer J.; Smith, Andrew; Hadicke, Amanda; Falcone, Josephine F.; Knott, Katrina; Kouba, Andrew J.
2015-01-01
Captive African (Loxodonta africana) and Asian (Elephas maximus) elephants can experience foot pathologies and arthritis. As a preventative measure against these pathologies and to alleviate the potential discomfort due to concrete substrates, some zoological institutions have renovated elephant housing to increase the amount of natural or shock-absorbent substrates. The objective of this study was to compare behavioral (diurnal and nocturnal) and glucorticoid (e.g., serum cortisol) responses of three female African elephants before, during, and after renovation to their indoor housing floor to assess whether renovations had short-term effects on the elephants’ behavior and stress physiology. Behavioral data were collected using scan-sampling methods, and activity budgets were constructed for each of the three elephants. In addition, the duration of all lying rest activities were recorded. Weekly serum cortisol concentrations were determined with enzyme immunoassay (EIA). Overall, eating was the most prevalent behavior exhibited outdoors during the day, while resting (either in a lying or standing position) were most common during the indoor, nocturnal periods. Although variation existed among the three elephants, all three females spent significantly more time walking and less time eating during the day after the completion of the renovations. The extent to which the three elephants exhibited nocturnal lying rest behavior varied among the elephants, with the oldest elephant exhibiting the least amount (an average of 13.2 ± 2.8% of the nightly behavioral scans) compared to the two younger elephants (an average of 34.5 ± 2.1% and 56.6 ± 2.8% of the nightly behavioral scans). There was a significant increase in lying rest behavior for one elephant and standing rest for a second elephant following renovations. Baseline cortisol concentrations prior to renovations were 3.0 ± 0.4 ng/ml, 4.5 ± 0.5 ng/ml, and 4.9 ± 0.5 ng/ml for the three elephants. Cortisol
Directory of Open Access Journals (Sweden)
Sarah A Boyle
Full Text Available Captive African (Loxodonta africana and Asian (Elephas maximus elephants can experience foot pathologies and arthritis. As a preventative measure against these pathologies and to alleviate the potential discomfort due to concrete substrates, some zoological institutions have renovated elephant housing to increase the amount of natural or shock-absorbent substrates. The objective of this study was to compare behavioral (diurnal and nocturnal and glucorticoid (e.g., serum cortisol responses of three female African elephants before, during, and after renovation to their indoor housing floor to assess whether renovations had short-term effects on the elephants' behavior and stress physiology. Behavioral data were collected using scan-sampling methods, and activity budgets were constructed for each of the three elephants. In addition, the duration of all lying rest activities were recorded. Weekly serum cortisol concentrations were determined with enzyme immunoassay (EIA. Overall, eating was the most prevalent behavior exhibited outdoors during the day, while resting (either in a lying or standing position were most common during the indoor, nocturnal periods. Although variation existed among the three elephants, all three females spent significantly more time walking and less time eating during the day after the completion of the renovations. The extent to which the three elephants exhibited nocturnal lying rest behavior varied among the elephants, with the oldest elephant exhibiting the least amount (an average of 13.2 ± 2.8% of the nightly behavioral scans compared to the two younger elephants (an average of 34.5 ± 2.1% and 56.6 ± 2.8% of the nightly behavioral scans. There was a significant increase in lying rest behavior for one elephant and standing rest for a second elephant following renovations. Baseline cortisol concentrations prior to renovations were 3.0 ± 0.4 ng/ml, 4.5 ± 0.5 ng/ml, and 4.9 ± 0.5 ng/ml for the three elephants
Analysis of piping system response to seismic excitations
International Nuclear Information System (INIS)
Wang, C.Y.
1987-01-01
This paper describes a numerical algorithm for analyzing piping system response to seismic excitations. The numerical model of the piping considers hoop, flexural, axial, and torsional modes of deformation. Hoop modes generated from internal hydrodynamic loading are superimposed on the bending and twisting modes by two extra degrees of freedom. A time-history analysis technique using the implicit temporal integration scheme is addressed. The time integrator uses a predictor-corrector successive iterative scheme which satisfies the equation of motion. Both geometrical and material nonlinearities are considered. Multiple support excitations, fluid effect, piping insulation, and material dampings can be included in the analysis. Two problems are presented to illustrate the method. The results are discussed in detail
Hydrodynamic response of viscous fluids under seismic excitation
International Nuclear Information System (INIS)
Ma, D.C.
1993-01-01
Hydrodynamic response of liquid-tank systems, such as reactor vessels, spent-fuel pools and liquid storage tanks have been studied extensively in the last decade (Chang et al. 1988; Ma et al. 1991). However, most of the studies are conducted with the assumption of an inviscid fluid. In recent years, the hydrodynamic response of viscous fluids has received increasing attention in high level waste storage tanks containing viscous waste material. This paper presents a numerical study on the hydrodynamic response of viscous fluids in a large 2-D fluid-tank system under seismic excitation. Hydrodynamic responses (i.e. sloshing wave height, fluid pressures, shear stress, etc.) are calculated for a fluid with various viscosities. Four fluid viscosities are considered. They are 1 cp, 120 cp, 1,000 cp and 12,000 cp (1 cp = 1.45 x 10 -7 lb-sec/in 2 ). Note that the liquid sodium of the Liquid-Metal Reactor (LMR) reactor has a viscosity of 1.38 x 10 -5 lb-sec/in 2 (about 95 cp) at an operational temperature of 900 degree F. Section 2 describes the pertinent features of the mathematical model. In Section 3, the fundamental sloshing phenomena of viscous fluid are examined. Sloshing wave height and shear stress for fluid with different viscosities are compared. The conclusions are given in Section 4
Soil-structure interaction effects on containment fragilities and floor response spectra statistics
International Nuclear Information System (INIS)
Pires, J.; Reich, M.; Chokshi, N.C.
1987-01-01
The probability-based method for the reliability evaluation of nuclear structures developed at Brookhaven National Laboratory (BNL) is extended to include soil-structure interaction effects. A reinforced concrete containment is analyzed in order to investigate the soil-structure interaction effects on: structural fragilities; floor response spectra statistics and acceleration response correlations. To include the effect of soil flexibility on the reliability assessment the following two step approach is used. In the first step, the lumped parameter method for soil-structure interaction analysis is used together with a stick model representation of the structure in order to obtain the motions of the foundation plate. These motions, which include both translations and rotations of the foundation plate, are expressed in terms of the power-spectral density of the free-field ground excitation and the transfer function of the total acceleration response of the foundation. The second step involves a detailed finite element model of the structure subjected to the interaction motions computed from step one. Making use of the structural model and interaction motion the reliability analysis method yields the limit stat probabilities and fragility data for the structure
Seismic analysis of nuclear piping system
International Nuclear Information System (INIS)
Shrivastava, S.K.; Pillai, K.R.V.; Nandakumar, S.
1975-01-01
To illustrate seismic analysis of nuclear power plant piping, a simple piping system running between two floors of the reactor building is assumed. Reactor building floor response is derived from time-history method. El Centre earthquake (1940) accelerogram is used for time-history analysis. The piping system is analysed as multimass lumped system. Behaviour of the pipe during the said earthquake is discussed. (author)
International Nuclear Information System (INIS)
Hilpert, H.J.
1987-01-01
In the general concept of the planned reprocessing plant for spent fuel elements, the main process building has the central function. This building will be designed to withstand earthquake, airplane crash and blast. This report deals with the stress on components and systems due to vibration of the building, the floor response spectra
Seismic Response of Low-Rise Masonry Buildings With Flexible Roof Diaphragms
National Research Council Canada - National Science Library
Cohen, Gregory
2001-01-01
This study compares the responses from shaking-table testing and analytical predictions evaluated in the context of geometric scaling, to provide a coherent description of the seismic response of low...
Advances in Rotational Seismic Measurements
Energy Technology Data Exchange (ETDEWEB)
Pierson, Robert [Applied Technology Associates, Albuquerque, NM (United States); Laughlin, Darren [Applied Technology Associates, Albuquerque, NM (United States); Brune, Robert [Applied Technology Associates, Albuquerque, NM (United States)
2016-10-19
Rotational motion is increasingly understood to be a significant part of seismic wave motion. Rotations can be important in earthquake strong motion and in Induced Seismicity Monitoring. Rotational seismic data can also enable shear selectivity and improve wavefield sampling for vertical geophones in 3D surveys, among other applications. However, sensor technology has been a limiting factor to date. The US Department of Energy (DOE) and Applied Technology Associates (ATA) are funding a multi-year project that is now entering Phase 2 to develop and deploy a new generation of rotational sensors for validation of rotational seismic applications. Initial focus is on induced seismicity monitoring, particularly for Enhanced Geothermal Systems (EGS) with fracturing. The sensors employ Magnetohydrodynamic (MHD) principles with broadband response, improved noise floors, robustness, and repeatability. This paper presents a summary of Phase 1 results and Phase 2 status.
International Nuclear Information System (INIS)
Jendrzejczyk, J.A.; Wambsganss, M.W.; Smith, R.K.; Rosas-Velez, P.
1993-08-01
To ensure successful operation of the APS, vibration of the storage ring quadrupole magnets must be limited to very low levels for frequencies >10 Hz. There will be many sources of vibration, such as pumps, fans, compressors, generators, and other rotating and reciprocating machinery when the APS is operational. In general, such vibration sources are isolated from the structural components and base foundations by vibration dampers and isolators. Pumps are typically mounted on seismic isolators, which are massive bases with response frequencies of <10 Hz, and fans are mounted with elastic-type isolators to minimize vibration coupling. The attenuation of expansion/isolation joints is a very important factor in predicting the response of the storage ring basemat to the various excitation sources. Several 75-hp pumps are located on the balcony of the rf extraction wing, which is close to the storage ring basemat. The pumps per se may prove to be a vibration excitation source of concern. Additional pumps will be placed in the RF extraction building and could add to the vibration levels. If the dynamic unbalance force of the pump motor, and the efficiency of the associated expansion joints were known, one could predict the response of the storage ring basemat. This information would also be useful in determining the placement of additional pumps. This report discusses vibration tests and measurements that were performed on July 28, 1993, in the rf extraction building. The purpose of the investigation was to study the efficiency of two specific expansion joints: (1) the joint that separates a structural column pad from the extraction wing floor, and (2) the joint that separates the extraction wing floor from the roof of the storage ring tunnel. A small electrodynamic exciter, with a maximum RMS force output of ∼0.5 lb at the frequencies of interest, was used
International Nuclear Information System (INIS)
Suzuki, K.; Sato, H.
1975-01-01
The power and the cross power spectrum analysis by which the vibration characteristic of structures, such as natural frequency, mode of vibration and damping ratio, can be identified would be effective for the confirmation of the characteristics after the construction is completed by using the response for small earthquakes or the micro-tremor under the operating condition. This method of analysis previously utilized only from the view point of systems with single input so far, is extensively applied for the analysis of a medium scale model of a piping system subjected to two seismic inputs. The piping system attached to a three storied concrete structure model which is constructed on a shaking table was excited due to earthquake motions. The inputs to the piping system were recorded at the second floor and the ceiling of the third floor where the system was attached to. The output, the response of the piping system, was instrumented at a middle point on the system. As a result, the multi-dimensional power spectrum analysis is effective for a more reliable identification of the vibration characteristics of the multi-input structure system
Seismic response of a sliding polar crane for a nuclear power plant
International Nuclear Information System (INIS)
Rieck, P.; Schlund, H.
1981-01-01
In the analysis, the bridge crane design is mathematically modeled in the vertical and lateral directions. The bridge crane system is postulated to vibrate in a linear-elastic fashion, until the dynamic reactions occurring at the crane wheel/support interface exceed the available resisting friction, at which time sliding is initiated. Sliding is postulated to continue until the relative velocity of the crane and supporting structure is zero, at which time a linear-elastic vibration mode is again developed. The analysis considers the variation in static and dynamic coefficients of friction and the variation of available friction resistance due to the crane vertical response. The initiation of sliding is modeled as an instantaneous event requiring a redescription of the crane system physical properties and coordinate system. Transfer from the vibrating system to the sliding system is governed by maintaining conservation of energy. Seismic excitation is defined using design floor response spectra appropriate for the crane system location. The design spectra are decomposed into a spectrum of acceleration time history harmonic motions which, when applied to a spectrum of single degree-of-freedom damped spring-mass oscillators, redevelops the original design spectra. The spectrum of acceleration times histories is used as base excitation to the mathematical model. Analytical results include sliding displacements and velocities, number of time sliding occurs, cumulative sliding displacements, and system kinetic and potential energy. A description of the crane system configuration and the development of the effective mass and stiffness values used in the analysis of the vibrating and sliding systems is presented. The equations of motions coupling the horizontal and vertical responses during the vibrating and sliding phases are presented. A discussion evaluating the applicability of the results, and how the results can be used for design, is also presented. (orig.)
Seismic response analysis with liquid-structure interaction
International Nuclear Information System (INIS)
Thomas, R.G.; Harrop, L.P.
1983-06-01
A linear transient finite element stress analysis of a water filled tank has been carried out using the proprietary computer code ANSYS. The containment structure was represented as rigidly fixed to ground. The flexibility of the tank wall was modelled together with the hydrostatic and hydrodynamic effects of the water contents and attached concentrated masses. The foundations were considered to be laid in solid rock, and no soil-structure interaction effects were included. The seismic input was a ground response spectrum conservatively representing both the Temblor and Parkfield modified time history records. It was found that the response of the structure was greatest at the front end (furthest from the point at which the tank is connected to a rigid internal structure), and that this was dominated by the fundamental mode. Higher modes are important at the back end. Buckling at the front end of the tank has been identified as a potential failure mechanism, and attention has also been called to the tensile capacity of the wall to base junction in this region. The requirement for a proper criterion against which to assess the margin against plastic collapse in a safe shutdown analysis has been noted. In certain regions the structure does not shake-down under the repeated reversed cyclic loading, and the need for an assessment of the implications of this for fatigue resistance has been indicated. (author)
Design of the Caltrans Seismic Response Modification Device (SRMD) test facility
International Nuclear Information System (INIS)
Benzoni, G.; Seible, F.
1998-01-01
In the Seismic retrofit design of California's Toll Bridges, seismic isolation is used in several bridges to limit the seismic force input into the superstructure and to avoid costly superstructure retrofit measures which would require partial lane closures and traffic interruptions. Isolation bearings and dampers of the size required for these large span bridges have not been built or tested to date. This paper describes the design and construction of a full scale testing facility which will allow the real-time 6-DOF dynamic characterization of the seismic response modification devices designed for California's Toll Bridges. (author)
International Nuclear Information System (INIS)
2016-07-01
The objective of this publication is to provide the state-of-the-art practice and detailed technical elements related to ground motion evaluation by ground motion prediction equations (GMPEs) and site response in the context of seismic hazard assessments as recommended in IAEA Safety Standards Series No. SSG-9, Seismic Hazards in Site Evaluation for Nuclear Installations. The publication includes the basics of GMPEs, ground motion simulation, selection and adjustment of GMPEs, site characterization, and modelling of site response in order to improve seismic hazard assessment. The text aims at delineating the most important aspects of these topics (including current practices, criticalities and open problems) within a coherent framework. In particular, attention has been devoted to filling conceptual gaps. It is written as a reference text for trained users who are responsible for planning preparatory seismic hazard analyses for siting of all nuclear installations and/or providing constraints for anti-seismic design and retrofitting of existing structures
Esposito, G.; Courage, W.
2003-01-01
This paper presents the results of a feasibility study of a seismic isolated 120.000 m^{3} LNG tank. A simple model was used to evaluate the seismic response of the isolated tank under Safe Shutdown Earthquake conditions. The frequency dependent dynamic stiffness of the foundation was
Directory of Open Access Journals (Sweden)
Patrícia Zaidan
Full Text Available Objective to investigate the response of the pelvic floor muscles (PFM, and urinary incontinence (UI, in patients having undergone a prostatectomy, after treatment using electrical stimulation. Materials and methods this observational study was conducted in an outpatient urogynecologic physical therapy clinic of Hospital dos Servidores in Rio de Janeiro, Brazil from August to September 2012. Ten patients (aged, 64 ± 7 years with urinary incontinence resulting from radical prostatectomy, having received surgery within six months of study entry, without urinary infection, and without metallic implants underwent electrical stimulation of the PFM, while in lateral decubitus position with knees and hips flexed. The parameters used were 65 Hz frequency, pulse width of 500 µs, biphasic current, intensity according to the tolerance level reported by the patient, perineal contraction time of four seconds, and rest time of eight seconds for 20 minutes twice a week, totaling 16 sessions of electrical stimulation with active-assisted contraction. Patients were evaluated before and after electrical stimulation through physical therapy evaluation of urinary incontinence, by being asked about the number of disposable guards used daily, using a visual analogue scale (VAS to measure how the UI interfered with activities of daily living, and by electromyographic biofeedback to measure the work of the PFM. Data were analyzed using Student’s paired t-tests and a significance level of 0.05. Results after 16 sessions of electrical stimulation, the electromyographic biofeedback evaluation showed a significant increase in muscle strength of 10.73 ± 8.64 to 17.16 ± 9.00 µV (t = -3.39, P = 0.008, a significant decrease in the number of diapers used before and after treatment (3.9 ± 1.2 to 1.8 ± 1.5, respectively; t = 5.16, P = 0.0006, and a significant decrease in the interference of urinary incontinence on daily activities of 9.6 ± 0.5 to 4.0 ± 3.8 (t = 5
Influence of epicentral distance on local seismic response in Kolkata ...
Indian Academy of Sciences (India)
Corresponding author. e-mail: wkmohanty@gg.iitkgp.ernet.in. The influence of source and .... specific or site-specific contribution to the ground motion amplitudes ...... Accounting for site effects in probabilistic seismic haz- ard analyses of ...
Numerical evaluation of seismic response of shallow foundation on ...
Indian Academy of Sciences (India)
Young's modulus of concrete ν. Poisson's ratio n. Porosity φ. Friction angle. C. Cohesion ..... which may occur due to plastic flow during seismic loading. Step 3. ... foundations, free-field boundary conditions in the ..... infinite media; J. Geotech.
Scaling laws for HTGR core block seismic response
International Nuclear Information System (INIS)
Dove, R.C.
1977-01-01
This paper discusses the development of scaling laws, physical modeling, and seismic testing of a model designed to represent a High Temperature Gas-Cooled Reactor (HTGR) core consisting of graphite blocks. The establishment of the proper scale relationships for length, time, force, and other parameters is emphasized. Tests to select model materials and the appropriate scales are described. Preliminary results obtained from both model and prototype systems tested under simulated seismic vibration are presented
Supporting shop floor intelligence
DEFF Research Database (Denmark)
Carstensen, Peter; Schmidt, Kjeld; Wiil, Uffe Kock
1999-01-01
Many manufacturing enterprises are now trying to introduce various forms of flexible work organizations on the shop floor. However, existing computer-based production planning and control systems pose severe obstacles for autonomous working groups and other kinds of shop floor control to become r......-to-day production planning by supporting intelligent and responsible workers in their situated coordination activities on the shop floor....
Seismic response of elastically restrained single bellows expansion joint in lateral mode
International Nuclear Information System (INIS)
Kameswara Rao, C.; Radhakrishna, M.
2003-01-01
The present paper attempts to derive an exact solution for the seismic response of U type of single bellows that are considered elastically restrained against rotation to classical fixed-fixed case considered by Morishita et al. (author)
Instantaneous response spectrum in seismic testing of nuclear power plant equipment
International Nuclear Information System (INIS)
Morrone, A.
1977-01-01
Seismic response spectra, as used in seismic analyses, give the maximum responses of single degree of freedom oscillators without consideration of the different time in the seismic time history at which each of the maximum responses occur. For response spectrum seismic analysis, the use of time-independent maximum responses is appropriate. The time dependece is considered in a statistical manner, for multi-degree of freedom systems, usually by combining the modal effects by the square root of the sum of the squares. For seismic testing of electrical equipment. IEEE Std. 344-1975 makes use of the response spectrum to define the input motion of the shake table. One of the basic requirements is that the test response spectrum (TRS) that is, the response spectrum produced by the shake table motion, should envelop the required response spectrum (RRS) calculated from the building analysis at the support point of the equipment being tested. This paper presents the concept of instantaneous response spectrum (IRS) as the response of single degree of freedom oscillators at a particular time. It demonstrates that a shake table random motion whose standard TRS envelops the RRS does not necessarily satisfy the enveloping requirement instantaneously. (Auth.)
Comparing Seismic And Magnetic Responses To Copper Gold Deposits Under Different Cover Sequences
Directory of Open Access Journals (Sweden)
Okan Evans Onojasun
2015-08-01
Full Text Available Appropriate application of geophysical techniques is required to effectively explore through the cover sequences that will allow the discovery of deep seated orebodies within the 1-3km depth range. Whilst potential field methods that are traditionally used for Cu-Au exploration seems effective they lack the expected resolution required to detect deeper mineral deposits under 500 m cover. Seismic reflection techniques offers a distinct advantage over all other geophysical techniques because of its ability to penetrate deeper into the subsurface without losing its resolution. We present in this report modelling results from magnetic and seismic responses to Cu-Au deposits when located within 100-1000m depth range. In the case of magnetic modelling we apply upward continuation filters which calculate the potential field that would have been recorded at 100m 250m 500m and 1000 m levels by filtering away shallow anomalies from the initial data. For seismic modelling simple but realistic geological model with varying cover thicknesses 100m 250m 500m and 1000m were created and then populate these models with petrophysical data. Simulated synthetic seismic responses from the models was processed using basic processing flows to obtained depth migrated images. Results show that for shower depths 0-100m good correlation exist between the magnetic and the seismic responses. From 100-250m depth cover though we can still see some magnetic anomalies within the target zone its effectiveness decreases with depths whereas seismic responses was maintain within the depth range. From 500m to 1000m magnetic response becomes spear or fuzzy as much useful information is practically missed out. Similarly high resolution power of seismic was ably demonstrated as the depth of even 2km did not degrade its resolution. Thus both magnetic and seismic methods are very useful for shallow investigation but at greater depth seismic method appears to be a more valid exploration
Scale model study of the seismic response of a nuclear reactor core
International Nuclear Information System (INIS)
Dove, R.C.; Dunwoody, W.E.; Rhorer, R.L.
1983-01-01
The use of scale models to study the dynamics of a system of graphite core blocks used in certain nuclear reactor designs is described. Scaling laws, material selecton, model instrumentation to measure collision forces, and the response of several models to simulated seismic excitation are covered. The effects of Coulomb friction between the blocks and the clearance gaps between the blocks on the system response to seismic excitation are emphasized
International Nuclear Information System (INIS)
Boaga, J; Vignoli, G; Cassiani, G
2011-01-01
Inversion is a critical step in all geophysical techniques, and is generally fraught with ill-posedness. In the case of seismic surface wave studies, the inverse problem can lead to different equivalent subsoil models and consequently to different local seismic response analyses. This can have a large impact on an earthquake engineering design. In this paper, we discuss the consequences of non-uniqueness of surface wave inversion on seismic responses, with both numerical and experimental data. Our goal is to evaluate the consequences on common seismic response analysis in the case of different impedance contrast conditions. We verify the implications of inversion uncertainty, and consequently of data information content, on realistic local site responses. A stochastic process is used to generate a set of 1D shear wave velocity profiles from several specific subsurface models. All these profiles are characterized as being equivalent, i.e. their responses, in terms of a dispersion curve, are compatible with the uncertainty in the same surface wave data. The generated 1D shear velocity models are then subjected to a conventional one-dimensional seismic ground response analysis using a realistic input motion. While recent analyses claim that the consequences of surface wave inversion uncertainties are very limited, our test points out that a relationship exists between inversion confidence and seismic responses in different subsoils. In the case of regular and relatively smooth increase of shear wave velocities with depth, as is usual in sedimentary plains, our results show that the choice of a specific model among equivalent solutions strongly influences the seismic response. On the other hand, when the shallow subsoil is characterized by a strong impedance contrast (thus revealing a characteristic soil resonance period), as is common in the presence of a shallow bedrock, equivalent solutions provide practically the same seismic amplification, especially in the
Directory of Open Access Journals (Sweden)
Clara Monaco
2016-09-01
Full Text Available Cetaceans use sound in many contexts, such as in social interactions, as well as to forage and to react in dangerous situations. Little information exists to describe how they respond physically and behaviorally to intense and long-term noise levels. Effects on cetaceans from seismic survey activities need to be understood in order to determine detailed acoustic exposure guidelines and to apply appropriated mitigation measures. This study examines direct behavioral responses of cetaceans in the southern Mediterranean Sea during seismic surveys with large airgun arrays (volume up to 5200 ci used in the TOMO-ETNA active seismic experiment of summer 2014. Wide Angle Seismic and Multi-Channel Seismic surveys had carried out with refraction and reflection seismic methods, producing about 25,800 air-gun shots. Visual monitoring undertaken in the 26 daylights of seismic exploration adopted the protocol of the Joint Nature Conservation Committee. Data recorded were analyzed to examine effects on cetaceans. Sighting rates, distance and orientation from the airguns were compared for different volume categories of the airgun arrays. Results show that cetaceans can be disturbed by seismic survey activities, especially during particularly events. Here we propose many integrated actions to further mitigate this exposure and implications for management.
Kim Ludovici; Robert Eaton; Stanley Zarnoch
2018-01-01
Removal of forest floor litter by pine needle raking and prescribed burning is a common practice in longleaf pine (Pinus palustris Mill.) stands on Coastal Plain sites in the Southeastern United States. Repeated removal of litter by raking and the loss of surface organic matter from controlled burns can affect the...
Changes in water table elevation at Yucca Mountain in response to seismic events
International Nuclear Information System (INIS)
Arnold, B.W.
1996-01-01
Investigation of mechanisms which could significantly alter the elevation of the water table at Yucca Mountain are motivated by the potential impacts such an occurrence would have on the performance of a high-level radioactive waste repository. In particular, we would like to evaluate the possibility of flooding a repository by water-table excursions. Changes in the water table could occur as relatively transient phenomena in response to seismic events by the seismic pumping mechanism. Quantitative evaluation of possible fluctuations of groundwater following earthquakes was undertaken in support of performance assessment calculations including seismicity
Seismic response of reinforced concrete frames at different damage levels
Morales-González, Merangeli; Vidot-Vega, Aidcer L.
2017-03-01
Performance-based seismic engineering is focused on the definition of limit states to represent different levels of damage, which can be described by material strains, drifts, displacements or even changes in dissipating properties and stiffness of the structure. This study presents a research plan to evaluate the behavior of reinforced concrete (RC) moment resistant frames at different performance levels established by the ASCE 41-06 seismic rehabilitation code. Sixteen RC plane moment frames with different span-to-depth ratios and three 3D RC frames were analyzed to evaluate their seismic behavior at different damage levels established by the ASCE 41-06. For each span-to-depth ratio, four different beam longitudinal reinforcement steel ratios were used that varied from 0.85 to 2.5% for the 2D frames. Nonlinear time history analyses of the frames were performed using scaled ground motions. The impact of different span-to-depth and reinforcement ratios on the damage levels was evaluated. Material strains, rotations and seismic hysteretic energy changes at different damage levels were studied.
Study of seismic responses of Candu-3 reactor building using isolator bearings
International Nuclear Information System (INIS)
Biswas, J.K.
1992-01-01
Seismic isolator bearings are known to increase reliability, reduce cost and increase the potential sitings for nuclear power plants located in regions of high seismicity. High seismic activities in Canada occur mainly in the western coast, the Grand Banks and regions of Quebec along the St. Lawrence river. In Canada, nuclear power plants are located in Ontario, Quebec and New Brunswick where the seismicity levels are low to moderate. Consequently, seismic isolator bearings have not been used in the existing nuclear power plants in Canada. The present paper examines the effect of using seismic isolator bearings in the design for the new CANDU3 which would be suitable for regions having high seismicity. The CANDU3 Nuclear Power Plant is rated at 450 MW of net output power and is a smaller version of its predecessor CANDU6 successfully operating in Canada and abroad. The design of CANDU3 is being developed by AECL CANDU. Advanced technologies for design, construction and plant operation have been utilized. During the conceptual development of the CANDU3 design, various design options including the use of isolator bearings were considered. The present paper presents an overview of seismic isolation technology and summarizes the analytical work for predicting the seismic behavior of the CANDU3 reactor building. A lumped-parameter dynamic model for the reactor building is used for the analysis. The characteristics of the bearings are utilized in the analysis work. The time-history modal analysis has been used to compute the seismic responses. Seismic responses of the reactor building with and without isolator bearings are compared. The isolator bearings are found to reduce the accelerations of the reactor building. As a result, a lower level of seismic qualification for components and systems would be required. The use of these bearings however increases rigid body seismic displacements of the structure requiring special considerations in the layout and interfaces for
Korhonen, H; Niemelä, P; Jauhiainen, L; Tupasela, T
Welfare-related physiological and behavioural responses were studied in farm-bred male blue foxes (Alopex lagopus). Three different-sized cages (80-cm long [CL80], 120-cm long [CL120], and 240-cm long [CL240]; each 105-cm wide x 70-cm high) with wire-mesh floors and one enlarged cage (CL240E) with both wire-mesh floor (240-cm long x 105-cm wide x 70-cm high) and earthen floor (80-cm long x 105-cm wide x 70-cm high) were compared. N = 30 males for each group. The experiments lasted from weaning in July to pelting in December. Statistical analyses were based on the models accounting for litter as a block effect. Breaking strength of tibia was highest for foxes having access to both wire-mesh and ground floors (CL240E). Stress-induced hyperthermia was evident during capture and immobilisation. The highest rectal temperature (mean +/- SEM) was found in CL240E (capture: 39.6 +/- 0.09 degrees C, restraint:40.0 +/- 0.09 degrees C) and the lowest in CL80 (capture: 39.1 +/- 0.09 degrees C, restraint: 39.7 +/- 0.09 degrees C). Likewise, capture time (median; interquartile range) in the home cage was highest in CL240E (29; 18 to 44) and lowest in CL80 (12; 9 to 14). During capture, foxes tended to withdraw to the farthest site within the cage. CL240E foxes typically showed the most fear towards human. The most confident animals were found in CL80. The cortisol:creatinine ratio (median; interquartile range) obtained from circadian urine did not reveal statistically significant differences among CL80 (3. 5; 2.6 to 4.1), CL120 (2.3; 1.5 to 3.8) and CL240 (2.3, 1.5 to 3.7). The earthen flooring complicated the urine sampling and conclusions for CL240E (1.7; 1.2 to 2.2). CL240E foxes were the most active and explorative on both wire-mesh- and ground-floored open-field arenas. Altogether, 53% of furs from CL240E were classified as very dirty. Dirtiness of furs in other test groups was slight. In conclusion, the present results did not reveal an unambiguous superiority of any of the
Seismic response and damping tests of small bore LMFBR piping and supports
International Nuclear Information System (INIS)
Barta, D.A.; Anderson, M.J.; Severud, L.K.; Lindquist, M.R.
1984-01-01
Seismic testing and analysis of a prototypical Liquid Metal Fast Breeder Reactor (LMFBR) small bore piping system is described. Measured responses to simulated seismic excitations are compared with analytical predictions based on NRC Regulatory Guide 1.61 and measured system damping values. The test specimen was representative of a typical LMFBR insulated small bore piping system, and it was supported from a rigid test frame by prototypic dead weight supports, mechanical snubbers and pipe clamps
Response of a Panel Building to Mining Induced Seismicity in Karvina Area (Czech Republic)
Czech Academy of Sciences Publication Activity Database
Hradil, P.; Kaláb, Zdeněk; Knejzlík, Jaromír; Kořínek, R.; Kanický, V.
2009-01-01
Roč. 14, č. 2 (2009), s. 143-151 ISSN 1335-1788 R&D Projects: GA ČR GA105/07/0878 Institutional research plan: CEZ:AV0Z30860518 Keywords : mining seismic ity * mathematical modeling * seismic response Subject RIV: DC - Siesmology, Volcanology, Earth Structure Impact factor: 0.097, year: 2009 http://actamont.tuke.sk/pdf/2009/n2/2hradil.pdf
Seismic response analyses of turbine hall and electrical building of RBMK-1000 MW type NPP
International Nuclear Information System (INIS)
Jordanov, M.J.; Karparov, K.T.
2003-01-01
This paper addresses results obtained during the study of turbine hall and electrical building of RBMK-1000 MW pair units at Leningradskaya NPP (LNPP) for seismic event. The study was performed in the frame of the Coordinated Research Program of the International Atomic Agency (IAEA) on Safety of RBMK type Nuclear Power Plants (NPP) in Relation of External Events. A 3-D finite element model of Main Building Complex was developed and seismic response analyses were performed taking into account the soil-structure interaction (SSI). The standard mode superposition method was used for evaluation of dynamic response of structure in time domain. The structure was assumed surface founded at the basemat level. Seismic response analyses were carried out considering shear wave propagation pattern for the input motion. The in-structure time histories and response spectra were generated in referenced locations. Conclusions are drawn for the reliability of the structural response evaluation considering the soil-structure interaction effects. (author)
Yilmaz, Zeynep
Typically, the vertical component of the ground motion is not considered explicitly in seismic design of bridges, but in some cases the vertical component can have a significant effect on the structural response. The key question of when the vertical component should be incorporated in design is answered by the probabilistic seismic hazard assessment study incorporating the probabilistic seismic demand models and ground motion models. Nonlinear simulation models with varying configurations of an existing bridge in California were considered in the analytical study. The simulation models were subjected to the set of selected ground motions in two stages: at first, only horizontal components of the motion were applied; while in the second stage the structures were subjected to both horizontal and vertical components applied simultaneously and the ground motions that produced the largest adverse effects on the bridge system were identified. Moment demand in the mid-span and at the support of the longitudinal girder and the axial force demand in the column are found to be significantly affected by the vertical excitations. These response parameters can be modeled using simple ground motion parameters such as horizontal spectral acceleration and vertical spectral acceleration within 5% to 30% error margin depending on the type of the parameter and the period of the structure. For a complete hazard assessment, both of these ground motion parameters explaining the structural behavior should also be modeled. For the horizontal spectral acceleration, Abrahamson and Silva (2008) model was used within many available standard model. A new NGA vertical ground motion model consistent with the horizontal model was constructed. These models are combined in a vector probabilistic seismic hazard analyses. Series of hazard curves developed and presented for different locations in Bay Area for soil site conditions to provide a roadmap for the prediction of these features for future
Statistical determination of significant curved I-girder bridge seismic response parameters
Seo, Junwon
2013-06-01
Curved steel bridges are commonly used at interchanges in transportation networks and more of these structures continue to be designed and built in the United States. Though the use of these bridges continues to increase in locations that experience high seismicity, the effects of curvature and other parameters on their seismic behaviors have been neglected in current risk assessment tools. These tools can evaluate the seismic vulnerability of a transportation network using fragility curves. One critical component of fragility curve development for curved steel bridges is the completion of sensitivity analyses that help identify influential parameters related to their seismic response. In this study, an accessible inventory of existing curved steel girder bridges located primarily in the Mid-Atlantic United States (MAUS) was used to establish statistical characteristics used as inputs for a seismic sensitivity study. Critical seismic response quantities were captured using 3D nonlinear finite element models. Influential parameters from these quantities were identified using statistical tools that incorporate experimental Plackett-Burman Design (PBD), which included Pareto optimal plots and prediction profiler techniques. The findings revealed that the potential variation in the influential parameters included number of spans, radius of curvature, maximum span length, girder spacing, and cross-frame spacing. These parameters showed varying levels of influence on the critical bridge response.
Salton Trough Post-seismic Afterslip, Viscoelastic Response, and Contribution to Regional Hazard
Parker, J. W.; Donnellan, A.; Lyzenga, G. A.
2012-12-01
The El Mayor-Cucapah M7.2 April 4 2010 earthquake in Baja California may have affected accumulated hazard to Southern California cities due to loading of regional faults including the Elsinore, San Jacinto and southern San Andreas, faults which already have over a century of tectonic loading. We examine changes observed via multiple seismic and geodetic techniques, including micro seismicity and proposed seismicity-based indicators of hazard, high-quality fault models, the Plate Boundary Observatory GNSS array (with 174 stations showing post-seismic transients with greater than 1 mm amplitude), and interferometric radar maps from UAVSAR (aircraft) flights, showing a network of aseismic fault slip events at distances up to 60 km from the end of the surface rupture. Finite element modeling is used to compute the expected coseismic motions at GPS stations with general agreement, including coseismic uplift at sites ~200 km north of the rupture. Postseismic response is also compared, with GNSS and also with the CIG software "RELAX." An initial examination of hazard is made comparing micro seismicity-based metrics, fault models, and changes to coulomb stress on nearby faults using the finite element model. Comparison of seismicity with interferograms and historic earthquakes show aseismic slip occurs on fault segments that have had earthquakes in the last 70 years, while other segments show no slip at the surface but do show high triggered seismicity. UAVSAR-based estimates of fault slip can be incorporated into the finite element model to correct Coloumb stress change.
Inertial Effects on Finite Length Pipe Seismic Response
Directory of Open Access Journals (Sweden)
Virginia Corrado
2012-01-01
Full Text Available A seismic analysis for soil-pipe interaction which accounts for length and constraining conditions at the ends of a continuous pipe is developed. The Winkler model is used to schematize the soil-structure interaction. The approach is focused on axial strains, since bending strains in a buried pipe due to the wave propagation are typically a second-order effect. Unlike many works, the inertial terms are considered in solving equations. Accurate numerical simulations are carried out to show the influence of pipe length and constraint conditions on the pipe seismic strain. The obtained results are compared with results inferred from other models present in the literature. For free-end pipelines, inertial effects have significant influence only for short length. On the contrary, their influence is always important for pinned pipes. Numerical simulations show that a simple rigid model can be used for free-end pipes, whereas pinned pipes need more accurate models.
Detailed comparison between computed and measured FBR core seismic responses
International Nuclear Information System (INIS)
Forni, M.; Martelli, A.; Melloni, R.; Bonacina, G.
1988-01-01
This paper presents a detailed comparison between seismic calculations and measurements performed for various mock-ups consisting of groups of seven and nineteen simplified elements of the Italian PEC fast reactor core. Experimental tests had been performed on shaking tables in air and water (simulating sodium) with excitations increasing up to above Safe Shutdown Earthquake. The PEC core-restraint ring had been simulated in some tests. All the experimental tests have been analysed by use of both the one-dimensional computer program CORALIE and the two-dimensional program CLASH. Comparisons have been made for all the instrumented elements, in both the time and the frequency domains. The good agreement between calculations and measurements has confirmed adequacy of the fluid-structure interaction model used for PEC core seismic design verification
Huerta, F. V.; Granados, I.; Aguirre, J.; Carrera, R. Á.
2017-12-01
Nowadays, in hydrocarbon industry, there is a need to optimize and reduce exploration costs in the different types of reservoirs, motivating the community specialized in the search and development of alternative exploration geophysical methods. This study show the reflection response obtained from a shale gas / oil deposit through the method of seismic interferometry of ambient vibrations in combination with Wavelet analysis and conventional seismic reflection techniques (CMP & NMO). The method is to generate seismic responses from virtual sources through the process of cross-correlation of records of Ambient Seismic Vibrations (ASV), collected in different receivers. The seismic response obtained is interpreted as the response that would be measured in one of the receivers considering a virtual source in the other. The acquisition of ASV records was performed in northern of Mexico through semi-rectangular arrays of multi-component geophones with instrumental response of 10 Hz. The in-line distance between geophones was 40 m while in cross-line was 280 m, the sampling used during the data collection was 2 ms and the total duration of the records was 6 hours. The results show the reflection response of two lines in the in-line direction and two in the cross-line direction for which the continuity of coherent events have been identified and interpreted as reflectors. There is certainty that the events identified correspond to reflections because the time-frequency analysis performed with the Wavelet Transform has allowed to identify the frequency band in which there are body waves. On the other hand, the CMP and NMO techniques have allowed to emphasize and correct the reflection response obtained during the correlation processes in the frequency band of interest. The results of the processing and analysis of ASV records through the seismic interferometry method have allowed us to see interesting results in light of the cross-correlation process in combination with
Shaking table test study on seismic performance of dehydrogenation fan for nuclear power plants
International Nuclear Information System (INIS)
Liu Kaiyan; Shi Weixing; Cao Jialiang; Wang Yang
2011-01-01
Seismic performance of the dehydrogenation fan for nuclear power plants was evaluated based on the shaking table test of earthquake simulation. Dynamic characteristics including the orthogonal tri-axial fundamental frequencies and equivalent damping ratios were measured by the white noise scanning method. Artificial seismic waves were generated corresponding to the floor acceleration response spectra for nuclear power plants. Furthermore, five OBE and one SSE shaking table tests for dehydrogenation fan were performed by using the artificial seismic waves as the seismic inputs along the orthogonal axis simultaneity. Operating function of dehydrogenation fan was monitored and observed during all seismic tests, and performance indexes of dehydrogenation fan were compared before and after seismic tests. The results show that the structural integrity and operating function of the dehydrogenation fan are perfect during all seismic tests; and the performance indexes of the dehydrogenation fan can remain consistent before and after seismic tests; the seismic performance of the dehydrogenation fan can satisfy relevant technical requirements. (authors)
International Nuclear Information System (INIS)
Park, Jinkyun; Kin, Yochan; Jung, Wondea; Jang, Seung Cheol
2014-01-01
This is because the PSA has been used for several decades as the representative tool to evaluate the safety of NPPs. To this end, it is inevitable to evaluate human error probabilities (HEPs) in conducting important tasks being considered in the PSA framework (i.e., HFEs; human failure events), which are able to significantly affect the safety of NPPs. In addition, it should be emphasized that the provision of a realistic human performance data is an important precondition for calculating HEPs under a seismic condition. Unfortunately, it seems that HRA methods being currently used for calculating HEPs under a seismic event do not properly consider the performance variation of human operators. For this reason, in this paper, a framework to estimate response time data that are critical for calculating HEPs is suggested with respect to a seismic intensity. This paper suggested a systematic framework for estimating response time data that would be one of the most critical for calculating HEPs. Although extensive review of existing literatures is indispensable for identifying response times of human operators who have to conduct a series of tasks prescribed in procedures based on a couple of wrong indications, it is highly expected that response time data for seismic HRA can be properly secured through revisiting response time data collected from diverse situations without concerning a seismic event
Use of a viscoelastic model for the seismic response of base-isolated buildings
International Nuclear Information System (INIS)
Uras, R.A.
1994-01-01
Due to recent developments in elastomer technology, seismic isolation using elastomer bearings is rapidly becoming an acceptable design tool to enhance structural seismic margins and to protect people and equipment from earthquake damage. With proper design of isolators, high-energy seismic input motions are transformed into low-frequency, low energy harmonic motions and the accelerations acting on the isolated building are significantly reduced. Several alternatives exist for the modeling of the isolators. This study is concerned with the use of a viscoelastic model to predict the seismic response of base-isolated buildings. The in-house finite element computer code has been modified to incorporate a viscoelastic spring element, and several simulations are performed. Then, the computed results have been compared with the corresponding observed data recorded at the test facility
State-of-the-art of development of floor spectra
International Nuclear Information System (INIS)
Singh, M.P.
1984-01-01
Floor spectra are used as seismic inputs for the design and qualification of subsystems and equipment. Until very recently, the time history analyses with single acceleration time history as input were very commonly used. However, this approach has been observed to give nonunique floor spectrum curves. Thus, as alternatives several direct approaches have been developed. The approaches which are based on the random vibration principles but employ response spectra directly have more rational appeal. Several such approaches are available. Four different approaches, employing the mode displacement and mode acceleration formulations, covering the proportionally as well as nonproportionally damped structures, are presented. The mode displacement formulations are most commonly used, although the mode acceleration formulations seem to be the better alternatives, both for the proportionally and nonproportionally damped structures. The need for the development of other forms of floor response spectra such as the relative velocity and relative acceleration spectra is also identified
Seismic response analysis of the deep saturated soil deposits in Shanghai
Huang, Yu; Ye, Weimin; Chen, Zhuchang
2009-01-01
The quaternary deposits in Shanghai are horizontal soil layers of thickness up to about 280 m in the urban area with an annual groundwater table between 0.5 and 0.7 m from the surface. The characteristics of deep saturated deposits may have important influences upon seismic response of the ground in Shanghai. Based on the Biot theory for porous media, the water-saturated soil deposits are modeled as a two-phase porous system consisting of solid and fluid phases, in this paper. A nonlinear constitutive model for predicting the seismic response of the ground is developed to describe the dynamic characters of the deep-saturated soil deposits in Shanghai. Subsequently, the seismic response of a typical site with 280 m deep soil layers, which is subjected to four base excitations (El Centro, Taft, Sunan, and Tangshan earthquakes), is analyzed in terms of an effective stress-based finite element method with the proposed constitutive model. Special emphasis is given to the computed results of accelerations, excess pore-water pressures, and settlements during the seismic excitations. It has been found that the analysis can capture fundamental aspects of the ground response and produce preliminary results for seismic assessment.
International Nuclear Information System (INIS)
Stevenson, J.D.
2003-01-01
The following topics are described and discussed: Historical development of NPP seismic design requirements: Peak ground acceleration; Response spectra and damping; Floor or amplified response spectra; Effective high frequency response spectra; Seismic modeling procedures; Impact on cost (site preparation and foundations; site seismic response and generation of site dependent spectra). Potential use of indirect earthquake experience data in design and construction of NPP. Seismic contribution to safety. The following facts are summarized in two Appendices: Seismic intensity scales, and GRS safety codes and guides. (P.A.)
Response spectrum analysis of coupled structural response to a three component seismic disturbance
International Nuclear Information System (INIS)
Boulet, J.A.M.; Carley, T.G.
1977-01-01
The work discussed herein is a comparison and evaluation of several response spectrum analysis (RSA) techniques as applied to the same structural model with seismic excitation having three spatial components. Lagrange's equations of motion for the system were written in matrix form and uncoupled with the modal matrix. Numerical integration (fourth order Runge-Kutta) of the resulting model equations produced time histories of system displacements in response to simultaneous application of three orthogonal components of ground motion, and displacement response spectra for each modal coordinate in response to each of the three ground motion components. Five different RSA techniques were used to combine the spectral displacements and the modal matrix to give approximations of maximum system displacements. These approximations were then compared with the maximum system displacements taken from the time histories. The RSA techniques used are the method of absolute sums, the square root of the sum of the squares, the double sum approach, the method of closely spaced modes, and Lin's method. The vectors of maximum system displacements as computed by the time history analysis and the five response spectrum analysis methods are presented. (Auth.)
International Nuclear Information System (INIS)
Oluwasusi, A. B.; Hussey, V.; Goulding, F. J.
2002-01-01
The Oso Field (OML 70) produces approximately 100 TBD of condensate from Miocene age shelfal sand reservoirs at approximately 10,000 feet below sea level. The field was discovered in 1967 while testing a deeply buried fault closure. Reservoirs are normally pressured, exceed 1 Darcy in permeability and range from 50 to 600 feet in thickness.There are seismic amplitudes associated with the shallower reservoirs on the existing conventional 3D dataset; however there are no anomalies associated with the deeper, condensate accumulations.The paper explores the physical rock and fluid properties associated with the Oso reservoirs and the resulting seismic responses. Modelled results have been calibrated with the actual seismic signatures for the water and hydrocarbon bearing zones. Results indicate that the deeper reservoirs exhibit a classic Class II AVG seismic response and that the use of longer offset and angle stack data can help predict the occurrence of these types of reservoirs. Examples of similar accumulations will be shared.Mobil Producing Nigeria is conducting a full reprocessing effort of the existing 3D dataset over the Joint Venture acreage with a goal of identifying and exploiting additional accumulations with Class II AVG seismic response. Preliminary results of the reprocessing over known accumulations will be presented
Seismic response of a nonsymmetric nuclear reactor building with a flexible stepped foundation
International Nuclear Information System (INIS)
Okano, H.; Sakai, A.; Takita, H.; Fukunishi, S.; Nakatogawa, T.; Kabayama, K.
1993-01-01
The effect of the non symmetry of a nuclear reactor building on its seismic response was studied. The nonsymmetric natures we considered, Included the eccentricity of the superstructure and the non symmetry of the cross section of the foundation. A three-dimensional analysis which employed Green's function was applied to study the interaction between the soil and the non symmetrically sectioned foundation. The effect of a flexible foundation on its seismic response was also studied by applying the sub structuring method, which combines the finite element method and Green's function method. (author)
Seismic response analysis of structural system subjected to multiple support excitation
International Nuclear Information System (INIS)
Wu, R.W.; Hussain, F.A.; Liu, L.K.
1978-01-01
In the seismic analysis of a multiply supported structural system subjected to nonuniform excitations at each support point, the single response spectrum, the time history, and the multiple response spectrum are the three commonly employed methods. In the present paper the three methods are developed, evaluated, and the limitations and advantages of each method assessed. A numerical example has been carried out for a typical piping system. Considerably smaller responses have been predicted by the time history method than that by the single response spectrum method. This is mainly due to the fact that the phase and amplitude relations between the support excitations are faithfully retained in the time history method. The multiple response spectrum prediction has been observed to compare favourably with the time history method prediction. Based on the present evaluation, the multiple response spectrum method is the most efficient method for seismic response analysis of structural systems subjected to multiple support excitation. (Auth.)
International Nuclear Information System (INIS)
DeGrassi, G.
1992-10-01
This report presents the results of a literature review on spent fuel rack seismic analysis methods and modeling procedures. The analysis of the current generation of free standing high density spent fuel racks requires careful consideration of complex phenomena such as rigid body sliding and tilting motions; impacts between adjacent racks, between fuel assemblies and racks, and between racks and pool walls and floor; fluid coupling and frictional effects. The complexity of the potential seismic response of these systems raises questions regarding the levels of uncertainty and ranges of validity of the analytical results. BNL has undertaken a program to investigate and assess the strengths and weaknesses of current fuel rack seismic analysis methods. The first phase of this program involved a review of technical literature to identify the extent of experimental and analytical verification of the analysis methods and assumptions. Numerous papers describing analysis methods for free standing fuel racks were reviewed. However, the extent of experimental verification of these methods was found to be limited. Based on the information obtained from the literature review, the report provides an assessment of the significance of the issues of concern and makes recommendations for additional studies
Directory of Open Access Journals (Sweden)
Jong Wan Hu
2014-12-01
Full Text Available Base isolation has been used as one of the most wildly accepted seismic protection systems that should substantially dissociate a superstructure from its substructure resting on a shaking ground, thereby sustainably preserving entire structures against earthquake forces as well as inside non-structural integrities. Base isolation devices can operate very effectively against near-fault (NF ground motions with large velocity pulses and permanent ground displacements. In this study, comparative advantages for using lead-rubber bearing (LRB isolation systems are mainly investigated by performing nonlinear dynamic time-history analyses with NF ground motions. The seismic responses with respects to base shears and inter-story drifts are compared according to the installation of LRB isolation systems in the frame building. The main function of the base LRB isolator is to extend the period of structural vibration by increasing lateral flexibility in the frame structure, and thus ground accelerations transferred into the superstructure can dramatically decrease. Therefore, these base isolation systems are able to achieve notable mitigation in the base shear. In addition, they make a significant contribution to reducing inter-story drifts distributed over the upper floors. Finally, the fact that seismic performance can be improved by installing isolation devices in the frame structure is emphasized herein through the results of nonlinear dynamic analyses.
Seismic response analysis of column supported natural draught cooling tower shells
International Nuclear Information System (INIS)
Ramanjaneyulu, K.; Gopalakrishnan, S.; Appa Rao, T.V.S.R.
2003-01-01
Natural draught cooling towers (NDCTs) belong to the category of large civil engineering structures and are commonly used in nuclear or thermal power plants. Detailed dynamic analysis has to be carried out for design of cooling towers subjected to seismic excitation, considering the flexibility of the columns. Finite ring element formulations for dynamic analysis of cooling tower shell subjected to seismic excitation are presented in this paper. The geometry of a typical tall natural draught cooling tower is considered in this study for carrying out investigations. Transient response of the hyperbolic cooling tower shell subjected to earthquake loading has been analysed by direct time integration using acceleration-time history of North-South component of El-Centro earthquake. Parametric studies have also been carried out to study the influence of flexibility of column supports and damping on the seismic response of cooling tower shell and the results are discussed in the paper. (author)
Effect of soil-foundation-structure interaction on the seismic response of wind turbines
Directory of Open Access Journals (Sweden)
Sam Austin
2017-09-01
Full Text Available Soil-foundation-structure interaction can affect the seismic response of wind turbines. This paper studies the effects of soil-foundation-structure interaction on the seismic response of 65 kW, 1 MW, and 2 MW horizontal-axis wind turbines with truncated cone steel towers. Four types of foundations with frequency-based design were analyzed, including spread foundation, mono pile, pile group with cap, and anchored spread foundation. Soil is modeled both implicitly (subgrade reaction modulus and explicitly. The finite element model developed using the ANSYS program was first validated using experimental data. Numerical models are then analyzed in both frequency and time domains using the Block Lanczos and generalized HHT-α formulations. Recommendations were given to simplify the soil-foundation-structure interaction analysis of wind turbines subjected to seismic loading.
International Nuclear Information System (INIS)
Kokusho, T.; Nishi, K.; Okamoto, T.; Tanaka, Y.; Ueshima, T.; Kudo, K.; Kataoka, T.; Ikemi, M.; Kawai, T.; Sawada, Y.; Suzuki, K.; Yajima, K.; Higashi, S.
1997-01-01
An international joint research program called HLSST is proceeding. HLSST is large-scale seismic test (LSST) to investigate soil-structure interaction (SSI) during large earthquake in the field in Hualien, a high seismic region in Taiwan. A 1/4-scale model building was constructed on the gravelly soil in this site, and the backfill material of crushed stone was placed around the model plant after excavation for the construction. Also the model building and the foundation ground were extensively instrumental to monitor structure and ground response. To accurately evaluate SSI during earthquakes, geotechnical investigation and forced vibration test were performed during construction process namely before/after base excavation, after structure construction and after backfilling. And the distribution of the mechanical properties of the gravelly soil and the backfill are measured after the completion of the construction by penetration test and PS-logging etc. This paper describes the distribution and the change of the shear wave velocity (V s ) measured by the field test. Discussion is made on the effect of overburden pressure during the construction process on V s in the neighbouring soil and, further on the numerical soil model for SSI analysis. (orig.)
PSMG switchgear seismic analysis
International Nuclear Information System (INIS)
Kuehster, C.J.
1977-01-01
LOFT primary coolant system motor generator (PSMG) switchgear boxes were analyzed for sliding and overturning during a seismic event. Boxes are located in TAN-650, Room B-239, with the PSMG generators. Both boxes are sufficiently anchored to the floor
Directory of Open Access Journals (Sweden)
Arash Behnia
Full Text Available Light weight and long span composite floors are common place in modern construction. A critical consequence of this application is undesired vibration which may cause excessive discomfort to occupants. This work investigates the composite floor vibration behavior of an existing building based on a comprehensive study of high modal dynamic responses, the range of which has been absent in previous studies and major analytical templates, of different panels under the influence of loads induced by human motion. The resulting fundamental natural frequency and vibration modes are first validated with respect to experimental and numerical evidences from literature. Departing from close correlation established in comparison, this study explores in detail the effects of intensity of passive live load as additional stationary mass due to crowd jumping as well as considering human structure interaction. From observation, a new approach in the simulation of passive live load through the consideration of human structure interaction and human body characteristics is proposed. It is concluded that higher vibration modes are essential to determine the minimum required modes and mass participation ratio in the case of vertical vibration. The results indicate the need to consider 30 modes of vibration to obtain all possible important excitations and thereby making third harmonic of load frequency available to excite the critical modes. In addition, presence of different intensities of passive live load on the composite floor showed completely different behavior in each particular panel associated with load location of panel and passive live load intensity. Furthermore, implementing human body characteristics in simulation causes an obvious increase in modal damping and hence better practicality and economical presentation can be achieved in structural dynamic behavior.
Earthquake Ground Motion Measures for Seismic Response Evaluation of Structures
Energy Technology Data Exchange (ETDEWEB)
Cho, In-Kil; Ahn, Seong-Moon; Choun, Young-Sun; Seo, Jeong-Moon
2007-03-15
This study used the assessment results of failure criteria - base shear, story drift, top acceleration and top displacement - for a PSC containment building subjected to 30 sets of near-fault ground motions to evaluate the earthquake ground motion intensity measures. Seven intensity measures, peak ground acceleration(PGA), peak ground velocity(PGV), spectral acceleration(Sa), velocity(Sv), spectrum intensity for acceleration(SIa), velocity(SIv) and displacement(SId), were used to represent alternative ground motion. The regression analyses of the failure criteria for a PSC containment building were carried out to evaluate a proper intensity measure by using two regression models and seven ground motion parameters. The regression analysis results demonstrate the correlation coefficients of the failure criteria in terms of the candidate IM. From the results, spectral acceleration(Sa) is estimated as the best parameter for a evaluation of the structural safety for a seismic PSA.
Response of Radon in a seismic calibration explosion, Israel
International Nuclear Information System (INIS)
Zafrir, H.; Steinitz, G.; Malik, U.; Haquin, G.; Gazit-Yaari, N.
2009-01-01
Radon measurements were performed at shallow levels during an in-land 20-ton seismic calibration explosion experiment, simulating a 2.6-M L earthquake, to investigate the influence of the explosive blast and the transitory seismic wave fields on the Radon transport in the country rock, adjacent to the focus of the explosion. The experiment was conducted in a basalt quarry in the northern margin of the Beit Shean valley (Israel). Five gamma-ray sensors were placed, at a depth of about 2 m, along a line located 17-150 m from the edge of the explosion zone. Measurements commenced 4 days before and continued for 9 days after the explosion with 15 min integrations. A 10-s sampling was used in the interval of several hours before and after the explosion itself. Diurnal variations of Radon, reflecting the typical variation pattern of Radon in the shallow environment, were registered before and after the explosion. No significant change in the overall Radon concentration was observed as a consequence of the main explosion as well as three smaller experimental shots (0.5-2 tons) in the 2 h prior to the calibration blast. The seismological data indicate that the transient excess pressure at the farthest Radon sensor was above 5 bar m -1 during 0.2-0.4 s, and evidently much higher at the nearest sensors, but none of the sensors responded by recording any exceptional change in the Radon concentration. Moreover the hypothesis that additional Radon may emanate from solid grains as a result of the excess local pressure exerted by the blast is also not observed. In contrast to a real earthquake event an explosion experiment has neither eventual preceding nor following geodynamic activity. Therefore the absence of significant Radon anomalies during or after the blast does not contradict assumptions, observations or conclusions as the occurrence of Radon anomalies prior or after an earthquake event due to associated long-term geodynamic processes.
Seismic response analysis of Wolsung NPP structure and equipment subjected to scenario earthquakes
Energy Technology Data Exchange (ETDEWEB)
Choi, In Kil; Ahn, Seong Moon; Choun, Young Sun; Seo, Jeong Moon
2005-03-15
The standard response spectrum proposed by US NRC has been used as a design earthquake for the design of Korean nuclear power plant structures. However, it does not reflect the characteristic of seismological and geological of Korea. In this study, the seismic response analysis of Wolsung NPP structure and equipment were performed. Three types of input motions, artificial time histories that envelop the US NRC Regulatory Guide 1.60 spectrum and the probability based scenario earthquake spectra developed for the Korean NPP site and a typical near-fault earthquake recorded at thirty sites, were used as input motions. The acceleration, displacement and shear force responses of Wolsung containment structure due to the design earthquake were larger than those due to the other input earthquakes. But, considering displacement response increases abruptly as Wolsung NPP structure does nonlinear behavior, the reassessment of the seismic safety margin based on the displacement is necessary if the structure does nonlinear behavior; although it has adequate the seismic safety margin within elastic limit. Among the main safety-related devices, electrical cabinet and pump showed the large responses on the scenario earthquake which has the high frequency characteristic. This has great effects of the seismic capacity of the main devices installed inside of the building. This means that the design earthquake is not so conservative for the safety of the safety related nuclear power plant equipments.
Seismic response analysis of Wolsung NPP structure and equipment subjected to scenario earthquakes
International Nuclear Information System (INIS)
Choi, In Kil; Ahn, Seong Moon; Choun, Young Sun; Seo, Jeong Moon
2005-03-01
The standard response spectrum proposed by US NRC has been used as a design earthquake for the design of Korean nuclear power plant structures. However, it does not reflect the characteristic of seismological and geological of Korea. In this study, the seismic response analysis of Wolsung NPP structure and equipment were performed. Three types of input motions, artificial time histories that envelop the US NRC Regulatory Guide 1.60 spectrum and the probability based scenario earthquake spectra developed for the Korean NPP site and a typical near-fault earthquake recorded at thirty sites, were used as input motions. The acceleration, displacement and shear force responses of Wolsung containment structure due to the design earthquake were larger than those due to the other input earthquakes. But, considering displacement response increases abruptly as Wolsung NPP structure does nonlinear behavior, the reassessment of the seismic safety margin based on the displacement is necessary if the structure does nonlinear behavior; although it has adequate the seismic safety margin within elastic limit. Among the main safety-related devices, electrical cabinet and pump showed the large responses on the scenario earthquake which has the high frequency characteristic. This has great effects of the seismic capacity of the main devices installed inside of the building. This means that the design earthquake is not so conservative for the safety of the safety related nuclear power plant equipments
Evaluation of response factors for seismic probabilistic safety assessment of nuclear power plants
International Nuclear Information System (INIS)
Ebisawa, K.; Abe, K.; Muramatsu, K.; Itoh, M.; Kohno, K.; Tanaka, T.
1994-01-01
This paper presents a method for evaluating 'response factors' of components in nuclear power plants for use in a seismic probabilistic safety assessment (PSA). The response factor here is a measure of conservatism included in response calculations in seismic design analysis of components and is defined as a ratio of conservative design resonse to actual response. This method has the following characteristic features: (1) The components are classified into several groups based on the differences in their location and in the vibration models used in design response analyses; (2) the response factors are decomposed into subfactors corresponding to the stages of the seismic response analyses in the design practices; (3) the response factors for components are calculated as products of subfactors; (4) the subfactors are expressed either as a single value or as a function of parameters that influence the response of components. This paper describes the outline of this method and results from an application to a sample problem in which response factors were quantified for examples of components selected from the groups. (orig.)
Seismic response of three-dimensional rockfill dams using the Indirect Boundary Element Method
International Nuclear Information System (INIS)
Sanchez-Sesma, Francisco J; Arellano-Guzman, Mauricio; Perez-Gavilan, Juan J; Suarez, Martha; Marengo-Mogollon, Humberto; Chaillat, Stephanie; Jaramillo, Juan Diego; Gomez, Juan; Iturraran-Viveros, Ursula; Rodriguez-Castellanos, Alejandro
2010-01-01
The Indirect Boundary Element Method (IBEM) is used to compute the seismic response of a three-dimensional rockfill dam model. The IBEM is based on a single layer integral representation of elastic fields in terms of the full-space Green function, or fundamental solution of the equations of dynamic elasticity, and the associated force densities along the boundaries. The method has been applied to simulate the ground motion in several configurations of surface geology. Moreover, the IBEM has been used as benchmark to test other procedures. We compute the seismic response of a three-dimensional rockfill dam model placed within a canyon that constitutes an irregularity on the surface of an elastic half-space. The rockfill is also assumed elastic with hysteretic damping to account for energy dissipation. Various types of incident waves are considered to analyze the physical characteristics of the response: symmetries, amplifications, impulse response and the like. Computations are performed in the frequency domain and lead to time response using Fourier analysis. In the present implementation a symmetrical model is used to test symmetries. The boundaries of each region are discretized into boundary elements whose size depends on the shortest wavelength, typically, six boundary segments per wavelength. Usually, the seismic response of rockfill dams is simulated using either finite elements (FEM) or finite differences (FDM). In most applications, commercial tools that combine features of these methods are used to assess the seismic response of the system for a given motion at the base of model. However, in order to consider realistic excitation of seismic waves with different incidence angles and azimuth we explore the IBEM.
Wang, W; Erf, G F; Wideman, R F
2002-11-01
Intravenous endotoxin has been shown to trigger a delayed pulmonary hypertensive response that varies widely in magnitude and duration among individual broilers. It was proposed that this individual variability may reflect immunological differences acquired during previous respiratory challenges that might have subsequently altered the endotoxin-initiated biochemical cascade. In Experiment 1, we tested the hypothesis that, when compared with broilers reared in clean stainless steel cages (Cage group), broilers reared on floor litter (Floor group) should experience a greater respiratory challenge and therefore may consistently exhibit a more enhanced pulmonary hypertensive response to intravenous endotoxin. Birds in the Cage group were grown in stainless steel cages at a low density (72 birds/8 m2 chamber), and fecal and dander materials were removed daily. Birds in the Floor group were reared on wood-shavings litter at a higher density (110 birds/8 m2 chamber). Pulmonary and systemic mean arterial pressures and blood-gas values were evaluated prior to and following the intravenous administration of 1 mg Salmonella typhimurium endotoxin. Broilers in the Floor and Cage groups exhibited pulmonary hypertensive responses to endotoxin that were very similar in terms of time of onset, duration, and magnitude, as well as variability in the response among individuals. Systemic hypotension also developed similarly in both groups following endotoxin injection. Blood-gas values indicated that the partial pressure of CO2 and the HCO3- concentration in arterial blood were higher (P broilers, and confirmed the negative impact of floor rearing on blood-gas values. We conclude that broilers reared on the floor inhaled litter dust and noxious fumes, which impaired pulmonary gas exchange and increased the arterial partial pressure of CO2 when compared with broilers reared in clean stainless steel cages. Nevertheless, the pulmonary hypertensive response to endotoxin did not differ
Liang, Fayun; Chen, Haibing; Huang, Maosong
2017-07-01
To provide appropriate uses of nonlinear ground response analysis for engineering practice, a three-dimensional soil column with a distributed mass system and a time domain numerical analysis were implemented on the OpenSees simulation platform. The standard mesh of a three-dimensional soil column was suggested to be satisfied with the specified maximum frequency. The layered soil column was divided into multiple sub-soils with a different viscous damping matrix according to the shear velocities as the soil properties were significantly different. It was necessary to use a combination of other one-dimensional or three-dimensional nonlinear seismic ground analysis programs to confirm the applicability of nonlinear seismic ground motion response analysis procedures in soft soil or for strong earthquakes. The accuracy of the three-dimensional soil column finite element method was verified by dynamic centrifuge model testing under different peak accelerations of the earthquake. As a result, nonlinear seismic ground motion response analysis procedures were improved in this study. The accuracy and efficiency of the three-dimensional seismic ground response analysis can be adapted to the requirements of engineering practice.
Incremental-hinge piping analysis methods for inelastic seismic response prediction
International Nuclear Information System (INIS)
Jaquay, K.R.; Castle, W.R.; Larson, J.E.
1989-01-01
This paper proposes nonlinear seismic response prediction methods for nuclear piping systems based on simplified plastic hinge analyses. The simplified plastic hinge analyses utilize an incremental series of flat response spectrum loadings and replace yielded components with hinge elements when a predefined hinge moment is reached. These hinge moment values, developed by Rodabaugh, result in inelastic energy dissipation of the same magnitude as observed in seismic tests of piping components. Two definitions of design level equivalent loads are employed: one conservatively based on the peaks of the design acceleration response spectra, the other based on inelastic frequencies determined by the method of Krylov and Bogolyuboff recently extended by Lazzeri to piping. Both definitions account for piping system inelastic energy dissipation using Newmark-Hall inelastic response spectrum reduction factors and the displacement ductility results of the incremental-hinge analysis. Two ratchet-fatigue damage models are used: one developed by Rodabaugh that conservatively correlates Markl static fatigue expressions to seismic tests to failure of piping components; the other developed by Severud that uses the ratchet expression of Bree for elbows and Edmunds and Beer for straights, and defines ratchet-fatigue interaction using Coffin's ductility based fatigue equation. Comparisons of predicted behavior versus experimental results are provided for a high-level seismic test of a segment of a representative nuclear plant piping system. (orig.)
Seismic Responses of a Cable-Stayed Bridge with Consideration of Uniform Temperature Load
Directory of Open Access Journals (Sweden)
Junjun Guo
2016-12-01
Full Text Available The effects of temperature load on the dynamic responses of cable-stayed bridges have attracted the attention of researchers in recent years. However, these investigations mainly focus on the influence of temperature on the dynamic characteristics of structures, such as vibration mode and frequency. This paper discusses the effects of uniform temperature changes on the seismic responses of a cable-stayed bridge. A three dimensional finite element model of a cable-stayed bridge using OpenSees is established for nonlinear time history analysis, and uniform temperature load is applied to the prototype bridge before the conducting of seismic excitation. Three ground motion records are selected from the PEER strong motion database based on the design spectrum. Case studies are then performed considering the varying temperature and the connections between the deck and pylons of the bridge. The result shows that the seismic responses of the bridge are significantly increased with the consideration of temperature load. Meanwhile, the types between the deck and pylon also have notable impacts on the seismic responses of the bridge with and without temperature changes. This research could provide a reference for designers during the design phase of cable-stayed brides.
Active seismic response control systems for nuclear power plant equipment facilities
International Nuclear Information System (INIS)
Kobori, Takuji; Kanayama, Hiroo; Kamagata, Shuichi
1989-01-01
To sustain severe earthquake ground motion, a new type of anti-seismic structure is proposed, called a Dynamic Intelligent Building (DIB) system, which is positioned as an active seismic response controlled the structure. The structural concept starts from a new recognition of earthquake ground motion, and the structural natural frequency is actively adjusted to avoid resonant vibration, and similarly the external counter-force cancels the resonant force which comes from the dynamic structural motion energy. These concepts are verified using an analytical simulator program. The advanced application of the DIB system, is the Active Supporting system and the Active Stabilizer system for nuclear power plant equipment facilities. (orig.)
Seismic Response Of Masonry Plane Walls: A Numerical Study On Spandrel Strength
International Nuclear Information System (INIS)
Betti, Michele; Galano, Luciano; Vignoli, Andrea
2008-01-01
The paper reports the results of a numerical investigation on masonry walls subjected to in-plane seismic loads. This research aims to verify the formulae of shear and flexural strength of masonry spandrels which are given in the recent Italian Standards. Seismic pushover analyses have been carried out using finite element models of unreinforced walls and strengthened walls introducing reinforced concrete (RC) beams at the floor levels. Two typologies of walls have been considered distinguished for the height to length ratio h/l of the spandrels: a) short beams (h/l = 1.33) and b) slender beams (h/l = 0.5). Results obtained for the unreinforced and the strengthened walls are compared with equations for shear and flexural strength provided in Standards [1]. The numerical analyses show that the reliability of these equations is at least questionable especially for the prediction of the flexural strength. In the cases in which the axial force has not been determined by the structural analysis, Standards seems to overestimate the flexural strength of short spandrels both for the unreinforced and the strengthened wall
Time Analysis of Building Dynamic Response Under Seismic Action. Part 2: Example of Calculation
Ufimtcev, E. M.
2017-11-01
The second part of the article illustrates the use of the time analysis method (TAM) by the example of the calculation of a 3-storey building, the design dynamic model (DDM) of which is adopted in the form of a flat vertical cantilever rod with 3 horizontal degrees of freedom associated with floor and coverage levels. The parameters of natural oscillations (frequencies and modes) and the results of the calculation of the elastic forced oscillations of the building’s DDM - oscillograms of the reaction parameters on the time interval t ∈ [0; 131,25] sec. The obtained results are analyzed on the basis of the computed values of the discrepancy of the DDS motion equation and the comparison of the results calculated on the basis of the numerical approach (FEM) and the normative method set out in SP 14.13330.2014 “Construction in Seismic Regions”. The data of the analysis testify to the accuracy of the construction of the computational model as well as the high accuracy of the results obtained. In conclusion, it is revealed that the use of the TAM will improve the strength of buildings and structures subject to seismic influences when designing them.
Seismic Response Of Masonry Plane Walls: A Numerical Study On Spandrel Strength
Betti, Michele; Galano, Luciano; Vignoli, Andrea
2008-07-01
The paper reports the results of a numerical investigation on masonry walls subjected to in-plane seismic loads. This research aims to verify the formulae of shear and flexural strength of masonry spandrels which are given in the recent Italian Standards [1]. Seismic pushover analyses have been carried out using finite element models of unreinforced walls and strengthened walls introducing reinforced concrete (RC) beams at the floor levels. Two typologies of walls have been considered distinguished for the height to length ratio h/l of the spandrels: a) short beams (h/l = 1.33) and b) slender beams (h/l = 0.5). Results obtained for the unreinforced and the strengthened walls are compared with equations for shear and flexural strength provided in Standards [1]. The numerical analyses show that the reliability of these equations is at least questionable especially for the prediction of the flexural strength. In the cases in which the axial force has not been determined by the structural analysis, Standards [1] seems to overestimate the flexural strength of short spandrels both for the unreinforced and the strengthened wall.
Effect of gravity loading on inelastic seismic response of reinforced concrete structures
International Nuclear Information System (INIS)
Chowdhury, Rajib; Reddy, G. Rami; Roy, Raghupati; Dutta, Sekhar Chandra
2003-01-01
The effect of gravity loading is not considered in inelastic seismic response to avoid complexity and to reduce the number of influencing parameters. However, the possibility of considerable effect of this factor is indicated in many studies on inelastic seismic behaviour of structures. Hence, it is necessary to study the nature and extent of this effect on inelastic seismic behaviour of structures. The present paper attempts to fulfill this objective by studying the variation of energy dissipation due to presence of various level of axial load. The study is further extended to see the effect of axial force due to gravity loading on the ductility demand of hysteretic energy demand arising in structural elements of a simple one storey structures. The study shows that the presence of axial force may increase the energy dissipation capacity of structure leading to a reduction in ductility demand. (author)
Seismic Response Analysis of Concrete Lining Structure in Large Underground Powerhouse
Directory of Open Access Journals (Sweden)
Xiaowei Wang
2017-01-01
Full Text Available Based on the dynamic damage constitutive model of concrete material and seismic rock-lining structure interaction analysis method, the seismic response of lining structure in large underground powerhouse is studied in this paper. In order to describe strain rate dependence and fatigue damage of concrete material under cyclic loading, a dynamic constitutive model for concrete lining considering tension and shear anisotropic damage is presented, and the evolution equations of damage variables are derived. The proposed model is of simple form and can be programmed into finite element procedure easily. In order to describe seismic interaction characteristics of the surrounding rock and lining, an explicit dynamic contact analysis method considering bond and damage characteristics of contact face between the surrounding rock and lining is proposed, and this method can integrate directly without iteration. The proposed method is applied to seismic stability calculation of Yingxiuwan Underground Powerhouse, results reveal that the amplitude and duration of input seismic wave determine the damage degree of lining structure, the damage zone of lining structure is mainly distributed in its arch, and the contact face damage has great influence on the stability of the lining structure.
Use of response envelopes for seismic margin assessment of reinforced concrete walls and slabs
Energy Technology Data Exchange (ETDEWEB)
Ile, Nicolas; Frau, Alberto, E-mail: alberto.frau@cea.fr
2017-04-01
Highlights: • Proposal of a method for application of the elliptical envelope to RC shell elements. • Proposal of new algorithms for the seismic margin evaluation for RC shell elements. • Verification of a RC wall 3D structure, using the proposed assessment approach. - Abstract: Seismic safety evaluations of existing nuclear facilities are usually based on the assumption of structural linearity. For the design basis earthquake (DBE), it is reasonable to apply a conventional evaluation of the seismic safety of building structures and carry out a linear elastic analysis to assess the load effects on structural elements. Estimating the seismic capacity of a structural element requires an estimation of the critical combination of responses acting in this structural element and compare this combination with the capacity of the element. By exploiting the response-spectrum-based procedure for predicting the response envelopes in linear structures formulated by Menun and Der Kiureghian (2000a), algorithms are developed for the seismic margin assessment of reinforced concrete shell finite elements. These algorithms facilitate the comparison of the response-spectrum-based envelopes to prescribed capacity surfaces for the purpose of assessing the safety margin of this kind of structures. The practical application of elliptical response envelopes in case of shell finite elements is based on the use of layer models such as those developed by Marti (1990), which transfer the generalized stress field to three layers under the assumption that the two outer layers carry membrane forces and the internal layer carries only the out-of-plane shears. The utility of the assessment approach is discussed with reference to a case study of a 3D structure made of reinforced concrete walls.
Use of response envelopes for seismic margin assessment of reinforced concrete walls and slabs
International Nuclear Information System (INIS)
Ile, Nicolas; Frau, Alberto
2017-01-01
Highlights: • Proposal of a method for application of the elliptical envelope to RC shell elements. • Proposal of new algorithms for the seismic margin evaluation for RC shell elements. • Verification of a RC wall 3D structure, using the proposed assessment approach. - Abstract: Seismic safety evaluations of existing nuclear facilities are usually based on the assumption of structural linearity. For the design basis earthquake (DBE), it is reasonable to apply a conventional evaluation of the seismic safety of building structures and carry out a linear elastic analysis to assess the load effects on structural elements. Estimating the seismic capacity of a structural element requires an estimation of the critical combination of responses acting in this structural element and compare this combination with the capacity of the element. By exploiting the response-spectrum-based procedure for predicting the response envelopes in linear structures formulated by Menun and Der Kiureghian (2000a), algorithms are developed for the seismic margin assessment of reinforced concrete shell finite elements. These algorithms facilitate the comparison of the response-spectrum-based envelopes to prescribed capacity surfaces for the purpose of assessing the safety margin of this kind of structures. The practical application of elliptical response envelopes in case of shell finite elements is based on the use of layer models such as those developed by Marti (1990), which transfer the generalized stress field to three layers under the assumption that the two outer layers carry membrane forces and the internal layer carries only the out-of-plane shears. The utility of the assessment approach is discussed with reference to a case study of a 3D structure made of reinforced concrete walls.
Response spectrum analysis of a stochastic seismic model
International Nuclear Information System (INIS)
Kimura, Koji; Sakata, Masaru; Takemoto, Shinichiro.
1990-01-01
The stochastic response spectrum approach is presented for predicting the dynamic behavior of structures to earthquake excitation expressed by a random process, one of whose sample functions can be regarded as a recorded strong-motion earthquake accelerogram. The approach consists of modeling recorded ground motion by a random process and the root-mean-square response (rms) analysis of a single-degree-of-freedom system by using the moment equations method. The stochastic response spectrum is obtained as a plot of the maximum rms response versus the natural period of the system and is compared with the conventional response spectrum. (author)
Seismic Safety Margins Research Program. Phase I final report - Subsystem response (Project V)
International Nuclear Information System (INIS)
Shieh, L.C.; Chuang, T.Y.; O'Connell, W.J.
1981-10-01
This document reports on (1) the computation of the responses of subsystems, given the input subsystem support motion for components and systems whose failure can lead to an accident sequence (radioactive release), and (2) the results of a sensitivity study undertaken to determine the contributions of the several links in the seismic methodology chain (SMC) - seismic input (SI), soil-structure interaction (SSI), structure response (STR), and subsystem response (SUB) - to the uncertainty in subsystem response. For the singly supported subsystems (e.g., pumps, turbines, electrical control panels, etc.), we used the spectral acceleration response of the structure at the point where the subsystem components were mounted. For the multiple supported subsystems, we developed 13 piping models of five safety-related systems, and then used the pseudostatic-mode method with multisupport input motion to compute the response parameters in terms of the parameters used in the fragility descriptions (i.e., peak resultant accelerations for valves and peak resultant moments for piping). Damping and frequency were varied to represent the sources of modeling and random uncertainty. Two codes were developed: a modified version of SAPIV which assembles the piping supports into groups depending on the support's location relative to the attached structure, and SAPPAC a stand-alone modular program from which the time-history analysis module is extracted. On the basis of our sensitivity study, we determined that the variability in the combined soil-structure interaction, structural response, and subsystem response areas contribute more to uncertainty in subsystem response than does the variability in the seismic input area, assuming an earthquake within the limited peak ground acceleration range, i.e., 0.15 to 0.30g. The seismic input variations were in terms of different earthquake time histories. (author)
Combined effects of traveling seismic waves and soil nonlinearity on nuclear power plant response
International Nuclear Information System (INIS)
Lee, T.H.; Charman, C.M.
1981-01-01
The effects of ground motion nonuniformity on the seismic input have been actively studied in recent years by considering the passage of traveling seismic waves. These studies gave rise to a new class of soil-structure interaction problems in which the seismic input is modified as a result of the spatial variations of ground motion. The phenomena were usually studied by using the elastic half-space simulation or discrete spring-models for modeling the soil medium. Finite element methods were also used recently on a limited scope. Results obtained from these investigations are often manifested by an attenuation of translational excitation along with an addition of rotational ground motion input. The decrease in structural response resulting from the input loss in the translational component was often insignificant since the response reduction tends to be offset by the effects from rotational input. The traveling wave effects have, so far, been investigated within the framework of linear theory with soil nonlinearity ignored. Conversely, the incorporation of soil nonlinearity in soil-structure interaction analyses has been done without including wave effect. Seismic analyses considering the hysteretic behavior of soil have been performed using highly idealized models for steady-state solution. More elaborate nonlinear seismic models deal with only the strain-dependent soil modulus rather than the transient unloading-reloading type of hysteretic characteristics of soil under a time-function input of earthquake trace. Apparently, the traveling wave effect and soil nonlinearity have been separately treated in the past. The purpose of this paper is to demonstrate that these two major effects can be combined in one model such that the influence of wave passage is reflected through the hysteretic behavior of soil particles, and thereby achieving significant reduction in seismic loads. (orig./RW)
Comparison of seismic response of ordinary and base-isolated structures
International Nuclear Information System (INIS)
Kuroda, T.; Kobatake, M.; Seidensticker, R.W.; Chang, Y.W.
1992-01-01
Seismic isolation is growing rapidly worldwide as a cost-effective and reliable design strategy for a wide range of critical and important facilities (e.g., hospitals, computer centers, etc.) Shimizu Corporation of Japan has a test facility at Tohoku University in Sendai, Japan. The test facility was constructed in 1986 and has two buildings: one is base isolated and the other is conventionally founded. The buildings are full-size, three-story reinforced concrete structures. The dimensions and construction of the superstructures are identical. For the past several years, Shimizu Corporation has installed a number of different isolation systems in the isolated building at the test facility to study the response of base isolation systems to actual earthquake motions. Argonne National Laboratory (ANL) has been deeply involved in the development of seismic isolation for use in nuclear facilities for the past decade. Using the funding and direction of the US Department of Energy (USDOE), ANL has been developing methodology needed to evaluate the usefulness and effectiveness of seismic isolation for advanced liquid metal-cooled reactors (LMRs). This paper compares the seismic responses of ordinary and base-isolated buildings. Earthquake records of significant importance from April 1989 to September 1991, after the installation of bearings have been analyzed. Numerical simulations of the building responses have been performed and correlated with earthquake observation data. It is hoped that the results of this study will provide guidelines for the future use of isolator bearings for mitigation of earthquake damages
Directory of Open Access Journals (Sweden)
Mac Nally, R
2002-05-01
Full Text Available In forests and woodlands, fallen timber (logs and large branches is an important habitat element for many species of animals. Fallen timber has been systematically stripped in many forests, eliminating an important structural element. This study describes results of a ‘meso-scale’ experiment in which fallen timber was manipulated in a floodplain forest of the Murray River in south-eastern Australia. A thousand tons of wood were redistributed after one-year’s pre-manipulation monitoring, while a further two-year’s post-manipulation monitoring was conducted. The response of the main forest-floor small-mammal species, the Yellow-footed Antechinus Antechinus flavipes, to alterations of fallen-wood loads is documented. Results of the experiment will help to frame guidelines for fallen-timber management in these extensive floodplain forests.
Seismic responses of a pool-type fast reactor with different core support designs
International Nuclear Information System (INIS)
Wu, Ting-shu; Seidensticker, R.W.
1989-01-01
In designing the core support system for a pool-type fast reactor, there are many issues which must be considered in order to achieve an optimum and balanced design. These issues include safety, reliability, as well as costs. Several design options are possible to support the reactor core. Different core support options yield different frequency ranges and responses. Seismic responses of a large pool-type fast reactor incorporated with different core support designs have been investigated. 4 refs., 3 figs
Directory of Open Access Journals (Sweden)
Li Tian
2010-01-01
Full Text Available The behavior of power transmission tower-line system subjected to spatially varying base excitations is studied in this paper. The transmission towers are modeled by beam elements while the transmission lines are modeled by cable elements that account for the nonlinear geometry of the cables. The real multistation data from SMART-1 are used to analyze the system response subjected to spatially varying ground motions. The seismic input waves for vertical and horizontal ground motions are also generated based on the Code for Design of Seismic of Electrical Installations. Both the incoherency of seismic waves and wave travel effects are accounted for. The nonlinear time history analytical method is used in the analysis. The effects of boundary conditions, ground motion spatial variations, the incident angle of the seismic wave, coherency loss, and wave travel on the system are investigated. The results show that the uniform ground motion at all supports of system does not provide the most critical case for the response calculations.
Earthquake response spectra for seismic design of nuclear power plants in the UK
International Nuclear Information System (INIS)
Bommer, Julian J.; Papaspiliou, Myrto; Price, Warren
2011-01-01
Highlights: → Seismic design of UK nuclear power plants usually based on PML response spectra. → We review derivation of PML spectra in terms of earthquake data used and procedure. → The data include errors and represent a small fraction of what is now available. → Seismic design loads in current practice are derived as mean uniform hazard spectra. → The need to capture epistemic uncertainty makes use of single equation indefensible. - Abstract: Earthquake actions for the seismic design of nuclear power plants in the United Kingdom are generally based on spectral shapes anchored to peak ground acceleration (PGA) values obtained from a single predictive equation. Both the spectra and the PGA prediction equation were derived in the 1980s. The technical bases for these formulations of seismic loading are now very dated if compared with the state-of-the-art in this field. Alternative spectral shapes are explored and the options, and the associated benefits and challenges, for generating uniform hazard response spectra instead of fixed shapes anchored to PGA are discussed.
International Nuclear Information System (INIS)
Zaman, M.; Mamoon, S.M.
1989-01-01
Analysis of seismic response of structures located at a site with potential for soil liquefaction has drawn attention of many researchers. The topic is particularly important in the design of critical facilities like nuclear reactors and defense installations. This paper presents the results of a study involving evaluation of coupled seismic response of structures (model nuclear reactors) and characteristics of soil liquefaction at a site. The analysis procedure employed is based on the nonlinear finite element (FE) technique and accounts for the interaction effects due to a neighboring structure. Emphasis is given to the following features: prediction of spatial and temporal variation of pore water pressure; identification of the on-set of liquefaction based on the effective stress approach, and tracing the propagation of the liquefied zones with time and resulting response of the structures
Seismic design method of free standing rack
International Nuclear Information System (INIS)
Taniguchi, Katsuhiko; Okuno, Daisaku; Iwasaki, Akihisa; Nekomoto, Yoshitsugu; Matsuoka, Toshihiro
2013-01-01
For high earthquake resistance and ease of installation, free standing racks which are not anchored to the pool floor or walls has been adopted in many countries. Under the earthquake, the response of the free standing rack is highly nonlinear and involves a complex combination of motions (sliding, rocking, twisting, and turning) and impacts between the fuel assemblies and the fuel cell walls, rack-to-rack, and the pit floor and rack pedestals. We carried out seismic experiments on the full-scale rack model in water and dry conditions to obtain the fundamental data about free standing rack (sliding, rocking and turning motions). We have developed the nonlinear dynamic analysis method to predict seismic response for the free standing rack utilizing the full-scale test result and verified the analysis evaluation method of the rack by comparison of test result. (author)
Seismic response of concrete gravity dams with finite reservoir
International Nuclear Information System (INIS)
Baumber, T.; Ghobarah, A.
1992-01-01
In most previous analyses of dam responses to earthquake ground motion, the upstream reservoir is assumed to be infinite in length and completely straight. The meandering nature of the river system, however, results in the creation of a finite length reservoir upstream of the dam structure. A study was carried out to examine the effects of the finite length of the reservoir on the dynamic behavior of the monolith. The effect of excitation of the far end of the boundary on the monolith's response is also of interest. The dam-foundation-reservoir system is modelled using a sub-structuring approach. The analysis is conducted in the frequency domain and utilizes the finite element technique. The water in the reservoir is assumed to be compressible, inviscid, and irrotational. The upstream reservoir is assumed to have a rectangular cross-section. It was found that the finite length reservoir assumption results in supplementary response peaks in the monolith's response. The finite reservoir length allows the reservoir to resonate both in horizontal and vertical directions. The magnitude and spacing of these supplementary response peaks are dependent on the length of the reservoir. The phase of the ground motion which affects the far end boundary of the reservoir was also found to have a significant effect on the dam monolith's response. 8 refs., 5 figs
Seismic qualification of a commercial grade emergency diesel generator system in high seismic zones
International Nuclear Information System (INIS)
Khan, Mohsin R.; Chen, Wayne W.H.; Chu, Winnie S.
2004-01-01
The paper presents the seismic qualification of a commercially procured emergency diesel generator (EDG) system for use in a nuclear power plant. Response spectrum analyses of finite element models, validated using in situ vibration test data, were performed to qualify the skid and floor mounted mechanical components whose functional capacity and structural integrity can be analyzed. Time history analyses of these models were also performed to obtain the amplified response spectra for seismic testing of small valves, electrical and electro-mechanical components whose functional capacity can not be analyzed to establish the seismic qualification. The operational loads were obtained by in-plant vibration monitoring. Full scale shake table testing was performed for auxiliary electrical cabinets. It is concluded that with some minor structural modifications, a commercial grade EDG system can be qualified for safety-related applications in nuclear power plants located in high seismic zones. (author)
Seismic response in archaeological areas: the case-histories of Rome
Donati, Stefano; Funiciello, Renato; Rovelli, Antonio
1999-03-01
Rome is affected by earthquakes associated to three different seismogenic districts: the Central Apennines area, the Colli Albani volcanic area and the Roman area. The major effects were exclusively due to Apennine seismicity and reached in some cases felt intensities up to VII-VIII degree (MCS scale). The predominant role in the damage distribution seems to be played by the local geological conditions. The historical centre of the city is characterized by the presence of two geomorphologic domains: the alluvial plain of Tiber river and the topographic relieves of Roman Hills, where tradition indicates the first site of the city foundation. In particular, the right river side is characterized by the outcropping of the regional bedrock along the Monte Mario-Gianicolo ridge, while the eastern relieves are the remnants of the Sabatini and Albani volcanic plateau, deeply eroded by the Tiber river and its tributaries during the last glacial low-stand (Würm). These domains are characterized by a large difference in seismic response, due to the high impedance contrast between Holocene coarse deposits filling the Tiber Valley and sedimentary and volcanic Plio-Pleistocene units. Seismic damage observed in 150 monuments of downtown Rome was indicating a significant concentration on alluvial recent deposits. This result was confirmed by the geographical distribution of conservation and retrofitting activities subsequent to main earthquakes, mostly related to local geological conditions. The cases of Marcus Aurelius' Column and Colosseum confirmed the influence of the Holocene alluvial network in local seismic response. During 2500 years of history, the monuments of Rome have `memorized' the seismic effects of historical earthquakes. In some cases, the integration of historical and geological research and macroseismic observations may provide original and useful indications to seismologists to define the seismic response of the city. Local site effects represent a serious
Seismic analysis of nuclear power plants
International Nuclear Information System (INIS)
Halbritter, A.L.
1984-01-01
Nuclear Power Plants require exceptional safety guarantees which are reflected in a rigorous control of the employed materials, advanced construction technology, sophisticated methods of analysis and consideration of non conventional load cases such as the earthquake loading. In this paper, the current procedures used in the seismic analysis of Nuclear Power Plants are presented. The seismic analysis of the structures has two objectives: the determination of forces in the structure in order to design it against earthquakes and the generation of floor response spectra to be used in the design of mechanical and electrical components and piping systems. (Author) [pt
Seismic response analysis of BWR buildings with embedded foundation
International Nuclear Information System (INIS)
Fukuzawa, R.; Chiba, O.; Tohdo, M.
1985-01-01
An investigation on the effect of various types of foundations embedded into soil deposit to the responses of BWR buildings is made. The frequency characteristics of massless rigid foundations such as impedance functions and input motion are first obtained, depending on the embedment depth, contact condition of side wall to soil and the thickness of surface layer in a two-layered soil. From the results it is found that the embedment depth and the thickness of surface layer have a distinct effect to the responses contributed by the impedance functions and the response values characterized by the input motions are obviously influenced by the embedment depth and the contact length of side wall to soil deposit. (orig.)
UMTS rapid response real-time seismic networks: implementation and strategies at INGV
Govoni, A.; Margheriti, L.; Moretti, M.; Lauciani, V.; Sensale, G.; Bucci, A.; Criscuoli, F.
2015-12-01
Universal Mobile Telecommunications System (UMTS) and its evolutions are nowadays the most affordable and widespread data communication infrastructure available almost world wide. Moreover the always growing cellular phone market is pushing the development of new devices with higher performances and lower power consumption. All these characteristics make UMTS really useful for the implementation of an "easy to deploy" temporary real-time seismic station. Despite these remarkable features, there are many drawbacks that must be properly taken in account to effectively transmit the seismic data: Internet security, signal and service availability, power consumption. - Internet security: exposing seismological data services and seismic stations to the Internet is dangerous, attack prone and can lead to downtimes in the services, so we setup a dedicated Virtual Private Network (VPN) service to protect all the connected devices. - Signal and service availability: while for temporary experiment a carefull planning and an accurate site selection can minimize the problem, this is not always the case with rapid response networks. Moreover, as with any other leased line, the availability of the UMTS service during a seismic crisis is basically unpredictable. Nowadays in Italy during a major national emergency a Committee of the Italian Civil Defense ensures unified management and coordination of emergency activities. Inside it the telecom companies are committed to give support to the crisis management improving the standards in their communication networks. - Power consumption: it is at least of the order of that of the seismic station and, being related to data flow and signal quality is largely unpredictable. While the most secure option consists in adding a second independent solar power supply to the seismic station, this is not always a very convenient solution since it doubles the cost and doubles the equipment on site. We found that an acceptable trade-off is to add an
Directory of Open Access Journals (Sweden)
Nikos Nanos
2013-01-01
Full Text Available This paper identifies the effects of infill wall existence and arrangement in the seismic response of frame structures utilising the global structural damage index after Park/Ang (GDIPA and the maximum interstorey drift ratio (MISDR to express structural seismic response. Five different infill wall topologies of a 10-storey frame structure have been selected and analysed presenting an improved damage distribution model for infill wall bearing frames, hence promoting the use of nonstructural elements as a means of improving frame structural seismic behaviour and highlighting important aspects of structural response, demonstrating the suitability of such element implementation beyond their intended architectural scope.
Effects of dead load on ductility of a floor system
International Nuclear Information System (INIS)
Fujisaki, E.; Sarkar, B.E.; Ho, H.; Reed, J.W.
1993-01-01
In seismic margin or seismic fragility calculations, the ductility scale factor F μ is often used to quantify the effect of inelastic energy absorption on structural capacity. In concept, the ductility scale factor can be thought of as a response spectrum reduction factor. For a given ductile structural element and input response spectrum, the product of F μ and the factor of safety against yield (F s ) provides a measure of the total factor of safety against failure (F). Testing and analytical studies by others have shown that structures such as shear walls and building frames (mounted vertically) subjected to horizontal input motions are capable of absorbing earthquake energy through inelastic behavior. Kennedy, 1984, Riddell, 1979, and Reed, 1991 studied the ductility scale factor and developed simplified procedures through the use of nonlinear analyses. For floor systems (mounted horizontally), we are mainly interested in the response to vertical input motions. Because of the constant downward pull of gravity, the nonlinear displacement of a floor structure is biased downward. This ratcheting phenomenon reduces the ductility scale factor for a horizontal element compared to the case where the same element is mounted vertically and is subjected to horizontal input motion. Through the use of nonlinear time history analyses, we investigated the effects of dead loads on the ductility scale factor of floor systems. We also developed a simple modification to the Riddell-Newmark procedure (Riddell, 1979), which is used to calculate the ductility scale factor for vertically mounted elements, to determine F μ for horizontally mounted elements
Seismic response computations for a long span bridge
International Nuclear Information System (INIS)
McCallen, D.B.
1994-01-01
The authors are performing large-scale numerical computations to simulate the earthquake response of a major long-span bridge that crosses the San Francisco Bay. The overall objective of the study is to estimate the response of the bridge to potential large-magnitude earthquakes generated on the nearby San Andreas and Hayward earthquake faults. Generation of a realistic model of the bridge system is complicated by the existence of large pile group foundations that extend deep into soft, saturated clay soils, and by the numerous expansion joints that segment the overall bridge structure. In the current study, advanced, nonlinear, finite element technology is being applied to rigorously model the detailed behavior of the bridge system and to shed light on the influence of the foundations and joints of the bridge
Seismic response of transamerical building. I. Data and preliminary analysis
Celebi, M.; Safak, E.
1991-01-01
The objective of this paper is to present preliminary analyses of a set of acceleration response records obtained during the October 17, 1989 Loma Prieta earthquake (Ms = 7.1) from the 60-story vertically tapered, pyramid-shaped Trans-america Building-a landmark of San Francisco. The building was instrumented in 1985 with 22 channels of synchronized sensors consisting of 13 uniaxial accelerometers deployed throughout the structure and connected to a central recording system and three triaxial strong-motion accelerographs at three different levels of the structure. No free-field accelerographs are at the site. The acceleration records permit the study of the behavior of this unique structure. The predominant translational response of the building and the associated frequency at approximately 0.28 Hz are identified from the records and their Fourier amplitude spectra. The records do not indicate any significant torsional motion. However, there is rocking type soil-structure interaction, and an associated frequency of approximately 2.0 Hz is identified from the Fourier amplitude spectra of the differential motions between the ground level and that at the basement. In addition, the response spectra for the basement motions indicate significant resonance in both directions at a period of approximately 0.5 seconds.
Computation of USGS Soil UHS and Comparison to NEHRP and PC 1 Seismic Response; FINAL
International Nuclear Information System (INIS)
Lee, R.C.
2000-01-01
Recently, new site-specific seismic design response spectra were developed for Savannah River Site (SRS) performance category (PC) 1,2,3 and 4 structures, systems and components (SSCs) (WSRC, 1997, 1998) in accordance with DOE Standards. The lower performance categories (PC1 and PC2) site-specific design basis were not compatible with the response spectrum generated if building code guidelines were used (National Earthquake Hazard Reduction Program Recommended Provisions for Seismic Regulations for New Building, (NEHRP), 1997). These differences in criteria and approach should be documented and understood. Thus, Westinghouse Savannah River Company (WSRC) initiated this study to evaluate the difference between the building code hazard assessment (NEHRP) and the site-specific hazard evaluations used for SRS design
Numerical calculation models of the elastoplastic response of a structure under seismic action
International Nuclear Information System (INIS)
Edjtemai, Nima.
1982-06-01
Two digital calculation models developed in this work have made it possible to analyze the exact dynamic behaviour of ductile structures with one or several degrees of liberty, during earthquakes. With the first model, response spectra were built in the linear and non-linear fields for different absorption and ductility values and two types of seismic accelerograms. The comparative study of these spectra made it possible to check the validity of certain hypotheses suggested for the construction of elastoplastic spectra from corresponding linear spectra. A simplified method of non-linear seismic calculation based on the modal analysis and the spectra of elastoplastic response was then applied to structures with a varying number of degrees of liberty. The results obtained in this manner were compared with those provided by an exact calculation provided by the second digital model developed by us [fr
DEFF Research Database (Denmark)
Damgaard, B M; Malmkvist, J; Pedersen, L J
2009-01-01
The aim of the present study was to study whether floor heating from 12 h after onset of nest building until 48 h after birth of the first piglet had any effect on measures related to body temperature, water consumption, stress response and immune competence in loose-housed sows (n = 23......). In conclusion, the present results indicate that floor heating for a limited period around parturition did not compromise physiological and immunological parameters, water intake and body temperature in loose-housed sows. The water intake peaked the day before parturition and the body temperature peaked...
Multiobjective Optimal Control of Longitudinal Seismic Response of a Multitower Cable-Stayed Bridge
Fangfang, Geng; Youliang, Ding
2016-01-01
The dynamic behavior of a multitower cable-stayed bridge with the application of partially longitudinal constraint system using viscous fluid dampers under real earthquake ground motions is presented. The study is based on the dynamic finite element model of the Jiashao Bridge, a six-tower cable-stayed bridge in China. The prime aim of the study is to investigate the effectiveness of viscous fluid dampers on the longitudinal seismic responses of the bridge and put forth a multiobjective optim...
Investigation and analysis of SSI effects in seismic response of NPPs EMO and EBO
International Nuclear Information System (INIS)
Juhasova, E.
1996-01-01
This progress report outlines and describes the analysis and investigations of soil-structure interaction effects in seismic response of Bohunice and Mochovce nuclear power plants. The work carries out consists of theoretical-numerical analysis of soil-structure interaction and the description of the experimental results obtained so far. Investigations were performed for different soil conditions and recommendations were elaborated as to prepare and use long-term monitoring of vibration activity at the Bohunice NPP site
Effect of viscosity on seismic response of waste storage tanks
International Nuclear Information System (INIS)
Tang, Yu; Uras, R.A.; Chang, Yao-Wen.
1992-06-01
The dynamic response of liquid-storage tanks subjected to harmonic excitations and earthquake ground motions has been studied. A rigid tank of negligible mass, rigidly supported at the base having a diameter of 50 ft. and fluid height of 20.4 ft. was used in the computer analysis. The liquid is assumed to have a density of 1.5 g/ml. Viscosity values, μ = 60, 200, 100, and 10,000 cP, were used in the numerical analyses to study the effects of viscosity on sloshing wave height, impulsive and convective pressure on the tank wall, base shear and base moments. Harmonic excitations as well as earthquake ground motions were used as input motions. The harmonic excitations used in the analyses covers a wide range of frequencies, including both the resonant and non-resonant frequencies. Two earthquake motions were used. One matches the Newmark-Hall median response spectrum and is anchored at 0.24 g for a rock site with a damping of 2% and a time duration of 10 s. The other is the 1978 Tabas earthquake which had a peak ZPA of 0.81 g and a time duration of 29 s. A small tank, about 1/15 the size of the typical waste storage tank, was used in the harmonic excitation study to investigate the effect of viscosity on the response of liquid-storage tanks and how the viscosity effect is affected by the size of the storage tank. The results of this study show that for the typical waste storage tank subjected to earthquake motions, the effect of viscosity on sloshing wave height and impulsive and convective pressures is very small and can be neglected. For viscosity effect to become noticeable in the response of the typical waste storage tank, the waste viscosity must be greater than 10,000 cP. This value is far greater than the estimated viscosity value of the high level wastes, which may range from 60 to 200 cP for some tanks
DEFF Research Database (Denmark)
Kurz-Besson, C.; Coûteaux, M.M.; Berg, Bjørn
2006-01-01
The forest floor needle mass and the decomposition rates of pine needle litter in a European climate transect were studied in order to estimate the impact of climate change on forest soil carbon sequestration. Eight pine forests preserved from fire were selected along a climatic latitudinal...... gradient from 40° to 60° N, from Spain and Portugal to Sweden. The forest floor (Oi and Oe layers) was sorted into five categories of increasing decomposition level according to morphological criteria. The needle mass loss in each category was determined using a linear mass density method. The needle...... and a recalcitrant one. NF was correlated with actual evapotranspiration (AET) whereas the decomposition parameters (decomposition rate of the decomposable fraction, first year mass loss, forest floor needle mass, age of the most-decomposed category) were related to a combined response function to climate (CRF...
DEFF Research Database (Denmark)
Jensen, Karin Hjelholt; Jørgensen, Lisbeth; Haugegaard, Svend
2017-01-01
of straw provided affected stomach health in a curvilinear manner. Provision of up to approximately 300 g straw/pig/day progressively decreased the risk of oesophageal ulceration and scarring. At larger amounts of straw the ulceroprotective effect of straw was reduced which requires further investigation...... the structure of the stomach contents as revealed by the increased weight and dry matter content and decreased sedimentation of the digesta. Provision of approximately 300 g straw/pig/day on the floor may be a potential strategy to reduce, but not inevitably eliminate, oesophageal ulceration in pigs......The aim of the present study was (1) to determine the dose-response relationship between the amount of straw provided on the floor and oesophageal ulceration in pigs kept under typical Danish production conditions (18 pigs/pen, 0.7 m2/pig, partly slatted floor, ad libitum access to feed), (2...
Phase space interrogation of the empirical response modes for seismically excited structures
Paul, Bibhas; George, Riya C.; Mishra, Sudib K.
2017-07-01
Conventional Phase Space Interrogation (PSI) for structural damage assessment relies on exciting the structure with low dimensional chaotic waveform, thereby, significantly limiting their applicability to large structures. The PSI technique is presently extended for structure subjected to seismic excitations. The high dimensionality of the phase space for seismic response(s) are overcome by the Empirical Mode Decomposition (EMD), decomposing the responses to a number of intrinsic low dimensional oscillatory modes, referred as Intrinsic Mode Functions (IMFs). Along with their low dimensionality, a few IMFs, retain sufficient information of the system dynamics to reflect the damage induced changes. The mutually conflicting nature of low-dimensionality and the sufficiency of dynamic information are taken care by the optimal choice of the IMF(s), which is shown to be the third/fourth IMFs. The optimal IMF(s) are employed for the reconstruction of the Phase space attractor following Taken's embedding theorem. The widely referred Changes in Phase Space Topology (CPST) feature is then employed on these Phase portrait(s) to derive the damage sensitive feature, referred as the CPST of the IMFs (CPST-IMF). The legitimacy of the CPST-IMF is established as a damage sensitive feature by assessing its variation with a number of damage scenarios benchmarked in the IASC-ASCE building. The damage localization capability, remarkable tolerance to noise contamination and the robustness under different seismic excitations of the feature are demonstrated.
Calculation of seismic response of a flexible rotor by complex modal method, 1
International Nuclear Information System (INIS)
Azuma, Takao; Saito, Shinobu
1984-01-01
In rotary machines, at the time of earthquakes, whether the rotating part and stationary part touch or whether the bearings and seals are damaged or not are problems. In order to examine these problems, it is necessary to analyze the seismic response of a rotary shaft or sometimes a casing system. But the conventional analysis methods are unsatisfactory. Accordingly, in the case of a general shaft system supported with slide bearings and on which gyro effect acts, complex modal method must be used. This calculation method is explained in detail in the book of Lancaster, however, when this method is applied to the seismic response of rotary shafts, the calculation time is considerably different according to the method of final integration. In this study, good results were obtained when the method which did not depend on numerical integration was attempted. The equation of motion and its solution, the displacement vector of a foundation, the verification of the calculation program and the example of calculating the seismic response of two coupled rotor shafts are reported. (Kako, I.)
Major structural response methods used in the seismic safety margins research program
International Nuclear Information System (INIS)
Chou, C.K.; Lo, T.; Vagliente, V.
1979-01-01
In order to evaluate the conservatisms in present nuclear power plant seismic safety requirements, a probabilistic based systems model is being developed. This model will also be used to develop improved requirements. In Phase I of the Seismic Safety Margins Research Program (SSMRP), this methodology will be developed for a specific nuclear power plant and used to perform probabilistic sensitivity studies to gain engineering insights into seismic safety requirements. Random variables in the structural response analysis area, or parameters which cause uncertainty in the response, are discussed and classified into three categories; i.e., material properties, structural dynamic characteristics and related modeling techniques, and analytical methods. The sensitivity studies are grouped into two categories; deterministic and probabilistic. In a system analysis, transfer functions in simple form are needed since there are too many responses which have to be calculated in a Monte Carlo simulation to use the usual straightforward calculation approach. Therefore, the development of these simple transfer functions is one of the important tasks in SSMRP. Simplified as well as classical transfer functions are discussed
Studies on Pounding Response Considering Structure-Soil-Structure Interaction under Seismic Loads
Directory of Open Access Journals (Sweden)
Peizhen Li
2017-12-01
Full Text Available Pounding phenomena considering structure–soil–structure interaction (SSSI under seismic loads are investigated in this paper. Based on a practical engineering project, this work presents a three-dimensional finite element numerical simulation method using ANSYS software. According to Chinese design code, the models of adjacent shear wall structures on Shanghai soft soil with the rigid foundation, box foundation and pile foundation are built respectively. In the simulation, the Davidenkov model of the soil skeleton curve is assumed for soil behavior, and the contact elements with Kelvin model are adopted to simulate pounding phenomena between adjacent structures. Finally, the dynamic responses of adjacent structures considering the pounding and SSSI effects are analyzed. The results show that pounding phenomena may occur, indicating that the seismic separation requirement for adjacent buildings of Chinese design code may not be enough to avoid pounding effect. Pounding and SSSI effects worsen the adjacent buildings’ conditions because their acceleration and shear responses are amplified after pounding considering SSSI. These results are significant for studying the effect of pounding and SSSI phenomena on seismic responses of structures and national sustainable development, especially in earthquake prevention and disaster reduction.
Seismic response of base-isolated buildings using a viscoelastic model
International Nuclear Information System (INIS)
Uras, R.A.
1993-01-01
Due to recent developments in elastomer technology,seismic isolation using elastomer bearings is rapidly gaining acceptance as a design tool to enhance structural seismic margins and to protect people and equipment from earthquake damage. With proper design of isolators, the fundamental frequency of the structure can be reduced to a value that is lower than the dominant frequencies of earthquake ground motions. The other feature of an isolation system is that it can provide a mechanism for energy dissipation. In the USA, the use of seismic base-isolation has become an alternate strategy for advanced Liquid Metal-cooled Reactors (LMRs). ANL has been deeply involved in the development and implementation of seismic isolation for use in both nuclear facilities and civil structures for the past decade. Shimizu Corporation of Japan has a test facility at Tohoku University in Sendai, Japan. The test facility has two buildings: one is base isolated and the other is conventionally founded. The buildings are full-size, three-story reinforced concrete structures. The dimensions and construction of the superstructures are identical. They were built side by side in a seismically active area. In 1988, the ANL/Shimizu Joint Program was established to study the differences in behavior of base-isolated and ordinarily founded structures when subjected to earthquake loading. A more comprehensive description of this joint program is presented in a companion paper (Wang et al. 1993). With the increased use of elastomeric polymers in industrial applications such as isolation bearings, the importance of constitutive modeling of viscoelastic materials is more and more pronounced. A realistic representation of material behavior is essential for computer simulations to replicate the response observed in experiments
International Nuclear Information System (INIS)
Tanimoto, K.; Ito, T.; Fujita, K.; Kurihara, C.; Sawada, Y.; Sakurai, A.
1988-01-01
The paper presents the seismic response of reactor vessel of pool type LMFBR with fluid-structure interaction. The reactor vessel has bottom support arrangement, the same core support system as Super-Phenix in France. Due to the bottom support arrangement, the level of core support is lower than that of the side support arrangement. So, in this reactor vessel, the displacement of the core top tends to increase because of the core's rocking. In this study, we investigated the vibration and seismic response characteristics of the reactor vessel. Therefore, the seismic experiments were carried out using one-eighth scale model and the seismic response including FSI and sloshing were investigated. From this study, the effect of liquid on the vibration characteristics and the seismic response characteristics of reactor vessel were clarified and sloshing characteristics were also clarified. It was confirmed that FEM analysis with FSI can reproduce the seismic behavior of the reactor vessel and is applicable to seismic design of the pool type LMFBR with bottom support arrangement. (author). 5 refs, 14 figs, 2 tabs
Seismic response analysis for hinged-leg type port crane
Energy Technology Data Exchange (ETDEWEB)
Kashiwazaki, A.; Kanayama, T.; Arai, K. [Ishikawajima-Harima Heavy Industries Co. Ltd., Tokyo (Japan)
2000-04-01
Container cranes and unloaders in Kobe Pont were severely damaged during the Southern Hyogo Prefecture Earthquake in 1995. Notably, some of the hinged-leg type of cranes with hinges at the end of sea-or land-side of legs were overturned. These damages were derived from the uplifting of their legs. To explain the uplifting and overturning behavior, we carried out nonlinear analyses and shaking table tests using a 1/8-scale model of the container crane. The results of nonlinear response analyses of hinged-leg type of crane, which are in an agreement with the state of damages in the Southern Hyogo Prefecture Earthquake and the result of shaking table tests, are described. (author)
Hata, Yoshiya; Ichii, Koji; Yamada, Masayuki; Tokida, Ken-Ichi; Takezawa, Koichiro; Shibao, Susumu; Mitsushita, Junji; Murata, Akira; Furukawa, Aiko; Koizumi, Keigo
Accurate evaluation on the seismic response characteristics of a road embankment is very important for the rational seismic assessment. However, in a lot of previous studies, the seismic response characteristics of an embankment were evaluated based on the results of shaking table test, centrifuge model test and dynamic FEM analysis. In this study, the transfer function and the shear wave velocity of a road embankment were evaluated based on the in-situ records of moderate earthquake observation and microtremor measurement. Test results show the possibility that the shear wave velocity of an embankment can be estimated by the earthquake observation or the microtremor measurement and the dynamic linear FEM analysis.
A calculation model for a HTR core seismic response
International Nuclear Information System (INIS)
Buland, P.; Berriaud, C.; Cebe, E.; Livolant, M.
1975-01-01
The paper presents the experimental results obtained at Saclay on a HTGR core model and comparisons with analytical results. Two series of horizontal tests have been performed on the shaking table VESUVE: sinusoidal test and time history response. Acceleration of graphite blocks, forces on the boundaries, relative displacement of the core and PCRB model, impact velocity of the blocks on the boundaries were recorded. These tests have shown the strongly non-linear dynamic behaviour of the core. The resonant frequency of the core is dependent on the level of the excitation. These phenomena have been explained by a computer code, which is a lumped mass non-linear model. Good correlation between experimental and analytical results was obtained for impact velocities and forces on the boundaries. This comparison has shown that the damping of the core is a critical parameter for the estimation of forces and velocities. Time history displacement at the level of PCRV was reproduced on the shaking table. The analytical model was applied to this excitation and good agreement was obtained for forces and velocities. (orig./HP) [de
International Nuclear Information System (INIS)
Praveen Kumar; Jangid, R.S.; Reddy, G.R.
2013-01-01
Highlights: ► Piping system with semi-active variable stiffness damper is investigated under different seismic excitations. ► Switching control law and modified switching control law are adopted. ► There exist an optimum parameters of the SAVSD. ► Substantial reduction of the seismic response of piping system with SAVSD is observed. ► Good amount of energy dissipation is observed. -- Abstract: Seismic loads on piping system due to earthquakes can cause excessive vibrations, which can lead to serious instability resulting in damage or complete failure. In this paper, semi-active variable stiffness dampers (SAVSDs) have been studied to mitigate seismic response and vibration control of piping system used in the process industries, fossil and fissile fuel power plant. The SAVSD changes its stiffness depending upon the piping response and accordingly adds the control forces in the piping system. A study is conducted on the performance of SAVSD due to variation in device stiffness ratios in the switching control law and modified switching control law, which plays an important role in the present control algorithm of the damper. The effectiveness of the SAVSD in terms of reduction in the responses, namely, displacements, accelerations and base shear of the piping system is investigated by comparing uncontrolled responses under four different artificial earthquake motions with increasing amplitudes. The analytical results demonstrate that the SAVSDs under particular optimum parameters are very effective and practically implementable for the seismic response mitigation, vibration control and seismic requalification of piping systems
Energy Technology Data Exchange (ETDEWEB)
Praveen Kumar, E-mail: praveen@barc.gov.in [Department of Civil Engineering, Indian Institute of Technology Bombay, Powai, Mumbai 400076 (India); Bhabha Atomic Research Centre, Trombay, Mumbai 400085 (India); Jangid, R.S. [Department of Civil Engineering, Indian Institute of Technology Bombay, Powai, Mumbai 400076 (India); Reddy, G.R. [Bhabha Atomic Research Centre, Trombay, Mumbai 400085 (India)
2013-05-15
Highlights: ► Piping system with semi-active variable stiffness damper is investigated under different seismic excitations. ► Switching control law and modified switching control law are adopted. ► There exist an optimum parameters of the SAVSD. ► Substantial reduction of the seismic response of piping system with SAVSD is observed. ► Good amount of energy dissipation is observed. -- Abstract: Seismic loads on piping system due to earthquakes can cause excessive vibrations, which can lead to serious instability resulting in damage or complete failure. In this paper, semi-active variable stiffness dampers (SAVSDs) have been studied to mitigate seismic response and vibration control of piping system used in the process industries, fossil and fissile fuel power plant. The SAVSD changes its stiffness depending upon the piping response and accordingly adds the control forces in the piping system. A study is conducted on the performance of SAVSD due to variation in device stiffness ratios in the switching control law and modified switching control law, which plays an important role in the present control algorithm of the damper. The effectiveness of the SAVSD in terms of reduction in the responses, namely, displacements, accelerations and base shear of the piping system is investigated by comparing uncontrolled responses under four different artificial earthquake motions with increasing amplitudes. The analytical results demonstrate that the SAVSDs under particular optimum parameters are very effective and practically implementable for the seismic response mitigation, vibration control and seismic requalification of piping systems.
Study on vertical seismic response model of BWR-type reactor building
International Nuclear Information System (INIS)
Konno, T.; Motohashi, S.; Izumi, M.; Iizuka, S.
1993-01-01
A study on advanced seismic design for LWR has been carried out by the Nuclear Power Engineering Corporation (NUPEC), under the sponsorship of the Ministry of International Trade and Industry (MITI) of Japan. As a part of the study, it has been investigated to construct an accurate analytical model of reactor buildings for a seismic response analysis, which can reasonably represent dynamic characteristics of the building. In Japan, vibration models of reactor buildings for horizontal ground motion have been studied and examined through many simulation analyses for forced vibration tests and earthquake observations of actual buildings. And now it is possible to establish a reliable horizontal vibration model on the basis of multi-lumped mass and spring model. However, vertical vibration models have not been so much studied as horizontal models, due to less observed data for vertical motions. In this paper, the vertical seismic response models of a BWR-type reactor building including soil-structure interaction effect are numerically studied, by comparing the dynamic characteristics of (1) three dimensional finite element model, (2) multi-stick lumped mass model with a flexible base-mat, (3) multi-stick lumped mass model with a rigid base-mat and (4) single-stick lumped mass model. In particular, the BWR-type reactor building has the long span truss roof which is considered to be one of the critical members to vertical excitation. The modelings of the roof trusses are also studied
Role and development of soil parameters for seismic responses of buried lifelines
Energy Technology Data Exchange (ETDEWEB)
Wang, L.R.L.
1983-01-01
Buried lifelines, e.g. oil, gas, water and sewer pipelines have been damaged heavily in recent earthquakes such as 1971 San Fernando Earthquake, in U.S.A., 1976 Tangshan Earthquake, in China, and 1978 MiyagiKen-Oki Earthquake, in Japan, among others. Researchers on the seismic performance of these buried lifelines have been initiated in the United States and many other countries. Various analytical models have been proposed. However, only limited experimental investigations are available. The sources of earthquake damage to buried lifelines include landslide, tectonic uplift-subsidence, soil liquefaction, fault displacement and ground shaking (effects of wave propagation). This paper is concerned with the behavior of buried lifeline systems subjected to surface faulting and ground shaking. The role and development of soil parameters that significantly influence the seismic responses are discussed. The scope of this paper is to examine analytically the influence of various soil and soilstructure interaction parameters to the seismic responses of buried pipelines, to report the currently available physical data of these and related parameters for immediate applications, and to describe the experiments to obtain additional information on soil resistant characteristics to longitudinal pipe motions.
Seismic Response of 3D Steel Buildings considering the Effect of PR Connections and Gravity Frames
Directory of Open Access Journals (Sweden)
Alfredo Reyes-Salazar
2014-01-01
Full Text Available The nonlinear seismic responses of 3D steel buildings with perimeter moment resisting frames (PMRF and interior gravity frames (IGF are studied explicitly considering the contribution of the IGF. The effect on the structural response of the stiffness of the beam-to-column connections of the IGF, which is usually neglected, is also studied. It is commonly believed that the flexibility of shear connections is negligible and that 2D models can be used to properly represent 3D real structures. The results of the study indicate, however, that the moments developed on columns of IGF can be considerable and that modeling buildings as plane frames may result in very conservative designs. The contribution of IGF to the lateral structural resistance may be significant. The contribution increases when their connections are assumed to be partially restrained (PR. The incremented participation of IGF when the stiffness of their connections is considered helps to counteract the no conservative effect that results in practice when lateral seismic loads are not considered in IGF while designing steel buildings with PMRF. Thus, if the structural system under consideration is used, the three-dimensional model should be used in seismic analysis and the IGF and the stiffness of their connections should be considered as part of the lateral resistance system.
Seismic Response of 3D Steel Buildings considering the Effect of PR Connections and Gravity Frames
Haldar, Achintya; López-Barraza, Arturo; Rivera-Salas, J. Luz
2014-01-01
The nonlinear seismic responses of 3D steel buildings with perimeter moment resisting frames (PMRF) and interior gravity frames (IGF) are studied explicitly considering the contribution of the IGF. The effect on the structural response of the stiffness of the beam-to-column connections of the IGF, which is usually neglected, is also studied. It is commonly believed that the flexibility of shear connections is negligible and that 2D models can be used to properly represent 3D real structures. The results of the study indicate, however, that the moments developed on columns of IGF can be considerable and that modeling buildings as plane frames may result in very conservative designs. The contribution of IGF to the lateral structural resistance may be significant. The contribution increases when their connections are assumed to be partially restrained (PR). The incremented participation of IGF when the stiffness of their connections is considered helps to counteract the no conservative effect that results in practice when lateral seismic loads are not considered in IGF while designing steel buildings with PMRF. Thus, if the structural system under consideration is used, the three-dimensional model should be used in seismic analysis and the IGF and the stiffness of their connections should be considered as part of the lateral resistance system. PMID:24995357
International Nuclear Information System (INIS)
Hahm, Dae-Gi; Park, Kwan-Soon; Koh, Hyun-Moo
2008-01-01
The awareness of a seismic hazard and risk is being increased rapidly according to the frequent occurrences of the huge earthquakes such as the 2008 Sichuan earthquake which caused about 70,000 confirmed casualties and a 20 billion U.S. dollars economic loss. Since an earthquake load contains various uncertainties naturally, the safety of a structural system under an earthquake excitation has been assessed by probabilistic approaches. In many structural applications for a probabilistic safety assessment, it is often regarded that the failure of a system will occur when the response of the structure firstly crosses the limit barrier within a specified interval of time. The determination of such a failure probability is usually called the 'first-passage problem' and has been extensively studied during the last few decades. However, especially for the structures which show a significant nonlinear dynamic behavior, an effective and accurate method for the estimation of such a failure probability is not fully established yet. In this study, we presented a new approach to evaluate the first-passage probability of an earthquake response of seismically isolated structures. The proposed method is applied to the seismic isolation system for the containment buildings of a nuclear power plant. From the numerical example, we verified that the proposed method shows accurate results with more efficient computational efforts compared to the conventional approaches
International Nuclear Information System (INIS)
Zeuch, W.R.; Wang, C.Y.
1985-01-01
This paper presents some of the current capabilities of the three-dimensional piping code SHAPS and demonstrates their usefulness in handling analyses encountered in typical LMFBR studies. Several examples demonstrate the utility of the SHAPS code for problems involving fluid-structure interactions and seismic-related events occurring in three-dimensional piping networks. Results of two studies of pressure wave propagation demonstrate the dynamic coupling of pipes and elbows producing global motion and rigorous treatment of physical quantities such as changes in density, pressure, and strain energy. Results of the seismic analysis demonstrate the capability of SHAPS to handle dynamic structural response within a piping network over an extended transient period of several seconds. Variation in dominant stress frequencies and global translational frequencies were easily handled with the code. 4 refs., 10 figs
Seismic Response of a Platform-Frame System with Steel Columns
Directory of Open Access Journals (Sweden)
Davide Trutalli
2017-04-01
Full Text Available Timber platform-frame shear walls are characterized by high ductility and diffuse energy dissipation but limited in-plane shear resistance. A novel lightweight constructive system composed of steel columns braced with oriented strand board (OSB panels was conceived and tested. Preliminary laboratory tests were performed to study the OSB-to-column connections with self-drilling screws. Then, the seismic response of a shear wall was determined performing a quasi-static cyclic-loading test of a full-scale specimen. Results presented in this work in terms of force-displacement capacity show that this system confers to shear walls high in-plane strength and stiffness with good ductility and dissipative capacity. Therefore, the incorporation of steel columns within OSB bracing panels results in a strong and stiff platform-frame system with high potential for low- and medium-rise buildings in seismic-prone areas.
Comparison of elastic and inelastic seismic response of high temperature piping systems
International Nuclear Information System (INIS)
Thomas, F.M.; McCabe, S.L.; Liu, Y.
1994-01-01
A study of high temperature power piping systems is presented. The response of the piping systems is determined when subjected to seismic disturbances. Two piping systems are presented, a main steam line, and a cold reheat line. Each of the piping systems are modeled using the ANSYS computer program and two analyses are performed on each piping system. First, each piping system is subjected to a seismic disturbance and the pipe material is assumed to remain linear and elastic. Next the analysis is repeated for each piping system when the pipe material is modeled as having elastic-plastic behavior. The results of the linear elastic analysis and elastic-plastic analysis are compared for each of the two pipe models. The pipe stresses, strains, and displacements, are compared. These comparisons are made so that the effect of the material yielding can be determined and to access what error is made when a linear analysis is performed on a system that yields
Time Analysis of Building Dynamic Response Under Seismic Action. Part 1: Theoretical Propositions
Ufimtcev, E. M.
2017-11-01
The first part of the article presents the main provisions of the analytical approach - the time analysis method (TAM) developed for the calculation of the elastic dynamic response of rod structures as discrete dissipative systems (DDS) and based on the investigation of the characteristic matrix quadratic equation. The assumptions adopted in the construction of the mathematical model of structural oscillations as well as the features of seismic forces’ calculating and recording based on the data of earthquake accelerograms are given. A system to resolve equations is given to determine the nodal (kinematic and force) response parameters as well as the stress-strain state (SSS) parameters of the system’s rods.
Seismic Response Analysis and Test of 1/8 Scale Model for a Spent Fuel Storage Cask
Energy Technology Data Exchange (ETDEWEB)
Lee, Jae Han; Park, C. G.; Koo, G. H.; Seo, G. S. [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of); Yeom, S. H. [Chungnam Univ., Daejeon (Korea, Republic of); Choi, B. I.; Cho, Y. D. [Korea Hydro and Nuclear Power Co. Ltd., Daejeon (Korea, Republic of)
2005-07-15
The seismic response tests of a spent fuel dry storage cask model of 1/8 scale are performed for an typical 1940 El-centro and Kobe earthquakes. This report firstly focuses on the data generation by seismic response tests of a free standing storage cask model to check the overturing possibility of a storage cask and the slipping displacement on concrete slab bed. The variations in seismic load magnitude and cask/bed interface friction are considered in tests. The test results show that the model gives an overturning response for an extreme condition only. A FEM model is built for the test model of 1/8 scale spent fuel dry storage cask using available 3D contact conditions in ABAQUS/Explicit. Input load for this analysis is El-centro earthquake, and the friction coefficients are obtained from the test result. Penalty and kinematic contact methods of ABAQUS are used for a mechanical contact formulation. The analysis methods was verified with the rocking angle obtained by seismic response tests. The kinematic contact method with an adequate normal contact stiffness showed a good agreement with tests. Based on the established analysis method for 1/8 scale model, the seismic response analyses of a full scale model are performed for design and beyond design seismic loads.
Floors: Selection and Maintenance.
Berkeley, Bernard
Flooring for institutional, commercial, and industrial use is described with regard to its selection, care, and maintenance. The following flooring and subflooring material categories are discussed--(1) resilient floor coverings, (2) carpeting, (3) masonry floors, (4) wood floors, and (5) "formed-in-place floors". The properties, problems,…
Comparative study for methods to determine the seismic response of NPP structures
International Nuclear Information System (INIS)
Varpasuo, P.
1995-01-01
There are many different important problem areas in evaluating the seismic response of structures. In this study the effort is concentrated on three of these areas. The first task is the mathematical formulation of earthquake excitation. The random vibration theory is taken as the tool in this task. The second area of interest in this study is the soil-structure interaction analysis. The approach of impedance functions is chosen and the focal point of interest is the significance of frequency dependent impedance functions. The third area of interest is the methods to determine the structural response. The following three methods were tested: the mode superposition time history method; the complex frequency response method; the response spectrum method. The comparison was made with the aid of MSC/NASTRAN code. The three methods gave for outer containment building response results which were in good agreement with each other. (author). 4 refs., 5 figs
International Nuclear Information System (INIS)
Adhikari, S.; Patnaik, A.
2012-01-01
Fibre reinforced concrete has gained acceptance in several civil engineering applications. The proclivity of new generation of engineers to use steel fibre reinforced concrete can be attributed to some distinct functional and structural benefits that it can provide compared to conventional reinforced concrete. Fibre reinforced concrete has been found to increase the post-cracking tensile strength of concrete thus facilitating pseudo-plastic response, improved energy absorption, and better energy dissipation capabilities that lead to better structural response under cyclic loading. These factors suggest benefits in considering the use of steel fibre reinforced concrete to enhance the structural response of reinforced concrete structures under earthquake loading. This paper summarizes useful background on steel fibre reinforced concrete, the benefits over conventional reinforced concrete, and its response to cyclic excitation. The authors believe that steel fibre reinforced concrete is a suitable ductile high performance material that is gaining acceptance for applications in frame structures and is particularly suitable for enhancing seismic response. (author)
3-D seismic response of a base-isolated fast reactor
International Nuclear Information System (INIS)
Kitamura, S.; Morishita, M.; Iwata, K.
1992-01-01
This paper describes a 3-D response analysis methodology development and its application to a base-isolated fast breeder reactor (FBR) plant. At first, studies on application of a base-isolation system to an FBR plant were performed to identify a range of appropriate characteristics of the system. A response analysis method was developed based on mathematical models for the restoring force characteristics of several types of the systems. A series of shaking table tests using a small scale model was carried out to verify the analysis method. A good agreement was seen between the test and analysis results in terms of the horizontal and vertical responses. Parametric studies were then made to assess the effects of various factors which might be influential to the seismic response of the system. Moreover, the method was applied to evaluate three-dimensional response of the base-isolated FBR. (author)
UMTS rapid response real-time seismic networks: implementation and strategies at INGV
Govoni, Aladino; Margheriti, Lucia; Moretti, Milena; Lauciani, Valentino; Sensale, Gianpaolo; Bucci, Augusto; Criscuoli, Fabio
2015-04-01
The benefits of portable real-time seismic networks are several and well known. During the management of a temporary experiment from the real-time data it is possible to detect and fix rapidly problems with power supply, time synchronization, disk failures and, most important, seismic signal quality degradation due to unexpected noise sources or sensor alignment/tampering. This usually minimizes field maintenance trips and maximizes both the quantity and the quality of the acquired data. When the area of the temporary experiment is not well monitored by the local permanent network, the real-time data from the temporary experiment can be fed to the permanent network monitoring system improving greatly both the real-time hypocentral locations and the final revised bulletin. All these benefits apply also in case of seismic crises when rapid deployment stations can significantly contribute to the aftershock analysis. Nowadays data transmission using meshed radio networks or satellite systems is not a big technological problem for a permanent seismic network where each site is optimized for the device power consumption and is usually installed by properly specialized technicians that can configure transmission devices and align antennas. This is not usually practical for temporary networks and especially for rapid response networks where the installation time is the main concern. These difficulties are substantially lowered using the now widespread UMTS technology for data transmission. A small (but sometimes power hungry) properly configured device with an omnidirectional antenna must be added to the station assembly. All setups are usually configured before deployment and this allows for an easy installation also by untrained personnel. We describe here the implementation of a UMTS based portable seismic network for both temporary experiments and rapid response applications developed at INGV. The first field experimentation of this approach dates back to the 2009 L
Seismic response of the EBR-II to the Mt. Borah earthquake
International Nuclear Information System (INIS)
Gale, J.G.; Lehto, W.K.
1985-01-01
On October 28, 1983, an earthquake of magnitude 7.3 occurred in the mountains of central Idaho at a distance of 114-km from the ANL-West site. The earthquake tripped the seismic sensors in the EBR-II reactor shutdown system causing a reactor scram. Visual and operability checks of structures, components, and systems showed no indication of damage or system abnormalities and reactor restart was initiated. As a result of the earthquake, questions arose as to the magnitude of the actual stress levels in critical components and what value of ground acceleration could be experienced without damage to reactor structures. EBR-II was designed prior to implementation of present day requirements for seismic qualification and appropriate analyses had not been conducted. A lumped-mass, finite element model of the primary tank, support structure, and the reactor was generated and analyzed using the response spectrum technique. The analysis showed that the stress levels in the primary tank system were very low during the Mount Borah earthquake and that the system could experience seismic loadings three to four times those of the Mount Borah earthquake without exceeding yield stresses in any of the components
Hirave, Vivek; Kalyanshetti, Mahesh
2018-02-01
Conventional fixed-base analysis ignoring the effect of soil-flexibility may result in unsafe design. Therefore, to evaluate the realistic behavior of structure the soil structure interaction (SSI) effect shall be incorporated in the analysis. In seismic analysis, provision of bracing system is one of the important option for the structure to have sufficient strength with adequate stiffness to resist lateral forces. The different configuration of these bracing systems alters the response of buildings, and therefore, it is important to evaluate the most effective bracing systems in view point of stability against SSI effect. In present study, three RC building frames, G+3, G+5 and G+7 and their respective scaled down steel model with two types of steel bracing system incorporating the effect of soil flexibility is considered for experimental and analytical study. The analytical study is carried out using Elastic continuum approach and the experimental study is carried out using Shake Table. The influence of SSI on various seismic parameters is presented. The study reveals that, steel bracing system is beneficial to control SSI effect and it is observed that V bracing is more effective, in resisting seismic load considering SSI.
Analysis and evaluation of seismic response of reactor building for Daya Bay Nuclear Power Plant
International Nuclear Information System (INIS)
Li Zhongcheng; China Guangdong Nuclear Power Company, Shenzhen; Li Zhongxian
2005-01-01
Daya Bay NPP has been operating safely and stably over 10 years since 1994, and its' seismic analysis of nuclear island was in accordance with the approaches in RCC-G standard for the model M310, in which the Simplified Impedance Matrix Method (SIMM) was employed for the consideration of SSI. Thanks to the rapid progress being made in upgrading the evaluation technology and the capability of data processing systems, methods and software tools for the SSI analysis have experienced significant development all over the world. Focused on the model of reactor building of the Daya Bay NPP, in his paper the more sophisticated 3D half-space continuum impedance method based on the Green functions is used to analyze the functions of the soil, and then the seismic responses of the coupled SSI system are calculated and compared with the corresponding design values. It demonstrates that the design method provides a set of conservatively safe results. The conclusions from the study is hopefully to provide some important references to the assessment of seismic safety margin for the operating NPPs. (authors)
International Nuclear Information System (INIS)
Si, Hongjun
2014-01-01
Ground motion data on seismic bedrock is important, but it is very difficult to obtain such data directly. The data from KiK-net and JNES/SODB is valuable and very useful in developing the attenuation relationship of response spectra on seismic bedrock. NIED has approximately 200 observation points on seismic bedrock with S-wave velocity of more than 2000 m/s in Japan. Using data from observation at these points, a Ground Motion Prediction Equation (GMPE) is under development. (author)
International Nuclear Information System (INIS)
Iijima, Tadashi
2005-01-01
We applied improved capacity spectrum method (ICSM) to a piping system with an asymmetric load-deformation relationship in a piping elbow. The capacity spectrum method can predict an inelastic response by balancing the structural capacity obtained from the load-deformation relationship with the seismic demand defined by an acceleration-displacement response spectrum. The ICSM employs (1) effective damping ratio and period that are based on a statistical methodology, (2) practical procedures necessary to obtain a balance between the structural capacity and the seismic demand. The effective damping ratio and period are defined so as to maximize the probability that predicted response errors lie inside the -10 to 20% range. However, without taking asymmetry into consideration the displacement calculated by using the load-deformation relationship on the stiffer side was 39% larger than that of a time history analysis by a direct integral method. On the other hand, when asymmetry was taken into account, the calculated displacement was only 14% larger than that of a time history analysis. Thus, we verified that the ICSM could predict the inelastic response with errors lying within the -10 to 20% range, by taking into account the asymmetric load-deformation relationship of the piping system. (author)
Hosseini, Kambod Amini; Jafari, Mohammad Kazem; Hosseini, Maziar; Mansouri, Babak; Hosseinioon, Solmaz
2009-10-01
This paper presents the results of research carried out to improve emergency response activities in earthquake-prone areas of Iran. The research concentrated on emergency response operations, emergency medical care, emergency transportation, and evacuation-the most important issues after an earthquake with regard to saving the lives of victims. For each topic, some guidelines and criteria are presented for enhancing emergency response activities, based on evaluations of experience of strong earthquakes that have occurred over the past two decades in Iran, notably Manjil (1990), Bam (2003), Firouz Abad-Kojour (2004), Zarand (2005) and Broujerd (2006). These guidelines and criteria are applicable to other national contexts, especially countries with similar seismic and social conditions as Iran. The results of this study should be incorporated into comprehensive plans to ensure sustainable development or reconstruction of cities as well as to augment the efficiency of emergency response after an earthquake.
Study on vertical seismic response characteristics of deeply embedded reactor building
International Nuclear Information System (INIS)
Morishita, H.; Nakamura, N.; Uchiyama, S.; Fukuoka, A.; Ishizaki, M.
1993-01-01
This paper describes vertical response characteristics, especially effects of embedment, and analytical methods for seismic design of a deeply embedded reactor building. The influence of embedment on vertical response was found to be minimal by evaluating results of forced vibration tests of a reactor building model and performing simplified analyses. Subsequently, simulation analyses of the forced vibration test and actual earthquake induced response were performed using both the axisymmetric FEM model and the simplified mass and spring model. It was concluded that the analytical models taking the embedment into the consideration closely simulated the observation records, and the omission of embedment in the analyses tended to increase the predicted response which was conservative in respect an actual design consideration. (author)
International Nuclear Information System (INIS)
Hagiwara, Y.; Yamamoto, K.; Akiyama, H.
1993-01-01
Reactor vessels of FBR are cylindrical shell structures, whose critical failure mode during earthquakes is plastic buckling in shear or bending mode. In buckling prevention of the vessels, it is of primary importance to realistically evaluate the plastic response reduction effect in the pre-buckling stage. Though the authors have already proposed a empirical formula to estimate the response reduction effect, the formula depends only on the pre-buckling ductility factor in the evaluation for the purpose of easy design practice. In this study, the effect of seismic motion characteristics on the response reduction effect was investigated both experimentally and numerically, and a improved version of the empirical expression of the reduction factor was proposed. In this new method, the response reduction effect is evaluated by an initial acceleration amplification factor in addition to the ductility of structures. (author)
Mozco, P.; Rovelli, A.; Labak, P.; Malagnini, L.
1995-01-01
The seismic response of the geologic structure beneath the Colosseum is investigated using a two-dimensional modeling for a vertically incident plane SH wave. Computations indicate that the southern part of the Colosseum may be exposed to a seismic ground motion with significantly larger amplitudes, differential motion and longer duration than the northern part. because the southern part of the Colosseum is underlain by a sedimentfilled valley created by sedimentary filling of the former trib...
Effect of frequency and flexibility ratio on the seismic response of deep tunnels
Directory of Open Access Journals (Sweden)
Eimar Sandoval
2017-06-01
Full Text Available Two-dimensional dynamic numerical analyses have been conducted, using FLAC 7.0, to evaluate the seismic response of underground structures located far from the seismic source, placed in either linear-elastic or nonlinear elastoplastic ground. The interaction between the ground and deep circular tunnels with a tied interface is considered. For the simulations, it is assumed that the liner remains in its elastic regime, and plane strain conditions apply to any cross section perpendicular to the tunnel axis. An elastoplastic constitutive model is implemented in FLAC to simulate the nonlinear ground. The effect of input frequency and relative stiffness between the liner and the ground, on the seismic response of tunnels, is evaluated. The response is studied in terms of distortions normalized with respect to those of the free field, and load demand (axial forces and bending moments in the liner. In all cases, i.e. for linear-elastic and nonlinear ground models, the results show negligible effect of the input frequency on the distortions of the cross section, for input frequencies smaller than 5 Hz; that is for ratios between the wave length and the tunnel opening (λ/D larger than ten for linear-elastic and nine for nonlinear ground. Larger normalized distortions are obtained for the nonlinear than for the linear-elastic ground, for the same relative stiffness, with differences increasing as the tunnel becomes more flexible, or when the amplitude of the dynamic input shear stress increases. It has been found that normalized distortions for the nonlinear ground do not follow a unique relationship, as it happens for the linear-elastic ground, but increase as the amplitude of the dynamic input increases. The loading in the liner decreases as the structure becomes more flexible with respect to the ground, and is smaller for a tunnel placed in a stiffer nonlinear ground than in a softer nonlinear ground, for the same flexibility ratio.
Development of Cold-Formed Steel Seismic Design Recommendations
2015-08-01
top beam attached to the hydraulic ram. This tube is far more flexible in bending than the beam/floor slab in the field, and therefore will not... torsional and out-of-plane response should not be significant, and the rocking response can be accounted for in refined Drain 2DX analysis when...209 11.9.3 Vertical distribution of lateral seismic forces ........................................................ 210 11.9.4 Torsion
Seismic stress of plants and equipment in nuclear power station construction
International Nuclear Information System (INIS)
Hampe, E.; Schwarz, J.
1984-01-01
The applicability of floor spectra for designing components of nuclear power plants taking into account seismic effects is discussed. Methods for the determination of seismic floor excitation and various kinds of floor spectra are presented. As an example the floor spectra method is applied to containment buildings
Seismic qualification for water chillers of nuclear power plant
International Nuclear Information System (INIS)
Wang Chunming
2005-01-01
Water chillers are important components of the electric building chilled water system of Nuclear Power Plant. In this article, we describe the seismic qualification methodology. A united method of seismic analysis and experiment testing were applied. Since the seismic classification of the evaporator, condenser and oil separator is 1F, the chillers must satisfy the function criteria. The functional and performance of the control panel were qualified by seismic test. In order to get the seismic time histories of the base of the motor, compressor and control panel, we did time histories analysis for the whole chillers using the seismic acceleration time history of the building floor on which the water chillers was located. Then, these curves were translated into required response spectrum (RRS), which were used by the seismic test of water chillers compressor sets. All passive components, such as evaporator, condenser, oil separator and support, were qualified by seismic stress analysis method. These components were verified to satisfy the standard when they were subjected to the seismic, gravitational, operational pressure and nozzle loads. The Chillers' components were qualified to the specification and the standard. The motor-compressor set and control panel were qualified to the functional and performance criteria. The applied of this methodology qualified the function of the water chillers compressor sets effectively, especially after the aging test. (author)
Poggi, V.; Burjanek, J.; Michel, C.; Fäh, D.
2017-08-01
The Swiss Seismological Service (SED) has recently finalised the installation of ten new seismological broadband stations in northern Switzerland. The project was led in cooperation with the National Cooperative for the Disposal of Radioactive Waste (Nagra) and Swissnuclear to monitor micro seismicity at potential locations of nuclear-waste repositories. To further improve the quality and usability of the seismic recordings, an extensive characterization of the sites surrounding the installation area was performed following a standardised investigation protocol. State-of-the-art geophysical techniques have been used, including advanced active and passive seismic methods. The results of all analyses converged to the definition of a set of best-representative 1-D velocity profiles for each site, which are the input for the computation of engineering soil proxies (traveltime averaged velocity and quarter-wavelength parameters) and numerical amplification models. Computed site response is then validated through comparison with empirical site amplification, which is currently available for any station connected to the Swiss seismic networks. With the goal of a high-sensitivity network, most of the NAGRA stations have been installed on stiff-soil sites of rather high seismic velocity. Seismic characterization of such sites has always been considered challenging, due to lack of relevant velocity contrast and the large wavelengths required to investigate the frequency range of engineering interest. We describe how ambient vibration techniques can successfully be applied in these particular conditions, providing practical recommendations for best practice in seismic site characterization of high-velocity sites.
International Nuclear Information System (INIS)
Surh, Han-Bum; Ryu, Tae-Young; Park, Jin-Sung; Ahn, Eun-Woo; Choi, Chul-Sun; Koo, Ja Choon; Choi, Jae-Boong; Kim, Moon Ki
2015-01-01
Highlights: • Piping system in the APR 1400 NPP with a base isolation design is studied. • Seismic response of piping system in base isolated building are investigated. • Stress classification method is examined for piping subjected to seismic loading. • Primary stress of piping is reduced due to base isolation design. • Substantial secondary stress is observed in the main steam piping. - Abstract: In this study, the stress response of the piping system in the advanced power reactor 1400 (APR 1400) with a base isolation design subjected to seismic loading is addressed. The piping system located between the auxiliary building with base isolation and the turbine building with a fixed base is considered since it can be subjected to substantial relative support movement during seismic events. First, the support responses with respect to the base characteristic are investigated to perform seismic analysis for multiple support excitations. Finite element analyses are performed to predict the piping stress response through various analysis methods such as the response spectrum, seismic support movement and time history method. To separately evaluate the inertial effect and support movement effect on the piping stress, the stress is decomposed into a primary and secondary stress using the proposed method. Finally, influences of the base isolation design on the piping system in the APR 1400 are addressed. The primary stress based on the inertial loading is effectively reduced in a base isolation design, whereas a considerable amount of secondary stress is generated in the piping system connecting a base isolated building with a fixed base building. It is also confirmed that both the response spectrum analysis and seismic support movement analysis provide more conservative estimations of the piping stress compared to the time history analysis
Response of a NPP reactor building under seismic action with regard to different soil properties
International Nuclear Information System (INIS)
Wagenknecht, E.
1987-01-01
The object of this investigation is the response of a reactor building on seismic action with systematic variation of the soil stiffness. A thin-walled orthotropic containment shell on varying heavy and rigid foundations is regarded as calculation model. The soil stiffness is simulated by meand of spring elements for horizontal translation and for rocking motions of the building. By the response spectra method the loads of the containment shell are calculated for a horizontal seismic excitation. The investigation is aimed at determining the influence of differentiated soil stiffnesses on the containment action effects and at recognizing the causes for the occuring effects. The results are thoroughly represented by selected quantities of the building's response, the effects from the soil-structure interaction are discussed and the causes of the effects cleary explained. Apossibility is provided for determining critical soil stiffnesses which cause a siginificat intensification effect. The results of the investigations show that both the soil stiffness and structural configuration of the reactor building particulary in case of the substructure being heavy and rigid, exert a decisive on the loading of the superstructure. (orig.)
Magnani, M. B.
2017-12-01
Alluvial rivers, even great rivers such as the Mississippi, respond to hydrologic and geologic controls. Temporal variations of valley gradient can significantly alter channel morphology, as the river responds syntectonically to attain equilibrium. The river will alter its sinuosity, in an attempt to maintain a constant gradient on a surface that changes slope through time. Therefore, changes of river pattern can be the first clue that active tectonics is affecting an area of pattern change. Here I present geomorphological and seismic imaging evidence of a previously unknown fault crossing the Mississippi river south of the New Madrid seismic zone, between Caruthersville, Missouri and Osceola, Arkansas, and show that both datasets support Holocene fault movement, with the latest slip occurring in the last 200 years. High resolution marine seismic reflection data acquired along the Mississippi river imaged a NW-SE striking north-dipping fault displacing the base of the Quaternary alluvium by 15 m with reverse sense of movement. The fault consistently deforms the Tertiary, Cretaceous and Paleozoic formations. Historical river channel planforms dating back to 1765 reveal that the section of the river channel across the fault has been characterized by high sinuosity and steep projected-channel slope compared to adjacent river reaches. In particular, the reach across the fault experienced a cutoff in 1821, resulting in a temporary lowering of sinuosity followed by an increase between the survey of 1880 and 1915. Under the assumption that the change in sinuosity reflects river response to a valley slope change to maintain constant gradient, I use sinuosity through time to calculate the change in valley slope since 1880 and therefore to estimate the vertical displacement of the imaged fault in the past 200 years. Based on calculations so performed, the vertical offset of the fault is estimated to be 0.4 m, accrued since at least 1880. If the base of the river alluvium
Yee, Eric
In this thesis I address a series of issues related to ground failure and ground motions during earthquakes. A major component is the evaluation of cyclic volumetric strain behavior of unsaturated soils, more commonly known as seismic compression, from advanced laboratory testing. Another major component is the application of nonlinear and equivalent linear ground response analyses to large-strain problems involving highly nonlinear dynamic soil behavior. These two components are merged in the analysis of a truly unique and crucial field case history of nonlinear site response and seismic compression. My first topic concerns dynamic soil testing for relatively small strain dynamic soil properties such as threshold strains, gammatv. Such testing is often conducted using specialized devices such as dual-specimen simple-shear, as devices configured for large strain testing produce noisy signals in the small strain range. Working with a simple shear device originally developed for large-strain testing, I extend its low-strain capabilities by characterizing noisy signals and utilizing several statistical methods to extract meaningful responses in the small strain range. I utilize linear regression of a transformed variable to estimate the cyclic shear strain from a noisy signal and the confidence interval on its amplitude. I utilize Kernel regression with the Nadaraya-Watson estimator and a Gaussian kernel to evaluate vertical strain response. A practical utilization of these techniques is illustrated by evaluating threshold shear strains for volume change with a procedure that takes into account uncertainties in the measured shear and vertical strains. My second topic concerns the seismic compression characteristics of non-plastic and low-plasticity silty sands with varying fines content (10 ≤ FC ≤ 60%). Simple shear testing was performed on various sand-fines mixtures at a range of modified Proctor relative compaction levels ( RC) and degrees-of-saturation (S
Note on nonlinear seismic response of reinforced concrete structures with low initial periods
International Nuclear Information System (INIS)
Sozen, M.A.
1985-01-01
This note was prepared to illustrate by specific examples an opinion on the seismic response of reinforced concrete structures with low initial periods. The object is to point out what the writer considers to be important in relation to the behavior of such structures at levels of ground shaking higher than indicated by design criteria. Structures of concern are assumed to have low initial periods. A structure with a low initial period is assumed to have both of two attributes: (a) its flexural stiffness is high so that its total overall lateral deformation is not dominated by flexural deformation and (b) its calculated period is below the one at which the calculated response spectrum may be idealized to change from the nearly-constant acceleration to the nearly-constant velocity response range
Seismic response of bridge pier on rigid caisson foundation in soil stratum
Tsigginos, C.; Gerolymos, N.; Assimaki, D.; Gazetas, G.
2008-03-01
An analytical method to study the seismic response of a bridge pier supported on a rigid caisson foundation embedded in a deep soil stratum underlain by a homogeneous half space is developed. The method reproduces the kinematic and inertial responses, using translational and rotational distributed Winkler springs and dashpots to simulate the soil-caisson interaction. Closed-form solutions are given in the frequency domain for vertical harmonic S-wave excitation. Comparison with results from finite element (FE) analysis and other available solutions demonstrates the reliability of the model. Results from parametric studies are given for the kinematic and inertial responses. The modification of the fundamental period and damping ratio of the bridge due to soil-structure interaction is graphically illustrated.
International Nuclear Information System (INIS)
Hasegawa, M.; Ichikawa, T.; Nakai, S.; Watanabe, T.
1987-01-01
A practical method to calculate the elasto-plastic seismic response of structures considering the dynamic soil-structure interaction is presented. The substructure technique in the time domain is utilized in the proposed method. A simple soil spring system with the coupling effects which are usually evaluated by the impedance matrix is introduced to consider the soil-structure interaction for embedded structures. As a numerical example, the response of a BWR-MARK II type reactor building embedded in the layered soil is calculated. The accuracy of the present method is verified by comparing its numerical results with exact solutions. The nonlinear behaivor and the soil-structure interaction effects on the response of the reactor building are also discussed in detail. It is concluded that the present method is effective for the aseismic design considering both the material nonlinearity of the nuclear reactor building and the dynamic soil-structure interaction. (orig.)
International Nuclear Information System (INIS)
Bhaumik, Lopamudra; Raychowdhury, Prishati
2013-01-01
Highlights: • Seismic response analysis of an internal shearwall of a reactor is done. • Incremental dynamic analysis is performed with 30 recorded ground motions. • Equivalent viscous damping increases up to twice when nonlinear SSI is considered. • Roof drift demand increases up to 25% upon consideration of foundation nonlinearity. • Base shear, base moment and ductility reduce up to 62%, 40%, and 35%, respectively. - Abstract: This study focuses on the seismic response analysis of an internal shearwall of a typical Indian reactor resting on a medium dense sandy silty soil, incorporating the nonlinear behavior of the soil-foundation interface. The modeling is done in an open-source finite element framework, OpenSees, where the soil-structure interaction (SSI) is modeled using a Beam-on-Nonlinear-Winkler-Foundation (BNWF) approach. Static pushover analysis and cyclic analysis are performed followed by an incremental dynamic analysis (IDA) with 30 recorded ground motions. For performing IDA, the spectral acceleration of each motion corresponding to the fundamental period, S a (T 1 )is incremented from 0.1 g to 1.0 g with an increment step of 0.1 g. It is observed from the cyclic analysis that the equivalent viscous damping of the system increases upto twice upon incorporation of inelastic SSI. The IDA results demonstrate that the average peak base shear, base moment and displacement ductility demand reduces as much as 62%, 40%, and 35%, respectively, whereas the roof drift demand increases up to 25% upon consideration of foundation nonlinearity for the highest intensity motion. These observations indicate the need of critical consideration of nonlinear soil-structure interaction as any deficient modeling of the same may lead to an inaccurate estimation of the seismic demands of the structure
Energy Technology Data Exchange (ETDEWEB)
Bhaumik, Lopamudra, E-mail: lbhaumi2@illinois.edu [University of Illinois at Urbana-Champaign (United States); Raychowdhury, Prishati, E-mail: prishati@iitk.ac.in [Indian Institute of Technology Kanpur (India)
2013-12-15
Highlights: • Seismic response analysis of an internal shearwall of a reactor is done. • Incremental dynamic analysis is performed with 30 recorded ground motions. • Equivalent viscous damping increases up to twice when nonlinear SSI is considered. • Roof drift demand increases up to 25% upon consideration of foundation nonlinearity. • Base shear, base moment and ductility reduce up to 62%, 40%, and 35%, respectively. - Abstract: This study focuses on the seismic response analysis of an internal shearwall of a typical Indian reactor resting on a medium dense sandy silty soil, incorporating the nonlinear behavior of the soil-foundation interface. The modeling is done in an open-source finite element framework, OpenSees, where the soil-structure interaction (SSI) is modeled using a Beam-on-Nonlinear-Winkler-Foundation (BNWF) approach. Static pushover analysis and cyclic analysis are performed followed by an incremental dynamic analysis (IDA) with 30 recorded ground motions. For performing IDA, the spectral acceleration of each motion corresponding to the fundamental period, S{sub a}(T{sub 1})is incremented from 0.1 g to 1.0 g with an increment step of 0.1 g. It is observed from the cyclic analysis that the equivalent viscous damping of the system increases upto twice upon incorporation of inelastic SSI. The IDA results demonstrate that the average peak base shear, base moment and displacement ductility demand reduces as much as 62%, 40%, and 35%, respectively, whereas the roof drift demand increases up to 25% upon consideration of foundation nonlinearity for the highest intensity motion. These observations indicate the need of critical consideration of nonlinear soil-structure interaction as any deficient modeling of the same may lead to an inaccurate estimation of the seismic demands of the structure.
Unresolved Safety Issue A-46 - seismic qualification of equipment in operating plants
International Nuclear Information System (INIS)
Anderson, N.
1985-01-01
Seismic Qualification of Equipment in Operating Plants was designated as an Unresolved Safety Issue (USI) in December, 1980. The USI A-46 program was developed in early 1981 to investigate the adequacy of mechanical and electrical equipment in operating plants to withstand a safe shutdown earthquake. The approach taken was to develop viable, cost effective alternatives to current seismic qualification licensing requirements which could be applied to operating nuclear power plants. The tasks investigated include: (1) identification of seismic sensitive systems and equipment; (2) assessment of adequacy of existing seismic qualification methods; (3) development and assessment of in-situ test procedures to assist in qualification of equipment; (4) seismic qualification of equipment using seismic experience data; and (5) development of methods to generate generic floor response spectra. Progress to date and plans for completion of resolution are reported
Seismic response prediction for cabinets of nuclear power plants by using impact hammer test
Energy Technology Data Exchange (ETDEWEB)
Koo, Ki Young [Department of Civil and Structural Engineering, University of Sheffield, Sheffield (United Kingdom); Gook Cho, Sung [JACE KOREA, Gyeonggi-do (Korea, Republic of); Cui, Jintao [Department of Civil Engineering, Kunsan National University, Jeonbuk (Korea, Republic of); Kim, Dookie, E-mail: kim2kie@kunsan.ac.k [Department of Civil Engineering, Kunsan National University, Jeonbuk (Korea, Republic of)
2010-10-15
An effective method to predict the seismic response of electrical cabinets of nuclear power plants is developed. This method consists of three steps: (1) identification of the earthquake-equivalent force based on the idealized lumped-mass system of the cabinet, (2) identification of the state-space equation (SSE) model of the system using input-output measurements from impact hammer tests, and (3) seismic response prediction by calculating the output of the identified SSE model under the identified earthquake-equivalent force. A three-dimensional plate model of cabinet structures is presented for the numerical verification of the proposed method. Experimental validation of the proposed method is carried out on a three-story frame which represents the structure of a cabinet. The SSE model of the frame is accurately identified by impact hammer tests with high fitness values over 85% of the actual frame characteristics. Shaking table tests are performed using El Centro, Kobe, and Northridge earthquakes as input motions and the acceleration responses are measured. The responses of the model under the three earthquakes are predicted and then compared with the measured responses. The predicted and measured responses agree well with each other with fitness values of 65-75%. The proposed method is more advantageous over other methods that are based on finite element (FE) model updating since it is free from FE modeling errors. It will be especially effective for cabinet structures in nuclear power plants where conducting shaking table tests may not be feasible. Limitations of the proposed method are also discussed.
Sea floor magnetic observatory
Korepanov, V.; Prystai, A.; Vallianatos, F.; Makris, J.
2003-04-01
The electromagnetic precursors of seismic hazards are widely accepted as strong evidence of the approaching earthquake or volcano eruption. The monitoring of these precursors are of main interest in densely populated areas, what creates serious problems to extract them at the strong industrial noise background. An interesting possibility to improve signal-to-noise ratio gives the installation of the observation points in the shelf zones near the possible earthquake places, what is fairly possible in most seismically active areas in Europe, e. g. in Greece and Italy. The serious restriction for this is the cost of the underwater instrumentation. To realize such experiments it requires the unification of efforts of several countries (e. g., GEOSTAR) or of the funds of some great companies (e. g., SIO magnetotelluric instrument). The progress in electronic components development as well as the appearance of inexpensive watertight glass spheres made it possible to decrease drastically the price of recently developed sea floor magnetic stations. The autonomous vector magnetometer LEMI-301 for sea bed application is described in the report. It is produced on the base of three-component flux-gate sensor. Non-magnetic housing and minimal magnetism of electronic components enable the instrument to be implemented as a monoblock construction where the electronic unit is placed close to the sensor. Automatic circuit provides convenient compensation of the initial field offset and readings of full value (6 digits) of the measured field. Timing by internal clock provides high accuracy synchronization of data. The internal flash memory assures long-term autonomous data storage. The system also has two-axes tilt measurement system. The methodological questions of magnetometer operation at sea bed were studied in order to avoid two types of errors appearing at such experimental cases. First is sea waving influence and second one magnetometer orientation at its random positioning on
Directory of Open Access Journals (Sweden)
Guo-Bo Wang
2017-01-01
Full Text Available The foundation might be separated from the supporting soil if the earthquake is big enough, which is known as base mat uplift. This paper proposed a simplified calculation model in which spring element is adopted to simulate the interaction between soil and structure. The load-deformation curve (F-D curve of the spring element can be designated to represent the base mat uplift, in which the pressure can be applied while tensile forces are not allowed. Key factors, such as seismic wave types, seismic wave excitation directions, seismic wave amplitudes, soil shear velocities, structure stiffness, and the ratio of structure height to width (H/B, were considered in the analysis. It is shown that (1 seismic wave type has significant influence on structure response due to different frequency components it contained; (2 the vertical input of seismic wave greatly affected structure response in vertical direction, while it has little impacts in horizontal direction; (3 base mat uplift is easier to take place in soil with higher shear velocity; (4 structure H/B value has complicated influence on base mat uplift. The outcome of this research is assumed to provide some references for the seismic design of the structure due to base mat uplift.
Jovanović Goran
2007-01-01
The paper presents the application of the principle of flexibility of architectonic space on the concrete example of flat composition. This example demonstrates that with a proper choice of structural spans dimensions and regular arrangement of sanitary and ventilation vertical assemblies, a structure with high flexibility in terms of flat space organization and floor space organization, can be achieved.
A report on upgraded seismic monitoring stations in Myanmar: Station performance and site response
Thiam, Hrin Nei; Min Htwe, Yin Myo; Kyaw, Tun Lin; Tun, Pa Pa; Min, Zaw; Htwe, Sun Hninn; Aung, Tin Myo; Lin, Kyaw Kyaw; Aung, Myat Min; De Cristofaro, Jason; Franke, Mathias; Radman, Stefan; Lepiten, Elouie; Wolin, Emily; Hough, Susan E.
2017-01-01
Myanmar is in a tectonically complex region between the eastern edge of the Himalayan collision zone and the northern end of the Sunda megathrust. Until recently, earthquake monitoring and research efforts have been hampered by a lack of modern instrumentation and communication infrastructure. In January 2016, a major upgrade of the Myanmar National Seismic Network (MNSN; network code MM) was undertaken to improve earthquake monitoring capability. We installed five permanent broadband and strong‐motion seismic stations and real‐time data telemetry using newly improved cellular networks. Data are telemetered to the MNSN hub in Nay Pyi Taw and archived at the Incorporated Research Institutions for Seismology Data Management Center. We analyzed station noise characteristics and site response using noise and events recorded over the first six months of station operation. Background noise characteristics vary across the array, but indicate that the new stations are performing well. MM stations recorded more than 20 earthquakes of M≥4.5 within Myanmar and its immediate surroundings, including an M 6.8 earthquake located northwest of Mandalay on 13 April 2016 and the Mw 6.8 Chauk event on 24 August 2016. We use this new dataset to calculate horizontal‐to‐vertical spectral ratios, which provide a preliminary characterization of site response of the upgraded MM stations.
Seismic Response of a Half-Scale Masonry Building with Flexible Diaphragms
National Research Council Canada - National Science Library
Sweeney, Steven C; Horney, Matthew A; Orton, Sarah L
2005-01-01
Unreinforced masonry (URM) buildings constructed on Army installations before the development of modern seismic codes may be susceptible to earthquake damage and therefore could benefit from seismic mitigation measures...
Seismicity rate surge on faults after shut-in: poroelastic response to fluid injection
Chang, K. W.; Yoon, H.; Martinez, M. J.
2017-12-01
Subsurface energy activities such as geological CO2 storage and wastewater injection require injecting large amounts of fluid into the subsurface, which will alter the states of pore pressure and stress in the storage formation. One of the main issues for injection-induced seismicity is the post shut-in increases in the seismicity rate, often observed in the fluid-injection operation sites. The rate surge can be driven by the following mechanisms: (1) pore-pressure propagation into distant faults after shut-in and (2) poroelastic stressing caused by well operations, depending on fault geometry, hydraulic and mechanical properties of the formation, and injection history. We simulate the aerial view of the target reservoir intersected by strike-slip faults, in which injection-induced pressure buildup encounters the faults directly. We examine the poroelastic response of the faults to fluid injection and perform a series of sensitivity tests considering: (1) permeability of the fault zone, (2) locations and the number of faults with respect to the injection point, and (3) well operations with varying the injection rate. Our analysis of the Coulomb stress change suggests that the sealing fault confines pressure diffusion which stabilizes or weakens the nearby conductive fault depending on the injection location. We perform the sensitivity test by changing injection scenarios (time-dependent rates), while keeping the total amount of injected fluids. Sensitivity analysis shows that gradual reduction of the injection rate minimizes the Coulomb stress change and the least seismicity rates are predicted. Sandia National Laboratories is a multimission laboratory managed and operated by National Technology and Engineering Solutions of Sandia, LLC., a wholly owned subsidiary of Honeywell International, Inc., for the U.S. Department of Energy's National Nuclear Security Administration under contract DE-NA-0003525.
International Nuclear Information System (INIS)
Morrone, A.
1979-01-01
A particular type of seismic analysis performed on the Nuclear Island Buildings (NIB) complex of a nuclear power plant and the methods developed to combine torsional, rotational and translational responses are described. The NIB complex analyzed consists of various buildings supported on a common foundation mat and tied together from the underground foundation to the roof levels. Three independent building mathematical models were used for the three components of the earthquake with a lumped-mass method utilizing direct integration of the coupled equations of motion. The input ground acceleration time histories were based on three 20 s long statistically independent records whose normalized response spectra enveloped those of Regulatory Guide 1.60. A linear stochastic model was used to generate these records which simulated strong motion earthquakes. Due to site characteristics, the soil material properties were calculated considering different ranges of soil moduli below and above the foundation. (orig.)
International Nuclear Information System (INIS)
Morrone, A.; Sigal, G.B.
1979-01-01
A particular type of seismic analysis performed on the Nuclear Island Buildings (NIB) complex of a nuclear power plant and the methods developed to combine torsional, rotational and translational responses are described. The NIB complex analyzed consists of various buildings supported on a common foundation mat and tied together from the underground foundation to the roof levels. Three independent building mathematical models were used for the three components of the earthquake with a lumped-mass method utilizing direct integration of the coupled equations of motion. The input ground acceleration time histories were based on three 20 s long statistically independent records whose mormalized response spectra enveloped those of Regulatory Guide 1.60. A linear stochastic model was used to generate these records which simulated strong motion earthquakes. Due to site characteristics, the soil material properties were calculated considering different ranges of soil moduli below and above the foundation
Effects of support masses on seismic response of piping and supports
International Nuclear Information System (INIS)
Iotti, R.C.; Dinkevich, S.
1985-01-01
A special methodology is presented for quantitatively predicting when the effect of piping restraint masses is significant and should be explicitly considered in piping seismic analyses which use the response spectrum method. It is concluded that the effect of support mass in the unrestrained direction is to increase piping and support responses by a percentage no larger than twice the ratio of the support to the pipe-supported span mass. In the restrained direction the mass of the support significantly reduces its dynamic stiffness so that for low support stiffnesses and relatively large mass the support can act as an amplifier of vibration. The dynamic effect, however, is negligible for very stiff supports. (orig.)
International Nuclear Information System (INIS)
Hasegawa, M.; Nakai, S.; Watanabe, T.
1985-01-01
A practical method for elasto-plastic seismic response analysis is described under considerations of nonlinear material law of a structure and dynamic soil-structure interaction. The method is essentially based on the substructure approach of time domain analysis. Verification of the present method is carried out for typical BWR-MARK II type reactor building which is embedded in a soil, and the results are compared with those of the frequency response analysis which gives good accuracy for linear system. As a result, the present method exhibits sufficient accuracy. Furthermore, elasto-plastic analyses considering the soil-structure interaction are made as an application of the present method, and nonlinear behaviors of the structure and embedment effects are discussed. (orig.)
An experimental scale-model study of seismic response of an underground opening in jointed rock mass
International Nuclear Information System (INIS)
Kana, D.D.; Fox, D.J.; Hsiung, S.; Chowdhury, A.H.
1997-02-01
This report describes an experimental investigation conducted by the Center for Nuclear Waste Regulatory Analyses (CNWRA) to (i) obtain a better understanding of the seismic response of an underground opening in a highly-fractured and jointed rock mass and (ii) generate a data set that can be used to evaluate the capabilities (analytical methods) to calculate such response. This report describes the design and implementation of simulated seismic experiments and results for a 1/15 scale model of a jointed rock mass with a circular tunnel in the middle. The discussion on the design of the scale model includes a description of the associated similitude theory, physical design rationale, model material development, preliminary analytical evaluation, instrumentation design and calibration, and model assembly and pretest procedures. The thrust of this discussion is intended to provide the information necessary to understand the experimental setup and to provide the background necessary to understand the experimental results. The discussion on the experimental procedures and results includes the seismic input test procedures, test runs, and measured excitation and response time histories. The closure of the tunnel due to various levels of seismic activity is presented. A threshold level of seismic input amplitude was required before significant rock mass motion occurred. The experiment, though designed as a two-dimensional representation of a rock mass, behaved in a somewhat three-dimensional manner, which will have an effect on subsequent analytical model comparison
Seismic responses of N-Reactor core. Independent review of Phase II work
International Nuclear Information System (INIS)
Chen, J.C.; Lo, T.; Chinn, D.J.; Murray, R.C.; Johnson, J.J.; Maslenikov, O.R.
1985-08-01
Seismic response of the N-Reactor core was independently analyzed to validate the results of Impell's analysis. The analysis procedure consists of two major stages: linear soil-structure interaction (SSI) analysis of the overall N-Reactor structure complex and nonlinear dynamic analysis of the reactor core. In the SSI analysis, CLASSI computer codes were used to calculate the SSI response of the structures and to generate the input motions for the nonlinear reactor core analysis. In addition, the response was compared to the response from the SASSI analysis under review. The impact of foundation modeling techniques and the effect of soil stiffness variation on SSI response were also investigated. In the core analysis, a nonlinear dynamic analysis model was developed. The stiffness representation of the model was calculated through a finite element analysis of several local core geometries. Finite element analyses were also used to study the block to block interaction characteristics. Using this nonlinear dynamic model along with the basemat time histories generated from CLASSI and SASSI, several dynamic analyses of the core were performed. A series of sensitivity studies was performed to investigate the discretization of the core, the effect of vertical acceleration, the effect of basemat rocking, and modeling assumptions. In general, our independent analysis of core response validates the order of magnitude of the displacement calculated by Impell. 11 refs., 110 figs., 12 tabs
Non-linear Response to a Type of Seismic Input Motion. Additional Information
International Nuclear Information System (INIS)
2011-06-01
This publication reports the results and findings of a coordinated research project on the safety significance of near-field earthquakes in the design of nuclear power plants. It describes the outcome of a benchmark exercise conducted by a number of institutions on the effects of low to moderate magnitude near-field earthquakes, comparing model analytical simulations with the results of a shaking test performed in France on a physical model of a conventional shear-wall structure. The results build the basis for proposals for possible evolution of engineering practices in order to realistically take into account the effects of near-field earthquakes. A CD is attached that contains the List of participants; Summary of the Research Coordination Meetings; Description of the Camus data; Description of the Japanese input motions: near-field earthquakes observed recently in Japan; Description of the output requested of the IAEA CRP participants; Summary of the participants' modelling; Results of Benchmark Step 1, 2 and 3; Scientific background on classification of seismic loads as primary or secondary; and Japanese practice on nonlinear seismic response analysis of safety related important structures.
International Nuclear Information System (INIS)
Basu, Prabir C.; Roshan, A.D.
2007-01-01
A number of shake table tests had been conducted on the scaled down model of a concrete wall as part of CAMUS experiment. The experiments were conducted between 1996 and 1998 in the CEA facilities in Saclay, France. Benchmarking of CAMUS experiments was undertaken as a part of the coordinated research program on 'Safety Significance of Near-Field Earthquakes' organised by International Atomic Energy Agency (IAEA). Technique of deflection-based method was adopted for benchmarking exercise. Non-linear static procedure of deflection-based method has two basic steps: pushover analysis, and determination of target displacement or performance point. Pushover analysis is an analytical procedure to assess the capacity to withstand seismic loading effect that a structural system can offer considering the redundancies and inelastic deformation. Outcome of a pushover analysis is the plot of force-displacement (base shear-top/roof displacement) curve of the structure. This is obtained by step-by-step non-linear static analysis of the structure with increasing value of load. The second step is to determine target displacement, which is also known as performance point. The target displacement is the likely maximum displacement of the structure due to a specified seismic input motion. Established procedures, FEMA-273 and ATC-40, are available to determine this maximum deflection. The responses of CAMUS test specimen are determined by deflection-based method and analytically calculated values compare well with the test results
Effect of Ground Motion Characteristics on the Seismic Response of a Monumental Concrete Arch Bridge
Caglayan, B. Ozden; Ozakgul, Kadir; Tezer, Ovunc
2008-07-01
Railway network in Turkey dates back to more than a hundred years ago and according to official records, there are approximately 18,000 railway bridges with spans varying between 50 cm up to 150 meters. One of them is a monumental concrete arch bridge with a total length of 210 meters having three major spans of 30 meters and a height of 65 meters, located in an earthquake-prone region in southern part of the country. Three-dimensional finite element model of the bridge was generated using a commercially available general finite element analysis software and based on the outcomes of a series of in-depth acceleration measurements that were conducted on-site, the model was refined. Types of ground motion records were used to investigate the seismic response and vulnerability of this massive structure in order to provide information regarding (i) damage-susceptible regions of the structure for monitoring purposes, and, (ii) seismic loads to be taken into account during evaluation and possible strengthening phases for this type of structures.
Effect of Ground Motion Characteristics on the Seismic Response of a Monumental Concrete Arch Bridge
International Nuclear Information System (INIS)
Caglayan, B. Ozden; Ozakgul, Kadir; Tezer, Ovunc
2008-01-01
Railway network in Turkey dates back to more than a hundred years ago and according to official records, there are approximately 18,000 railway bridges with spans varying between 50 cm up to 150 meters. One of them is a monumental concrete arch bridge with a total length of 210 meters having three major spans of 30 meters and a height of 65 meters, located in an earthquake-prone region in southern part of the country. Three-dimensional finite element model of the bridge was generated using a commercially available general finite element analysis software and based on the outcomes of a series of in-depth acceleration measurements that were conducted on-site, the model was refined. Types of ground motion records were used to investigate the seismic response and vulnerability of this massive structure in order to provide information regarding (i) damage-susceptible regions of the structure for monitoring purposes, and, (ii) seismic loads to be taken into account during evaluation and possible strengthening phases for this type of structures
Non-linear Response to a Type of Seismic Input Motion
International Nuclear Information System (INIS)
2011-06-01
This publication reports the results and findings of a coordinated research project on the safety significance of near-field earthquakes in the design of nuclear power plants. It describes the outcome of a benchmark exercise conducted by a number of institutions on the effects of low to moderate magnitude near-field earthquakes, comparing model analytical simulations with the results of a shaking test performed in France on a physical model of a conventional shear-wall structure. The results build the basis for proposals for possible evolution of engineering practices in order to realistically take into account the effects of near-field earthquakes. A CD is attached that contains the List of participants; Summary of the Research Coordination Meetings; Description of the CAMUS data; Description of the Japanese input motions: near-field earthquakes observed recently in Japan; Description of the output requested of the IAEA CRP participants; Summary of the participants' modelling; Results of Benchmark Step 1, 2 and 3; Scientific background on classification of seismic loads as primary or secondary; and Japanese practice on nonlinear seismic response analysis of safety related important structures.
Simulation of Seismic Response of Reinforced Concrete Beam-Column Joints with Nurbs Surface Fitting
Directory of Open Access Journals (Sweden)
Mirhosseini R. Tabatabaei
2017-09-01
Full Text Available This paper presents an approach based on NURBS (non-uniform rational B-splines to achieve a seismic response surface (SRS from a group of points obtained by using an analytical model of RC joints. NURBS based on the genetic algorithm is an important mathematical tool and consists of generalizations of Bezier curves and surfaces and B-splines. Generally, the accuracy of the design process of joints depends on the number of control points that are captured in the results of experimental research on real specimens. The values obtained from the specimens are the best tools to use in seismic analysis, though more expensive when compared to values simulated by SRSs. The SRS proposed in this paper can be applied to obtain surfaces that show site effect results on destructions of beam-column joint, taking into account different site conditions for a specific earthquake. The efficiency of this approach is demonstrated by the retrieval of simulated-versus-analytical results.
A comparison of experimental and theoretical investigations of embedment effects on seismic response
International Nuclear Information System (INIS)
Hadjian, A.H.; Howard, G.E.; Smith, C.B.
1975-01-01
A research program has been conducted to both gain insight into the effects of embedment on the seismic response of nuclear power plant containment structures and to verify current analytical methods for the prediction of their seismic response. Tests were first performed on small wooden cylinders, rectangles, and cubes using a shake table to conduct parametric studies in the effects of geometry, height to diameter ratio, and amount of embedment. The effects of the shake table were isolated by repeating the tests on specimens buried in actual soils. Next, a larger-scale concrete model (height - 2 meters, weight - 1700 kg) was fabricated and tested at varying embedments using an eccentric mass structural vibrator. Additionally, an attempt was made to correlate the experimental results with simplified and finite element models that included both embedment and nonlinear effects. The embedment effects in the simplified model were taken as an increase of the impedance coefficients used for structures on the ground. Nonlinear effects were incorporated by calculating strain levels and using published data to adjust the site soil parameters. The results reported are applicable to cases where the foundation materials under and around the structure are similar. It was found that when very law strains (10 -5 -10 -3 %) were applied, the embedment effect was progressively more important as the depth-to-diameter ratio increased. However, with layer strain (10 -2 -10 -1 %) where the response of the cylinder was in the range of 0.75 to 1.25 g's, the effect of embedment was negligible up to a depth-to-diameter ratio of 0.5. This phenomenon can be explained by the plastic deformation of the surrounding soil and loss of effective contact with the cylinder
International Nuclear Information System (INIS)
Juhasova, E.
1999-01-01
The work described in this report was devoted to investigation of expected seismic response of the structures of WWER-440/213 type NPPs, namely Mochovce and Bohunice. Special attention was devoted to the properties of subsoil materials and the transfer of seismic waves from the bedrock to the foundation structures. Theoretical background was elaborated and discussed for wave propagation of surface waves. Alternative procedure was derived for non-linear media accounting for complex modulus theory. Material characteristics of subsoils were investigated for both NPPs. The obtained results were used as a basis for forecasting and calculation of expected seismic response when the time history records from Paks explosion were used an input. It was pointed out that the used procedure, together with previous calculation of subsoil transfer characteristics completed well the comparison with experimental results
Response Analysis of an RC Cooling Tower Under Seismic and Windstorm Effects
Directory of Open Access Journals (Sweden)
D. Makovička
2006-01-01
Full Text Available The paper compares the RC structure of a cooling tower unit under seismic loads and under strong wind loads. The calculated values of the envelopes of the displacements and the internal forces due to seismic loading states are compared with the envelopes of the loading states due to the dead, operational and live loads, wind and temperature actions. The seismic effect takes into account the seismic area of ground motion 0.3 g and the ductility properties of a relatively rigid structure. The ductility is assessed as the reduction in seismic load. In this case the actions of wind pressure are higher than the seismicity effect under ductility correction. The seismic effects, taking into account the ductility properties of the structure, are lower than the actions of the wind pressure. The other static loads, especially temperature action due to the environment and surface insulation are very important for the design of the structure.
Seismic upgrading of the Brookhaven High Flux Beam Research Reactor
International Nuclear Information System (INIS)
Subudhi, M.
1985-01-01
In recent years the High Flux Beam Research (HFBR) reactor facility at Brookhaven National Laboratory (BNL) was upgraded from 40 to 50 MW power level. The reactor plant was built in the early sixties to the seismic design requirements of the period, using the static load approach. While the plant power level was upgraded, the seismic design was also improved according to current design criteria. This included the development of new floor response spectra for the facility and an overall seismic analysis of those systems important to the safe shutdown of the reactor. Items included in the reanalysis are the containment building with its internal structure, the piping systems, tanks, equipment, and heat exchangers. This paper describes the procedure utilized in developing the floor response spectra for the existing facility. Also included in the paper are the findings and recommendations, based on the seismic analysis, regarding the seismic adequacy of structural and mechanical systems vital to achieving the safe shutdown of the reactor. 11 references, 4 figures, 1 table
Directory of Open Access Journals (Sweden)
Mosbeh R. Kaloop
2017-01-01
Full Text Available Modeling response of structures under seismic loads is an important factor in Civil Engineering as it crucially affects the design and management of structures, especially for the high-risk areas. In this study, novel applications of advanced soft computing techniques are utilized for predicting the behavior of centrically braced frame (CBF buildings with lead-rubber bearing (LRB isolation system under ground motion effects. These techniques include least square support vector machine (LSSVM, wavelet neural networks (WNN, and adaptive neurofuzzy inference system (ANFIS along with wavelet denoising. The simulation of a 2D frame model and eight ground motions are considered in this study to evaluate the prediction models. The comparison results indicate that the least square support vector machine is superior to other techniques in estimating the behavior of smart structures.
Inelastic seismic response of precast concrete frames with constructed plastic hinges
Sucuoglu, H.
1995-07-01
A modified seismic design concept is introduced for precast concrete frames in which beam plastic hinges with reduced yield capacities are constructed away from the precast beam-column connections arranged at the column faces. Plastic hinge location and yield capacity are employed as the basic parameters of an analytical survey in which the inelastic dynamic responses of a conventional precast frame and its modified counterparts are calculated and compared under two earthquake excitations by using a general purpose computer program for dynamic analysis of inelastic frames (left bracket) 1, 2 (right bracket). An optimum design is obtained by providing plastic hinges on precast beams located at one depth away from the beam ends, in which primary (negative) bending moment yield capacities are reduced between one-third and one-quarter of the beam design end moments. With such plastic hinge configurations, precast beam-column connections at the column faces can be designed to remain elastic under strong earthquake excitations.
Improved seismic response of rc frame structures by using fluid viscous dampers
International Nuclear Information System (INIS)
Khan, Q.S.; Qazi, A.U.; Ilyas, M.
2013-01-01
In modern era passive control devices are used to improve the seismic response of structures during large magnitude earthquakes. In this research an analytical study is carried out on commercial FEM program SAP 2000 by modeling five, seven and nine storey RC frame structures. Response to four earthquake ground motions on modeled frame structures is studied and is effectively controlled by varying the characteristic properties of Fluid viscous dampers (FVD). Response in terms of frequency, displacement, velocity, acceleration, storey drift, base shear and energy dissipation is studied. Quantitatively in the modeled frames damage in terms of percentage change in global stiffness and natural frequency is determined. Qualitatively damage in terms of performance levels as per ATC-40 and FEMA-440 is considered. With an increase in Additional Stiffness Ratio of FVD corresponding increase in natural frequency and reduction in dynamic response is observed. FVDs significantly improve structural performance level of frames from Completely Damage to Immediate Occupancy/Operational Level during large magnitude earthquakes. (author)
Evaluation of high frequency ground motion effects on the seismic capacity of NPP equipments
International Nuclear Information System (INIS)
Choi, In Kil; Seo, Jeong Moon; Choun, Young Sun
2003-04-01
In this study, the uniform hazard spectrum for the example Korean nuclear power plants sites were developed and compared with various response spectra used in past seismic PRA and SMA. It shows that the high frequency ground motion effects should be considered in seismic safety evaluations. The floor response spectra were developed using the direct generation method that can develop the floor response spectra from the input response spectrum directly with only the dynamic properties of structures obtained from the design calculation. Most attachment of the equipments to the structure has a minimum distortion capacity. This makes it possible to drop the effective frequency of equipment to low frequency before it is severely damaged. The results of this study show that the high frequency ground motion effects on the floor response spectra were significant, and the effects should be considered in the SPRA and SMA for the equipments installed in a building. The high frequency ground motion effects are more important for the seismic capacity evaluation of functional failure modes. The high frequency ground motion effects on the structural failure of equipments that attached to the floor by welding can be reduced by the distortion capacity of welded anchorage
Cappa, F.; Guglielmi, Y.; De Barros, L.; Wynants-Morel, N.; Duboeuf, L.
2017-12-01
During fluid injection, the observations of an enlarging cloud of seismicity are generally explained by a direct response to the pore pressure diffusion in a permeable fractured rock. However, fluid injection can also induce large aseismic deformations which provide an alternative mechanism for triggering and driving seismicity. Despite the importance of these two mechanisms during fluid injection, there are few studies on the effects of fluid pressure on the partitioning between seismic and aseismic motions under controlled field experiments. Here, we describe in-situ meter-scale experiments measuring synchronously the fluid pressure, the fault motions and the seismicity directly in a fault zone stimulated by controlled fluid injection at 280 m depth in carbonate rocks. The experiments were conducted in a gallery of an underground laboratory in south of France (LSBB, http://lsbb.eu). Thanks to the proximal monitoring at high-frequency, our data show that the fluid overpressure mainly induces a dilatant aseismic slip (several tens of microns up to a millimeter) at the injection. A sparse seismicity (-4 laws, we simulated an experiment and investigated the relative contribution of the fluid pressure diffusion and stress transfer on the seismic and aseismic fault behavior. The model reproduces the hydromechanical data measured at injection, and show that the aseismic slip induced by fluid injection propagates outside the pressurized zone where accumulated shear stress develops, and potentially triggers seismicity. Our models also show that the permeability enhancement and friction evolution are essential to explain the fault slip behavior. Our experimental results are consistent with large-scale observations of fault motions at geothermal sites (Wei et al., 2015; Cornet, 2016), and suggest that controlled field experiments at meter-scale are important for better assessing the role of fluid pressure in natural and human-induced earthquakes.
Energy Technology Data Exchange (ETDEWEB)
Kim, Joon Kyoung [Semyung Univ., Research Institute of Industrial Science and Technol , Jecheon (Korea, Republic of)
1996-12-15
Objective of this study is to investigate and develop the methodologies and corresponding computer codes, compatible to the domestic seismological and geological environments, for estimating ground response spectrum and probabilistic seismic hazard. Using the PSHA computer program, the Cumulative Probability Functions(CPDF) and Probability Functions (PDF) of the annual exceedence have been investigated for the analysis of the uncertainty space of the annual probability at ten interested seismic hazard levels (0.1 g to 0.99 g). The cumulative provability functions and provability functions of the annual exceedence have been also compared to those results from the different input parameter spaces.
Contreras Zazueta, M. A.; Perton, M.; Sanchez-Sesma, F. J.; Sánchez-Alvaro, E.
2013-12-01
The seismic hazard assessment of extended developments, such as a dam, a bridge or a pipeline, needs the strong ground motion simulation taking into account the effects of surface geology. In many cases the incoming wave field can be obtained from attenuation relations or simulations for layered media using Discrete Wave Number (DWN). Sometimes there is a need to include in simulations the seismic source as well. A number of methods to solve these problems have been developed. Among them the Finite Element and Finite Difference Methods (FEM and FDM) are generally preferred because of the facility of use. Nevertheless, the analysis of realistic dynamic loading induced by earthquakes requires a thinner mesh of the entire domain to consider high frequencies. Consequently this may imply a high computational cost. The Indirect Boundary Element Method (IBEM) can also be employed. Here it is used to study the response of a site to historical seismic activity. This method is particularly suited to model wave propagation through wide areas as it requires only the meshing of boundaries. Moreover, it is well suited to represent finely the diffraction that can occur on a fault. However, the IBEM has been applied mainly to simple geometrical configurations. In this communication significant refinements of the formulation are presented. Using IBEM we can simulate wave propagation in complex geometrical configurations such as a stratified medium crossed by thin faults or having a complex topography. Two main developments are here described; one integrates the DWN method inside the IBEM in order to represent the Green's functions of stratified media with relatively low computational cost but assuming unbounded parallel flat layers, and the other is the extension of IBEM to deal with multi-regions in contact which allows more versatility with a higher computational cost compared to the first one but still minor to an equivalent FEM formulation. The two approaches are fully
Directory of Open Access Journals (Sweden)
E. Çelebi
2012-11-01
Full Text Available The objective of this paper focuses primarily on the numerical approach based on two-dimensional (2-D finite element method for analysis of the seismic response of infinite soil-structure interaction (SSI system. This study is performed by a series of different scenarios that involved comprehensive parametric analyses including the effects of realistic material properties of the underlying soil on the structural response quantities. Viscous artificial boundaries, simulating the process of wave transmission along the truncated interface of the semi-infinite space, are adopted in the non-linear finite element formulation in the time domain along with Newmark's integration. The slenderness ratio of the superstructure and the local soil conditions as well as the characteristics of input excitations are important parameters for the numerical simulation in this research. The mechanical behavior of the underlying soil medium considered in this prediction model is simulated by an undrained elasto-plastic Mohr-Coulomb model under plane-strain conditions. To emphasize the important findings of this type of problems to civil engineers, systematic calculations with different controlling parameters are accomplished to evaluate directly the structural response of the vibrating soil-structure system. When the underlying soil becomes stiffer, the frequency content of the seismic motion has a major role in altering the seismic response. The sudden increase of the dynamic response is more pronounced for resonance case, when the frequency content of the seismic ground motion is close to that of the SSI system. The SSI effects under different seismic inputs are different for all considered soil conditions and structural types.
Analysis of Seismic Soil-Structure Interaction for a Nuclear Power Plant (HTR-10
Directory of Open Access Journals (Sweden)
Xiaoxin Wang
2017-01-01
Full Text Available The response of nuclear power plants (NPPs to seismic events is affected by soil-structure interactions (SSI. In the present paper, a finite element (FE model with transmitting boundaries is used to analyse the SSI effect on the response of NPP buildings subjected to vertically incident seismic excitation. Analysis parameters that affect the accuracy of the calculations, including the dimension of the domain and artificial boundary types, are investigated through a set of models. A numerical SSI analysis for the 10 MW High Temperature Gas Cooled Test Reactor (HTR-10 under seismic excitation was carried out using the developed model. The floor response spectra (FRS produced by the SSI analysis are compared with a fixed-base model to investigate the SSI effect on the dynamic response of the reactor building. The results show that the FRS at foundation level are reduced and those at higher floor levels are altered significantly when taking SSI into account. The peak frequencies of the FRS are reduced due to the SSI, whereas the acceleration at high floor levels is increased at a certain frequency range. The seismic response of the primary system components, however, is reduced by the analysed SSI for the HTR-10 on the current soil site.
Seismic response analysis and upgrading design of pump houses of Kozloduy NPP units 5 and 6
International Nuclear Information System (INIS)
Jordanov, M.; Marinov, M.; Krutzik, N.
2001-01-01
The main objective of the presented project was to perform a feasibility study for seismic/structural evaluation of the safety related structures at Kozloduy NPP Units 5 and 6 for the new site seismicity and determine if they satisfy current international safety standards. The evaluation of the Pump House 3 (PH3) building is addressed in this paper, which was carried out by applying appropriate modeling techniques combined with failure mode and seismic margin analyses. The scope of the work defined was to present the required enhancement of the seismic capacity of the Pump House structures.(author)
GA-based optimum design of a shape memory alloy device for seismic response mitigation
International Nuclear Information System (INIS)
Ozbulut, O E; Roschke, P N; Lin, P Y; Loh, C H
2010-01-01
Damping systems discussed in this work are optimized so that a three-story steel frame structure and its shape memory alloy (SMA) bracing system minimize response metrics due to a custom-tailored earthquake excitation. Multiple-objective numerical optimization that simultaneously minimizes displacements and accelerations of the structure is carried out with a genetic algorithm (GA) in order to optimize SMA bracing elements within the structure. After design of an optimal SMA damping system is complete, full-scale experimental shake table tests are conducted on a large-scale steel frame that is equipped with the optimal SMA devices. A fuzzy inference system is developed from data collected during the testing to simulate the dynamic material response of the SMA bracing subcomponents. Finally, nonlinear analyses of a three-story braced frame are carried out to evaluate the performance of comparable SMA and commonly used steel braces under dynamic loading conditions and to assess the effectiveness of GA-optimized SMA bracing design as compared to alternative designs of SMA braces. It is shown that peak displacement of a structure can be reduced without causing significant acceleration response amplification through a judicious selection of physical characteristics of the SMA devices. Also, SMA devices provide a recentering mechanism for the structure to return to its original position after a seismic event
Dynamic Behaviour and Seismic Response of Ground Supported Cylindrical Water Tanks
Asha, Joseph; Glory, Joseph
2018-05-01
Liquid storage tank such as in water distribution systems, petroleum plants etc., constitute a vital component of life line systems. Reducing earthquake effects on liquid storage tanks, to minimize the environmental and economic impact of these effects, have always been an important engineering concern. In this paper, the dynamic behavior of cylindrical ground supported concrete water tanks with different aspect ratios is investigated using finite element software ANSYS. The natural frequencies and modal responses are obtained for impulsive and convective modes of vibration. The natural frequency of vibration of the tank is observed to be the lowest at maximum water depth. The fundamental impulsive frequency increases as water level reduces and for water level less than 1/3 of tank height, there is significantly no change in impulsive frequency. The effect of wall flexibility on dynamic behavior of the tank is investigated by performing the modal analysis of flexible and rigid tanks. For a partially filled tank, the results of the present study are of significant relevance. The response of the tank to the transient loading as horizontal ground motion of El Centro earthquake is studied for various water heights. As the height of water on the tank increases, the ultimate maximum seismic response parameters are also observed to be increased. The location of maximum hoop stress varies in accordance with the variations in input ground motion and water fill condition whereas shear and bending moment are maximum at the base.
Celebi, M.
2006-01-01
This paper introduces the state of the art, real-time and broad-band seismic monitoring network implemented for the 1206 m [3956 ft] long, cable-stayed Bill Emerson Memorial Bridge in Cape Girardeau (MO), a new Mississippi River crossing, approximately 80 km from the epicentral region of the 1811-1812 New Madrid earthquakes. The bridge was designed for a strong earthquake (magnitude 7.5 or greater) during the design life of the bridge. The monitoring network comprises a total of 84 channels of accelerometers deployed on the superstructure, pier foundations and at surface and downhole free-field arrays of the bridge. The paper also presents the high quality response data obtained from the network. Such data is aimed to be used by the owner, researchers and engineers to assess the performance of the bridge, to check design parameters, including the comparison of dynamic characteristics with actual response, and to better design future similar bridges. Preliminary analyses of ambient and low amplitude small earthquake data reveal specific response characteristics of the bridge and the free-field. There is evidence of coherent tower, cable, deck interaction that sometimes results in amplified ambient motions. Motions at the lowest tri-axial downhole accelerometers on both MO and IL sides are practically free from any feedback from the bridge. Motions at the mid-level and surface downhole accelerometers are influenced significantly by feedback due to amplified ambient motions of the bridge. Copyright ASCE 2006.
Seismic structural response analysis using consistent mass matrices having dynamic coupling
International Nuclear Information System (INIS)
Shaw, D.E.
1977-01-01
The basis for the theoretical development of this paper is the linear matrix equations of motion for an unconstrained structure subject to support excitation. The equations are formulated in terms of absolute displacement, velocity and acceleration vectors. By means of a transformation of the absolute response vectors into displacements, velocities and accelerations relative to the support motions, the homogeneous equations become non-homogeneous and the non-homogeneous boundary conditions become homogeneous with relative displacements, velocities and accelerations being zero at support points. The forcing function or inertial loading vector is shown to consist of two parts. The first part is comprised of the mass matrix times the suppport acceleration function times a vector of structural displacements resulting from a unit vector of support displacements in the direction of excitation. This inertial loading corresponds to the classical seismic loading vector and is indeed the only loading vector for lumped-mass systems. The second part of he inertial loading vectors consists of the mass matrix times the support acceleration function times a vector of structural accelerations resulting from unit support accelerations in the direction of excitation. This term is not present in classical seismic analysis formulations and results from the presence of off-diagonal terms in the mass matrices which give rise to dynamic coupling through the mass matrix. Thus, for lumped-mass models, the classical formulation of the inertial loading vector is correct. However, if dynamic coupling terms are included through off-diagonal terms in the mass matrix, an additional inertia loading vector must be considered
Directory of Open Access Journals (Sweden)
Yang Hui
2018-01-01
Full Text Available In order to study the internal force characteristics of shallow-bias tunnel with a small clear distance in earthquake, a large-scale shaking table slope model test was designed, and the geometric scale was 1 : 10. In the model test, the Wenchuan (WC seismic wave was used as the excitation wave. Then, the three-dimensional numerical model was established by using MIDAS-NX, and the reliability of the numerical model was verified by comparing the acceleration of the test results. The axial force, bending moment, and shear force of the tunnel cross section and longitudinal direction were calculated by the numerical model under different excitation directions included the horizontal direction (X, the vertical direction (Z, and the horizontal and vertical direction (XZ. The results show the following. (1 The internal force of right arch foot of left hole and the left arch foot of right hole is larger than other part of the tunnels because the distance between the two tunnels is smaller and they interact with each other. (2 The loading direction of single direction loading method is different and the variation trend of tunnel force are different, so the loading direction of seismic wave has a significant influence on the seismic force response of the tunnel. (3 All of the internal force values of tunnel lining under the seismic wave action in bidirection are larger than those in single direction. The value is not a simple superposition of two directions and has some coupling effect. The influence of the vertical seismic wave cannot be ignored in dynamic response research. These results improve the understanding of the rock slope with small spacing tunnel under seismic action.
de Moor, A.; Trehu, A. M.; Tryon, M. D.
2015-12-01
To investigate the dynamic response of the outer accretionary wedge updip from the patch of greatest slip during the Mw8.8 2010 Maule earthquake, 10 Ocean Bottom Seismometers (OBS) were deployed from May 2012 to March 2013 in a small array with an inter-instrument spacing of ~12 km . Nine instruments were recovered, with 4 recording data on 3 intermediate-band 3-component seismometers and a differential pressure gauge and 5 recording data from absolute pressure gauges. [note: All instruments were also equipped with a fluid flow meter sensitive to flow rates as low as 0.0001 cm/yr in or out of the sediments. However, no flow signal was detected.] Here we present hypocenters for 569 local events that have S-P times less than 17 seconds (i.e. within ~125 km of the array) using hand-picked arrival times and a 1D velocity model derived from a 2D seismic refraction profile through the region (Moscoso et al 2011, EPSL). We analyze the distribution of seismicity in the context of published slip models, ChilePEPPER high-resolution seismic reflection data, critical taper analysis done by Cubas et al 2013 (EPSL), and offshore gravity data. The data show distinct segmentation within the outer prism. The northern section of the study area is characterized by a lack of seismicity, accretion of nearly all incoming sediment and a prism at critical taper. In contrast, abundant seismicity, significant sediment underthrusting at the deformation front and a prism below critical taper angle characterize the southern part of the study area. Both coseismic slip and post-rupture local seismicity can be related to density anomalies within the upper plate as revealed by free air gravity data corrected for the effects of bathymetry and the subducting plate. [ChilePEPPER - Project Evaluating Prism Post-Earthquake Response
Non-linear seismic response of base-isolated liquid storage tanks to bi-directional excitation
International Nuclear Information System (INIS)
Shrimali, M.K.; Jangid, R.S.
2002-01-01
Seismic response of the liquid storage tanks isolated by lead-rubber bearings is investigated for bi-directional earthquake excitation (i.e. two horizontal components). The biaxial force-deformation behaviour of the bearings is considered as bi-linear modelled by coupled non-linear differential equations. The continuous liquid mass of the tank is modelled as lumped masses known as convective mass, impulsive mass and rigid mass. The corresponding stiffness associated with these lumped masses has been worked out depending upon the properties of the tank wall and liquid mass. Since the force-deformation behaviour of the bearings is non-linear, as a result, the seismic response is obtained by the Newmark's step-by-step method. The seismic responses of two types of the isolated tanks (i.e. slender and broad) are investigated under several recorded earthquake ground to study the effects of bi-directional interaction. Further, a parametric study is also carried out to study the effects of important system parameters on the effectiveness of seismic isolation for liquid storage tanks. The various important parameters considered are: (i) the period of isolation, (ii) the damping of isolation bearings and (iii) the yield strength level of the bearings. It has been observed that the seismic response of isolated tank is found to be insensitive to interaction effect of the bearing forces. Further, there exists an optimum value of isolation damping for which the base shear in the tank attains the minimum value. Therefore, increasing the bearing damping beyond a certain value may decrease the bearing and sloshing displacements but it may increase the base shear
Seismic demand evaluation based on actual earthquake records
International Nuclear Information System (INIS)
Jhaveri, D.P.; Czarnecki, R.M.; Kassawara, R.P.; Singh, A.
1990-01-01
Seismic input in the form of floor response spectra (FRS) are needed in seismic design and evaluation of equipment in nuclear power plants (NPPs). These are typically determined by analytical procedures using mathematical models of NPP structures and are known to be very conservative. Recorded earthquake data, in the form of acceleration response spectra computed from the recorded acceleration time histories, have been collected from NPP structures located in seismically active areas. Statistics of the ratios, or amplification factors, between the FRS at typical floors and the acceleration response spectra at the basemat or in the freefield, are obtained for typical NPP structures. These amplification factors are typically in terms of the peak spectral and zero period values, as well as a function of frequency. The average + 1σ values of these ratios, for those cases where enough data are available, are proposed to be used as limits to analytically calculated FRS, or for construction of simplified FRS for determining seismic input or demand in equipment qualification. (orig.)
International Nuclear Information System (INIS)
Bennett, J.G.; Dove, R.C.; Dunwoody, W.E.; Farrar, C.R.
1987-01-01
The paper reports the results from tests including reduced stiffnesses found in the prototype and 1/4 scale model, implications of the test results on the validity of past tests, and implications of these results from the 1986 tests on the seismic behavior of actual Seismic Category I Structures and their attached equipment. (orig./HP)
International Nuclear Information System (INIS)
Saxena, Navjeev; Paul, D.K.
2012-01-01
Highlights: ► Both the slip and separation of reactor base reduce with increase in embedment. ► The slip and separation become insignificant beyond 1/4 and 1/2 embedment respectively. ► The stresses in reactor reduce significantly upto 1/4 embedment. ► The stress reduction with embedment is more pronounced in case of tensile stresses. ► The modeling of interface is important beyond 1/8 embedment as stresses are underestimated otherwise. - Abstract: The seismic response of nuclear reactor containment building considering the effects of embedment, slip and separation at soil–structure interface requires modeling of the soil, structure and interface altogether. Slip and separation at the interface causes stress redistribution in the soil and the structure around the interface. The embedment changes the dynamic characteristics of the soil–structure system. Consideration of these aspects allows capturing the realistic response of the structure, which has been a research gap and presented here individually as well as taken together. Finite element analysis has been carried out in time domain to attempt the highly nonlinear problem. The study draws important conclusions useful for design of nuclear reactor containment building.
International Nuclear Information System (INIS)
Jerez, Sandra; Mebarki, Ahmed
2010-01-01
This paper develops a new modified uncoupled modal response history analysis (M-UMRHA) in order to study the seismic behavior of structures. It aims to provide an acceptable accuracy with reduced calculation duration in comparison to complete analysis, i.e. the THA. The proposed method improves the existing UMRHA, developed by Chopra and Goel [1], by considering an energy based approach to build the capacity curve [2] and a pseudo-adaptive feature to account for changes in modal shapes after yielding, motivated by an adaptive method [3]. Validation is made by comparison with NLTHA as well as other simplified methods. Low and medium-rise RC buildings were analyzed under real ground motion records. Results show good estimates of structural parameters and give good correlation between damage and story displacements as well as drifts. Like other simplified methods, accuracy decreases in the inelastic domain. However, this procedure gives acceptable estimates of structural response with a few additional calculations and it has the potential to be used in large scale studies, and probabilistic approaches.
Seismic response of elevated rectangular water tanks considering soil structure interaction
Visuvasam, J.; Simon, J.; Packiaraj, J. S.; Agarwal, R.; Goyal, L.; Dhingra, V.
2017-11-01
The overhead staged water tanks are susceptible for high lateral forces during earthquakes. Due to which, the failure of beam-columns joints, framing elements and toppling of tanks arise. To avoid such failures, they are analyzed and designed for lateral forced induced by devastating earthquakes assuming the base of the structures are fixed and considering functional needs, response reduction, soil types and severity of ground shaking. In this paper, the flexible base was provided as spring stiffness in order to consider the effect of soil properties on the seismic behaviour of water tanks. A linear time history earthquake analysis was performed using SAP2000. Parametric studies have been carried out based on various types of soils such as soft, medium and hard. The soil stiffness values highly influence the time period and base shear of the structure. The ratios of time period of flexible to fixed base and base shear of flexible to fixed base were observed against capacities of water tank and the overall height of the system. The both responses are found to be increased as the flexibility of soil medium decreases
Analysis of recorded earthquake response data at the Hualien large-scale seismic test site
International Nuclear Information System (INIS)
Hyun, C.H.; Tang, H.T.; Dermitzakis, S.; Esfandiari, S.
1997-01-01
A soil-structure interaction (SSI) experiment is being conducted in a seismically active region in Hualien, Taiwan. To obtain earthquake data for quantifying SSI effects and providing a basis to benchmark analysis methods, a 1/4-th scale cylindrical concrete containment model similar in shape to that of a nuclear power plant containment was constructed in the field where both the containment model and its surrounding soil, surface and sub-surface, are extensively instrumented to record earthquake data. In between September 1993 and May 1995, eight earthquakes with Richter magnitudes ranging from 4.2 to 6.2 were recorded. The author focuses on studying and analyzing the recorded data to provide information on the response characteristics of the Hualien soil-structure system, the SSI effects and the ground motion characteristics. An effort was also made to directly determine the site soil physical properties based on correlation analysis of the recorded data. No modeling simulations were attempted to try to analytically predict the SSI response of the soil and the structure. These will be the scope of a subsequent study
Obtaining and Estimating Low Noise Floors in Vibration Sensors
DEFF Research Database (Denmark)
Brincker, Rune; Larsen, Jesper Abildgaard
2007-01-01
For some applications like seismic applications and measuring ambient vibrations in structures, it is essential that the noise floors of the sensors and other system components are low and known to the user. Some of the most important noise sources are reviewed and it is discussed how the sensor...... can be designed in order to obtain a low noise floor. Techniques to estimate the noise floors for sensors are reviewed and are demonstrated on a commercial commonly used sensor for vibration testing. It is illustrated how the noise floor can be calculated using the coherence between simultaneous...
SiSeRHMap v1.0: a simulator for mapped seismic response using a hybrid model
Grelle, Gerardo; Bonito, Laura; Lampasi, Alessandro; Revellino, Paola; Guerriero, Luigi; Sappa, Giuseppe; Guadagno, Francesco Maria
2016-04-01
The SiSeRHMap (simulator for mapped seismic response using a hybrid model) is a computerized methodology capable of elaborating prediction maps of seismic response in terms of acceleration spectra. It was realized on the basis of a hybrid model which combines different approaches and models in a new and non-conventional way. These approaches and models are organized in a code architecture composed of five interdependent modules. A GIS (geographic information system) cubic model (GCM), which is a layered computational structure based on the concept of lithodynamic units and zones, aims at reproducing a parameterized layered subsoil model. A meta-modelling process confers a hybrid nature to the methodology. In this process, the one-dimensional (1-D) linear equivalent analysis produces acceleration response spectra for a specified number of site profiles using one or more input motions. The shear wave velocity-thickness profiles, defined as trainers, are randomly selected in each zone. Subsequently, a numerical adaptive simulation model (Emul-spectra) is optimized on the above trainer acceleration response spectra by means of a dedicated evolutionary algorithm (EA) and the Levenberg-Marquardt algorithm (LMA) as the final optimizer. In the final step, the GCM maps executor module produces a serial map set of a stratigraphic seismic response at different periods, grid solving the calibrated Emul-spectra model. In addition, the spectra topographic amplification is also computed by means of a 3-D validated numerical prediction model. This model is built to match the results of the numerical simulations related to isolate reliefs using GIS morphometric data. In this way, different sets of seismic response maps are developed on which maps of design acceleration response spectra are also defined by means of an enveloping technique.
Seismic intrusion detector system
Hawk, Hervey L.; Hawley, James G.; Portlock, John M.; Scheibner, James E.
1976-01-01
A system for monitoring man-associated seismic movements within a control area including a geophone for generating an electrical signal in response to seismic movement, a bandpass amplifier and threshold detector for eliminating unwanted signals, pulse counting system for counting and storing the number of seismic movements within the area, and a monitoring system operable on command having a variable frequency oscillator generating an audio frequency signal proportional to the number of said seismic movements.
Energy Technology Data Exchange (ETDEWEB)
R. Quittmeyer
2006-09-25
This technical work plan (TWP) describes the efforts to develop and confirm seismic ground motion inputs used for preclosure design and probabilistic safety 'analyses and to assess the postclosure performance of a repository at Yucca Mountain, Nevada. As part of the effort to develop seismic inputs, the TWP covers testing and analyses that provide the technical basis for inputs to the seismic ground-motion site-response model. The TWP also addresses preparation of a seismic methodology report for submission to the U.S. Nuclear Regulatory Commission (NRC). The activities discussed in this TWP are planned for fiscal years (FY) 2006 through 2008. Some of the work enhances the technical basis for previously developed seismic inputs and reduces uncertainties and conservatism used in previous analyses and modeling. These activities support the defense of a license application. Other activities provide new results that will support development of the preclosure, safety case; these results directly support and will be included in the license application. Table 1 indicates which activities support the license application and which support licensing defense. The activities are listed in Section 1.2; the methods and approaches used to implement them are discussed in more detail in Section 2.2. Technical and performance objectives of this work scope are: (1) For annual ground motion exceedance probabilities appropriate for preclosure design analyses, provide site-specific seismic design acceleration response spectra for a range of damping values; strain-compatible soil properties; peak motions, strains, and curvatures as a function of depth; and time histories (acceleration, velocity, and displacement). Provide seismic design inputs for the waste emplacement level and for surface sites. Results should be consistent with the probabilistic seismic hazard analysis (PSHA) for Yucca Mountain and reflect, as appropriate, available knowledge on the limits to extreme ground
International Nuclear Information System (INIS)
R. Quittmeyer
2006-01-01
This technical work plan (TWP) describes the efforts to develop and confirm seismic ground motion inputs used for preclosure design and probabilistic safety 'analyses and to assess the postclosure performance of a repository at Yucca Mountain, Nevada. As part of the effort to develop seismic inputs, the TWP covers testing and analyses that provide the technical basis for inputs to the seismic ground-motion site-response model. The TWP also addresses preparation of a seismic methodology report for submission to the U.S. Nuclear Regulatory Commission (NRC). The activities discussed in this TWP are planned for fiscal years (FY) 2006 through 2008. Some of the work enhances the technical basis for previously developed seismic inputs and reduces uncertainties and conservatism used in previous analyses and modeling. These activities support the defense of a license application. Other activities provide new results that will support development of the preclosure, safety case; these results directly support and will be included in the license application. Table 1 indicates which activities support the license application and which support licensing defense. The activities are listed in Section 1.2; the methods and approaches used to implement them are discussed in more detail in Section 2.2. Technical and performance objectives of this work scope are: (1) For annual ground motion exceedance probabilities appropriate for preclosure design analyses, provide site-specific seismic design acceleration response spectra for a range of damping values; strain-compatible soil properties; peak motions, strains, and curvatures as a function of depth; and time histories (acceleration, velocity, and displacement). Provide seismic design inputs for the waste emplacement level and for surface sites. Results should be consistent with the probabilistic seismic hazard analysis (PSHA) for Yucca Mountain and reflect, as appropriate, available knowledge on the limits to extreme ground motion at
Seismic response of unanchored and partially anchored liquid-storage tanks. Final report
International Nuclear Information System (INIS)
Malhotra, P.K.; Veletsos, A.S.
1995-12-01
Ground-mounted vertical storage tanks are important components of nuclear plant safety systems. A systematic study is made of the principal effects of base uplifting on the seismic response of laterally excited, unanchored and partially anchored cylindrical liquid-storage tanks. The study consists of two parts: the first deals with the static uplifting resistance of the flexible base plate, and the second deals with the dynamic response of the uplifting system. An insight into the behavior of the uplifting base plate is first gained with the help of a prismatic beam solution. In Section 2, the solution is implemented exactly, whereas in Section 3 it is implemented approximately by use of the Ritz energy procedure. Solutions are next presented for axisymmetrically and asymmetrically uplifted base plate of tanks, in Section 4. For the axisymmetric case the solution is implemented exactly, as well as approximately by modeling the plate by a series of semiinfinite prismatic beams. The accuracy of the latter approach is confirmed by comparing its predictions with those of the former. In Section 5, a highly efficient and rational method is presented for the dynamic response analysis of uplifting tanks. Both unanchored tanks and partially anchored tanks, for which the number of anchor bolts at the base is insufficient to ensure full fixity, are considered. It is shown that base uplifting may reduce significantly the hydrodynamic pressures, but these reductions may be associated with increased axial compressive stresses in the tank wall and large plastic rotations at the plate-shell junction. For partially anchored tanks, energy loss due to bolt yielding is found to be small
Intelligent seismic risk mitigation system on structure building
Suryanita, R.; Maizir, H.; Yuniorto, E.; Jingga, H.
2018-01-01
Indonesia located on the Pacific Ring of Fire, is one of the highest-risk seismic zone in the world. The strong ground motion might cause catastrophic collapse of the building which leads to casualties and property damages. Therefore, it is imperative to properly design the structural response of building against seismic hazard. Seismic-resistant building design process requires structural analysis to be performed to obtain the necessary building responses. However, the structural analysis could be very difficult and time consuming. This study aims to predict the structural response includes displacement, velocity, and acceleration of multi-storey building with the fixed floor plan using Artificial Neural Network (ANN) method based on the 2010 Indonesian seismic hazard map. By varying the building height, soil condition, and seismic location in 47 cities in Indonesia, 6345 data sets were obtained and fed into the ANN model for the learning process. The trained ANN can predict the displacement, velocity, and acceleration responses with up to 96% of predicted rate. The trained ANN architecture and weight factors were later used to build a simple tool in Visual Basic program which possesses the features for prediction of structural response as mentioned previously.
[Functional aspects of pelvic floor surgery].
Wagenlehner, F M E; Gunnemann, A; Liedl, B; Weidner, W
2009-11-01
Pelvic floor dysfunctions are frequently seen in females. The human pelvic floor is a complex structure and heavily stressed throughout female life. Recent findings in the functional anatomy of the pelvic floor have led to a much better understand-ing, on the basis of which enormous improvements in the therapeutic options have arisen. The pelvic floor activity is regulated by three main muscular forces that are responsible for vaginal tension and suspension of the pelvic floor -organs, bladder and rectum. For different reasons laxity in the vagina or its supporting ligaments as a result of altered connective tissue can distort this functional anatomy. A variety of symptoms can derive from these pelvic floor dysfunctions, such as urinary urge and stress incontinence, abnormal bladder emptying, faecal incontinence, obstructive bowel disease syndrome and pelvic pain. Pelvic floor reconstruction is nowadays driven by the concept that in the case of pelvic floor symptoms restoration of the anatomy will translate into restoration of the physiology and ultimately improve the patients' symptoms. The exact surgical reconstruction of the anatomy is there-fore almost exclusively focused on the restoration of the lax pelvic floor ligaments. An exact identification of the anatomic lesions preoperatively is eminently necessary, to allow for an exact anatomic reconstruction with respect to the muscular forces of the pelvic floor. Georg Thieme Verlag Stuttgart * New York.
John Lu; Marc Chorney; Lowell Peterson
2009-01-01
Different trailer flooring materials, including wood-based, aluminum, steel, and synthetic plastic floors, were evaluated in accordance with their durability and sustainability to our natural environment. Wood-based trailer flooring is an eco-friendly product. It is the most sustainable trailer flooring material compared with fossil fuel-intensive steel, aluminum, and plastics. It is renewable and recyclable. Oak, hard maple, and apitong are strong and durable hardwood species that are curren...
Analysis for seismic response of dry storage facility for spent fuel
International Nuclear Information System (INIS)
Ko, Y.-Y.; Hsu, S.-Y.; Chen, C.-H.
2009-01-01
Most of the dry storage systems for spent fuel are freestanding, which leads to stability concerns in an earthquake. In this study, as a safety check, the ABAQUS/Explicit code is adopted to analyse the seismic response of the dry storage facility planned to be installed at Nuclear Power Plant no. 1 (NPP1) in Taiwan. A 3D coupled finite element (FE) model was established, which consisted of a freestanding cask, a concrete pad, and underneath soils interacting with frictional contact interfaces. The scenario earthquake used in the model included an artificial earthquake compatible to the design spectrum of NPP1, and a strong ground motion modified from the time history recorded during the Chi-Chi earthquake. The results show that the freestanding cask will slide, but not tip over, during strong earthquakes. The scale of the sliding is very small and a collision between casks will not occur. In addition, the differential settlement of the foundation pad that takes place due to the weight of the casks increases the sliding potential of the casks during earthquakes
Multiobjective Optimal Control of Longitudinal Seismic Response of a Multitower Cable-Stayed Bridge
Directory of Open Access Journals (Sweden)
Geng Fangfang
2016-01-01
Full Text Available The dynamic behavior of a multitower cable-stayed bridge with the application of partially longitudinal constraint system using viscous fluid dampers under real earthquake ground motions is presented. The study is based on the dynamic finite element model of the Jiashao Bridge, a six-tower cable-stayed bridge in China. The prime aim of the study is to investigate the effectiveness of viscous fluid dampers on the longitudinal seismic responses of the bridge and put forth a multiobjective optimization design method to determine the optimized parameters of the viscous fluid dampers. The results of the investigations show that the control objective of the multitower cable-stayed bridge with the partially longitudinal constraint system is to yield maximum reductions in the base forces of bridge towers longitudinally restricted with the bridge deck, with slight increases in the base forces of bridge towers longitudinally unrestricted with the bridge deck. To this end, a multiobjective optimization design method that uses a nondominating sort genetic algorithm II (NSGA-II is used to optimize parameters of the viscous fluid dampers. The effectiveness of the proposed optimization design method is demonstrated for the multitower cable-stayed bridge with the partially longitudinal constraint system, which reveals that a design engineer can choose a set of proper parameters of the viscous fluid dampers from Pareto optimal fronts that can satisfy the desired performance requirements.
Diefenbach, A. K.; Hurwitz, S.; Murphy, F.; Evans, W.
2013-12-01
The Mud Volcano thermal area in Yellowstone National Park comprises many hydrothermal features including fumaroles, mudpots, springs, and thermal pools. Observations of hydrothermal changes have been made for decades in the Mud Volcano thermal area, and include reports of significant changes (the appearance of new features, increased water levels in pools, vigor of activity, and tree mortality) following an earthquake swarm in 1978 that took place beneath the area. However, no quantitative method to map and measure surface feature changes through time has been applied. We present an analysis of aerial photographs from 1954 to present to track temporal changes in the boundaries between vegetated and thermally barren areas, as well as location, extent, color, clarity, and runoff patterns of hydrothermal features within the Mud Volcano thermal area. This study attempts to provide a detailed, long-term (>50 year) inventory of hydrothermal features and change detection at Mud Volcano thermal area that can be used to identify changes in hydrothermal activity in response to seismicity, uplift and subsidence episodes of the adjacent Sour Creek resurgent dome, or other potential causes.
International Nuclear Information System (INIS)
Kaznovski, S.
1996-01-01
The method for examination and ensuring of equipment seismic resistance is based on the resonance character of the seismic influence on structures and equipment. Values of natural dynamic characteristics are obtained by using external source for exciting the vibrations of the testing unit. These characteristics with the floor response spectra enabled calculations of the seismic resistance. For tests of Kozloduy NPP equipment a simple shock method was used. The presentation includes the list of inspected equipment. The calculations of the equipment seismic resistance were carried out on the basis of Russian and International standards and demands
Decontamination of floor surfaces
International Nuclear Information System (INIS)
Smirous, F.
1983-01-01
Requirements are presented put on the surfaces of floors of radiochemical workplaces. The mechanism is described of retaining the contaminant in the surface of the flooring, ways of reducing the hazards of floor surface contamination, decontamination techniques and used decontamination agents. (J.P.)
International Nuclear Information System (INIS)
Carbonari, S.; Dezi, F.; Leoni, G.
2008-01-01
This paper presents a study on the seismic response of coupled wall-frame structures founded on piles. A complete soil-structure interaction analysis is carried out with reference to a case study. Three different soils and seven real accelerograms are considered. Local site response analyses are performed in order to evaluate the incoming free-field motion at different depths and the ground motion amplifications. A numerical model, accounting for the pile-soil-pile interaction and for material and radiation damping, is used to evaluate the impedance matrix and the foundation input motion. The domain decomposition technique is adopted to perform time-domain seismic analyses introducing Lumped Parameter Models to take into account the impedance of the soil-structure system. Applications show that the rocking phenomena affect the behaviour of the structure by changing the base shear distribution within the wall and the frame and by increasing the structural displacements
2010-02-01
This interdisciplinary project combined seismic data recorded at bridge sites with computer models to identify how highway bridges built on permanently and seasonally frozen ground behave during an earthquake. Two sites one in Anchorage and one in...
International Nuclear Information System (INIS)
Herbert, R.
1988-01-01
To ensure that a nuclear reactor or other damage-susceptible installation is, so far as possible, tripped and already shut down before the arrival of an earthquake shock at its location, a ring of monitoring seismic sensors is provided around it, each sensor being spaced from it by a distance (possibly several kilometres) such that (taking into account the seismic-shock propagation velocity through the intervening ground) a shock monitored by the sensor and then advancing to the installation site will arrive there later than a warning signal emitted by the sensor and received at the installation, by an interval sufficient to allow the installation to trip and shut down, or otherwise assume an optimum anti-seismic mode, in response to the warning signal. Extra sensors located in boreholes may define effectively a three-dimensional (hemispherical) sensing boundary rather than a mere two-dimensional ring. (author)
International Nuclear Information System (INIS)
Sollogoub, Pierre
2001-01-01
This lecture deals with: qualification methods for seismic testing; objectives of seismic testing; seismic testing standards including examples; main content of standard; testing means; and some important elements of seismic testing
Directory of Open Access Journals (Sweden)
Mostafa Farajian
2017-03-01
Full Text Available Soil-structure interaction (SSI could affect the seismic response of structures. Since liquid storage tanks are vital structures and must continue their operation under severe earthquakes, their seismic behavior should be studied. Accordingly, the seismic response of two types of steel liquid storage tanks (namely, broad and slender, with aspect ratios of height to radius equal to 0.6 and 1.85 founded on half-space soil is scrutinized under different earthquake ground motions. For a better comparison, the six considered ground motions are classified, based on their pulse-like characteristics, into two groups, named far and near fault ground motions. To model the liquid storage tanks, the simplified mass-spring model is used and the liquid is modeled as two lumped masses known as sloshing and impulsive, and the interaction of fluid and structure is considered using two coupled springs and dashpots. The SSI effect, also, is considered using a coupled spring and dashpot. Additionally, four types of soils are used to consider a wide variety of soil properties. To this end, after deriving the equations of motion, MATLAB programming is employed to obtain the time history responses. Results show that although the SSI effect leads to a decrease in the impulsive displacement, overturning moment, and normalized base shear, the sloshing (or convective displacement is not affected by such effects due to its long period.
Directory of Open Access Journals (Sweden)
El Abbas N.
2016-01-01
Full Text Available This work deals with seismic analysis of structures by taking into account soil-structure interaction where the structure is modeled by an equivalent flexible beam mounted on a rigid foundation that is supported by a Winkler like soil. The foundation is assumed to undergo local uplift and the rotations are considered to be large. The coupling of the system is represented by a series of springs and damping elements that are distributed over the entire width of the foundation. The non-linear equations of motion of the system were derived by taking into account the equilibrium of the coupled foundation-structure system where the structure was idealized as a single-degree-of-freedom. The seismic response of the structure was calculated under the occurrence of foundation uplift for both large and small rotations. The non-linear differential system of equations was integrated by using the Matlab command ode15s. The maximum response has been determined as function of the intensity of the earthquake, the slenderness of the structure and the damping ratio. It was found that considering local uplift with small rotations of foundation under seismic loading leads to unfavorable structural response in comparison with the case of large rotations.
Nishikawa, Hayato; Miyajima, Masakatsu
In this study, we evaluate an acceleration Fourier and response spectra at Ichihasama and Koromogawa seismic intensity observation sites which observed JMA seismic intensity of 6 upper but seismic waveform records don't exist during the Iwate-Miyagi Nairiku earthquake in 2008. Firstly, formula to evaluate acceleration Fourier and response spectra are developed using peak ground acceleration, JMA seismic intensity and predominant period of earthquake spectra based on records obtained from crustal earthquakes with Magnitude of 6 to 7. Acceleration Fourier and response spectra are evaluated for another local government site which are not chosen for development of the formula. The evaluated values mostly agree with the observed ones. Finally, acceleration Fourier and response spectra are evaluated for Ichihasama and Koromogawa observation sites. It is clarified that short period below 1 second was predominated in the evaluated spectra.
International Nuclear Information System (INIS)
Ma, D.; Prato, C.; Godoy, A.
1992-10-01
A seismic Safety Review Mission to assist in the evaluation of the design of seismic upgrading for Kozloduy NPP was performed in Sofia from 19-23 October 1992. The objectives of the mission were to assist the Bulgarian authorities in: the evaluation of the floor response spectra of the main buildings of units 1-4 at Kozloduy NPP, calculated for the new defined seismic parameters at site (Review Level Earthquake - RLE); the evaluation of the remedial and strengthening measures proposed for the seismic upgrading of the pump house and diesel generator buildings to the new defined RLE. This mission completed the scope of previous IAEA mission - BUL/9/012-18b - (see Report 3262) performed from 3-7 August 1992, with regard to tasks which were not evaluated at that time because they had not been finished. 2 tabs
Directory of Open Access Journals (Sweden)
John Lu
2009-05-01
Full Text Available Different trailer flooring materials, including wood-based, aluminum, steel, and synthetic plastic floors, were evaluated in accordance with their durability and sustainability to our natural environment. Wood-based trailer flooring is an eco-friendly product. It is the most sustainable trailer flooring material compared with fossil fuel-intensive steel, aluminum, and plastics. It is renewable and recyclable. Oak, hard maple, and apitong are strong and durable hardwood species that are currently extensively used for trailer flooring. For manufacture, wood-based flooring is higher in energy efficiency and lower in carbon emission than steel, aluminum and plastics. Moreover, wood per se is a natural product that sequesters carbon. Accordingly, using more wood-based trailer flooring is effective to reduce global warming.
International Nuclear Information System (INIS)
Lee, T.H.; Thompson, R.W.; Charman, C.M.
1983-01-01
The effects of soil-structure interaction during seismic events upon the dynamic response of a High Temperature Gas-Cooled Reactor plant (HTGR) have been investigated for both surface-founded and embedded basemats. The influence from foundation embedment has been quantitatively assessed through a series of theoretical studies on plants of various sizes. The surface-founded analyses were performed using frequency-independent soil impedance parameters, while the embedded plant analyses utilized finite element models simulated on the FLUSH computer program. The seismic response of the surface-founded plants has been used to establish the standard-site design in-structure response spectra. These analyses were performed by using the linear modal formulation based on conventional soil stiffness and damping values. They serve as reference solutions to which the response data of the corresponding embedded plants are compared. In these comparison studies the responses of embedded plants were generally found to be lower than those of the corresponding surface-founded plants. Additional studies on the surface-founded plants have recently been performed by considering inelastic soil behavior. These inelastic solutions, which treat the soil as an elasto-plastic medium exhibiting hysteretic unloading-reloading characteristics in time, have reduced the response of surface-founded plants. Numerical results are presented in terms of in-structure response spectra along with other pertinent seismic load data at key levels of the plant. Analysis techniques for future studies using viscoelastic halfspace representation and inelastic finite element modeling for soil are also discussed
Seismic response of earth dams considering dynamic properties of unsaturated zone
Directory of Open Access Journals (Sweden)
Ariyan M.
2016-01-01
Full Text Available It is conventionally assumed in the analysis and design of earth dams that the soil located above the phreatic line, i.e. the uppermost seepage flow line, is completely dry. However, there is often an unsaturated flow of water through an unsaturated zone above this borderline and variation in moisture content in this zone results in variation of matric suction throughout this region. Variation of matric suction, in turn, results in variation of effective stresses in this zone. In this research, the seismic response of earth dams in terms of the displacement and acceleration at the crown of the dam as well as the stress distribution in the dam body is investigated. Taking into account the effect of unsaturated zone, a comparison is made to investigate the effect of conventional simplification in ignoring the dynamic characteristics of the unsaturated zone above the phreatic line and the more complicated analysis which includes the unsaturated zone. A function for the soil-water retention curve (SWRC was assigned to the soil in the unsaturated zone to determine the variation of matric suction in this zone and analyses were made using finite difference software (FLAC. Results are then compared to the conventional method for homogeneous dams. In these analyzes the soil shear modulus was assumed to vary with the mean effective stress both for saturated and unsaturated zones. Among various results, it was notable that the history of crest x-displacement, and acceleration show higher values in models accounting for the unsaturated region. It was attributed to the considerably lower values of damping ratio in the crest region in the unsaturated models.
International Nuclear Information System (INIS)
Miyagawa, Yoshinori; Sato, Hiroaki
2015-01-01
A bushing is a device for insulation and support of a conductor. Especially it is called center-clamp type when it is connected with a metal holder through clamping force. As a consequence of damage of center-clamp type bushings in Tohoku Earthquake in 2011, refinement of the response analysis method and review of the seismic design procedure became necessary. In the present report, the fiber model, which can evaluate non-linear behavior in the section subjected to axial force and bending moment, was implemented to the CRIEPI's finite element analysis program 'Mastrd' considering following characteristics of center-clamp type bushings. a) The gasket section between a porcelain tube and a metal holder has a torus shape. b) Springs around the top of the bushing give clamping force, but they lock in excessive base rotation. c) The gasket does not resist against tension. d) Local resistance against compression due to bending increases in use of very thin gaskets. The developed program was verified through comparison with the shaking table test result for real bushings whose voltage classes were 154 kV and 275 kV. Deformation indices as rotation angle and base opening due to bending were influenced by damping conditions. Though there was not the condition which brought about remarkable underestimation, reduction of damping for a fiber model element was preferable for safety. On the other hand, bending moment was consistent with experimental results because it tended not to fluctuate in the non-linear region. (author)
Directory of Open Access Journals (Sweden)
P. Labak
1995-06-01
Full Text Available The seismic response of the geologic structure beneath the Colosseum is investigated using a two-dimensional modeling for a vertically incident plane SH wave. Computations indicate that the southern part of the Colosseum may be exposed to a seismic ground motion with significantly larger amplitudes, differential motion and longer duration than the northern part. because the southern part of the Colosseum is underlain by a sedimentfilled valley created by sedimentary filling of the former tributary of the River Tiber. A 2-D resonance may develop in the valley. Unlike the previous theoretical studies on 2-D resonance in sediment-filled valleys, an effect of heterogeneous valley surroundings on the resonance is partly investigated. A very small sensitivity of the maximum spectral amplifications connected with the fundamental and first higher modes to the presence of a horizontal surface layer (with an intermediate velocity in the valley surroundings is observed in the studied models.
Directory of Open Access Journals (Sweden)
Ehsan Nikbakht
Full Text Available Precast bridge columns have shown increasing demand over the past few years due to the advantages of such columns when compared against conventional bridge columns, particularly due to the fact that precast bridge columns can be constructed off site and erected in a short period of time. The present study analytically investigates the behaviour of self-centring precast segmental bridge columns under nonlinear-static and pseudo-dynamic loading at different prestressing strand levels. Self-centring segmental columns are composed of prefabricated reinforced concrete segments which are connected by central post-tensioning (PT strands. The present study develops a three dimensional (3D nonlinear finite element model for hybrid post-tensioned precast segmental bridge columns. The model is subjected to constant axial loading and lateral reverse cyclic loading. The lateral force displacement results of the analysed columns show good agreement with the experimental response of the columns. Bonded post-tensioned segmental columns at 25%, 40% and 70% prestressing strand stress levels are analysed and compared with an emulative monolithic conventional column. The columns with a higher initial prestressing strand levels show greater initial stiffness and strength but show higher stiffness reduction at large drifts. In the time-history analysis, the column samples are subjected to different earthquake records to investigate the effect post-tensioning force levels on their lateral seismic response in low and higher seismicity zones. The results indicate that, for low seismicity zones, post-tensioned segmental columns with a higher initial stress level deflect lower lateral peak displacement. However, in higher seismicity zones, applying a high initial stress level should be avoided for precast segmental self-centring columns with low energy dissipation capacity.
The ANSS response to the Mw 5.8 Central Virginia Seismic Zone earthquake of August 23, 2011
McNamara, D. E.; Horton, S.; Benz, H.; Earle, P. S.; Withers, M. M.; Hayes, G. P.; Kim, W. Y.; Chapman, M. C.; Herrmann, R. B.; Petersen, M. D.; Williams, R. A.
2011-12-01
An Mw 5.8 earthquake (depth=6km) occurred on August 23, 2011 (17:51:04 UTC) near Mineral, Virginia, which was widely felt from Maine to Georgia along the eastern seaboard and west to Chicago and western Tennessee. The USGS tallied nearly 142,000 felt reports submitted to the Did You Feel It (DYFI) internet community intensity system, making it the most widely felt earthquake since the web-site began, and demonstrating that more people felt this earthquake than any other in U.S. history. Significant damage was reported in the epicentral area and as far away as Washington D.C. (135 km away); minor damage was reported in Baltimore (200 km). The reverse faulting earthquake occurred on a northeast-striking plane within a region of diffuse seismicity known as the Central Virginia Seismic Zone. Within the first week, the mainshock was followed by 17 aftershocks with magnitude greater than 2, including Mw 4.5, 4.2, and 3.8 events. In the days following the mainshock, 46 portable seismic stations were deployed by several organizations, making this among the best-recorded aftershock sequence in the eastern U.S. Within 24 hours of the mainshock, 8 portable stations were deployed in time to record the largest aftershock to date (M4.5). We will present the results of our post-earthquake response, including attenuation and site amplification observations using portable aftershock station data, details on the initial USGS NEIC post earthquake response products and an assessment of the seismotectonics of the Central Virginia Seismic Zone based on aftershock locations and source parameter modeling of the larger earthquakes.
Seismic analysis of a reactor building with eccentric layout
International Nuclear Information System (INIS)
Itoh, T.; Deng, D.Z.F.; Lui, K.
1987-01-01
Conventional design for a reactor building in a high seismic area has adopted an essentially concentric layout in response to fear of excessive torsional effect due to horizontal seismic load on an eccentric plant. This concentric layout requirement generally results in an inflexible arrangement of the plant facilities and thus increases the plant volume. This study is performed to investigate the effect of eccentricity on the overall seismic structural response and to provide technical information in this regard to substantiate the volume reduction of the overall power plant. The plant layout is evolved from the Bechtel standard plan of a PWR plant by integrating the reactor building and the auxiliary building into a combined building supported on a common basemat. This plant layout is optimized for volume utilization and to reduce the length of piping systems. The mass centers at various elevations of the combined building do not coincide with the rigidity center (RC) of the respective floor and the geometric center of the basemat, thus creating an eccentric response of the building in a seismic environment. Therefore, the torsional effects of the structure have to be taken into account in the seismic analysis
Seismic tests on models of reinforced-concrete Category I buildings
International Nuclear Information System (INIS)
Dove, R.C.; Endebrock, E.G.; Dunwoody, W.E.; Bennett, J.G.
1985-01-01
The behavior of reinforced concrete (R/C), Category I noncontainment nuclear power plant structures subjected to seismic events of magnitude greater than used in their original design has been investigated using two sizes of scale models. Test results were analyzed to determine (1) maximum input for the response to remain linear/elastic; (2) changes in stiffness, damping, and modal frequency that are produced by seismic input greater than that causing linear elastic response; (3) changes in floor response spectra when the structure's response is nonlinear/inelastic; and (4) the magnitude of the seismic event necessary to fail (excessively crack) these structures. By constructing models of two sizes, it was possible to make two independent predictions of prototype behavior and to compare the results from the two models. 1 ref., 4 figs., 1 tab
Rutqvist, J.; Cappa, F.; Mazzoldi, A.; Rinaldi, A.
2012-12-01
The importance of geomechanics associated with large-scale geologic carbon storage (GCS) operations is now widely recognized. There are concerns related to the potential for triggering notable (felt) seismic events and how such events could impact the long-term integrity of a CO2 repository (as well as how it could impact the public perception of GCS). In this context, we review a number of modeling studies and field observations related to the potential for injection-induced fault reactivations and seismic events. We present recent model simulations of CO2 injection and fault reactivation, including both aseismic and seismic fault responses. The model simulations were conducted using a slip weakening fault model enabling sudden (seismic) fault rupture, and some of the numerical analyses were extended to fully dynamic modeling of seismic source, wave propagation, and ground motion. The model simulations illustrated what it will take to create a magnitude 3 or 4 earthquake that would not result in any significant damage at the groundsurface, but could raise concerns in the local community and could also affect the deep containment of the stored CO2. The analyses show that the local in situ stress field, fault orientation, fault strength, and injection induced overpressure are critical factors in determining the likelihood and magnitude of such an event. We like to clarify though that in our modeling we had to apply very high injection pressure to be able to intentionally induce any fault reactivation. Consequently, our model simulations represent extreme cases, which in a real GCS operation could be avoided by estimating maximum sustainable injection pressure and carefully controlling the injection pressure. In fact, no notable seismic event has been reported from any of the current CO2 storage projects, although some unfelt microseismic activities have been detected by geophones. On the other hand, potential future commercial GCS operations from large power plants
International Nuclear Information System (INIS)
Srinivasan, M.G.; Kot, C.A.; Hsieh, B.J.
1989-01-01
As part of the earthquake investigations at the HDR (Heissdampfreaktor) Test Facility in Kahl/Main, FRG, simulated seismic tests (SHAM) were performed during April--May 1988 on the VKL (Versuchskreislauf) piping system. The purpose of these experiments was to study the behavior of piping subjected to a range of seismic excitation levels including those that exceed design levels manifold and that might induce failure of pipe supports or plasticity in the pipe runs, and to establish seismic margins for piping and pipe supports. Data obtained in the tests are also used to validate analysis methods. Detailed reports on the SHAM experiments are given elsewhere. The objective of this document is to evaluate a subsystem analysis module of the SMACS code. This module is a linear finite-element based program capable of calculating the response of nuclear power plant subsystems subjected to independent multiple-acceleration input excitation. The evaluation is based on a comparison of computational results of simulation of SHAM tests with corresponding test measurements
Directory of Open Access Journals (Sweden)
Daogang Lu
2015-01-01
Full Text Available Huge water storage tank on the top of many buildings may affect the safety of the structure caused by fluid-structure interaction (FSI under the earthquake. AP1000 passive containment cooling system water storage tank (PCCWST placed at the top of shield building is a key component to ensure the safety of nuclear facilities. Under seismic loading, water will impact the wall of PCCWST, which may pose a threat to the integrity of the shield building. In the present study, an FE model of AP1000 shield building is built for the modal and transient seismic analysis considering the FSI. Six different water levels in PCCWST were discussed by comparing the modal frequency, seismic acceleration response, and von Mises stress distribution. The results show the maximum von Mises stress emerges at the joint of shield building roof and water around the air inlet. However, the maximum von Mises stress is below the yield strength of reinforced concrete. The results may provide a reference for design of the AP1000 and CAP1400 in the future.
2010-02-01
The state of Alaska is located in one of the most seismically active zones in the world. Several large magnitude earthquakes (the Prince William Sound Earthquake, March 1964 and the Denali Earthquake, November 2002) have occurred in the state and cau...
Draganov, D.
2007-01-01
One of the goals of exploration geophysics is to obtain an image of the subsurface. In petroleum exploration and near-surface geophysics, this is best achieved using reflected waves. For this, a controlled seismic or electromagnetic source is placed at the surface, activated, and the wavefields that
Directory of Open Access Journals (Sweden)
Faheem Butt
2012-01-01
Full Text Available This paper presents analyses of the seismic responses of two reinforced concrete buildings monitored for a period of more than two years. One of the structures was a three-storey reinforced concrete (RC frame building with a shear core, while the other was a three-storey RC frame building without a core. Both buildings are part of the same large complex but are seismically separated from the rest of it. Statistical analysis of the relationships between maximum free field accelerations and responses at different points on the buildings was conducted and demonstrated strong correlation between those. System identification studies using recorded accelerations were undertaken and revealed that natural frequencies and damping ratios of the building structures vary during different earthquake excitations. This variation was statistically examined and relationships between identified natural frequencies and damping ratios, and the peak response acceleration at the roof level were developed. A general trend of decreasing modal frequencies and increasing damping ratios was observed with increased level of shaking and response. Moreover, the influence of soil structure interaction (SSI on the modal characteristics was evaluated. SSI effects decreased the modal frequencies and increased some of the damping ratios.
1979-09-30
were presumed nuclear explosions announced by ERDA. Of the last, 11 were at the Semipalatinsk test site , 2 at the Western Kazakh test site , 2 in Novaya...which will fulfill U.S. ob- ligations that may be incurred under a possible future Comprehensive Test Ban Treaty. This report includes 9 contributions...which could assume U.S. seismic-data-management responsibilities in the event that international agreement is reached on a Comprehensive Test Ban
International Nuclear Information System (INIS)
Takaki, Yu; Taniguchi, Katsuhiko; Kishimoto, Junichi; Iwasaki, Akihisa; Nekomoto, Yoshitsugu; Kuga, Tohru; Kameyama, Masashi
2017-01-01
Free standing racks which are not anchored to the pool floor nor walls have never been adopted in Japan. Under an earthquake, behaviors of free standing racks are nonlinear and involve a complex combination of motions (sliding, rocking, and twisting) and impacts between a fuel assembly and the fuel cell walls and between a pit floor and rack pedestals. To predict a seismic response of free standing racks, the seismic analysis requires careful considerations of these complex phenomena (sliding, rocking, and twisting), fluid coupling effects and frictional effects. We carried out seismic experiments on the full-scale rack model in both water and dry conditions and obtained the fundamental data about behavior of free standing racks (sliding, and rocking motions). We have developed the nonlinear dynamic analysis method to predict seismic response of free standing racks utilizing the full-scale test result and verified the analysis evaluation method of free standing rack by comparison between analysis results and experimental data. Furthermore, we applied the seismic design method to the free standing rack in the Japanese nuclear plant (Mihama nuclear power station Unit 3), and verified that the free standing rack was applicable to Japanese nuclear plant. (author)
Introductory guide to floors and flooring
CSIR Research Space (South Africa)
Billingham, PA
1977-01-01
Full Text Available not make use of the warming and cooling effects of direct contact with the ground. Indeed the precautions that are necessary to protect such floors against damp and decay may actually reduce the comfort levels within a house. This is because there is a... with resultant discomfort and extra heating costs. Today, in South Africa, most modern homesareof singlestorey con- struction with aconcrete floor slab in direct contact with theground which once again makes its full contribution to the comfort and structural...
Seismic performance for vertical geometric irregularity frame structures
Ismail, R.; Mahmud, N. A.; Ishak, I. S.
2018-04-01
This research highlights the result of vertical geometric irregularity frame structures. The aid of finite element analysis software, LUSAS was used to analyse seismic performance by focusing particularly on type of irregular frame on the differences in height floors and continued in the middle of the building. Malaysia’s building structures were affected once the earthquake took place in the neighbouring country such as Indonesia (Sumatera Island). In Malaysia, concrete is widely used in building construction and limited tension resistance to prevent it. Analysing structural behavior with horizontal and vertical static load is commonly analyses by using the Plane Frame Analysis. The case study of this research is to determine the stress and displacement in the seismic response under this type of irregular frame structures. This study is based on seven-storey building of Clinical Training Centre located in Sungai Buloh, Selayang, Selangor. Since the largest earthquake occurs in Acheh, Indonesia on December 26, 2004, the data was recorded and used in conducting this research. The result of stress and displacement using IMPlus seismic analysis in LUSAS Modeller Software under the seismic response of a formwork frame system states that the building is safe to withstand the ground and in good condition under the variation of seismic performance.
International Nuclear Information System (INIS)
Schneeberger, B.; Breuleux, R.
1977-01-01
Assuming that earthquake ground motion is a stationary time function, the seismic analysis of a linear structure can be done by probailistic methods using the 'power spectral density function' (PSD), instead of applying the more traditional time-step-integration using earthquake time histories (TH). A given structure was analysed both by PSD and TH methods computing and comparing 'floor response spectra'. The analysis using TH was performed for two different TH and different frequency intervals for the 'floor-response-spectra'. The analysis using PSD first produced PSD functions of the responses of the floors and these were then converted into 'foor-response-spectra'. Plots of the resulting 'floor-response-spectra' show: (1) The agreement of TH and PSD results is quite close. (2) The curves produced by PSD are much smoother than those produced by TH and mostly form an enelope of the latter. (3) The curves produced by TH are quite jagged with the location and magnitude of the peaks depending on the choice of frequencies at which the 'floor-response-spectra' were evaluated and on the choice of TH. (Auth.)
Seismic analysis of freestanding fuel racks
International Nuclear Information System (INIS)
Gilmore, C.B.
1982-01-01
This paper presents a nonlinear transient dynamic time-history analysis of freestanding spent fuel storage racks subjected to seismic excitation. This type of storage rack is structurally unrestrained and submerged in water in the spent fuel pool of a nuclear power complex, holds (spent) fuel assemblies which have been removed from the reactor core. Nonlinearities in the fuel rack system include impact between the fuel assembly and surrounding cell due to clearances between them, friction due to sliding between the fuel rack support structure and spent fuel pool floor, and the lift-off of the fuel rack support structure from the spent fuel pool floor. The analysis of the fuel rack system includes impacting due to gap closures, energy losses due to impacting bodies, Coulomb damping between sliding surfaces, and hydrodynamic mass effects. Acceleration time history excitation development is discussed. Modeling considerations, such as the initial status of nonlinear elements, number of mode shapes to include in the analysis, modal damping, and integration time-step size are presented. The response of the fuel rack subjected to two-dimensional seismic excitation is analyzed by the modal superposition method, which has resulted in significant computer cost savings when compared to that of direct integration
Strinna, Elisa; Ferrari, Graziano
2015-04-01
The project started in 2008 as a sound installation, a collaboration between an artist, a barrel organ builder and a seismologist. The work differs from other attempts of sound transposition of seismic records. In this case seismic frequencies are not converted automatically into the "sound of the earthquake." However, it has been studied a musical translation system that, based on the organ tonal scale, generates a totally unexpected sequence of sounds which is intended to evoke the emotions aroused by the earthquake. The symphonies proposed in the project have somewhat peculiar origins: they in fact come to life from the translation of graphic tracks into a sound track. The graphic tracks in question are made up by copies of seismograms recorded during some earthquakes that have taken place around the world. Seismograms are translated into music by a sculpture-instrument, half a seismograph and half a barrel organ. The organ plays through holes practiced on paper. Adapting the documents to the instrument score, holes have been drilled on the waves' peaks. The organ covers about three tonal scales, starting from heavy and deep sounds it reaches up to high and jarring notes. The translation of the seismic records is based on a criterion that does match the highest sounds to larger amplitudes with lower ones to minors. Translating the seismogram in the organ score, the larger the amplitude of recorded waves, the more the seismogram covers the full tonal scale played by the barrel organ and the notes arouse an intense emotional response in the listener. Elisa Strinna's Seismic Symphonies installation becomes an unprecedented tool for emotional involvement, through which can be revived the memory of the greatest disasters of over a century of seismic history of the Earth. A bridge between art and science. Seismic Symphonies is also a symbolic inversion: the instrument of the organ is most commonly used in churches, and its sounds are derived from the heavens and
International Nuclear Information System (INIS)
Zhang Hongkun; Cen Song; Wang Haitao; Cheng Huanyu
2012-01-01
An efficient 3D approach is proposed for simulating the complicated responses of the multi-body structure in reactor core under seismic loading. By utilizing the rigid-body and connector functions of the software Abaqus, the multi-body structure of the reactor core is simplified as a mass-point system interlinked by spring-dashpot connectors. And reasonable schemes are used for determining various connector coefficients. Furthermore, a scripting program is also complied for the 3D parametric modeling. Numerical examples show that, the proposed method can not only produce the results which satisfy the engineering requirements, but also improve the computational efficiency more than 100 times. (authors)
Oviedo, J. A. (Juan Andrés)
2011-01-01
This paper investigates the influence of the story stiffness of reinforced concrete (R/C) frame on the seismic response of R/C buildings with proportional hysteretic dampers. For this purpose, non-linear time-history analyses were conducted on a series of multi-degree-of-freedom system models that include a wide range of structural parameters and vertical distributions of story stiffnesses and strengths of R/C main frame and dampers. Although the basic purpose of damper installation is to red...
International Nuclear Information System (INIS)
Stevenson, J.D.
1985-01-01
The purpose of this paper is to summarize the observations and experience which has been developed relative to the seismic behavior of above-ground, building-supported, industrial type piping (similar to piping used in nuclear power plants) in strong motion earthquakes. The paper also contains observations regarding the response of piping in experimental tests which attempted to excite the piping to failure. Appropriate conclusions regarding the behavior of such piping in large earthquakes and recommendations as to future design of such piping to resist earthquake motion damage are presented based on observed behavior in large earthquakes and simulated shake table testing
Maxillary Sinus Floor Augmentation
DEFF Research Database (Denmark)
Starch-Jensen, Thomas; Jensen, Janek Dalsgaard
2017-01-01
, radiological and histomorphometric outcome as well as complications are presented after maxillary sinus floor augmentation applying the lateral window technique with a graft material, maxillary sinus membrane elevation without a graft material and osteotome-mediated sinus floor elevation with or without...
Post Office Dept., Washington, DC.
Guidelines, methods and policies regarding the care and maintenance of post office building floors are overviewed in this handbook. Procedures outlined are concerned with maintaining a required level of appearance without wasting manpower. Flooring types and characteristics and the particular cleaning requirements of each type are given along with…
McGrath, John
2012-01-01
With all of the hype that green building is receiving throughout the school facility-management industry, it's easy to overlook some elements that may not be right in front of a building manager's nose. It is helpful to examine the role floor covering plays in a green building project. Flooring is one of the most significant and important systems…
Solving decontaminable flooring problems
International Nuclear Information System (INIS)
Anon.
1989-01-01
Pennsylvania Power and Light wanted to cover deteriorating concrete in unit 2 of its Susquehanna BWR with a smooth, durable, decontaminable coating. Traditionally, floors in the plant had been coated with epoxy paint, but many of these floors suffered delamination, and failed in three to five years. Painting with epoxy would also interrupt operations for as much as three days while the floor dried, yet critical instruments in some areas had to be monitored at least once per shift. In addition, conventional floor surface preparation produced dust and vibration around sensitive equipment. The solution was a dustless scabbling system for surface preparation, followed by the installation of a high-strength acrylic industrial floor known as Silakal. The work was carried out by Pentek. Silikal bonds to the underlying concrete, so that delamination of the floor will not occur even under severe traffic conditions. Another advantage of this type of flooring is that it cures in one hour, so floor resurfacing has only minimal impact on plant operations. (author)
Energy Technology Data Exchange (ETDEWEB)
Radtke, U
1984-02-01
The question of whether PPC- and VPE-floor heating pipes can endure damage when incompletely imbedded in the floor finish is investigated in an experimental setup. An expansion of the pipe, caused by a temperature increase from 20/sup 0/C to 50/sup 0/C was measured and considered too small to deduce the degree of danger from the damage.
Directory of Open Access Journals (Sweden)
Said Elias
Full Text Available Abstract The effect of soil-structure interaction (SSI on the dynamic responses of seismically isolated three-span continuous reinforced concrete (RC bridge is investigated. Also, tuned mass damper(s (TMD/s is/are installed to control undesirable bearing displacement, even under the SSI effect. The TMDs are placed at the mid-span of the bridge and each tuned with a modal frequency, while controlling up to first few modes as desirable. The soil surrounding the foundation of pier is modeled by frequency independent coefficients. Dynamic analysis is carried out in time domain using direct integration method. In order to specify the effects of the SSI, the responses of the non-isolated, isolated, and controlled isolated bridge are compared. It is observed that the soil surrounding the pier has significant effects on the bearing displacement of the isolated RC bridges. In addition, it is observed that the seismic responses of isolated RC bridge reduced significantly with installation of the TMDs.
Directory of Open Access Journals (Sweden)
Mosbeh R. Kaloop
2016-10-01
Full Text Available The present study investigates the prediction efficiency of nonlinear system-identification models, in assessing the behavior of a coupled structure-passive vibration controller. Two system-identification models, including Nonlinear AutoRegresive with eXogenous inputs (NARX and adaptive neuro-fuzzy inference system (ANFIS, are used to model the behavior of an experimentally scaled three-story building incorporated with a tuned mass damper (TMD subjected to seismic loads. The experimental study is performed to generate the input and output data sets for training and testing the designed models. The parameters of root-mean-squared error, mean absolute error and determination coefficient statistics are used to compare the performance of the aforementioned models. A TMD controller system works efficiently to mitigate the structural vibration. The results revealed that the NARX and ANFIS models could be used to identify the response of a controlled structure. The parameters of both two time-delays of the structure response and the seismic load were proven to be effective tools in identifying the performance of the models. A comparison based on the parametric evaluation of the two methods showed that the NARX model outperforms the ANFIS model in identifying structures response.
Directory of Open Access Journals (Sweden)
Jianguo Ding
2014-11-01
Full Text Available Portal frame structures are widely used in industrial building design but unfortunately are often damaged during an earthquake. As a result, a study on the seismic response of this type of structure is important to both human safety and future building designs. Traditionally, finite element methods such as the ANSYS and MIDAS have been used as the primary methods of computing the response of such a structure during an earthquake; however, these methods yield low calculation efficiencies. In this paper, the mechanical model of a single-story portal frame structure with two spans is constructed based on the transfer matrix method of multibody system (MS-TMM; both the transfer matrix of the components in the model and the total transfer matrix equation of the structure are derived, and the corresponding MATLAB program is compiled to determine the natural period and seismic response of the structure. The results show that the results based on the MS-TMM are similar to those obtained by ANSYS, but the calculation time of the MS-TMM method is only 1/20 of that of the ANSYS method. Additionally, it is shown that the MS-TMM method greatly increases the calculation efficiency while maintaining accuracy.
International Nuclear Information System (INIS)
Benzoni, Gianmario
2015-01-01
Few observations obtained from extensive experimental programs for the characterization of anti-seismic devices are proposed hereafter. Specifically, few current code requirements, originally intended for the acquisition of fundamental characteristics of performance, proved difficult to be implemented and of questionable significance for the design phase of a seismic isolation application. In particular, for commonly used devices as elastomeric and friction-based isolators, the experimentally validated variation of performance parameters is often not addressed in existing codes and typically neglected in structural models, based on extreme simplification of the device behaviour. The goal of this paper is to suggest an update to specific codes but particularly to solicit the designer’s awareness against oversimplification in the modelling phase of the device performance [it
Directory of Open Access Journals (Sweden)
Mathey Charlie
2015-01-01
Full Text Available The present work investigates on the influence of small geometrical defects on the behavior of slender rigid blocks. A comprehensive experimental campaign was carried out on one of the shake tables of CEA/Saclay in France. The tested model was a massive steel block with standard manufacturing quality. Release, free oscillations tests as well as shake table tests revealed a non-negligible out-of-plane motion even in the case of apparently plane initial conditions or excitations. This motion exhibits a highly reproducible part for a short duration that was used to calibrate a numerical geometrically asymmetrical model. The stability of this model when subjected to 2 000 artificial seismic horizontal bidirectional signals was compared to the stability of a symmetrical one. This study showed that the geometrical imperfections slightly increase the rocking and overturning probabilities under bidirectional seismic excitations in a narrow range of peak ground acceleration.
SONATINA-1: a computer program for seismic response analysis of column in HTGR core
International Nuclear Information System (INIS)
Ikushima, Takeshi
1980-11-01
An computer program SONATINA-1 for predicting the behavior of a prismatic high-temperature gas-cooled reactor (HTGR) core under seismic excitation has been developed. In this analytical method, blocks are treated as rigid bodies and are constrained by dowel pins which restrict relative horizontal movement but allow vertical and rocking motions. Coulomb friction between blocks and between dowel holes and pins is also considered. A spring dashpot model is used for the collision process between adjacent blocks and between blocks and boundary walls. Analytical results are compared with experimental results and are found to be in good agreement. The computer program can be used to predict the behavior of the HTGR core under seismic excitation. (author)
Waveform modeling of the seismic response of a mid-ocean ridge axial melt sill
Xu, Min; Stephen, R. A.; Canales, J. Pablo
2017-12-01
Seismic reflections from axial magma lens (AML) are commonly observed along many mid-ocean ridges, and are thought to arise from the negative impedance contrast between a solid, high-speed lid and the underlying low-speed, molten or partially molten (mush) sill. The polarity of the AML reflection ( P AML P) at vertical incidence and the amplitude vs offset (AVO) behavior of the AML reflections (e.g., P AML P and S-converted P AML S waves) are often used as a diagnostic tool for the nature of the low-speed sill. Time-domain finite difference calculations for two-dimensional laterally homogeneous models show some scenarios make the interpretation of melt content from partial-offset stacks of P- and S-waves difficult. Laterally heterogeneous model calculations indicate diffractions from the edges of the finite-width AML reducing the amplitude of the AML reflections. Rough seafloor and/or a rough AML surface can also greatly reduce the amplitude of peg-leg multiples because of scattering and destructive interference. Mid-crustal seismic reflection events are observed in the three-dimensional multi-channel seismic dataset acquired over the RIDGE-2000 Integrated Study Site at East Pacific Rise (EPR, cruise MGL0812). Modeling indicates that the mid-crustal seismic reflection reflections are unlikely to arise from peg-leg multiples of the AML reflections, P-to- S converted phases, or scattering due to rough topography, but could probably arise from deeper multiple magma sills. Our results support the identification of Marjanović et al. (Nat Geosci 7(11):825-829, 2014) that a multi-level complex of melt lenses is present beneath the axis of the EPR.
International Nuclear Information System (INIS)
Saha, S.; Dasgupta, A.; Basu, P.C.
1993-01-01
Seismic analysis of a Reactor Building is performed idealising the system as a beam model (BM) and also an Axi-symmetric model (ASM) and the results compared. In both the cases effect of Soil-Structure Interaction have been taken Into account. Since the lower boundary of the ASM was at a depth much lower than that of the BM, deconvolution of the specified Free-Field Motion (FFM) was necessary. The deconvolution has been performed using frequency domain approach. (author)
Damage assessment for seismic response of recycled concrete filled steel tube columns
Huang, Yijie; Xiao, Jianzhuang; Shen, Luming
2016-09-01
A model for evaluating structural damage of recycled aggregate concrete filled steel tube (RCFST) columns under seismic effects is proposed in this paper. The proposed model takes the lateral deformation and the effect of repeated cyclic loading into account. Available test results were collected and utilized to calibrate the parameters of the proposed model. A seismic test for six RCFST columns was also performed to validate the proposed damage assessment model. The main test parameters were the recycled coarse aggregate (RCA) replacement percentage and the bond-slip property. The test results indicated that the seismic performance of the RCFST member depends on the RCA contents and their damage index increases as the RCA replacement percentage increases. It is also indicated that the damage degree of RCFST changes with the variation of the RCA replacement percentage. Finally, comparisons between the RCA contents, lateral deformation ratio and damage degree were implemented. It is suggested that an improvement procedure should be implemented in order to compensate for the performance difference between the RCFST and normal concrete filled steel tubes (CFST).
Perceived floor slipperiness and floor roughness in a gait experiment.
Yu, Ruifeng; Li, Kai Way
2015-01-01
Slips and falls contribute to occupational injuries and fatalities globally. Both floor slipperiness and floor roughness affect the occurrence of slipping and falling. Investigations on fall-related phenomena are important for the safety and health of workers. The purposes of this study were to: compare the perceived floor slipperiness before and after walking on the floor; compare the perceived floor slipperiness with and without shoes for males and females; discuss the perceived floor roughness based on barefoot walking; and establish regression models to describe the relationship between perceived floor slipperiness and actual friction of the floors. Male and female subjects walked on 3 m walkways with or without shoes. The perceived floor slipperiness ratings both before and after their walk were collected. The perceived floor slipperiness both before and after walking were significantly affected by both floor and surface conditions. Gender, floor, surface, and footwear conditions were all significant factors affecting the adjustment of perceived floor slipperiness. The subjects made more adjustment on perceived floor slipperiness rating when they had shoes on than when they were barefooted. Regression models were established to describe the relationship between perceived floor slipperiness and floor coefficient of friction. These models may be used to estimate perceived floor slipperiness, or in reverse, the coefficient of friction of the floor, so as to prevent slipping and falling in workplaces.
Seismic analysis of plutonium glovebox by MSC/NASTRAN
International Nuclear Information System (INIS)
Hirata, Masaru; Ishikawa, Kazuya; Korosawa, Makoto; Fukushima, Susumu; Hoshina, Hirofumi.
1993-01-01
Seismic analysis of the structural strength of gloveboxes is important for plutonium confinement evaluation. However, the analytical methods must be developed for evaluating the mutual displacement between the window frame and acrylic resin window panel with regard to plutonium confinement during an earthquake. Therefore, seismic analysis for a standard glovebox in Plutonium Fuel Research Facility at Oarai Research Establishment of JAERI has been conducted by FEM (Finite Element Method) computer code MSC/NASTRAN (MacNeal-Schwendler Corporation NASA Structural Analysis). Modelling of glovebox window frame has been investigated from the results of natural frequency analysis and static analysis. After the acquisition of a suitable model, displacement around the window frame and glovebox structural strength have been evaluated in detail by use of floor response spectrum analysis and time-history (transient response) analysis. (author)
Picozzi, M.; Bindi, D.; Pittore, M.; Kieling, K.; Parolai, S.
2013-04-01
Earthquake early warning systems (EEWS) are considered to be an effective, pragmatic, and viable tool for seismic risk reduction in cities. While standard EEWS approaches focus on the real-time estimation of an earthquake's location and magnitude, innovative developments in EEWS include the capacity for the rapid assessment of damage. Clearly, for all public authorities that are engaged in coordinating emergency activities during and soon after earthquakes, real-time information about the potential damage distribution within a city is invaluable. In this work, we present a first attempt to design an early warning and rapid response procedure for real-time risk assessment. In particular, the procedure uses typical real-time information (i.e., P-wave arrival times and early waveforms) derived from a regional seismic network for locating and evaluating the size of an earthquake, information which in turn is exploited for extracting a risk map representing the potential distribution of damage from a dataset of predicted scenarios compiled for the target city. A feasibility study of the procedure is presented for the city of Bishkek, the capital of Kyrgyzstan, which is surrounded by the Kyrgyz seismic network by mimicking the ground motion associated with two historical events that occurred close to Bishkek, namely the 1911 Kemin ( M = 8.2; ±0.2) and the 1885 Belovodsk ( M = 6.9; ±0.5) earthquakes. Various methodologies from previous studies were considered when planning the implementation of the early warning and rapid response procedure for real-time risk assessment: the Satriano et al. (Bull Seismol Soc Am 98(3):1482-1494, 2008) approach to real-time earthquake location; the Caprio et al. (Geophys Res Lett 38:L02301, 2011) approach for estimating moment magnitude in real time; the EXSIM method for ground motion simulation (Motazedian and Atkinson, Bull Seismol Soc Am 95:995-1010, 2005); the Sokolov (Earthquake Spectra 161: 679-694, 2002) approach for estimating
The roles of the seismic safety and monitoring systems in the PEC fast reactor
International Nuclear Information System (INIS)
Masoni, P.; Di Tullio, E.M.; Massa, B.; Martelli, A.; Sano, T.
1988-01-01
Two different seismic systems are foreseen in the case of PEC: the seismic safety system, that provides the automatic scram, and the seismic monitoring system. During earthquake, three triaxial seismic switches are triggered if a threshold value of the ground acceleration is exceeded. In this case, the signals from the seismic switches are processed by the safety system (with a 2/3 logic) and the shutdown system is triggered. Peak acceleration is the parameter used by the safety system to quantify the seismic event. This way, however, no information is obtained with regard to earthquake frequency content. Thus, reactor safety is guaranteed by adopting a threshold considerably lower than the Z.P.A. of the Design Basis Earthquake. Furthermore, in the case of significant earthquakes, the seismic motion is measured by about 20 triaxial accelerometers, located both in the free field and on the plant's structures. Data are digitazed and recordered by the seismic monitoring system. This system also elaborates the recordered time-histories providing floor response spectra and compares such spectra to the design values. The above-mentioned elaborations and comparisons are performed in short time for two triaxial measuring positions, thus allowing the Operator to immediately get a more complete information on the seismic event. The complete set of data recorded by the seismic monitoring system also allows the actual dynamic response of the plant to be determined and compared to the design values. On the basis of this comparison the necessary safety analysis can be carried out to verify whether the design limits of the plant were respected: in the positive case the reactor can be restarted. (author)
Seismic analysis and testing of nuclear power plants
International Nuclear Information System (INIS)
1979-01-01
The following subjects are discussed in this guide: General Recommendations for seismic classification, loading combinations and allowable limits; seismic analysis methods; implications for seismic design; seismic testing and qualification; seismic instrumentation; modelling techniques; material property characterization; seismic response of soil deposits and earth structures; liquefaction and ground failure; slope stability; sloshing effects in water pools; qualification testing by means of the transport vehicle
Directory of Open Access Journals (Sweden)
Takuya Suzuki
2016-09-01
Full Text Available The uplift behavior of structures subjected to severe seismic motion has not been clarified. This paper presents experimental and analytical studies conducted for clarifying this problem of spread foundation structures on rock. First, centrifugal loading tests are conducted to determine the uplift behavior of these structures, and the uplift behavior of these structures is confirmed. Then, simulation analyses are performed using a three-dimensional FE model and the accuracy of these analyses is confirmed. A comparison between test and analyses results clarified the important analytical conditions required for maintaining analysis precision and the limit of analysis precision.
Validation Data and Model Development for Fuel Assembly Response to Seismic Loads
International Nuclear Information System (INIS)
Bardet, Philippe; Ricciardi, Guillaume
2016-01-01
Vibrations are inherently present in nuclear reactors, especially in cores and steam generators of pressurized water reactors (PWR). They can have significant effects on local heat transfer and wear and tear in the reactor and often set safety margins. The simulation of these multiphysics phenomena from first principles requires the coupling of several codes, which is one the most challenging task in modern computer simulation. Here an ambitious multiphysics multidisciplinary validation campaign is conducted. It relied on an integrated team of experimentalists and code developers to acquire benchmark and validation data for fluid-structure interaction codes. Data are focused on PWR fuel bundle behavior during seismic transients.
Validation Data and Model Development for Fuel Assembly Response to Seismic Loads
Energy Technology Data Exchange (ETDEWEB)
Bardet, Philippe [George Washington Univ., Washington, DC (United States); Ricciardi, Guillaume [Atomic Energy Commission (CEA) (France)
2016-01-31
Vibrations are inherently present in nuclear reactors, especially in cores and steam generators of pressurized water reactors (PWR). They can have significant effects on local heat transfer and wear and tear in the reactor and often set safety margins. The simulation of these multiphysics phenomena from first principles requires the coupling of several codes, which is one the most challenging tasks in modern computer simulation. Here an ambitious multiphysics multidisciplinary validation campaign is conducted. It relied on an integrated team of experimentalists and code developers to acquire benchmark and validation data for fluid-structure interaction codes. Data are focused on PWR fuel bundle behavior during seismic transients.
Subsystem response determination for the US NRC Seismic Safety Margins Research Program
International Nuclear Information System (INIS)
Johnson, J.J.
1979-01-01
The initial portion of the task described deals with a definition of the state-of-the-art of seismic qualification methods for subsystems. Too facilitate treatment of this broad class of subsystems, three classifications have been identified: multiply supported subsystems (e.g., piping systems); mechanical components (e.g., valves, pumps, control rod drives, hydraulic systems, etc.); and electrical components (e.g., electrical control panels). Descriptions of the available analysis and/or testing techniques for the above classifications are sought. The results of this assessment will be applied to the development of structural subsystem transfer functions
ANALYSIS FOR EFFECT OF FPS-TYPED TMD CONTROLLING SEISMIC RESPONSES%FPS型TMD控震效应分析
Institute of Scientific and Technical Information of China (English)
李大望; 关罡; 霍达
2001-01-01
Based on the differential vibration equations of the multi-layer shear-type st ructure controlled by FPS-TMD,the seismic response laws of the structure are ca lculated and analyzed;the results display that the earthquake responses of the b uilding structures can be improved with a reasonable designed FPS-TMD.%基于FPS(Friction Pendulum System)型TMD(Turned Mass Damper)控制的多层剪切型结构振动微分方程，通过时程计算分析了FPS型TMD控震响应规律。结果表明，合理设计的FPS型TMD 控振系统可以改善结构的振动响应。
International Nuclear Information System (INIS)
Goins, N.R.; Lazarewicz, A.R.
1979-01-01
During the Viking mission to Mars, the seismometer on Lander II collected approximately 0.24 Earth years of observations data, excluding periods of time dominated by wind-induced Lander vibration. The ''quiet-time'' data set contains no confirmed seismic events. A proper assessment of the significance of this fact requires quantitative estimates of the expected detection rate of the Viking seismometer. The first step is to calculate the minimum magnitude event detectable at a given distance, including the effects of geometric spreading, anelastic attenuation, seismic signal duration, seismometer frequency response, and possible poor ground coupling. Assuming various numerical quantities and a Martian seismic activity comparable to that of intraplate earthquakes, the appropriate integral gives an expected annual detection rate of 10 events, nearly all of which are local. Thus only two to three events would be expected in the observational period presently on hand and the lack of observed events is not in gross contradiction to reasonable expectations. Given the same assumptions, a seismometer 20 times more sensitive than the present instrument would be expected to detect about 120 events annually
Seismic analysis of ITER fourth PF (Poloidal Field Coil) feeder
International Nuclear Information System (INIS)
Liu, Sumei; Chen, Wei; Song, Yuntao; Ni, Xiaojun; Wang, Zhongwei; Chen, Yonghua; Gong, Chenyu
2014-01-01
The ITER feeder systems connect the ITER magnet systems located inside the main cryostat to the cryo-plant, power-supply and control system interfaces outside the cryostat. The main purpose of the feeders is to convey the cryogenic supply and electrical power to the coils as well as house the instrumentation wiring. The PF busbar which carries 52 kA current will suffer from high Lorentz force due to the background magnetic field inspired by the coils and the self-field between every pair of busbars. Except their mechanical strength and thermal insulation performance must be achieved, the dynamic mechanism on PF structure should be assessed. This paper presents the simulation and seismic analysis on ITER 4th PF feeder including the Coil Terminal Box and S-bend Box (CTB and SBB), the Cryostat Feed-through (CFT), the In-Cryostat-Feeder (ICF), especially for the ground supports and main outer-tube firstly. This analysis aims to study seismic resistance on system design under local seismograms with floor response spectrum, the structural response vibration mode and response duration results of displacement, membrane stress, and bending stress on structure under different directions actuating signals were obtained by using the single-seismic spectrum analysis and Dead Weight analysis respectively. Based on the simulative and analytical results, the system seismic resistance and the integrity of the support structure in the 4th PF feeder have been studied and the detail design confirmed
DEFF Research Database (Denmark)
Olesen, Bjarne W.
2008-01-01
In many countries, hydronic radiant floor systems are widely used for heating all types of buildings such as residential, churches, gymnasiums, hospitals, hangars, storage buildings, industrial buildings, and smaller offices. However, few systems are used for cooling.This article describes a floor...... cooling system that includes such considerations as thermal comfort of the occupants, which design parameters will influence the cooling capacity and how the system should be controlled. Examples of applications are presented....
Seismic and dynamic qualification methods
International Nuclear Information System (INIS)
Lin, C.W.
1985-01-01
This book presents the papers given at a conference on seismic effects on nuclear power plants. Topics considered at the conference included seismic qualification of equipment, multifrequency test methodologies, damping in piping systems, the amplification factor, thermal insulation, welded joints, and response factors for seismic risk analysis of piping
Experimental studies of the seismic response of structures incorporating base isolation systems
International Nuclear Information System (INIS)
Kelly, J.M.; Aiken, I.D.
1989-01-01
Whereas the concept of base isolating structures from the damaging effects of earthquake motions is not new, implementation of the technique is a relatively new occurrence. This has mainly been due to the need for several important developments in materials science and experimental and analytical modeling before base isolation could evolve into a practical approach for seismic design. One of these developments has been the ability to test large-scale isolation systems using simulated seismic loads. These tests have not only proven the performance and reliability of the isolation systems and hardware, but have enabled correlation studies to be undertaken which have confirmed the accuracy of analytical methods and the acceptability of current design procedures. The Earthquake Engineering Research Center (EERC) at the University of California at Berkeley has been an active participant in this work, and this paper reviews some of the achievements of the Center in the last few years. Component tests on single isolators are described. Tests on plain and high damping natural rubber bearings, lead-rubber bearings, sliding bearings, and bearings incorporating uplift resistance mechanisms have been performed. High-shear strain tests on large (up to full scale) elastomeric bearings have been conducted to determine the stability characteristics and limit states of the isolators
International Nuclear Information System (INIS)
Avila, Jorge A.; Martinez, Eduardo
2008-01-01
Based on a ductile frames 25 level building, a non-linear analysis with increased monotonically lateral loads (Push-Over) was made in order to determine its collapse and its principal responses were compared against the time-history seismic responses determined with the SCT-EW-85 record. The seismic-resistance design and faced to gravitational loads was made according to the Complementary Technical Norms of Concrete Structures Design (NTC-Concrete) and the NTC-Seismic of the Mexico City Code (RDF-04), satisfying the limit service states (relative lateral displacement between story height maximum relations, story drifts ≤0.012) and failure (seismic behavior factor, Q = 3). The compressible (soft) seismic zone III b and the office use type (group B) were considered. The non-lineal responses were determined with nominal and over-resistance effects. The comparison were made with base shear force-roof lateral displacement relations, global distribution of plastic hinges, failure mechanics tendency, lateral displacements and story drift and its distribution along the height of the building, local and global ductility demands, etc. For the non-linear static analysis with increased monotonically lateral loads, was important to select the type of lateral forces distribution
Energy Technology Data Exchange (ETDEWEB)
You, Bong; Lee, Jae Han; Ku, Kyung Hoi [Korea Atomic Energy Research Institute, Daeduk (Korea, Republic of)
1996-05-01
The evaluation of acceleration responses of isolated and nonisolated structures according to mechanical features of soils is important. The kinds of soils taken in analyses are soft, medium and hard rocks, and a fixed base condition is also taken for the comparison. The horizontal isolation frequency used is 0.5 Hz. The time history analyses of reference power plant using 1940 El Centro horizontal (NS) and vertical earthquakes are performed to investigate the seismic responses varying with soil characteristics for isolated and nonisolated structures. The horizontal acceleration responses of the horizontal isolated-structures show almost similar values irrespective of the various kinds of soils and are largely decreased in the frequency ranges above 2 hz. The vertical natural frequency, 21Hz of high damping rubber bearing does not affect the vertical acceleration responses in case of soft rock, but largely affects in hard rock condition. For nonisolated structures, the acceleration responses are decreased in both horizontal and vertical directions by taking into account the soils in the analysis model. The extent of reduction of acceleration responses is larger in vertical direction than in horizontal one, as the stiffness of rock becomes softer. 8 tabs., 21 figs., 8 refs. (Author) .new.
International Nuclear Information System (INIS)
You, Bong; Lee, Jae Han; Ku, Kyung Hoi
1996-05-01
The evaluation of acceleration responses of isolated and nonisolated structures according to mechanical features of soils is important. The kinds of soils taken in analyses are soft, medium and hard rocks, and a fixed base condition is also taken for the comparison. The horizontal isolation frequency used is 0.5 Hz. The time history analyses of reference power plant using 1940 El Centro horizontal (NS) and vertical earthquakes are performed to investigate the seismic responses varying with soil characteristics for isolated and nonisolated structures. The horizontal acceleration responses of the horizontal isolated-structures show almost similar values irrespective of the various kinds of soils and are largely decreased in the frequency ranges above 2 hz. The vertical natural frequency, 21Hz of high damping rubber bearing does not affect the vertical acceleration responses in case of soft rock, but largely affects in hard rock condition. For nonisolated structures, the acceleration responses are decreased in both horizontal and vertical directions by taking into account the soils in the analysis model. The extent of reduction of acceleration responses is larger in vertical direction than in horizontal one, as the stiffness of rock becomes softer. 8 tabs., 21 figs., 8 refs. (Author) .new
International Nuclear Information System (INIS)
Mizuno, N.; Iida, T.; Tsushima, Y.; Araki, T.; Nojima, O.
1977-01-01
In this paper, the seismic response analysis is described in detail for estimating the soil-structure interaction effects with the torsional behavior. The analytical method is firstly shown for estimating the stiffness of reactor building by the bending-shear and torsion theory of the thin wall sections in regard to the behavior of structure. The three-dimensional behavior of structure can be obtained more briefly and simply by the proposed method. Secondly, the dynamical soil-foundation coefficient for estimating the dissipation of vibrational energy on the ground is derived by H. Tajimi's theory which is based on a solution of the propagation of seismic waves caused by point excitation on the surface of the elastic half-space medium. The above results give the vibrational impedances of the soil-foundation corresponding to the static soil coefficient, which is defined to the excitation force in the frequency domain. In order to analyze to the equivalues of reactor building, the authors thirdly attempt to approximate the dynamic soil-foundation coefficient as the frequency transfer function of displacement. The complex damping is used for more suitably estimating the elastic structural damping effects of structure. The regression analysis of many degrees of freedom is fourthly attempted for estimating the natural periods annd equivalent viscous damping ratios directly from the experimental results by the forced vibrational test performed in 1974. The analytical results are finally shown for simulating and comparing with the above-mentioned experimental results
Vanacore, E. A.; Baez-Sanchez, G.; Huerfano, V.; Lopez, A. M.; Lugo, J.
2017-12-01
The Puerto Rico Seismic Network (PRSN) is an integral part of earthquake and tsunami monitoring in Puerto Rico and the Virgin Islands. The PRSN conducts scientific research as part of the University of Puerto Rico Mayaguez, conducts the earthquake monitoring for the region, runs extensive earthquake and tsunami education and outreach programs, and acts as a Tsunami Warning Focal Point Alternate for Puerto Rico. During and in the immediate aftermath of Hurricane Maria, the PRSN duties and responsibilities evolved from a seismic network to a major information and communications center for the western side of Puerto Rico. Hurricane Maria effectively destroyed most communications on island, critically between the eastern side of the island where Puerto Rico's Emergency Management's (PREMA) main office and the National Weather Service (NWS) is based and the western side of the island. Additionally, many local emergency management agencies on the western side of the island lost a satellite based emergency management information system called EMWIN which provides critical tsunami and weather information. PRSN's EMWIN system remained functional and consequently via this system and radio communications PRSN became the only information source for NWS warnings and bulletins, tsunami alerts, and earthquake information for western Puerto Rico. Additionally, given the functional radio and geographic location of the PRSN, the network became a critical communications relay for local emergency management. Here we will present the PRSN response in relation to Hurricane Maria including the activation of the PRSN devolution plan, adoption of duties, experiences and lessons learned for continuity of operations and adoption of responsibilities during future catastrophic events.
Improving total-building seismic performance using linear fluid viscous dampers
Del Gobbo, GM; Blakeborough, A; Williams, MS
2018-01-01
Previous research has revealed that Eurocode-compliant structures can experience structural and nonstructural damage during earthquakes. Retrofitting buildings with fluid viscous dampers (FVDs) can improve interstorey drifts and floor accelerations, two structural parameters that characterize seismic demand. Previous research focusing on FVD applications for improving seismic performance has focused on structural performance. Structural parameters such as interstorey drifts and floor accelera...
Improta, Luigi; di Giulio, Giuseppe; Rovelli, Antonio
The city of Benevento (Southern Italy) has been repeatedly struck by large historical earthquakes. A heterogeneous geologic structure and widespread soft soil conditions make the estimation of site effects crucial for the seismic hazard assessment of the city. From 2000 until 2004, we installed seismic stations to collect earthquake data over zones with different geological conditions. Despite the high level of urban noise, we recorded more than 150 earthquakes at twelve sites. This data set yields the first, well documented experimental evidence for weak to moderate local amplifications. We investigated site effects primarily by the classical spectral ratio technique (CSR) using a rock station placed on the Benevento hill as reference. All sites in the Calore river valley and in the eastern part of the Benevento hill show a moderate high-frequency (f > 4 Hz) amplification peak. Conversely, sites in the Sabato river valley share weak-to-moderate amplification in a wide frequency band (from 1-2 to 7-10 Hz), without evident frequency peaks. Application of no-reference-site techniques to earthquake and noise data confirms the results of the CSRs in the sites of the Calore river valley and of the eastern part of the Benevento hill, but fails in providing indications for site effects in the Sabato river valley, being the H/V ratios nearly flat. One-dimensional modeling indicates that the ground motion amplification can be essentially explained in terms of a vertically varying geologic structure. High-frequency narrow peaks are caused by the strong impedance contrast existing between near-surface soft deposits and stiff cemented conglomerates. Conversely, broad-band amplifications in the Sabato river valley are likely due to a more complex layering with weak impedance contrasts both in the shallow and deep structure of the valley.
Musters, G. D.; Bemelman, W. A.; Tanis, P. J.
2014-01-01
Jensen et al describe their experience with reconstruction of the pelvic floor using a biological mesh after extralevator abdominoperineal excision (ELAPE)[1]. The title states that a biological mesh leads to low perineal wound complications and perineal hernia rates. Surprisingly the authors
S. Palmroth; Chris A. Maier; Heather R. McCarthy; A. C. Oishi; H. S. Kim; Kurt H. Johnsen; Gabrial G. Katul; Ram Oren
2005-01-01
Forest floor C02 efflux (Fff) depends on vegetation type, climate, and soil physical properties. We assessed the effects of biological factors on Fff by comparing a maturing pine plantation (PP) and a nearby mature Oak-Hickory-type hardwood forest (HW). Fff was measured...
International Nuclear Information System (INIS)
Scott, M.A.; Holmes, P.A.
1991-01-01
A simplified static analysis methodology is presented for qualifying equipment in moderate and high-hazard facility-use category structures, where the facility use is defined in Design and Evaluation Guidelines for Department of Energy Facilities Subjected to Natural Phenomena Hazards, UCRL-15910. Currently there are no equivalent simplified static methods for determining seismic loads on equipment in these facility use categories without completing dynamic analysis of the facility to obtain local floor accelerations or spectra. The requirements of UCRL-15910 specify the use of open-quotes dynamicclose quotes analysis methods, consistent with Seismic Design Guidelines for Essential Buildings, Chapter 6, open-quotes Nonstructural Elements,close quotes TM5-809-10-1, be used for determining seismic loads on mechanical equipment and components. Chapter 6 assumes that the dynamic analysis of the facility has generated either floor response spectra or model floor accelerations. These in turn are utilized with the dynamic modification factor and the actual demand and capacity ratios to determine equipment loading. This complex methodology may be necessary to determine more exacting loads for hard to qualify equipment but does not provide a simple conservative loading methodology for equipment with ample structural capacity
International Nuclear Information System (INIS)
Park, Jinkyun; Kim, Yochan; Kim, Jung Han; Jung, Wondea; Jang, Seung Cheol
2015-01-01
Highlights: • Response times under seismic events are necessary for human reliability analysis. • Conceptual framework to estimate response times under a seismic event is suggested. • Four kinds of representative contexts in seismic events are considered. • Rules for estimating response times on the representative contexts are extracted. - Abstract: After the Fukushima accident, a couple of novel issues have raised in terms of the safety assessment of nuclear power plants (NPPs). This means that the performance of human operators should be properly evaluated under an extreme event. However, it is unrealistic to collect a sufficient amount of human performance data from a real event, such as a great earthquake. As one of the promising solutions, a conceptual framework is suggested in this paper, which is helpful for estimating the response time data of human operators working in the main control room of NPPs under a seismic event. To this end, the four kinds of representative contexts that could be anticipated from seismic events are identified. Then the response times of human operators who are faced with similar contexts are reviewed from existing literatures and databases. As a result, a couple of rules that allow us to extrapolate the response times of human operators under seismic events are extracted. Although underlying rationales being used for determining these rules are still arguable, it is expected that response times under seismic events could be properly understood along with accumulating those of human operators against non-seismic conditions
Energy Technology Data Exchange (ETDEWEB)
Takeda, T.; Yamanobe, S.; Niihara, Y. [Kajima Corp., Tokyo (Japan)
1994-10-31
It is important in designing a PC cable-stayed bridge to properly estimate the seismic response of the bridge for reduction of the response. In this paper, an improvement of the seismic resistance of PC cable-stayed bridges when dampers are installed between the deck and piers and lateral vibration of the deck is restricted is investigated using a time history response model. PC cable-stayed bridges with a span length of 400 m, particularly two types of bridges of harp and semi-harp are investigated and the following is found by analyzing the case where there are installed hysteresis type dampers (with 1 cm yield displacement and secondary rigidity assumed to be 1/10 times that of initial rigidity, the initial rigidity being parametrically changed.) or viscous type dampers (a damping factor is changed.) The result shows that the dampers can reduce the seismic response of a PC cable-stayed bridge and that a semi-harp configuration of stay cables where stay cable members are substantially vertically arranged is more effective than a harp configuration for the seismic performance of PC cable-stayed bridges. The damper partly bear inertial force of the bridge upon earthquake whereby tension of the stay cable members is reduced and bending moment of the deck is reduced. There is existing an optimum characteristic value of the damper concerning the bending moment of the piers. 5 refs., 7 figs., 2 tabs.
International Nuclear Information System (INIS)
1984-06-01
RFS or Regles Fondamentales de Surete (Basic Safety Rules) applicable to certain types of nuclear facilities lay down requirements with which compliance, for the type of facilities and within the scope of application covered by the RFS, is considered to be equivalent to compliance with technical French regulatory practice. The object of the RFS is to take advantage of standardization in the field of safety, while allowing for technical progress in that field. They are designed to enable the operating utility and contractors to know the rules pertaining to various subjects which are considered to be acceptable by the Service Central de Surete des Installations Nucleaires, or the SCSIN (Central Department for the Safety of Nuclear Facilities). These RFS should make safety analysis easier and lead to better understanding between experts and individuals concerned with the problems of nuclear safety. The SCSIN reserves the right to modify, when considered necessary, any RFS and specify, if need be, the terms under which a modification is deemed retroactive. The aim of this RFS is to define the type, location and operating conditions for seismic instrumentation needed to determine promptly the seismic response of nuclear power plants features important to safety to permit comparison of such response with that used as the design basis
Seismic sensitivity study of a generic CANDU nuclear power plant: Soil-structure interaction
International Nuclear Information System (INIS)
Lee, L.S.S.; Duff, C.G.
1983-01-01
The seismic sensitivity and capability study for a generic CANDU Plant is part of an overall development program of design standardization. The purpose of this paper is to investigate the sensitivities of structural responses and floor response spectra (FRS) to variations of structural and soil parameters. In the seismic design standardization, a wide range of soil conditions is considered and the envelopes of the resulting site spectra (soil-structure interaction effect) are then used for the design of the generic plant. The nuclear island structures considered herein have different relative stiffness and one of them has two layout/structure schemes: one is relatively flexible and the other is moderately stiff. In the preliminary phase of the seismic sensitivity study presented hereby, the soil-structure interaction seismic analysis is based on the half-space modelling (soil-spring lumped-mass) method and the response spectrum method for the seismic responses. Distinct patterns and sensitivity of the site spectrum analysis for structure schemes of different relative stiffness and for different structural elevations are observed and discussed. (orig.)
2003-01-01
MGS MOC Release No. MOC2-357, 11 May 2003This Mars Global Surveyor (MGS) Mars Orbiter Camera (MOC) picture shows a pattern of polygons on the floor of a northern plains impact crater. These landforms are common on crater floors at high latitudes on Mars. Similar polygons occur in the arctic and antarctic regions of Earth, where they indicate the presence and freeze-thaw cycling of ground ice. Whether the polygons on Mars also indicate water ice in the ground is uncertain. The image is located in a crater at 64.8oN, 292.7oW. Sunlight illuminates the scene from the lower left.
Kleinbrod, Ulrike; Burjánek, Jan; Hugentobler, Marc; Amann, Florian; Fäh, Donat
2017-12-01
In this study, the seismic response of two slope instabilities is investigated with seismic ambient vibration analysis. Two similar sites have been chosen: an active deep-seated slope instability at Cuolm da Vi and the geologically, structurally and morphologically similar, but presently not moving Alp Caschlè slope. Both slopes are located at the upper Vorderrheintal (Canton Graubünden, Switzerland). Ambient vibrations were recorded on both slopes and processed by time-frequency polarization and site-to-reference spectral ratio analysis. The data interpretation shows correlations between degree of disintegration of the rock mass and amplification. However, the ambient vibration analysis conducted, does not allow retrieving a resonance frequency that can be related to the total depth of the instability of Cuolm da Vi. Even though seismic waves can be hardly traced in rock instabilities containing open fractures, it was possible to retrieve a dispersion curve and a velocity profile from the array measurement at Cuolm da Vi due to the high level of disintegration of the rock material down to a depth of about 100 m. From the similar amplification pattern at the two sites, we expect a similar structure, indicating that also the slope at Alp Caschlè was active in the past in a similar manner as Cuolm da Vi. However, a smoother increase of amplification with frequency is observed at Alp Caschlè, which might indicate less disintegration of the rock mass in a particular depth range at this site, when comparing to Cuolm da Vi where a high level of disintegration is observed, resulting from the high activity at the slope. From the frequency-dependent amplification, we can distinguish between two parts within both instabilities, one part showing decreasing disintegration of the rock mass with increasing depth, for the other parts less-fractured blocks are observed. Since the block structures are found in the lower part of the instabilities, they might contribute to the
PP and PS seismic response from fractured tight gas reservoirs: a case study
International Nuclear Information System (INIS)
Jianming, Tang; Shaonan, Zhang; Li, Xiang-Yang
2008-01-01
In this paper, we present an example of using PP and PS converted-wave data recorded by digital micro-eletro-mechanical-systems (MEMS) to evaluate a fractured tight gas reservoir from the Xinchang gas field in Sichuan, China. For this, we analyse the variations in converted shear-wave splitting, Vp/Vs ratio and PP and PS impedance, as well as other attributes based on absorption and velocity dispersion. The reservoir formation is tight sandstone, buried at a depth of about 5000 m, and the converted-wave data reveal significant shear-wave splitting over the reservoir formation. We utilize a rotation technique to extract the shear-wave polarization and time delay from the data, and a small-window correlation method to build time-delay spectra that allow the generation of a time-delay section. At the reservoir formation, the shear-wave time delay is measured at 20 ms, about 15% shear-wave anisotropy, correlating with the known gas reservoirs. Furthermore, the splitting anomalies are consistent with the characteristics of other attributes such as Vp/Vs ratio and P- and S-wave acoustic and elastic impedance. The P-wave shows consistent low impedance over the reservoir formation, whilst the S-wave impedance shows relatively high impedance. The calculated gas indicator based on absorption and velocity dispersion yields a high correlation with the gas bearing formations. This confirms the benefit of multicomponent seismic data from digital MEMS sensors
Intermediate disconnection of structures to improve the dynamic and the seismic response
International Nuclear Information System (INIS)
Fabrizio, Cristiano; De Leo, Andrea M.; Di Egidio, Angelo
2016-01-01
In the last years some studies have started to investigate the opportunity to improve the seismic behavior of conventional structures by disconnecting one or more upper stories. An archetype model, constituted by a simple two-degree of freedom system, has been taken as representative of structures where a base isolation or a tuned mass damper scheme is used. The system has a constant total mass, while stiffness and mass ratios are taken as variable parameters. An extensive parametric analysis has been performed to characterize the system. Two different types of behavior maps, one referring to the base isolation and the other to the tuned mass damper, have been obtained. In these maps the regions where a base isolation or a tuned mass damper system works properly are well recognizable and it is also possible to point out some other regions of the parameters space where both systems work well. Some numerical simulations, performed on shear-type systems, have been performed to confirm the results provided by the archetype model.
Seismic response of a nuclear power plant in the presence of a waterproof lining
International Nuclear Information System (INIS)
Chesi, C.; Mitsopoulou, E.
1981-01-01
In the presence of a high water table level or of a deeply embedded foundation a waterproof lining is generally requested. If this lies between two plane surfaces of concrete, a severe earthquake is likely to provoke relative displacements. Thus the lining may break and displacements may be too large for complying with the requirements of pipes, tunnels or adjacent structures. Though, a favourable result is also expected: a reduction of the structure accelerations. The present paper deals with the evaluation of these relative displacements and of the acceleration reduction. The friction properties of linings are studied experimentally and a relative velocity-shear friction relationship is deduced. With reference to this the behaviour of a simple structure is analyzed under seismic excitations - artificial accelerograms and strong motion records - characterized by a noticeable content of medium-low frequency components. The main result is that for a ground acceleration greater than 0.3/0.4 g the sliding is an efficient mechanism to reduce inertia forces (a reduction of about 25% for a ground acceleration of 0.5 g is expected). On the other hand the maximum displacement of the structure from its initial position, in the examined case, is no more than 2 cm, and for this range of values the technological problem of the integrity of the liner is under control. (orig.)
International Nuclear Information System (INIS)
Lee, R.C.; Stephenson, D.E.
1992-01-01
In support of the Savannah River Technology Center (SRTC) effort to develop K-Reactor seismic design basis ground motions, SRTC monitored local high-explosive tests at a ''free-field'' site adjacent to K-Reactor and on the -40 level on the foundation of K-Reactor. The high-explosive tests were part of the SRTC/United States Geological Survey (USGS) regional refraction and attenuation experiment that used deeply buried high explosive charges near New Ellenton, Snelling, and at more distant South Carolina sites. The primary purpose of the Reactor measurements are to compare the relative amplitude and frequency content of ambient noise and shot generated ground motions measured at the K-Reactor foundation level and in the ''free-field'' so that foundation effects to ground motions can be documented and possibly incorporated in the facility design basis. Data analysis indicates that one of the five high explosive tests provided sufficient excitations at K-Reactor to produce satisfactory signal-to-noise between about 1 Hz and 15 Hz. Within this frequency band, Fourier spectral amplitude ratios of motions recorded within the first 10 seconds of first motion show substantial reductions (30 endash 50%) on shot radial and transverse components for frequencies greater than about 3 to 5 Hz. Approximately 50% reductions between 10 to 15 Hz were seen on vertical component ratios, and amplifications of 100% at 4 Hz and 5 Hz endash 6 Hz
Seismic response of three-dimensional topographies using a time-domain boundary element method
Janod, François; Coutant, Olivier
2000-08-01
We present a time-domain implementation for a boundary element method (BEM) to compute the diffraction of seismic waves by 3-D topographies overlying a homogeneous half-space. This implementation is chosen to overcome the memory limitations arising when solving the boundary conditions with a frequency-domain approach. This formulation is flexible because it allows one to make an adaptive use of the Green's function time translation properties: the boundary conditions solving scheme can be chosen as a trade-off between memory and cpu requirements. We explore here an explicit method of solution that requires little memory but a high cpu cost in order to run on a workstation computer. We obtain good results with four points per minimum wavelength discretization for various topographies and plane wave excitations. This implementation can be used for two different aims: the time-domain approach allows an easier implementation of the BEM in hybrid methods (e.g. coupling with finite differences), and it also allows one to run simple BEM models with reasonable computer requirements. In order to keep reasonable computation times, we do not introduce any interface and we only consider homogeneous models. Results are shown for different configurations: an explosion near a flat free surface, a plane wave vertically incident on a Gaussian hill and on a hemispherical cavity, and an explosion point below the surface of a Gaussian hill. Comparison is made with other numerical methods, such as finite difference methods (FDMs) and spectral elements.
A Study of Seismic Capacity of Nuclear Equipment with Seismic Isolation System
Energy Technology Data Exchange (ETDEWEB)
Kim, Min Kyu; Choun, Young Sun; Choi, In Kil; Seo, Jeong Moon
2004-05-15
In this study, the base isolation systems for equipment are presented and the responses of each isolation system are investigated. As for the base isolation systems, a natural rubber bearing (NRB), a high damping rubber bearing (HDRB) and a friction pendulum system (FPS) are selected. The shaking table tests are carried out for three kinds of structural types. As input motions, artificial time histories enveloping the US NRC RG 1.60 spectrum and the probability-based scenario earthquake spectra developed for the Korean nuclear power plant site as well as a typical near-fault earthquake record are used. Uniaxial, biaxial, and triaxial excitations are conducted with PGAs of 0.05, 0.1, 0.2 and 0.25g. Acceleration responses are measured at the top of the equipment model and the floors using an accelerometer. The reduction of the seismic forces transmitted to the equipment models are determined for different isolation systems and input motions.
A Study of Seismic Capacity of Nuclear Equipment with Seismic Isolation System
International Nuclear Information System (INIS)
Kim, Min Kyu; Choun, Young Sun; Choi, In Kil; Seo, Jeong Moon
2004-05-01
In this study, the base isolation systems for equipment are presented and the responses of each isolation system are investigated. As for the base isolation systems, a natural rubber bearing (NRB), a high damping rubber bearing (HDRB) and a friction pendulum system (FPS) are selected. The shaking table tests are carried out for three kinds of structural types. As input motions, artificial time histories enveloping the US NRC RG 1.60 spectrum and the probability-based scenario earthquake spectra developed for the Korean nuclear power plant site as well as a typical near-fault earthquake record are used. Uniaxial, biaxial, and triaxial excitations are conducted with PGAs of 0.05, 0.1, 0.2 and 0.25g. Acceleration responses are measured at the top of the equipment model and the floors using an accelerometer. The reduction of the seismic forces transmitted to the equipment models are determined for different isolation systems and input motions
Effect of the flexibility of the base mat on seismic response of a PWR-reactor building
International Nuclear Information System (INIS)
Waas, G.; Riggs, H.R.
1983-01-01
The flexibility of the base mat influences the stiffness and the radiation damping of foundations, In this paper its effect on the seismic response of an axisymmetric PWR-reactor building is investigated. The base mat of the building is stiffened by cylindrical concrete walls and by a rigid block in the center. Soft and stiff soil conditions are considered. The structure and its foundation are modelled by axisymmetric shell and volume elements with Fourier expansions in the circumferential direction. The soil is treated as a horizontally layered viscoelastic medium. Soil and structure are coupled along nodal rings. The stiffness matrix of the soil is computed using an explicit semi-analytic solution for displacements caused by ring loads acting on the surface or within a layered medium. The analysis is performed in the frequency domain, and the response in the time domain is computed by the fast Fourier transformation. The earthquake response is computed with and without including the flexibility of the relatively stiff base mat. The comparison shows that including the flexibility of the mat has hardly any effect on the resonant frequencies and the damping of the fundamental rocking and vertical modes. This is the case for soft and stiff soil conditions. However, the flexibility of the mat strongly affects the first structural deformation mode, in which the external and internal structures deflect in opposite directions. (orig./HP)
International Nuclear Information System (INIS)
Namita, Yoshio; Kawahata, Jun-ichi; Ichihashi, Ichiro; Fukuda, Toshihiko.
1995-01-01
Component and piping systems in current nuclear power plants and chemical plants are designed to employ many supports to maintain safety and reliability against earthquakes. However, these supports are rigid and have a slight energy-dissipating effect. It is well known that applying high-damping supports to the piping system is very effective for reducing the seismic response. In this study, we investigated the design method of the elastoplastic damper [energy absorber (EAB)] and the seismic design method for a piping system supported by the EAB. Our final goal is to develop technology for applying the EAB to the piping system of an actual plant. In this paper, the vibration test results of the three-dimensional piping model are presented. From the test results, it is confirmed that EAB has a large energy-dissipating effect and is effective in reducing the seismic response of the piping system, and that the seismic design method for the piping system, which is the response spectrum mode superposition method using each modal damping and requires iterative calculation of EAB displacement, is applicable for the three-dimensional piping model. (author)
Response of the ionospheric electron density to different types of seismic events
Directory of Open Access Journals (Sweden)
Y. He
2011-08-01
Full Text Available The electron density data recorded by the Langmuir Probe Instrument (ISL, Instrument Sonde de Langmuir onboard the DEMETER satellite have been collected for nearly 4 yr (during 2006–2009 to perform a statistical analysis. During this time, more than 7000 earthquakes with a magnitude larger than or equal to 5.0 occurred all over the world. For the statistical studies, all these events have been divided into various categories on the basis of the seismic information, including Southern or Northern Hemisphere earthquakes, inland or sea earthquakes, earthquakes at different magnitude levels, earthquakes at different depth levels, isolated events and all events. To distinguish the pre-earthquake anomalies from the possible ionospheric anomalies related to the geomagnetic activity, the data were filtered with the K_{p} index. The statistical results obviously show that the electron density increases close to the epicentres both in the Northern and the Southern Hemisphere, but the position of the anomaly is slightly shifted to the north in the Northern Hemisphere and to the south in the Southern Hemisphere. The electron density related to both inland and sea earthquakes presents an anomaly approximately close to the epicentres, but the anomaly for sea earthquakes is more significant than for inland earthquakes. The intensity of the anomalies is enhanced when the magnitude increases and is reduced when the depth increases. A similar anomaly can also be seen in the statistical results concerning the isolated earthquakes. All these statistical results can help to better understand the preparation process of the earthquakes and their influence up to the ionospheric levels.
Instantaneous response spectrum in seismic testing of nuclear power plant equipment
International Nuclear Information System (INIS)
Morrone, A.
1977-01-01
This paper presents the concept of instantaneous response spectrum (IRS) as the response of single degree of freedom oscillators at a particular time. It demonstrates that a shake table random motion whose standard TRS envelops the RRS does not necessarily satisfy the enveloping requirement instantaneously. That is, any one (or more) instantaneous required response spectrum (IRRS) is not enveloped by any instantaneous test response spectrum (ITRS). Response spectra from different time histories, including single frequency sine beat motion used in resonance testing, are compared for enveloping with maximum response and with the actual response at particular times. These comparisons are given for the enveloping of RRS and IRRS derived with a time history response calculated at a particular building elevation of a nuclear power plant. For the test motion, several of the most severe ITRS derived with a modified EL Centro motion and with a sine beat motion with ten cycles per beat were used. It is shown that although the TRS with the modified EL Centro motion enveloped the given RRS, the selected modified EL Centro ITRS did not envelop the corresponding IRRS. With the sine beat motion, even though the TRS did not fully envelop the given RRS, the resulting sine beat ITRS did not require a larger factor for full IRRS enveloping than those of the modified EL Centro motion
Pelvic floor muscle function in women with pelvic floor dysfunction
DEFF Research Database (Denmark)
Tibaek, Sigrid; Dehlendorff, Christian
2014-01-01
The objectives of this study were to investigate the level of pelvic floor muscle (PFM) function in women with pelvic floor dysfunction (PFD) referred by gynaecologists and urologists for in-hospital pelvic floor muscle training (PFMT), and to identity associated factors for a low level of PFM...
Snieder, R.; Safak, E.
2006-01-01
The motion of a building depends on the excitation, the coupling of the building to the ground, and the mechanical properties of the building. We separate the building response from the excitation and the ground coupling by deconvolving the motion recorded at different levels in the building and apply this to recordings of the motion in the Robert A. Millikan Library in Pasadena, California. This deconvolution allows for the separation of instrinsic attenuation and radiation damping. The waveforms obtained from deconvolution with the motion in the top floor show a superposition of one upgoing and one downgoing wave. The waveforms obtained by deconvolution with the motion in the basement can be formulated either as a sum of upgoing and downgoing waves, or as a sum over normal modes. Because these deconvolved waves for late time have a monochromatic character, they are most easily analyzed with normal-mode theory. For this building we estimate a shear velocity c = 322 m/sec and a quality factor Q = 20. These values explain both the propagating waves and the normal modes.
Directory of Open Access Journals (Sweden)
Jong Wan Hu
2015-01-01
Full Text Available This paper mainly deals with seismic response and performance for self-centering friction damping braces (SFDBs subjected to several maximum- or design-leveled earthquake ground motions. The self-centering friction damping brace members consist of core recentering components fabricated with superelastic shape memory alloy wires and energy dissipation devices achieved through shear friction mechanism. As compared to the conventional brace members for use in the steel concentrically braced frame structure, these self-centering friction damping brace members make the best use of their representative characteristics to minimize residual deformations and to withstand earthquake loads without member replacement. The configuration and response mechanism of self-centering friction damping brace systems are firstly described in this study, and then parametric investigations are conducted through nonlinear time-history analyses performed on numerical single degree-of-freedom spring models. After observing analysis results, adequate design methodologies that optimally account for recentering capability and energy dissipation according to their comparative parameters are intended to be suggested in order to take advantage of energy capacity and to minimize residual deformation simultaneously.
Ghorbanirenani, Iman
This thesis presents two experimental programs together with companion numerical studies that were carried out on reinforced concrete shear walls: static tests and dynamic (shake table) tests. The first series of experiments were monotonic and cyclic quasi-static testing on ductile reinforced concrete shear wall specimens designed and detailed according to the seismic provisions of NBCC 2005 and CSA-A23.3-04 standard. The tests were carried out on full-scale and 1:2.37 reduced scale wall specimens to evaluate the seismic design provisions and similitude law and determine the appropriate scaling factor that could be applied for further studies such as dynamic tests. The second series of experiments were shake table tests conducted on two identical 1:2.33 scaled, 8-storey moderately ductile reinforced concrete shear wall specimens to investigate the effects of higher modes on the inelastic response of slender walls under high frequency ground motions expected in Eastern North America. The walls were designed and detailed according to the seismic provisions of NBCC 2005 and CSA-A23.3-04 standard. The objectives were to validate and understand the inelastic response and interaction of shear, flexure and axial loads in plastic hinge zones of the walls considering the higher mode effects and to investigate the formation of second hinge in upper part of the wall due to higher mode responses. Second mode response significantly affected the response of the walls. This caused inelastic flexural response to develop at the 6th level with approximately the same rotation ductility compared to that observed at the base. Dynamic amplification of the base shear forces was also observed in both walls. Numerical modeling of these two shake table tests was performed to evaluate the test results and validate current modeling approaches. Nonlinear time history analyses were carried out by the reinforced concrete fibre element (OpenSees program) and finite element (VecTor2 program
Comparison of seismic isolation concepts for FBR
International Nuclear Information System (INIS)
Shiojiri, H.; Mazda, T.; Kasai, H.; Kanda, J.N.; Kubo, T.; Madokoro, M.; Shimomura, T.; Nojima, O.
1989-01-01
This paper seeks to verify the reliability and effectiveness of seismic isolation for FBR. Some results of the preliminary study of the program are described. Seismic isolation concepts and corresponding seismic isolation devices were selected. Three kinds of seismically-isolated FBR plant concepts were developed by applying promising seismic isolation concepts to the non-isolated FBR plant, and by developing plant component layout plans and building structural designs. Each plant was subjected to seismic response analysis and reduction in the amount of material of components and buildings were estimated for each seismic isolation concepts. Research and development items were evaluated
Wave passage effects on the seismic response of a maglev vehicle moving on multi-span guideway
Directory of Open Access Journals (Sweden)
J. D. Yau
Full Text Available As a seismic wave travels along the separate supports of an extended structure, the structure is subjected to multiple-support excitation due to seismic wave propagation. Considering the seismic wave passage effect, this paper describes seismic analysis of a maglev vehicle moving on a multiply supported gudieway. The guideway system is modeled as a series of simple beams and the vehicle as a four degrees-of-freedom (DOFs rigid bar equipped with multiple onboard PI+LQR hybrid controllers. The controller is used to regulate control voltage for tuning both magnetic forces of uplift levitation and lateral guidance in the maglev system. Numerical studies show that as a maglev vehicle is equipped with more supported magnets then they can provide more control gains for tuning the guidance forces of the moving vehicle, and mitigate seismic-induced lateral vibration of a maglev vehicle running a guideway.
Ren, Z.; Zhang, Z.; Zhang, H.; Zheng, W.; Zhang, P. Z.
2017-12-01
The widely held understanding that reverse-faulting earthquakes play an important role in building mountains has been challenged by recent studies suggesting that co-seismic landslides of the 2008 Mw 7.9 Wenchuan earthquake led to a net co-seismic lowering of surface height. We use precise estimates of co-seismic landslide volumes to calculate the long-term isostatic response to landsliding during the 2008 Wenchuan earthquake. The total isostatic respond volume is 2.0 km3 which did not change much associated with thickness of Te, however, the distribution of the rebound changes associated with thickness of Te. The total co-seismic mass change could be 1.8 km3. The maximum isostatic response due to Wenchuan earthquake may have been as high as 0.9 meters in the highest Pengguan massif of the central Longmen Shan. We also find that the average net uplift is 0.16 meters within the total landslide region due to the Wenchuan earthquake. Our findings suggest that the local topographic evolution of the middle Longmen Shan region is closely related to repeated tectonic events such as the 2008 Wenchuan Earthquake.
Surgical reconstruction of pelvic floor descent: anatomic and functional aspects.
Wagenlehner, F M E; Bschleipfer, T; Liedl, B; Gunnemann, A; Petros, P; Weidner, W
2010-01-01
The human pelvic floor is a complex structure and pelvic floor dysfunction is seen frequently in females. This review focuses on the surgical reconstruction of the pelvic floor employing recent findings on functional anatomy. A selective literature research was performed by the authors. Pelvic floor activity is regulated by 3 main muscular forces that are responsible for vaginal tension and suspension of the pelvic floor organs, bladder and rectum. A variety of symptoms can derive from pelvic floor dysfunctions, such as urinary urge and stress incontinence, abnormal bladder emptying, fecal incontinence, obstructive bowel disease syndrome and pelvic pain. These symptoms mainly derive, for different reasons, from laxity in the vagina or its supporting ligaments as a result of altered connective tissue. Pelvic floor reconstruction is nowadays driven by the concept that in case of pelvic floor symptoms, restoration of the anatomy will translate into restoration of the physiology and ultimately improve patients' symptoms. The surgical reconstruction of the anatomy is almost exclusively focused on the restoration of the lax pelvic floor ligaments. Exact preoperative identification of the anatomical lesions is necessary to allow for exact anatomical reconstruction with respect to the muscular forces of the pelvic floor. Copyright 2010 S. Karger AG, Basel.
Seismic response characteristics of full-size buildings with base isolation system
International Nuclear Information System (INIS)
Wang, C.Y.; Gvildys, J.
1991-01-01
This paper investigates the response characteristics of full-size reinforced concrete buildings via numerical simulations and actual observations. The test facility consists of two identical three-story buildings constructed side by side at Tohoku University in Sendai, Japan. Since the installation of high-damping isolation bearings in April 1989, data from over twenty earthquakes have been recorded. In this paper, three representative earthquake records, No. 2, No. 6, and No. 17 are used to study the detailed response characteristics. Numerical simulations are carried out with the system response program, SISEC. In general, good agreement has been found between numerical solutions and actual observations. The system is stiff enough to prevent the building displacement under minor earthquakes and wind loads, but is relatively soft for reducing the acceleration response during earthquakes with moderate and strong ground motion. Lessons learned in this effort are applicable to base isolation design of nuclear power plants. 7 refs., 16 figs., 3 tabs
Site-Specific Seismic Site Response Model for the Waste Treatment Plant, Hanford, Washington
Energy Technology Data Exchange (ETDEWEB)
Rohay, Alan C.; Reidel, Steve P.
2005-02-24
This interim report documents the collection of site-specific geologic and geophysical data characterizing the Waste Treatment Plant site and the modeling of the site-specific structure response to earthquake ground motions.
Methods for seismic analysis of nuclear power plants
International Nuclear Information System (INIS)
Gantenbein, F.
1990-01-01
The seismic analysis of a complex structure, such as a nuclear power plant, is done in various steps. An overview of the methods, used in each of these steps will be given in the following chapters: Seismic analysis of the buildings taking into account structures with important mass or stiffness. The input to the building analysis, called ground motion, is described by an accelerogram or a response spectra. In this step, soil structure interaction has to be taken into account. Various methods are available: Impedance, finite element. The response of the structure can be calculated by spectral method or by time history analysis; advantages and limitations of each method will be shown. Calculation of floor response spectrum which are the data for the equipment analysis. Methods to calculate this spectrum will be described. Seismic analysis of the equipments. Presentation of the methods for both monosupported and multisupported equipment will be given. In addition methods to analyse equipments which present non-linearities associated to the boundary conditions such as impacts, sliding will be presented. (author). 30 refs, 15 figs
Chronic pelvic floor dysfunction.
Hartmann, Dee; Sarton, Julie
2014-10-01
The successful treatment of women with vestibulodynia and its associated chronic pelvic floor dysfunctions requires interventions that address a broad field of possible pain contributors. Pelvic floor muscle hypertonicity was implicated in the mid-1990s as a trigger of major chronic vulvar pain. Painful bladder syndrome, irritable bowel syndrome, fibromyalgia, and temporomandibular jaw disorder are known common comorbidities that can cause a host of associated muscular, visceral, bony, and fascial dysfunctions. It appears that normalizing all of those disorders plays a pivotal role in reducing complaints of chronic vulvar pain and sexual dysfunction. Though the studies have yet to prove a specific protocol, physical therapists trained in pelvic dysfunction are reporting success with restoring tissue normalcy and reducing vulvar and sexual pain. A review of pelvic anatomy and common findings are presented along with suggested physical therapy management. Copyright © 2014 Elsevier Ltd. All rights reserved.
Force-displacement response of unreinforced masonry walls for seismic design
International Nuclear Information System (INIS)
Petry, S.
2015-01-01
This thesis submitted to the Swiss Federal Institute of Technology EPFL contributes to the improvement of the design and assessment methods for unreinforced masonry (URM) wall structures built with modern hollow core clay bricks. First, an experimental campaign on the lateral nonlinear in-plane response of URM walls is presented; secondly, an existing dataset on URM walls is extended and reanalysed. A newly developed mechanical model which describes the full force-displacement response of URM walls is described. Two series of URM walls tested under lateral in-plane loading are presented. Throughout the quasi-cyclic tests of all URM walls, the deformations were recorded using a digital photogrammetric measurement system which tracked the displacement field of the walls. Based on these findings, a new mechanical model is proposed which describes the nonlinear force-displacement response of flexural dominated URM walls up to near collapse
Directory of Open Access Journals (Sweden)
Rildova
2005-01-01
Full Text Available Based on the observations in the past earthquake events, the traction elevators in buildings are known to be vulnerable to earthquake induced ground motions. Among several components of an elevator, the counterweight being heaviest is also known to be more susceptible than others. The inertial effects of the counterweight can overstress the guide rails on which it moves. Here we investigate to use the well-known acceleration feedback-based active and semi-active control methods to reduce stresses in the rails. The only way a control action can be applied to a moving counterweight-rail system is through a mass damper placed in the plane of the counterweight. For this, a part of the counterweight mass can be configured as a mass damper attached to a small actuator for an active scheme or to a magneto-rheological damper for a semi-active scheme. A comprehensive numerical study is conducted to evaluate the effectiveness of the proposed configuration of control system. It is observed that the two control schemes are effective in reducing the stress response by about 20 to 25% and improve the system fragility over a good range of seismic intensities.
Valente, Marco; Milani, Gabriele; Shehu, Rafael
2017-07-01
This study presents some FE results regarding the behavior under horizontal loads of two existing masonry towers located in South-East Lombardy, Italy. The towers, albeit unique for geometric and architectural features, show some affinities that justify a comparative analysis, as for instance the location and the similar masonry material. Their structural behavior under horizontal loads is therefore influenced by geometrical issues, such as slenderness, walls thickness, perforations, irregularities, presence of internal vaults, etc., which may be responsible for a peculiar output. The geometry of the towers is deduced from both existing available documentation and in-situ surveys. On the basis of such geometrical data, a detailed 3D realistic mesh is conceived, with a point by point characterization of each single geometric element. The FE models are analyzed under seismic loads acting along geometric axes of the plan section, with non-linear dynamic excitation assumptions. A damage-plasticity material model exhibiting softening in both tension and compression, already available in the commercial code Abaqus, is used for masonry. Non-linear dynamic analyses are performed along both the X and Y directions with a real accelerogram scaled to different peak ground accelerations. Some results presented in this paper show the high vulnerability of ancient masonry towers under horizontal loads.
Green's function representations for seismic interferometry
Wapenaar, C.P.A.; Fokkema, J.T.
2006-01-01
The term seismic interferometry refers to the principle of generating new seismic responses by crosscorrelating seismic observations at different receiver locations. The first version of this principle was derived by Claerbout (1968), who showed that the reflection response of a horizontally layered
Thate, Robert
2012-01-01
The modular flooring system (MFS) was developed to provide a portable, modular, durable carpeting solution for NASA fs Robotics Alliance Project fs (RAP) outreach efforts. It was also designed to improve and replace a modular flooring system that was too heavy for safe use and transportation. The MFS was developed for use as the flooring for various robotics competitions that RAP utilizes to meet its mission goals. One of these competitions, the FIRST Robotics Competition (FRC), currently uses two massive rolls of broadloom carpet for the foundation of the arena in which the robots are contained during the competition. The area of the arena is approximately 30 by 72 ft (approximately 9 by 22 m). This carpet is very cumbersome and requires large-capacity vehicles, and handling equipment and personnel to transport and deploy. The broadloom carpet sustains severe abuse from the robots during a regular three-day competition, and as a result, the carpet is not used again for competition. Similarly, broadloom carpets used for trade shows at convention centers around the world are typically discarded after only one use. This innovation provides a green solution to this wasteful practice. Each of the flooring modules in the previous system weighed 44 lb (.20 kg). The improvements in the overall design of the system reduce the weight of each module by approximately 22 lb (.10 kg) (50 %), and utilize an improved "module-to-module" connection method that is superior to the previous system. The MFS comprises 4-by-4-ft (.1.2-by- 1.2-m) carpet module assemblies that utilize commercially available carpet tiles that are bonded to a lightweight substrate. The substrate surface opposite from the carpeted surface has a module-to-module connecting interface that allows for the modules to be connected, one to the other, as the modules are constructed. This connection is hidden underneath the modules, creating a smooth, co-planar flooring surface. The modules are stacked and strapped
International Nuclear Information System (INIS)
1996-01-01
The Co-ordinated research programme on the benchmark study for the seismic analysis and testing of WWER-type nuclear power plants was initiated subsequent to the request from representatives of Member States. The conclusions adopted at the Technical Committee Meeting on Seismic Issues related to existing nuclear power plants held in Tokyo in 1991 called for the harmonization of methods and criteria used in Member States in issues related to seismic safety. The Consulltants' Meeting which followed resulted in producing a working document for CRP. It was decided that a benchmark study is the most effective way to achieve the principal objective. Two types of WWER reactors (WWER-440/213 and WWER-1000) were selected as prototypes for the benchmark exercise to be tested on a full scale using explosions and/or vibration generators. The two prototypes are Kozloduy Units 5/6 for WWER-1000 and Paks for WWER-440/213 nuclear power plants. This volume of Working material contains reports on data related to floor response spectra of Kozloduy NPP; calculational-experimental examination and ensuring of equipment and pipelines seismic resistance at starting and operating WWER-type NPPs; analysis of design floor response spectra and testing of the electrical systems; experimental investigations and seismic analysis Kozloduy NPP; testing of components on the shaking table facilities and contribution to full scale dynamic testing of Kozloduy NPP; seismic evaluation of the main steam line, piping systems, containment pre-stressing and steel ventilation chimney of Kozloduy NPP
Glazed Tiles as Floor Finish in Nigeria
Directory of Open Access Journals (Sweden)
Toyin Emmanuel AKINDE
2013-09-01
Full Text Available Tile is no doubt rich in antiquity; its primordial show, came as mosaic with primary prospect in sacred floor finish before its oblivion, courtesy of, later consciousness towards wall finish in banquets, kitchens, toilets, restaurants and even bars. Today, its renaissance as floor finish is apparent in private and public architectural structures with prevalence in residential, recreational, commercial, governmental and other spaces. In Nigeria, the use of glazed tiles as floor finish became apparent, supposedly in mid-twentieth century; and has since, witnessed ever increasing demands from all sundry; a development that is nascent and has necessitated its mass production locally with pockets of firms in the country. The latter however, is a resultant response to taste cum glazed tiles affordability, whose divergent sophistication in design, colour, size and shape is believed preferred to terrazzo, carpet and floor flex tile. Accessible as glazed tile and production is, in recent times; its dearth of a holistic literature in Nigeria is obvious. In the light of the latter, this paper examine glazed tiles as floor finish in Nigeria, its advent, usage, production, challenge, benefit and prospect with the hope of opening further frontier in discipline specifics.
Seismic response of high temperature gas-cooled reactor core with block-type fuel, (2)
International Nuclear Information System (INIS)
Ikushima, Takeshi; Honma, Toshiaki.
1980-01-01
For the aseismic design of a high temperature gas-cooled reactor (HTGR) with block-type fuel, it is necessary to predict the motion and force of core columns and blocks. To reveal column vibration characteristics in three-dimensional space and impact response, column vibration tests were carried out with a scale model of a one-region section (seven columns) of the HTGR core. The results are as follows: (1) the column has a soft spring characteristic based on stacked blocks connected with loose pins, (2) the column has whirling phenomena, (3) the compression spring force simulating the gas pressure has the effect of raising the column resonance frequency, and (4) the vibration behavior of the stacked block column and impact response of the surrounding columns show agreement between experiment and analysis. (author)
International Nuclear Information System (INIS)
Ghafory-Ashtiany, M.
2001-01-01
In this paper, the effect of random eccentricity, mass and stiffness parameter on the dynamic characteristics of structure and story shear and torsional response has been comprehensively examined. Numerical results are obtained for a five-story torsional building excited by random excitation with various damping ration and frequency parameter values using both approaches of response calculations-a more accurate complex mode and an approximate normal mode have been used. The results show that the introduction of eccentricity in a direction introduces torsional moments in the system and reduces the direct story shear. For a safe design, eccentricity should be neglected in the calculations for shear, and a value of 0.05 of radius of gyration for calculation of torsional moment should be considered, even if a structure is intended to be symmetrical
Seismic response of the Pickering pressure relief duct to the 1985 Nahanni earthquake
International Nuclear Information System (INIS)
Ghobarah, A.
1995-05-01
The objective of this study is to examine the structural response of the Pickering pressure relief duct when subjected to the ground motion records of the 1985 Nahanni earthquake (December 23, 05:16 GMT, Site 1 - Iverson, N.W.T.). It also includes an estimate of the possible impact on the nuclear safety function of the duct. The structural models developed in an earlier study were used in this analysis. The response to the earthquake ground motion was determined on the basis of the estimated capacities of various components of the duct. The ability of the structure to fulfill its nuclear safety function is discussed. (author). 6 refs., 1 tab., 17 figs
Seleznev, V. S.; Soloviev, V. M.; Emanov, A. F.
The paper is devoted to researches of influence of seismic actions for industrial and civil buildings and people. The seismic actions bring influence directly on the people (vibration actions, force shocks at earthquakes) or indirectly through various build- ings and the constructions and can be strong (be felt by people) and weak (be fixed by sensing devices). The great number of work is devoted to influence of violent seismic actions (first of all of earthquakes) on people and various constructions. This work is devoted to study weak, but long seismic actions on various buildings and people. There is a need to take into account seismic oscillations, acting on the territory, at construction of various buildings on urbanized territories. Essential influence, except for violent earthquakes, man-caused seismic actions: the explosions, seismic noise, emitted by plant facilities and moving transport, radiation from high-rise buildings and constructions under action of a wind, etc. can exert. Materials on increase of man- caused seismicity in a number of regions in Russia, which earlier were not seismic, are presented in the paper. Along with maps of seismic microzoning maps to be built indicating a variation of amplitude spectra of seismic noise within day, months, years. The presence of an information about amplitudes and frequencies of oscillations from possible earthquakes and man-caused oscillations in concrete regions allows carry- ing out soundly designing and construction of industrial and civil housing projects. The construction of buildings even in not seismically dangerous regions, which have one from resonance frequencies coincident on magnitude to frequency of oscillations, emitted in this place by man-caused objects, can end in failure of these buildings and heaviest consequences for the people. The practical examples of detail of engineering- seismological investigation of large industrial and civil housing projects of Siberia territory (hydro power
2010-07-01
... seismic risks in those buildings. Risks and Risk Reduction Strategies ... 41 Public Contracts and Property Management 3 2010-07-01 2010-07-01 false What are Federal... Public Contracts and Property Management Federal Property Management Regulations System (Continued...
International Nuclear Information System (INIS)
Kennedy, R.P.; Short, S.A.; Wesley, D.A.; Lee, T.H.
1975-01-01
The importance of the nonlinear soil-structure interaction effects resulting from substantial base slab uplift occurring during a seismic excitation are evaluated. The structure considered consisted of the containment building and prestressed concrete reactor vessel for a typical HTGR plant. A simplified dynamic mathematical model was utilized consisting of a conventional lumped mass structure with soil-structure interaction accounted for by translational and rotational springs whose properties are determined by elastic half space theory. Three different site soil conditions (a rock site, a moderately stiff soil and a soft soil site) and two levels of horizontal ground motion (0.3g and 0.5g earthquakes) were considered. It may be concluded that linear analysis can be used to conservatively estimate the important behavior of the base slab, even under conditions of substantial base slab uplift. For all cases investigated, linear analysis resulted in higher base overturning moments, greater toe pressures, and greater heel uplift distances than nonlinear analyses. It may also be concluded that the nonlinear effect of uplift does not result in any significant lengthening of the fundamental period of the structure. Also, except in the short period region only negligible differences exist between instructure response spectra based on linear analysis and those based on nonlinear analysis. Finally, for sites in which soil-structure interaction is not significant, as for the rock site, the peak structural response at all locations above the base mat are not significantly influenced by the nonlinear effects of base slab uplift. However, for the two soil sites, the peak shears and moments are, in a few instances, significantly different between linear and nonlinear analyses
The significance of the structural regularity for the seismic response of buildings
International Nuclear Information System (INIS)
Hampe, E.; Goldbach, R.; Schwarz, J.
1991-01-01
The paper gives an state-of-the-art report about the international design practice and submits fundamentals for a systematic approach to the solution of that problem. Different criteria of regularity are presented and discussed with respect to EUROCODE Nr. 8. Still remaining questions and the main topics of future research activities are announced and come into consideration. Frame structures with or without additional stiffening wall elements are investigated to illustrate the qualitative differences of the vibrational properties and the earthquake response of regular and irregular systems. (orig./HP) [de
Seismic response of the 'Cut-and Cover' type reactor containment considering nonlinear soil behavior
International Nuclear Information System (INIS)
El-Tahan, H.; Reddy, D.V.
1979-01-01
This paper describes some parametric studies of dynamic soil-structure interaction for the 'cut-and-cover' reactor concept. The dynamic loading considered is a horizontal earthquake motion. The high frequency ranges, which must be considered in the study of soil-structure interaction for nuclear power plants, and the nonlinearity of soil behavior during strong earthquakes are adequately taken into account. Soil nonlinearity is accounted for in an approximate manner using a combination of the 'equivalent linear method' and the method of complex response with complex moduli. The structure considered is a reinforced concrete containment for a 1100 - MWe power plant, buried in a dense sand medium. (orig.)
Inelastic response of piping systems subjected to in-structure seismic excitation
International Nuclear Information System (INIS)
Campbell, R.D.; Kennedy, R.P.; Trasher, R.D.
1983-01-01
A study was undertaken to examine the inelastic response of single-degree-of-freedom systems and a simple piping system to varying levels of earthquake loading with superimposed static loading. The objective was to examine the conservatism inherent in ASME code rules for the design of piping systems by quantifying the ratio of the dynamic margin to the static margin for various degrees of inelastic strain, system frequencies and instructure time histories. Previous studies of elastic, perfectly-plastic and bilinear strain-hardening, single-degree-of-freedom models subjected to earthquake ground motion records have demonstrated the conservatism in current design methodology and design codes for earthquake resistant design of structures. This study compares response of single degree of freedom and simple piping system subjected to typical in-structure earthquake time histories and focuses on the excess margin inherent in current design criteria for piping systems. It is shown that the factor of safety against failure is variable and is dependent upon the frequency content of the loading, the dynamic characteristics of the piping system and the allowable system ductility. A recommendation is made for revision to current criteria on the basis of maintaining a constant factor of safety for dynamic and static loading
Directory of Open Access Journals (Sweden)
Tsubasa Tani
2017-10-01
Full Text Available A new structural control system using damper-installed shear walls in lower stories with reduced stiffness is proposed for vibration control of high-rise RC buildings. That system has some design variables, i.e., height of shear wall, degree of stiffness reduction at lower stories, and quantity of dampers. In this paper, some parametric studies on the shear-beam model with a stiff beam against two kinds of ground motion, a pulse-type sinusoidal wave and a resonant sinusoidal wave, are conducted to clarify the vibration characteristics of the proposed structural control system. It is shown that the optimal combination of design parameters depends on the input ground motion. It is also shown that it is possible to prevent from increasing the response under the one-cycle sinusoidal input resonant to the lowest mode and reduce the steady-state response under the harmonic input with the resonant fundamental period by reducing the stiffness in the lower structure and increasing the damper deformation.
International Nuclear Information System (INIS)
Riggio, M.D.; Jarecki, S.J.
1977-10-01
This report presents the results of the analysis performed for the seismic qualification of the rotary relay for use in the Trojan and Diablo Canyon Auxiliary Safeguards Cabinets. A finite element model of the cabinet was developed from seismic test results. This model was analytically subjected to a simulated 3D floor acceleration time history that enveloped, simultaneously, the Trojan and the June 1969 Diablo Canyon Safe Shutdown Earthquake requirements. The dynamic response of the cabinet at the mounting location of the rotary relays was determined. The calculated acceleration time histories were converted to response spectra and these response spectra were compared to the test response spectra successfully achieved during the rotary relay seismic qualification tests. It was found that the dynamic motion levels at the rotary relays, when mounted in the Trojan or Diablo Canyon Auxiliary Safeguards Cabinets, do not exceed the levels for which they were previously seismically qualified by tests. Consequently, the rotary relays are seismically qualified for use in the Trojan or Diablo Canyon Auxiliary Safeguards Cabinets
Role of closely spaced modes in the seismic response of equipment and structures
International Nuclear Information System (INIS)
Nelson, F.C.
1975-01-01
The genesis for this study was a need for an explanation of how to combine the peak accelerations, displacements, stresses, etc., which result from a response spectrum analysis of nuclear power plant structures and equipment. The explanation was intended to be comprehensive in the sense that it would be based on a general principle from which the absolute sum, square root of the sum of the squares (SRSS), and double-sum modal recombination rules could be extracted as special cases. The purpose of such a comprehensive explanation was to convince design engineers that these rules, in particular the recently proposed double-sum rule, were logical in their formulation and therefore sensible in their application
Influence of Poroelasticity on the 3D Seismic Response of Complex Geological Media
Directory of Open Access Journals (Sweden)
Wuttke Frank
2017-06-01
Full Text Available Elastic wave propagation in 3D poroelastic geological media with localized heterogeneities, such as an elastic inclusion and a canyon is investigated to visualize the modification of local site responses under consideration of water saturated geomaterial. The extended computational environment herein developed is a direct Boundary Integral Equation Method (BIEM, based on the frequency-dependent fundamental solution of the governing equation in poro-visco elastodynamics. Bardet’s model is introduced in the analysis as the computationally efficient viscoelastic isomorphism to Biot’s equations of dynamic poroelasticity, thus replacing the two-phase material by a complex valued single-phase one. The potential of Bardet’s analogue is illustrated for low frequency vibrations and all simulation results demonstrate the dependency of wave field developed along the free surface on the properties of the soil material.
Effect of lumped mass and support stiffness on pipe seismic response
International Nuclear Information System (INIS)
Chang, P.S.Y.
1986-01-01
In performing pipe stress analysis, generic support stiffness values are typically used to predict the response of the piping systems. Consistent design of every support to match the generic stiffness value is difficult. The difference between the actual and generic stiffness may affect the results of pipe stresses and support reactions. The objective of this study is to develop an acceptance criteria for the actual support stiffness and to avoid unnecessary reanalysis. The support mass in the restraint direction and mass within the pipe span can also affect the piping system behavior and this study will discuss this mass effect as well. Added mass and change in support stiffness will cause the piping system to shift frequency
USE OF BOUNDING ANALYSES TO ESTIMATE THE PREFORMANCE OF A SEISMICALLY ISOLATED STRUCTURE
Directory of Open Access Journals (Sweden)
Gökhan ÖZDEMİR
2017-03-01
Full Text Available Current design approach for seismic isolated structures is to perform bounding analyses. These analyses provide an envelope for the response of the seismic isolated structure rather than focusing on the actual performance. In this study, the success of bounding analyses to estimate performance of a seismic isolated structure, in which the isolation is provided by means of lead rubber bearings (LRBs, is evaluated in a comparative manner. For this purpose, nonlinear response history analyses were performed under the effect of bidirectional ground motion excitations. In bounding analyses, non-deteriorating hysteretic representations were used to model the hysteretic behavior of LRBs. On the other hand, to estimate the actual performance of both the superstructure and isolator units, deteriorating hysteretic idealizations were employed. The deterioration in strength of LRBs was defined as a function of temperature rise in the lead core. The analyzed structure is an existing seismically isolated hospital building and analytically modeled in accordance with its reported design properties for both isolation units and superstructure. Results obtained from analyses where LRBs are idealized by both deteriorating and non-deteriorating hysteretic representations are used in the comparisons. The response quantities used in the comparisons are maximum isolator displacement, maximum isolator force, maximum absolute floor acceleration, and maximum relative story displacements. In an average sense, bounding analyses is found to provide conservative estimates for the selected response quantities and fulfills its intended purpose. However, it is revealed that there may be individual cases where bounding analyses fails to provide a safe envelope.
Seismic dynamic analysis of Heat Exchangers inside of the Auxiliary Buildings in AP1000TM NPP
International Nuclear Information System (INIS)
Di Fonzo, M.; Aragon, J.; Moraleda, F.; Palazuelos, M.; San Vicente, J. L.
2011-01-01
Seismic dynamic analysis was carried out for the Heat Exchangers (RNS-HR) located inside of the Auxiliary Building in AP 1000 T M NPP. The main function of the RNS-HX is to provide shutdown reactor cooling. These equipment's are safety-related. So the seismic analysis was done using the methodology for Seismic Category I (SCI) structures. The most important topic is that the RNS-HX shall withstand the effects of the Safe Shutdown Earthquake (SSE) and maintain the specified design functions. for the analysis, two finite element models (FEM) were built in order to investigate the structural response of the couple system of building and equipment. The response spectra method was used. The floor response spectra (FRS) at the slab-wall connection were used as input Lateral seismic restrain was necessary to added in order to achieve the natural frequency of 33 Hz. The global structural response was obtained by means of the modal combination method indicated in the Regulatory Guide 1.92.
Seismic re-evaluation of Mochovce nuclear power plant. Seismic reevaluation of civil structures
International Nuclear Information System (INIS)
Podrouzek, P.
1997-01-01
In this contribution, an overview of seismic design procedures used for reassessment of seismic safety of civil structures at the Mochovce NPP in Slovak Republic presented. As an introduction, the objectives, history, and current status of seismic design of the NPP have been explained. General philosophy of design methods, seismic classification of buildings, seismic data, calculation methods, assumptions on structural behavior under seismic loading and reliability assessment were described in detail in the subsequent section. Examples of calculation models used for dynamic calculations of seismic response are given in the last section. (author)
International Nuclear Information System (INIS)
Costello, J.F.; Ludwigsen, J.S.; Luk, V.K.; Hessheimer, M.F.
2000-01-01
The Nuclear Power Engineering Corporation of Japan and the US Nuclear Regulatory Commission Office of Nuclear Regulatory Research, are co-sponsoring and jointly funding a Cooperative Containment Research Program at Sandia National Laboratories, Albuquerque, New Mexico, USA. As a part of this program, a steel containment vessel model and contact structure assembly was tested to failure with over pressurization at Sandia on December 11--12, 1996. The steel containment vessel model was a mixed-scale model (1:10 in geometry and 1:4 in shell thickness) of a steel containment for an improved Mark-II Boiling Water Reactor plant in Japan. The contact structure, which is a thick, bell-shaped steel shell separated at a nominally uniform distance from the model, provides a simplified representation of features of the concrete reactor shield building in the actual plant. The objective of the internal pressurization test was to provide measurement data of the structural response of the model up to its failure in order to validate analytical modeling, to find its pressure capacity, and to observe the failure model and mechanisms
International Nuclear Information System (INIS)
Melkumyan, Mikayel; Gevorgyan, Emma
2008-01-01
In recent years seismic isolation technologies in Armenia were extensively applied in construction of multistory buildings. These are 10-17-story residential complexes with parking floors and with floors envisaged for offices, shopping centers, fitness clubs, etc. Also there is a 20-story business centre designed in 2006, which is currently under construction. All mentioned complexes are briefly described in the paper, which is, however, mainly dedicated to the 17-story residential complex designed in 2007. The structural concept, including the new approach on installation of seismic isolation rubber bearings in this building, is described and detailed results of the earthquake response analysis for two cases, i.e. when the building is base isolated and when it has a fixed base, are given. Several time histories were used in the analysis and for both cases the building was analyzed also according to the requirements of the Armenian Seismic Code. Comparison of the obtained results indicates the high effectiveness of the proposed structural concept of isolation system and the need for further improvement of Seismic Code provisions regarding the values of the reduction factors
Seismic Consequence Abstraction
International Nuclear Information System (INIS)
Gross, M.
2004-01-01
The primary purpose of this model report is to develop abstractions for the response of engineered barrier system (EBS) components to seismic hazards at a geologic repository at Yucca Mountain, Nevada, and to define the methodology for using these abstractions in a seismic scenario class for the Total System Performance Assessment - License Application (TSPA-LA). A secondary purpose of this model report is to provide information for criticality studies related to seismic hazards. The seismic hazards addressed herein are vibratory ground motion, fault displacement, and rockfall due to ground motion. The EBS components are the drip shield, the waste package, and the fuel cladding. The requirements for development of the abstractions and the associated algorithms for the seismic scenario class are defined in ''Technical Work Plan For: Regulatory Integration Modeling of Drift Degradation, Waste Package and Drip Shield Vibratory Motion and Seismic Consequences'' (BSC 2004 [DIRS 171520]). The development of these abstractions will provide a more complete representation of flow into and transport from the EBS under disruptive events. The results from this development will also address portions of integrated subissue ENG2, Mechanical Disruption of Engineered Barriers, including the acceptance criteria for this subissue defined in Section 2.2.1.3.2.3 of the ''Yucca Mountain Review Plan, Final Report'' (NRC 2003 [DIRS 163274])
Seismic Consequence Abstraction
Energy Technology Data Exchange (ETDEWEB)
M. Gross
2004-10-25
The primary purpose of this model report is to develop abstractions for the response of engineered barrier system (EBS) components to seismic hazards at a geologic repository at Yucca Mountain, Nevada, and to define the methodology for using these abstractions in a seismic scenario class for the Total System Performance Assessment - License Application (TSPA-LA). A secondary purpose of this model report is to provide information for criticality studies related to seismic hazards. The seismic hazards addressed herein are vibratory ground motion, fault displacement, and rockfall due to ground motion. The EBS components are the drip shield, the waste package, and the fuel cladding. The requirements for development of the abstractions and the associated algorithms for the seismic scenario class are defined in ''Technical Work Plan For: Regulatory Integration Modeling of Drift Degradation, Waste Package and Drip Shield Vibratory Motion and Seismic Consequences'' (BSC 2004 [DIRS 171520]). The development of these abstractions will provide a more complete representation of flow into and transport from the EBS under disruptive events. The results from this development will also address portions of integrated subissue ENG2, Mechanical Disruption of Engineered Barriers, including the acceptance criteria for this subissue defined in Section 2.2.1.3.2.3 of the ''Yucca Mountain Review Plan, Final Report'' (NRC 2003 [DIRS 163274]).
International Nuclear Information System (INIS)
Selvaraj, T.; Chellapandi, P.; Chetal, S.C.
2003-01-01
For the seismic design of nuclear power plants, time history of earthquake ground motion is required basically to generate time histories at various floors of nuclear island as well as at the component support locations. From such time histories, floor response spectra (FRS) can be generated. The basic input is specified as site dependent response spectra (SDRS), from which a set of uncorrelated time histories is generated whose own response spectrum matches with the design response spectra. These time histories have got a great impact on the structural design and economy. For Kalpakkam, the site for PFBR, the seismic input is defined in terms of SDRS for various damping values and its shapes have been arrived already. Synthetic accelerograms have been generated such that the time-history generated response spectrum (THRS) closely matches the SDRS for 5% of critical damping. Time histories have been developed using CASTEM 2000, a multi purpose FE code. This paper deals with the generation methodology and their compliance with ASCE 4-98. (author)
DRY TRANSFER FACILITY SEISMIC ANALYSIS
International Nuclear Information System (INIS)
EARNEST, S.; KO, H.; DOCKERY, W.; PERNISI, R.
2004-01-01
The purpose of this calculation is to perform a dynamic and static analysis on the Dry Transfer Facility, and to determine the response spectra seismic forces for the design basis ground motions. The resulting seismic forces and accelerations will be used in a subsequent calculation to complete preliminary design of the concrete shear walls, diaphragms, and basemat
Community Seismic Network (CSN)
Clayton, R. W.; Heaton, T. H.; Kohler, M. D.; Cheng, M.; Guy, R.; Chandy, M.; Krause, A.; Bunn, J.; Olson, M.; Faulkner, M.; Liu, A.; Strand, L.
2012-12-01
between five and 22 stories tall have been constructed using Google SketchUp. Ambient vibration records are used to identify the first set of horizontal vibrational modal frequencies of the buildings. These frequencies are used to compute the response on every floor of the building, given either observed data or scenario ground motion input at the buildings' base.
Harris, Debra D
2015-01-01
Three flooring materials, terrazzo, rubber, and carpet tile, in patient unit corridors were compared for absorption of sound, comfort, light reflectance, employee perceptions and preferences, and patient satisfaction. Environmental stressors, such as noise and ergonomic factors, effect healthcare workers and patients, contributing to increased fatigue, anxiety and stress, decreased productivity, and patient safety and satisfaction. A longitudinal comparative cohort study comparing three types of flooring assessed sound levels, healthcare worker responses, and patient Hospital Consumer Assessment of Healthcare Providers and Systems (HCAHPS) ratings over 42 weeks. A linear mixed model analysis was conducted to determine significant differences between the means for participant responses and objective sound meter data during all three phases of the study. A significant difference was found for sound levels between flooring type for equivalent continuous sound levels. Carpet tile performed better for sound attenuation by absorption, reducing sound levels 3.14 dBA. Preferences for flooring materials changed over the course of the study. The HCAHPS ratings aligned with the sound meter data showing that patients perceived the noise levels to be lower with carpet tiles, improving patient satisfaction ratings. Perceptions for healthcare staff and patients were aligned with the sound meter data. Carpet tile provides sound absorption that affects sound levels and influences occupant's perceptions of environmental factors that contribute to the quality of the indoor environment. Flooring that provides comfort underfoot, easy cleanability, and sound absorption influence healthcare worker job satisfaction and patient satisfaction with their patient experience. © The Author(s) 2015.
Epackachi, Siamak
The seismic performance of rectangular steel-plate concrete (SC) composite shear walls is assessed for application to buildings and mission-critical infrastructure. The SC walls considered in this study were composed of two steel faceplates and infill concrete. The steel faceplates were connected together and to the infill concrete using tie rods and headed studs, respectively. The research focused on the in-plane behavior of flexure- and flexure-shear-critical SC walls. An experimental program was executed in the NEES laboratory at the University at Buffalo and was followed by numerical and analytical studies. In the experimental program, four large-size specimens were tested under displacement-controlled cyclic loading. The design variables considered in the testing program included wall thickness, reinforcement ratio, and slenderness ratio. The aspect ratio (height-to-length) of the four walls was 1.0. Each SC wall was installed on top of a re-usable foundation block. A bolted baseplate to RC foundation connection was used for all four walls. The walls were identified to be flexure- and flexure-shear critical. The progression of damage in the four walls was identical, namely, cracking and crushing of the infill concrete at the toes of the walls, outward buckling and yielding of the steel faceplates near the base of the wall, and tearing of the faceplates at their junctions with the baseplate. A robust finite element model was developed in LS-DYNA for nonlinear cyclic analysis of the flexure- and flexure-shear-critical SC walls. The DYNA model was validated using the results of the cyclic tests of the four SC walls. The validated and benchmarked models were then used to conduct a parametric study, which investigated the effects of wall aspect ratio, reinforcement ratio, wall thickness, and uniaxial concrete compressive strength on the in-plane response of SC walls. Simplified analytical models, suitable for preliminary analysis and design of SC walls, were
Establishing seismic design criteria to achieve an acceptable seismic margin
International Nuclear Information System (INIS)
Kennedy, R.P.
1997-01-01
In order to develop a risk based seismic design criteria the following four issues must be addressed: (1) What target annual probability of seismic induced unacceptable performance is acceptable? (2). What minimum seismic margin is acceptable? (3) Given the decisions made under Issues 1 and 2, at what annual frequency of exceedance should the Safe Shutdown Earthquake ground motion be defined? (4) What seismic design criteria should be established to reasonably achieve the seismic margin defined under Issue 2? The first issue is purely a policy decision and is not addressed in this paper. Each of the other three issues are addressed. Issues 2 and 3 are integrally tied together so that a very large number of possible combinations of responses to these two issues can be used to achieve the target goal defined under Issue 1. Section 2 lays out a combined approach to these two issues and presents three potentially attractive combined resolutions of these two issues which reasonably achieves the target goal. The remainder of the paper discusses an approach which can be used to develop seismic design criteria aimed at achieving the desired seismic margin defined in resolution of Issue 2. Suggestions for revising existing seismic design criteria to more consistently achieve the desired seismic margin are presented
Experimental Verification of an Instrument to Test Flooring Materials
Philip, Rony; Löfgren, Hans, Dr
2018-02-01
The focus of this work is to validate the fluid model with different flooring materials and the measurements of an instrument to test flooring materials and its force attenuating capabilities using mathematical models to describe the signature and coefficients of the floor. The main contribution of the present work focus on the development of a mathematical fluid model for floors. The aim of the thesis was to analyze, compare different floor materials and to study the linear dynamics of falling impacts on floors. The impact of the hammer during a fall is captured by an accelerometer and response is collected using a picoscope. The collected data was analyzed using matlab least square method which is coded as per the fluid model. The finding from this thesis showed that the fluid model works with more elastic model but it doesn’t work for rigid materials like wood. The importance of parameters like velocity, mass, energy loss and other coefficients of floor which influences the model during the impact of falling on floors were identified and a standardized testing method was set.
Motor cortical representation of the pelvic floor muscles.
Schrum, A; Wolff, S; van der Horst, C; Kuhtz-Buschbeck, J P
2011-07-01
Pelvic floor muscle training involves rhythmical voluntary contractions of the external urethral sphincter and ancillary pelvic floor muscles. The representation of these muscles in the motor cortex has not been located precisely and unambiguously. We used functional magnetic resonance imaging to determine brain activity during slow and fast pelvic floor contractions. Cerebral responses were recorded in 17 healthy male volunteers, 21 to 47 years old, with normal bladder control. Functional magnetic resonance imaging was performed during metronome paced slow (0.25 Hertz) and fast (0.7 Hertz) contractions of the pelvic floor that mimicked the interruption of voiding. To study the somatotopy of the cortical representations, flexion-extension movements of the right toes were performed as a control task. Functional magnetic resonance imaging during pelvic floor contractions detected activity of the supplementary motor area in the medial wall and of the midcingulate cortex, insula, posterior parietal cortex, putamen, thalamus, cerebellar vermis and upper ventral pons. There were no significant differences in activation between slow and fast contractions. Toe movements involved significantly stronger activity of the paracentral lobule (ie the medial primary motor cortex) than did the pelvic floor contractions. Otherwise the areas active during pelvic floor and leg muscle contractions overlapped considerably. The motor cortical representation of pelvic floor muscles is located mostly in the supplementary motor area. It extends further ventrally and anteriorly than the representation of distal leg muscles. Copyright © 2011 American Urological Association Education and Research, Inc. Published by Elsevier Inc. All rights reserved.
Czech Academy of Sciences Publication Activity Database
Kleinbrod, U.; Burjánek, Jan; Hugentobler, M.; Amann, F.; Fäh, D.
2017-01-01
Roč. 211, č. 3 (2017), s. 1428-1448 ISSN 0956-540X Institutional support: RVO:67985530 Keywords : seismic noise * site effects * wave propagation Subject RIV: DC - Siesmology, Volcanology, Earth Structure OBOR OECD: Volcanology Impact factor: 2.414, year: 2016
Czech Academy of Sciences Publication Activity Database
Poggi, V.; Burjánek, Jan; Michel, C.; Fäh, D.
2017-01-01
Roč. 210, č. 2 (2017), s. 645-659 ISSN 0956-540X Institutional support: RVO:67985530 Keywords : joint inversion * earthquake ground motions * seismic noise * site effects Subject RIV: DC - Siesmology, Volcanology, Earth Structure OBOR OECD: Volcanology Impact factor: 2.414, year: 2016
Floor heating maximizes residents` comfort
Energy Technology Data Exchange (ETDEWEB)
Tirkkanen, P.; Wikstroem, T.
1996-11-01
Storing heat in floors by using economical night-time electricity does not increase the specific consumption of heating. According to studies done by IVO, the optimum housing comfort is achieved if the room is heated mainly by means of floor heating that is evened out by window or ceiling heating, or by a combination of all three forms of heating. (orig.)
Seismic isolation in New Zealand
International Nuclear Information System (INIS)
Skinner, R.I.; Robinson, W.H.; McVerry, G.H.
1989-01-01
Bridges, buildings, and industrial equipment can be given increased protection from earthquake damage by limiting the earthquake attack through seismic isolation. A broad summary of the seismic responses of base-isolated structures is of considerable assistance for their preliminary design. Seismic isolation as already used in New Zealand consists of a flexible base or support combined with some form of energy-dissipating device, usually involving the hysteretic working of steel or lead. This paper presents examples of the New Zealand experience, where seismic isolation has been used for 42 bridges, 3 buildings, a tall chimney, and high-voltage capacitor banks. Additional seismic response factors, which may be important for nuclear power plants, are also discussed briefly
Risk based seismic design criteria
International Nuclear Information System (INIS)
Kennedy, R.P.
1999-01-01
In order to develop a risk based seismic design criteria the following four issues must be addressed: (1) What target annual probability of seismic induced unacceptable performance is acceptable? (2) What minimum seismic margin is acceptable? (3) Given the decisions made under Issues 1 and 2, at what annual frequency of exceedance should the safe-shutdown-earthquake (SSE) ground motion be defined? (4) What seismic design criteria should be established to reasonably achieve the seismic margin defined under Issue 2? The first issue is purely a policy decision and is not addressed in this paper. Each of the other three issues are addressed. Issues 2 and 3 are integrally tied together so that a very large number of possible combinations of responses to these two issues can be used to achieve the target goal defined under Issue 1. Section 2 lays out a combined approach to these two issues and presents three potentially attractive combined resolutions of these two issues which reasonably achieves the target goal. The remainder of the paper discusses an approach which can be used to develop seismic design criteria aimed at achieving the desired seismic margin defined in resolution of Issue 2. Suggestions for revising existing seismic design criteria to more consistently achieve the desired seismic margin are presented. (orig.)
International Nuclear Information System (INIS)
Mohanty, W.K.; Yanger Walling, M.; Vaccari, F.; Tripathy, T.; Panza, G.F.
2008-02-01
The P-SV- and SH-wave field in the Talchir basin is simulated along eight profiles: four profiles strike across the basin and the other four are along the basin. The hybrid method, which combines two computational techniques, modal Summation and finite differences, is used to produce multiphase synthetic seismograms. An M = 6 earthquake is considered, with hypocenter along the North Orissa Boundary Fault (NOBF) at a depth of 5 km and with the focal mechanisms parameters: dip = 90 deg., strike = 160 deg. and rake = 180 deg. The peak acceleration (AMAX) along each profile is determined considering the maximum acceleration obtained at the horizontal components. The response spectra ratio (RSR) as a function of frequency is computed for the eight profiles and the higher amplification is seen to increase in correspondence with the thicker sedimentary cover, especially for the radial component. Higher site amplification for all the profiles is observed in the frequency range from 0.5 to 1.4 Hz. To validate the obtained site-effects, the sources, for the profiles across the basin, are placed near to the southern end of the profile and the site amplifications are recomputed. Even if the spatial distribution of AMAX is mainly controlled by the epicentral distance, i.e. the geometrical spreading prevails on local soil effects, the RSR shows a pattern that can be easily correlated with the local site conditions. The RSR at the intersection of the profiles is dependent not only upon the local lithology and sediment thickness but also upon the epicentral distance. The Talchir basin is classified into three zones based on the RSR values: low RSR zone (1.0 - 1.9), intermediate RSR zone (2.0 - 2.8) and high RSR zone (2.9 - 5.2). The PGA estimated for the bedrock model by Bhatia et al. (1999) for the study region is around 0.05 to 0.10 g while the Indian seismic zonation map estimated it to be in the range from 0.1 to 0.2g. In the present study, that considers the effects of
Stuge, Britt; Sætre, Kaja; Ingeborg Hoff, Brækken
2013-08-01
The active straight leg raise (ASLR) test has been proposed as a clinical test for the assessment of pelvic girdle pain (PGP). Little is known about the activation of the pelvic floor muscles (PFM) during ASLR. The main aim of this study was to examine the automatic PFM contraction during ASLR. Specific aims were to compare automatic contraction to rest and to voluntary contraction, to compare PFM contraction during ASLR with and without compression and to examine whether there were any differences in PFM contraction between women with and without clinically diagnosed PGP during ASLR. Forty-nine pairs of women participated in a cross-sectional study with individual, one-to-one matched cases and controls. PFM was assessed by reliable and valid 3D ultrasound at rest, during voluntary and automatic contraction. Test-retest data for the levator hiatus during ASLR showed good repeatability. Significantly automatic PFM contractions occurred when ASLR tests were performed. There was a strong positive correlation between voluntary and automatic PFM contractions. Manual compression reduced the automatic P