Active power compensator of the current harmonics based on the instantaneous power theory
Directory of Open Access Journals (Sweden)
Marian GAICEANU
2005-12-01
Full Text Available The quality of the electrical current becomes a major concern. The proliferation of the power electronic converters, which are used extensively to control electrical apparatus in industrial and commercial applications (dc and ac variable speed motor drives, induction furnaces, power line conditioners, and industrial power supplies, is at the origin of the AC current distribution network pollution and the reactive power demand. These power electronic converters typically draw non-sinusoidal currents from the utility, causing interference with adjacent sensitive loads and limit the utilization of the available electrical supply. The quality of the electrical current thus becomes a significant concern for the distributors of energy and their customers. Recent progress as regards technology of the power electronics brings a capacity of compensation and correction of the harmonic distortion generated by the nonlinear loads. In this paper a parallel active filter prototype capable of reducing the total harmonic distortion in the supply for most current source or adjustable speed drive type loads is presented. A 33 kVA active power filter was developed for harmonic and reactive power compensation based on the instantaneous power theory. The active filter configuration requires the measurement of both the load and filter currents. Experimental results from a prototype active power filter confirm the suitability of the proposed approach. The actual 33kVA prototype converter has been built and tested in the SIEI S.p.A. (Italy laboratory under the Marie Curie Post Doctoral research. The active power compensator is controlled by a high performance DSP platform, resulting in the following active filter features: source current reduction up to the 25th harmonic, 10% THD achievable for current source type loads, efficiency above 97%, does not cause resonance with other loads, operation in the presence of unbalanced loads, reactive power and harmonics
Instantaneous power theory and applications to power conditioning
Akagi, Hirofumi; Aredes, Mauricio
2017-01-01
This new edition, written by a team of experts in the field, is fully updated with information on the latest electric power technology. The instantaneous power theory, or “the p-q theory,” makes clear the physical meaning of what instantaneous real and imaginary power is in a three-phase circuit. Moreover, it provides insight into how energy flows from a source to a load, or circulates between phases, in a three-phase circuit. This theory can be used in the design and understanding of FACTS (Flexible AC Transmission System) compensators. The book introduces many concepts in the field of active filtering that are unique to this edition. It provides a study tool for final year undergraduate students, graduate students and engineers dealing ith harmonic pollution problems, reactive power compensation or power quality in general.
Advanced configuration of hybrid passive filter for reactive power and harmonic compensation
Kececioglu, O. Fatih; Acikgoz, Hakan; Sekkeli, Mustafa
2016-01-01
Harmonics is one of the major power quality problems for power systems. The harmonics can be eliminated by power filters such as passive, active, and hybrid. In this study, a new passive filter configuration has been improved in addition to the existing passive filter configurations. Conventional hybrid passive filters are not successful to compensate rapidly changing reactive power demand. The proposed configure are capable of compensating both harmonics and reactive power at the same time. ...
Advanced configuration of hybrid passive filter for reactive power and harmonic compensation.
Kececioglu, O Fatih; Acikgoz, Hakan; Sekkeli, Mustafa
2016-01-01
Harmonics is one of the major power quality problems for power systems. The harmonics can be eliminated by power filters such as passive, active, and hybrid. In this study, a new passive filter configuration has been improved in addition to the existing passive filter configurations. Conventional hybrid passive filters are not successful to compensate rapidly changing reactive power demand. The proposed configure are capable of compensating both harmonics and reactive power at the same time. Simulation results show that performance of reactive power and harmonic compensation with advanced hybrid passive filter is better than conventional hybrid passive filters.
Directory of Open Access Journals (Sweden)
T. Demirdelen
2016-10-01
Full Text Available In recent years, shunt hybrid active power filters are being increasingly considered as a viable alternative to both passive filters and active power filters for compensating harmonics. In literature, their applications are restricted to balanced systems and low voltage applications and therefore not for industrial applications. This paper investigates the performance of a modular cascaded multilevel inverter based Shunt Hybrid Active Power Filter (SHAPF for reactive power compensation and selective harmonics elimination under distorted/unbalanced grid voltage conditions in medium voltage levels. In the proposed control method, reactive power compensation is achieved successfully with a perceptible amount and the performance results of harmonic compensation are satisfactory. Theoretical analysis and simulation results are obtained from an actual industrial network model in PSCAD. The simulation results are presented for a proposed system in order to demonstrate that the harmonic compensation performance meets the IEEE-519 standard.
DEFF Research Database (Denmark)
Zou, Zhixiang; Wang, Zheng; Cheng, Ming
2012-01-01
This paper presents an digital dual-mode-structure repetitive control approach for the single-phase shunt active power filter (APF), which aims to enhance the tracking ability and eliminate arbitrary order harmonic. The proposed repetitive control scheme blends the characteristics of both odd......-harmonic repetitive control and even-harmonic repetitive control. Moreover, the convergence rate is faster than conventional repetitive controller. Additionally, the parameters have been designed and optimized for the dual-mode structure repetitive control to improve the performance of APF system. Experimental...
Harmonic Analysis and Active Filtering in Offshore Wind Power Plants
DEFF Research Database (Denmark)
Chaudhary, Sanjay Kumar; Freijedo Fernandez, Francisco Daniel; Guerrero, Josep M.
2015-01-01
Due to presence of long high voltage cable networks, and power transformers for the grid connection, the offshore wind power plants (OWPPs) are susceptible to harmonic distortion and resonances. The grid connection of OWPP should not cause the harmonic distortion beyond the permissible limits...... at the point of common coupling (PCC). The resonance conditions should be avoided in all cases. This paper describes the harmonic analysis techniques applied on an OWPP network model. A method is proposed to estimate the harmonic current compensation from a shunt-connected active power filter to mitigate...
Energy Technology Data Exchange (ETDEWEB)
Watanabe, Edson H.; Aredes, Mauricio [Universidade Federal, Rio de Janeiro, RJ (Brazil). Coordenacao dos Programas de Pos-graduacao de Engenharia. Lab. de Eletronica de Potencia]. E-mail: watanabe@coe.ufrj.br, aredes@cce.ufrj.br
1998-07-01
A tutorial about the instantaneous active and reactive power theory, which is valid for balanced and unbalanced three-phase systems, with and without harmonics is presented. Based on this theory the basic concepts involving the operation and design of shunt and series active and passive filters are also discussed. The advantage of the association of active and passive filters are also discussed. The association of shunt and series active filters to form the UPQC (Universal Power Quality Conditions), which guarantees the total compensation of voltage and current harmonics is also presented. As a result of the generalization of the UPFC (Unified Power Flow Controller) associated with the UPQC, the UPLC (Universal Active Power Line Conditioner) is proposed to compensate voltage and current harmonics as well as to control the power flow in a transmission line and regulate the ac bus voltage. (author)
Evaluation of harmonic detection methods for active power filter applications
DEFF Research Database (Denmark)
Asiminoaei, Lucian; Blaabjerg, Frede; Hansen, Steffan
2005-01-01
In the attempt to minimize the harmonic disturbances created by the non-linear loads the choice of the active power filters comes out to improve the filtering efficiency and to solve many issues existing with classical passive filters. One of the key points for a proper implementation of an active...... theories. Then, the work here proposes a simulation setup that decouples the harmonic reference generator from the active filter model and its controller. In this way the selected methods can be equally analyzed and compared with respect to their performance, which helps anticipating possible...
Directory of Open Access Journals (Sweden)
José Luis Monroy-Morales
2017-03-01
Full Text Available Active Power Filters (APFs have been used for reducing waveform distortion and improving power quality. However, this function can be improved by means of a selective harmonic compensation. Since an APF has rating restrictions, it is convenient to have the option of selecting an individual or a set of particular harmonics in order to compensate and apply the total APF capabilities to eliminate these harmonics, in particular those with a greater impact on the Total Harmonic Distortion (THD. This paper presents the development of a new APF prototype based on a three-phase three-level Neutral Point Clamped (NPC inverter with selective harmonic compensation capabilities and reactive power compensation. The selective harmonic compensation approach uses several Synchronous Rotating Frames (SRF, to detect and control individual or a set of harmonics using d and q variables. The APF includes a Three-Dimensional Space Vector Modulator (3D-SVPWM in order to generate the compensation currents. Because of its multilevel topology, the proposed active power filter can be used in diverse power quality applications at sub-transmission and distribution voltage levels. Simulation and experimental results are shown to validate the proposed solution and assess the prototype performance in different scenarios.
Directory of Open Access Journals (Sweden)
Yap Hoon
2017-02-01
Full Text Available In this paper, a refined reference current generation algorithm based on instantaneous power (pq theory is proposed, for operation of an indirect current controlled (ICC three-level neutral-point diode clamped (NPC inverter-based shunt active power filter (SAPF under non-sinusoidal source voltage conditions. SAPF is recognized as one of the most effective solutions to current harmonics due to its flexibility in dealing with various power system conditions. As for its controller, pq theory has widely been applied to generate the desired reference current due to its simple implementation features. However, the conventional dependency on self-tuning filter (STF in generating reference current has significantly limited mitigation performance of SAPF. Besides, the conventional STF-based pq theory algorithm is still considered to possess needless features which increase computational complexity. Furthermore, the conventional algorithm is mostly designed to suit operation of direct current controlled (DCC SAPF which is incapable of handling switching ripples problems, thereby leading to inefficient mitigation performance. Therefore, three main improvements are performed which include replacement of STF with mathematical-based fundamental real power identifier, removal of redundant features, and generation of sinusoidal reference current. To validate effectiveness and feasibility of the proposed algorithm, simulation work in MATLAB-Simulink and laboratory test utilizing a TMS320F28335 digital signal processor (DSP are performed. Both simulation and experimental findings demonstrate superiority of the proposed algorithm over the conventional algorithm.
Three phase active power filter with selective harmonics elimination
Directory of Open Access Journals (Sweden)
Sozański Krzysztof
2016-03-01
Full Text Available This paper describes a three phase shunt active power filter with selective harmonics elimination. The control algorithm is based on a digital filter bank. The moving Discrete Fourier Transformation is used as an analysis filter bank. The correctness of the algorithm has been verified by simulation and experimental research. The paper includes exemplary results of current waveforms and their spectra from a three phase active power filter.
Voltage Harmonics Mitigation through Hybrid Active Power Filter
Directory of Open Access Journals (Sweden)
Anwer Ali Sahito
2016-01-01
Full Text Available Fast dynamic response, high efficiency, low cost and small size of power electronic converters have exponentially increased their use in modern power system which resulted in harmonically distorted voltage and currents. Voltage harmonics mainly caused by current harmonics are more dangerous as performance and expected operating life of other power system equipment are affected by harmonically distorted supply voltage. Electronic filter circuits are used to improve system power quality by mitigating adverse effects of harmonics. Hybrid filters having advantages of both passive and active filters are preferred to resolve the problem of harmonics efficiently and avoiding any chance of resonance. In this paper, a three phase three wire network is considered to supply an adjustable speed drive represented by a resistive load connected across a three phase bridge rectifier. Simulation of the considered system shows THD (Total Harmonic Distortion of 18.91 and 7.61% in supply current and voltage respectively. A HAPF (Hybrid Active Power Filter is proposed to reduce these THD values below 5% as recommended by IEEE Standard-519. P-Q theorem is used to calculate required parameters for proposed filter, which is implemented through hysteresis control. Simulation results confirm the effectiveness of the designed filter as THD for both current and voltage have reduced below allowable limit of 5%.
Instantaneous Power Compensation in Three-Phase Systems by Using p-q-r Theory
DEFF Research Database (Denmark)
Kim, Hyosung; Blaabjerg, Frede; Bak-Jensen, Birgitte
2002-01-01
Three linearly independent instantaneous powers have been defined in the time domain in three-phase four-wire systems with the use of p-q-r theory. Any three-phase circuit can be transformed into three single-phase circuits by the p-q-r transformation Thus the instantaneous powers in any three...
Fujita, Hideaki; Akagi, Hirofumi
1991-01-01
The authors present a combined system with a passive filter and a small-rated active filter, both connected in series with each other. The passive filter removes load produced harmonics just as a conventional filter does. The active filter plays a role in improving the filtering characteristics of the passive filter. This results in a great reduction of the required rating of the active filter and in eliminating all the limitations faced by using only the passive filter, leading to a practica...
Directory of Open Access Journals (Sweden)
Руслан Володимирович Власенко
2016-07-01
Full Text Available Electricity quality improving is extremely relevant nowadays. With such industrial loads as induction motors, induction furnaces, welding machines, controlled or uncontrolled rectifiers, frequency converters and others reactive power, harmonics and unbalance are generated in power grid. Reactive power, higher harmonic currents and asymmetry loads influence the functioning of electric devices and electrical mains. An effective technical solution is the use of new compensating devices, that is active power filters. The emergence of consumers with a unit capacity of four wire networks requires a new approach to building system control active power filter. When designing the active power filter control system the current flowing in the neutral wire must be taken into account. To assess the power balance in the four wire active power filter, scientists have proposed to apply pqr theory of power based on the Clarke transformation. There are different topologies of three-phase four wire active power filters. A visual simulation of Matlab / Simulink model with an active power filter based on pqr theory of power has been created. A method of pulse width modulation with four control channels was used as pulses forming systems with transistor keys. Operating conditions of three-phase four wire active power filter with asymmetry, non-sinosoidal voltage source and asymmetric load have been studied. The correction taking into account the means improving the active power filter has been offered as pqr theory of power does not take into account non-sinosoidal voltage
Shunt hybrid active power filter for harmonic mitigation: A practical ...
Indian Academy of Sciences (India)
The increasing importance of Power Quality problems has been responsible for several improvements in Active Power Filter (APF) typologies in the last decade. The increased cost and switching losses make a pure shunt APF economically impractical for high power applications. In higher power levels shunt Hybrid Active ...
Shunt hybrid active power filter for harmonic mitigation: A practical ...
Indian Academy of Sciences (India)
2016-08-26
Aug 26, 2016 ... The increasing importance of Power Quality problems has been responsible for several improvements in Active Power Filter (APF) typologies in the last decade. The increased cost and switching losses make a pure shunt APF economically impractical for high power applications. In higher power levels ...
Directory of Open Access Journals (Sweden)
Karthikrjan Senthilnathan
2018-02-01
Full Text Available This paper describes about the Hybrid Shunt Active Power Filter (HSAPF for the elimination of the current harmonics in the line side of the three phase three wire systems. The Active Power Filter is based on the Voltage Source Converter (VSC topology. The control strategy for the converter is based on Synchronous Reference Frame (SRF theory. The compensation of harmonics is done by the APF which is connected in the shunt configuration to the system. The Shunt APF has the better compensation of current harmonics. The design and implementation of Shunt active power filter is done by MATLAB/Simulink. The real time implementation by using the ATMEGA 8 Microcontroller. The Simulation and Hardware results shows that the current harmonics are eliminated in the system
Directory of Open Access Journals (Sweden)
Rachid DEHINI
2010-12-01
Full Text Available In this paper, the main aim is to confront the performance of shunt active power filter (SAPF and the shunt hybrid active power filter (SHAPF to achieve flexibility and reliability of the filter devices. Both of the two devices used the classical proportional-integral controller for pulse generation to trigger the inventers MOSFETs. In the adopted hybrid active filter there is a passive power filter with high power rating to filter the low order harmonies and one active filter with low power rating to filter the other high order harmonies. In order to investigate the effectiveness of (SHAPF, the studies have been accomplished using simulation with the MATLAB-SIMULINK. The results show That (SHAPF is more effective than (SAPF, and has lower cost.
Harmonic Active Filtering and Impedance-based Stability Analysis in Offshore Wind Power Plants
DEFF Research Database (Denmark)
Dhua, Debasish; Yang, Guangya; Zhang, Zhe
2017-01-01
installation and provides effectively similar functionality as passive filters. This work is focused on harmonic propagation studies in wind power plants, power quality evaluation at the point of connection and harmonic mitigation by active filtering. Finally, an impedance-based stability analysis......Nowadays, to eliminate harmonics injected by the wind turbines in offshore wind power plants there is a need to install passive filters. Moreover, the passive filters are not adaptive to harmonic profile changes due to topology changes, grid loading etc. Therefore, active filters in wind turbines...... are proposed as a flexible harmonic mitigation measure. The motivation of this study is to explore the possibility of embedding active filtering in wind turbine grid-side converters without having to change the system electrical infrastructure. The active filtering method can prevent additional equipment...
DEFF Research Database (Denmark)
Sun, Xiaofeng; Han, Ruijing; Shen, Hong
2016-01-01
voltages. This paper proposes a double-resistive active power filter (D-RAPF) system consisting of a terminal-RAPF and an attenuation-RAPF for each individual harmonic. The terminal-RAPF operating as the characteristic impedance of the feeder is installed at the end bus to suppress harmonic propagation......Harmonic propagation between power-factor correction capacitors and system inductors seriously deteriorates power quality in a radial power distribution feeder. Installation of a resistive active power filter (RAPF) at the end bus only suppresses harmonic propagation, not attenuates harmonic...... at all harmonic frequencies. The attenuation-RAPF, whose control gain can be set according to the requirements of the harmonic voltage distortion limit, is installed at a specific position for each individual harmonic to attenuate the corresponding harmonic voltages. The D-RAPF system not only suppresses...
Series active power filter in power conditioning
Energy Technology Data Exchange (ETDEWEB)
Turunen, J.
2009-07-01
Power quality has become an important issue nowadays for several reasons, e.g. modern society's growing dependence on electricity and the fact that poor power quality may generate significant economic losses in few moments. Probable power quality problems are, e.g. harmonics, flicker, voltage dips and supply interruptions. The power quality may be improved by using filters and compensators.The purpose of this thesis is to research the operation of the series active power filter (SAPF) in power conditioning. Therefore, this thesis presents a comparison of three series hybrid active power filters (SHAPFs) in current harmonics filtering. In addition to this, it is shown how the voltage dip compensation performance of the SAPF is improved in a unified power quality conditioner (UPQC) application.The three SHAPFs included in the comparison are series connected topology (SCT), filter connected topology (FCT) and electrically tuned LC shunt circuit (ETLC). The operating principle of these filters is to direct the harmonic currents produced by the load to flow in the LC shunt circuits instead of the supply. In the case of the SCT this phenomenon is boosted by applying so-called active resistance in the supply branch using the SAPF. In the case of the FCT a similar action is achieved by applying the compensation voltage in series with the LC shunt circuits using the SAPF. In the case of the ETLC the performance of the LC shunt circuit is enhanced by applying so-called active inductances in series with the LC shunt circuit using the SAPF. The SHAPFs are compared by searching for their best current filtering performance using various main circuit and control system configurations and loads. The operation of the SHAPFs is first analysed mathematically. After this, the current filtering performance of the SHAPFs is inspected using simulations and experimental tests. The experimental tests are carried out using SHAPF prototypes. As a result, it is shown that the current
Swain, Sushree Diptimayee; Ray, Pravat Kumar; Mohanty, K. B.
2016-06-01
This research paper discover the design of a shunt Passive Power Filter (PPF) in Hybrid Series Active Power Filter (HSAPF) that employs a novel analytic methodology which is superior than FFT analysis. This novel approach consists of the estimation, detection and classification of the signals. The proposed method is applied to estimate, detect and classify the power quality (PQ) disturbance such as harmonics. This proposed work deals with three methods: the harmonic detection through wavelet transform method, the harmonic estimation by Kalman Filter algorithm and harmonic classification by decision tree method. From different type of mother wavelets in wavelet transform method, the db8 is selected as suitable mother wavelet because of its potency on transient response and crouched oscillation at frequency domain. In harmonic compensation process, the detected harmonic is compensated through Hybrid Series Active Power Filter (HSAPF) based on Instantaneous Reactive Power Theory (IRPT). The efficacy of the proposed method is verified in MATLAB/SIMULINK domain and as well as with an experimental set up. The obtained results confirm the superiority of the proposed methodology than FFT analysis. This newly proposed PPF is used to make the conventional HSAPF more robust and stable.
DEFF Research Database (Denmark)
Chen, Zhe; Pedersen, John Kim; Blaabjerg, Frede
2004-01-01
A hybrid compensation system consisting of an active filter and a group of distributed passive filters has been studied previously. The passive filters are used for each distorting load or Dispersed Generation (DG) unit to remove major harmonics and provide reactive power compensation. The active...... filter is connected in parallel with the distributed passive filters and loads/DGs to correct the system unbalance and remove the remaining harmonic components. The effectiveness of the presented compensation system has also been demonstrated. This paper studies the performance of the hybrid compensation...... demonstrated that the harmonic resonance can be damped effectively. The hybrid filter system is an effective compensation system for dispersed generation systems. In the compensation system, the passive filters are mainly responsible for main harmonic and reactive power compensation of each individual load/ DG...
DEFF Research Database (Denmark)
Lee, Tzung-Lin; Wang, Yen-Ching; Li, Jian-Cheng
2015-01-01
Unintentional series and/or parallel resonances, due to the tuned passive filter and the line inductance, may result in severe harmonic distortion in the industrial power system. This paper presents a hybrid active filter to suppress harmonic resonance and reduce harmonic distortion as well...... expensive. A reasonable trade-off between filtering performances and cost is to use the hybrid active filter. Design consideration are presented and experimental results are provided to validate effectiveness of the proposed method. Furthermore, this paper discusses filtering performances on line impedance...
A hybrid active filter for damping of harmonic resonance in industrial power systems
Fujita, Hideaki; Yamasaki, Takahiro; Akagi, Hirofumi
1998-01-01
This paper proposes a hybrid active filter for damping of harmonic resonance in industrial power systems. The hybrid filter consists of a small-rated active filter and a 5th tuned passive filter. The active filter is characterized by detecting the 5th harmonic current flowing into the passive filter. It is controlled in such a way as to behave as a negative or positive resistor by adjusting a feedback gain from a negative to positive value, and vice versa. The negative resistor presented by t...
Direct harmonic voltage control strategy for shunt active power filter
DEFF Research Database (Denmark)
Munir, Hafiz Mudassir; Zou, JianXiao; Xie, Chuan
2017-01-01
generation system (DPGS) where the nonlinear loads are highly dispersed. Local harmonic voltage detection based Resistive-APF (R-APF) seems more suitable to be applied in the DPGS, however, R-APF suffers from poor compensation performance and difficulty of parameter tuning. In this paper, a direct harmonic...... voltage control strategy for the S-APF is proposed with local point of common coupling (PCC) voltage detection only. The control strategy design procedure is given in detail. Simulation is conducted in Matlab/Simulink to compare the performance between the R-APF and the proposed method. The results...
Shunt hybrid active power filter for harmonic mitigation: A practical ...
Indian Academy of Sciences (India)
shunt HAPF, APF is connected in series with PPF and the whole system is connected in parallel to the load. ... LC filter, it will force a fundamental reactive current to flow into it. ..... Since SHAPF is operating as a boost rectifier, d.c. voltage.
Study on A Control Method of PAPF for Resonance Damping and Harmonics Compensation in Power System
DEFF Research Database (Denmark)
Zhou, Fang; Wu, Longhui; Chen, Zhe
2009-01-01
In power system, capacitors are widely used to compensate reactive power, which generally cause resonance problems in harmonic distorted network. In this paper, A method of using a parallel active power filter (PAPF) to damp the resonances is proposed. The proposed method is compound with traditi......In power system, capacitors are widely used to compensate reactive power, which generally cause resonance problems in harmonic distorted network. In this paper, A method of using a parallel active power filter (PAPF) to damp the resonances is proposed. The proposed method is compound...... with traditional method, it shows that whether the capacitor current is included in the detecting current of PAPF or not. Also the PAPF with proposed method has strong ability in harmonic compensation. Finally, the experiment results are presented to verify the analysis....
de Rooij, Michael Andrew; Steigerwald, Robert Louis; Delgado, Eladio Clemente
2008-12-16
Photovoltaic power converter system including a controller configured to reduce load harmonics is provided. The system comprises a photovoltaic array and an inverter electrically coupled to the array to generate an output current for energizing a load connected to the inverter and to a mains grid supply voltage. The system further comprises a controller including a first circuit coupled to receive a load current to measure a harmonic current in the load current. The controller includes a second circuit to generate a fundamental reference drawn by the load. The controller further includes a third circuit for combining the measured harmonic current and the fundamental reference to generate a command output signal for generating the output current for energizing the load connected to the inverter. The photovoltaic system may be configured to compensate harmonic currents that may be drawn by the load.
Analysis and control of a shunt active power filter
Energy Technology Data Exchange (ETDEWEB)
Ottersten, R.; Petersson, Andreas [Chalmers Univ. of Technology, Goeteborg (Sweden). Dept. of Electric Power Engineering
1999-09-01
This report deals with active power filtering of low-frequency current harmonics. The active filter consists of a forced-commutated voltage source inverter with a digital control system. The aim of this master thesis is to investigate the performance of a shunt active power filter, and the parameters influence on the system performance. Three different harmonic identification methods are presented and compared. The shunt active power filter is very well suited for harmonic current reduction, provided that the phase shift due to the digital implementation of the control system is compensated. The performance of the active power filter depends on the switching frequency. When using individual harmonic detection methods the amount of compensation can be fully controlled for each current harmonic.
A Lyapunov Stability Theory-Based Control Strategy for Three-Level Shunt Active Power Filter
Directory of Open Access Journals (Sweden)
Yijia Cao
2017-01-01
Full Text Available The three-phase three-wire neutral-point-clamped shunt active power filter (NPC-SAPF, which most adopts classical closed-loop feedback control methods such as proportional-integral (PI, proportional-resonant (PR and repetitive control, can only output 1st–25th harmonic currents with 10–20 kHz switching frequency. The reason for this is that the controller design must make a compromise between system stability and harmonic current compensation ability under the condition of less than 20 kHz switching frequency. To broaden the bandwidth of the compensation current, a Lyapunov stability theory-based control strategy is presented in this paper for NPC-SAPF. The proposed control law is obtained by constructing the switching function on the basis of the mathematical model and the Lyapunov candidate function, which can avoid introducing closed-loop feedback control and keep the system globally asymptotically stable. By means of the proposed method, the NPC-SAPF has compensation ability for the 1st–50th harmonic currents, the total harmonic distortion (THD and each harmonic content of grid currents satisfy the requirements of IEEE Standard 519-2014. In order to verify the superiority of the proposed control strategy, stability conditions of the proposed strategy and the representative PR controllers are compared. The simulation results in MATLAB/Simulink (MathWorks, Natick, MA, USA and the experimental results obtained on a 6.6 kVA NPC-SAPF laboratory prototype validate the proposed control strategy.
Singh, Yashi; Hussain, Ikhlaq; Singh, Bhim; Mishra, Sukumar
2018-03-01
In this paper, power quality features such as harmonics mitigation, power factor correction with active power filtering are addressed in a single-stage, single-phase solar photovoltaic (PV) grid tied system. The Power Balance Theory (PBT) with perturb and observe based maximum power point tracking algorithm is proposed for the mitigation of power quality problems in a solar PV grid tied system. The solar PV array is interfaced to a single phase AC grid through a Voltage Source Converter (VSC), which provides active power flow from a solar PV array to the grid as well as to the load and it performs harmonics mitigation using PBT based control. The solar PV array power varies with sunlight and due to this, the solar PV grid tied VSC works only 8-10 h per day. At night, when PV power is zero, the VSC works as an active power filter for power quality improvement, and the load active power is delivered by the grid to the load connected at the point of common coupling. This increases the effective utilization of a VSC. The system is modelled and simulated using MATLAB and simulated responses of the system at nonlinear loads and varying environmental conditions are also validated experimentally on a prototype developed in the laboratory.
Power quality issues current harmonics
Mikkili, Suresh
2015-01-01
Power Quality Issues: Current Harmonics provides solutions for the mitigation of power quality problems related to harmonics. Focusing on active power filters (APFs) due to their excellent harmonic and reactive power compensation in two-wire (single phase), three-wire (three-phase without neutral), and four-wire (three-phase with neutral) AC power networks with nonlinear loads, the text:Introduces the APF technology, describing various APF configurations and offering guidelines for the selection of APFs for specific application considerationsCompares shunt active filter (SHAF) control strategi
Energy Technology Data Exchange (ETDEWEB)
Mino Aguilar, Gerardo
1999-05-01
In here it is presented a brief review of the state of art of power active filters used in the common coupling points between AC sources and nonlinear loads formed by static converters of AC/DC, for the suppression of harmonic currents and instantaneous compensation of the reactive power. Starting off from the active filters that affect only the three balanced currents of the three-phase systems of 3 wires, it is arrived at the subject of this thesis, whose objective is to solve the problem of the reactive compensation and suppression of harmonic currents in the three phases as well as in the neuter of the three-phase systems of 4 wires. The main contribution of this thesis is the design, analysis and simulation of an active filter that besides of suppressing the harmonic currents and compensating the power factor in the three phases of an unbalanced three-phase system, also has the capacity of removing the current that circulates in the neuter due to the unbalance of the phase currents. This design is based on the extension of the theory of the instantaneous reactive power that includes the existence of the zero sequence components of in the phase currents. It is set out in the thesis a novel filter based on an three-phase inverter of 4 branches, 3 branches of phase and one branch of neuter, that to the best knowledge of the author it has not been reported in the literature. Use is made of an extensive number of simulation results to prove the validity of this filter, whose behavior is superior to the filters for suppression of currents in the neuter existing in the literature, of which also a comparative study is presented. The thesis also includes a mathematical and graphical analysis of the symmetrical components in balanced and unbalanced systems in order to know the nature of the harmonic currents of zero sequence. It is included a section on causes and effects of the harmonic contamination problem. [Spanish] Se presenta un breve revision del estado del
Energy Technology Data Exchange (ETDEWEB)
Karimi, S.; Saadate, S. [Groupe de Recherche en Electrotechnique et Electronique de Nancy, GREEN-UHP, CNRS UMR 7037 (France); Poure, P. [Laboratoire d' Instrumentation Electronique de Nancy, LIEN, EA 3440, France Nancy Universite - Universite Henri Poincare de Nancy I, BP 239, 54506 Vandoeuvre les Nancy cedex (France)
2008-11-15
This paper discusses the design, implementation, experimental validation and performances of a fully digital fast power switch fault detection and compensation for three-phase shunt active power filters. The approach introduced in this paper minimizes the time interval between the fault occurrence and its diagnosis. This paper demonstrates the possibility to detect a faulty switch of the active filter in less than 10 {mu}s by using simultaneously a ''time criterion'' and a ''voltage criterion''. In order to attain this fast detection time a FPGA (Field Programmable Gate Array) is used. The other feature introduced in this approach is that the control scheme used to compensate the current load harmonics and fault tolerant scheme are both programmed in only one FPGA. ''FPGA in the loop'' prototyping results and fully experimental results based on a real active power filter verify satisfactory performances of the proposed method. (author)
International Nuclear Information System (INIS)
Chao, C; To, H P; Grantham, C; Rahman, M F
2006-01-01
An active power filter improves the electric power quality through the compensation of harmonics in the power network. A current-source active power filter using a conventional copper inductor for its energy storage has a significant power loss. The loss in the copper inductor can be substantially reduced by using a high-temperature superconducting (HTS) inductor instead. Experiments have been conducted on a prototype current-source active power filter for studying the power loss reduction effect and harmonics compensation performance of the active power filter using a HTS inductor. Experimental results are analysed and discussed in this paper
Energy Technology Data Exchange (ETDEWEB)
Kilic, Tomislav; Milun, Stanko; Petrovic, Goran [FESB University of Split, Faculty of Electrical Engineering, Machine Engineering and Naval Architecture, R. Boskovica bb, 21000, Split (Croatia)
2007-02-15
The shunt active power filters are used to attenuate the harmonic currents in power systems by injecting equal but opposite compensating currents. Successful control of the active filters requires an accurate current reference. In this paper the current reference determination based on predictive filtering structure is presented. Current reference was obtained by taking the difference of load current and its fundamental harmonic. For fundamental harmonic determination with no time delay a combination of digital predictive filter and low pass filter is used. The proposed method was implemented on a laboratory prototype of a three-phase active power filter. The algorithm for current reference determination was adapted and implemented on DSP controller. Simulation and experimental results show that the active power filter with implemented predictive filtering structure gives satisfactory performance in power system harmonic attenuation. (author)
HARMONICS ANALYSIS OF SYSTEM USING SHUNT ACTIVE POWER FILTER BY MATLAB SIMULATION
VAISHALI PARDHI; Dr.A K KORI
2017-01-01
The widely use of nonlinear loads, such as diode and thyristor, rectifiers, computers, consumer electronics, uninterruptible power supplies and adjustable speed drives results in the distorted current waveforms in the electrical distribution systems. Harmonics is a major problem in power systems that have become serious recently owing to the wide use of power electronics-related equipment. The input power factor of most of these equipments is poor. There is a great need to reduce these harmon...
Directory of Open Access Journals (Sweden)
Ali CHEBABHI
2015-05-01
Full Text Available This article discusses and compares two control strategies applied to a 3-phase 4-wire 4-leg shunt active power filter. These two control strategies, including the cross-vector theory called CV theory and the direct method called PQR theory, are based on the instantaneous control of active and reactive power. On one hand, it is shown that, in some cases, cross-vector theory requires elimination of the zero sequence currents in a 3-phase 4-wire 4-leg shunt active power filter, which needs a power storage element, and on the other hand pretreatment system voltage is necessary to obtain compensated sinusoidal current and a degree of freedom. By relying on the cross-vector theory, the PQR theory is used to extract and remove harmonic currents components. In this control technique, there are two internal current control loops and an external voltage control loop, these control loops have been realized by PI controllers when applied 3D-SVM of switching technique. We choose as criteria for comparison the transient and the Total Harmonic Distortion in the line current. A series of simulations in MATLAB/ Simulink environment have been presented and discussed to show the performance of the two control strategies.
Load compensation for single phase system using series active filter
African Journals Online (AJOL)
user
Keywords: Active power filter (APF), current source type of harmonic load ... Single phase active filters could attract less attention than three phase due to its low ..... Generalised single-phase p-q theory for active power filtering: simulation and.
Directory of Open Access Journals (Sweden)
Niancheng Zhou
2014-08-01
Full Text Available The influence of electric vehicle charging stations on power grid harmonics is becoming increasingly significant as their presence continues to grow. This paper studies the operational principles of the charging current in the continuous and discontinuous modes for a three-phase uncontrolled rectification charger with a passive power factor correction link, which is affected by the charging power. A parameter estimation method is proposed for the equivalent circuit of the charger by using the measured characteristic AC (Alternating Current voltage and current data combined with the charging circuit constraints in the conduction process, and this method is verified using an experimental platform. The sensitivity of the current harmonics to the changes in the parameters is analyzed. An analytical harmonic model of the charging station is created by separating the chargers into groups by type. Then, the harmonic current amplification caused by the shunt active power filter is researched, and the analytical formula for the overload factor is derived to further correct the capacity of the shunt active power filter. Finally, this method is validated through a field test of a charging station.
Grid-Connected Photovoltaic System with Active Power Filtering Functionality
Directory of Open Access Journals (Sweden)
Joaquín Vaquero
2018-01-01
Full Text Available Solar panels are an attractive and growing source of renewable energy in commercial and residential applications. Its use connected to the grid by means of a power converter results in a grid-connected photovoltaic system. In order to optimize this system, it is interesting to integrate several functionalities into the power converter, such as active power filtering and power factor correction. Nonlinear loads connected to the grid generate current harmonics, which deteriorates the mains power quality. Active power filters can compensate these current harmonics. A photovoltaic system with added harmonic compensation and power factor correction capabilities is proposed in this paper. A sliding mode controller is employed to control the power converter, implemented on the CompactRIO digital platform from National Instruments Corporation, allowing user friendly operation and easy tuning. The power system consists of two stages, a DC/DC boost converter and a single-phase inverter, and it is able to inject active power into the grid while compensating the current harmonics generated by nonlinear loads at the point of common coupling. The operation, design, simulation, and experimental results for the proposed system are discussed.
Power system harmonics and passive filter designs
Das, J C
2015-01-01
J.C. Das is a consultant of electrical power systems at Power Systems Studies, Inc., USA. He is Life Fellow of IEEE (UK), Fellow of IET (India), and has authored approximately sixty technical papers and published 190 study reports of real-world power systems. He is the author of three books including ARC Flash Hazard Analysis and Mitigation. He is a registered P.E. in the states of Georgia and Oklahoma, C.Eng. in UK, and Eur Ing in Europe. J. C. Das is also a member of CIGRE, Federation of European Engineers, and other technical associations and organizations.
Generalized design of high performance shunt active power filter with output LCL filter
DEFF Research Database (Denmark)
Tang, Yi; Loh, Poh Chiang; Wang, Peng
2012-01-01
parameters, interactions between resonance damping and harmonic compensation, bandwidth design of the closed-loop system, and active damping implementation with fewer current sensors. These described design concerns, together with their generalized design procedure, are applied to an analytical example......This paper concentrates on the design, control, and implementation of an LCL-filter-based shunt active power filter (SAPF), which can effectively compensate for harmonic currents produced by nonlinear loads in a three-phase three-wire power system. With an LCL filter added at its output...
Design, control, and implementation of LCL-filter-based shunt active power filters
DEFF Research Database (Denmark)
Tang, Yi; Loh, Poh Chiang; Wang, Peng
2011-01-01
This paper concentrates on the design, control and implementation of an LCL-filter-based shunt active power filter (SAPF), which can effectively compensate harmonic currents produced by nonlinear loads in a three-phase three-wire power system. The use of LCL-filter at the output end of SAPF offer......-loop control system, and active damping implemented with fewer current sensors are all addressed here. An analytical design example is finally presented, being supported with experimental results, to verify its effectiveness and practicality.......This paper concentrates on the design, control and implementation of an LCL-filter-based shunt active power filter (SAPF), which can effectively compensate harmonic currents produced by nonlinear loads in a three-phase three-wire power system. The use of LCL-filter at the output end of SAPF offers...
PHOTOVOLTAIC BASED SHUNT ACTIVE FILTER FOR POWER QUALITY IMPROVEMENT USING ICOSΦ THEORY
Directory of Open Access Journals (Sweden)
VIJAYAKUMAR G.
2015-11-01
Full Text Available This paper presents an optimal operation of Photovoltaic based Shunt Active Filter as (PV-SAF for significant energy conservation, harmonic mitigation and reactive power compensation. When the PV system generates excessive or equal power required to the load demand, then the coordinating logic disconnects the service grid from the load and with a consequent reduction of panel tariff and global warming gasses. The PV module is connected to the DC side of SAF through the DC-DC converter. Converter switch is controlled by fuzzy based Perturb & Observe (P&O Maximum Power Point Tracking (MPPT algorithm and it eliminates the drawback in the conventional PV system. The reference currents are extracted by the Fuzzy logic controller based ICosΦ control strategy. This proposed PV-SAF, if connected at the terminals of a small industry or a home or a small enlightening institution can avoid the use of interruptible power supply and individual stabilizer. An emulation using MATLAB Simulink is presented to validate the advantage of the proposed system.
DSP control of photovoltaic power generation system adding the function of shunt active power filter
Energy Technology Data Exchange (ETDEWEB)
Seo, H.-R.; Kim, K.-H.; Park, Y.-G.; Park, M.; Yu, I.-K. [Changwon National Univ., SarimDong (Korea, Republic of). Dept. of Electrical Engineering
2007-07-01
The growing number of power electronics-based equipment has created a problem on the quality of electric power supply since both high power industrial loads and domestic loads cause harmonics in the network voltage. Power quality problems can occur in the system or can be caused by the consumer. Active filter (AF) is widely used to compensate current harmonics and/or current imbalance of harmonic-producing loads. The power output of a photovoltaic (PV) system is directly affected by weather conditions. When alternating current (AC) power supply is required, power conversion by an inverter and an MPPT control is necessary. The proliferation of nonlinear loads such as inverter of PV power generation system can be treated as a harmonic source for the power distribution system. As such, the PV system combined with the function of the active filter system can be useful for the application in power distribution systems. This paper described a PV-AF system using DSP to prove that it is possible to combine AF theory to the three phase PV system connected to utility and verify it through experimental results. The paper described the control method of the PV-AF system, with reference to the photovoltaic power generation system, shunt active filter and PV-AF system. The experimental set-up was also presented. A laboratory system was designed and constructed to confirm the viability of the proposed PV-AF system. The test results revealed the stability and effectiveness of the proposed PV-AF system. 12 refs., 1 tabs., 12 figs.
Directory of Open Access Journals (Sweden)
FERDI Brahim
2014-05-01
Full Text Available This paper proposes a novel application of the instantaneous P-Q theory in a wind energy conversion system (WECS. The proposed WECS is formed by permanent magnet synchronous generator (PMSG wind turbine system connected to the grid through parallel active power filter (PAPF. PAPF uses the generated wind energy to feed loads connected at the point of common coupling (PPC, compensates current harmonics and injects the excess of this energy into the grid using P-Q theory as control method. To demonstrate the feasibility and the performance of the proposed control scheme, simulation of this wind system has been realized using MATLAB/SIMULINK software. Simulation results show the accuracy and validity of the proposed control scheme for the PMSGPAPF system.
Control strategies of active filters in the context of power conditioning
DEFF Research Database (Denmark)
Dan, Stan George; Benjamin, Doniga Daniel; Magureanu, R.
2005-01-01
performance of active filters, and thus constitute a viable improved approach for harmonic compensation. In this paper a parallel hybrid filter is studied for current harmonic compensation. The hybrid filter is formed by a single tuned LC filter per phase and a small-rated power three-phase active filter......Active Power Filters have been intensively explored in the past decade. Various topologies and control schemes have been documented aiming at reducing the cost and improving the performance of the compensation system. Hybrid active filters inherit the efficiency of passive filters and the improved......, which are directly connected in series without any matching transformer. The required rating of the active filter is much smaller than a conventional standalone active filter would be. No additional switching-ripple filter is required for the hybrid filter because the LC filter functions not only...
DEFF Research Database (Denmark)
Luo, Zhaoxu; Su, Mei; Yang, Jian
2016-01-01
these disadvantages, many repetitive controllers with reduced delay time have been proposed, which can selectively compensate the odd harmonics or 6k±1 harmonics with delay time reduced to T0/2 and T0/3,repectively. To further study in this area, this paper proposes an improved repetitive scheme implemented...... in stationary reference frame, which only compensates the 6k+1 harmonics (e.g. -5, +7, -11, +13) in three-phase systems and reduces the time delay to T0/6 . So compared with the earlier reduced delay time repetitive controllers, the robustness and transient performance is further improved, the waste of control...... effort is reduced, and the possibility of amplifying and even injecting any harmonic noises into system is avoided to the greatest extent. Moreover, the proposed repetitive scheme is used in the control of a three-phase hybrid active power filter. The experimental results validate the effectiveness...
Voltage harmonics mitigation through hybrid active power filer
International Nuclear Information System (INIS)
Sahito, A.A.; Tunio, S.M.; Khizer, A.N.
2016-01-01
Fast dynamic response, high efficiency, low cost and small size of power electronic converters have exponentially increased their use in modern power system which resulted in harmonically distorted voltage and currents. Voltage harmonics mainly caused by current harmonics are more dangerous as performance and expected operating life of other power system equipment are affected by harmonically distorted supply voltage. Electronic filter circuits are used to improve system power quality by mitigating adverse effects of harmonics. Hybrid filters having advantages of both passive and active filters are preferred to resolve the problem of harmonics efficiently and avoiding any chance of resonance. In this paper, a three phase three wire network is considered to supply an adjustable speed drive represented by a resistive load connected across a three phase bridge rectifier. Simulation of the considered system shows THD (Total Harmonic Distortion) of 18.91 and 7.61 percentage in supply current and voltage respectively. A HAPF (Hybrid Active Power Filter) is proposed to reduce these THD values below 5 percentage as recommended by IEEE Standard-519. P-Q theorem is used to calculate required parameters for proposed filter, which is implemented through hysteresis control. Simulation results confirm the effectiveness of the designed filter as THD for both current and voltage have reduced below allowable limit of 5 percentage. (author)
DEFF Research Database (Denmark)
Lorzadeh, Iman; Askarian Abyaneh, Hossein; Savaghebi, Mehdi
2017-01-01
To address inaccurate load demand sharing problems among parallel inverter-interfaced voltage-controlled distributed generation (DG) units in islanded microgrids with different DG power ratings and mismatched feeder impedances, an enhanced voltage control scheme based on actively compensation of ...
A Series-LC-Filtered Active Trap Filter for High Power Voltage Source Inverter
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Loh, Poh Chiang
2016-01-01
Passive trap filters are widely used in high power Voltage Source Inverters (VSI) for the switching harmonic attenuation. The usage of the passive trap filters requires clustered and fixed switching harmonic spectrum, which is not the case for low pulse-ratio or Variable Switching Frequency (VSF...... current control of the auxiliary converter, which can be challenging considering that the switching harmonics have very high orders. In this paper, an Active Trap Filter (ATF) based on output impedance shaping is proposed. It is able to bypass the switching harmonics by providing nearly zero output...... impedance. A series-LC-filter is used to reduce the power rating and synthesize the desired output impedance of the ATF. Compared with the existing approaches, the compensated frequency range is greatly enlarged. Also, the current reference is simply set to zero, which reduces the complexity of the control...
DEFF Research Database (Denmark)
Hashempour, Mohammad M.; Firoozabadi, Mehdi Savaghebi; Quintero, Juan Carlos Vasquez
2016-01-01
This paper proposes a control architecture of distributed generators (DGs) inverters and shunt active power filters (APFs) in microgrids to compensate voltage harmonics in a coordinated way. For this, a hierarchical control structure is proposed that includes two control levels. The primary (local......) control consists of power controllers, selective virtual impedance loops and proportional-resonant (PR) voltage/current controllers. The secondary (central) control manages the compensation level of voltage harmonic distortion of sensitive load bus (SLB). Compensation of SLB harmonics by control of DGs...... excessive harmonics or overloading of interface inverters. Effectiveness of the proposed control scheme is demonstrated through simulation studies....
DEFF Research Database (Denmark)
Hashempour, Mohammad M.; Savaghebi, Mehdi; Quintero, Juan Carlos Vasquez
2016-01-01
This paper proposes a control architecture of distributed generators (DGs) inverters and shunt active power filters (APFs) in microgrids to compensate voltage harmonics in a coordinated way. For this, a hierarchical control structure is proposed that includes two control levels. The primary (local......) control consists of power controllers, selective virtual impedance loops and proportional-resonant (PR) voltage/current controllers. The secondary (central) control manages the compensation level of voltage harmonic distortion of sensitive load bus (SLB). Compensation of SLB harmonics by control of DGs...... excessive harmonics or overloading of interface inverters. Effectiveness of the proposed control scheme is demonstrated through simulation studies....
Performance Improvement of Shunt Active Power Filter With Dual Parallel Topology
DEFF Research Database (Denmark)
Asiminoaei, Lucian; Lascu, Cristian; Blaabjerg, Frede
2007-01-01
loop and the other is in a feedforward loop for harmonic compensation. Thus, both active power filters bring their own characteristic advantages, i.e., the feedback filter improves the steady-state performance of the harmonic mitigation and the feedforward filter improves the dynamic response. Another......This paper describes the control and parallel operation of two active power filters (APFs). Possible parallel operation situations of two APFs are investigated, and then the proposed topology is analyzed. The filters are coupled in a combined topology in which one filter is connected in a feedback...
DEFF Research Database (Denmark)
Kim, Hyosung; Blaabjerg, Frede; Bak-Jensen, Birgitte
2002-01-01
This paper proposes a novel power compensation algorithm in three-phase four-wire systems by using p-q-r theory. The p-q-r theory is compared with two previous instantaneous power theories, p-q theory and cross-vector theory. The p-q-r theory provides two-degrees of freedom to control the system...
Directory of Open Access Journals (Sweden)
Ioannis Bouloumpasis
2015-03-01
Full Text Available This work presents a method of current harmonic reduction in a distorted distribution system. In order to evaluate the proposed method a grid with high-order current harmonics is assumed. The reduction of current distortion is feasible due to the pulse modulation of an active filter, which consists of a buck-boost converter connected back-to-back to a polarity swapping inverter. For a practical application, this system would be the power electronic interface of a Renewable Energy Source (RES and therefore it changes a source of harmonics to a damping harmonics system. Using the proposed method, the current Total Harmonic Distortion (THD of the grid is reduced below the acceptable limits and thus the general power quality of the system is improved. Simulations in the MATLAB/SIMULINK platform and experiments have been performed in order to verify the effectiveness of the proposed method.
El-Sharkawi, Mohamed A.; Venkata, Subrahmanyam S.; Chen, Mingliang; Andexler, George; Huang, Tony
1992-01-01
A system and method for determining and providing reactive power compensation for an inductive load. A reactive power compensator (50,50') monitors the voltage and current flowing through each of three distribution lines (52a, 52b, 52c), which are supplying three-phase power to one or more inductive loads. Using signals indicative of the current on each of these lines when the voltage waveform on the line crosses zero, the reactive power compensator determines a reactive power compensator capacitance that must be connected to the lines to maintain a desired VAR level, power factor, or line voltage. Alternatively, an operator can manually select a specific capacitance for connection to each line, or the capacitance can be selected based on a time schedule. The reactive power compensator produces control signals, which are coupled through optical fibers (102/106) to a switch driver (110, 110') to select specific compensation capacitors (112) for connections to each line. The switch driver develops triggering signals that are supplied to a plurality of series-connected solid state switches (350), which control charge current in one direction in respect to ground for each compensation capacitor. During each cycle, current flows from ground to charge the capacitors as the voltage on the line begins to go negative from its positive peak value. The triggering signals are applied to gate the solid state switches into a conducting state when the potential on the lines and on the capacitors reaches a negative peak value, thereby minimizing both the potential difference and across the charge current through the switches when they begin to conduct. Any harmonic distortion on the potential and current carried by the lines is filtered out from the current and potential signals used by the reactive power compensator so that it does not affect the determination of the required reactive compensation.
Energy Technology Data Exchange (ETDEWEB)
El-Sharkawi, Mohamed A. (Renton, WA); Venkata, Subrahmanyam S. (Woodinville, WA); Chen, Mingliang (Kirkland, WA); Andexler, George (Everett, WA); Huang, Tony (Seattle, WA)
1992-01-01
A system and method for determining and providing reactive power compensation for an inductive load. A reactive power compensator (50,50') monitors the voltage and current flowing through each of three distribution lines (52a, 52b, 52c), which are supplying three-phase power to one or more inductive loads. Using signals indicative of the current on each of these lines when the voltage waveform on the line crosses zero, the reactive power compensator determines a reactive power compensator capacitance that must be connected to the lines to maintain a desired VAR level, power factor, or line voltage. Alternatively, an operator can manually select a specific capacitance for connection to each line, or the capacitance can be selected based on a time schedule. The reactive power compensator produces control signals, which are coupled through optical fibers (102/106) to a switch driver (110, 110') to select specific compensation capacitors (112) for connections to each line. The switch driver develops triggering signals that are supplied to a plurality of series-connected solid state switches (350), which control charge current in one direction in respect to ground for each compensation capacitor. During each cycle, current flows from ground to charge the capacitors as the voltage on the line begins to go negative from its positive peak value. The triggering signals are applied to gate the solid state switches into a conducting state when the potential on the lines and on the capacitors reaches a negative peak value, thereby minimizing both the potential difference and across the charge current through the switches when they begin to conduct. Any harmonic distortion on the potential and current carried by the lines is filtered out from the current and potential signals used by the reactive power compensator so that it does not affect the determination of the required reactive compensation.
Design and control of LCL-filter with active damping for Active Power Filter
DEFF Research Database (Denmark)
Zeng, Guohong; Rasmussen, Tonny Wederberg; Ma, L
2010-01-01
of LCL-filter for APF is introduced, which is aimed for simplified the implementation. To suppress the resonance that may be excited in the system, which brings in stability problems, an active damping control strategy using the current feed-back of the filter capacitor is adopted. By selecting two equal......In the application of shunt Active Power Filter (APF) to compensate nonlinear load's harmonic, reactive and negative sequence current, it is more effective to use a LCL-filter than an L-filter as an interface between the Voltage Source Converter (VSC) and grid. In this paper, a designing procedure...... or similar inductances, the filter designing become more simple and effective, meanwhile the capacitance requirement is minimized. A pole-zero automatic cancellation phenomenon is discussed in this paper, which can be applied to simplify the current regulator designing. The tuning method is presented, based...
Indirect Control of a low power Single-Phase Active Power Filter
Directory of Open Access Journals (Sweden)
SILVIU EPURE
2010-12-01
Full Text Available This paper deals with a low power, single phase active filter used to compensate nonlinear loads. The filter uses the indirect control method and it is based on a particular connection between filter, polluting load and grid to avoid timeconsuming mathematic operations or signal processing computations and assures good rejection of harmonic currents injected by the nonlinear load into the grid. A scale model was first simulated in Simulink and then physically implemented. The paper presents simulation and experimental results, and highlight problems encountered during experiments.
Adan, N. F.; Soomro, D. M.
2017-01-01
Power factor correction capacitor (PFCC) is commonly installed in industrial applications for power factor correction (PFC). With the expanding use of non-linear equipment such as ASDs, power converters, etc., power factor (PF) improvement has become difficult due to the presence of harmonics. The resulting capacitive impedance of the PFCC may form a resonant circuit with the source inductive reactance at a certain frequency, which is likely to coincide with one of the harmonic frequency of the load. This condition will trigger large oscillatory currents and voltages that may stress the insulation and cause subsequent damage to the PFCC and equipment connected to the power system (PS). Besides, high PF cannot be achieved due to power distortion. This paper presents the design of a three-phase hybrid filter consisting of a single tuned passive filter (STPF) and shunt active power filter (SAPF) to mitigate harmonics and resonance in the PS through simulation using PSCAD/EMTDC software. SAPF was developed using p-q theory. The hybrid filter has resulted in significant improvement on both total harmonic distortion for voltage (THDV) and total demand distortion for current (TDDI) with maximum values of 2.93% and 9.84% respectively which were within the recommended IEEE 519-2014 standard limits. Regarding PF improvement, the combined filters have achieved PF close to desired PF at 0.95 for firing angle, α values up to 40°.
International Nuclear Information System (INIS)
Eisa, A.A.A.E
2008-01-01
Excessive use of nonlinear loads connected to electric power systems distorts the AC power current, and consequently the AC voltage drop. Thereby resulting in the flow of harmonic currents in the system. This can introduce many problems through out the system. If such problems are unavoidable, then remedy or mitigation and cost of such action should be properly accounted for as fairly as possible. Due to this reason, it is important to determine precisely the quantity and direction of energy and power for each harmonic order. This will be very useful while constructing energy billing and rate structure.This thesis concerns with this matter, which is called reverse harmonic study. It introduces a new method to determine the attributes for each harmonic order at the point of common coupling (PCC) between the supplier and the consumer.Depending on the premise that harmonics cause power flow in power systems, just as fundamental frequency does, the thesis analytically introduces a new approach to develop the power theory. The purpose of this approach is to determine an accurate, fair, practical method for measuring the harmonic power components and energy transfer.There is consensus that the present definitions used to evaluate the flow of energy and power in electric networks are not adequate for conducting studies when non-sinusoidal voltage or current are present. For that reason the thesis suggests a new notion in power theory for periodic current and voltage waveforms. The idea of this notion has been inspired from the concept of instantaneous power. This term has been defined for convenience in representing the energy content of a system, since it satisfies the law of c onservation of energy . By this new approach we have analytically introduced definitions and formulas that determine precisely proper instantaneous power components in ac power systems under sinusoidal and non-sinusoidal conditions. The rapid progression of digital sampling technology in power
Directory of Open Access Journals (Sweden)
Ming-Hung Chen
2015-01-01
Full Text Available This paper proposes a new adaptive filter for wind generators that combines instantaneous reactive power compensation technology and current prediction controller, and therefore this system is characterized by low harmonic distortion, high power factor, and small DC-link voltage variations during load disturbances. The performance of the system was first simulated using MATLAB/Simulink, and the possibility of an adaptive digital low-pass filter eliminating current harmonics was confirmed in steady and transient states. Subsequently, a digital signal processor was used to implement an active power filter. The experimental results indicate, that for the rated operation of 2 kVA, the system has a total harmonic distortion of current less than 5.0% and a power factor of 1.0 on the utility side. Thus, the transient performance of the adaptive filter is superior to the traditional digital low-pass filter and is more economical because of its short computation time compared with other types of adaptive filters.
Chen, Ming-Hung
2015-01-01
This paper proposes a new adaptive filter for wind generators that combines instantaneous reactive power compensation technology and current prediction controller, and therefore this system is characterized by low harmonic distortion, high power factor, and small DC-link voltage variations during load disturbances. The performance of the system was first simulated using MATLAB/Simulink, and the possibility of an adaptive digital low-pass filter eliminating current harmonics was confirmed in steady and transient states. Subsequently, a digital signal processor was used to implement an active power filter. The experimental results indicate, that for the rated operation of 2 kVA, the system has a total harmonic distortion of current less than 5.0% and a power factor of 1.0 on the utility side. Thus, the transient performance of the adaptive filter is superior to the traditional digital low-pass filter and is more economical because of its short computation time compared with other types of adaptive filters.
Amelioration of Electrical Power Quality based on Modulated Power Filter Compensator
Directory of Open Access Journals (Sweden)
Karrar Hameed Kadhim
2017-08-01
Full Text Available This paper deals with the performance of modeling and implementation of Modulated Power Filter Compensator ( MPFC based on synchronous generator to enhance Electrical Power Quality (EPQ performance , rectification power factor , voltage fixity and decreasing transmission line losses for 300 km transmission line . In this paper (MPFC sketch attendants for intelligent network stability and optimum exploitation. The proposal Flexible AC Transmission Systems ( FACTS can be expanded to distributed renewable energy interface and exploitation systems and also will be easy to modify for voltage fixity, Achieve the required stability, perfect usage and Compensation requirements. MATLAB SIMLINK version R2009b were used as a model of (MPFC.
DEFF Research Database (Denmark)
Han, Yang; Shen, Pan; Zhao, Xin
2016-01-01
In this paper, an enhanced hierarchical control structure with multiple current loop damping schemes for voltage unbalance and harmonics compensation in ac islanded microgrid is proposed to address unequal power sharing problems. The distributed generation (DG) is properly controlled to autonomou......In this paper, an enhanced hierarchical control structure with multiple current loop damping schemes for voltage unbalance and harmonics compensation in ac islanded microgrid is proposed to address unequal power sharing problems. The distributed generation (DG) is properly controlled...... to autonomously compensate voltage unbalance and harmonics while sharing the compensation effort for the real power, reactive power, unbalance and harmonic powers. The proposed control system of the microgrid mainly consists of the positive sequence real and reactive power droop controllers, voltage and current......) technique is adopted to send the compensation command of the secondary control and auxiliary control from the microgrid control center (MGCC) to the local controllers of DG unit. Finally, the hardware-in-the-loop (HIL) results using dSPACE 1006 platform are presented to demonstrate the effectiveness...
Reduced order generalized integrators with phase compensation for three-phase active power filter
DEFF Research Database (Denmark)
Xie, Chuan; Li, Kai; Zhao, Xin
2017-01-01
-order generalized integrators (SOGIs) are utilized to achieve those objectives. However, it will increase the computational burden due to calculation of the multiple paralleled SOGIs. To overcome this issue, phase compensated reduced order generalized integrator (ROGI) is proposed in this paper. Compared...... paralleled ROGIs in positive and negative resonant frequencies. Moreover, the controller parameters are designed and optimized by means of Nyquist diagrams and sensitivity functions in z-domain for directly digital implementation. Finally, the laboratory tests of APF are performed to validate the feasibility...
Hysteresis Control for Shunt Active Power Filter under Unbalanced Three-Phase Load Conditions
Directory of Open Access Journals (Sweden)
Z. Chelli
2015-01-01
Full Text Available This paper focuses on a four-wire shunt active power filter (APF control scheme proposed to improve the performance of the APF. This filter is used to compensate harmonic distortion in three-phase four-wire systems. Several harmonic suppression techniques have been widely proposed and applied to minimize harmonic effects. The proposed control scheme can compensate harmonics and reactive power of the nonlinear loads simultaneously. This approach is compared to the conventional shunt APF reference compensation strategy. The developed algorithm is validated by simulation tests using MATLAB Simulink. The obtained results have demonstrated the effectiveness of the proposed scheme and confirmed the theoretical developments for balanced and unbalanced nonlinear loads.
Advanced nonlinear control of three phase series active power filter
Directory of Open Access Journals (Sweden)
Abouelmahjoub Y.
2014-01-01
Full Text Available The problem of controlling three-phase series active power filter (TPSAPF is addressed in this paper in presence of the perturbations in the voltages of the electrical supply network. The control objective of the TPSAPF is twofold: (i compensation of all voltage perturbations (voltage harmonics, voltage unbalance and voltage sags, (ii regulation of the DC bus voltage of the inverter. A controller formed by two nonlinear regulators is designed, using the Backstepping technique, to provide the above compensation. The regulation of the DC bus voltage of the inverter is ensured by the use of a diode bridge rectifier which its output is in parallel with the DC bus capacitor. The Analysis of controller performances is illustrated by numerical simulation in Matlab/Simulink environment.
Energy Technology Data Exchange (ETDEWEB)
Albuquerque, F.L.; Moraes, A.J.; Guimaraes, G.C.; Sanhueza, S.M.R.; Vaz, A.R. [Federal University of Uberlandia (UFU), MG (Brazil)
2009-07-01
In the case of photovoltaic solar systems (PV) acting as a distributed generation (DG), the DC energy obtained is fed through the power-conditioning unit (inverter) to the grid. The majority of contemporary inverters used in DG systems are current source inverters (CSI) operating at unity power factor. If, however, we assume that voltage source inverters (VSI) can be utilized instead of CSI, we can generate reactive power commensurate with the remaining unused capacity at any given point in time. According to the theory of instantaneous power, the reactive and active power of inverter can be regulated by changing the amplitude and the phase of the output voltage of the inverter. Based on this theory, the active power output and the reactive power compensation (RPC) of the system are realized simultaneously. When the insolation is weak or the PV modules are inoperative at night, the RPC feature of PV system can still be used to improve the utilization factor of the inverter. The MATLAB simulation results validate the feasibility of the method. (author)
Energy Technology Data Exchange (ETDEWEB)
1980-01-01
The Proceedings of the Conference comprises 12 papers dealing with the following themes: the history of apparent power; active and apparent power of periodical currents in single-phase and multiphase systems with periodical voltages of any shape of curve; power values in unsteady state processes; power and harmonic relations in mains-controlled direct frequency converters; power electronic devices for apparent power compensation; electric arc effects on power system: characteristics, measurement methods, compensation; harmonic compensation by means of impedance wave trap filters in rectifiers; compensation of apparent power by filter circuits; apparent power effects on ac railroad power systems; effects of apparent power in low-voltage networks of public power supply.
Design and control of hybrid active power filters
Lam, Chi-Seng
2014-01-01
Design and Control of Hybrid Active Power Filters presents an overview of the current quality problems and their compensators. To get a balance between the system cost and performance, hybrid active power filters (HAPFs) are valuable. The book presents the coverage of resonance phenomena prevention capability, filtering performance and system robustness analysis of HAPF; nonlinear inverter current slope characteristics and their linear operation region requirement analysis of the hysteresis PWM for the HAPF; minimum inverter capacity design procedure of HAPF, adaptive dc-link voltage controller for the HAPF and the real design example of a 220V 10kVA HAPF, in which the system performance analysis method, minimum dc voltage deduction concept and adaptive dc voltage idea can be further extended into the other active compensators, such as APF, static synchronous compensator STATCOM, etc. This book will benefit researchers, graduate students, and electrical power engineers in the field of power-quality compensati...
Aissa, Oualid; Moulahoum, Samir; Colak, Ilhami; Babes, Badreddine; Kabache, Nadir
2017-10-12
This paper discusses the use of the concept of classical and predictive direct power control for shunt active power filter function. These strategies are used to improve the active power filter performance by compensation of the reactive power and the elimination of the harmonic currents drawn by non-linear loads. A theoretical analysis followed by a simulation using MATLAB/Simulink software for the studied techniques has been established. Moreover, two test benches have been carried out using the dSPACE card 1104 for the classic and predictive DPC control to evaluate the studied methods in real time. Obtained results are presented and compared in this paper to confirm the superiority of the predictive technique. To overcome the pollution problems caused by the consumption of fossil fuels, renewable energies are the alternatives recommended to ensure green energy. In the same context, the tested predictive filter can easily be supplied by a renewable energy source that will give its impact to enhance the power quality.
Phase Coordinate System and p-q Theory Based Methods in Active Filtering Implementation
Directory of Open Access Journals (Sweden)
POPESCU, M.
2013-02-01
Full Text Available This paper is oriented towards implementation of the main theories of powers in the compensating current generation stage of a three-phase three-wire shunt active power system. The system control is achieved through a dSPACE 1103 platform which is programmed under the Matlab/Simulink environment. Four calculation blocks included in a specifically designed Simulink library are successively implemented in the experimental setup. The first two approaches, namely those based on the Fryze-Buchholz-Depenbrock theory and the generalized instantaneous reactive power theory, make use of phase quantities without any transformation of the coordinate system and provide the basis for calculating the compensating current when total compensation is desired. The others are based on the p-q theory concepts and require the direct and reverse transformation to/from the two-phases stationary reference frame. They are used for total compensation and partial compensation of the current harmonic distortion. The experimental results, in terms of active filtering performances, validate the control strategies implementation and provide arguments in choosing the most appropriate method.
Indirect control of a single-phase active power filter
Directory of Open Access Journals (Sweden)
Mihai CULEA
2006-12-01
Full Text Available The control of shunt active power filters using PWM inverters consists in generating a reference by separating, using different methods, the harmonics to be eliminated. The methods used are time-consuming and need dedicated control and signal processing equipments. To avoid these setbacks a new method is proposed in the paper. The active power filter is a current PWM rectifier with voltage output and with a capacitor on the DC side. The PWM rectifier is controlled so that the sum of its current and the load’s current is a sinusoid. The control block as well as simulation results are presented.
Energy Technology Data Exchange (ETDEWEB)
Abdusalam, Mohamed; Karimi, Shahram; Saadate, Shahrokh [Groupe de Recherche en Electrotechnique et Electronique de Nancy (GREEN), CNRS UMR 7037 (France); Poure, Philippe [Laboratoire d' Instrumentation Electronique de Nancy (LIEN), EA 3440, Universite Henri Poincare - Nancy Universite, B.P. 239, 54506 Vandoeuvre les Nancy Cedex (France)
2009-05-15
In this paper, a new reference current computation method suitable for shunt active power filter control under distorted voltage conditions is proposed. The active power filter control is based on the use of self-tuning filters (STF) for the reference current generation and on a modulated hysteresis current controller. This active filter is intended for harmonic compensation of a diode rectifier feeding a RL load under distorted voltage conditions. The study of the active filter control is divided in two parts. The first one deals with the harmonic isolator which generates the harmonic reference currents and is experimentally implemented in a DS1104 card of a DSPACE prototyping system. The second part focuses on the generation of the switching pattern of the inverter by using a modulated hysteresis current controller, implemented in an analogue card. The use of STF instead of classical extraction filters allows extracting directly the voltage and current fundamental components in the {alpha}-{beta} axis without phase locked loop (PLL). The performances are good even under distorted voltage conditions. First, the effectiveness of the new proposed method is mathematically studied and verified by computer simulation. Then, experimental results are presented using a DSPACE system associated with the analogue current controller for a real shunt active power filter. (author)
THE PHASE REACTOR INDUCTANCE SELECTION TECHNIQUE FOR POWER ACTIVE FILTER
Directory of Open Access Journals (Sweden)
D. V. Tugay
2016-12-01
Full Text Available Purpose. The goal is to develop technique of the phase inductance power reactors selection for parallel active filter based on the account both low-frequency and high-frequency components of the electromagnetic processes in a power circuit. Methodology. We have applied concepts of the electrical circuits theory, vector analysis, mathematical simulation in Matlab package. Results. We have developed a new technique of the phase reactors inductance selection for parallel power active filter. It allows us to obtain the smallest possible value of THD network current. Originality. We have increased accuracy of methods of the phase reactor inductance selection for power active filter. Practical value. The proposed technique can be used in the design and manufacture of the active power filter for real objects of energy supply.
International Nuclear Information System (INIS)
Ouchen, Sabir; Betka, Achour; Abdeddaim, Sabrina; Menadi, Abdelkrim
2016-01-01
Highlights: • An implementation on dSPACE 1104 of a double stage grid connected photovoltaic system, associated with an active power filter. • A fuzzy logic controller for maximum power point tracking of photovoltaic generator using a boost converter. • Predictive direct power control almost eliminates the effect of harmonics under a unite power factor. • The robustness of control strategies was examined in different irradiance level conditions. - Abstract: The present paper proposes a real time implementation of an optimal operation of a double stage grid connected photovoltaic system, associated with a shunt active power filter. On the photovoltaic side, a fuzzy logic based maximum power point taking control is proposed to track permanently the optimum point through an adequate tuning of a boost converter regardless the solar irradiance variations; whereas, on the grid side, a model predictive direct power control is applied, to ensure both supplying a part of the load demand with the extracted photovoltaic power, and a compensation of undesirable harmonic contents of the grid current, under a unity power factor operation. The implementation of the control strategies is conducted on a small scale photovoltaic system, controlled via a dSPACE 1104 single card. The obtained experimental results show on one hand, that the proposed Fuzzy logic based maximum power taking point technique provides fast and high performances under different irradiance levels while compared with a sliding mode control, and ensures 1.57% more in efficiency. On the other hand, the predictive power control ensures a flexible settlement of active power amounts exchanges with the grid, under a unity power functioning. Furthermore, the grid current presents a sinusoidal shape with a tolerable total harmonic distortion coefficient 4.71%.
Robust filtering for dynamic compensation of self-powered neutron detectors
International Nuclear Information System (INIS)
Peng, Xingjie; Li, Qing; Zhao, Wenbo; Gong, Helin; Wang, Kan
2014-01-01
Highlights: • Three dynamic compensation methods based on robust filtering theory are proposed. • Filter design problems are converted into linear matrix inequality problems. • Rhodium and Vanadium self-powered neutron detectors are used to validate the use of these three dynamic compensation methods. • The numerical simulation results show that all three methods can provide a reasonable balance between response speed and noise suppression. - Abstract: Self-powered neutron detectors (SPNDs), which are widely used in nuclear reactors to obtain core neutron flux distribution, are accurate at steady state but respond slowly to changes in neutron flux. Dynamic compensation methods are required to improve the response speed of the SPNDs and make it possible to apply the SPNDs for core monitoring and surveillance. In this paper, three digital dynamic compensation methods are proposed. All the three methods are based on the convex optimization framework using linear matrix inequalities (LMIs). The simulation results show that all three methods can provide a reasonable balance between response speed and noise suppression
Real-time modelling and simulation of an active power filter
Energy Technology Data Exchange (ETDEWEB)
Beaulieu, S.; Ouhrouche, M. [Quebec Univ., Chicoutimi, PQ (Canada); Dufour, C.; Allaire, P.F. [Opal RT Technologies Inc., Montreal, PQ (Canada)
2007-07-01
Power electronics converters generate harmonics and cause electromagnetic compatibility problems. Active power filter (APF) technology has advanced to the point that it can compensate for harmonics in electrical networks and provide reactive power and neutral current in AC networks. This paper presented a contribution in the design of a shunt APF for harmonics compensation in real-time simulation using the RT-LAB software package running on a simple personal computer. Real-time simulations were performed to validate the effectiveness of the proposed model. Several high-tech industries have adopted this tool for rapid control prototyping and for Hardware-in-the-Loop applications. The switching signals of the APF are determined by the hysteresis band current controller. The suitable current reference signals were determined by the algorithm based on synchronous reference frame. Real-time simulation runs showed good performance in harmonics compensation, thus satisfying the requirements of IEEE Standard 519-1992. The rate of total harmonic distortion for the source current decreased from 30 to 5 per cent. 12 refs., 1 tab., 9 figs.
International Nuclear Information System (INIS)
Yoon, Dong-Hee; Lee, Hansang; Park, Byungju; Jang, Gilsoo
2011-01-01
Highlights: → The low power factor and power quality problems are occurred by the operation of the PF facility in KSTAR system. We model the power system of KSTAR system including the PF facility. We show a method of the filter insertion to improve the problem and conduct the simulations to verify our method. - Abstract: The KSTAR system, which includes a large amount of nonlinear load, is a relatively high reactive power consumption load which injects harmonic currents into the power system which could result in the possibility for a power system perturbation to occur in the transmission lines, affecting nearby customers. In order to maintain the power quality and power factor in the inner system of the KSTAR system and the adjacent distribution lines, the assessment of the effect of the DC power supply in the KSTAR system is required for appropriate countermeasures to be put in place. In this paper, on the basis of a preliminary inspection of the power system near a KSTAR system, the simulation of a compensating device is performed for the prevention of abnormal voltage variations caused by a large amount of reactive and nonlinear load. In addition, through the comparison of the pre- and post-application of compensation devices in the actual power system, it is verified that a stable operation of the KSTAR nuclear fusion experimental system can be achieved.
Directory of Open Access Journals (Sweden)
V. N. Radkevich
2016-01-01
Full Text Available The paper considers evaluation procedure for the degree of active power losses reduction in the power transmission lines under 1 kV and 6–10 kV of the systems of electric power supply of industrial enterprises with compensating installations mounted at the side of the customer. The capacitor installations conform to the applied voltage level and factor in dielectric losses in the capacitors. The voltage at the compensating device terminal changes from 0.95 to 1.05 of the capacitors nominal voltage. The study did not account for reactive power losses in the line, nor did it for its charge capacity, conditioned by relative shortness of the cable lines generally operating in the mains of industrial enterprises. For this reason, the quantities of reactive power being consumed and generated by the transmission line are negligible and do not significantly affect the reactive power flux. The researchers obtain functional relations that allow estimating the degree of power loss reduction in the transmission line factoring in its explicit initial data. They perform mathematical analysis of the obtained functional relations and study the function by means of derivatives. The function extremum points are found as well as the intervals of its increment and decrement. A graphical research of the obtained functional relation is performed. It is ascertained that reduction of the active power losses is contingent on the line and the capacitor-installation engineering factors, the electrical energy consumer reactive load value as well as the voltage applied to the capacitor installation. The functional relations presented in the article can be employed in scoping calculation necessary for decision making on the reactive power compensation in systems of the industrial facilities electric power supply. Their account will allow a more accurate estimate of technical and economic effect of the capacitor bank installation in the electrical mains under 1 kV and 6
Improvement of active filter for HIMAC power sources
Energy Technology Data Exchange (ETDEWEB)
Kumada, Masayuki [National Inst. of Radiological Sciences, Chiba (Japan); Kubo, Hiroshi; Furuzeki, Shoichiro; Kanazawa, Toru
1996-03-01
For the power sources of the synchrotron electromagnets for the heavy particle beam cancer therapy apparatus HIMAC in National Institute of Radiological Science, in order to stabilize the taken-out beam, the ripple property as low as below 1 x 10{sup -6} is required. As for this electromagnet power sources, various devices were applied to lower ripples, and the required specifications have been satisfied. Also the beam spill is stable, but slight variation has been observed, therefore, by improving the performance of the active filter, the ripples were improved. The specifications of the electromagnet power sources and the whole constitution of the power source system are shown. In the HIMAC power sources, the means for having realized the low ripple performance so far are explained. Those are the absorption of the ineffective power generated from the power sources, the control of the ripples of common made due to the transducer thyristor, and the sure compensation of ripples by the control circuit for the power sources. By adding the band pass filters to the active filter, its characteristics were improved. As the result, 1200 Hz ripple component was reduced by 41 db, thus the sufficient effect was obtained. Hereafter, by the high sensitivity measurement of the current of electromagnets and the evaluation of magnetic fields, the validity will be evaluated. (K.I.)
Novel concept of a PV power generation system adding the function of shunt active filter
Energy Technology Data Exchange (ETDEWEB)
Park, Y.G.; Park, M.; Yu, I.K. [Changwon National Univ., Changwon City (Korea, Republic of). Dept. of Electrical Engineering
2005-07-01
A new photovoltaics (PV) power generation system that used an active filter (AF) function was proposed. The AF was installed to condition reactive power and harmonic compensation as well as flicker and voltage regulation. A maximum point power tracking (MPPT) control system was used to stabilize the voltage source inverter (VSI) output current. A general dq transformation was used to compensate the negative components and the harmonics component. The output terminal of the PV array was connected to a smoothing capacitor interfacing the PV-AF inverter. A voltage source PWM converter was controlled with feedback loops of the output current of the inverter. Optimal values of the power inverter gains and filter constants were tuned to obtain responses. The PV system was simulated using real weather conditions. Results of the study demonstrated the stability and effectiveness of the proposed system. It was concluded that the PV-AF can also be used to provide harmonic damping throughout power distribution systems. 12 refs., 3 tabs., 9 figs.
Control of a three-phase four-wire shunt-active power filter based on DC-bus energy regulation
DEFF Research Database (Denmark)
Blaabjerg, Frede; Teodorescu, Remus; Rodriguez, Pedro
2008-01-01
This paper presents a nonconventional three-phase four-wire shunt active power filter (APF) topology controlled by using an energy approach. A general study of power terms involved in the operation of the four-wire APF is conducted in order to evidence the relationship between instantaneous energy...... stored in the DC bus and active power requirements on the APF. Harmonics and imbalances both on the utility voltage and load current have been considered and the power developed by the active power filter has been evaluated. This study allows designing a controller for the APF based on the regulation...
Development of DC active filter for high magnetic field stable power supply
International Nuclear Information System (INIS)
Wang Lei; Liu Xiaoning
2008-01-01
The DC active filter (DAF), with very low current ripple, of the stable power supply system of high magnetic field device is developed by using the PWM and parallel active power filter technique. Due to the PWM control technique, the required DAF current can be obtained and the current ripple can be compensated by means of monitoring the load voltage, and the current ripple becomes very low by adjusting the load voltage. The simulation and analysis show that this system can respond to the reference quickly and is effective in suppressing the harmonics, especially the low-order harmonics. The feasibility of the proposed scheme is proved on the equipment built in the laboratory. (authors)
New series active power filter for computers loads and small non-linear loads
Energy Technology Data Exchange (ETDEWEB)
Tarnini, M.Y. [Hariri Canadian Univ., Meshref (Lebanon)
2009-07-01
This paper proposed the use of a single-phase series active power filter to reduce voltage total harmonic distortion and provide improved power quality. Control schemes were developed using simple control algorithms and a reduced number of current transducers. The circuit was comprised of a power supply and zero crossing detector; a hall-effect current sensor and signal conditioning circuit; a microcontroller circuit; a driving circuit; and an inverter bridge. The filter corrected fundamental and sinusoidal voltage amplitudes. The amplitude of the fundamental current in the series filter was controlled using a microcontroller placed between the load voltage and a pre-established reference point. Experiments were conducted to test the source voltage and source current after compensation using a prototype of the filter. The control system provided effective correction of the power factor and harmonic distortion, and reached steady state in approximately 2 cycles. It was concluded that the compensator can also be adapted for use in 3-phase systems. 13 refs., 1 tab., 14 figs.
Reactive power compensating system
Energy Technology Data Exchange (ETDEWEB)
Williams, Timothy J. (Redondo Beach, CA); El-Sharkawi, Mohamed A. (Renton, WA); Venkata, Subrahmanyam S. (Seattle, WA)
1987-01-01
The reactive power of an induction machine is compensated by providing fixed capacitors on each phase line for the minimum compensation required, sensing the current on one line at the time its voltage crosses zero to determine the actual compensation required for each phase, and selecting switched capacitors on each line to provide the balance of the compensation required.
Feedback Linearization Control of a Shunt Active Power Filter Using a Fuzzy Controller
Directory of Open Access Journals (Sweden)
Tianhua Li
2013-09-01
Full Text Available In this paper, a novel feedback linearization based sliding mode controlled parallel active power filter using a fuzzy controller is presented in a three-phase three-wire grid. A feedback linearization control with fuzzy parameter self-tuning is used to implement the DC side voltage regulation while a novel integral sliding mode controller is applied to reduce the total harmonic distortion of the supply current. Since traditional unit synchronous sinusoidal signal calculation methods are not applicable when the supply voltage contains harmonics, a novel unit synchronous sinusoidal signal computing method based on synchronous frame transforming theory is presented to overcome this disadvantage. The simulation results verify that the DC side voltage is very stable for the given value and responds quickly to the external disturbance. A comparison is also made to show the advantages of the novel unit sinusoidal signal calculating method and the super harmonic treatment property of the designed active power filter.
Voltage Feedback based Harmonic Compensation for an Offshore Wind Power Plant
DEFF Research Database (Denmark)
Chaudhary, Sanjay K.; Lascu, Cristian; Teodorescu, Remus
2016-01-01
When an offshore wind power plant is connected to the grid, there is a risk of amplification of certain harmonics and appearance resonances at the point of connection due to the interaction between the grid network and the wind power plant network. Hence, the plant developer is obliged to maintain...
DEFF Research Database (Denmark)
Mousazadeh, Seyyed Yousef; Jalilain, Alireza; Savaghebi, Mehdi
2018-01-01
In microgrids, Voltage Source Inverters (VSIs) interfacing Distributed Generation (DG) units can be operated in Voltage or Current Controlled Modes (VCM/CCM). In this paper, a coordinated control of CCM and VCM units for reactive power sharing and voltage harmonics compensation is proposed....... This decentralized control scheme is based on the local measurement of signals. In this way, the need for communication links is removed which results in a simpler and more reliable structure compared to the communication based control structures. To be more exact, the VCM units contribute to harmonics compensation....... Experimental and simulation studies show that the harmonics compensation is achieved by using only local measurements in presence of virtual admittance/impedance schemes of CCM/VCM units. Furthermore, it is demonstrated that the reactive power sharing among the CCM and VCM units is obtained based...
A grid-voltage-sensorless resistive active power filter with series LC-filter
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
Voltage-sensorless control has been investigated for Voltage Source Inverters (VSIs) for many years due to the reduced system cost and potentially improved system reliability. The VSI based Resistive Active Power Filters (R-APFs) are now widely used to prevent the harmonic resonance in power...... distribution network, for which the voltage sensors are needed in order to obtain the current reference. In this paper a grid-voltage-sensorless control strategy is proposed for the R-APF with series LC-filter. Unlike the traditional resistance emulation method, this proposed control method re...
A Grid-Voltage-Sensorless Resistive Active Power Filter with Series LC-Filter
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Blaabjerg, Frede
2018-01-01
Voltage-sensorless control has been investigated for Voltage Source Inverters (VSIs) for many years due to the reduced system cost and potentially improved system reliability. The VSI based Resistive Active Power Filters (R-APFs) are now widely used to prevent the harmonic resonance in power...... distribution network, for which the voltage sensors are needed in order to obtain the current reference. In this paper a grid-voltage-sensorless control strategy is proposed for the R-APF with series LC-filter. Unlike the traditional resistance emulation method, this proposed control method re...
A Novel Sliding Mode Control Technique for Indirect Current Controlled Active Power Filter
Directory of Open Access Journals (Sweden)
Juntao Fei
2012-01-01
Full Text Available A novel sliding mode control (SMC method for indirect current controlled three-phase parallel active power filter is presented in this paper. There are two designed closed loops in the system: one is the DC voltage controlling loop and the other is the reference current tracking loop. The first loop with a PI regulator is used to control the DC voltage approximating to the given voltage of capacitor, and the output of PI regulator through a low-pass filter is applied as the input of the power supply reference currents. The second loop implements the tracking of the reference currents using integral sliding mode controller, which can improve the harmonic treating performance. Compared with the direct current control technique, it is convenient to be implemented with digital signal processing system because of simpler system structure and better harmonic treating property. Simulation results verify that the generated reference currents have the same amplitude with the load currents, demonstrating the superior harmonic compensating effects with the proposed shunt active power filter compared with the hysteresis method.
Variable speed DFIG wind energy system for power generation and harmonic current mitigation
Energy Technology Data Exchange (ETDEWEB)
Gaillard, A.; Saadate, S. [Groupe de Recherche en Electrotechnique et Electronique de Nancy, Nancy Universite - Universite Henri Poincare Nancy 1, BP239, 54506 Vandoeuvre les Nancy Cedex (France); Poure, P. [Laboratoire d' Instrumentation Electronique de Nancy, Nancy Universite - Universite Henri Poincare Nancy 1, BP239, 54506 Vandoeuvre les Nancy Cedex (France); Machmoum, M. [IREENA, 37 Boulevard de l' Universite, BP 406, 44602 Saint-Nazaire Cedex (France)
2009-06-15
This paper presents a novel approach for simultaneous power generation and harmonic current mitigation using variable speed WECS with DFIG. A new control strategy is proposed to upgrade the DFIG control to achieve simultaneously a green active and reactive power source with active filtering capability. To ensure high filtering performance, we studied an improved harmonic isolator in the time-domain, based on a new high selectivity filter developed in our laboratory. We examined two solutions for harmonic current mitigation: first, by compensating the whole harmonic component of the grid currents or second, by selective isolation of the predominant harmonic currents to ensure active filtering of the 5th and 7th harmonics. Simulation results for a 3 MW WECS with DFIG confirm the effectiveness and the performance of the two proposed approaches. (author)
Directory of Open Access Journals (Sweden)
Mansoor Ahmed Soomro
2012-01-01
Full Text Available The automation of IPS (Industrial Power System has brought about several advantages of increased productivity and efficiency but it suffers from incompatible problems of overheating, noise, complexity etc, which disturb its smooth and fault tolerant implication. When the resonance condition is reached, these effects become detrimental and disturb the whole power system. The purpose of this research work is to include single tuned shunt type passive filter for harmonic elimination of the components used in industrial power system. For this purpose, MATLAB simulation using sim Power system tool has been used to analyze the effects of current harmonics. Third harmonic effects have been removed by the addition of six pulse converter technique. The simulation results show that implication of single tuned shunt (parallel connected passive filter removes effects of succeeding order current harmonics i.e. fifth, seventh and eleventh etc. which are causing substantial damage to industrial power system. The effects of current harmonics can be solved by installing without and with the application of proposed filter. Further, it is observed that these filters contribute in reduction of THD (Total Harmonic Current Distortion followed by improvement in power factor. These results are taken considering limits of IEEE 519-1992 standards.
Andreh, Angga Muhamad; Subiyanto, Sunardiyo, Said
2017-01-01
Development of non-linear loading in the application of industry and distribution system and also harmonic compensation becomes important. Harmonic pollution is an urgent problem in increasing power quality. The main contribution of the study is the modeling approach used to design a shunt active filter and the application of the cascade multilevel inverter topology to improve the power quality of electrical energy. In this study, shunt active filter was aimed to eliminate dominant harmonic component by injecting opposite currents with the harmonic component system. The active filter was designed by shunt configuration with cascaded multilevel inverter method controlled by PID controller and SPWM. With this shunt active filter, the harmonic current can be reduced so that the current wave pattern of the source is approximately sinusoidal. Design and simulation were conducted by using Power Simulator (PSIM) software. Shunt active filter performance experiment was conducted on the IEEE four bus test system. The result of shunt active filter installation on the system (IEEE four bus) could reduce THD current from 28.68% to 3.09%. With this result, the active filter can be applied as an effective method to reduce harmonics.
Modified SOGI based shunt active power filter to tackle various grid voltage abnormalities
Directory of Open Access Journals (Sweden)
Kalpeshkumar Patil
2017-10-01
Full Text Available Shunt Active Power Filters (SAPF have been effectively used to compensate the harmonics generated by the non-linear loads. The SAPF’s performance depends on the accurate generation of reference current, which is dependent greatly on the template of supply voltage. When the grid voltage (or its template is characterized by different abnormalities like presence of harmonics, imbalance, dc-offset etc., some of the conventional techniques of frequency estimation may fail to correctly estimate the frequency. This ultimately affects the reference current generation and hence, the SAPF operation, ultimately leading to high distortion of the grid currents. The paper presents modified dual second-order generalized integrator (MDSOGI based SAPF to ensure effective compensation of harmonics, even when the grid voltage is characterized by all the abnormalities mentioned above. It is highlighted with one case that when the sensed voltage is having dc-offset, DSOGI-SAPF results into the source current with THD, dc-offset and harmonic with values 5.82%, 0.8% and 4.5%, respectively. For the same case, the proposed technique yields grid current which is free of dc-offset and 2nd harmonic and has THD = 3.57%. The dynamic performance of the MDSOGI-SAPF is validated and its superior performance over DSOGI-SAPF is illustrated even with experimental results.
Coelho, A C; Cannon, D T; Cao, R; Porszasz, J; Casaburi, R; Knorst, M M; Rossiter, H B
2015-03-01
A rapid switch from hyperbolic to isokinetic cycling allows the velocity-specific decline in maximal power to be measured, i.e., fatigue. We reasoned that, should the baseline relationship between isokinetic power (Piso) and electromyography (EMG) be reproducible, then contributions to fatigue may be isolated from 1) the decline in muscle activation (muscle activation fatigue); and 2) the decline in Piso at a given activation (muscle fatigue). We hypothesized that the EMG-Piso relationship is linear, velocity dependent, and reliable for instantaneous fatigue assessment at intolerance during and following whole body exercise. Healthy participants (n = 13) completed short (5 s) variable-effort isokinetic bouts at 50, 70, and 100 rpm to characterize baseline EMG-Piso. Repeated ramp incremental exercise tests were terminated with maximal isokinetic cycling (5 s) at 70 rpm. Individual baseline EMG-Piso relationships were linear (r(2) = 0.95 ± 0.04) and velocity dependent (analysis of covariance). Piso at intolerance (two legs, 335 ± 88 W) was ∼45% less than baseline [630 ± 156 W, confidence interval of the difference (CIDifference) 211, 380 W, P fatigue and muscle fatigue (one leg) were 97 ± 55 and 60 ± 50 W, respectively. Mean bias ± limits of agreement for reproducibility were as follows: baseline Piso 1 ± 30 W; Piso at 0-min recovery 3 ± 35 W; and EMG at Piso 3 ± 14%. EMG power is linear, velocity dependent, and reproducible. Deviation from this relationship at the limit of tolerance can quantify the "activation" and "muscle" related components of fatigue during cycling. Copyright © 2015 the American Physiological Society.
Matrix pencil method-based reference current generation for shunt active power filters
DEFF Research Database (Denmark)
Terriche, Yacine; Golestan, Saeed; Guerrero, Josep M.
2018-01-01
response and works well under distorted and unbalanced voltage. Moreover, the proposed method can estimate the voltage phase accurately; this property enables the algorithm to compensate for both power factor and current unbalance. The effectiveness of the proposed method is verified using simulation...... are using the discrete Fourier transform (DFT) in the frequency domain or the instantaneous p–q theory and the synchronous reference frame in the time domain. The DFT, however, suffers from the picket-fence effect and spectral leakage. On the other hand, the DFT takes at least one cycle of the nominal...... frequency. The time-domain methods show a weakness under voltage distortion, which requires prior filtering techniques. The aim of this study is to present a fast yet effective method for generating the RCC for SAPFs. The proposed method, which is based on the matrix pencil method, has a fast dynamic...
Inverted Unified Power Quality Conditioner to compensate overvoltage
Directory of Open Access Journals (Sweden)
Yeison Alberto Garcés Gómez
2017-07-01
Full Text Available Introduction: The use of unified power quality conditioners UPQC in the electric systems can correct waveform distortions in a steady state, like harmonics, flicker, and the power factor. Objective: This paper presents a novel approach for active compensation of overvoltage with a UPQC in dual topology or iUPQC. Methodology: The study it is presented in five stages, the section I shows an introduction and the state of the art, section II presents the unified power quality conditioner UPQC, section III describes the generalized reactive power theory applied to the iUPQC (dual topology, section IV shows the numerical simulations and the results and section V presents the conclusions of the study. Results: The results for the application of the iUPQC to the compensation of overvoltage are proved and compared with the more representative theory related to compensation of harmonics and low power factor. Conclusions: The control algorithm presented for the unified power quality conditioner in dual topology allows to compensate the overvoltage in three-phase systems as well as voltage and current harmonics and the low power factor.
Energy Technology Data Exchange (ETDEWEB)
Pettersson, S.
2009-07-01
During the past two decades, active power filters have increasingly grown their popularity as a viable method for improving electric power quality. The main reasons for this have been the advent of fast self-commutating solid-state devices, the progression of digital technology and the improved sensor technology. Four-wire active power filters provide an efficient solution for improving the quality of supply in grounded three-phase systems or three-phase systems with neutral conductors, which are commonly used for powering residential, office and public buildings. Four-wire active power filters are applicable in compensating current harmonics, reactive power, neutral current and load phase imbalance.This thesis presents a comparative study of microcontroller controlled four-wire voltage and current source shunt active power filters. The study includes two voltage source topologies and a current source topology with two different dc-link energy storage structures, which are compared on the basis of their filtering properties, filtering performance and efficiency. The obtained results are used for determining the suitability of current source technology for four-wire active power filtering and finding the most viable four-wire shunt active power filter topology. One commonly recognized disadvantage of the current source active power filter has always been the bulky dc-link inductor. To reduce the size of the dc-link inductor, an alternative dc-link structure for current source active power filters was introduced in the late 80's. The hybrid energy storage consists of both inductive and capacitive energy storage elements, two diodes and two controllable semiconductor switching devices. Since the capacitive element is used as a main storage unit, the inductance of the dc-link inductor can be considerably reduced. However, the original dc current control method proposed is not able to utilize the full potential of the hybrid energy storage and the inductance
Performance improvement of shunt active power filter based on non-linear least-square approach
DEFF Research Database (Denmark)
Terriche, Yacine
2018-01-01
Nowadays, the shunt active power filters (SAPFs) have become a popular solution for power quality issues. A crucial issue in controlling the SAPFs which is highly correlated with their accuracy, flexibility and dynamic behavior, is generating the reference compensating current (RCC). The synchron......Nowadays, the shunt active power filters (SAPFs) have become a popular solution for power quality issues. A crucial issue in controlling the SAPFs which is highly correlated with their accuracy, flexibility and dynamic behavior, is generating the reference compensating current (RCC......). The synchronous reference frame (SRF) approach is widely used for generating the RCC due to its simplicity and computation efficiency. However, the SRF approach needs precise information of the voltage phase which becomes a challenge under adverse grid conditions. A typical solution to answer this need....... This paper proposes an improved open loop strategy which is unconditionally stable and flexible. The proposed method which is based on non-linear least square (NLS) approach can extract the fundamental voltage and estimates its phase within only half cycle, even in the presence of odd harmonics and dc offset...
A New Generalized Discontinuous-PWM Strategy for Active Power Filters
DEFF Research Database (Denmark)
Asiminoaei, Lucian; Rodriguez, Pedro; Blaabjerg, Frede
2007-01-01
losses in any operating point. This paper proposes a new discontinuous pulse width modulation strategy applied to shunt active power filters. The proposed modulation strategy detects the current vector position relative to the inverter voltage reference and determines instantaneously the optimum clamped...
Load compensation for single phase system using series active filter ...
African Journals Online (AJOL)
Load compensation for single phase system using series active filter. ... KK Mishra, R Gupta ... load varies from time to time, the non linear load ranging from voltage source type harmonic load (VSHL) dominant to current source type harmonic ...
Directory of Open Access Journals (Sweden)
Zhiqun Cheng
2017-01-01
Full Text Available The design, implementation, and measurements of a high efficiency and high power wideband GaN HEMT power amplifier are presented. Package parasitic effect is reduced significantly by a novel compensation circuit design to improve the accuracy of impedance matching. An improved structure is proposed based on the traditional Class-F structure with all even harmonics and the third harmonic effectively controlled, respectively. Also the stepped-impedance matching method is applied to the third harmonic control network, which has a positive effect on the expansion bandwidth. CGH40025F power transistor is utilized to build the power amplifier working at 0.8 to 2.7 GHz, with the measured saturated output power 20–50 W, drain efficiency 52%–76%, and gain level above 10 dB. The second and the third harmonic suppression levels are maintained at −16 to −36 dBc and −16 to −33 dBc, respectively. The simulation and the measurement results of the proposed power amplifier show good consistency.
Reactive Power Compensating System.
Energy Technology Data Exchange (ETDEWEB)
Williams, Timothy J.; El-Sharkawi, Mohamed A.; Venkata, Subrahmanyam S.
1985-01-04
The circuit was designed for the specific application of wind-driven induction generators. It has great potential for application in any situation where a varying reactive power load is present, such as with induction motors or generators, or for transmission network compensation.
Künzi, R.
2015-06-15
Power converters require passive low-pass filters which are capable of reducing voltage ripples effectively. In contrast to signal filters, the components of power filters must carry large currents or withstand large voltages, respectively. In this paper, three different suitable filter struc tures for d.c./d.c. power converters with inductive load are introduced. The formulas needed to calculate the filter components are derived step by step and practical examples are given. The behaviour of the three discussed filters is compared by means of the examples. P ractical aspects for the realization of power filters are also discussed.
Directory of Open Access Journals (Sweden)
Meenakshi Jayaraman
2017-11-01
Full Text Available Recently, multilevel inverters are more researched due to the advantages they offer over conventional voltage source inverters in grid connected applications. Passive filters are connected at the output of these inverters to produce sinusoidal waveforms with reduced harmonics and to satisfy grid interconnection standard requirements. This work proposes a new passive filter topology for a pulse width modulated five-level cascaded inverter interfaced grid connected system. The proposed passive filter inserts an additional resistance-capacitance branch in parallel to the filter capacitor of the traditional inductive–capacitive–inductive filter in addition to a resistance in series with it to reduce damping power loss. It can attenuate the switching frequency harmonic current components much better than the traditional filter while maintaining the same overall inductance, reduced capacitance and resistance values. The basic parameter design procedure and an approach to discover the parameters of the proposed filter is introduced. Further, a novel methodology using Particle Swarm Optimization (PSO is recommended to guarantee minimum damping loss while ensuring reduced peak during resonance. In addition, PSO algorithm is newly employed in this work to maximize harmonic attenuation in and around the switching frequency on the premise of allowable values of filter inductance and capacitance. A comparative discussion considering traditional passive filters and the proposed filter is presented and evaluated through experiments conducted on a 110 V, 1 kW five-level grid connected inverter. The modulation algorithm for the multilevel inverter is implemented using a SPARTAN 6-XC6SLX25 Field Programmable Gate Array (FPGA processor. The analysis shows that the proposed filter not only provides decreased damping power loss but also is capable of providing considerable harmonic ripple reduction in the high frequency band, improved output waveforms and lesser
DEFF Research Database (Denmark)
Sun, Xiaofeng; Zeng, Jian; Chen, Zhe
2013-01-01
, and analyze the harmonic voltage propagation caused by the background harmonic voltage in power systems. Then, a new strategy is proposed for the site selection of resistive active power filter to damp the background harmonic voltage in power systems. Experiments have been performed to verify the theoretical......Series resonance between capacitance and line inductance may magnify background harmonic voltage and worsen the harmonic voltage distortion in power systems. To solve this problem, in this paper, the transmission line theory is used to set up the distributed parameter model of power system feeders...
DSP Control of Line Hybrid Active Filter
DEFF Research Database (Denmark)
Dan, Stan George; Benjamin, Doniga Daniel; Magureanu, R.
2005-01-01
Active Power Filters have been intensively explored in the past decade. Hybrid active filters inherit the efficiency of passive filters and the improved performance of active filters, and thus constitute a viable improved approach for harmonic compensation. In this paper a parallel hybrid filter...... is studied for current harmonic compensation. The hybrid filter is formed by a single tuned Le filter and a small-rated power active filter, which are directly connected in series without any matching transformer. Thus the required rating of the active filter is much smaller than a conventional standalone...... active filter. Simulation and experimental results obtained in laboratory confirmed the validity and effectiveness of the control....
Directory of Open Access Journals (Sweden)
Suleiman Musa
2017-05-01
Full Text Available Harmonic distortion in power networks has greatly reduced power quality and this affects system stability. In order to mitigate this power quality issue, the shunt active power filter (SAPF has been widely applied and it is proven to be the best solution to current harmonics. This paper evaluates the performance of the modified synchronous reference frame extraction (MSRF algorithm with fuzzy logic controller (FLC based current control pulse width modulation (PWM inverter of three-phase three-wire SAPF to mitigate current harmonics. The proposed FLC is designed with a reduced amount of membership functions (MFs and rules, and thus significantly reduces the computational time and memory size. Modeling and simulations of SAPF are carried out using MATLAB/Simulink R2012a with the power system toolbox under steady-state condition, and this is followed with hardware implementation using a TMS320F28335 digital signal processor (DSP, Specrum Digital Inc., Stafford, TX, USA. The results obtained demonstrate a good and satisfactory response to mitigate the harmonics in the system. The total harmonic distortion (THD for the system has been reduced from 25.60% to 0.92% and 1.41% in the simulation study with and without FLC, respectively. Similarly for the experimental study, the SAPF can compensate for the three-phase load current by reducing THD to 5.07% and 7.4% with and without FLC, respectively.
Compensating active power imbalances in power system with large-scale wind power penetration
DEFF Research Database (Denmark)
Basit, Abdul; Hansen, Anca Daniela; Altin, Müfit
2016-01-01
Large-scale wind power penetration can affectthe supply continuity in the power system. This is a matterof high priority to investigate, as more regulating reservesand specified control strategies for generation control arerequired in the future power system with even more highwind power penetrat...
An Active Trap Filter for Switching Harmonics Attenuation of Low-Pulse-Ratio Inverters
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Loh, Poh Chiang
2017-01-01
method has also been proposed for the ATF to better enforce its active switching harmonic bypassing ability. Compared with conventional schemes for controlling active power filters, the proposed method is more readily implemented, since it requires neither current reference generation nor high......-bandwidth current control loop. Moreover, the use of a series LC-filter at its ac-side helps the ATF to reduce its inverter voltage and power ratings. Compensated frequency range of the ATF can hence be enlarged by using a comparably higher switching frequency and a proper step-by-step design procedure...
Application of Discontinuous PWM Modulation in Active Power Filters
DEFF Research Database (Denmark)
Blaabjerg, Frede; Asiminoaei, Lucian; Rodriguez, Pedro
2008-01-01
Classical discontinuous pulsewidth modulations (DPWMs) may not be efficiently applied in active power filters (APFs), because it is hard to predict the peak values of the inverter current, and consequently it is difficult to calculate the position of the clamped interval, that minimizes...
Power theories for improved power quality
Pasko, Marian
2012-01-01
Power quality describes a set of parameters of electric power and the load’s ability to function properly under specific conditions. It is estimated that problems relating to power quality costs the European industry hundreds of billions of Euros annually. In contrast, financing for the prevention of these problems amount to fragments of these costs. Power Theories for Improved Power Quality addresses this imbalance by presenting and assessing a range of methods and problems related to improving the quality of electric power supply. Focusing particularly on active compensators and the DSP based control algorithms, Power Theories for Improved Power Quality introduces the fundamental problems of electrical power. This introduction is followed by chapters which discuss: •‘Power theories’ including their historical development and application to practical problems, •operational principles of active compensator’s DSP control based algorithms using examples and results from laboratory research, and •t...
Protective Controller against Cascade Outages with Selective Harmonic Compensation Function
Abramovich, B. N.; Kuznetsov, P. A.; Sychev, Yu A.
2018-05-01
The paper presents data on the power quality and development of protective devices for the power networks with distributed generation (DG).The research has shown that power quality requirements for DG networks differ from conventional ones. That is why main tendencies, protective equipment and filters should be modified. There isa developed algorithm for detection and prevention of cascade outages that can lead to the blackoutin DG networks and there was a proposed structural scheme for a new active power filter for selective harmonics compensation. Analysis of these theories and equipment led to the development of protective device that could monitor power balance and cut off non-important consumers. The last part of the article describes a microcontroller prototype developed for connection to the existing power station control center.
Control Strategy of Active Power Filter Based on Modular Multilevel Converter
Xie, Xifeng
2018-03-01
To improve the capacity, pressure resistance and the equivalent switching frequency of active power filter (APF), a control strategy of APF based on Modular Multilevel Converter (MMC) is presented. In this Control Strategy, the indirect current control method is used to achieve active current and reactive current decoupling control; Voltage Balance Control Strategy is to stabilize sub-module capacitor voltage, the predictive current control method is used to Track and control of harmonic currents. As a result, the harmonic current is restrained, and power quality is improved. Finally, the simulation model of active power filter controller based on MMC is established in Matlab/Simulink, the simulation proves that the proposed strategy is feasible and correct.
Energy Technology Data Exchange (ETDEWEB)
Park, M.G.; Kim, Y.H.; Cha, K.H.; Kim, M.K. [Korea Electric Power Research Institute, Taejon (Korea)
1999-07-01
A method is described to develop and H{infinity} filtering method for the dynamic compensation of self-powered neutron detectors normally used for fixed incore instruments. An H{infinity} norm of the filter transfer matrix is used as the optimization criteria in the worst-case estimation error sense. Filter modeling is performed for both continuous- and discrete-time models. The filter gains are optimized in the sense of noise attenuation level of H{infinity} setting. By introducing Bounded Real Lemma, the conventional algebraic Riccati inequalities are converted into Linear Matrix Inequalities (LMIs). Finally, the filter design problem is solved via the convex optimization framework using LMIs. The simulation results show that remarkable improvements are achieved in view of the filter response time and the filter design efficiency. (author). 15 refs., 4 figs., 3 tabs.
Modelling and Simulation of Single-Phase Series Active Compensator for Power Quality Improvement
Verma, Arun Kumar; Mathuria, Kirti; Singh, Bhim; Bhuvaneshwari, G.
2017-10-01
A single-phase active series compensator is proposed in this work to reduce harmonic currents at the ac mains and to regulate the dc link voltage of a diode bridge rectifier (DBR) that acts as the front end converter for a voltage source inverter feeding an ac motor. This ac motor drive is used in any of the domestic, commercial or industrial appliances. Under fluctuating ac mains voltages, the dc link voltage of the DBR depicts wide variations and hence the ac motor is used at reduced rating as compared to its name-plate rating. The active series compensator proposed here provides dual functions of improving the power quality at the ac mains and regulating the dc link voltage thus averting the need for derating of the ac motor.
Dharmalingam, Rajasekaran; Dash, Subhransu Sekhar; Senthilnathan, Karthikrajan; Mayilvaganan, Arun Bhaskar; Chinnamuthu, Subramani
2014-01-01
This paper deals with the performance of unified power quality conditioner (UPQC) based on current source converter (CSC) topology. UPQC is used to mitigate the power quality problems like harmonics and sag. The shunt and series active filter performs the simultaneous elimination of current and voltage problems. The power fed is linked through common DC link and maintains constant real power exchange. The DC link is connected through the reactor. The real power supply is given by the photovoltaic system for the compensation of power quality problems. The reference current and voltage generation for shunt and series converter is based on phase locked loop and synchronous reference frame theory. The proposed UPQC-CSC design has superior performance for mitigating the power quality problems.
Directory of Open Access Journals (Sweden)
Rajasekaran Dharmalingam
2014-01-01
Full Text Available This paper deals with the performance of unified power quality conditioner (UPQC based on current source converter (CSC topology. UPQC is used to mitigate the power quality problems like harmonics and sag. The shunt and series active filter performs the simultaneous elimination of current and voltage problems. The power fed is linked through common DC link and maintains constant real power exchange. The DC link is connected through the reactor. The real power supply is given by the photovoltaic system for the compensation of power quality problems. The reference current and voltage generation for shunt and series converter is based on phase locked loop and synchronous reference frame theory. The proposed UPQC-CSC design has superior performance for mitigating the power quality problems.
Dharmalingam, Rajasekaran; Dash, Subhransu Sekhar; Senthilnathan, Karthikrajan; Mayilvaganan, Arun Bhaskar; Chinnamuthu, Subramani
2014-01-01
This paper deals with the performance of unified power quality conditioner (UPQC) based on current source converter (CSC) topology. UPQC is used to mitigate the power quality problems like harmonics and sag. The shunt and series active filter performs the simultaneous elimination of current and voltage problems. The power fed is linked through common DC link and maintains constant real power exchange. The DC link is connected through the reactor. The real power supply is given by the photovoltaic system for the compensation of power quality problems. The reference current and voltage generation for shunt and series converter is based on phase locked loop and synchronous reference frame theory. The proposed UPQC-CSC design has superior performance for mitigating the power quality problems. PMID:25013854
Harmonic Mitigation Methods in Large Offshore Wind Power Plants
DEFF Research Database (Denmark)
Kocewiak, Łukasz Hubert; Chaudhary, Sanjay; Hesselbæk, Bo
2013-01-01
Various sources of harmonic problems in large wind power plants (WPPs) and optimized harmonic mitigation methods are presented in this paper. The harmonic problems such as sources of harmonic emission and amplification as well as harmonic stability are identified. Also modern preventive...... and remedial harmonic mitigation methods in terms of passive and active filtering are described. It is shown that WPP components such as long HVAC cables and park transformers can introduce significant low-frequency resonances which can affect wind turbine control system operation and overall WPP stability...... as well as amplification of harmonic distortion. It is underlined that there is a potential in terms of active filtering in modern grid-side converters in e.g. wind turbines, STATCOMs or HVDC stations utilized in modern large WPPs. It is also emphasized that the grid-side converter controller should...
Duan, Jiandong; Fan, Shaogui; Wu, Fengjiang; Sun, Li; Wang, Guanglin
2018-06-01
This paper proposes an instantaneous power control method for high speed permanent magnet synchronous generators (PMSG), to realize the decoupled control of active power and reactive power, through vector control based on a sliding mode observer (SMO), and a phase locked loop (PLL). Consequently, the high speed PMSG has a high internal power factor, to ensure efficient operation. Vector control and accurate estimation of the instantaneous power require an accurate estimate of the rotor position. The SMO is able to estimate the back electromotive force (EMF). The rotor position and speed can be obtained using a combination of the PLL technique and the phase compensation method. This method has the advantages of robust operation, and being resistant to noise when estimating the position of the rotor. Using instantaneous power theory, the relationship between the output active power, reactive power, and stator current of the PMSG is deduced, and the power constraint condition is analysed for operation at the unit internal power factor. Finally, the accuracy of the rotor position detection, the instantaneous power detection, and the control methods are verified using simulations and experiments.
Cooperative Control of Active Power Filters in Power Systems without Mutual Communication
Czech Academy of Sciences Publication Activity Database
Tlustý, J.; Škramlík, Jiří; Švec, J.; Valouch, Viktor
2010-01-01
Roč. 2010, č. 517184 (2010), s. 1-13 ISSN 1024-123X R&D Projects: GA AV ČR IAA200760703 Institutional research plan: CEZ:AV0Z20570509 Keywords : active power filter * power system * wireless cooperation Subject RIV: JA - Electronics ; Optoelectronics, Electric al Engineering Impact factor: 0.689, year: 2010 http://www.hindawi.com/journals/mpe/2010/517184.html
DEFF Research Database (Denmark)
Naderipour, A.; Mohd Zin, A. A.; Habibuddin, M.H.
2015-01-01
devices, such as Active Power Filters (APFs). The proposed control method is composed of the Adjustable Synchronous Reference Frame (ASRF) and the Synchronous Reference Frame (SRF) methods. The ASRF and SRF are proposed to control the power injection and harmonic current compensation, respectively......In this paper, a new method is proposed to control the interface Inverter of distributed generators (DGs) in a microgrid. The objective of this method is to effectively compensate for the harmonic currents at the Point of Common Coupling (PCC) and the MG with the Absence of dedicated compensation....... The merged control methods are proposed for the interface inverter to perform the comprehensive activity of compensating for the harmonics, such as a correction of the system imbalance and the removal of the harmonics. The operation principle of the proposed control method is analyzed in detail, and its...
Bush, Craig R.
This dissertation presents a novel current source converter topology that is primarily intended for single-phase photovoltaic (PV) applications. In comparison with the existing PV inverter technology, the salient features of the proposed topology are: a) the low frequency (double of line frequency) ripple that is common to single-phase inverters is greatly reduced; b) the absence of low frequency ripple enables significantly reduced size pass components to achieve necessary DC-link stiffness and c) improved maximum power point tracking (MPPT) performance is readily achieved due to the tightened current ripple even with reduced-size passive components. The proposed topology does not utilize any electrolytic capacitors. Instead an inductor is used as the DC-link filter and reliable AC film capacitors are utilized for the filter and auxiliary capacitor. The proposed topology has a life expectancy on par with PV panels. The proposed modulation technique can be used for any current source inverter where an unbalanced three-phase operation is desires such as active filters and power controllers. The proposed topology is ready for the next phase of microgrid and power system controllers in that it accepts reactive power commands. This work presents the proposed topology and its working principle supported by with numerical verifications and hardware results. Conclusions and future work are also presented.
Directory of Open Access Journals (Sweden)
Ye. I. Sokol
2017-08-01
Full Text Available Purpose. Information technologies allow multidimensional analysis of information about the state of the power system in a single information space in terms of providing network-centric approach to control and use of unmanned aerial vehicles as tools for condition monitoring of three-phase network. Methodology. The idea of energy processes in three independent (rather than four dependent curves vector-functions with values in the arithmetic three-dimensional space adequately for both 4-wire and 3–wire circuits. The presence of zero sequence current structural (and mathematically features a 4-wire scheme of energy from a 3-wire circuit. The zero sequence voltage caused by the displacement of the zero voltage phases. Offset zero in the calculations can be taken into account by appropriate selection of the reference voltages. Both of these energetic phenomena with common methodical positions are described in the framework of the general mathematical model, in which a significant role is played by the ort zero sequence. Results. Vector approach with a unified voice allows us to obtain and analyze new energy characteristics for 4–wire and 3–wire circuits in sinusoidal and non-sinusoidal mode, both in temporal and frequency domain. Originality. Symmetric sinusoidal mode is balanced, even with non-zero reactive power. The converse is not true. The mode can be balanced and unbalanced load. The mode can be balanced and unbalanced voltage. Practical value. Assessing balance in network mode and the impact of instantaneous power on the magnitude of the losses, will allow to avoid the appearance of zero sequence and, thus, to improve the quality of electricity.
Multi-objective Design Method for Hybrid Active Power Filter
Yu, Jingrong; Deng, Limin; Liu, Maoyun; Qiu, Zhifeng
2017-10-01
In this paper, a multi-objective optimal design for transformerless hybrid active power filter (HAPF) is proposed. The interactions between the active and passive circuits is analyzed, and by taking the interactions into consideration, a three-dimensional objective problem comprising of performance, efficiency and cost of HAPF system is formulated. To deal with the multiple constraints and the strong coupling characteristics of the optimization model, a novel constraint processing mechanism based on distance measurement and adaptive penalty function is presented. In order to improve the diversity of optimal solution and the local searching ability of the particle swarm optimization (PSO) algorithm, a chaotic mutation operator based on multistage neighborhood is proposed. The simulation results show that the optimums near the ordinate origin of the three-dimension space make better tradeoff among the performance, efficiency and cost of HAPF, and the experimental results of transformerless HAPF verify the effectiveness of the method for multi-objective optimization and design.
Dynamic impedance compensation for wireless power transfer using conjugate power
Liu, Suqi; Tan, Jianping; Wen, Xue
2018-02-01
Wireless power transfer (WPT) via coupled magnetic resonances has been in development for over a decade. However, the frequency splitting phenomenon occurs in the over-coupled region. Thus, the output power of the two-coil system achieves the maximum output power at the two splitting angular frequencies, and not at the natural resonant angular frequency. According to the maximum power transfer theorem, the impedance compensation method was adopted in many WPT projects. However, it remains a challenge to achieve the maximum output power and transmission efficiency in a fixed-frequency mode. In this study, dynamic impedance compensation for WPT was presented by utilizing the compensator within a virtual three-coil WPT system. First, the circuit model was established and transfer characteristics of a system were studied by utilizing circuit theories. Second, the power superposition of the WPT system was carefully researched. When a pair of compensating coils was inserted into the transmitter loop, the conjugate power of the compensator loop was created via magnetic coupling of the two compensating coils that insert into the transmitter loop. The mechanism for dynamic impedance compensation for wireless power transfer was then provided by investigating a virtual three-coil WPT system. Finally, the experimental circuit of a virtual three-coil WPT system was designed, and experimental results are consistent with the theoretical analysis, which achieves the maximum output power and transmission efficiency.
Dynamic impedance compensation for wireless power transfer using conjugate power
Directory of Open Access Journals (Sweden)
Suqi Liu
2018-02-01
Full Text Available Wireless power transfer (WPT via coupled magnetic resonances has been in development for over a decade. However, the frequency splitting phenomenon occurs in the over-coupled region. Thus, the output power of the two-coil system achieves the maximum output power at the two splitting angular frequencies, and not at the natural resonant angular frequency. According to the maximum power transfer theorem, the impedance compensation method was adopted in many WPT projects. However, it remains a challenge to achieve the maximum output power and transmission efficiency in a fixed-frequency mode. In this study, dynamic impedance compensation for WPT was presented by utilizing the compensator within a virtual three-coil WPT system. First, the circuit model was established and transfer characteristics of a system were studied by utilizing circuit theories. Second, the power superposition of the WPT system was carefully researched. When a pair of compensating coils was inserted into the transmitter loop, the conjugate power of the compensator loop was created via magnetic coupling of the two compensating coils that insert into the transmitter loop. The mechanism for dynamic impedance compensation for wireless power transfer was then provided by investigating a virtual three-coil WPT system. Finally, the experimental circuit of a virtual three-coil WPT system was designed, and experimental results are consistent with the theoretical analysis, which achieves the maximum output power and transmission efficiency.
DEFF Research Database (Denmark)
Wang, Xiongfei; Blaabjerg, Frede; Loh, Poh Chiang
2015-01-01
Active damping and harmonic compensation are two common challenges faced by LCL-filtered voltage source converters. To manage them holistically, this paper begins by proposing a virtual RC damper in parallel with the passive filter capacitor. The virtual damper is actively inserted by feeding back...... the passive capacitor current through a high-pass filter, which indirectly, furnishes two superior features. They are the mitigation of phase lag experienced by a conventional damper and the avoidance of instability caused by the negative resistance inserted unintentionally. Moreover, with the virtual RC...
Chen, Jun; Zhu, Guang; Yang, Weiqing; Jing, Qingshen; Bai, Peng; Yang, Ya; Hou, Te-Chien; Wang, Zhong Lin
2013-11-13
A harmonic-resonator-based triboelectric nanogenerator (TENG) is presented as a sustainable power source and an active vibration sensor. It can effectively respond to vibration frequencies ranging from 2 to 200 Hz with a considerably wide working bandwidth of 13.4 Hz. This work not only presents a new principle in the field of vibration energy harvesting but also greatly expands the applicability of TENGs. © 2013 WILEY-VCH Verlag GmbH & Co. KGaA, Weinheim.
A Study of Parallel Operation of an active Filter and passive Filters
DEFF Research Database (Denmark)
Chen, Zhe; Blaabjerg, Frede; Pedersen, John Kim
2002-01-01
This paper reports investigations of the parallel operations of a current controlled active filter and passive filters in a system with current harmonic sources. The task of reactive power and harmonic compensation is shared by the active filter and passive filters. The passive filters are used...... arrangements of the active and passive filters can operate relatively independently, also the compensation flexibility of the active filter can be fully exploited, such as one active filter for several harmonic sources.The simulation studies on various systems have been performed to evaluate the effectiveness...... of the systems. The results show that the power factor is corrected by the passive filters, harmonics are minimized by both active and passive filters and overloading of the filter system can be avoided....
Harmonics in transmission power systems
DEFF Research Database (Denmark)
Wiechowski, Wojciech Tomasz
. The comparison shows that results obtained used both types of the cores are the same, so it is concluded that both cores can be used for harmonic measurements. Low-inductance resistors are introduced in the secondary circuits, in series with the metering and protective relaying. On those resistors, the harmonic......Some time ago, Energinet.dk, the Transmission System Operator of the 150 kV and 400 kV transmission network in Denmark, had experienced operational malfunctions of some of the measuring and protection equipment. Also an overloading of a harmonic filter has been reported, and therefore, a need...... end only so the ground is not used as a return path. A way to reduce the capacitive coupling is to provide shielding. Harmonic currents are measured using the conventional inductive voltage transformers. Both protective and metering cores were compared if they could be used for harmonic measurements...
Reduction of dc-link capacitance for three-phase three-wire shunt active power filters
DEFF Research Database (Denmark)
Jin, Chi; Tang, Yi; Wang, Peng
2013-01-01
. This paper presents the concept of dc-link compensator (DLC) that aims to decouple the harmonic power from the dc-link of APF. With proper system sizing and design, most of the harmonic power can be eliminated by this DLC circuit and very small electrolytic capacitors or even film type capacitors can be used...
Harmonic Resonances in Wind Power Plants
DEFF Research Database (Denmark)
Fernandez, Francisco Daniel Freijedo; Chaudhary, Sanjay; Teodorescu, Remus
2015-01-01
This work reviews the state-of-the-art in the field of harmonic resonance problems in Wind Power Plants (WPPs). Firstly, a generic WPP is modeled according to the equivalent circuits of its passive and active components. Main focus is put on modeling active components, i.e. the ones based on power...... converters. Subsequently, pros and cons of frequency and time domain analysis methods are outlined. The next sections are devoted to mitigation methods implemented in the power electronics converters. From the wind turbine perspective, different techniques to enhance the robustness of the controller...... are analyzed. Subsequently, the suitability for active damping of harmonics using STATCOM devices is assessed, with focus both on control techniques and power converter technologies....
DEFF Research Database (Denmark)
Golestan, Saeed; Monfared, Mohammad; Guerrero, Josep M.
2013-01-01
The reference current generation (RCG) is a crucial part in the control of a shunt active power filter (APF). A variety of RCG techniques have been proposed in literature. Among these, the instantaneous reactive power theory, called pq theory, is probably the most widely used technique. The pq...... theory offers advantages such as satisfactory steady-state and dynamic performance, and at the same time simple digital implementation, however its application was limited to three-phase systems. To exploit the advantages of pq theory in single-phase systems, the single-phase pq theory has been proposed...... recently. In this paper, a simple and effective implementation of the single phase pq theory for single-phase shunt APFs is proposed. The suggested approach is based on employing second order generalized integrators (SOGI), and a phase locked loop (PLL). To fine tune the control parameters, a systematic...
Modelling and Simulation of Grid Connected SPV System with Active Power Filtering Features
Saroha, Jaipal; Pandove, Gitanjali; Singh, Mukhtiar
2017-09-01
In this paper, the detailed simulation studies for a grid connected solar photovoltaic system (SPV) have been presented. The power electronics devices like DC-DC boost converter and grid interfacing inverter are most important components of proposed system. Here, the DC-DC boost converter is controlled to extract maximum power out of SPV under different irradiation levels, while the grid interfacing inverter is utilized to evacuate the active power and feed it into grid at synchronized voltage and frequency. Moreover, the grid interfacing inverter is also controlled to sort out the issues related to power quality by compensating the reactive power and harmonics current component of nearby load at point of common coupling. Besides, detailed modeling of various component utilized in proposed system is also presented. Finally, extensive simulations have been performed under different irradiation levels with various kinds of load to validate the aforementioned claims. The overall system design and simulation have been performed by using Sim Power System toolbox available in the library of MATLAB.
Active Power Filter DC Bus Voltage Piecewise Reaching Law Variable Structure Control
Directory of Open Access Journals (Sweden)
Baolian Liu
2014-01-01
Full Text Available The DC bus voltage stability control is one key technology to ensure that Active Power Filter (APF operates stably. The external disturbances such as power grid and load fluctuation and the system parameters changing may affect the stability of APF DC bus voltage and the normal operation of APF. The mathematical model of DC bus voltage is established according to power balance principle and a DC bus voltage piecewise reaching law variable structure control algorithm is proposed to solve the above problem, and the design method is given. The simulation and experiment results proved that the proposed variable structure control algorithm can eliminate the chattering problem existing in traditional variable structure control effectively, is insensitive to system disturbance, and has good robustness and fast dynamic response speed and stable DC bus voltage with small fluctuation. The above advantages ensure the compensation effect of APF.
Static compensators (STATCOMs) in power systems
Shahnia, Farhad; Ghosh, Arindam
2014-01-01
A static compensator (STATCOM), also known as static synchronous compensator, is a member of the flexible alternating current transmission system (FACTS) devices. It is a power-electronics based regulating device which is composed of a voltage source converter (VSC) and is shunt-connected to alternating current electricity transmission and distribution networks. The voltage source is created from a DC capacitor and the STATCOM can exchange reactive power with the network. It can also supply some active power to the network, if a DC source of power is connected across the capacitor. A STATCOM
A New Synchronous Reference Frame-Based Method for Single-Phase Shunt Active Power Filters
DEFF Research Database (Denmark)
Monfared, Mohammad; Golestan, Saeed; Guerrero, Josep M.
2013-01-01
This paper deals with the design of a novel method in the synchronous reference frame (SRF) to extract the reference compensating current for single-phase shunt active power filters (APFs). Unlike previous works in the SRF, the proposed method has an innovative feature that it does not need...... the fictitious current signal. Frequency-independent operation, accurate reference current extraction and relatively fast transient response are other key features of the presented strategy. The effectiveness of the proposed method is investigated by means of detailed mathematical analysis. The results confirm...
An active trap filter for high-power voltage source converters
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Loh, Poh Chiang
2015-01-01
This paper proposes a power electronic based device to actively trap the switching current ripples for highpower converters. Control principle and system design of the active trap filter are discussed first. Comparisons of the active trap filter with LCL and LLCL filters are then carried out...
A High Power Density Integrated Charger for Electric Vehicles with Active Ripple Compensation
Pan, Liwen; Zhang, Chengning
2015-01-01
This paper suggests a high power density on-board integrated charger with active ripple compensation circuit for electric vehicles. To obtain a high power density and high efficiency, silicon carbide devices are reported to meet the requirement of high-switching-frequency operation. An integrated bidirectional converter is proposed to function as AC/DC battery charger and to transfer energy between battery pack and motor drive of the traction system. In addition, the conventional H-bridge cir...
A High Power Density Integrated Charger for Electric Vehicles with Active Ripple Compensation
Directory of Open Access Journals (Sweden)
Liwen Pan
2015-01-01
Full Text Available This paper suggests a high power density on-board integrated charger with active ripple compensation circuit for electric vehicles. To obtain a high power density and high efficiency, silicon carbide devices are reported to meet the requirement of high-switching-frequency operation. An integrated bidirectional converter is proposed to function as AC/DC battery charger and to transfer energy between battery pack and motor drive of the traction system. In addition, the conventional H-bridge circuit suffers from ripple power pulsating at second-order line frequency, and a scheme of active ripple compensation circuit has been explored to solve this second-order ripple problem, in which a pair of power switches shared traction mode, a ripple energy storage capacitor, and an energy transfer inductor. Simulation results in MATLAB/Simulink validated the eligibility of the proposed topology. The integrated charger can work as a 70 kW motor drive circuit or a converter with an active ripple compensation circuit for 3 kW charging the battery. The impact of the proposed topology and control strategy on the integrated charger power losses, efficiency, power density, and thermal performance has also been analysed and simulated.
Probabilistic Harmonic Modeling of Wind Power Plants
DEFF Research Database (Denmark)
Guest, Emerson; Jensen, Kim H.; Rasmussen, Tonny Wederberg
2017-01-01
A probabilistic sequence domain (SD) harmonic model of a grid-connected voltage-source converter is used to estimate harmonic emissions in a wind power plant (WPP) comprised of Type-IV wind turbines. The SD representation naturally partitioned converter generated voltage harmonics into those...... with deterministic phase and those with probabilistic phase. A case study performed on a string of ten 3MW, Type-IV wind turbines implemented in PSCAD was used to verify the probabilistic SD harmonic model. The probabilistic SD harmonic model can be employed in the planning phase of WPP projects to assess harmonic...
A novel control technique for active shunt power filters for aircraft applications
Lavopa, Elisabetta
2011-01-01
The More Electric Aircraft is a technological trend in modern aerospace industry to increasingly use electrical power on board the aircraft in place of mechanical, hydraulic and pneumatic power to drive aircraft subsystems. This brings major changes to the aircraft electrical system, increasing the complexity of the network topology together with stability and power quality issues. Shunt active power filters are a viable solution for power quality enhancement, in order to comply with the stan...
Grid-Connection Half-Bridge PV Inverter System for Power Flow Controlling and Active Power Filtering
Directory of Open Access Journals (Sweden)
Chih-Lung Shen
2012-01-01
Full Text Available A half-bridge photovoltaic (PV system is proposed, which can not only deal with bidirectional power flowing but also improve power quality. According to varying insolation, the system conditions real power for dc and ac loads to accommodate different amounts of PV power. Furthermore, the system eliminates current harmonics and improves power factor simultaneously. As compared with conventional PV inverter, the total number of active switches and current sensors can be reduced so that its cost is lower significantly. For current command determination, a linear-approximation method (LAM is applied to avoid the complicated calculation and achieve the maximum power point tracking (MPPT feature. For current controlling, a direct-source-current-shaping (DSCS algorithm is presented to shape the waveform of line current. Simulation results and practical measurements also demonstrate the feasibility of the proposed half-bridge PV system.
Instantaneous input electrical power measurements of HITU transducer
Energy Technology Data Exchange (ETDEWEB)
Karaboece, B; Guelmez, Y [Tuebitak Ulusal Metroloji Enstituesue (UME), P.K. 54 41470 Gebze-Kocaeli (Turkey); Rajagapol, S; Shaw, A, E-mail: baki.karaboce@ume.tubitak.gov.t [National Physical Laboratory (NPL), Hampton Road, Teddington TW11 0LW (United Kingdom)
2011-02-01
HITU (High Intensity Theraupetic Ultrasound) transducers are widely used in therapeutic ultrasound in medicine. The output ultrasonic power of HITU transducer can be measured in number of methods described in IEC 61161 standard [1]. New IEC standards specifically for measurement of HITU equipment are under development. The ultrasound power radiated from a transducer is dependent on applied input electrical voltage and current and consequently power. But, up to now, no standardised method has been developed and adopted for the input electrical power measurements. Hence, a workpackage was carried out for the establishment of such method in the frequency range of 1 to 3 MHz as a part of EURAMET EMRP Era-net plus 'External Beam Cancer Therapy' project. Several current shunts were developed and evaluated. Current measurements were also realized with Philips current probe and preamplifier at NPL and Agilent current probe at UME. In this paper, a method for the measurement of instantaneous electrical power delivered to a reactive ultrasound transducer in the required frequency range is explored.
Instantaneous input electrical power measurements of HITU transducer
International Nuclear Information System (INIS)
Karaboece, B; Guelmez, Y; Rajagapol, S; Shaw, A
2011-01-01
HITU (High Intensity Theraupetic Ultrasound) transducers are widely used in therapeutic ultrasound in medicine. The output ultrasonic power of HITU transducer can be measured in number of methods described in IEC 61161 standard [1]. New IEC standards specifically for measurement of HITU equipment are under development. The ultrasound power radiated from a transducer is dependent on applied input electrical voltage and current and consequently power. But, up to now, no standardised method has been developed and adopted for the input electrical power measurements. Hence, a workpackage was carried out for the establishment of such method in the frequency range of 1 to 3 MHz as a part of EURAMET EMRP Era-net plus 'External Beam Cancer Therapy' project. Several current shunts were developed and evaluated. Current measurements were also realized with Philips current probe and preamplifier at NPL and Agilent current probe at UME. In this paper, a method for the measurement of instantaneous electrical power delivered to a reactive ultrasound transducer in the required frequency range is explored.
Harmonics in a Wind Power Plant: Preprint
Energy Technology Data Exchange (ETDEWEB)
Preciado, V.; Madrigal, M.; Muljadi, E.; Gevorgian, V.
2015-04-02
Wind power generation has been growing at a very fast pace for the past decade, and its influence and impact on the electric power grid is significant. As in a conventional power plant, a wind power plant (WPP) must ensure that the quality of the power being delivered to the grid is excellent. At the same time, the wind turbine should be able to operate immune to small disturbances coming from the grid. Harmonics are one of the more common power quality issues presented by large WPPs because of the high switching frequency of the power converters and the possible nonlinear behavior from electric machines (generator, transformer, reactors) within a power plant. This paper presents a summary of the most important issues related to harmonics in WPPs and discusses practical experiences with actual Type 1 and Type 3 wind turbines in two WPPs.
A Multi-Functional Power Electronic Converter in Distributed Generation Power Systems
DEFF Research Database (Denmark)
Chen, Zhe; Blaabjerg, Frede; Pedersen, John Kim
2005-01-01
of the converter interfacing a wind power generation unit is also given. The power electronic interface performs the optimal operation in the wind turbine system to extract the maximum wind power, while it also plays a key role in a hybrid compensation system that consists of the active power electronic converter......This paper presents a power electronic converter which is used as an interface for a distributed generation unit/energy storage device, and also functioned as an active power compensator in a hybrid compensation system. The operation and control of the converter have been described. An example...... and passive filters connected to each distorting load or distributed generation (DG) unit. The passive filters are distributely located to remove major harmonics and provide reactive power compensation. The active power electronic filter corrects the system unbalance, removes the remaining harmonic components...
Kwak, Kiho; Kwak, Dongmin; Yoon, Joohong
2015-08-01
A design of an Instantaneous High Power Supply System (IHPSS) with a power distribution management (PDM) for portable military devices is newly addressed. The system includes a power board and a hybrid battery that can not only supply instantaneous high power but also maintain stable operation at critical low temperature (-30 °C). The power leakage and battery overcharge are effectively prevented by the optimal PDM. The performance of the proposed system under the required pulse loads and the operating conditions of a Korean Advanced Combat Rifle employed in the battlefield is modeled with simulations and verified experimentally. The system with the IHPSS charged the fuse setter with 1.7 times higher voltage (8.6 V) than the one without (5.4 V) under the pulse discharging rate (1 A at 0.5 duty, 1 ms) for 500 ms.
Transients in reactors for power systems compensation
Abdul Hamid, Haziah
This thesis describes new models and investigations into switching transient phenomena related to the shunt reactors and the Mechanically Switched Capacitor with Damping Network (MSCDN) operations used for reactive power control in the transmission system. Shunt reactors and MSCDN are similar in that they have reactors. A shunt reactor is connected parallel to the compensated lines to absorb the leading current, whereas the MSCDN is a version of a capacitor bank designed as a C-type filter for use in the harmonic-rich environment. In this work, models have been developed and transient overvoltages due to shunt reactor deenergisation were estimated analytically using MathCad, a mathematical program. Computer simulations used the ATP/EMTP program to reproduce both single-phase and three-phase shunt reactor switching at 275 kV operational substations. The effect of the reactor switching on the circuit breaker grading capacitor was also examined by considering various switching conditions.. The main original achievement of this thesis is the clarification of failure mechanisms occurring in the air-core filter reactor due to MSCDN switching operations. The simulation of the MSCDN energisation was conducted using the ATP/EMTP program in the presence of surge arresters. The outcome of this simulation shows that extremely fast transients were established across the air-core filter reactor. This identified transient event has led to the development of a detailed air-core reactor model, which accounts for the inter-turn RLC parameters as well as the stray capacitances-to-ground. These parameters are incorporated into the transient simulation circuit, from which the current and voltage distribution across the winding were derived using electric field and equivalent circuit modelling. Analysis of the results has revealed that there are substantial dielectric stresses imposed on the winding insulation that can be attributed to a combination of three factors. (i) First, the
Sitaram, Mahesh I; Padiyar, KR; Ramanarayanan, V
1998-01-01
Active filters have long been in use for the filtering of power system load harmonics. In this paper, the digital simulation results of a hybrid active power filter system for a rectifier load are presented. The active filter is used for filtering higher order harmonics as the dominant harmonics are filtered by the passive filter. This reduces the rating of the active filter significantly. The DC capacitor voltage of the active filter is controlled using a PI controller.
Power Divider for Waveforms Rich in Harmonics
Sims, William Herbert, III
2005-01-01
A method for dividing the power of an electronic signal rich in harmonics involves the use of an improved divider topology. A divider designed with this topology could be used, for example, to propagate a square-wave signal in an amplifier designed with a push-pull configuration to enable the generation of more power than could be generated in another configuration.
Reactive power compensation a practical guide
Hofmann, Wolfgang; Just, Wolfgang
2012-01-01
The comprehensive resource on reactive power compensation, presenting the design, application and operation of reactive power equipment and installations The area of reactive power compensation is gaining increasing importance worldwide. If suitably designed, it is capable of improving voltage quality significantly, meaning that losses in equipment and power systems are reduced, the permissible loading of equipment can be increased, and the over-all stability of system operation improved. Ultimately, energy use and CO2 emisson are reduced. This unique guide discusses the
Active Power Filter DC Bus Voltage Piecewise Reaching Law Variable Structure Control
Liu, Baolian; Ding, Zujun; Zhao, Huanyu; Jin, Defei
2014-01-01
The DC bus voltage stability control is one key technology to ensure that Active Power Filter (APF) operates stably. The external disturbances such as power grid and load fluctuation and the system parameters changing may affect the stability of APF DC bus voltage and the normal operation of APF. The mathematical model of DC bus voltage is established according to power balance principle and a DC bus voltage piecewise reaching law variable structure control algorithm is proposed to solve the ...
Active filter for INDUS-2 Q4 and Q5 power supplies
International Nuclear Information System (INIS)
Singh, Y.P.; Thakurta, A.C.; Kotaiah, S.
2003-01-01
Q4 and Q5 power supplies are SCR based power supplies wherein the rectified voltage is fed to a passive filter to reduce the ripple voltage. The output of the passive filter still contains some ripple particularly on the low frequency side. Attenuation of this ripple with passive filter necessitates increase in size of L and C and leads to sluggishness of the system. The design and the test results of an active filter module have been discussed wherein the low frequency attenuation can be very effectively taken care of by, allowing this to be absorbed in a coupling transformer put after the passive filter. Considerable size reduction has been achieved by using switching techniques. Low frequency attenuation has been made quite a simple task. This filter also helps in handling transients from input. (author)
Modeling and analysis of harmonic resonance in a power electronics based AC power system
DEFF Research Database (Denmark)
Wang, Xiongfei; Blaabjerg, Frede; Chen, Zhe
2013-01-01
The dynamic interactions among the interconnected power converters may bring in harmonic resonance in a power electronics based power system. This paper addresses this issue in a power system dominated by multiple current- and voltage-controlled inverters with LCL- and LC-filters. The impedance...... stability criterion. To validate the theoretical analysis, the time domain simulations and experimental tests on a three-inverter-based system are presented....
Optimal Selective Harmonic Control for Power Harmonics Mitigation
DEFF Research Database (Denmark)
Zhou, Keliang; Yang, Yongheng; Blaabjerg, Frede
2015-01-01
of power harmonics. The proposed optimal SHC is of hybrid structure: all recursive SHC modules with weighted gains are connected in parallel. It bridges the real “nk+-m order RC” and the complex “parallel structure RC”. Compared to other IMP based control solutions, it offers an optimal trade-off among...
D.C. side active filter for high stability accelerator magnet power supplies
International Nuclear Information System (INIS)
Singh, Yash Pal; Thakurta, A.C.; Kotaiah, S.
2006-01-01
Accelerator d.c, magnets have to produce a highly stable magnetic field which in turn needs highly stable d.c. current sources to energise them. Indus-II Q4 and Q5 power supplies are SCR based power supplies wherein the rectified voltage is fed to a passive filter to reduce the ripple voltage. The output of the passive filter still contains some ripple particularly on the low frequency side. The design and the test results of an active filter module have been discussed wherein the low frequency attenuation can be very effectively taken care of by allowing this to be absorbed in a coupling transformer put after the passive filter. Considerable size reduction has been achieved by using switching techniques. Low frequency attenuation has been made quite a simple task. This filter also helps in handling transients from input. (author)
Dynamic impedance compensation for wireless power transfer using conjugate power
Suqi Liu; Jianping Tan; Xue Wen
2018-01-01
Wireless power transfer (WPT) via coupled magnetic resonances has been in development for over a decade. However, the frequency splitting phenomenon occurs in the over-coupled region. Thus, the output power of the two-coil system achieves the maximum output power at the two splitting angular frequencies, and not at the natural resonant angular frequency. According to the maximum power transfer theorem, the impedance compensation method was adopted in many WPT projects. However, it remains a c...
A PLL-based multirate structure for time-varying power systems harmonic/interharmonic estimation
Carvalho, de J.R.; Duque, C.A.; Ribeiro, M.V.; Cerqueira, A.S.; Baldwin, T.L.; Ribeiro, P.F.
2009-01-01
This paper describes a phase-locked-loop (PLL)-based power systems harmonic estimation algorithm, which uses an analysis filter bank and multirate processing. The filter bank is composed of bandpass filters. The initial center frequency of each filter is purposely chosen to be equal to harmonic
An Enhanced Islanding Microgrid Reactive Power, Imbalance Power, and Harmonic Power Sharing Scheme
DEFF Research Database (Denmark)
He, Jinwei; Lin, Yun Wei; Blaabjerg, Frede
2015-01-01
To address inaccurate power sharing problems in autonomous islanding microgrids, an enhanced droop control method through online virtual impedance adjustment is proposed. First, a term associated with DG reactive power, imbalance power, or harmonic power is added to the conventional real power...
DEFF Research Database (Denmark)
He, Jinwei; Li, Yun Wei; Blaabjerg, Frede
2013-01-01
To address inaccurate power sharing problems in autonomous islanding microgrids, an enhanced droop control method through adaptive virtual impedance adjustment is proposed. First, a term associated with DG reactive power, imbalance power or harmonic power is added to the conventional real power...
Microgrid Reactive and Harmonic Power Sharing Using Enhanced Virtual Impedance
DEFF Research Database (Denmark)
He, Jinwei; Wei Li, Yun; Guerrero, Josep M.
2013-01-01
To address the load sharing problem in islanding microgrids, this paper proposes an improved approach which regulates the distributed generation (DG) unit interfacing virtual impedance at fundamental and selected harmonic frequencies. In contrast to the conventional virtual impedance control where...... only a line current feed-forward term is added to the DG voltage reference, the proposed virtual impedances at fundamental and harmonic frequencies are realized using DG line current and point of common coupling (PCC) voltage feed-forward terms, respectively. With this modification, the mismatched DG...... feeder impedances can be properly compensated, resulting in accurate reactive and harmonic power sharing at the same time. In addition, this paper shows that the microgrid PCC harmonic voltages can be mitigated by reducing the magnitude of DG unit equivalent harmonic impedance. Finally, an improved...
DEFF Research Database (Denmark)
Blaabjerg, Frede; Asiminoaei, Lucian; Malinowski, M.
2008-01-01
The classical discontinuous pulsewidth modulations (DPWMs) cannot be efficiently applied in active power filters (APFs) because it is difficult to predict the peak values of the inverter current. Consequently, it is difficult to calculate the optimal position of the clamped interval to minimize t...
A Decoupling Control Method for Shunt Hybrid Active Power Filter Based on Generalized Inverse System
Directory of Open Access Journals (Sweden)
Xin Li
2017-01-01
Full Text Available In this paper, a novel decoupling control method based on generalized inverse system is presented to solve the problem of SHAPF (Shunt Hybrid Active Power Filter possessing the characteristics of 2-input-2-output nonlinearity and strong coupling. Based on the analysis of operation principle, the mathematical model of SHAPF is firstly built, which is verified to be invertible using interactor algorithm; then the generalized inverse system of SHAPF is obtained to connect in series with the original system so that the composite system is decoupled under the generalized inverse system theory. The PI additional controller is finally designed to control the decoupled 1-order pseudolinear system to make it possible to adjust the performance of the subsystem. The simulation results demonstrated by MATLAB show that the presented generalized inverse system strategy can realise the dynamic decoupling of SHAPF. And the control system has fine dynamic and static performance.
Directory of Open Access Journals (Sweden)
Fuka Ikeda
2017-06-01
Full Text Available This paper discusses harmonic current compensation of the constant DC-capacitor voltage-control (CDCVC-based strategy of smart chargers for electric vehicles (EVs in single-phase three-wire distribution feeders (SPTWDFs under nonlinear load conditions. The basic principle of the CDCVC-based harmonics compensation strategy under nonlinear load conditions is discussed in detail. The instantaneous power flowing into the three-leg pulse-width modulated (PWM rectifier, which performs as a smart charger, shows that the CDCVC-based strategy achieves balanced and sinusoidal source currents with a unity power factor. The CDCVC-based harmonics compensation strategy does not require any calculation blocks of fundamental reactive, unbalanced active, and harmonic currents. Thus, the authors propose a simplified algorithm to compensate for reactive, unbalanced active, and harmonic currents. A digital computer simulation is implemented to confirm the validity and high practicability of the CDCVC-based harmonics compensation strategy using PSIM software. Simulation results demonstrate that balanced and sinusoidal source currents with a unity power factor in SPTWDFs are obtained on the secondary side of the pole-mounted distribution transformer (PMDT during both the battery-charging and discharging operations in EVs, compensating for the reactive, unbalanced active, and harmonic currents.
ARTIFICIAL INTELLIGENT SYSTEM FOR MEASUREMENT OF HARMONIC POWERS
Directory of Open Access Journals (Sweden)
Jovitha Jerome
2017-11-01
Full Text Available The importance of the electric power quality (PQ demands new methodologies and measurement tools in the power industry for the analysis and measurement of the basic electric magnitudes necessary. This paper presents a new measurement procedure based on neural networks for the estimation of harmonic amplitudes of current/voltage and respective harmonic powers. The measurement scheme is built with two neural network modules. The first module is an adaptive linear neuron (ADALINE that is the kernel part of estimation of complex harmonic coefficients of the current/voltage. The second module is feedforward neural network that obtains the harmonic active/reactive powers. In order to perform digital simulation the Feedforward and Adaline neural network tools were developed in LabVIEW. This measurement algorithm was tested for the practical cases and found to be robust, computationally fast and efficient.
An introduction to reactive power compensation for wind farms
International Nuclear Information System (INIS)
Nigim, K.A.; Cairo Univ., Giza; Zobaa, A.F.; El Amin, I.
2005-01-01
The paper summarises the refereed contributions of seven articles reviewed for publication in the IJETP - Special Issue on 'Reactive compensation for wind farms'. The main goal of the special issue is to provide a forum to exchange information on the reactive power compensation requirements for wind farms and introducing possible price mechanisms for today's deregulated power industry. Uncompensated reactive power causes stress on the hosting utility grid as well as added expenses, which create in difficulties for power purchasing agreements from independent wind energy producers. Wind power producers need to comply with the hosting utility grid interconnection standards, e.g., voltage and frequency, as well as to provide controllable active and reactive sources of power. Active power supply is mainly dependent on the potential of wind power produced and the turbine design. Reactive power demand on the other hand depends on the conversion devices and the recovered power quantity fed to the grid. Static Var Compensators (SVC), Unified Power Quality Conditioners (UPQC), Unified Power Flow Controllers (UPFC), and the Distributed Static Synchronous Compensators (DSTATCOM) are all new emerging devices aimed at regulating the reactive power requirements. The excellent controllability of these devices has paved the way to flexible and dynamic controllers that are capable of regulating the flow of active and reactive power components. These devices are now suggested for the control of the reactive power requirement of wind generators. Studies have demonstrated acceptable voltage stabilisation results. This has increased the penetration level of wind power into existing distribution networks in many countries. (Author)
Voltage harmonic elimination with RLC based interface smoothing filter
International Nuclear Information System (INIS)
Chandrasekaran, K; Ramachandaramurthy, V K
2015-01-01
A method is proposed for designing a Dynamic Voltage Restorer (DVR) with RLC interface smoothing filter. The RLC filter connected between the IGBT based Voltage Source Inverter (VSI) is attempted to eliminate voltage harmonics in the busbar voltage and switching harmonics from VSI by producing a PWM controlled harmonic voltage. In this method, the DVR or series active filter produces PWM voltage that cancels the existing harmonic voltage due to any harmonic voltage source. The proposed method is valid for any distorted busbar voltage. The operating VSI handles no active power but only harmonic power. The DVR is able to suppress the lower order switching harmonics generated by the IGBT based VSI. Good dynamic and transient results obtained. The Total Harmonic Distortion (THD) is minimized to zero at the sensitive load end. Digital simulations are carried out using PSCAD/EMTDC to validate the performance of RLC filter. Simulated results are presented. (paper)
Shunt Active-Power-Filter Topology Based on Parallel Interleaved Inverters
DEFF Research Database (Denmark)
Blaabjerg, Frede; Asiminoaei, Lucian; Aeloiza, E.
2008-01-01
In this paper, an interleaved active-power-filter concept with reduced size of passive components is discussed. The topology is composed of two pulsewidth-modulation interleaved voltage-source inverters connected together on the ac line and sharing the same dc-link capacitor. The advantages......, because the power sharing allows one to use a higher switching frequency in each inverter. This paper analyzes the design of the passive components and gives a practical and low-cost solution for the minimization of the circulation currents between the inverters, by using common-mode coils. Several...
The active filter voltage ripple correction system of the Brookhaven AGS main magnet power supply
International Nuclear Information System (INIS)
Marneris, I.; Bonati, R.; Geller, J.; Sandberg, J.N.; Soukas, A.
1995-01-01
This paper, and a companion paper, describe the improvements to the Main Magnet Power Supply (MMPS) so that it enables a more flexible operation of the AGS, enhances its reliability, and also improves the MMPS's ultimate performance specifications. One of the major areas for the latter is the fixed target program operating off the AGS slow extracted beam lines. The active filter, by improving the MMPS output ripple, is instrumental in the improvement of the ultimate duty factor of the extraction beam spill
Unified Digital Periodic Signal Filters for Power Converter Systems
DEFF Research Database (Denmark)
Yang, Yongheng; Xin, Zhen; Zhou, Keliang
2017-01-01
Periodic signal controllers like repetitive and resonant controllers have demonstrated much potential in the control of power electronic converters, where periodic signals (e.g., ac voltages and currents) can be precisely regulated to follow references. Beyond the control of periodic signals, ac...... signal processing (e.g., in synchronization and pre-filtering) is also very important for power converter systems. Hence, this paper serves to unify digital periodic signal filters so as to maximize their roles in power converter systems (e.g., enhance the control of ac signals). The unified digital...... periodic signal filters behave like a comb filter, but it can also be configured to selectively filter out the harmonics of interest (e.g., the odd-order harmonics in single-phase power converter systems). Moreover, a virtual variable-sampling-frequency unit delay that enables frequency adaptive periodic...
Reactive power compensation and loss reduction in large industrial enterprises
Energy Technology Data Exchange (ETDEWEB)
Jovanovic, S; Gajic, B; Mijailovic, S [Institute Nikola Tesla, Beograd (Yugoslavia)
1991-12-01
This paper considers the reactive power compensation and the active power and energy loss reduction of large radial power networks in the Serbian mine and smelting industry. It gives an efficient optimization procedure for positioning and sizing capacitors in large industrial systems integrated with a simple network analysis method. (Author).
Best control strategy for unified power quality conditioner (UPQC) based on simulation
Energy Technology Data Exchange (ETDEWEB)
Shayanfar, H.A. [Iran Univ. of Science and Technology, Tehran (Iran, Islamic Republic of). Dept. of Electrical Engineering; Tabatabaei, N.M. [Azarbaijan Univ. of Tarbiat Moallem, Tabriz (Iran, Islamic Republic of). Dept. of Electrical Engineering; Mokhtarpour, A. [Islamic Azad Univ., Tabriz (Iran, Islamic Republic of). Dept. of Electrical Engineering
2007-07-01
Electronic devices used in both industry and residences need high-quality energy to work properly. Unified Power Quality Conditioners (UPQC) solve any power quality problems faced by these devices. Three new control strategies for UPQCs were presented and their operation was investigated and compared using the MATLAB Simulink simulation software package. A UPQC consists of a Shunt-Active Filter and a Series Active Filter with a common direct current link to compensate for any source currents and delivered voltage to the load. As such, it isolates the utility from current quality problems associated with load. It also isolates the load from the voltage quality problems of the utility. In the first control strategy, the Parallel Active Filter (PAF) and Series Active Filter (SAF) are based on the Fourier transform theory. In the second control strategy, the Parallel Active Filter is based on the power quality theory and the Series Active Filter is based on the Fourier transform theory. In the third control strategy, the Parallel Active Filter is based on Fourier transform theory and the Series Active Filter is based on positive sequence detection. Operating the PAF using these methods compensates for reactive power and current harmonics, while operating the SAF compensates for imbalances, voltage harmonics and positive and zero sequences of utility voltages. MATLAB simulation software was used to explain the compensation resolution and speed of the 3 new control strategies. According to simulation test results, it was concluded that the best compensation speed and resolution can be obtained using the third control strategy. 7 refs., 2 tabs., 24 figs.
A Novel Control Algorithm for Static Series Compensators by Use of PQR Instantaneous Power Theory
DEFF Research Database (Denmark)
Lee, Sang-Joon; Kim, Hyosung; Sul, Seung-Ki
2004-01-01
in coordinates is very simple and clear, has better steady state and dynamic performance. The controlled variables in coordinates are then inversely transformed to the original coordinates without time delay, generating control signals to SSCs. The control algorithm can be used for various kinds of SSCs...
Harmonic Detection at Initialization With Kalman Filter
DEFF Research Database (Denmark)
Hussain, Dil Muhammad Akbar; Imran, Raja Muhammad; Shoro, Ghulam Mustafa
2014-01-01
Most power electronic equipment these days generate harmonic disturbances, these devices hold nonlinear voltage/current characteristic. The harmonics generated can potentially be harmful to the consumer supply. Typically, filters are integrated at the power source or utility location to filter out...... the affect of harmonics on the supply. For the detection of these harmonics various techniques are available and one of that technique is the Kalman filter. In this paper we investigate that what are the consequences when harmonic detection system based on Kalman Filtering is initialized...
Energy Technology Data Exchange (ETDEWEB)
Grosse-Gehling, Martin; Just, Wolfgang; Reese, Juergen; Schlabbach, Juergen
2013-11-01
Reactive power compensation is playing an increasingly important role as the need for an efficient use of operating equipment and power grids continues to grow. This book presents the fundamentals of reactive power compensation in low and medium voltage grids, offering a wealth of application and calculation examples that will further the reader's understanding of the following topics: 1. design, dimensioning and operation of capacitors and capacitor installations; 2. long-term stability and ageing of capacitor installations; 3. use of passive and active filters; 4. improvement of voltage quality by means of filters and capacitor installations; 5. provision of reactive power compensation by means of power electronics; 6. costs and economic efficiency of reactive power compensation and filter equipment; 7. considerations from the viewpoint of the power supply industry; price regulations; 8. information requirements concerning PCB-containing capacitors; 9. climate protection and energy efficiency through reactive power compensation; 10. technical connection requirements and guidelines; 11. special technical issues concerning the use of reactive power compensation installations. [German] Die Blindleistungskompensation gewinnt angesichts der Notwendigkeit zur erhoehten Ausnutzung der Betriebsmittel und Netze zunehmend an Bedeutung. In diesem Buch werden die Grundlagen der Blindleistungskompensation in Nieder- und Mittelspannungsnetzen beschrieben und folgende Themen anhand zahlreicher Anwendungs- und Berechnungsbeispiele vertieft: 1. Aufbau, Auslegung und Betrieb von Kondensatoren und Kondensatoranlagen, 2. Langzeitstabilitaet und Alterung von Kondensatoranlagen, 3. Einsatz passiver und aktiver Filter, 4. Verbesserung der Spannungsqualitaet durch Filter und Kondensatoranlagen, 5. Blindleistungsbereitstellung mit Leistungselektronik, 6. Kosten und Wirtschaftlichkeit von Kompensations- und Filteranlagen, 7. Elektrizitaetswirtschaftliche Betrachtungen
Iodine filters in nuclear power stations
International Nuclear Information System (INIS)
Wilhelm, J.G.
1977-04-01
On the basis of calculated and recorded release rates of nuclear power plants, the significance of iodine releases in the invironmental impact relative to other nuclides is discussed. The release pathways for iodine in LWR-type reactors and the efficiency of various methods to lower the activity release are given. The airborne species of iodine are discussed with regard to their removal in iodine sorption filters and environmental impact. The technical status of iodine removal by means of iodine sorption filters is studied for normal operation and accident conditions in nuclear power stations on the basis of the data given in the relevant literature for the efficiency of a number of iodine sorption materials. The applicability of concepts for ventilation and containment and their influence on iodine filter systems are discussed. Design, structure, and testing of iodine sorption filters are treated in detail; recommendations for design are given, and failure sources are mentioned. (orig.) [de
DEFF Research Database (Denmark)
Zhuo, Fang; Wu, Longhui; Chen, Zhe
2009-01-01
on zero-cross detection can't work effectively in small rating stand-alone power grid. Then a soft phase locked loop with additional filter is proposed. It can lock the phase angle on to the positive sequence of fundamental voltage accurately and rapidly. It ensures the performance of APF applied...... in the small rating stand-alone power grid. Moreover, the soft phase locked loop is easy to be implemented in a Digital Signal Processor (DSP). Simulation and experimental results validate that the soft phase locked loop has satisfactory performance.......Traditional LC filters can't work stably in small rating stand-alone power grid. So active power filter (APF) is becoming an important tool to solve the power quality problem in small rating stand-alone power grid. In most current detection algorithm of APF, it needs a synchronizing signal. Firstly...
A Method for Harmonic Sources Detection based on Harmonic Distortion Power Rate
Lin, Ruixing; Xu, Lin; Zheng, Xian
2018-03-01
Harmonic sources detection at the point of common coupling is an essential step for harmonic contribution determination and harmonic mitigation. The harmonic distortion power rate index is proposed for harmonic source location based on IEEE Std 1459-2010 in the paper. The method only based on harmonic distortion power is not suitable when the background harmonic is large. To solve this problem, a threshold is determined by the prior information, when the harmonic distortion power is larger than the threshold, the customer side is considered as the main harmonic source, otherwise, the utility side is. A simple model of public power system was built in MATLAB/Simulink and field test results of typical harmonic loads verified the effectiveness of proposed method.
An introduction to reactive power compensation for wind farms
Energy Technology Data Exchange (ETDEWEB)
Nigim, K.A. [Waterloo Univ., Ont. (Canada). Dept. of Electrical and Computer Engineering; Cairo Univ., Giza (Egypt). Faculty of Engineering; Zobaa, A.F.; El Amin, I. [King Fahd Univ. of Petroleum and Minerals, Dhahran (Saudi Arabia). Dept. of Electrical Engineering
2005-07-01
The paper summarises the refereed contributions of seven articles reviewed for publication in the IJETP - Special Issue on 'Reactive compensation for wind farms'. The main goal of the special issue is to provide a forum to exchange information on the reactive power compensation requirements for wind farms and introducing possible price mechanisms for today's deregulated power industry. Uncompensated reactive power causes stress on the hosting utility grid as well as added expenses, which create in difficulties for power purchasing agreements from independent wind energy producers. Wind power producers need to comply with the hosting utility grid interconnection standards, e.g., voltage and frequency, as well as to provide controllable active and reactive sources of power. Active power supply is mainly dependent on the potential of wind power produced and the turbine design. Reactive power demand on the other hand depends on the conversion devices and the recovered power quantity fed to the grid. Static Var Compensators (SVC), Unified Power Quality Conditioners (UPQC), Unified Power Flow Controllers (UPFC), and the Distributed Static Synchronous Compensators (DSTATCOM) are all new emerging devices aimed at regulating the reactive power requirements. The excellent controllability of these devices has paved the way to flexible and dynamic controllers that are capable of regulating the flow of active and reactive power components. These devices are now suggested for the control of the reactive power requirement of wind generators. Studies have demonstrated acceptable voltage stabilisation results. This has increased the penetration level of wind power into existing distribution networks in many countries. (Author)
Directory of Open Access Journals (Sweden)
Le Ge
2014-01-01
Full Text Available To rely on joint active disturbance rejection control (ADRC and repetitive control (RC, in this paper, a compound control law for active power filter (APF current control system is proposed. According to the theory of ADRC, the uncertainties in the model and from the circumstance outside are considered as the unknown disturbance to the system. The extended state observer can evaluate the unknown disturbance. Next, RC is introduced into current loop to improve the steady characteristics. The ADRC is used to get a good dynamic performance, and RC is used to get a good static performance. A good simulation result is got through choosing and changing the parameters, and the feasibility, adaptability, and robustness of the control are testified by this result.
Selective Compensation of Voltage Harmonics in a Grid-Connected Microgrid
DEFF Research Database (Denmark)
Savaghebi, M.; Guerrero, Josep M.; Jalilian, A.
2011-01-01
In this paper, a method for selective voltage harmonic compensation in a grid-connected microgrid is presented. Harmonic compensation is done through proper control of distributed generators (DGs) interface converters. In order to achieve proper sharing of compensation effort among the DGs, a power...... named “Harmonic Distortion Power (HDP)” is defined. In the proposed method, active and reactive power control loops are considered to control the powers injected by the DGs. Also, a virtual impedance loop and voltage and current proportional-resonant controllers are included. Simulation results show...
Puhan, Pratap Sekhar; Ray, Pravat Kumar; Panda, Gayadhar
2016-12-01
This paper presents the effectiveness of 5/5 Fuzzy rule implementation in Fuzzy Logic Controller conjunction with indirect control technique to enhance the power quality in single phase system, An indirect current controller in conjunction with Fuzzy Logic Controller is applied to the proposed shunt active power filter to estimate the peak reference current and capacitor voltage. Current Controller based pulse width modulation (CCPWM) is used to generate the switching signals of voltage source inverter. Various simulation results are presented to verify the good behaviour of the Shunt active Power Filter (SAPF) with proposed two levels Hysteresis Current Controller (HCC). For verification of Shunt Active Power Filter in real time, the proposed control algorithm has been implemented in laboratory developed setup in dSPACE platform.
Parallel power electronics filters in three-phase four-wire systems principle, control and design
Wong, Man-Chung; Lam, Chi-Seng
2016-01-01
This book describes parallel power electronic filters for 3-phase 4-wire systems, focusing on the control, design and system operation. It presents the basics of power-electronics techniques applied in power systems as well as the advanced techniques in controlling, implementing and designing parallel power electronics converters. The power-quality compensation has been achieved using active filters and hybrid filters, and circuit models, control principles and operational practice problems have been verified by principle study, simulation and experimental results. The state-of-the-art research findings were mainly developed by a team at the University of Macau. Offering background information and related novel techniques, this book is a valuable resource for electrical engineers and researchers wanting to work on energy saving using power-quality compensators or renewable energy power electronics systems. .
Dynamic Performance of the ITER Reactive Power Compensation System
International Nuclear Information System (INIS)
Sheng Zhicai; Fu Peng; Xu Liuwei
2011-01-01
Dynamic performance of a reactive power compensation (RPC) system for the international thermonuclear experimental reactor (ITER) power supply is presented. Static var compensators (SVCs) are adopted to mitigate voltage fluctuation and reduce the reactive power down to a level acceptable for the French/European 400 kV grid. A voltage feedback and load power feedforward controller for SVC is proposed, with the feedforward loop intended to guarantee short response time and the feedback loop ensuring good dynamics and steady characteristics of SVC. A mean filter was chosen to measure the control signals to improve the dynamic response. The dynamic performance of the SVC is verified by simulations using PSCAD/EMTDC codes.
Analysis of Even Harmonics Generation in an Isolated Electric Power System
Kanao, Norikazu; Hayashi, Yasuhiro; Matsuki, Junya
Harmonics bred from loads are mainly odd order because the current waveform has half-wave symmetry. Since the even harmonics are negligibly small, those are not generally measured in electric power systems. However, even harmonics were measured at a 500/275/154kV substation in Hokuriku Electric Power Company after removal of a transmission line fault. The even harmonics caused malfunctions of protective digital relays because the relays used 4th harmonics at the input filter as automatic supervisory signal. This paper describes the mechanism of generation of the even harmonics by comparing measured waveforms with ATP-EMTP simulation results. As a result of analysis, it is cleared that even harmonics are generated by three causes. The first cause is a magnetizing current of transformers due to flux deviation by DC component of a fault current. The second one is due to harmonic conversion of a synchronous machine which generates even harmonics when direct current component or even harmonic current flow into the machine. The third one is that increase of harmonic impedance due to an isolated power system produces harmonic voltages. The design of the input filter of protective digital relays should consider even harmonics generation in an isolated power system.
Directory of Open Access Journals (Sweden)
Zeyu Shi
2017-01-01
Full Text Available Active power filter (APF is the most popular device in regulating power quality issues. Currently, most literatures ignored the impact of grid impedance and assumed the load voltage is ideal, which had not described the system accurately. In addition, the controllers applied PI control; thus it is hard to improve the compensation quality. This paper establishes a precise model which consists of APF, load, and grid impedance. The Bode diagram of traditional simplified model is obviously different with complete model, which means the descriptions of the system based on the traditional simplified model are inaccurate and incomplete. And then design exact feedback linearization and quasi-sliding mode control (FBL-QSMC is based on precise model in inner current loop. The system performances in different parameters are analyzed and dynamic performance of proposed algorithm is compared with traditional PI control algorithm. At last, simulations are taken in three cases to verify the performance of proposed control algorithm. The results proved that the proposed feedback linearization and quasi-sliding mode control algorithm has fast response and robustness; the compensation performance is superior to PI control obviously, which also means the complete modeling and proposed control algorithm are correct.
Instantaneous stochastic perturbation theory
International Nuclear Information System (INIS)
Lüscher, Martin
2015-01-01
A form of stochastic perturbation theory is described, where the representative stochastic fields are generated instantaneously rather than through a Markov process. The correctness of the procedure is established to all orders of the expansion and for a wide class of field theories that includes all common formulations of lattice QCD.
Compact Unequal Power Divider with Filtering Response
Directory of Open Access Journals (Sweden)
Wei-Qiang Pan
2015-01-01
Full Text Available We present a novel unequal power divider with bandpass responses. The proposed power divider consists of five resonators and a resistor. The power division ratio is controlled by altering the coupling strength among the resonators. The output ports have the characteristic impedance of 50 Ω and impedance transformers in classical Wilkinson power dividers are not required in this design. Use of resonators enables the filtering function of the power divider. Two transmission zeros are generated near the passband edges, resulting in quasielliptic bandpass responses. For validation, a 2 : 1 filtering power divider is implemented. The fabricated circuit size is 0.22 λg × 0.08 λg, featuring compact size for unequal filtering power dividers, which is suitable for the feeding networks of antenna arrays.
DEFF Research Database (Denmark)
He, Jinwei; Wei Li, Yun; Wang, Xiongfei
2013-01-01
In order to utilize DG unit interfacing converters to actively compensate distribution system harmonics, this paper proposes an enhanced current control approach. It seamlessly integrates system harmonic mitigation capabilities with the primary DG power generation function. As the proposed current...... controller has two well decoupled control branches to independently control fundamental and harmonic DG currents, phase-locked loops (PLL) and system harmonic component extractions can be avoided during system harmonic compensation. Moreover, a closed-loop power control scheme is also employed to derive...... the fundamental current reference. The proposed power control scheme effectively eliminates the impacts of steady-state fundamental current tracking errors in the DG units. Thus, an accurate power control is realized even when the harmonic compensation functions are activated. Experimental results from a single...
Energy Technology Data Exchange (ETDEWEB)
Auer, Jan-Hendrik von [Alstom Grid GmbH, Berlin (Germany). Team Leistungselektronik und Kompensationsanlagen
2012-07-01
Even today, many HP lines have reached their limits. It is therefore highly urgent to find measures for optimum utilization of the available overhead transmssion capacities, e.g. by idle power compensation. Together with a filter for harmonics reduction, this will ensure higher grid stability and enhance transport capacities while reducing transport losses, thus saving money and reducing CO{sub 2} emissions. (orig./AKB)
Harmonic currents Compensator Grid-Connected Inverter at the Microgrid
DEFF Research Database (Denmark)
Asuhaimi Mohd Zin, A.; Naderipour, A.; Habibuddin, M.H.
2016-01-01
The main challenge associated with the grid-connected inverter in distributed generation (DG) systems is to maintain the harmonic contents in output current below the specified values and compensates for unbalanced loads even when the grid is subject to disturbances such as harmonic distortion...... and unbalanced loads. To overcome these challenges, a current control strategy for a three-phase grid-connected inverter under unbalanced and nonlinear load conditions is presented. It enables grid-connected inverter by the proposed control method to inject balanced clean currents to the grid even when the local...... loads are unbalanced and/or nonlinear and also compensate of the harmonic currents and control the active and reactive power. The main advantage and objective of this method is to effectively compensate for the harmonic currents content of the grid current and microgrid without using any compensation...
DEFF Research Database (Denmark)
Wang, Xiongfei; Blaabjerg, Frede; Loh, Poh Chiang
2014-01-01
This paper addresses the interaction between harmonic resonant controllers and active damping of LCL resonance in voltage source converters. A virtual series R-C damper in parallel with the filter capacitor is proposed with the capacitor current feedback loop. The phase lag resulting from...... crossover frequency defined by the proportional gain of current controller. This is of particular interest for high-performance active harmonic filtering applications and low-pulse-ratio converters. Case studies in experiments validate the theoretical analysis....
DEFF Research Database (Denmark)
Barote, L.; Marinescu, C.; Teodorescu, Remus
2012-01-01
This paper deals with the design and implementation of PR current control method in the αβ stationary reference frame for the grid side converter in Distributed Power Generation Systems (DPGS) applications. The goals of this paper are to implement a control technique for the grid side inverter...... including a LC filter, a compensation technique for low-order harmonics and to examine the grid current harmonic content with and without harmonic compensation. A comparative study in terms of current harmonic distortion between two different values of PR proportional gain running in steady state condition...
Directory of Open Access Journals (Sweden)
Zaidi Maryam Nabihah
2018-01-01
Full Text Available This paper present the project designed to correcting power factor for medical industries in Malaysia automatically. Which with hope to make the cost and energy usage efficient, because the energy source are depleting due to increase in population. Power factor is the ratio of real power and apparent power. This definition is mathematically represented as kW/kVA where kW is active power and kVA is apparent power (active + reactive. Reactive power is the non-working power generated by the magnetic and inductive load to generate magnetic flux. The increase in reactive power increase the apparent power so the power factor will decrease. Low pF will cause the industry to meet high demand thus making it less efficient. The main aim of this project is to increasing the current power factor of medical industries from 0.85 to 0.90. Power factor compensation contribute to reduction in current-dependent losses and increase energy efficiency while expanding the reliability of planning for future energy network. As technology develops, the gradual cost and efficiency penalty should reduce. Therefore, automatic power factor compensation device should become cost-effective and smaller device over time. That is the reason this project is using programmable device as it is a miniature architecture device.
Detection of Harmonic Occurring using Kalman Filtering
DEFF Research Database (Denmark)
Hussain, Dil Muhammad Akbar; Shoro, Ghulam Mustafa; Imran, Raja Muhammed
2014-01-01
/current characteristic. These harmonics are not to be allowed to grow beyond a certain limit to avoid any grave consequence to the customer’s main supply. Filters can be implemented at the power source or utility location to eliminate these harmonics. In this paper we detect the instance at which these harmonics occur...
Low power adder based auditory filter architecture.
Rahiman, P F Khaleelur; Jayanthi, V S
2014-01-01
Cochlea devices are powered up with the help of batteries and they should possess long working life to avoid replacing of devices at regular interval of years. Hence the devices with low power consumptions are required. In cochlea devices there are numerous filters, each responsible for frequency variant signals, which helps in identifying speech signals of different audible range. In this paper, multiplierless lookup table (LUT) based auditory filter is implemented. Power aware adder architectures are utilized to add the output samples of the LUT, available at every clock cycle. The design is developed and modeled using Verilog HDL, simulated using Mentor Graphics Model-Sim Simulator, and synthesized using Synopsys Design Compiler tool. The design was mapped to TSMC 65 nm technological node. The standard ASIC design methodology has been adapted to carry out the power analysis. The proposed FIR filter architecture has reduced the leakage power by 15% and increased its performance by 2.76%.
Low Power Adder Based Auditory Filter Architecture
Directory of Open Access Journals (Sweden)
P. F. Khaleelur Rahiman
2014-01-01
Full Text Available Cochlea devices are powered up with the help of batteries and they should possess long working life to avoid replacing of devices at regular interval of years. Hence the devices with low power consumptions are required. In cochlea devices there are numerous filters, each responsible for frequency variant signals, which helps in identifying speech signals of different audible range. In this paper, multiplierless lookup table (LUT based auditory filter is implemented. Power aware adder architectures are utilized to add the output samples of the LUT, available at every clock cycle. The design is developed and modeled using Verilog HDL, simulated using Mentor Graphics Model-Sim Simulator, and synthesized using Synopsys Design Compiler tool. The design was mapped to TSMC 65 nm technological node. The standard ASIC design methodology has been adapted to carry out the power analysis. The proposed FIR filter architecture has reduced the leakage power by 15% and increased its performance by 2.76%.
A New MPPT Control for Photovoltaic Panels by Instantaneous Maximum Power Point Tracking
Tokushima, Daiki; Uchida, Masato; Kanbei, Satoshi; Ishikawa, Hiroki; Naitoh, Haruo
This paper presents a new maximum power point tracking control for photovoltaic (PV) panels. The control can be categorized into the Perturb and Observe (P & O) method. It utilizes instantaneous voltage ripples at PV panel output terminals caused by the switching of a chopper connected to the panel in order to identify the direction for the maximum power point (MPP). The tracking for the MPP is achieved by a feedback control of the average terminal voltage of the panel. Appropriate use of the instantaneous and the average values of the PV voltage for the separate purposes enables both the quick transient response and the good convergence with almost no ripples simultaneously. The tracking capability is verified experimentally with a 2.8 W PV panel under a controlled experimental setup. A numerical comparison with a conventional P & O confirms that the proposed control extracts much more power from the PV panel.
Institute of Scientific and Technical Information of China (English)
Mohammadi Mohammad
2017-01-01
Due to development of distribution systems and increase in electricity demand, the use of capacitor banks increases. From the other point of view, nonlinear loads generate and inject considerable harmonic currents into power system. Under this condition if capacitor banks are not properly selected and placed in the power system, they could amplify and propagate these harmonics and deteriorate power quality to unacceptable levels. With attention of disadvantages of passive filters, such as occurring resonance, nowadays the usage of this type of harmonic compensator is restricted. On the other side, one of parallel multi-function compensating devices which are recently used in distribution system to mitigate voltage sag and harmonic distortion, performs power factor correction, and improves the overall power quality as active power conditioner (APC). Therefore, the utilization of APC in harmonic distorted system can affect and change the optimal location and size of shunt capacitor bank under harmonic distortion condition. This paper presents an optimization algorithm for improvement of power quality using simultaneous optimal placement and sizing of APC and shunt capacitor banks in radial distribution networks in the presence of voltage and current harmonics. The algorithm is based on particle swarm optimization (PSO). The objective function includes the cost of power losses, energy losses and those of the capacitor banks and APCs.
Hybrid power filter for advanced power quality in industrial systems
Czech Academy of Sciences Publication Activity Database
Švec, J.; Müller, Z.; Kasembe, A. G.; Tlustý, J.; Valouch, Viktor
2013-01-01
Roč. 103, october 2013 (2013), s. 157-167 ISSN 0378-7796 R&D Projects: GA AV ČR IAA200760703 Institutional research plan: CEZ:AV0Z20570509 Institutional support: RVO:61388998 Keywords : hybrid power filter * power quality * industrial system Subject RIV: JA - Electronics ; Optoelectronics, Electrical Engineering Impact factor: 1.595, year: 2013 http://www.sciencedirect.com/science/article/pii/S0378779613001417
A Multipath Technique for Cancelling Harmonics and Sidebands in a Wideband Power Upconverter
Shrestha, R.; Mensink, E.; Klumperink, Eric A.M.; Wienk, Gerhardus J.M.; Nauta, Bram
2006-01-01
Switching mixers are power-efficient but produce unwanted harmonics and sidebands. A multipath technique to clean up the spectrum using digital circuits and mixers, but no filters, is applied to a 0.13µm CMOS power upconverter. The circuit delivers 8mW from dc to 2.4GHz with 11% drain efficiency,
DC-pass filter design with notch filters superposition for CPW rectenna at low power level
Rivière, J.; Douyère, A.; Alicalapa, F.; Luk, J.-D. Lan Sun
2016-03-01
In this paper the challenging coplanar waveguide direct current (DC) pass filter is designed, analysed, fabricated and measured. As the ground plane and the conductive line are etched on the same plane, this technology allows the connection of series and shunt elements to the active devices without via holes through the substrate. Indeed, this study presents the first step in the optimization of a complete rectenna in coplanar waveguide (CPW) technology: key element of a radio frequency (RF) energy harvesting system. The measurement of the proposed filter shows good performance in the rejection of F0=2.45 GHz and F1=4.9 GHz. Additionally, a harmonic balance (HB) simulation of the complete rectenna is performed and shows a maximum RF-to-DC conversion efficiency of 37% with the studied DC-pass filter for an input power of 10 µW at 2.45 GHz.
Compulsator, a high power compensated pulsed alternator
International Nuclear Information System (INIS)
Weldon, W.F.; Bird, W.L.; Driga, M.D.; Rylander, H.G.; Tolk, K.M.; Woodson, H.H.
1983-01-01
This chapter describes a pulsed power supply utilizing inertial energy storage as a possible replacement for large capacitor banks. The compulsator overcomes many of the limitations of the pulsed homopolar generators previously developed by the Center for Electromechanics and elsewhere in that it offers high voltage (10's of kV) and consequently higher pulse rise times, is self commutating, and offers the possibility of generating repetitive pulses. The compulsator converts rotational inertial energy directly into electrical energy utilizing the principles of both magnetic induction and flux compression. The theory of operation, a prototype compulsator design, and advanced compulsator designs are discussed
DEFF Research Database (Denmark)
Mu, Xiaobin; Wang, Jiuhe; Wu, Weimin
2018-01-01
The passivity-based control (PBC) has a better control performance using an accurate mathematical model of the control object. It can offer an alternative tracking control scheme for the shunt active power filter (SAPF). However, the conventional PBC-based SAPF cannot achieve zero steady...
Voltage Sag Mitigation and Load Reactive Power Compensation by UPQC
Ajitha, P; Jananisri, D
2014-01-01
This paper presents Unified Power Quality Conditioner(UPQC) that consist of series inverter and shunt inverter in back to back configuration which simultaneously compensate the power quality(PQ) problems of both voltage sag and load reactive power compensation . In this paper ,Neural network is tool which is considered for solving power quality problems. The simulation results from MATLAB/SIMULINK are discussed to validate the proposed method.
Energy Technology Data Exchange (ETDEWEB)
Contreras Ordaz, Marco Antonio
2007-08-15
With the development of semiconductor devices and the increase of non-linear loads based on static power converters, the power quality of transmission, distribution and consumption systems has been affected. The harmonics present in a distribution system are mainly result of the current harmonics generated by the non-linear loads and their effect on the impedance of the distribution system. There are several problems generated by the presence of current and voltage harmonics in a power distribution system. One of these problems is the harmonic propagation phenomenon, which has become important on the matter of power distribution systems. This phenomenon is manifested by the harmonic voltage amplification in distribution lines, generating levels of distortion that affect the electric facilities, and the life expectancy of equipment (CA motors, transformers, capacitor banks, etc.). There is also a reduction in the power transmission capacity of electric distribution lines. The harmonic propagation is mainly produced by the resonance between the line impedance and the power factor correction of capacitor banks installed along the distribution line and the consumers' equipment. The utilization of passive filters is not a sufficient solution, because the harmonic propagation exists even with no loads on the electric network, and the resonance frequencies do not correspond to the characteristic harmonics. This problem is solved by using active filters in radial distribution systems, mainly in low voltage. The objective of using an active filter is neither to compensate a particular load, nor a group of centralized loads; its objective is to reduce the voltage distortion and avoid the harmonic propagation by placing the filter in a branch of feeder of the electric system. This thesis presents a thorough study of the harmonic propagation phenomenon in ring networks and its damping with an active filter. An important point is to identify the location of the active
DEFF Research Database (Denmark)
Qin, Zian; Tang, Yi; Loh, Poh Chiang
2015-01-01
studied, where the commercially available film capacitors, circuit topologies, and control strategies for active power decoupling are all taken into account. Then, an adaptive decoupling voltage control method is proposed to further improve the performance of dc decoupling in terms of efficiency...... and reliability. The feasibility and superiority of the identified solution for active power decoupling together with the proposed adaptive decoupling voltage control method are finally verified by both the experimental results obtained on a 2 kW single-phase inverter.......This paper presents the benchmark study of ac and dc active power decoupling circuits for second-order harmonic mitigation in kW-scale single-phase inverters. First of all, the best solutions of active power decoupling to achieve high efficiency and power density are identified and comprehensively...
DEFF Research Database (Denmark)
Qin, Zian; Tang, Yi; Loh, Poh Chiang
2016-01-01
efficiency and high power density is identified and comprehensively studied, and the commercially available film capacitors, the circuit topologies, and the control strategies adopted for active power decoupling are all taken into account. Then, an adaptive decoupling voltage control method is proposed...... to further improve the performance of dc decoupling in terms of efficiency and reliability. The feasibility and superiority of the identified solution for active power decoupling together with the proposed adaptive decoupling voltage control method are finally verified by both the simulation and experimental......This paper presents the benchmark study of ac and dc active power decoupling circuits for second order harmonic mitigation in kW scale single-phase inverters. First of all, a brief comparison of recently reported active power decoupling circuits is given, and the best solution that can achieve high...
Harmonics and voltage stability analysis in power systems including
Indian Academy of Sciences (India)
In this study, non-sinusoidal quantities and voltage stability, both known as power quality criteria, are examined together in detail. The widespread use of power electronics elements cause the existence of signiﬁcant non-sinusoidal quantities in the system. These non-sinusoidal quantities can create serious harmonic ...
Harmonics in power systems of ships with electrical propulsion drives. Effects on the equipment
Energy Technology Data Exchange (ETDEWEB)
Lehtonen, M [VTT Energy, Espoo (Finland). Energy Systems
1996-11-01
In this report the effect of harmonics on the power system equipment and loads, with special attention given to the circumstances in ships, is discussed. Some guidelines are given for the computation of additional harmonic losses in power cables and transformers. It is also shown, that if the system is rich in harmonics, these losses must be taken into account when sizing the equipment. The effect of harmonics on electrical machines is also discussed. The influence on induction machines is usually small. However, in large synchronous machines a significant degree of harmonic losses may be expected. Especially in the high voltage system the harmonics must be taken into account when selecting the machine ratings. Also the harmonic resonances, which may arise when using reactive power compensation capacitors, are discussed. Due to the risk of harmonic resonances, the use of capacitors is not recommended in marine power systems. Also the immunity of different load devices to harmonic distortion is discussed. The equipment considered are resistive loads, discharge lamps, universal machines and electronic equipment. Finally a brief survey is given on the standards and recommendations for the maximum distortion levels allowed. (author)
Cancellation of neutral current harmonics by using a four-branch star hybrid filter
DEFF Research Database (Denmark)
Blaabjerg, Frede; Rodriguez, Pedro; Candela, I.
2008-01-01
filtering topology to a three-phase four-wire system. An extensive evaluation using simulation and experimental results are conducted in this work to validate the good performance of the proposed solution for canceling current harmonics flowing through the neutral conductor.......This paper presents a new technique for filtering current harmonics in three-phase four-wire networks based on the usage of a four-branch star (FBS) filter topology. Based on single-phase inductors and capacitors, the specific layout of the FBS filter topology allows achieving a power filter...... is improved by integrating a power converter into its structure. This paper analyzes the FBS topology and presents fundamental concepts regarding the control of a generic FBS hybrid power filter. A neutral current hybrid power filter and var compensator is presented as an illustrative example applying the FBS...
Estimation and reduction of harmonic currents from power converters
DEFF Research Database (Denmark)
Asiminoaei, Lucian
-based method depends very much on the amount and accuracy of collected data in the development stage. The outcome of this investigation is a Harmonic Calculation Software compiled into a Graphical User Interface PC-software application, which can be applied for fast estimations of the harmonic currents...... control of the proposed topologies are given together with laboratory tests. One harmonic current mitigation solution found is to connect (two) smaller power APF's in parallel, sharing the same ac- and dc-bus. It is proven that parallel APF's may have lower passive components although other issues arises......, like circulation currents, which is removed here by common mode coils. Another harmonic solution is to use cascade connection of (two) independent APF's that cooperatively share the task of the harmonic mitigation. Two cooperative control methods are proposed called load-sharing and harmonic-sharing...
Hybrid compensation arrangement in dispersed generation systems
DEFF Research Database (Denmark)
Chen, Zhe; Blaabjerg, Frede; Pedersen, John Kim
2005-01-01
This paper presents a hybrid compensation system consisting of an active filter and distributed passive filters. In the system, each individual passive filter is connected to a distortion source and designed to eliminate main harmonics and supply reactive power for the distortion source, while...... filter system consisting of distributed passive filters and an active filter....... the active filter is responsible for the correction of the system unbalance and the cancellation of the remaining harmonics. The paper also analyzes the effects of the circuit configuration on the system impedance characteristics and consequently the effectiveness of the filter system. Simulation studies...
Khadkikar, Vinod
The present doctoral work is based on the philosophy of optimal utilization of the available resources in a most effective and efficient way to improve the product efficiency and to reduce the overall cost. This work proposes a novel control philosophy termed as power angle control (PAC), in which both the series and shunt inverters share the load reactive power in co-ordination with each other without affecting the basic UPQC compensation capabilities. This eventually results in a better utilization of the series inverter, reduction in the shunt inverter rating to some extent and ultimately in the reduction of the overall cost of UPQC. Moreover, in this thesis work several other control approaches are also proposed, such as, unit vector template generation, quadrature voltage injection, generalized single-phase p-q theory and novel current unbalance compensation approach. All the developed concepts are successfully validated through digital simulation as well as extensive experimental investigations. Keywords. power quality, active power filter, unified power quality conditioner, reactive power compensation, harmonics compensation.
ANN based controller for three phase four leg shunt active filter for power quality improvement
Directory of Open Access Journals (Sweden)
J. Jayachandran
2016-03-01
Full Text Available In this paper, an artificial neural network (ANN based one cycle control (OCC strategy is proposed for the DSTATCOM shunted across the load in three phase four wire distribution system. The proposed control strategy mitigates harmonic/reactive currents, ensures balanced and sinusoidal source current from the supply mains that are nearly in phase with the supply voltage and compensates neutral current under varying source and load conditions. The proposed control strategy is superior over conventional methods as it eliminates, the sensors needed for sensing load current and coupling inductor current, in addition to the multipliers and the calculation of reference currents. ANN controllers are implemented to maintain voltage across the capacitor and as a compensator to compensate neutral current. The DSTATCOM performance is validated for all possible conditions of source and load by simulation using MATLAB software and simulation results prove the efficacy of the proposed control over conventional control strategy.
Directory of Open Access Journals (Sweden)
Yanjian Peng
2016-04-01
Full Text Available Unlike the traditional method for power quality improvement and low-voltage ride through (LVRT capability enhancement of wind farms, this paper proposes a new wind power integrated system by means of an inductive filtering method, especially if it contains a grid-connected transformer, a static synchronous compensator (STATCOM and fully-tuned (FT branches. First, the main circuit topology of the new wind power integrated system is presented. Then, the mathematical model is established to reveal the mechanism of harmonic suppression and the reactive compensation of the proposed wind power integrated system, and then the realization conditions of the inductive filtering method is obtained. Further, the control strategy of STATCOM is introduced. Based on the measured data for a real wind farm, the simulation studies are carried out to illustrate the performance of the proposed new wind power integrated system. The results indicate that the new system can not only enhance the LVRT capability of wind farms, but also prevent harmonic components flowing into the primary (grid winding of the grid-connected transformer. Moreover, since the new method can compensate for reactive power in a wind farm, the power factor at the grid side can be improved effectively.
Harmonizing power cables and power lines. Harmonisierung der Starkstromkabel und -leitungen
Energy Technology Data Exchange (ETDEWEB)
Heinhold, L [Siemens A.G., Erlangen (Germany, F.R.); Retzlaff, E; Warner, A [Verband Deutscher Elektrotechniker (VDE) e.V., Frankfurt am Main (Germany, F.R.)
1976-01-01
The article gives a summarizing view of the present level of harmonization in the field of power cables and lines. Special attention is paid to problems referring to using harmonized designs for flexible lines and using lines for solid layout with PVC and rubber insulation in the German standards DIN 57281/VDE 0281 and DIN 57282/VDE 0282 and problems of taking the types used until today out of use. A general view of the power lines fully harmonized is given and a harmonization-labelling (common labelling) for cables and lines is described.
Coordination of baseload power plant group control with static reactive power compensator control
Directory of Open Access Journals (Sweden)
Zbigniew Szczerba
2012-06-01
Full Text Available Reactive power sources in power system nodes: generators and static reactive power compensators, are controlled by control systems. Generators – by generator node group controllers, compensators – by voltage controllers. The paper presents issues of these control systems’ coordination and proposals for its implementation.
Instantaneous response spectrum in seismic testing of nuclear power plant equipment
International Nuclear Information System (INIS)
Morrone, A.
1977-01-01
This paper presents the concept of instantaneous response spectrum (IRS) as the response of single degree of freedom oscillators at a particular time. It demonstrates that a shake table random motion whose standard TRS envelops the RRS does not necessarily satisfy the enveloping requirement instantaneously. That is, any one (or more) instantaneous required response spectrum (IRRS) is not enveloped by any instantaneous test response spectrum (ITRS). Response spectra from different time histories, including single frequency sine beat motion used in resonance testing, are compared for enveloping with maximum response and with the actual response at particular times. These comparisons are given for the enveloping of RRS and IRRS derived with a time history response calculated at a particular building elevation of a nuclear power plant. For the test motion, several of the most severe ITRS derived with a modified EL Centro motion and with a sine beat motion with ten cycles per beat were used. It is shown that although the TRS with the modified EL Centro motion enveloped the given RRS, the selected modified EL Centro ITRS did not envelop the corresponding IRRS. With the sine beat motion, even though the TRS did not fully envelop the given RRS, the resulting sine beat ITRS did not require a larger factor for full IRRS enveloping than those of the modified EL Centro motion
Novel miniature high power ring filter
International Nuclear Information System (INIS)
Huang Huifen; Mao Junfa; Luo Zhihua
2005-01-01
The power handling capability of high temperature superconducting (HTS) filters is limited due to current concentration at the edges of the superconducting films. This problem can be overcome by using ring resonator, which employs the edge current free and reduces the current concentration. However, this kind of filter has large size. In order to reduce the cost and size and increase the power handling capability, in this paper a HTS photonic bandgap (PBG) structure filter is developed. The proposed pass band filter with PBG structure exhibits center frequency 12.23 GHz, steepness (about 35 dB/GHz), bandwidth (-3 dB bandwidth is 0.045 GHz), and low insertion loss (about -0.5 dB), and can handle input power up to 1 W (this value was limited by the measurement instrument used in the experiment). The size is reduced by 25%, insertion loss reduced by 37.5%, and steeper roll-off of the filter is also obtained compared with that in published literature
Directory of Open Access Journals (Sweden)
Tao Lin
2017-10-01
Full Text Available Harmonic resonance may cause abnormal operation and even damage of power facilities, further threatening normal and safe operation of power systems. For renewable energy generations, controlled loads and parallel reactive power compensating equipment, their operating statuses can vary frequently. Therefore, the parameters of equivalent fundamental and harmonic admittance/impedance of these components exist in uncertainty, which will change the elements and eigenvalues of harmonic network admittance matrix. Consequently, harmonic resonance in power grid is becoming increasingly more complex. Hence, intense research about prevention and suppression of harmonic resonance, particularly the parameter feasible domain (PFD which can keep away from harmonic resonance, are needed. For rapid online evaluation of PFD, a novel method without time-consuming pointwise precise eigenvalue computations is proposed. By analyzing the singularity of harmonic network admittance matrix, the explicit sufficient condition that the matrix elements should meet to prevent harmonic resonance is derived by the extended Gersgorin theorem. Further, via the non-uniqueness of similar transformation matrix (STM, a strategy to determine the appropriate STM is proposed to minimize the conservation of the obtained PFD. Eventually, the availability and advantages in computation efficiency and conservation of the method, are demonstrated through four different scale benchmarks.
Bus Participation Factor Analysis for Harmonic Instability in Power Electronics Based Power Systems
DEFF Research Database (Denmark)
Ebrahimzadeh, Esmaeil; Blaabjerg, Frede; Wang, Xiongfei
2018-01-01
Compared with the conventional power systems, large-scale power electronics based power systems present a more complex situation, where harmonic instability may be induced by the mutual interactions between the inner control loops of the converters. This paper presents an approach to locate which...... power converters and buses are more sensitive and have significant contribution to the harmonic instability. In the approach, a power electronics based system is introduced as a Multi-Input Multi-Output (MIMO) dynamic system by means of a dynamic admittance matrix. Bus Participation Factors (PFs......) are calculated by the oscillatory mode sensitivity analysis versus the elements of the MIMO transfer function matrix. The PF analysis detects which power electronic converters or buses have a higher participation in harmonic instability excitation than others or at which buses such instability problems have...
Kondo, Ryota; Akagi, Hirofumi
This paper presents a transformerless hybrid active filter that is integrated into medium-voltage adjustable-speed motor drives for fans, pumps, and compressors without regenerative braking. The authors have designed and constructed a three-phase experimental system rated at 400V and 15kW, which is a downscaled model from a feasible 6.6-kV 1-MW motor drive system. This system consists of the hybrid filter connecting a passive filter tuned to the 7th harmonic filter in series with an active filter that is based on a three-level diode-clamped PWM converter, as well as an adjustable-speed motor drive in which a diode rectifier is used as the front end. The hybrid filter is installed on the ac side of the diode rectifier with no line-frequency transformer. The downscaled system has been exclusively tested so as to confirm the overall compensating performance of the hybrid filter and the filtering performance of a switching-ripple filter for mitigating switching-ripple voltages produced by the active filter. Experimental results verify that the hybrid filter achieves harmonic compensation of the source current in all the operating regions from no-load to the rated-load conditions, and that the switching-ripple filter reduces the switching-ripple voltages as expected.
Predicting Harmonic Distortion of Multiple Converters in a Power System
Directory of Open Access Journals (Sweden)
P. M. Ivry
2017-01-01
Full Text Available Various uncertainties arise in the operation and management of power systems containing Renewable Energy Sources (RES that affect the systems power quality. These uncertainties may arise due to system parameter changes or design parameter choice. In this work, the impact of uncertainties on the prediction of harmonics in a power system containing multiple Voltage Source Converters (VSCs is investigated. The study focuses on the prediction of harmonic distortion level in multiple VSCs when some system or design parameters are only known within certain constraints. The Univariate Dimension Reduction (UDR method was utilized in this study as an efficient predictive tool for the level of harmonic distortion of the VSCs measured at the Point of Common Coupling (PCC to the grid. Two case studies were considered and the UDR technique was also experimentally validated. The obtained results were compared with that of the Monte Carlo Simulation (MCS results.
Directory of Open Access Journals (Sweden)
Sergio Salas-Duarte
2016-01-01
Full Text Available The realization of an improved predictive current controller based on a trapezoidal model is described, and the impact of this technique is assessed on the performance of a 2 kW, 21.6 kHz, four-wire, Active Power Filter for utility equipment of Metro Railway, Power-Land Substations. The operation of the trapezoidal predictive current controller is contrasted with that of a typical predictive control technique, based on a single Euler approximation, which has demonstrated generation of high-quality line currents, each using a 400 V DC link to improve the power quality of an unbalanced nonlinear load of Metro Railway. The results show that the supply current waveforms become virtually sinusoidal waves, reducing the current ripple by 50% and improving its power factor from 0.8 to 0.989 when the active filter is operated with a 1.6 kW load. The principle of operation of the trapezoidal predictive controller is analysed together with a description of its practical development, showing experimental results obtained with a 2 kW prototype.
Standard compensation for power cuts. Working group report
International Nuclear Information System (INIS)
2002-07-01
The Working Group was commissioned to draw up a proposal in the form of a Government Bill for provisions to be included in the Electricity Market Act on imposing an obligation on the distribution net operator to pay a standard compensation to the users of electricity for the event that they get no access to electricity. The Working Group should consider especially a model of standard compensation presented in the final report by Mr. Jarl Forsten, Deputy Director General of the Technical Research Centre of Finland VTT, published on 30 April 2002 that the amount of standard compensation should not depend on the reason for the power cut. The Working Group proposes that the Electricity Market Act should be amended by provisions providing that a distribution net operator shall pay to the user of electricity a standard compensation for power cuts lasting over 12 hours. The amount of compensation shall be based on the annual network service fee and a sliding scale of compensation related to the duration of the power cut shall be applied. The maximum compensation shall be paid when the power cut lasts more than five days. The maximum amount of individual compensations shall be fixed at EUR 700. The proposed provisions on standard compensation in the event of power cuts are aimed at amending the provisions in Chapter 6a of the Electricity Market Act on price reduction and compensation because of fault in the supply of electricity. The aim of the introduction of standard compensation for power cuts is to persuade distribution net operators to make an effort to minimize the time for power cuts. (orig.)
Four-branch Star Hybrid Power Filter for Three-phase Four-wire Systems
DEFF Research Database (Denmark)
Blaabjerg, Frede; Teodorescu, Remus; Rodriguez, Pedro
2008-01-01
and derives fundamental concepts about the control of the resulting hybrid power filter. From this analysis, a specifc implementation of a three-phase four-wire hybrid power filter is presented as an illustrative application of the filtering topology. An extensive evaluation using simulation and experimental......This paper presents a new concept for filtering current harmonics in three-phase four-wire networks. The four-branch star (FBS) filtering topology presented in this work is characterized by a particular layout consisting of single-phase inductances and capacitors. Via this layout, a power filter...
Energy Technology Data Exchange (ETDEWEB)
Michalak, P.
1996-12-31
The connection of certain private electric power producers on the source station bus bars may disturb the 175 Hz or 188 Hz centralized control system signals, which carry tariff messages to the Electricite de France (EDF) grid clients. A new active filter has been developed by EDF and Schlumberger, which raise the tariff signal level at the bus bars by injection of a signal with the same frequency. A prototype has been tested in real conditions
Reduksi Harmonisa Pada Uninterruptible Power Supply (UPS) Dengan Single Tuned Passive Filter
Nasution, Agus Almi
2017-01-01
Using non-linier load in Uninterruptible Power Supply (UPS) can cause harmonic distortion which will eventually have the effect on power quality. The research was designed as a single-turned passive filter to cope will harmonic distortion in UPS. In this phase, THDv, THDi, and IHDi were measured in UPS. MATLAB/Simulink was used for simulation of filter testing. After single-turned passive filter was installed, the third order of harmonic current decreased from 47,69% to 7,08% or reduced 40.61...
DEFF Research Database (Denmark)
Wickramasinghe Abeywardana, Damith Buddika; Acuna, Pablo; Hredzak, Branislav
2018-01-01
Vehicle to grid (V2G) reactive power compensation using electric vehicle (EV) onboard chargers helps to ensure grid power quality by achieving unity power factor operation. However, the use of EVs for V2G reactive power compensation increases the second-order harmonic ripple current component...... from the grid, exposes the EV battery to these undesirable ripple current components for a longer period and discharges the battery due to power conversion losses. This paper presents a way to provide V2G reactive power compensation through a boost inverter-based single stage EV charger and a DC...
Reusing balanced power flow object components for developing harmonic power flow
Energy Technology Data Exchange (ETDEWEB)
Nadarajah, S. [Peninsular Malaysia Electric Utility Co., Kuala Lumpur (Malaysia). Tenaga Nasional Berhad; Nor, K.M.; Abdel-Akher, M. [Malaysia Univ., Kuala Lumpur (Malaysia). Dept. of Electrical Engineering
2005-07-01
Harmonic power flows are used to examine the effects of nonlinear loads on power systems. In this paper, component technology was re-used for the development of a harmonic power flow. The object-oriented power system model (OO-PSM) was developed separately from a solution algorithm. Nodes, lines, and transformers were modelled as entity objects by classes. Power flow solution algorithms were modelled as control objects and encapsulated inside independent software components within the power system component software architecture (PS-COM). Both the OO-PSM and the PS-COM of the balanced power flow were re-used for developing the proposed harmonic power flow. A no-interaction hypothesis was used to consider both fundamental voltages and nonlinear device data dependence. A direct solution voltage node method was also used. The accuracy of the method was demonstrated using IEEE 14 bus and 30 bus test systems. It was concluded that component technology can be used to develop harmonic power flow programs. 7 refs., 2 tabs., 9 figs.
Harmonics and voltage stability analysis in power systems including ...
Indian Academy of Sciences (India)
R. Narasimhan (Krishtel eMaging) 1461 1996 Oct 15 13:05:22
two parameters affecting power quality – harmonics and voltage stability. ... is necessary to pay attention to energy system stability in the planning, management, and ... where k ∈ {m, m + 1,... ,n} and n is total number of the buses in the system.
Research on Compensating Power Converter used for Artillery
Directory of Open Access Journals (Sweden)
Xing Wang
2014-11-01
Full Text Available Aiming at the low efficiency shortage of traditional power supply converter used for artillery, a novel compensating power converter used for artillery was proposed, and its work mode was analyzed. The current expression of inductor was given and work statuses under two working modes were analyzed. Finally an experimental prototype based on DSP was built, the results indicate that the compensating power converter own low current and voltage stress and high efficiency because only part of power pass through the converter, thus, the converter own large potential application value.
Hanif, Muhammad
2017-03-31
The high hardware cost associated with multiple antennas at the secondary transmitter of an underlay cognitive radio (CR) can be reduced by antenna selection. This paper analyzes different power adaptive transmit antenna selection (TAS) schemes for an underlay CR, which ensure that the instantaneous interference caused by the secondary transmitter to the primary receiver is below a predetermined level. We consider the optimal continuous power adaptive TAS and present a low-complexity antenna and power level selection scheme, named sequential antenna and power level selection scheme (SAPS), for discrete power adaptation. Exact statistical characterizations of the signal-to-interference plus noise ratio at the secondary receiver are derived for the considered schemes. Based on the newly derived statistics, we prove that the considered schemes achieve the highest diversity order equaling the number of antennas at the secondary transmitter. Further, we also derive a closed-form expression of the ergodic capacity for the underlay CR with SAPS scheme. Finally, we show that the proposed scheme outperforms existing schemes in terms of ergodic capacity.
DEFF Research Database (Denmark)
Elmholdt, Claus Westergård; Fogsgaard, Morten
2016-01-01
and creativity suggests that when managers give people the opportunity to gain power and explicate that there is reason to be more creative, people will show a boost in creative behaviour. Moreover, this process works best in unstable power hierarchies, which implies that power is treated as a negotiable....... It is thus a central point that power is not necessarily something that breaks down and represses. On the contrary, an explicit focus on the dynamics of power in relation to creativity can be productive for the organisation. Our main focus is to elaborate the implications of this for practice and theory...
Manufacture of sockets of volume compensators in nuclear power plants
International Nuclear Information System (INIS)
Andreev, V.P.; Tshekotilo, L.V.; Shevtshenko, N.T.; Sevruk, A.N.; Wolacek, W.J.; Irsicek, L.; Vrbensky, J.
1982-01-01
Experience is reported with regard to electroslag casting of sockets of volume compensators or steam separators used in nuclear power plants. According to the method the raw pieces are casted directly at the surface of the enclosures
Improvement of the dynamic response of the ITER Reactive Power Compensation system
International Nuclear Information System (INIS)
Finotti, Claudio; Gaio, Elena; Song, Inho; Tao, Jun; Benfatto, Ivone
2015-01-01
Highlights: • The slow response reasons of the classic ITER Reactive Power Compensation (RPC) control are explained. • The dynamic behaviors of the ac/dc converter and of the RPC are characterized. • New control concept to speed up the RPC response is developed. • Good performance of the new RPC control is verified even during fast transient conditions. - Abstract: The ITER ac/dc conversion system can absorb a total active and reactive power up to 500 MW and 950 Mvar, respectively. The Reactive Power Compensation (RPC) system is rated for a nominal power of 750 Mvar necessary to comply with the allowable reactive power limit value from the grid of 200 Mvar. This system is currently under construction and is based on Static Var Compensation technology with Thyristor Controlled Reactor (TCR) and Tuned Filters. The RPC has to minimize the demand of reactive power from the grid; its control is based on a feed-forward method, where the corrective input is the measurement of the reactive power consumption of the ac/dc converters, derived from the 50 Hz component of the Fast Fourier Transform (FFT) of the three-phase voltages and currents. The delay introduced by the FFT calculation and the slow response of the TCR could make the response speed of the RPC not sufficient to face fast variations of the reactive power demand and therefore in this paper a new controller of the RPC able to overcome this shortcoming is proposed and evaluated. It is based on the calculation of the predicted consumption of the reactive power by using the voltage reference signals coming from the Plasma Control System and the measurements of the dc current of the ac/dc converters and of the 66 kV busbar voltage, and on the speed up of the RPC control by introducing a lead–lag transfer function.
Improvement of the dynamic response of the ITER Reactive Power Compensation system
Energy Technology Data Exchange (ETDEWEB)
Finotti, Claudio, E-mail: claudio.finotti@igi.cnr.it [Consorzio RFX (CNR, ENEA, INFN, Università di Padova, Acciaierie Venete SpA), Corso Stati Uniti 4, 35127 Padova (Italy); Gaio, Elena [Consorzio RFX (CNR, ENEA, INFN, Università di Padova, Acciaierie Venete SpA), Corso Stati Uniti 4, 35127 Padova (Italy); Song, Inho; Tao, Jun; Benfatto, Ivone [ITER Organization, Route de Vinon-sur-Verdon, CS 90 046, 13067 St. Paul Lez Durance Cedex (France)
2015-10-15
Highlights: • The slow response reasons of the classic ITER Reactive Power Compensation (RPC) control are explained. • The dynamic behaviors of the ac/dc converter and of the RPC are characterized. • New control concept to speed up the RPC response is developed. • Good performance of the new RPC control is verified even during fast transient conditions. - Abstract: The ITER ac/dc conversion system can absorb a total active and reactive power up to 500 MW and 950 Mvar, respectively. The Reactive Power Compensation (RPC) system is rated for a nominal power of 750 Mvar necessary to comply with the allowable reactive power limit value from the grid of 200 Mvar. This system is currently under construction and is based on Static Var Compensation technology with Thyristor Controlled Reactor (TCR) and Tuned Filters. The RPC has to minimize the demand of reactive power from the grid; its control is based on a feed-forward method, where the corrective input is the measurement of the reactive power consumption of the ac/dc converters, derived from the 50 Hz component of the Fast Fourier Transform (FFT) of the three-phase voltages and currents. The delay introduced by the FFT calculation and the slow response of the TCR could make the response speed of the RPC not sufficient to face fast variations of the reactive power demand and therefore in this paper a new controller of the RPC able to overcome this shortcoming is proposed and evaluated. It is based on the calculation of the predicted consumption of the reactive power by using the voltage reference signals coming from the Plasma Control System and the measurements of the dc current of the ac/dc converters and of the 66 kV busbar voltage, and on the speed up of the RPC control by introducing a lead–lag transfer function.
Energy Technology Data Exchange (ETDEWEB)
Reyes Trujillo, Eleazar
2005-08-15
In this work it is presented the pattern of an active filter of current and their implementation in the program Simulink of MatLab to reduce the content of harmonics generated for different non lineal load. For the active filter of current they were developed each one of the stages that integrate it, from the obtaining of references, the control block and the stage of power. For the obtaining of references, the reactivates instantaneous power theory was used. For the control of the shots of the IGBT's a control knot was used based on a hysteresis band and for the stage of power, an inversor complete bridge was used with a capacitor like source of direct voltage. To analyze the behavior of the active filter, a real industrial electric system was modeled with a lineal load RL and two non lineal load, a using a converter to diodes of 6 pulses and other a working of a machine of dc with a converter to tiristores of 6 pulses. These configurations were used because their content of harmonicas is high. To this system was integrated the active filter modeled in the exit of the non lineal load to avoid that the harmonic components generated by the loads non lineal distortions the current signals. The current signals, voltage signals, power flow, power factor and the harmonic components that circulate in the industrial electric system were analyzed. [Spanish] Actualmente, la presencia de equipos basados en electronica de potencia cuya operacion es no lineal, instalados en los sistemas electricos industriales, ha incrementado la presencia de distorsion en la senal de corriente y/o tension electrica por armonicos, originando problemas en la calidad de la energia electrica. Como una solucion a este problema, en este trabajo, se presenta el modelo de un filtro activo de corriente y su implementacion en el programa Simulink de MatLab para reducir el contenido de armonicos generados por diferentes cargas no lineales. Para el filtro activo de corriente se desarrollaron cada
СURRENT FILTERING IN A THREE-PHASE THREE-WIRE POWER SYSTEM AT ASYMMETRIC SINUSOIDAL VOLTAGES
Directory of Open Access Journals (Sweden)
M. Yu. Artemenko
2018-04-01
Full Text Available Purpose. Investigation of the optimal current distribution between source, shunt active filter and reactive compensator of a three-phase three-wire system that provides consumption of a sinusoidal symmetric current under asymmetric source voltages with minimal power losses was provided. Methodology. The tasks were solved by conducting theoretical and experimental studies. The main provisions of the theory of electrical circuits, the apparatus of mathematical analysis, methods for solving linear differential and algebraic equations, elements of matrix and complex calculus and vector algebra are used. During the development, modern methods and software of computer simulation of electrical engineering complexes and dynamic systems were applied: Matlab-Simulink, MATHCAD. Originality. The principle of compensating current distribution between PAF and reactive compensator of a three-phase three-wire power system with asymmetric sinusoidal voltage was proposed at which the input current is equal to the positive-sequence active current and rms value of PAF current is minimal. The feasibility to compensate the inactive sinusoidal Fryze current by reactive elements under arbitrary combination of load and source parameters was proved and expression for direct calculation of the reactive compensator parameters for generation of inactive Fryze current in the source unbalanced mode was obtained. Practical value. The simulative example for transmission line load showed that combined application of PAF and reactive compensator with the specified distribution of compensating currents ensured a reduction of power losses in 3.273 times and rms value of the SAF current is 12.9 % of rms value total compensation current.
International Nuclear Information System (INIS)
Molina, Marcelo G.; Mercado, Pedro E.; Watanabe, Edson H.
2007-01-01
Power systems security in the case of contingencies is ensured by maintaining adequate 'short-term generation reserve'. This reserve must be appropriately activated by means of the primary frequency control (PFC). Because the generation is an electro-mechanical process, the primary control reserve controllability is not as fast as required, especially by modern power systems. Since the new improvements achieved on the conventional control methods have not been enough to satisfy the high requirements established, the necessity of enhancing the performance of the PFC has arisen. At present, the new energy storage systems (ESS) are a feasible alternative to store excess energy for substituting for the primary control reserve. In this way, it is possible to combine this new ESS with power converter based flexible ac transmission systems (FACTS). This allows an effective exchange of active power with the electric grid and, thus, enhances the PFC. This paper presents an improved PFC scheme incorporating a static synchronous compensator (STATCOM) coupled with a superconducting magnetic energy storage (SMES) device. A detailed full model and a control algorithm based on a decoupled current control strategy of the enhanced compensator are proposed. The integrated STATCOM/SMES controller topology includes three level, multi-pulse, voltage source inverters (VSI) with phase control and incorporates a two quadrant, three level, dc-dc chopper as the interface between the STATCOM and the SMES coil. A novel three level control scheme is proposed by using concepts of instantaneous power in the synchronous rotating d-q reference frame. The dynamic performance of the presented control algorithms is evaluated through digital simulation performed by using SimPowerSystems of SIMULINK/MATLAB T M , and technical analysis is performed to obtain conclusions about the benefits of using SMES devices in the PFC of the electric system. Presently, a laboratory scale prototype device based on
Compensation of Reactive Power from Wind Turbines with Power Electronics Equipment
DEFF Research Database (Denmark)
Pedersen, Jørgen Kaas
1996-01-01
Wind turbines with induction generators consume reactive power. Apart from the no load consumption, which is nearing constant and is being compensated for using capacitors, the consumption of reactive power varies almost proportional with the power production, which can vary immensely. Except tha...
Kalman filtering for rhodium self-powered neutron detectors
International Nuclear Information System (INIS)
Kantrowitz, M.L.
1988-01-01
Rhodium self-powered neutron detectors are utilized in many pressurized water reactors to determine the neutronic behavior within the core. In order to compensate for the inherent time delay associated with the response of these detectors, a dynamic compensation algorithm is currently used in Combustion Engineering plants to reconstruct the dynamic flux signal which is being sensed by the rhodium detectors. This paper describes a new dynamic compensation algorithm, based on Kalman filtering, which improves on the noise gain and response time characteristics of the algorithm currently used, and offers the possibility of utilizing the proven rhodium detector based fixed in-core detector system as an integral part of advanced core control and/or protection systems
New Application’s Approach to Unified Power Quality Conditioners for Mitigation of Surge Voltages
Directory of Open Access Journals (Sweden)
Yeison Alberto Garcés Gomez
2016-01-01
Full Text Available This paper outlines a new approach for the compensation of power systems presented through the use of a unified power quality conditioner (UPQC which compensates impulsive and oscillatory electromagnetic transients. The newly proposed control technique involves a dual analysis of the UPQC where the parallel compensator is modelled as a sinusoidal controlled voltage source, while the series compensator is modelled as a sinusoidal controlled current source, opposed to the traditional approach where the parallel and series compensators are modelled as current and voltage nonsinusoidal sources, respectively. Also a new compensation algorithm is proposed through the application of the theory of generalized reactive power; this is then compared with the theory of active and reactive instantaneous power, or pq theory. The results are presented by means of simulations in MATLAB-Simulink®.
Sun, Dongye; Lin, Xinyou; Qin, Datong; Deng, Tao
2012-11-01
Energy management(EM) is a core technique of hybrid electric bus(HEB) in order to advance fuel economy performance optimization and is unique for the corresponding configuration. There are existing algorithms of control strategy seldom take battery power management into account with international combustion engine power management. In this paper, a type of power-balancing instantaneous optimization(PBIO) energy management control strategy is proposed for a novel series-parallel hybrid electric bus. According to the characteristic of the novel series-parallel architecture, the switching boundary condition between series and parallel mode as well as the control rules of the power-balancing strategy are developed. The equivalent fuel model of battery is implemented and combined with the fuel of engine to constitute the objective function which is to minimize the fuel consumption at each sampled time and to coordinate the power distribution in real-time between the engine and battery. To validate the proposed strategy effective and reasonable, a forward model is built based on Matlab/Simulink for the simulation and the dSPACE autobox is applied to act as a controller for hardware in-the-loop integrated with bench test. Both the results of simulation and hardware-in-the-loop demonstrate that the proposed strategy not only enable to sustain the battery SOC within its operational range and keep the engine operation point locating the peak efficiency region, but also the fuel economy of series-parallel hybrid electric bus(SPHEB) dramatically advanced up to 30.73% via comparing with the prototype bus and a similar improvement for PBIO strategy relative to rule-based strategy, the reduction of fuel consumption is up to 12.38%. The proposed research ensures the algorithm of PBIO is real-time applicability, improves the efficiency of SPHEB system, as well as suite to complicated configuration perfectly.
Sequential Power-Dependence Theory
Buskens, Vincent; Rijt, Arnout van de
2008-01-01
Existing methods for predicting resource divisions in laboratory exchange networks do not take into account the sequential nature of the experimental setting. We extend network exchange theory by considering sequential exchange. We prove that Sequential Power-Dependence Theory—unlike
Energy Technology Data Exchange (ETDEWEB)
Havashki, Asghar
2009-10-15
channel estimation must be upheld, in particular at medium-to-high Channel Signal to Noise Ratios (CSNR). Furthermore, reducing the power consumption through word-length optimization, when realizing such estimators, is an attractive approach. Due to the characteristics of the input signal to such estimators, a special treatment of channel estimation error due to quantization of estimator filter coefficients is needed. In this thesis we investigate the impact of finite coefficient word length on channel estimator performance. A theoretical analysis of the increase in channel estimation error due to quantization of estimator coefficients is performed, and the behavior of this error in different fading environments and for different filter orders is studied. The power consumed in a channel estimator is also influenced by the switching activity in the input signal of the estimator. Characterizing the switching activity in the input signal, including how this activity changes in different environments, e.g., in the presence of noise, is a subject of the work performed in this thesis. In this study we give an expression for direct calculation of the correlation coefficient for the most significant bit in a signal, using the word-level correlation coefficient. We also derive expressions for accurately calculating the variance and word-level correlation coefficient for a correlated signal, when an additional noise of a given variance is added to the signal. This can be used to estimate the bit-level switching activity in a signal in the presence of noise, based on the Dual Bit Type (DBT) method. The impact the additional noise has on the switching activity of a correlated signal has also been studied. These results make it possible for a designer to model the actual input switching activity in different real life noisy environments, enabling realistic power consumption estimation. A study on switching activity reduction in estimator filters using a coefficient reordering method
Modified Perfect Harmonics Cancellation Control of a Grid Interfaced SPV Power Generation
Singh, B.; Shahani, D. T.; Verma, A. K.
2015-03-01
This paper deals with a grid interfaced solar photo voltaic (SPV) power generating system with modified perfect harmonic cancellation (MPHC) control for power quality improvement in terms of mitigation of the current harmonics, power factor correction, control of point of common coupling (PCC) voltage with reactive power compensation and load balancing in a three phase distribution system. The proposed grid interfaced SPV system consists of a SPV array, a dc-dc boost converter and a voltage source converter (VSC) used for the compensation of other connected linear and nonlinear loads at PCC. The reference grid currents are estimated using MPHC method and control signals are derived by using pulse width modulation (PWM) current controller of VSC. The SPV power is fed to the common dc bus of VSC and dc-dc boost converter using maximum power point tracking (MPPT). The dc link voltage of VSC is regulated by using dc voltage proportional integral (PI) controller. The analysis of the proposed SPV power generating system is carried out under dc/ac short circuit and severe SPV-SX and SPV-TX intrusion.
Jin, Tao; Chen, Yiyang; Flesch, Rodolfo C. C.
2017-11-01
Harmonics pose a great threat to safe and economical operation of power grids. Therefore, it is critical to detect harmonic parameters accurately to design harmonic compensation equipment. The fast Fourier transform (FFT) is widely used for electrical popular power harmonics analysis. However, the barrier effect produced by the algorithm itself and spectrum leakage caused by asynchronous sampling often affects the harmonic analysis accuracy. This paper examines a new approach for harmonic analysis based on deducing the modifier formulas of frequency, phase angle, and amplitude, utilizing the Nuttall-Kaiser window double spectrum line interpolation method, which overcomes the shortcomings in traditional FFT harmonic calculations. The proposed approach is verified numerically and experimentally to be accurate and reliable.
A seven harmonic actively compensated Langmuir probe for the GEC Cell
Goodyear, A.; Nolle, L.; Hopgood, A. A.; Picton, P. D.; Braithwaite, N.
2001-10-01
The uncertainty of Langmuir probe measurements in capacitively coupled discharges depends to a great extent on how well harmonic components in the plasma potential are accounted for. The extent to which individual harmonics distort a probe characteristic has been determined across power and pressure parameter-space in the GEC cell. Langmuir probe current-voltage measurements are distorted by RF components across the probe sheath. A seven harmonic waveform was applied to the probe tip to actively match that generated by the plasma. In some circumstances harmonics above the 3rd contributed RF components of the order of the electron temperature in magnitude. Measurement of the EEDF was found to be particularly sensitive to these components. Optimization of the applied waveform (seven amplitudes and seven phases) was achieved using artificially intelligent control. This is advantageous given the large number of (possibly interacting) parameters and permits tracking of changes in plasma conditions. An algorithm utilizing simulated annealing determines the optimum waveform in a far shorter time than a skilled human operator can.
Energy Technology Data Exchange (ETDEWEB)
Lehtonen, M [VTT Energy, Espoo (Finland). Energy Systems
1996-11-01
In this report the effects of harmonics in marine power systems is discussed and a comparison is given between the most typical converter types, including pulse width modulated drives, load commutated inverters and cycloconverters. The effect of harmonic distortion on the power system equipment and loads is first briefly discussed. Special attention is given to the circumstances in the low voltage distribution system, where general load equipment is connected. In addition to the total harmonic distortion the effect of voltage deviation to the supply quality is also considered. The origin of harmonics in the load currents of the three converter types is then considered. The differences between the converters are outlined, and the most typical spectra are presented. The possible means for reducing the harmonic distortion are also studied. The solutions considered are the increasing of the short circuit level, the use of harmonic filters and the increasing of the pulse number. In the case of cycloconverters, the optimization of the phase shift between the parallel operating bridges is also presented. Finally the effects of different converter types on the voltage quality are compared using calculations made for a typical marine power system. (author)
DEFF Research Database (Denmark)
Glasdam, Jakob Bærholm
Introduction The trend in power generation is to partly replace conventional power plants with renewable energy sources. Offshore wind power has been selected to take up a significant proportion of the renewable energy production. The grid codes have been updated to accommodate the rising share...... of wind power. The onshore as well as offshore wind power plants (OWPPs) therefore have to meet the same stringent requirement as the conventional power plants. This can be accommodated by employment of flexible alternating current transmission system (FACTS) devices, such as the static compensator...... gives rise to a number of challenges to the wind power industry with regard to construction, installation as well as transmission of the generated energy. The STATCOM and the voltage-sourced converter high-voltage direct current (VSC-HVDC) are attractive solutions for grid connection of remotely located...
DEFF Research Database (Denmark)
Kouchaki, Alireza; Nymand, Morten
2016-01-01
This paper presents LCL filter design method for three-phase two-level power factor correction (PFC) using line impedance stabilization network (LISN). A straightforward LCL filter design along with variation in grid impedance is not simply achievable and inevitably lead to an iterative solution...... for filter. By introducing of fast power switches for PFC applications such as silicon-carbide, major current harmonics around the switching frequency drops in the region that LISN can actively provide well-defined impedance for measuring the harmonics (i.e. 9 kHz- 30MHz). Therefore, LISN can be replaced...... is derived using the current ripple behavior of converter-side inductor. The grid-side inductor is achieved as a function of LISN impedance to fulfill the grid regulation. To verify the analyses, an LCL filter is designed for a 5 kW SiC-based PFC. The simulation and experimental results support the validity...
Control of a hybrid compensator in a power network by an artificial neural network
Directory of Open Access Journals (Sweden)
I. S. Shaw
1998-07-01
Full Text Available Increased interest in the elimination of distortion in electrical power networks has led to the development of various compensator topologies. The increasing cost of electrical energy necessitates the cost-effective operation of any of these topologies. This paper considers the development of an artificial neural network based controller, trained by means of the backpropagation method, that ensures the cost-effective operation of the hybrid compensator consisting of various converters and filters.
Harmonic Stability and Resonance Analysis in Large PMSG-Based Wind Power Plants
DEFF Research Database (Denmark)
Ebrahimzadeh, Esmaeil; Blaabjerg, Frede; Wang, Xiongfei
2018-01-01
Compared to the conventional power systems, large Wind Power Plants (WPPs) present a more challenging system where the interactions between the passive elements and the wideband control systems of power converters may result in harmonic instability and new resonance frequencies. Most of researches...... system and the resonance frequencies are identified based on the element amplitudes of the MIMO matrix. An active damping controller is used to set the poles of the WPP in a desired location in order to mitigate the harmonic instability problems. Multiple case studies are provided to depict that Wind...
Stator Current Harmonic Reduction in a Novel Half Quasi-Z-Source Wind Power Generation System
Directory of Open Access Journals (Sweden)
Shoudao Huang
2016-09-01
Full Text Available The generator stator current gets distorted with unacceptable levels of total harmonic distortion (THD because impedance-source wind power generation systems use three-phase diode rectifiers. The stator current harmonics will cause increasing losses and torque ripple, which reduce the efficiency and stability of the system. This paper proposes a novel half quasi-Z-source inverter (H-qZSI for grid-connected wind power generation systems, which can reduce the generator stator current harmonics a great deal. When H-qZSI operates in the shoot-through zero state, the derivative of the generator stator current is only determined by the instantaneous value of the generator stator voltage, so the nonlinear relationship between generator stator current and stator voltage is improved compared with the traditional impedance-source inverter. Theoretically, it is indicated that the stator current harmonics can be reduced effectively by means of the proposed H-qZSI. Finally, simulation and experimental results are given to verify the theoretical analysis.
Flexible Compensation of Voltage and Current Unbalance and Harmonics in Microgrids
DEFF Research Database (Denmark)
Mousazadeh, Seyyed Yousef; Jalilian, Alireza; Savaghebi, Mehdi
2017-01-01
In recent years, the harmonics and unbalance problem endanger the voltage and current quality of power systems due to increasing usage of nonlinear and unbalance loads. Using DG interfacing inverters is proposed for voltage or current compensation. In this paper, a flexible control method...... is proposed to compensate voltage and current unbalance and harmonics using the Distributed Generation (DG) interfacing inverters. This method is applicable to both grid-connected and islanded microgrids. In the proposed method, not only the proper control of active and reactive powers can be achieved......) frame. An extensive simulation study has been performed and the results demonstrate the effectiveness of the proposed control scheme. The results show that depending on the compensation mode, the harmonics and unbalance compensation of DGs’ output current, MG’s injected current to the grid as well...
DEFF Research Database (Denmark)
Wu, Weimin; Liu, Yuan; He, Yuanbin
2017-01-01
Grid-tied voltage source inverters using LCL filter have been widely adopted in distributed power generation systems (DPGSs). As high-order LCL filters contain multiple resonant frequencies, switching harmonics generated by the inverter and current harmonics generated by the active/passive loads...... innovative damping methods have been proposed. A comprehensive overview on those contributions and their classification on the inverter- and grid-side damping measures are presented. Based on the concept of the impedance-based stability analysis, all damping methods can ensure the system stability...
Directory of Open Access Journals (Sweden)
M. Jamali
2011-09-01
Full Text Available The phenomenon of magnetizing inrush is a transient condition, which occurs primarily when a transformer is energized. The magnitude of inrush current may be as high as ten times or more times of transformer rated current that causes malfunction of protection system. So, for safe running of a transformer, it is necessary to distinguish inrush current from fault currents. In this paper, an equivalent instantaneous inductance (EII technique is used to discriminate inrush current from fault currents. For this purpose, a three-phase power transformer has been simulated in Maxwell software that is based on finite elements. This three-phase power transformer has been used to simulate different conditions. Then, the results have been used as inputs in MATLAB program to implement the equivalent instantaneous inductance technique. The results show that in the case of inrush current, the equivalent instantaneous inductance has a drastic variation, while it is almost constant in the cases of fault conditions.
DSP based adaptive hysteresis-band current controlled active filter ...
African Journals Online (AJOL)
The use of non-linear loads critically affects the quality of supply by drawing harmonic currents and reactive power from the electrical distribution system. Active power filters are the most viable solution for solving such power quality problems in compliance with the harmonic standards. This article presents a digital signal ...
Effects of series compensation on spot price power markets
International Nuclear Information System (INIS)
Shrestha, G.B.; Wang Feng
2005-01-01
The operation of a deregulated power market becomes more complex as the generation scheduling is dependent on suppliers' and consumers' bids. With large number of transactions in the power market changing in time, it is more likely for some transmission lines to face congestion. Series compensation, such as TCSC, with its ability to directly control the power flow can be very helpful to improve the operation of transmission networks. The effects of TCSC on the operation of a spot price power market are studied in this paper using the modified IEEE 14-bus system. Optimal Power Flow incorporating TCSC is used to implement the spot price market. Linear bids are used to model suppliers' and consumers' bids. Issues of location and cost of TCSC are discussed. The effects of levels of TCSC compensation on wide range of system quantities are studied. The effects on the total social benefit, the spot prices, transmission congestion, total generation and consumption, benefit to individual supplier and consumer etc. are discussed. It is demonstrated that though use of TCSC makes the system more efficient and augments competition in the market, it is not easy to establish general relationships between the levels of compensation and various market quantities. Simulation studies like these can be used to assess the effects of TCSC in specific systems. (Author)
Index-based reactive power compensation scheme for voltage regulation
Dike, Damian Obioma
2008-10-01
Increasing demand for electrical power arising from deregulation and the restrictions posed to the construction of new transmission lines by environment, socioeconomic, and political issues had led to higher grid loading. Consequently, voltage instability has become a major concern, and reactive power support is vital to enhance transmission grid performance. Improved reactive power support to distressed grid is possible through the application of relatively unfamiliar emerging technologies of "Flexible AC Transmission Systems (FACTS)" devices and "Distributed Energy Resources (DERS)." In addition to these infrastructure issues, a lack of situational awareness by system operators can cause major power outages as evidenced by the August 14, 2003 widespread North American blackout. This and many other recent major outages have highlighted the inadequacies of existing power system indexes. In this work, a novel "Index-based reactive compensation scheme" appropriate for both on-line and off-line computation of grid status has been developed. A new voltage stability index (Ls-index) suitable for long transmission lines was developed, simulated, and compared to the existing two-machine modeled L-index. This showed the effect of long distance power wheeling amongst regional transmission organizations. The dissertation further provided models for index modulated voltage source converters (VSC) and index-based load flow analysis of both FACTS and microgrid interconnected power systems using the Newton-Raphson's load flow model incorporated with multi-FACTS devices. The developed package has been made user-friendly through the embodiment of interactive graphical user interface and implemented on the IEEE 14, 30, and 300 bus systems. The results showed reactive compensation has system wide-effect, provided readily accessible system status indicators, ensured seamless DERs interconnection through new islanding modes and enhanced VSC utilization. These outcomes may contribute
Active Power Quality Improvement Strategy for Grid-connected Microgrid Based on Hierarchical Control
DEFF Research Database (Denmark)
Wei, Feng; Sun, Kai; Guan, Yajuan
2018-01-01
proposes an active, unbalanced, and harmonic GCC suppression strategy based on hierarchical theory. The voltage error between the bus of the DCGC-MG and the grid’s PCC was transformed to the dq frame. On the basis of the grid, an additional compensator, which consists of multiple resonant voltage......When connected to a distorted grid utility, droop-controlled grid-connected microgrids (DCGC-MG) exhibit low equivalent impedance. The harmonic and unbalanced voltage at the point of common coupling (PCC) deteriorates the power quality of the grid-connected current (GCC) of DCGC-MG. This work...... regulators, was then added to the original secondary control to generate the negative fundamental and unbalanced harmonic voltage reference. Proportional integral and multiple resonant controllers were adopted as voltage controller at the original primary level to improve the voltage tracking performance...
Passive wide spectrum harmonic filter for adjustable speed drives in oil and gas industry
Al Jaafari, Khaled Ali
Non-linear loads such as variable speed drives constitute the bulky load of oil and gas industry power systems. They are widely used in driving induction and permanent magnet motors for variable speed applications. That is because variable speed drives provide high static and dynamic performance. Moreover, they are known of their high energy efficiency and high motion quality, and high starting torque. However, these non-linear loads are main sources of current and voltage harmonics and lower the quality of electric power system. In fact, it is the six-pulse and twelve-pulse diode and thyristor rectifiers that spoil the AC power line with the dominant harmonics (5th, 7th, 11th). They provide DC voltage to the inverter of the variable speed drives. Typical problems that arise from these harmonics are Harmonic resonances', harmonic losses, interference with electronic equipment, and line voltage distortion at the Point of Common Coupling (PCC). Thus, it is necessary to find efficient, reliable, and economical harmonic filters. The passive filters have definite advantage over active filters in terms of components count, cost and reliability. Reliability and maintenance is a serious issue in drilling rigs which are located in offshore and onshore with extreme operating conditions. Passive filters are tuned to eliminate a certain frequency and therefore there is a need to equip the system with more than one passive filter to eliminate all unwanted frequencies. An alternative solution is Wide Spectrum Harmonic passive filter. The wide spectrum harmonic filters are becoming increasingly popular in these applications and found to overcome some of the limitations of conventional tuned passive filter. The most important feature of wide spectrum harmonic passive filters is that only one capacitor is required to filter a wide range of harmonics. Wide spectrum filter is essentially a low-pass filter for the harmonic at fundamental frequency. It can also be considered as a
Energy Technology Data Exchange (ETDEWEB)
Marques, Hugo S.; Anunciada, Victor; Borges, Beatriz V. [Power Electronics Group, Instituto de Telecomunicacoes, Lisbon (Portugal); Instituto Superior Tecnico - Universidade Tecnica de Lisboa, Lisbon (Portugal)
2010-01-15
The great majority of the existing hybrid active power filter solutions is normally focused in 3{phi} systems and, in general, concentrates its domain of application in specific loads with deterministic behavior. Because common use grids do not exhibit these characteristics, it is mandatory to develop solutions for more generic scenarios, encouraging the use of less classical hybrid solutions. In fact, due to the widely use of switch mode converters in a great variety of consumer electronics, the problematic of mains current harmonic mitigation is no longer an exclusive matter of 3{phi} systems. The contribution of this paper is to present a shunt hybrid active power filter topology, initially conceived to work in 1{phi} domestic grids, able to operate the inverter at a voltage rate that can be lower than 10% of the mains voltage magnitude, even under nonspecific working conditions. In addition, the results shown in this paper demonstrate that this topology can, without lack of generality, be suitable to medium voltage (1{phi} or 3{phi}) systems. A new control approach for the proposed topology is discussed in this paper. The control method exhibits an extremely simple architecture requiring single point current sensing only, with no need for any kind of reference. Its practical implementation can be fulfilled by using very few, common use, operational amplifiers. The principle of operation, design criteria, simulation predictions and experimental results are presented and discussed. (author)
Novel Control Strategy for VSI and CSI Active Filters and Comparing These Two Types of Filters
Directory of Open Access Journals (Sweden)
Gholam Reza Arab
2014-10-01
Full Text Available Recently to eliminate the harmonics and improve the power factor of the power networks, much attention has been attracted to active filters. The advantages of these filters are lower volume and their better compensating characteristics than the passive filters. In conventional sliding mode controllers, the source current waveform is fluctuated in near to zero values. In this paper, using a new sliding technique, lower Total Harmonic Distortion (THD in source current is obtained and the current waveform is improved. As well as, two novel control strategies for two types of active filters, VSI and CSI is proposed and then these two types of filters are compared to reduce THD value of source current.The proposed controlled strategies are simulated by MATLAB/Simulink. The Simulation results confirm that the proposed strategies reduce the THD of source current more than other strategies, and active filter based on CSI has a better performance than active filter based on VSI with a dead time area (for avoiding short circuit of the source in high powers.
DEFF Research Database (Denmark)
Loh, P.; Tang, Y.; Blaabjerg, Frede
2011-01-01
In this study, repetitive current controllers operating in either the mixed or stationary frame are proposed for high-precision reference tracking and disturbance rejection of power converters. Both controllers use a proportional-resonant regulator in the stationary frame for regulating...... the positive- and negative-sequence fundamental currents, which are known to directly influence the flow of active and reactive power in most energy conversion systems. Moreover, for the tracking or compensation of harmonics, the controllers include a repetitive control path in either the synchronous...... or stationary frame, whose inherent feedback and feedforward structure is proven to resemble a bank of resonant filters in either reference frames. Unlike other existing controllers, the proposed repetitive controllers function by introducing multiple resonant peaks at only those harmonic frequencies typically...
Magallanes, Francisco Cabaleiro; Viarouge, Philippe; Cros, Jérôme
2015-01-01
This paper proposes a novel topological solution for pulsed power converters based on capacitor-discharge topologies, integrating a Fast Voltage Compensator which allows an operation at constant power consumption from the utility grid. This solution has been retained as a possible candidate for the CLIC project under study at CERN, which requires more than a thousand synchronously-operated klystron modulators producing a total pulsed power of almost 40 GW. The proposed Fast Voltage Compensator is integrated in the modulator such that it only has to treat the capacitor charger current and a fraction of the charging voltage, meaning that its dimensioning power and cost are minimized. This topology can be used to improve the AC power quality of any pulsed converters based on capacitor-discharge concept. A prototype has been built and exploited to validate the operating principle and demonstrate the benefits of the proposed solution.
Zaidi Maryam Nabihah; Ali Adlan
2018-01-01
This paper present the project designed to correcting power factor for medical industries in Malaysia automatically. Which with hope to make the cost and energy usage efficient, because the energy source are depleting due to increase in population. Power factor is the ratio of real power and apparent power. This definition is mathematically represented as kW/kVA where kW is active power and kVA is apparent power (active + reactive). Reactive power is the non-working power generated by the mag...
Study on UPF Harmonic Current Detection Method Based on DSP
Energy Technology Data Exchange (ETDEWEB)
Zhao, H J [Northwestern Polytechnical University, Xi' an 710072 (China); Pang, Y F [Xi' an University of Technology, Xi' an 710048 (China); Qiu, Z M [Xi' an University of Technology, Xi' an 710048 (China); Chen, M [Northwestern Polytechnical University, Xi' an 710072 (China)
2006-10-15
Unity power factor (UPF) harmonic current detection method applied to active power filter (APF) is presented in this paper. The intention of this method is to make nonlinear loads and active power filter in parallel to be an equivalent resistance. So after compensation, source current is sinusoidal, and has the same shape of source voltage. Meanwhile, there is no harmonic in source current, and the power factor becomes one. The mathematic model of proposed method and the optimum project for equivalent low pass filter in measurement are presented. Finally, the proposed detection method applied to a shunt active power filter experimental prototype based on DSP TMS320F2812 is developed. Simulation and experiment results indicate the method is simple and easy to implement, and can obtain the real-time calculation of harmonic current exactly.
Smart — STATCOM control strategy implementation in wind power plants
DEFF Research Database (Denmark)
Sintamarean, Nicolae Christian; Cantarellas, Antoni Mir; Miranda, H.
2012-01-01
High penetration of wind energy into the grid may introduce stability and power quality problems due to the fluctuating nature of the wind and the increasing complexity of the power system. By implementing advanced functionalities in power converters, it is possible to improve the performance...... of the wind farm and also to provide grid support, as it is required by the grid codes. One of the main compliance difficulties that can be found in such power plants are related to reactive power compensation and to keep the harmonics content between the allowed limits, even if the power of the WPP...... converters is increasing. This paper deals with an advanced control strategy design of a three-level converter performing STATCOM and Active Filter functionalities. The proposed system is called Smart-STATCOM since it has the capability of self-controlling reactive power and harmonic voltages at the same...
Directory of Open Access Journals (Sweden)
D. T. Do
2017-09-01
Full Text Available In this investigation, we consider wireless powered relaying systems, where energy is scavenged by a relay via radio frequency (RF signals. We explore hybrid time switching-based and power splitting-based relaying protocol (HTPSR and compare performance of Amplify-and-Forward (AF with Decode-and-Forward (DF scheme under imperfect channel state information (CSI. Most importantly, the instantaneous rate, achievable bit error rate (BER are determined in the closed-form expressions under the impact of imperfect CSI. Through numerical analysis, we evaluate system insights via different parameters such as power splitting (PS and time switching (TS ratio of the considered HTPSR which affect outage performance and BER. It is noted that DF relaying networks outperform AF relaying networks. Besides that, the numerical results are given to prove the optimization problems of PS and TS ratio to obtain optimal instantaneous rate.
Improved cable compensation technique for self powered neutron detectors
International Nuclear Information System (INIS)
Nieuwenhove, R. van
1996-01-01
Measurements with cobalt self powered neutron detectors on the BR2 reactor have revealed that the currents induced by external gamma radiation can be of the same order as the neutron induced signal and that the gamma induced current on the emitter and the compensator wires are not symmetric. In this case, the standard detection electronic setup leads to erroneous results. It is shown that a slightly modified electronic setup, in which this asymmetry is compensated for, can nevertheless allow to obtain correct neutron flux measurements. Measures to reduce the influence of external gamma radiation in general will also be discussed. (orig.)
Performance improvement of shunt active power filter based on non-linear least-square approach
DEFF Research Database (Denmark)
Terriche, Yacine
2018-01-01
. This paper proposes an improved open loop strategy which is unconditionally stable and flexible. The proposed method which is based on non-linear least square (NLS) approach can extract the fundamental voltage and estimates its phase within only half cycle, even in the presence of odd harmonics and dc offset......). The synchronous reference frame (SRF) approach is widely used for generating the RCC due to its simplicity and computation efficiency. However, the SRF approach needs precise information of the voltage phase which becomes a challenge under adverse grid conditions. A typical solution to answer this need...
Power filtering of nth order in the fractional Fourier domain
International Nuclear Information System (INIS)
Alieva, Tatiana; Calvo, Maria Luisa; Bastiaans, Martin J.
2002-01-01
The main properties of the power filtering operation in the fractional Fourier domain and its relationship to the differentiation operation are considered. The application of linear power filtering for solving the phase retrieval problem from intensity distributions only is proposed. The optical configuration for the experimental realization of the method is discussed. (author)
Yan Lu; Wing-Hung Ki
2014-06-01
A full-wave active rectifier switching at 13.56 MHz with compensated bias current for a wide input range for wirelessly powered high-current biomedical implants is presented. The four diodes of a conventional passive rectifier are replaced by two cross-coupled PMOS transistors and two comparator- controlled NMOS switches to eliminate diode voltage drops such that high voltage conversion ratio and power conversion efficiency could be achieved even at low AC input amplitude |VAC|. The comparators are implemented with switched-offset biasing to compensate for the delays of active diodes and to eliminate multiple pulsing and reverse current. The proposed rectifier uses a modified CMOS peaking current source with bias current that is quasi-inversely proportional to the supply voltage to better control the reverse current over a wide AC input range (1.5 to 4 V). The rectifier was fabricated in a standard 0.35 μm CMOS N-well process with active area of 0.0651 mm(2). For the proposed rectifier measured at |VAC| = 3.0 V, the voltage conversion ratios are 0.89 and 0.93 for RL=500 Ω and 5 kΩ, respectively, and the measured power conversion efficiencies are 82.2% to 90.1% with |VAC| ranges from 1.5 to 4 V for RL=500 Ω.
Design and Optimisation of a Simple Filter Group for Reactive Power Distribution
Directory of Open Access Journals (Sweden)
Ryszard Klempka
2016-01-01
Full Text Available Basic methods are presented to design a simple filter group and a method of shaping the resultant of the filter group’s impedance characteristics (distribution of the characteristics’ extremes and then project equations were transformed into a uniform, common form that addresses issues of the reactive power distribution between component filters. The analysis also takes into account the filters’ detuning from the reduced harmonics and quality factors of passive elements. Another important factor of the analysis considered was the power grid equivalent impedance affecting the filtration effectiveness. A criterion for the filter group’s filtration effectiveness evaluation was proposed and optimisation was completed for the reactive power distribution between separate filters in the function of the power grid’s equivalent inductance.
A Hierarchical Control Scheme for Reactive Power and Harmonic Current Sharing in Islanded Microgrids
DEFF Research Database (Denmark)
Lorzadeh, Iman; Firoozabadi, Mehdi Savaghebi; Askarian Abyaneh, Hossein
2015-01-01
In this paper, a hierarchical control scheme consisting of primary and secondary levels is proposed for achieving accurate reactive power and harmonic currents sharing among interface inverters of distributed generators (DGs) in islanded microgrids. Firstly, fundamental and main harmonic componen...
Low Power Systolic Array Based Digital Filter for DSP Applications
Directory of Open Access Journals (Sweden)
S. Karthick
2015-01-01
Full Text Available Main concepts in DSP include filtering, averaging, modulating, and correlating the signals in digital form to estimate characteristic parameter of a signal into a desirable form. This paper presents a brief concept of low power datapath impact for Digital Signal Processing (DSP based biomedical application. Systolic array based digital filter used in signal processing of electrocardiogram analysis is presented with datapath architectural innovations in low power consumption perspective. Implementation was done with ASIC design methodology using TSMC 65 nm technological library node. The proposed systolic array filter has reduced leakage power up to 8.5% than the existing filter architectures.
DEFF Research Database (Denmark)
Freijedo Fernandez, Francisco Daniel; Chaudhary, Sanjay Kumar; Guerrero, Josep M.
2015-01-01
-domain. As an alternative, a power based averaged modelling is also proposed. Type IV wind turbine harmonic signature and STATCOM active harmonic mitigation are considered for the simulation case studies. Simulation results provide a good insight of the features and limitations of the proposed methodologies.......This paper approaches modelling methodologies for integration of wind turbines and STATCOM in harmonic resonance studies. Firstly, an admittance equivalent model representing the harmonic signature of grid connected voltage source converters is provided. A simplified type IV wind turbine modelling...... is then straightforward. This linear modelling is suitable to represent the wind turbine in the range of frequencies at which harmonic interactions are likely. Even the admittance method is suitable both for frequency and time domain studies, some limitations arise in practice when implementing it in the time...
Power and Aging Characterization of Digital FIR Filters Architectures
DEFF Research Database (Denmark)
Calimera, Andrea; Liu, Wei; Macii, Enrico
2012-01-01
-variation, temperature and aging induced variations pose new challenges in the fabrication of the next generation of ICs. This work presents a detailed power and aging characterization of digital FIR filters in an industrial 45nm CMOS technology, and a design space exploration of different filter architectures...... with respect to throughput, area, power dissipation and aging. The exploration is intended to provide new design guidelines when considering aging of components in power/performance tradeoffs....
Directory of Open Access Journals (Sweden)
E. P. Zabello
2005-01-01
Full Text Available The method is proposed to make a correction in payment for consumption of reactive energy and power which is attributed to deviation of actual activation energy losses for reactive power compensation from their standard value. It is recommended to calculate standard loss values for every voltage level and actual loss values are to be determined with the help of application of remote electronic accounting means in the current mode of power consumption.
Harmonic and power balance tools for tapping-mode atomic force microscope
International Nuclear Information System (INIS)
Sebastian, A.; Salapaka, M. V.; Chen, D. J.; Cleveland, J. P.
2001-01-01
The atomic force microscope (AFM) is a powerful tool for investigating surfaces at atomic scales. Harmonic balance and power balance techniques are introduced to analyze the tapping-mode dynamics of the atomic force microscope. The harmonic balance perspective explains observations hitherto unexplained in the AFM literature. A nonconservative model for the cantilever - sample interaction is developed. The energy dissipation in the sample is studied and the resulting power balance equations combined with the harmonic balance equations are used to estimate the model parameters. Experimental results confirm that the harmonic and power balance tools can be used effectively to predict the behavior of the tapping cantilever. [copyright] 2001 American Institute of Physics
DEFF Research Database (Denmark)
Zhou, Jianguo; Kim, Sunghyok; Zhang, Huaguang
2018-01-01
This paper investigates the issue of accurate reactive, harmonic and imbalance power sharing in a microgrid. Harmonic and imbalance droop controllers are developed to proportionally share the harmonic power and the imbalance power among distributed generation (DG) units and improve the voltage...... voltage. With the proposed methods, the microgrid system reliability and flexibility can be enhanced and the knowledge of the line impedance is not required. And the reactive, harmonic and imbalance power can be proportionally shared among the DG units. Moreover, the quality of the voltage at PCC can...
Investigating power factor compensation capacity calculation in medium sized industry
International Nuclear Information System (INIS)
Chudhry, M.A.; Hanif, A.
2008-01-01
There are a variety of techniques developed in order to improve the efficiency of electrical systems and reduce cost of providing electricity to the consumer. This paper presents a new technique for power-factor capacity calculation in medium-sized industrial/ commercial setups. Various loads of similar nominal power-factor are categorized and demand-factor of loads is so selected that it has engineering justifications. The developed system works on the principle of low-voltage power-factor correction, which substantially reduces electricity bill and increases loading-capacity of the electrical system. It allows commercial and industrial consumers to save on their power cost appreciably. This work utilizes software, which takes few inputs and produces numerous useful results. Adoption of this system can help the user in computing compensation-capacity, system KVA (size of transformer) and cost of compensation. A feature of this system is prediction of low PF penalty. Moreover, it also suggests the tentative payback period. (author)
Enhanced Electric Power Transmission by Hybrid Compensation Technique
International Nuclear Information System (INIS)
Palanichamy, C; Kiu, G Q
2015-01-01
In today's competitive environment, new power system engineers are likely to contribute immediately to the task, without years of seasoning via on-the-job training, mentoring, and rotation assignments. At the same time it is becoming obligatory to train power system engineering graduates for an increasingly quality-minded corporate environment. In order to achieve this, there is a need to make available better-quality tools for educating and training power system engineering students and in-service system engineers too. As a result of the swift advances in computer hardware and software, many windows-based computer software packages were developed for the purpose of educating and training. In line with those packages, a simulation package called Hybrid Series-Shunt Compensators (HSSC) has been developed and presented in this paper for educational purposes. (paper)
Conjugate Image Theory Applied on Capacitive Wireless Power Transfer
Ben Minnaert; Nobby Stevens
2017-01-01
Wireless power transfer using a magnetic field through inductive coupling is steadily entering the market in a broad range of applications. However, for certain applications, capacitive wireless power transfer using electric coupling might be preferable. In order to obtain a maximum power transfer efficiency, an optimal compensation network must be designed at the input and output ports of the capacitive wireless link. In this work, the conjugate image theory is applied to determine this opti...
Kalman filtering of self-powered neutron detectors
International Nuclear Information System (INIS)
Kantrowitz, M.L.
1992-01-01
Pressurized water reactors employ a wide variety of in-core detectors to determine the neutronic behavior within the core. Among the detectors used are rhodium and vanadium self-powered detectors (SPDs), which are very accurate, but respond slowly to changes in neutron flux. This paper describes a new dynamic compensation algorithm, based on Kalman filtering, which converts delayed-responding rhodium and vanadium SPDs into prompt-responding detectors by reconstructing the dynamic flux signal sensed by the detectors from the prompt and delayed components. This conversion offers the possibility of utilizing current fixed in-core detector systems based on these delayed-responding detectors for core control and/or core protection functions without the need for fixed in-core detectors which are prompt-responding. As a result, the capabilities of current fixed in-core detector systems could be expanded significantly without a major hardware investment
Kubo, N
1995-04-01
To improve the quality of single-photon emission computed tomographic (SPECT) images, a restoration filter has been developed. This filter was designed according to practical "least squares filter" theory. It is necessary to know the object power spectrum and the noise power spectrum. The power spectrum is estimated from the power spectrum of a projection, when the high-frequency power spectrum of a projection is adequately approximated as a polynomial exponential expression. A study of the restoration with the filter based on a projection power spectrum was conducted, and compared with that of the "Butterworth" filtering method (cut-off frequency of 0.15 cycles/pixel), and "Wiener" filtering (signal-to-noise power spectrum ratio was a constant). Normalized mean-squared errors (NMSE) of the phantom, two line sources located in a 99mTc filled cylinder, were used. NMSE of the "Butterworth" filter, "Wiener" filter, and filtering based on a power spectrum were 0.77, 0.83, and 0.76 respectively. Clinically, brain SPECT images utilizing this new restoration filter improved the contrast. Thus, this filter may be useful in diagnosis of SPECT images.
International Nuclear Information System (INIS)
Kubo, Naoki
1995-01-01
To improve the quality of single-photon emission computed tomographic (SPECT) images, a restoration filter has been developed. This filter was designed according to practical 'least squares filter' theory. It is necessary to know the object power spectrum and the noise power spectrum. The power spectrum is estimated from the power spectrum of a projection, when the high-frequency power spectrum of a projection is adequately approximated as a polynomial exponential expression. A study of the restoration with the filter based on a projection power spectrum was conducted, and compared with that of the 'Butterworth' filtering method (cut-off frequency of 0.15 cycles/pixel), and 'Wiener' filtering (signal-to-noise power spectrum ratio was a constant). Normalized mean-squared errors (NMSE) of the phantom, two line sources located in a 99m Tc filled cylinder, were used. NMSE of the 'Butterworth' filter, 'Wiener' filter, and filtering based on a power spectrum were 0.77, 0.83, and 0.76 respectively. Clinically, brain SPECT images utilizing this new restoration filter improved the contrast. Thus, this filter may be useful in diagnosis of SPECT images. (author)
Directory of Open Access Journals (Sweden)
Hae-Gwang Jeong
2013-01-01
Full Text Available This paper proposes a second-order harmonic reduction technique using a proportional-resonant (PR controller for a photovoltaic (PV power conditioning system (PCS. In a grid-connected single-phase system, inverters create a second-order harmonic at twice the fundamental frequency. A ripple component unsettles the operating points of the PV array and deteriorates the operation of the maximum power point tracking (MPPT technique. The second-order harmonic component in PV PCS is analyzed using an equivalent circuit of the DC/DC converter and the DC/AC inverter. A new feed-forward compensation technique using a PR controller for ripple reduction is proposed. The proposed algorithm is advantageous in that additional devices are not required and complex calculations are unnecessary. Therefore, this method is cost-effective and simple to implement. The proposed feed-forward compensation technique is verified by simulation and experimental results.
Active and reactive power control of a current-source PWM-rectifier using space vectors
Energy Technology Data Exchange (ETDEWEB)
Salo, M.; Tuusa, H. [Tampere University of Technology (Finland). Department of Electrical Engineering, Power Electronics
1997-12-31
In this paper the current-source PWM-rectifier with active and reactive power control is presented. The control system is realized using space vector methods. Also, compensation of the reactive power drawn by the line filter is discussed. Some simulation results are shown. (orig.) 8 refs.
Device for measuring active, reactive and apparent power
Energy Technology Data Exchange (ETDEWEB)
Bartosinski, E.; Wieland, J.
1982-09-30
The plan consists of a traditional electrodynamic mechanism for measuring power (IM) supplemented by three switches, two rectifiers, resistor, included in parallel, and phaseshifting throttle included in series with the voltage coil of the IM. This makes it possible by selection to perform three types of measurements: active power of alternating current or power of direct current, only the voltage coils and the IM current are engaged; reactive power, the resistor and the throttle are additionally engaged by the aforementioned method; complete (apparent) power--the current and the voltage are supplied directly to the IM coils, but in contrast to the first case, through rectifiers. The influence of the highest harmonic components of voltage and current which are not significant for industrial measurements can be eliminated in necessary cases using filtering devices.
Ripple characteristic of the main ring magnet power supply for the KEK 12 GeV PS
International Nuclear Information System (INIS)
Sato, Hikaru; Sueno, Tuyosi; Mikawa, Katsuhiko
1995-01-01
First of all, general description of the main ring magnet power supply for the KEK 12 GeV PS will be described. The main power supply consists of thyristor rectifiers, DC filters, reactive power compensators, AC harmonic filters and control systems. Devices and control systems for suppressing ripple component of magnet field will be described. (author)
Flexible Compensation of Voltage and Current Unbalance and Harmonics in Microgrids
Directory of Open Access Journals (Sweden)
Seyyed Yousef Mousazadeh Mousavi
2017-10-01
Full Text Available In recent years, the harmonics and unbalance problems endanger the voltage and current quality of power systems, due to increasing usage of nonlinear and unbalanced loads. Use of Distributed Generation (DG-interfacing inverters is proposed for voltage or current compensation. In this paper, a flexible control method is proposed to compensate voltage and current unbalance and harmonics using the distributed generation (DG-interfacing inverters. This method is applicable to both grid-connected and islanded Microgrids (MGs. In the proposed method, not only the proper control of active and reactive powers can be achieved, but also there is flexibility in compensating the voltage or current quality problems at DG terminals or Points of Common Coupling (PCCs. This control strategy consists of active and reactive power controllers and a voltage/current quality-improvement block. The controller is designed in a stationary (αβ frame. An extensive simulation study has been performed and the results demonstrate the effectiveness of the proposed control scheme. Depending on the compensation modes, the harmonics and unbalance compensation of DG output current, MG-injected current to the grid, as well as PCC and DG voltages, can be achieved in grid-connected operation of MG while in the islanded operation, and the PCC and DG voltages compensation can be obtained through the proposed control scheme.
Line filter design of parallel interleaved VSCs for high power wind energy conversion systems
DEFF Research Database (Denmark)
Gohil, Ghanshyamsinh Vijaysinh; Bede, Lorand; Teodorescu, Remus
2015-01-01
The Voltage Source Converters (VSCs) are often connected in parallel in a Wind Energy Conversion System (WECS) to match the high power rating of the modern wind turbines. The effect of the interleaved carriers on the harmonic performance of the parallel connected VSCs is analyzed in this paper...... limit. In order to achieve the desired filter performance with optimal values of the filter parameters, the use of a LC trap branch with the conventional LCL filter is proposed. The expressions for the resonant frequencies of the proposed line filter are derived and used in the design to selectively...
Power Ramp Limitation capabilities of Large PV Power Plants with Active Power Reserves
DEFF Research Database (Denmark)
Bogdan, Craciun; Kerekes, Tamas; Sera, Dezso
2017-01-01
Power Ramp Limitation (PRL) is likely to become a requirement for large scale photovoltaic power plants (LPVPPs) in order to allow the increase of PV penetration levels. Especially in islands with reduced inertia capability, this problem is more stringent: high power ramp can be caused by either...... fast irradiance changes or other participant generators for example wind power, or loads. In order to compensate for the power mismatch, LPVPPs must use Active Power Reserve (APR), by either curtailment or auxiliary storage. The paper proposes a PRL control structure for dynamic APR sizing...... and deployment. The selected test case is the power system of Puerto Rico (PREPA), modeled using the modified IEEE 12 bus benchmark system, with different levels of PV penetration. It is shown that LPVPP with PRL can effectively reduce the ramping rate of the participating generators. Considering that the large...
Principles and theory of resonance power supplies
International Nuclear Information System (INIS)
Sreenivas, A.; Karady, G.G.
1991-01-01
The resonance power supply is widely used and proved to be an efficient method to supply accelerator magnets. The literature describes several power supply circuits but no comprehensive theory of operation is presented. This paper presents a mathematical method which describes the operation of the resonance power supply and it can be used for accurate design of components
Efficient Reactive Power Compensation Algorithm for Distribution Network
Directory of Open Access Journals (Sweden)
J. Jerome
2017-12-01
Full Text Available The use of automation and energy efficient equipment with electronic control would greatly improve industrial production. These new devices are more sensitive to supply voltage deviation and the characteristics of the power system that was previously ignored are now very important. Hence the benefits of distribution automation have been widely acknowledged in recent years. This paper proposes an efficient load flow solution technique extended to find optimum location for reactive power compensation and network reconfiguration for planning and day-to-day operation of distribution networks. This is required as a part of the distribution automation system (DAS for taking various control and operation decisions. The method exploits the radial nature of the network and uses forward and backward propagation technique to calculate branch currents and node voltages. The proposed method has been tested to analyze several practical distribution networks of various voltage levels and also having high R/X ratio.
A Voltage Feedback Based Harmonic Compensation Strategy for Current-Controlled Converters
DEFF Research Database (Denmark)
Zhao, Xin; Meng, Lexuan; Xie, Chuan
2018-01-01
Harmonics have been considered as one of the major issues in future power grids. With the increasing demand in advanced control functions, power electronic converter interfaced distributed generators (DGs) are expected to perform harmonic compensation when necessary. It has been demonstrated in a...
Milood Almelian, Mohamad; Mohd, Izzeldin I.; Asghaiyer Omran, Mohamed; Ullah Sheikh, Usman
2018-04-01
Power quality-related issues such as current and voltage distortions can adversely affect home and industrial appliances. Although several conventional techniques such as the use of passive and active filters have been developed to increase power quality standards, these methods have challenges and are inadequate due to the increasing number of applications. The Unified Power Quality Conditioner (UPQC) is a modern strategy towards correcting the imperfections of voltage and load current supply. A UPQC is a combination of both series and shunt active power filters in a back-to-back manner with a common DC link capacitor. The control of the voltage of the DC link capacitor is important in achieving a desired UPQC performance. In this paper, the UPQC with a Fuzzy logic controller (FLC) was used to precisely eliminate the imperfections of voltage and current harmonics. The results of the simulation studies using MATLAB/Simulink and Simpower system programming for R-L load associated through an uncontrolled bridge rectifier was used to assess the execution process. The UPQC with FLC was simulated for a system with distorted load current and a system with distorted source voltage and load current. The outcome of the comparison of %THD in the load current and source voltage before and after using UPQC for the two cases was presented.
Compensator design for corrector magnet power supply of TPS facility
International Nuclear Information System (INIS)
Wong, Y.-S.; Chen, J.-F.; Liu, K.-B.; Liu, C.-Y.; Wang, B.-S.
2017-01-01
From 2012 to 2015, Taiwan government has a most important technology project is Taiwan Photon Source (TPS), the total budget of TPS fund to over US300 million. It set up a synchrotron storage ring (electron energy of 3.3 GeV, circumference of 518 m, and low emittance) that provides one of the world's brightest synchrotron sources of x-rays. This study presents a compensator design for corrector magnet power supply to avoid limitations in stabilizing the frequency when the machine output current load is valid. A lead-lag compensator had been built in a full-bridge converter to improve the system bandwidth. Lead-lag compensators influence various disciplines, such as robotics, satellite control, automobile diagnostics, and laser frequency stabilization. These components are important building blocks in analog control systems and can also be used in digital control. A 50V output voltage and 10A output current prototype converter is fabricated in the laboratory. From the experimental results, the effectiveness of the control loop design can be verified from the gain margin and phase margin.
Compensator design for corrector magnet power supply of TPS facility
Wong, Y.-S.; Chen, J.-F.; Liu, K.-B.; Liu, C.-Y.; Wang, B.-S.
2017-10-01
From 2012 to 2015, Taiwan government has a most important technology project is Taiwan Photon Source (TPS), the total budget of TPS fund to over US300 million. It set up a synchrotron storage ring (electron energy of 3.3 GeV, circumference of 518 m, and low emittance) that provides one of the world's brightest synchrotron sources of x-rays. This study presents a compensator design for corrector magnet power supply to avoid limitations in stabilizing the frequency when the machine output current load is valid. A lead-lag compensator had been built in a full-bridge converter to improve the system bandwidth. Lead-lag compensators influence various disciplines, such as robotics, satellite control, automobile diagnostics, and laser frequency stabilization. These components are important building blocks in analog control systems and can also be used in digital control. A 50V output voltage and 10A output current prototype converter is fabricated in the laboratory. From the experimental results, the effectiveness of the control loop design can be verified from the gain margin and phase margin.
Wintucky, Edwin G.; Simons, Rainee N.
2014-01-01
This paper presents the design, fabrication and test results for a novel waveguide multimode directional coupler (MDC). The coupler fabricated from two dissimilar waveguides is capable of isolating the power at the second harmonic frequency from the fundamental power at the output port of a traveling-wave tube (TWT). In addition to accurate power measurements at harmonic frequencies, a potential application of the MDC is in the design of a beacon source for atmospheric propagation studies at millimeter-wave frequencies.
Bak, Claus Leth; Bak-Jensen, Birgitte; Wiechowski, Wojciech
2008-01-01
This paper demonstrates the results of implementation and verification of an already existing algorithm that allows for calculating saturation characteristics of singlephase power transformers. The algorithm was described for the first time in 1993. Now this algorithm has been implemented using the DIgSILENT Programming Language (DPL) as an external script in the harmonic domain calculations of a power system analysis tool PowerFactory [10]. The algorithm is verified by harmonic measurements ...
Amir Nagizadeh Ghoogdareh; Aref Doroudi; Mohammad Poormonfared Azimi
2013-01-01
One of the most important power quality aspects in wind farms is voltage fluctuation or flicker which should be investigated due to the nature of wind speed variations. These variations result in power and voltage fluctuations at the load bus. Moreover, the wind generation systems may be assumed as a harmonics source because of their power electronic converters. There are numerous factors that affect flicker and harmonic emission of grid-connected wind turbines during continuous operation, su...
Harmonic analysis of electric locomotive and traction power system based on wavelet singular entropy
Dun, Xiaohong
2018-05-01
With the rapid development of high-speed railway and heavy-haul transport, the locomotive and traction power system has become the main harmonic source of China's power grid. In response to this phenomenon, the system's power quality issues need timely monitoring, assessment and governance. Wavelet singular entropy is an organic combination of wavelet transform, singular value decomposition and information entropy theory, which combines the unique advantages of the three in signal processing: the time-frequency local characteristics of wavelet transform, singular value decomposition explores the basic modal characteristics of data, and information entropy quantifies the feature data. Based on the theory of singular value decomposition, the wavelet coefficient matrix after wavelet transform is decomposed into a series of singular values that can reflect the basic characteristics of the original coefficient matrix. Then the statistical properties of information entropy are used to analyze the uncertainty of the singular value set, so as to give a definite measurement of the complexity of the original signal. It can be said that wavelet entropy has a good application prospect in fault detection, classification and protection. The mat lab simulation shows that the use of wavelet singular entropy on the locomotive and traction power system harmonic analysis is effective.
Institute of Scientific and Technical Information of China (English)
无
2007-01-01
Representing earthquake ground motion as time varying ARMA model, the instantaneous spectrum can only be determined by the time varying coefficients of the corresponding ARMA model. In this paper, unscented Kalman filter is applied to estimate the time varying coefficients. The comparison between the estimation results of unscented Kalman filter and Kalman filter methods shows that unscented Kalman filter can more precisely represent the distribution of the spectral peaks in time-frequency plane than Kalman filter, and its time and frequency resolution is finer which ensures its better ability to track the local properties of earthquake ground motions and to identify the systems with nonlinearity or abruptness. Moreover, the estimation results of ARMA models with different orders indicate that the theoretical frequency resolving power ofARMA model which was usually ignored in former studies has great effect on the estimation precision of instantaneous spectrum and it should be taken as one of the key factors in order selection of ARMA model.
DEFF Research Database (Denmark)
Micallef, Alexander; Apap, Maurice; Spiteri-Staines, Cyril
2013-01-01
Parallel inverters having LCL output filters cause voltage distortions at the point of common coupling (PCC) in islanded microgrids when non-linear loads are present. A capacitive virtual impedance loop could be used to provide selective harmonic compensation in islanded microgrids, instead of in...... resistance for selective harmonic compensation in islanded microgrids. Simulation results were given to show the suitability of the proposed algorithms in reducing the voltage harmonics at the PCC.......Parallel inverters having LCL output filters cause voltage distortions at the point of common coupling (PCC) in islanded microgrids when non-linear loads are present. A capacitive virtual impedance loop could be used to provide selective harmonic compensation in islanded microgrids, instead...... of introducing additional active or passive filters into the system that could compromise the stability of the microgrid. However, the performance of these compensation loops becomes degraded when a virtual resistance is introduced with the aim to improve the overall stability of the parallel inverters...
Compensating for Tissue Changes in an Ultrasonic Power Link for Implanted Medical Devices.
Vihvelin, Hugo; Leadbetter, Jeff; Bance, Manohar; Brown, Jeremy A; Adamson, Robert B A
2016-04-01
Ultrasonic power transfer using piezoelectric devices is a promising wireless power transfer technology for biomedical implants. However, for sub-dermal implants where the separation between the transmitter and receiver is on the order of several acoustic wavelengths, the ultrasonic power transfer efficiency (PTE) is highly sensitive to the distance between the transmitter and receiver. This sensitivity can cause large swings in efficiency and presents a serious limitation on battery life and overall performance. A practical ultrasonic transcutaneous energy transfer (UTET) system design must accommodate different implant depths and unpredictable acoustic changes caused by tissue growth, hydration, ambient temperature, and movement. This paper describes a method used to compensate for acoustic separation distance by varying the transmit (Tx) frequency in a UTET system. In a benchtop UTET system we experimentally show that without compensation, power transfer efficiency can range from 9% to 25% as a 5 mm porcine tissue sample is manipulated to simulate in situ implant conditions. Using an active frequency compensation method, we show that the power transfer efficiency can be kept uniformly high, ranging from 20% to 27%. The frequency compensation strategy we propose is low-power, non-invasive, and uses only transmit-side measurements, making it suitable for active implanted medical device applications.
Aggregated wind power generation probabilistic forecasting based on particle filter
International Nuclear Information System (INIS)
Li, Pai; Guan, Xiaohong; Wu, Jiang
2015-01-01
Highlights: • A new method for probabilistic forecasting of aggregated wind power generation. • A dynamic system is established based on a numerical weather prediction model. • The new method handles the non-Gaussian and time-varying wind power uncertainties. • Particle filter is applied to forecast predictive densities of wind generation. - Abstract: Probability distribution of aggregated wind power generation in a region is one of important issues for power system daily operation. This paper presents a novel method to forecast the predictive densities of the aggregated wind power generation from several geographically distributed wind farms, considering the non-Gaussian and non-stationary characteristics in wind power uncertainties. Based on a mesoscale numerical weather prediction model, a dynamic system is established to formulate the relationship between the atmospheric and near-surface wind fields of geographically distributed wind farms. A recursively backtracking framework based on the particle filter is applied to estimate the atmospheric state with the near-surface wind power generation measurements, and to forecast the possible samples of the aggregated wind power generation. The predictive densities of the aggregated wind power generation are then estimated based on these predicted samples by a kernel density estimator. In case studies, the new method presented is tested on a 9 wind farms system in Midwestern United States. The testing results that the new method can provide competitive interval forecasts for the aggregated wind power generation with conventional statistical based models, which validates the effectiveness of the new method
The social distance theory of power.
Magee, Joe C; Smith, Pamela K
2013-05-01
We propose that asymmetric dependence between individuals (i.e., power) produces asymmetric social distance, with high-power individuals feeling more distant than low-power individuals. From this insight, we articulate predictions about how power affects (a) social comparison, (b) susceptibility to influence, (c) mental state inference and responsiveness, and (d) emotions. We then explain how high-power individuals' greater experienced social distance leads them to engage in more abstract mental representation. This mediating process of construal level generates predictions about how power affects (a) goal selection and pursuit, (b) attention to desirability and feasibility concerns, (c) subjective certainty, (d) value-behavior correspondence, (e) self-control, and (f) person perception. We also reassess the approach/inhibition theory of power, noting limitations both in what it can predict and in the evidence directly supporting its proposed mechanisms. Finally, we discuss moderators and methodological recommendations for the study of power from a social distance perspective.
Low-power adaptive filter based on RNS components
DEFF Research Database (Denmark)
Bernocchi, Gian Luca; Cardarilli, Gian Carlo; Del Re, Andrea
2007-01-01
In this paper a low-power implementation of an adaptive FIR filter is presented. The filter is designed to meet the constraints of channel equalization for fixed wireless communications that typically requires a large number of taps, but a serial updating of the filter coefficients, based...... on the least mean squares (LMS) algorithm, is allowed. Previous work showed that the use of the residue number system (RNS) for the variable FIR filter grants advantages both in area and power consumption. On the other hand, the use of a binary serial implementation of the adaptation algorithm eliminates...... the need for complex scaling circuits in RNS. The advantages in terms of area and speed of the presented filter, with respect to its two's complement counterpart, are evaluated for implementations in standard cells....
An aggregated approach to harmonic modelling of loads in power distribution networks
Energy Technology Data Exchange (ETDEWEB)
Moellerstedt, E.
1998-06-01
The use of power electronics have given possibilities for more sophisticated control of power networks. This creates new demands on power network modelling. The models must not only allow for efficient and accurate simulation, but also be suitable for analysis and control design. The Harmonic Norton Equivalent presented in this thesis addresses two problems that are central in control theory, namely model reduction and system identification. It is essential to have simple representations of large systems, and there must be a way to obtain these simple models experimentally, as detailed modelling most often is too complicated. The Harmonic Norton Equivalent has its roots in the method of harmonic balance. It is a frequency domain description of loads in electric networks and describes a linear relation between the current spectrum and the voltage spectrum. The linearization implies that aggregation of loads for model reduction is a straightforward, non-iterative procedure. The models can be obtained through analytical calculations, measurements or time domain simulations. A procedure for experimental estimation of model parameters is presented. The procedure is used to estimate the parameters of a dimmer model from measurements on a real dimmer. The obtained model shows a very good agreement with validation data 24 refs, 24 figs
Uzunoglu, B.; Hussaini, Y.
2017-12-01
Implicit Particle Filter is a sequential Monte Carlo method for data assimilation that guides the particles to the high-probability by an implicit step . It optimizes a nonlinear cost function which can be inherited from legacy assimilation routines . Dynamic state estimation for almost real-time applications in power systems are becomingly increasingly more important with integration of variable wind and solar power generation. New advanced state estimation tools that will replace the old generation state estimation in addition to having a general framework of complexities should be able to address the legacy software and able to integrate the old software in a mathematical framework while allowing the power industry need for a cautious and evolutionary change in comparison to a complete revolutionary approach while addressing nonlinearity and non-normal behaviour. This work implements implicit particle filter as a state estimation tool for the estimation of the states of a power system and presents the first implicit particle filter application study on a power system state estimation. The implicit particle filter is introduced into power systems and the simulations are presented for a three-node benchmark power system . The performance of the filter on the presented problem is analyzed and the results are presented.
Zuikafly, Siti Nur Fatin; Khalifa, Ali; Ahmad, Fauzan; Shafie, Suhaidi; Harun, SulaimanWadi
2018-06-01
The Q-switched pulse regime is demonstrated by integrating conductive graphene as passive saturable absorber producing relatively high instantaneous peak power and pulse energy. The fabricated conductive graphene is investigated using Raman spectroscopy. The single wavelength Q-switching operates at 1558.28 nm at maximum input pump power of 151.47 mW. As the pump power is increased from threshold power of 51.6 mW to 151.47 mW, the pulse train repetition rate increases proportionally from 47.94 kHz to 67.8 kHz while the pulse width is reduced from 9.58 μs to 6.02 μs. The generated stable pulse produced maximum peak power and pulse energy of 32 mW and 206 nJ, respectively. The first beat node of the measured signal-to-noise ratio is about 62 dB indicating high pulse stability.
Voting Power and Shareholder Activism
DEFF Research Database (Denmark)
Strand, Therese; Poulsen, Thomas; Thomsen, Steen
2010-01-01
The article discusses the development of a voting power theory that is applied to a unique data set on Swedish shareholder meetings. The authors hypothesize that there is a positive relationship between shareholder activism and the largest shareholder's sensitivity to greater participation by small...... shareholders. It is shown that firms' amenability to small shareholder influence results in more proposals by nomination committees that are dominated by large shareholders, but fewer proposals by other shareholders. The importance of local institutions are highlighted and a call for more research regarding...... shareholder activism in alternative institutional settings is mad...
Kalman Filter Application to Symmetrical Fault Detection during Power Swing
DEFF Research Database (Denmark)
Khodaparast, Jalal; Silva, Filipe Miguel Faria da; Khederzadeh, M.
2016-01-01
capability of Kalman Filter. The proposed index is calculated by assessing the difference between predicted and actual samples of impedance. The predicted impedance samples are obtained using Kalman filter and Taylor expansion, which is used in this paper to track the phasor precisely. Second order of Taylor...... expansion is used to decrease corrugation effect of impedance estimation and increase the reliability of proposed method. The instantaneous estimation and prediction capability of Kalman filter are two reasons for proposing utilizing Kalman filter....
DEFF Research Database (Denmark)
Liu, Yuan; Wu, Weimin; Li, Yun
2016-01-01
The capacitor-current-feedback active damping method is attractive for high-order-filter-based high power grid-tied inverter when the grid impedance varies within a wide range. In order to improve the system control bandwidth and attenuate the high order grid background harmonics by using the quasi....... In this paper, a low pass filter is proposed to be inserted in the capacitor current feedback loop op LLCL-filter based grid-tied inverter together with a digital proportional and differential compensator. The detailed theoretical analysis is given. For verification, simulations on a 2kW/220V/10kHz LLCL...
Power system static state estimation using Kalman filter algorithm
Directory of Open Access Journals (Sweden)
Saikia Anupam
2016-01-01
Full Text Available State estimation of power system is an important tool for operation, analysis and forecasting of electric power system. In this paper, a Kalman filter algorithm is presented for static estimation of power system state variables. IEEE 14 bus system is employed to check the accuracy of this method. Newton Raphson load flow study is first carried out on our test system and a set of data from the output of load flow program is taken as measurement input. Measurement inputs are simulated by adding Gaussian noise of zero mean. The results of Kalman estimation are compared with traditional Weight Least Square (WLS method and it is observed that Kalman filter algorithm is numerically more efficient than traditional WLS method. Estimation accuracy is also tested for presence of parametric error in the system. In addition, numerical stability of Kalman filter algorithm is tested by considering inclusion of zero mean errors in the initial estimates.
Comparison of dynamic compensation methods for delayed self-powered neutron detector
International Nuclear Information System (INIS)
In, Wang Kee; Kim, Joon Sung; Auh, Geun Sun; Yoon, Tae Young
1993-01-01
Dynamic compensation methods for rhodium self-powered neutron detector have been developed by Banda and Hoppe to compensate for the time delay associated with detector signals. The time delay is due to the decay of the neutron-activated rhodium and results in delayed detector response. Two digital dynamic compensation methods, were compared for step change of neutron flux in this paper. The inverse kinetics method gave slightly better response time and noise gain. However, the inverse kinetics method also showed overshooting of neutron flux for the step change. (Author)
High efficiency fourth-harmonic generation from nanosecond fiber master oscillator power amplifier
Mu, Xiaodong; Steinvurzel, Paul; Rose, Todd S.; Lotshaw, William T.; Beck, Steven M.; Clemmons, James H.
2016-03-01
We demonstrate high power, deep ultraviolet (DUV) conversion to 266 nm through frequency quadrupling of a nanosecond pulse width 1064 nm fiber master oscillator power amplifier (MOPA). The MOPA system uses an Yb-doped double-clad polarization-maintaining large mode area tapered fiber as the final gain stage to generate 0.5-mJ, 10 W, 1.7- ns single mode pulses at a repetition rate of 20 kHz with measured spectral bandwidth of 10.6 GHz (40 pm), and beam qualities of Mx 2=1.07 and My 2=1.03, respectively. Using LBO and BBO crystals for the second-harmonic generation (SHG) and fourth-harmonic generation (FHG), we have achieved 375 μJ (7.5 W) and 92.5 μJ (1.85 W) at wavelengths of 532 nm and 266 nm, respectively. To the best of our knowledge these are the highest narrowband infrared, green and UV pulse energies obtained to date from a fully spliced fiber amplifier. We also demonstrate high efficiency SHG and FHG with walk-off compensated (WOC) crystal pairs and tightly focused pump beam. An SHG efficiency of 75%, FHG efficiency of 47%, and an overall efficiency of 35% from 1064 nm to 266 nm are obtained.
The harmonics detection method based on neural network applied ...
African Journals Online (AJOL)
user
Keywords: Artificial Neural Networks (ANN), p-q theory, (SAPF), Harmonics, Total ..... Genetic algorithm-based self-learning fuzzy PI controller for shunt active filter, ... Verification of global optimality of the OFC active power filters by means of ...
Active power line conditioners design, simulation and implementation for improving power quality
Revuelta, Patricio Salmeron; Litrán, Salvador Pérez
2015-01-01
Active Power Line Conditioners: Design, Simulation and Implementation for Improving Power Quality presents a rigorous theoretical and practical approach to active power line conditioners, one of the subjects of most interest in the field of power quality. Its broad approach offers a journey that will allow power engineering professionals, researchers, and graduate students to learn more about the latest landmarks on the different APLC configurations for load active compensation. By introducing the issues and equipment needs that arise when correcting the lack of power quality in power grids
Schwarz, John H.
1995-01-01
A proposed duality between type IIB superstring theory on R^9 X S^1 and a conjectured 11D fundamental theory (``M theory'') on R^9 X T^2 is investigated. Simple heuristic reasoning leads to a consistent picture relating the various p-branes and their tensions in each theory. Identifying the M theory on R^{10} X S^1 with type IIA superstring theory on R^{10}, in a similar fashion, leads to various relations among the p-branes of the IIA theory.
Directory of Open Access Journals (Sweden)
Selami KESLER
2009-01-01
Full Text Available The power flow of the rotor circuit is controlled by different methods in induction machines used for producing high torque in applications involved great power and constant output power with constant frequency in wind turbines. The voltage with slip frequency can be applied on rotor windings to produce controlled high torque and obtain optimal power factor and speed control. In this study, firstly, the dynamic effects of the voltage applying on rotor windings through the rings in slip-ring induction machines are researched and undesirable aspects of the method are exposed with simulations supported by experiments. Afterwards, a fuzzy logic based inverter model on rotor side is proposed with a view to improving the dynamic effects, controlling high torque producing and adjusting machine speed in instantaneous forced conditions. For the simulation model of the system in which the stator side is directly connected to the grid in steady state operation, a C/C++ algorithm is developed and the results obtained for different load conditions are discussed.
Filtering for increased power for microarray data analysis
Directory of Open Access Journals (Sweden)
Hess Ann M
2009-01-01
Full Text Available Abstract Background Due to the large number of hypothesis tests performed during the process of routine analysis of microarray data, a multiple testing adjustment is certainly warranted. However, when the number of tests is very large and the proportion of differentially expressed genes is relatively low, the use of a multiple testing adjustment can result in very low power to detect those genes which are truly differentially expressed. Filtering allows for a reduction in the number of tests and a corresponding increase in power. Common filtering methods include filtering by variance, average signal or MAS detection call (for Affymetrix arrays. We study the effects of filtering in combination with the Benjamini-Hochberg method for false discovery rate control and q-value for false discovery rate estimation. Results Three case studies are used to compare three different filtering methods in combination with the two false discovery rate methods and three different preprocessing methods. For the case studies considered, filtering by detection call and variance (on the original scale consistently led to an increase in the number of differentially expressed genes identified. On the other hand, filtering by variance on the log2 scale had a detrimental effect when paired with MAS5 or PLIER preprocessing methods, even when the testing was done on the log2 scale. A simulation study was done to further examine the effect of filtering by variance. We find that filtering by variance leads to higher power, often with a decrease in false discovery rate, when paired with either of the false discovery rate methods considered. This holds regardless of the proportion of genes which are differentially expressed or whether we assume dependence or independence among genes. Conclusion The case studies show that both detection call and variance filtering are viable methods of filtering which can increase the number of differentially expressed genes identified. The
International Nuclear Information System (INIS)
Wang Jisuo; Sun Changyong; He Jinyu
1996-01-01
The eigenstates of the higher power of the annihilation operator a qs k (k≥3) of the two-parameter deformed harmonic oscillator are constructed. Their completeness is demonstrated in terms of the qs-integration
DEFF Research Database (Denmark)
Glasdam, Jakob Bærholm; Bak, Claus Leth; Kocewiak, Lukasz Hubert
2018-01-01
system with 201 voltage levels, without loss of accuracy compared to conventional modelling of the converter. Harmonic stability is a core concern for both existing and future offshore wind power plants (OWPPs). A harmonic stability study will be undertaken with focus on the number of wind turbine...
A Unified Voltage Harmonic Control Strategy for Coordinated Compensation with VCM and CCM Converters
DEFF Research Database (Denmark)
Zhao, Xin; Meng, Lexuan; Xie, Chuan
2018-01-01
-controlled mode (VCM) and current-controlled mode (CCM), need to cooperatively provide the compensation function. Aiming at this objective, this paper proposes a unified voltage harmonic mitigation strategy for VCM and CCM converters with high harmonic current sharing accuracy. Another advantage of the proposal......Harmonics have been considered as one of the major issues in modern power grids. Considering the high penetration level of power electronic converter interfaced distributed generators (DGs), it is of interest to provide ancillary services through DG interfacing converters, such as harmonic...... compensation. In case of that, multiple DG interfacing converters are utilized to compensate harmonics, and the compensation effort should be properly shared among these converters. However, it is rarely considered in existing literatures that converters operating in different modes, such as voltage...
Hybrid VAR compensator with improved efficiency
Directory of Open Access Journals (Sweden)
V. V. Burlaka
2015-03-01
Full Text Available In modern electrical networks thyristor-switched capacitors (TSC are most used devices for VAR compensation. These devices don’t contain rotating parts and mechanical contacts, provide a stepwise control of reactive power and no generation of harmonics to the network. However, with the help of TSC it’s not possible to ensure smooth control of reactive power and capacitor banks (CB are exposed to the negative impact of higher harmonic components of the network voltage. Hybrid VAR compensator don’t have such drawbacks. It consists of active filter (AF and capacitor bank with discrete regulation. The main drawback of such systems is the necessity of accessing all six terminals of CB, while most of them are manufactured with three terminals, internally delta-connected. In the article, the topology and control system of hybrid VAR compensator free from beforementioned drawback, is proposed. The control system provides operating modes of overcompensation or undercompensation reactive power. VAR distribution regulator performs redistribution of reactive power between active filter and capacitor banks with the condition to minimize active filter’s power. Scheme of the hybrid VAR compensator, which includes a three-phase three-terminal delta-connected capacitor banks, is shown. Proposed approach allows to provide smooth control of reactive power, isolate the capacitor bank from harmonic currents and use a more effective low-voltage power components
Improving the performance of the power supply of the MGC-20 cyclotron harmonic coils
International Nuclear Information System (INIS)
Hagras, A.A.M
2008-01-01
Correction of lower harmonics of the MGC-20 cyclotron magnetic field is of great importance for its operation. Actually, stability of the acceleration process, attainment of the final energy of the accelerated beam and efficiency of the beam extraction system depend on the lower harmonics control. Error in the magnetic field lower harmonics can reduce the efficiency of the beam extraction resulting in complete disappearance of the extracted beam of the cyclotron. For control of the cyclotron MGC-20 magnetic field lower harmonics, the so called inner and outer harmonic coils are provided.These harmonic coils must be fed by a very high accuracy current source power supply. This power supply must be equipped with a high resolution measurement and control scheme to achieve the imposed requirements of adjustment of the first harmonic magnetic field.Harmonic coils are supplied with conventional SCR controlled converters with analog control strategy. Frequent interruption of operation and difficulties in the adjustment of harmonic coil current lead to economical and research - time losses.This research project aims to replace this conventional system with a more effective, accurate and less complicated digital control system based on Motorola DSP56F807 and high switching frequency power circuit. Actually all the bulky modules including the analog integrator, the signal monitoring and protection, the pulse phase modulator and the comparator are all replaced by a single module circuit.
Standard filter approximations for low power Continuous Wavelet Transforms.
Casson, Alexander J; Rodriguez-Villegas, Esther
2010-01-01
Analogue domain implementations of the Continuous Wavelet Transform (CWT) have proved popular in recent years as they can be implemented at very low power consumption levels. This is essential for use in wearable, long term physiological monitoring systems. Present analogue CWT implementations rely on taking mathematical a approximation of the wanted mother wavelet function to give a filter transfer function that is suitable for circuit implementation. This paper investigates the use of standard filter approximations (Butterworth, Chebyshev, Bessel) as an alternative wavelet approximation technique. This extends the number of approximation techniques available for generating analogue CWT filters. An example ECG analysis shows that signal information can be successfully extracted using these CWT approximations.
Evaluation of Harmonic Content from a Tap Transformer Based Grid Connection System for Wind Power
Directory of Open Access Journals (Sweden)
S. Apelfröjd
2013-01-01
Full Text Available Simulations done in MATLAB/Simulink together with experiments conducted at the Ångströms laboratory are used to evaluate and discuss the total harmonic distortion (THD and total demand distortion (TDD of a tap transformer based grid connection system. The grid connection topology can be used with different turbine and generator topologies and is here applied on a vertical axis wind turbine (VAWT with a permanent magnet synchronous generator (PMSG and its operational scheme. The full variable-speed wind conversion system consists of a diode rectifier, DC link, IGBT inverter, LCL-filter, and tap transformer. The full variable-speed operation is enabled by the use of the different step-up ratios of the tap transformer. In the laboratory study, a full experimental setup of the system was used, a clone of the on-site PMSG driven by a motor was used, and the grid was replaced with a resistive load. With a resistive load, grid harmonics and possible unbalances are removed. The results show a TDD and THD below 5% for the full operating range and harmonic values within the limits set up by IEEE-519. Furthermore, a change in tap, going to a lower step-up ratio, results in a reduction in both THD and TDD for the same output power.
Directory of Open Access Journals (Sweden)
S. V. Bordusov
2010-01-01
Full Text Available The paper presents results of investigations pertaining to the possibility of regulating instantaneous power output in a magnetron of M-105 (M-112-type by changing the capacity value of a capacitor in structure diagram for doubling voltage of high-voltage power supply on the basis of a step-up transformer operating in the saturation regime.
Instantaneous response spectrum in seismic testing of nuclear power plant equipment
International Nuclear Information System (INIS)
Morrone, A.
1977-01-01
Seismic response spectra, as used in seismic analyses, give the maximum responses of single degree of freedom oscillators without consideration of the different time in the seismic time history at which each of the maximum responses occur. For response spectrum seismic analysis, the use of time-independent maximum responses is appropriate. The time dependece is considered in a statistical manner, for multi-degree of freedom systems, usually by combining the modal effects by the square root of the sum of the squares. For seismic testing of electrical equipment. IEEE Std. 344-1975 makes use of the response spectrum to define the input motion of the shake table. One of the basic requirements is that the test response spectrum (TRS) that is, the response spectrum produced by the shake table motion, should envelop the required response spectrum (RRS) calculated from the building analysis at the support point of the equipment being tested. This paper presents the concept of instantaneous response spectrum (IRS) as the response of single degree of freedom oscillators at a particular time. It demonstrates that a shake table random motion whose standard TRS envelops the RRS does not necessarily satisfy the enveloping requirement instantaneously. (Auth.)
Designing Asynchronous Circuits for Low Power: An IFIR Filter
DEFF Research Database (Denmark)
Nielsen, Lars Skovby; Sparsø, Jens
1999-01-01
This paper addresses the design of asynchronous circuits for low power through an example: a filter bank for a digital hearing aid. The asynchronous design re-implements an existing synchronous circuit which is used in a commercial product. For comparison, both designs have been fabricated...
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
For the efficiency and simplicity of electric systems, the dc power electronic systems are widely used in a variety of applications such as electric vehicles, ships, aircraft and also in homes. In these systems, there could be a number of dynamic interactions and frequency coupling between network...... with different switching frequency or harmonics from ac-dc converters makes that harmonics and frequency coupling are both problems of ac system and challenges of dc system. This paper presents a modeling and simulation method for a large dc power electronic system by using Harmonic State Space (HSS) modeling...
Settlement of reactive power compensation in the light of white certificates
Zajkowski, Konrad
2017-10-01
The article discusses the problem of the determination of savings on active energy as a result of a reactive power compensation. Statutory guidance on the required energy audit to obtain white certificates in the European Union was followed. The analysis was made on the basis of the Polish Law. The paper presents a detailed analytical method and an estimation method taking into account the impact on the line, the transformer and the generator. According to the relevant guidelines in the European Union, the reduction of CO2 emissions by calculating the saving of active power should be determined. The detailed method and an estimation method proposed for the determination of savings on active energy as a result of the reactive power compensation carried out possess some errors and inconvenience. The detailed method requires knowledge of the network topology and a determination of reactive power Q at each point of the network. The estimation method of analysis is easy in execution, especially if the consumer of energy is the main or the most significant purchaser of electricity in the network. Unfortunately, this latter method can be used only for activities that do not require high computational accuracy. The results obtained by this method are approximate values that can be used for the calculation of economic indicators. The estimation method is suitable for determining the number of white certificates when a power audit concerns a recipient of electricity, the structure of which is a large number of divisions scattered at many different locations in the power system.
Power Load Prediction Based on Fractal Theory
Jian-Kai, Liang; Cattani, Carlo; Wan-Qing, Song
2015-01-01
The basic theories of load forecasting on the power system are summarized. Fractal theory, which is a new algorithm applied to load forecasting, is introduced. Based on the fractal dimension and fractal interpolation function theories, the correlation algorithms are applied to the model of short-term load forecasting. According to the process of load forecasting, the steps of every process are designed, including load data preprocessing, similar day selecting, short-term load forecasting, and...
Chen, Chiun-Fan; Bikson, Marom; Chou, Li-Wei; Shan, Chunlei; Khadka, Niranjan; Chen, Wen-Shiang; Fregni, Felipe
2017-03-03
It is well established that electrical-stimulation frequency is crucial to determining the scale of induced neuromodulation, particularly when attempting to modulate corticospinal excitability. However, the modulatory effects of stimulation frequency are not only determined by its absolute value but also by other parameters such as power at harmonics. The stimulus pulse shape further influences parameters such as excitation threshold and fiber selectivity. The explicit role of the power in these harmonics in determining the outcome of stimulation has not previously been analyzed. In this study, we adopted an animal model of peripheral electrical stimulation that includes an amplitude-adapted pulse train which induces force enhancements with a corticospinal contribution. We report that the electrical-stimulation-induced force enhancements were correlated with the amplitude of stimulation power harmonics during the amplitude-adapted pulse train. In an exploratory analysis, different levels of correlation were observed between force enhancement and power harmonics of 20-80 Hz (r = 0.4247, p = 0.0243), 100-180 Hz (r = 0.5894, p = 0.0001), 200-280 Hz (r = 0.7002, p harmonics. This is a pilot, but important first demonstration that power at high order harmonics in the frequency spectrum of electrical stimulation pulses may contribute to neuromodulation, thus warrant explicit attention in therapy design and analysis.
To the issue of increasing efficiency of VAR compensation
Directory of Open Access Journals (Sweden)
Світлана Костянтинівна Поднебенна
2015-11-01
Full Text Available This article describes the features of VAR compensation of variable loads. One of the most common non-symmetric non-linear power consumers are welding power sources. Time and duration of the work of these sources vary randomly. To compensate the consumption of reactive power on the basis of consumption data from the three-phase electricity meters is inefficient. Compensation devices power should be calculated taking into account the asymmetrical consumption/generation of reactive power per phase and changing consumption patterns. Thyristor-controlled reactor, thyristor-switched capacitors, hybrid VAR compensators, active compensators (STATCOMs, «dynamic capacitors» can be used as the VAR compensation devices. Thyristor-controlled reactors can provide smooth regulation of reactive power, but they have high weight and size parameters and are additional sources of higher harmonics. Thyristor-switched capacitors provide stepwise adjustment of reactive power and are subject to the current higher harmonics. Hybrid VAR compensators make it possible to isolate capacitors from the higher harmonics and ensure smooth regulation, which is achieved by active filter introduction to the reactive power compensation devices based on thyristor-switched capacitors. However, this increases the cost of a compensator and complicates its control system. STATCOMs provide smooth regulation of reactive power, but they are too expensive.Perspective direction in the development of effective VAR compensation devices is «dynamic capacitor». As a result of a feasibility study the prospects for further research of electrical grids power efficiency through the development of effective devices for VAR compensation have been established
Testing Rastall's theory using matter power spectrum
International Nuclear Information System (INIS)
Batista, C.E.M.; Fabris, J.C.; Daouda, M.H.
2010-01-01
Rastall's theory is a modification of the General Relativity theory leading to a different expression for the conservation law in the matter sector compared with the usual one. It has been argued recently that such a theory may have applications to the dark energy problem, since a pressureless fluid may lead to an accelerated universe. In the present work we confront Rastall's theory with the power spectrum data. The results indicate a configuration that essentially reduces Rastall's theory to General Relativity, unless the non-usual conservation law refers to a scalar field, situation where other configurations are eventually possible.
On-line reconstruction of in-core power distribution by harmonics expansion method
International Nuclear Information System (INIS)
Wang Changhui; Wu Hongchun; Cao Liangzhi; Yang Ping
2011-01-01
Highlights: → A harmonics expansion method for the on-line in-core power reconstruction is proposed. → A harmonics data library is pre-generated off-line and a code named COMS is developed. → Numerical results show that the maximum relative error of the reconstruction is less than 5.5%. → This method has a high computational speed compared to traditional methods. - Abstract: Fixed in-core detectors are most suitable in real-time response to in-core power distributions in pressurized water reactors (PWRs). In this paper, a harmonics expansion method is used to reconstruct the in-core power distribution of a PWR on-line. In this method, the in-core power distribution is expanded by the harmonics of one reference case. The expansion coefficients are calculated using signals provided by fixed in-core detectors. To conserve computing time and improve reconstruction precision, a harmonics data library containing the harmonics of different reference cases is constructed. Upon reconstruction of the in-core power distribution on-line, the two closest reference cases are searched from the harmonics data library to produce expanded harmonics by interpolation. The Unit 1 reactor of DayaBay Nuclear Power Plant (DayaBay NPP) in China is considered for verification. The maximum relative error between the measurement and reconstruction results is less than 5.5%, and the computing time is about 0.53 s for a single reconstruction, indicating that this method is suitable for the on-line monitoring of PWRs.
Multilayer mirrors as power filters in insertion device beamlines
International Nuclear Information System (INIS)
Kortright, J.B.; DiGennaro, R.S.
1988-08-01
The power-filtering capabilities of multilayer band-pass x-ray mirrors relative to total reflection low-pass mirrors is presented. Results are based on calculations assuming proposed wiggler sources on the upcoming generation of low energy (1.5 GeV) and high energy (7.0 GeV) synchrotron radiation sources. Results show that multilayers out-perform total reflection mirrors in terms of reduction in reflected power by roughly an order of magnitude, with relatively small increases in total absorbed power and power density over total reflection mirrors, and with comparable reflected flux values. Various aspects of this potential application of multilayer x-ray optics are discussed. 13 refs., 3 figs., 1 tab
The power of perturbation theory
Energy Technology Data Exchange (ETDEWEB)
Serone, Marco [SISSA International School for Advanced Studies and INFN Trieste, Via Bonomea 265, 34136, Trieste (Italy); Abdus Salam International Centre for Theoretical Physics, Strada Costiera 11, 34151, Trieste (Italy); Spada, Gabriele [SISSA International School for Advanced Studies and INFN Trieste, Via Bonomea 265, 34136, Trieste (Italy); Villadoro, Giovanni [Abdus Salam International Centre for Theoretical Physics, Strada Costiera 11, 34151, Trieste (Italy)
2017-05-10
We study quantum mechanical systems with a discrete spectrum. We show that the asymptotic series associated to certain paths of steepest-descent (Lefschetz thimbles) are Borel resummable to the full result. Using a geometrical approach based on the Picard-Lefschetz theory we characterize the conditions under which perturbative expansions lead to exact results. Even when such conditions are not met, we explain how to define a different perturbative expansion that reproduces the full answer without the need of transseries, i.e. non-perturbative effects, such as real (or complex) instantons. Applications to several quantum mechanical systems are presented.
Concept for power scaling second harmonic generation using a cascade of nonlinear crystals
DEFF Research Database (Denmark)
Hansen, Anders Kragh; Tawfieq, Mahmoud; Jensen, Ole Bjarlin
2015-01-01
for efficient power scaling of single-pass SHG beyond such limits using a cascade of nonlinear crystals, in which the first crystal is chosen for high nonlinear efficiency and the subsequent crystal(s) are chosen for power handling ability. Using this highly efficient singlepass concept, we generate 3.7 W...... successfully combines the high efficiency of the first stage with the good power handling properties of the subsequent stages. The concept is generally applicable and can be expanded with more stages to obtain even higher efficiency, and extends also to other combinations of nonlinear media suitable for other......Within the field of high-power second harmonic generation (SHG), power scaling is often hindered by adverse crystal effects such as thermal dephasing arising from the second harmonic (SH) light, which imposes limits on the power that can be generated in many crystals. Here we demonstrate a concept...
A Reduced Switch Voltage Stress Class E Power Amplifier Using Harmonic Control Network
Ali Reza Zirak; Sobhan Roshani
2016-01-01
In this paper, a harmonic control network (HCN) is presented to reduce the voltage stress (maximum MOSFET voltage) of the class E power amplifier (PA). Effects of the HCN on the amplifier specifications are investigated. The results show that the proposed HCN affects several specifications of the amplifier, such as drain voltage, switch current, output power capability (Cp factor), and drain impedance. The output power capability of the presented amplifier is also improved, compared with the ...
Application of VSC-HVDC with Shunt Connected SMES for Compensation of Power Fluctuation
Linn, Zarchi; Kakigano, Hiroaki; Miura, Yushi; Ise, Toshifumi
This paper describes the application of VSC-HVDC (High Voltage DC Transmission using Voltage Source Converter) with shunt connected SMES (Superconducting Magnetic Energy Storage) for compensation of power fluctuation caused by fluctuating power source such as photovoltaics and wind turbines. The objectives of this proposed system is to smooth out fluctuating power in one terminal side of HVDC in order to avoid causing power system instability and frequency deviation by absorbing or providing power according to the system requirement while another terminal side power is fluctuated. The shunt connected SMES charges and discharges the energy to and from the dc side and it compensates required power of fluctuation to obtain constant power flow in one terminal side of VSC-HVDC system. This system configuration has ability for power system stabilization in the case of power fluctuation from natural energy source. PSCAD/EMTDC simulation is used to evaluate the performance of applied system configuration and control method.
COGNITIONS AND BEHAVIOR IN A HIERARCHY - MULDERS POWER THEORY REVISITED
WILKE, HAM
1992-01-01
In this study, Mulder's power theory consisting of the power distance reduction tendency (PDR) of less powerful group members towards more powerful others, and the power distance enlargement tendency (PDE) of more powerful group members towards less powerful others, is investigated. In particular,
Power control of water reactors using nitrogen 16 activity measurements
International Nuclear Information System (INIS)
Gariod, R.; Merchie, F.; O'byrne, G.
1964-01-01
At the Grenoble Nuclear Research Centre, the open-core swimming pool reactors Melusine (2 MW) and Siloe (15 MW) are controlled at a constant overall power using nitrogen-16 channels. The conventional linear control channels react instantaneously to the rapid power fluctuations, this being necessary for the safety of the reactors, but their power indications are erroneous since they are affected by local deformations of the thermal flux caused by the compensation movements of the control rods. The nitrogen-16 channels on the other hand give an indication of the overall power proportional to the mean fission flux and independent of the rod movements, but their response time is 15 seconds, A constant overall power control is thus possible by a slow correction of the reference signal given by the automatic control governed by thu linear channels by means of a correction term given by the 'N-16' channels: This is done automatically in Melusine and manually in Siloe. (authors) [fr
Settlement of reactive power compensation in the light of white certificates
Directory of Open Access Journals (Sweden)
Zajkowski Konrad
2017-01-01
The detailed method and an estimation method proposed for the determination of savings on active energy as a result of the reactive power compensation carried out possess some errors and inconvenience. The detailed method requires knowledge of the network topology and a determination of reactive power Q at each point of the network. The estimation method of analysis is easy in execution, especially if the consumer of energy is the main or the most significant purchaser of electricity in the network. Unfortunately, this latter method can be used only for activities that do not require high computational accuracy. The results obtained by this method are approximate values that can be used for the calculation of economic indicators. The estimation method is suitable for determining the number of white certificates when a power audit concerns a recipient of electricity, the structure of which is a large number of divisions scattered at many different locations in the power system.
SPHERICAL HARMONIC ANALYSES OF INTENSITY MAPPING POWER SPECTRA
Energy Technology Data Exchange (ETDEWEB)
Liu, Adrian; Zhang, Yunfan; Parsons, Aaron R., E-mail: acliu@berkeley.edu [Department of Astronomy and Radio Astronomy Laboratory, University of California Berkeley, Berkeley, CA 94720 (United States)
2016-12-20
Intensity mapping is a promising technique for surveying the large-scale structure of our universe from z = 0 to z ∼ 150, using the brightness temperature field of spectral lines to directly observe previously unexplored portions of our cosmic timeline. Examples of targeted lines include the 21 cm hyperfine transition of neutral hydrogen, rotational lines of carbon monoxide, and fine-structure lines of singly ionized carbon. Recent efforts have focused on detections of the power spectrum of spatial fluctuations, but have been hindered by systematics such as foreground contamination. This has motivated the decomposition of data into Fourier modes perpendicular and parallel to the line of sight, which has been shown to be a particularly powerful way to diagnose systematics. However, such a method is well-defined only in the limit of a narrow-field, flat-sky approximation. This limits the sensitivity of intensity mapping experiments, as it means that wide surveys must be separately analyzed as a patchwork of smaller fields. In this paper, we develop a framework for analyzing intensity mapping data in a spherical Fourier–Bessel basis, which incorporates curved sky effects without difficulty. We use our framework to generalize a number of techniques in intensity mapping data analysis from the flat sky to the curved sky. These include visibility-based estimators for the power spectrum, treatments of interloper lines, and the “foreground wedge” signature of spectrally smooth foregrounds.
Game theory and power theory : a critical comparison
Balzer, Wolfgang
1992-01-01
Social actions can be formulated in the frame of game theory or in a frame using, and foccussing on, the notion of power. The two frames are described and clarified. The comparison of theories from these two branches are evaluated from the point of theory of science.
Dynamic Reactive Power Compensation of Large Scale Wind Integrated Power System
DEFF Research Database (Denmark)
Rather, Zakir Hussain; Chen, Zhe; Thøgersen, Paul
2015-01-01
wind turbines especially wind farms with additional grid support functionalities like dynamic support (e,g dynamic reactive power support etc.) and ii) refurbishment of existing conventional central power plants to synchronous condensers could be one of the efficient, reliable and cost effective option......Due to progressive displacement of conventional power plants by wind turbines, dynamic security of large scale wind integrated power systems gets significantly compromised. In this paper we first highlight the importance of dynamic reactive power support/voltage security in large scale wind...... integrated power systems with least presence of conventional power plants. Then we propose a mixed integer dynamic optimization based method for optimal dynamic reactive power allocation in large scale wind integrated power systems. One of the important aspects of the proposed methodology is that unlike...
Power line harmonic radiation observed by the DEMETER spacecraft at 50/60Hz and low harmonics
Czech Academy of Sciences Publication Activity Database
Němec, F.; Parrot, M.; Santolík, Ondřej
2015-01-01
Roč. 120, č. 10 (2015), s. 8954-8967 ISSN 2169-9380 R&D Projects: GA ČR(CZ) GA14-31899S; GA MŠk LH12231 Institutional support: RVO:68378289 Keywords : PLHR * power line harmonic radiation * DEMETER Subject RIV: BL - Plasma and Gas Discharge Physics Impact factor: 3.318, year: 2015 http://onlinelibrary.wiley.com/doi/10.1002/2015JA021682/full
International Nuclear Information System (INIS)
Sill, C.W.; Scarpellino, C.D.; Tkachyk, J.W.; Grey, A.E.; Frank, C.W.
1985-05-01
Laboratory analysis of activated carbon is required by nuclear power plant technical specifications for use in Engineered Safety Feature (ESF) ventilation systems to determine the capability of those systems to remove radioiodines from air during normal operation and following a design basis accident (DBA). The lask of agreement of laboratory results from a recent round robin raised concerns regarding the adequacy of the analyses, using the ASTM D3803-79 standard, to assure compliance with plant technical specifications. EG and G Idaho was contracted by the NRC to conduct a program to provide the bases for resolving these concerns. This EG and G report serves as an interim Technical Evaluation Report (TER) of the program and presents reviews of the ASTM D3803-79 standard and the commercial testing laboratories. Results of EG and G laboratory studies and the NRC/EG and G Interlaboratory Comparison are presented with conclusions and recommendations concerning changes required to improve the standard and its application. Possible revisions to plant technical specifications required to reflect the true capability of activated carbon to remove radioiodines are also presented
Analytical Design of Passive LCL Filter for Three-phase Two-level Power Factor Correction Rectifiers
DEFF Research Database (Denmark)
Kouchaki, Alireza; Nymand, Morten
2017-01-01
This paper proposes a comprehensive analytical LCL filter design method for three-phase two-level power factor correction rectifiers (PFCs). The high frequency converter current ripple generates the high frequency current harmonics that need to be attenuated with respect to the grid standards...
Enhanced power quality based single phase photovoltaic distributed generation system
Panda, Aurobinda; Pathak, M. K.; Srivastava, S. P.
2016-08-01
This article presents a novel control strategy for a 1-ϕ 2-level grid-tie photovoltaic (PV) inverter to enhance the power quality (PQ) of a PV distributed generation (PVDG) system. The objective is to obtain the maximum benefits from the grid-tie PV inverter by introducing current harmonics as well as reactive power compensation schemes in its control strategy, thereby controlling the PV inverter to achieve multiple functions in the PVDG system such as: (1) active power flow control between the PV inverter and the grid, (2) reactive power compensation, and (3) grid current harmonics compensation. A PQ enhancement controller (PQEC) has been designed to achieve the aforementioned objectives. The issue of underutilisation of the PV inverter in nighttime has also been addressed in this article and for the optimal use of the system; the PV inverter is used as a shunt active power filter in nighttime. A prototype model of the proposed system is developed in the laboratory, to validate the effectiveness of the control scheme, and is tested with the help of the dSPACE DS1104 platform.
Adaptive Harmonic Compensation in Residential Distribution Grid by Roof-Top PV Systems
DEFF Research Database (Denmark)
Zangeneh Bighash, Esmaeil; Sadeghzadeh, Seyed Mohammad; Ebrahimzadeh, Esmaeil
2018-01-01
grid- connected roof-top PV inverters in residential distribution grid can be an opportunity to engage these systems in the power quality issues as custom power devices. By implementing a proper control for roof-top PV inverters, these systems may in addition to inject the fundamental current......, additionally act like a virtual harmonic resistance and dedicate their additional current capacity to compensate the harmonics of residential distribution grid. In this paper, each roof-top PV system is a grid harmonic supervisor, where it continually measures the PCC voltage harmonics by Sliding Discrete...
Evaluation of the Harmonic Impedance of Frydlant (Line 53 Power Network
Directory of Open Access Journals (Sweden)
Shehab Abdulwadood Ali
2013-01-01
Full Text Available The harmonic impedance of the power system is an important quantity, which describes the behaviour of the power system with the existence of different frequencies beside the fundamental. The harmonic study belongs to the most difficult part of the electrical measurements and calculations even by using computer software. The main problem accompanying the calculating methods is to obtain the exact data of the electrical network parameters or to know the exact operational status of the system. In this paper the harmonic impedance of Frydlant (line 53, 22~kV in Czech Republic power network was calculated by using a very specialized software and suitable for solving such calculations called "NetCalc. version 3.0" [1].
Reactive Power Compensation Using an Energy Management System
2014-09-01
compiled to VHDL code using Xilinx System Generator software [12], which is used by the FPGA to command the EMS. The FPGA development board is the middle...controller was implemented in the lab to correct iems because the EMS hardware currently does not have a sensor on the source current. Adding a...shown in Figure 13 as φsource changes over time. 20 The function of the power factor correction diagram shown in Figure 14 is to implement the power
Precise Model Analysis for 3-phase High Power Converter using the Harmonic State Space Modeling
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Blaabjerg, Frede
2015-01-01
This paper presents about the generalized multi-frequency modeling and analysis methodology, which can be used in control loop design and stability analysis. In terms of the switching frequency of high power converter, there can be harmonics interruption if the voltage source converter has a low...... switching frequency ratio or multi-sampling frequency. The range of the control bandwidth can include the switching component. Thus, the systems become unstable. This paper applies the Harmonic State Space (HSS) Modeling method in order to find out the transfer function for each harmonics terms...
Non-Characteristic Harmonics Analysis of the ITER Pulsed Power Supply
International Nuclear Information System (INIS)
Yang Wei; Xu Liuwei; Fu Peng; Lu Huawei; Sheng Zhicai
2009-01-01
The ITER pulsed power supply system will be operated in non-ideal conditions including an asymmetric firing angle, an unbalanced AC supply and an unbalanced AC side impedance of the transformer. In this study the switching functions approach is used to calculate non-characteristic harmonics in ITER, possibly caused by an AC-DC convertor in non-ideal conditions. A PSCAD simulation model is set up to study the non-characteristic harmonics in those non-ideal conditions. It is found that the non-characteristic harmonic does appear and the simulation result is in accordance with the calculating strategy. (fusion engineering)
Site selection of active damper for stabilizing power electronics based power distribution system
DEFF Research Database (Denmark)
Yoon, Changwoo; Wang, Xiongfei; Bak, Claus Leth
2015-01-01
electronics based power device, which provides an adjustable damping capability to the power system where the voltage harmonic instability is measured. It can stabilize by adjusting the equivalent node impedance with its plug and play feature. This feature gives many degrees of freedom of its installation......Stability in the nowadays distribution power system is endangered by interaction problems that may arise from newly added power-electronics based power devices. Recently, a new concept to deal with this higher frequency instability, the active damper, has been proposed. The active damper is a power...... point when the system has many nodes. Therefore, this paper addresses the proper placement of an active damper in an unstable small-scale power distribution system. A time-domain model of the Cigre benchmark low-vltage network is used as a test field. The result shows the active damper location...
Analysis of losses within SMES system for compensating output fluctuation of wind power farm
Energy Technology Data Exchange (ETDEWEB)
Park, S. I.; Kim, J. H.; Le, T. D.; Lee, D. H.; Kim, H. M. [Jeju National University, Jeju (Korea, Republic of); Yoon, Y. S. [Dept. of Electrical Engineering, Shin Ansan University, Ansan (Korea, Republic of); Yoon, K. Y. [Dept. of lectrical and Electronic Engineering, Yonsei University, Seoul (Korea, Republic of)
2014-12-15
Output fluctuation which is generated in wind power farm can hinder stability of total power system. The electric energy storage (EES) reduces unstable output, and superconducting magnetic energy storage (SMES) of various EESs has the proper performance for output compensation of wind power farm since it charges and discharges large scale power quickly with high efficiency. However, because of the change of current within SMES, the electromagnetic losses occur in the process of output compensation. In this paper, the thermal effect of the losses that occur in SMES system while compensating in wind power farm is analyzed. The output analysis of wind power farm is processed by numerical analysis, and the losses of SMES system is analyzed by 3D finite element analysis (FEA) simulation tool.
Analysis of losses within SMES system for compensating output fluctuation of wind power farm
International Nuclear Information System (INIS)
Park, S. I.; Kim, J. H.; Le, T. D.; Lee, D. H.; Kim, H. M.; Yoon, Y. S.; Yoon, K. Y.
2014-01-01
Output fluctuation which is generated in wind power farm can hinder stability of total power system. The electric energy storage (EES) reduces unstable output, and superconducting magnetic energy storage (SMES) of various EESs has the proper performance for output compensation of wind power farm since it charges and discharges large scale power quickly with high efficiency. However, because of the change of current within SMES, the electromagnetic losses occur in the process of output compensation. In this paper, the thermal effect of the losses that occur in SMES system while compensating in wind power farm is analyzed. The output analysis of wind power farm is processed by numerical analysis, and the losses of SMES system is analyzed by 3D finite element analysis (FEA) simulation tool.
Directory of Open Access Journals (Sweden)
Amir Nagizadeh Ghoogdareh
2013-01-01
Full Text Available One of the most important power quality aspects in wind farms is voltage fluctuation or flicker which should be investigated due to the nature of wind speed variations. These variations result in power and voltage fluctuations at the load bus. Moreover, the wind generation systems may be assumed as a harmonics source because of their power electronic converters. There are numerous factors that affect flicker and harmonic emission of grid-connected wind turbines during continuous operation, such as wind characteristics (e.g. mean wind speed, turbulence intensity, type of generator and grid conditions (e.g. short circuit capacity, grid impedance angle. In this paper, an IEC based flickermeter is first modeled and then a variable speed wind turbine has been simulated by Matlab/Simulink software. The flicker and harmonics emissions of wind turbines equipped with DFIG during continuous operation and using output reactive control are investigated. The simulation results show that control of wind turbine output reactive power is an effective means for flicker mitigation during continuous operation. However, there should be a compromise between flicker reduction and harmonics level increase to enhance the whole power quality of wind turbine.
Directory of Open Access Journals (Sweden)
Ahmad Ghasemloonia
2011-01-01
Full Text Available The role of gears in industry for speed and torque variation purposes is obvious. The gearbox diagnostic methods have been improved quickly in recent years. In this paper, two of the newest methods, the resonance demodulation technique (R.D, and the instantaneous power spectrum technique (IPS are applied to gearbox vibration signals and their capabilities in fault detection are compared. Yet, the important role of time averaging should not be dispensed with, as it is the primary step for both techniques. In the present study, the mathematical method of these techniques, according to the mathematical vibration model of gears, is introduced, these techniques are applied to the test rig data, and finally the results of both methods are compared. The results indicate that in each method, the location of fault can be estimated and it is located in the same angular position in both methods. The IPS method is applicable to severe faults, whereas the resonance demodulation technique is a simple tool to recognize the fault at each severity and at the early stages of fault generation.
Harmonic filter design consideration for a tire-rubber factory
Energy Technology Data Exchange (ETDEWEB)
Zebardast, A. [Azad Univ., Tehran (Iran, Islamic Republic of). Abhar Branch]|[Sharif Univ., Tehran (Iran, Islamic Republic of); Mokhtari, H. [Azad Univ., Tehran (Iran, Islamic Republic of)
2005-07-01
Nonlinear loads and arc furnace loads are the main sources of harmonic currents in power distribution systems. Harmonic currents can cause reductions in system efficiency, and shorten the lifespan of transformers and capacitor banks. This paper provided details of a filter designed to attenuate harmonic currents at a tire company in Iran. The tire company was supplied by 3 distribution transformers and an emergency transformer. Main supply was through a 132 kV/20 kV transformer, which was connected to 2 A and B stations. The AC/DC drivers generated harmonics. Harmonic measurements were performed to determine the type and size of the required filters. A summary of site harmonic measurements was provided. A passive filter was placed at a medium voltage location. A sensitivity analysis was then performed in order to assess loading effects on filter performance. The analysis was performed on all possible configurations in the plant, including load change, capacitor bank step change, and transformer energization. Resonance conditions were also examined. Results showed that attention must be paid to the filter component rating in addition to potential resonant conditions. It was concluded that resonant conditions alter when system operating conditions change. 5 refs., 7 figs.
A Review of Passive Power Filters for Three-Phase Grid-Connected Voltage-Source Converters
DEFF Research Database (Denmark)
Beres, Remus Narcis; Wang, Xiongfei; Liserre, Marco
2016-01-01
and source impedances. Furthermore, the stabilizing effect is more difficult to be guaranteed for cost-optimized filters, which are characterized by low inductance and high capacitance passive components. In this paper, several passive filter topologies used to interface voltage source converters......In order to reduce size and cost, high-order passive filters are generally preferred in power converters to cancel out high frequency harmonics caused by pulse width modulation. However, the filter resonance peaks may require the use of passive dampers to stabilize the interactions between the load...
1989-03-01
Jon s (n)e-"’ z(121) SA+ -jO where N-1 Ck = s(n)s (n - k) k > 0 (122) n=z+k and + =ck = -c~k) (123) Now, to get the digital equivalents of (2),(4) we...Paulo NI. D. M6nica de Oliveira 2 Direcpto do Servi(;o de Instru~ao e Treino Edificjo da Adniinistraqdo Central de Marinha Praoa do Comercio I I...Lisboa Portugal 89 12. Lt. Paulo M. D. NM6nica de Oliveira2 Direc Ao do Servi~o de 1nstruqao e Treino Edificio da Adnistraqo Central de Marinha Praoa do Comercio 1 100 Lisboa Portuoal 89
Directory of Open Access Journals (Sweden)
Runze Zhang
2017-10-01
Full Text Available Pulse width modulation (PWM technology is widely used in traction converters for high-speed railways. The harmonic distribution caused by PWM is quite extensive, and increases the possibility of grid–train coupling resonance in the traction power supply system (TPSS. This paper first analyzes the mechanism of resonance, when the characteristic harmonic frequency of a four-quadrant converter (4QC current that injects into the traction grid matches the resonant frequency of the traction grid, which may result in resonance in the system. To suppress resonance, this paper adopts specific harmonic elimination–pulse width modulation (SHE-PWM technology combined with a transient direct current control strategy to eliminate the harmonics in the resonant frequency, which may suppress the grid–train coupling resonance. Due to the fact that the SHE-PWM process with multiple switching angles contains complex transcendental equations, the initial value is difficult to provide, and is difficult to solve using ordinary iterative algorithms. In this paper, an active-set secondary optimization method is used to solve the equation. The algorithm has the benefits of low dependence on initial values, fast convergence and high solution accuracy. Finally, the feasibility of the resonant suppression algorithm is verified by means of Matlab simulation.
Design of Compact Wilkinson Power Divider with Harmonic Suppression using T-Shaped Resonators
Siahkamari, Hesam; Yasoubi, Zahra; Jahanbakhshi, Maryam; Mousavi, Seyed Mohammad Hadi; Siahkamari, Payam; Nouri, Mohammad Ehsan; Azami, Sajad; Azadi, Rasoul
2018-04-01
A novel scheme of a shrunken Wilkinson power divider with harmonic suppression, using two identical resonators in the conventional Wilkinson power divider is designed. Moreover, the LC equivalent circuit and its relevant formulas are provided. To substantiate the functionality and soundness of design, a microstrip implementation of this design operating at 1 GHz with the second to eighth harmonic suppression, is developed. The proposed circuit is relatively smaller than the conventional circuit, (roughly 55% of the conventional circuit). Simulation and measurement results for the proposed scheme, which are highly consistent with one another, indicate a good insertion loss about 3.1 dB, input return loss of 20 dB and isolation of 20 dB, while sustaining high-power handling capability over the Wilkinson power divider.
Efficient Approach for Harmonic Resonance Identification of Large Wind Power Plants
DEFF Research Database (Denmark)
Ebrahimzadeh, Esmaeil; Blaabjerg, Frede; Wang, Xiongfei
2016-01-01
Unlike conventional power systems where the resonance frequencies are mainly determined by the passive components parameters, large Wind Power Plants (WPPs) may introduce additional harmonic resonances because of the interactions of the wideband control systems of power converters with each other...... and with passive components. This paper presents an efficient approach for identification of harmonic resonances in large WPPs containing power electronic converters, cable, transformer, capacitor banks, shunt reactors, etc. The proposed approach introduces a large WPP as a Multi-Input Multi-Output (MIMO) control...... system by considering the linearized models of the inner control loops of grid-side converters. Therefore, the resonance frequencies of the WPP resulting from passive components and the control loop interactions are identified based on the determinant of the transfer function matrix of the introduced...
DEFF Research Database (Denmark)
Bak, Claus Leth; Bak-Jensen, Birgitte; Wiechowski, Wojciech
2008-01-01
This paper demonstrates the results of implementation and verification of an already existing algorithm that allows for calculating saturation characteristics of singlephase power transformers. The algorithm was described for the first time in 1993. Now this algorithm has been implemented using...... the DIgSILENT Programming Language (DPL) as an external script in the harmonic domain calculations of a power system analysis tool PowerFactory [10]. The algorithm is verified by harmonic measurements on a single-phase power transformer. A theoretical analysis of the core nonlinearities phenomena...... in single and three-phase transformers is also presented. This analysis leads to the conclusion that the method can be applied for modelling nonlinearities of three-phase autotransformers....
Conjugate Image Theory Applied on Capacitive Wireless Power Transfer
Directory of Open Access Journals (Sweden)
Ben Minnaert
2017-01-01
Full Text Available Wireless power transfer using a magnetic field through inductive coupling is steadily entering the market in a broad range of applications. However, for certain applications, capacitive wireless power transfer using electric coupling might be preferable. In order to obtain a maximum power transfer efficiency, an optimal compensation network must be designed at the input and output ports of the capacitive wireless link. In this work, the conjugate image theory is applied to determine this optimal network as a function of the characteristics of the capacitive wireless link, as well for the series as for the parallel topology. The results are compared with the inductive power transfer system. Introduction of a new concept, the coupling function, enables the description of the compensation network of both an inductive and a capacitive system in two elegant equations, valid for the series and the parallel topology. This approach allows better understanding of the fundamentals of the wireless power transfer link, necessary for the design of an efficient system.
Third harmonic generation of high power far infrared radiation in semiconductors
Energy Technology Data Exchange (ETDEWEB)
Urban, M [Ecole Polytechnique Federale, Lausanne (Switzerland). Centre de Recherche en Physique des Plasma (CRPP)
1996-04-01
We investigated the third harmonic generation of high power infrared radiation in doped semiconductors with emphasis on the conversion efficiency. The third harmonic generation effect is based on the nonlinear response of the conduction band electrons in the semiconductor with respect to the electric field of the incident electromagnetic wave. Because this work is directed towards a proposed application in fusion plasma diagnostics, the experimental requirements for the radiation source at the fundamental frequency are roughly given as follows: a wavelength of the radiation at the fundamental frequency in the order of 1 mm and an incident power greater than 1 MW. The most important experiments of this work were performed using the high power far infrared laser of the CRPP. With this laser a new laser line was discovered, which fits exactly the source specifications given above: the wavelength is 676 {mu}m and the maximum power is up to 2 MW. Additional experiments were carried out using a 496 {mu}m laser and a 140 GHz (2.1 mm) gyrotron. The main experimental progress with respect to previous work in this field is, in addition to the use of a very high power laser, the possibility of an absolute calibration of the detectors for the far infrared radiation and the availability of a new type of detector with a very fast response. This detector made it possible to measure the power at the fundamental as well as the third harmonic frequency with full temporal resolution of the fluctuations during the laser pulse. Therefore the power dependence of the third harmonic generation efficiency could be measured directly. The materials investigated were InSb as an example of a narrow gap semiconductor and Si as standard material. The main results are: narrow gap semiconductors indeed have a highly nonlinear electronic response, but the narrow band gap leads at the same time to a low power threshold for internal breakdown, which is due to impact ionization. figs., tabs., refs.
Multimode harmonic power measurement of 40 MW pulsed S-band klystrons
International Nuclear Information System (INIS)
Fowkes, W.R.; Wu, E.S.
1984-08-01
An array of 12 calibrated RF electric field probes on the waveguide walls are used to sample the complex field profile at the second and third harmonics where the fundamental power is in the 40 MW range at 2856 MHx. The measured amplitude and phase signals from these are Fourier analyzed to determine with good accuracy the power in each of the many possible propagating modes
International Nuclear Information System (INIS)
Carroll, D.P.; Kasturi, S.; Subudhi, M.; Gunther, W.
1992-01-01
Most previous analysis on the effects of geomagnetically induced currents (GIC) on electric utility systems has steady-state phenomena, with the main interest in the generator step-up transformer and the off-site power system. This paper begins to investigate the possible effects that a GIC event might have on the power plant itself, by examining the harmonic distortion that could exist at various voltage levels in the on-site distribution system
Economic Decision-Making for Coal Power Flexibility Retrofitting and Compensation in China
Directory of Open Access Journals (Sweden)
Chunning Na
2018-01-01
Full Text Available In China, in order to integrate more renewable energy into the power grid, coal power flexibility retrofitting is imperative. This paper elaborates a generic method for estimating the flexibility potential from the rapid ramp rate and peak shaving operation using nonlinear programming, and defines three flexibility elastic coefficients to quantify the retrofitted targets. The optimized range of the retrofitted targets determined by the flexibility elastic coefficients have a reference significance on coal power flexibility retrofitting. Then, in order to enable economic decisions for coal power flexibility retrofitting, we address a profit maximizing issue regarding optimization decisions for coal power flexibility retrofitting under an assumption of perfect competition, further analyzing the characteristic roots of marginal cost equal to marginal revenue. The rationality of current compensation standards for peak shaving in China can also be judged in the analysis. The case study results show that economic decision-making depends on the compensation standard and the peak shaving depth and time. At a certain peak shaving depth and time, with rational compensation standard power plants are willing to carry out coal power flexibility retrofitting. The current compensation standard in Northeast China is high enough to carry out coal power flexibility retrofitting. These research conclusions have theoretical significance for China’s peak shaving compensation standards formulation.
Llewellyn-Jones, D. T.; Knight, R. J.; Gebbie, H. A.
1980-07-01
A new technique of measuring absolute power exploiting an untuned cavity and Fourier spectroscopy has been used to examine the power spectrum of the harmonics and other overtones produced by a 95 GHz IMPATT oscillator. The conditions which favor the production of a rich harmonic spectrum are not those which maximize the fundamental power. Under some conditions of mismatch at the fundamental frequency it is possible to produce over 200 microW of harmonic power in the 100-200 GHz region comparable with the fundamental power from the oscillator.
López Santos, Oswaldo
2010-01-01
Los filtros activos de potencia, son hoy en día, la solución más atractiva para la reducción de las problemáticas de armónicos y energía reactiva en las redes eléctricas, debido a la gran cantidad de convertidores electrónicos contaminantes instalados en las décadas anteriores. Por esta razón y con especial interés en la necesidad del aprovechamiento eficiente y responsable de los recursos, es trabajo pertinente y necesario el estudio de los filtros activos de potencia. El mencionado estudio ...
UPWARD POWER TENDENCIES IN A HIERARCHY - POWER DISTANCE THEORY VERSUS BUREAUCRATIC RULE
WILKE, HAM
1993-01-01
Two contrasting notions concerning upward power tendencies within hierarchically structured groups are investigated. Power Distance Theory assumes that people have a desire for power that results in a tendency to reduce the power distance towards a more powerful other, and this tendency is assumed
Harmonic analysis of traction power supply system based on wavelet decomposition
Dun, Xiaohong
2018-05-01
With the rapid development of high-speed railway and heavy-haul transport, AC drive electric locomotive and EMU large-scale operation in the country on the ground, the electrified railway has become the main harmonic source of China's power grid. In response to this phenomenon, the need for timely monitoring of power quality problems of electrified railway, assessment and governance. Wavelet transform is developed on the basis of Fourier analysis, the basic idea comes from the harmonic analysis, with a rigorous theoretical model, which has inherited and developed the local thought of Garbor transformation, and has overcome the disadvantages such as window fixation and lack of discrete orthogonally, so as to become a more recently studied spectral analysis tool. The wavelet analysis takes the gradual and precise time domain step in the high frequency part so as to focus on any details of the signal being analyzed, thereby comprehensively analyzing the harmonics of the traction power supply system meanwhile use the pyramid algorithm to increase the speed of wavelet decomposition. The matlab simulation shows that the use of wavelet decomposition of the traction power supply system for harmonic spectrum analysis is effective.
International Nuclear Information System (INIS)
Pochelon, A. . E-mail : Antoine.Pochelon@epfl.ch; Arnoux, G.; Camenen, Y.
2003-01-01
This paper summarises the present effort aimed at developing high elongation heated discharges and testing their confinement properties at normalised currents for which the highest ideal MHD β-limits are predicted. 2nd harmonic (X2) far off-axis ECH/CD is used to stabilise the plasma vertically at high elongation by broadening the current profile in stationary conditions (during the current flat top and over several current diffusion times). Current broadening is maximal for a power deposition in a narrow region (∼a/5), for a finite toroidal injection angle and for high plasma density using upper lateral launchers to minimise refraction. In these discharges which are twice X2 overdense in the centre, 3rd harmonic (X3) is injected from a top launcher to deposit power in the centre and increase the central pressure, simultaneously with far off-axis X2. Using modulated X3, full absorption is measured by the diamagnetic probe. Absorption higher than calculated by thermal ray tracing is occasionally found, indicating absorption on the electron bulk as well as in the suprathermal electron population sometimes with a hollow deposition profile. The high sensitivity of the power coupling to the beam angle stresses the need for developing a mirror feedback scheme to increase the coupling efficiency in transient heating scenarios. (author)
Longer operating times of nuclear power plants. Options for compensating public utility advantages
International Nuclear Information System (INIS)
Bode, Sven; Kondziella, Hendrik; Bruckner, Thomas
2010-01-01
The current German government of CDU/CSU and FDP intends to prolong the operating time of existing nuclear power plants in Germany. The advantages resulting for public utilities are to be compensated. The authors discuss how compensation may be achieved and outline the available instruments. (orig.)
DEFF Research Database (Denmark)
Yoon, Changwoo; Bai, Haofeng; Wang, Xiongfei
2015-01-01
Stability analysis of distributed power generation system becomes complex when there are many numbers of grid inverters in the system. In order to analyze system stability, the overall network impedance will be lumped and needs to be analyzed one by one. However, using a unified bulky transfer-fu...... and then it is expanded for generalizing its concept to an overall radial structured network....
O. I. Bondar; I. L. Bondar
2009-01-01
In this work the generalized mathematical model of an electrical network of the electrified railway junction is proposed. An estimation of influence of static var compensators installation on electric power losses in a network is executed on the basis of given model.
Behavior of gasketless deep bed charcoal filters for radioiodine removal in LWR power plants
International Nuclear Information System (INIS)
Wilhelm, J.G.; Deuber, H.; Furrer, J.; Gerlach, K.
1981-01-01
The removal efficiency of radioiodine filters can be affected by mechanical leakage, aging and poisoning, desorption of radioiodine originally removed by the activated carbon and also by the occurrence of penetrating iodine compounds. To provide high decontamination factors only the gasketless deep bed filter type seems to be appropriate. The experience gathered and the data given in this paper are based on the surveillance testing of radioiodine filters in all German nuclear power plants and on laboratory research work which has been done over years to evaluate the operating behavior of deep bed radioiodine filters and to prove their reliability
X-Band GaN Power Amplifier MMIC with a Third Harmonic-Tuned Circuit
Directory of Open Access Journals (Sweden)
Kyung-Tae Bae
2017-11-01
Full Text Available This paper presents an X-band GaN HEMT power amplifier with a third harmonic-tuned circuit for a higher power density per area and a higher power-added efficiency (PAE using a 0.25 μm GaN HEMT process of WIN semiconductors, Inc. The optimum load impedances at the fundamental and third harmonic frequencies are extracted from load-pull simulations at the transistor’s extrinsic plane, including the drain-source capacitance and the series drain inductance. The third harmonic-tuned circuit is effectively integrated with the output matching circuit at the fundamental frequency, without complicating the whole output matching circuit. The input matching circuit uses a lossy matching scheme, which allows a good return loss and a simple LC low-pass circuit configuration. The fabricated power amplifier monolithic microwave integrated circuit (MMIC occupies an area of 13.26 mm2, and shows a linear gain of 20 dB or more, a saturated output power of 43.2~44.7 dBm, and a PAE of 35~37% at 8.5 to 10.5 GHz.
Detecting Power Voltage Dips using Tracking Filters - A Comparison against Kalman
Directory of Open Access Journals (Sweden)
STANCIU, I.-R.
2012-11-01
Full Text Available Due of its significant economical impact, Power-Quality (PQ analysis is an important domain today. Severe voltage distortions affect the consumers and disturb their activity. They may be caused by short circuits (in this case the voltage drops significantly or by varying loads (with a smaller drop. These two types are the PQ currently issues. Monitoring these phenomena (called dips or sags require powerful techniques. Digital Signal Processing (DSP algorithms are currently employed to fulfill this task. Discrete Wavelet Transforms, (and variants, Kalman filters, and S-Transform are currently proposed by researchers to detect voltage dips. This paper introduces and examines a new tool to detect voltage dips: the so-called tracking filters. Discovered and tested during the cold war, they can estimate a parameter of interest one-step-ahead based on the previously observed values. Two filters are implemented. Their performance is assessed by comparison against the Kalman filter?s results.
Canedo-Rodriguez, Adrian; Rodriguez, Jose Manuel; Alvarez-Santos, Victor; Iglesias, Roberto; Regueiro, Carlos V
2015-04-30
In wireless positioning systems, the transmitter's power is usually fixed. In this paper, we explore the use of varying transmission powers to increase the performance of a wireless localization system. To this extent, we have designed a robot positioning system based on wireless motes. Our motes use an inexpensive, low-power sub-1-GHz system-on-chip (CC1110) working in the 433-MHz ISM band. Our localization algorithm is based on a particle filter and infers the robot position by: (1) comparing the power received with the expected one; and (2) integrating the robot displacement. We demonstrate that the use of transmitters that vary their transmission power over time improves the performance of the wireless positioning system significantly, with respect to a system that uses fixed power transmitters. This opens the door for applications where the robot can localize itself actively by requesting the transmitters to change their power in real time.
Directory of Open Access Journals (Sweden)
Adrian Canedo-Rodriguez
2015-04-01
Full Text Available In wireless positioning systems, the transmitter’s power is usually fixed. In this paper, we explore the use of varying transmission powers to increase the performance of a wireless localization system. To this extent, we have designed a robot positioning system based on wireless motes. Our motes use an inexpensive, low-power sub-1-GHz system-on-chip (CC1110 working in the 433-MHz ISM band. Our localization algorithm is based on a particle filter and infers the robot position by: (1 comparing the power received with the expected one; and (2 integrating the robot displacement. We demonstrate that the use of transmitters that vary their transmission power over time improves the performance of the wireless positioning system significantly, with respect to a system that uses fixed power transmitters. This opens the door for applications where the robot can localize itself actively by requesting the transmitters to change their power in real time.
Directory of Open Access Journals (Sweden)
A.V. Erisov
2016-05-01
Full Text Available Purpose. Simplification of accounting ratio to determine the magnetic field strength of electric power lines, and assessment of their environmental safety. Methodology. Description of the transmission lines of the magnetic field by using techniques of spatial harmonic analysis in the cylindrical coordinate system is carried out. Results. For engineering calculations of electric power lines magnetic field with sufficient accuracy describes their first spatial harmonic magnetic field. Originality. Substantial simplification of the definition of the impact of the construction of transmission line poles on the value of its magnetic field and the bands of land alienation sizes. Practical value. The environmentally friendly projection electric power lines on the level of the magnetic field.
Active Power Controls from Wind Power: Bridging the Gaps
Energy Technology Data Exchange (ETDEWEB)
Ela, E. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Gevorgian, V. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Fleming, P. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Zhang, Y. C. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Singh, M. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Muljadi, E. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Scholbrook, A. [National Renewable Energy Lab. (NREL), Golden, CO (United States); Aho, J. [Univ. of Colorado, Boulder, CO (United States); Buckspan, A. [Univ. of Colorado, Boulder, CO (United States); Pao, L. [Univ. of Colorado, Boulder, CO (United States); Singhvi, V. [Electric Power Research Inst. (EPRI), Palo Alto, CA (United States); Tuohy, A. [Electric Power Research Inst. (EPRI), Palo Alto, CA (United States); Pourbeik, P. [Electric Power Research Inst. (EPRI), Palo Alto, CA (United States); Brooks, D. [Electric Power Research Inst. (EPRI), Palo Alto, CA (United States); Bhatt, N. [Electric Power Research Inst. (EPRI), Palo Alto, CA (United States)
2014-01-01
This paper details a comprehensive study undertaken by the National Renewable Energy Laboratory, Electric Power Research Institute, and the University of Colorado to understand how the contribution of wind power providing active power control (APC) can benefit the total power system economics, increase revenue streams, improve the reliability and security of the power system, and provide superior and efficient response while reducing any structural and loading impacts that may reduce the life of the wind turbine or its components. The study includes power system simulations, control simulations, and actual field tests using turbines at NREL's National Wind Technology Center (NWTC). The study focuses on synthetic inertial control, primary frequency control, and automatic generation control, and analyzes timeframes ranging from milliseconds to minutes to the lifetime of wind turbines, locational scope ranging from components of turbines to large wind plants to entire synchronous interconnections, and additional topics ranging from economics to power system engineering to control design.
Directory of Open Access Journals (Sweden)
Wenge Christoph
2017-12-01
Full Text Available Electric vehicles (EVs can be utilized as mobile storages in a power system. The use of battery chargers can cause current harmonics in the supplied AC system. In order to analyze the impact of different EVs with regardto their number and their emission of current harmonics, a generic harmonic current model of EV types was built and implemented in the power system simulation tool PSS®NETOMAC. Based on the measurement data for different types of EVs three standardized harmonic EV models were developed and parametrized. Further, the identified harmonic models are used by the computation of load flow in a modeled, German power distribution system. As a benchmark, a case scenario was studied regarding a high market penetration of EVs in the year 2030 for Germany. The impact of the EV charging on the power distribution system was analyzed and evaluated with valid power quality standards.
Application of Load Compensation in Voltage Controllers of Large Generators in the Polish Power Grid
Directory of Open Access Journals (Sweden)
Bogdan Sobczak
2014-03-01
Full Text Available The Automatic Voltage Regulator normally controls the generator stator terminal voltage. Load compensation is used to control the voltage which is representative of the voltage at a point either within or external to the generator. In the Polish Power Grid (PPG compensation is ready to use in every AVR of a large generator, but it is utilized only in the case of generators operating at the same medium voltage buses. It is similar as in most European Power Grids. The compensator regulating the voltage at a point beyond the machine terminals has significant advantages in comparison to the slower secondary Voltage and Reactive Power Control System (ARNE1. The compensation stiffens the EHV grid, which leads to improved voltage quality in the distribution grid. This effect may be particularly important in the context of the dynamic development of wind and solar energy.
Electric power quality analysis methods. Application to voltage dips and harmonic disturbances
International Nuclear Information System (INIS)
Vanya, Ignatova
2006-10-01
The power quality concerns all the actors in the energy domains, that they are network administrators, suppliers, producers, or consumers of electricity. The research work presented in this PhD thesis is situated in the field of the power quality monitoring. Its objective is to introduce new techniques for analysis of power quality problems. There are different methods designed for the analysis of the power quality disturbances. This method reaches very good performances in the voltage dips analysis, as it allows segmenting, classifying and characterising these power quality disturbances. The periodic systems method allows the theoretical study of the generation and the propagation of harmonic disturbances in the network. Finally, the statistical matrix method has the objective to represent statistically electrical signals without loss of important information. (author)
Purification of power plant waters with high gradient magnetic filters
International Nuclear Information System (INIS)
Rosenberg, R.
1993-04-01
This is a report of a literature survey. Magnetic high gradient filtration is suitable for separations in difficult surroundings because it can be used in high pressure and temperature, the filtration can be automated and the filter does not contain components which have to be replaced. Magnetic separators for purification of power plant waters have been manufactured commercially for a long time, but they have not always worked satisfactorily especially when separating small particles. The corrosion products in power plant waters are usually ferrimagnetic or paramagnetic and are well suited for magnetic separation. The particle sizes varies considerable but at least in nuclear power plants they are mostly in the range 0.1-30 μ, some even smaller. According to different publications most 60 Co is in particles, while other publications indicate that more than 70 % is in solution. Similarly the data on the purification efficiency of 60 Co varies significantly. Even small magnetic fields are sufficient to separate large ferrimagnetic particles, but the separation of small and paramagnetic particles requires a field more than 20 kT and the high gradient. Presently available commercial separators are so efficient that its seems not to be economically worthwhile to develop them further to improve the filtration efficiency for small particles. Instead it might be worthwhile to investigate methods to increase the particle size by water chemistry methods. (Au). (25 refs., 2 figs.)
Transient Stability Enhancement in Power System Using Static VAR Compensator (SVC
Directory of Open Access Journals (Sweden)
Youssef MOULOUDI
2012-12-01
Full Text Available In this paper, an indirect adaptive fuzzy excitation and static VAR (unit of reactive power, volt-ampere reactive compensator (SVC controller is proposed to enhance transient stability for the power system, which based on input-output linearization technique. A three-bus system, which contains a generator and static VAR compensator (SVC, is considered in this paper, the SVC is located at the midpoint of the transmission lines. Simulation results show that the proposed controller compared with a controller based on tradition linearization technique can enhance the transient stability of the power system under a large sudden fault, which may occur nearly at the generator bus terminal.
Energy Technology Data Exchange (ETDEWEB)
Atkinson-Hope, Gary; Stemmet, W.C. [Cape Peninsula University of Technology, Cape Town Campus, Cape Town (South Africa)
2006-07-01
The purpose of this paper is to assess the DlgSILENT PowerFactory software power definitions (indices) in terms of phase and sequence components for balanced and unbalanced networks when harmonic distortion is present and to compare its results to hand calculations done, following recommendation made by the IEEE Working Group on this topic. This paper also includes the development of a flowchart for calculating power indices in balanced and unbalanced three-phase networks when non-sinusoidal voltages and currents are present. A further purpose is to determine how two industrial grade harmonic analysis software packages (DlgSILENT and ERACS) model three-phase harmonic sources used for current penetration studies and to compare their results when applied to a network. From the investigations, another objective was to develop a methodology for modelling harmonic current sources based on a spectrum obtained from measurements. Three case studies were conducted and the assessment and developed methodologies were shown to be effective. (Author)
Optimized control strategy for crowbarless solid state modular power supply
International Nuclear Information System (INIS)
Upadhyay, R.; Badapanda, M.K.; Tripathi, A.; Hannurkar, P.R.; Pithawa, C.K.
2009-01-01
Solid state modular power supply with series connected IGBT based power modules have been employed as high voltage bias power supply of klystron amplifier. Auxiliary compensation of full wave inverter bridge with ZVS/ZCS operations of all IGBTs over entire operating range is incorporated. An optimized control strategy has been adopted for this power supply needing no output filter, making this scheme crowbarless and is presented in this paper. DSP based fully digital control with same duty cycle for all power modules, have been incorporated for regulating this power supply along with adequate protection features. Input to this power supply is taken directly from 11 kV line and the input system is intentionally made 24 pulsed to reduce the input harmonics, improve the input power factor significantly, there by requiring no line filters. Various steps have been taken to increase the efficiency of major subsystems, so as to improve the overall efficiency of this power supply significantly. (author)
Directory of Open Access Journals (Sweden)
Yi Wang
2017-12-01
Full Text Available In this study, in order to determine the reasonable accuracy of the compensation capacitances satisfying the requirements on the output characteristics for a wireless power transfer (WPT system, taking the series-series (SS compensation structure as an example, the calculation formulas of the output characteristics, such as the power factor, output power, coil transfer efficiency, and capacitors’ voltage stress, are given under the condition of incomplete compensation according to circuit theory. The influence of compensation capacitance errors on the output characteristics of the system is then analyzed. The Taylor expansions of the theoretical formulas are carried out to simplify the formulas. The influence degrees of compensation capacitance errors on the output characteristics are calculated according to the simplified formulas. The reasonable error ranges of the compensation capacitances are then determined according to the requirements of the output characteristics of the system in the system design. Finally, the validity of the theoretical analysis and the simplified processing is verified through experiments. The proposed method has a certain guiding role for practical engineering design, especially in mass production.
International Nuclear Information System (INIS)
Peng, Xingjie; Li, Qing; Wang, Kan
2017-01-01
Highlights: • The current spike problem is observed in the dynamic compensation process of SPNDs. • The current spike is caused by unphysical current change due to range switching. • Modification on the compensation algorithm is introduced to deal with current spike. - Abstract: Dynamic compensation methods are required to improve the response speed of the Self-Powered Neutron Detectors (SPNDs) and make it possible to apply the SPNDs for core monitoring and surveillance. During the experimental test of the compensation method based on linear matrix inequality (LMI), spikes are observed in the compensated SPND current. After analyzing the measurement data, the cause is fixed on the unphysical change of the uncompensated SPND current due to range switching. Then some modifications on the dynamic compensation algorithms are proposed to solve the current spike problem.
Modeling of large aperture third harmonic frequency conversion of high power Nd:glass laser systems
International Nuclear Information System (INIS)
Henesian, M.A.; Wegner, P.J.; Speck, D.R.; Bibeau, C.; Ehrlich, R.B.; Laumann, C.W.; Lawson, J.K.; Weiland, T.L.
1991-01-01
To provide high-energy, high-power beams at short wavelengths for inertial-confinement-fusion experiments, we routinely convert the 1.053-μm output of the Nova, Nd:phosphate-glass, laser system to its third-harmonic wavelength. We describe performance and conversion efficiency modeling of the 3 x 3 arrays potassium-dihydrogen-phosphate crystal plates used for type II/type II phase-matched harmonic conversion of Nova 0.74-m diameter beams, and an alternate type I/type II phase-matching configuration that improves the third-harmonic conversion efficiency. These arrays provide energy conversion of up to 65% and intensity conversion to 70%. 19 refs., 11 figs
Phan, Anh Tuan; Ho, Duc Du; Hermann, Gilles; Wira, Patrice
2015-12-01
For power quality issues like reducing harmonic pollution, reactive power and load unbalance, the estimation of the fundamental frequency of a power lines in a fast and precise way is essential. This paper introduces a new state-space model to be used with an extended Kalman filter (EKF) for estimating the frequency of distorted power system signals in real-time. The proposed model takes into account all the characteristics of a general three-phase power system and mainly the unbalance. Therefore, the symmetrical components of the power system, i.e., their amplitude and phase angle values, can also be deduced at each iteration from the proposed state-space model. The effectiveness of the method has been evaluated. Results and comparisons of online frequency estimation and symmetrical components identification show the efficiency of the proposed method for disturbed and time-varying signals.
Directory of Open Access Journals (Sweden)
Ahmed M. Othman
2017-06-01
Full Text Available This paper presents a design of microgrid (MG with enhanced dynamic performance. Distributed energy resources (DER are widely used in MGs to match the various load types and profiles. DERs include solar PV cells, wind energy sources, fuel cells, batteries, micro gas-engines and storage elements. MG will include AC/DC circuits, developed power electronics devices, inverters and power electronic controllers. A novel modulated power filters (MPF device will be applied in MG design. Enhanced bacterial foraging optimization (EBFO will be proposed to optimize and set the MPF parameters to enhance and tune the MG dynamic response. Recent dynamic control is applied to minimize the harmonic reference content. EBFO will adapt the gains of MPF dynamic control. The present research achieves an enhancement of MG dynamic performance, in addition to ensuring improvements in the power factor, bus voltage profile and power quality. MG operation will be evaluated by the dynamic response to be fine-tuned by MPF based on EBFO. Digital simulations have validated the results to show the effectiveness and efficient improvement by the proposed strategy.
Power system measurements in presence of harmonics. Misure nelle reti in presenza di armoniche
Energy Technology Data Exchange (ETDEWEB)
Pesavento, G. (Padua Univ. (Italy)); Rinaldi, M. (Bologna Univ. (Italy))
1993-03-01
The paper, after a short analysis of possible sources of harmonics and the range of frequencies of interest, deals with the problems related to the measurement of electrical quantities in the presence of distorted wave forms and non-linear loads. In general, the characteristics of available instrumentation are sufficient to provide a good accuracy; electronic apparatus, both analog and digital can easily reach bandwidths of several kHz. Among apparatus connected to power lines, voltage transformers appear to be critical from the point of view of bandwidth. Induction power meters are also affected by the presence of harmonics but, in normal cases, the resulting error is within a few percent margins. Problems arise with definitions related to specific quantities and with the associated physical meaning that might be lost when passing from sinusoidal to distorted conditions.
On Aggregation Requirements for Harmonic Stability Analysis in Wind Power Plants
DEFF Research Database (Denmark)
Dowlatabadi, Mohammadkazem Bakhshizadeh; Hjerrild, Jesper; Kocewiak, Łukasz
2017-01-01
In harmonic stability studies, stable operation of a power system must be ensured at any possible configuration. This leads to a large number of cases due to the high number of components in a power system. An aggregated model can be used to lower the complexity and to reduce the number...... of different cases. In other words, several similar converters (e.g. Wind Turbine Generators) can be replaced by a converter with larger ratings. In most cases, aggregated models work well for stability studies, however, in some cases the aggregation might result in a wrong evaluation of stability...
DEFF Research Database (Denmark)
Liu, Wenzhao; Tarasiuk, Tomasz; Gorniak, Mariusz
2018-01-01
were proposed and carried out in a real ship under sea-going conditions to address this problem. The ship experimental results were presented and discussed considering non-linear bow thruster load and high power ballast pump loads under unbalanced and harmonic voltage conditions. In addition......, the analysis of voltage transient dips during ballast pump starting up is presented. Further, the voltage/current distortions of working generator, bow thruster and pump loads are analyzed. The paper provides a valuable analysis for coping with PQ issues in the real ship power system....
High-power waveguide resonator second harmonic device with external conversion efficiency up to 75%
Stefszky, M.; Ricken, R.; Eigner, C.; Quiring, V.; Herrmann, H.; Silberhorn, C.
2018-06-01
We report on a highly efficient waveguide resonator device for the production of 775 nm light using a titanium indiffused LiNbO3 waveguide resonator. When scanning the resonance, the device produces up to 110 mW of second harmonic power with 140 mW incident on the device—an external conversion efficiency of 75%. The cavity length is also locked, using a Pound–Drever–Hall type locking scheme, involving feedback to either the cavity temperature or the laser frequency. With laser frequency feedback, a stable output power of approximately 28 mW from a 52 mW pump is seen over one hour.
Third harmonic generation of high power far infrared radiation in semiconductors
International Nuclear Information System (INIS)
Urban, M.
1996-04-01
In this work we investigated the third harmonic generation of high power infrared radiation in doped semiconductors with emphasis on the conversion efficiency. The third harmonic generation effect is based on the nonlinear response of the conduction band electrons in the semiconductor with respect to the electric field of the incident electromagnetic wave. Because this work is directed towards a proposed application in fusion plasma diagnostics, the experimental requirements for the radiation source at the fundamental frequency are roughly given as follows: a wavelength of the radiation at the fundamental frequency in the order of 1 mm and an incident power greater than 1 MW. The most important experiments of this work were performed using the high power far infrared laser of the CRPP. With this laser a new laser line was discovered, which fits exactly the source specifications given above: the wavelength is 676 μm and the maximum power is up to 2 MW. Additional experiments were carried out using a 496 μm laser and a 140 GHz (2.1 mm) gyrotron. The main experimental progress with respect to previous work in this field is, in addition to the use of a very high power laser, the possibility of an absolute calibration of the detectors for the far infrared radiation and the availability of a new type of detector with a very fast response. This detector made it possible to measure the power at the fundamental as well as the third harmonic frequency with full temporal resolution of the fluctuations during the laser pulse. Therefore the power dependence of the third harmonic generation efficiency could be measured directly. The materials investigated were InSb as an example of a narrow gap semiconductor and Si as standard material. The main results are: narrow gap semiconductors indeed have a highly nonlinear electronic response, but the narrow band gap leads at the same time to a low power threshold for internal breakdown, which is due to impact ionization. (author) figs
Power system damping - Structural aspects of controlling active power
Energy Technology Data Exchange (ETDEWEB)
Samuelsson, O.
1997-04-01
Environmental and economical aspects make it difficult to build new power lines and to reinforce existing ones. The continued growth in demand for electric power must therefore to a great extent be met by increased loading of available lines. A consequence is that power system damping is reduced, leading to a risk of poorly damped power oscillations between the generators. This thesis proposes the use of controlled active loads to increase damping of such electro-mechanical oscillations. The focus is on structural aspects of controller interaction and of sensor and actuator placement. On-off control based on machine frequency in a single machine infinite bus system is analysed using energy function analysis and phase plane plots. An on-off controller with estimated machine frequency as input has been implemented. At a field test it damped oscillations of a 0.9 MW hydro power generator by controlling a 20kW load. The linear analysis uses two power system models with three and twenty-three machines respectively. Each damper has active power as output and local bus frequency or machine frequency as input. The power system simulator EUROSTAG is used both for generation of the linearized models and for time simulations. Measures of active power mode controllability and phase angle mode observability are obtained from the eigenvectors of the differential-algebraic models. The geographical variation in the network of these quantities is illustrated using the resemblance to bending modes of flexible mechanical structures. Eigenvalue sensitivities are used to determine suitable damper locations. A spring-mass equivalent to an inter-area mode provides analytical expressions, that together with the concept of impedance matching explain the structural behaviour of the power systems. For large gains this is investigated using root locus plots. 64 refs, 99 figs, 20 tabs
A zero power harmonic transponder sensor for ubiquitous wireless μL liquid-volume monitoring
Huang, Haiyu; Chen, Pai-Yen; Hung, Cheng-Hsien; Gharpurey, Ranjit; Akinwande, Deji
2016-01-01
Autonomous liquid-volume monitoring is crucial in ubiquitous healthcare. However, conventional approach is based on either human visual observation or expensive detectors, which are costly for future pervasive monitoring. Here we introduce a novel approach based on passive harmonic transponder antenna sensor and frequency hopping spread spectrum (FHSS) pattern analysis, to provide a very low cost wireless μL-resolution liquid-volume monitoring without battery or digital circuits. In our conceptual demonstration, the harmonic transponder comprises of a passive nonlinear frequency multiplier connected to a metamaterial-inspired 3-D antenna designed to be highly sensitive to the liquid-volume within a confined region. The transponder first receives some FHSS signal from an interrogator, then converts such signal to its harmonic band and re-radiates through the antenna sensor. The harmonic signal is picked up by a sniffer receiver and decoded through pattern analysis of the high dimensional FHSS signal strength data. A robust, zero power, absolute accuracy wireless liquid-volume monitoring is realized in the presence of strong direct coupling, background scatters, distance variance as well as near-field human-body interference. The concepts of passive harmonic transponder sensor, metamaterial-inspired antenna sensor, and FHSS pattern analysis based sensor decoding may help establishing cost-effective, energy-efficient and intelligent wireless pervasive healthcare monitoring platforms.
Performance of a grid connected PV system used as active filter
International Nuclear Information System (INIS)
Calleja, Hugo; Jimenez, Humberto
2004-01-01
In this paper, the performance of a grid connected photovoltaic (PV) system used as an active filter is presented. Its main feature is the capability to compensate the reactive and harmonic currents drawn by nonlinear loads while simultaneously injecting into the grid the maximum power available from the cells. The system can also operate as a stand alone active filter. The system was connected to a 1 kW PV array and tested with the loads typically found in households: small motors, personal computers and electronic ballasts. The results show that the system can correct the power factor to values close to unity for all the cases tested, thereby improving the efficiency of the electric energy supply
National Research Council Canada - National Science Library
Dhillon, Santpal
2001-01-01
...) notch filter with a simplified adaptation algorithm for removal of power line frequency from ECG signals, The performance of this filter is better as compared to a second order infinite impulse response (IIR...
Economic estimation of risk and compensation of damage from accidents in power engineering objects
International Nuclear Information System (INIS)
Lesnykh, V.V.
1996-01-01
Place and basic peculiarities of the task relative to compensation of damage due to accidents in the problem on technical-economical studies of the power engineering objects, including NPPs, are analyzed. Certain approaches in the task of the risk economical estimates and basic provisions of the economical damage compensation system are presented. Description of imitated and analytical approach in the task of estimating financial state is given and certain study results are presented. 11 refs., 8 figs
Harmonic Resonance in Power Transmission Systems due to the Addition of Shunt Capacitors
Patil, Hardik U.
Shunt capacitors are often added in transmission networks at suitable locations to improve the voltage profile. In this thesis, the transmission system in Arizona is considered as a test bed. Many shunt capacitors already exist in the Arizona transmission system and more are planned to be added. Addition of these shunt capacitors may create resonance conditions in response to harmonic voltages and currents. Such resonance, if it occurs, may create problematic issues in the system. It is main objective of this thesis to identify potential problematic effects that could occur after placing new shunt capacitors at selected buses in the Arizona network. Part of the objective is to create a systematic plan for avoidance of resonance issues. For this study, a method of capacitance scan is proposed. The bus admittance matrix is used as a model of the networked transmission system. The calculations on the admittance matrix were done using Matlab. The test bed is the actual transmission system in Arizona; however, for proprietary reasons, bus names are masked in the thesis copy intended for the public domain. The admittance matrix was obtained from data using the PowerWorld Simulator after equivalencing the 2016 summer peak load (planning case). The full Western Electricity Coordinating Council (WECC) system data were used. The equivalencing procedure retains only the Arizona portion of the WECC. The capacitor scan results for single capacitor placement and multiple capacitor placement cases are presented. Problematic cases are identified in the form of 'forbidden response. The harmonic voltage impact of known sources of harmonics, mainly large scale HVDC sources, is also presented. Specific key results for the study indicated include: (1) The forbidden zones obtained as per the IEEE 519 standard indicates the bus 10 to be the most problematic bus. (2) The forbidden zones also indicate that switching values for the switched shunt capacitor (if used) at bus 3 should be
Nonlinear Robust Disturbance Attenuation Control Design for Static Var Compensator in Power System
Directory of Open Access Journals (Sweden)
Ting Liu
2013-01-01
Full Text Available The problem of designing an adaptive backstepping controller for nonlinear static var compensator (SVC system is addressed adopting two perspectives. First, instead of artificially assuming an upper bound or inequality scaling, the minimax theory is used to treat the external unknown disturbances. The system is insensitive to effects of large disturbances due to taking into account the worst case disturbance. Second, a parameter projection mechanism is introduced in adaptive control to force the parameter estimate within a prior specified interval. The proposed controller handles the nonlinear parameterization without compromising control smoothness and at the same time the parameter estimate speed is improved and the robustness of system is strengthened. Considering the short-circuit ground fault and mechanical power perturbation, a simulation study is carried out. The results show the effectiveness of the proposed control method.
Directory of Open Access Journals (Sweden)
Manna Giustino
2010-01-01
Full Text Available Many probabilistic safety assessment studies completed to the date have demonstrated that the risk dealing with low power and shutdown operation of nuclear power plants is often comparable with the risk of at-power operation, and the main contributors to the low power and shutdown risk often deal with human factors. Since the beginning of the nuclear power generation, human performance has been a very important factor in all phases of the plant lifecycle: design, commissioning, operation, maintenance, surveillance, modification, decommissioning and dismantling. The importance of this aspect has been confirmed by recent operating experience. This paper provides the insights and conclusions of a workshop organized in 2007 by the IAEA and the Joint Research Centre of the European Commission, on Harmonization of low power and shutdown probabilistic safety assessment for WWER nuclear power plants. The major objective of the workshop was to provide a comparison of the approaches and the results of human reliability analyses and gain insights in the enhanced handling of human factors.
Model Predictive Current Control for High-Power Grid-Connected Converters with Output LCL Filter
DEFF Research Database (Denmark)
Delpino, Hernan Anres Miranda; Teodorescu, Remus; Rodriguez, Pedro
2009-01-01
A model predictive control strategy for a highpower, grid connected 3-level neutral clamped point converter is presented. Power losses constraints set a limit on commutation losses so reduced switching frequency is required, thus producing low frequency current harmonics. To reduce these harmonics...
Analog Electronic Filters Theory, Design and Synthesis
Dimopoulos, Hercules G
2012-01-01
Filters are essential subsystems in a huge variety of electronic systems. Filter applications are innumerable; they are used for noise reduction, demodulation, signal detection, multiplexing, sampling, sound and speech processing, transmission line equalization and image processing, to name just a few. In practice, no electronic system can exist without filters. They can be found in everything from power supplies to mobile phones and hard disk drives and from loudspeakers and MP3 players to home cinema systems and broadband Internet connections. This textbook introduces basic concepts and methods and the associated mathematical and computational tools employed in electronic filter theory, synthesis and design. This book can be used as an integral part of undergraduate courses on analog electronic filters. Includes numerous, solved examples, applied examples and exercises for each chapter. Includes detailed coverage of active and passive filters in an independent but correlated manner. Emphasizes real filter...
The Theory of Separation of Powers in Nigeria: An Assessment
African Journals Online (AJOL)
gold
2012-07-26
Jul 26, 2012 ... The Theory of Separation of Powers means that, a different body of persons .... legislature enacting oppressive laws which the executive will .... Nigeria, separation of powers is a fundamental constitutional principle which.
Characterization of benign and malignant solid breast masses in harmonic 3D power Doppler imaging
International Nuclear Information System (INIS)
Hsiao, Y.-H.; Huang, Y.-L.; Kuo, S.-J.; Liang, W.-M.; Chen, S.-T.; Chen, D.-R.
2009-01-01
Purpose: The authors assessed the characteristics of benign and malignant solid breast tumors in harmonic three-dimensional (3D) power Doppler imaging and proposed decision models to classify benign and malignant breast tumors. Materials and methods: A total of 86 malignant and 97 benign harmonic 3D power Doppler US images were analyzed. All the harmonic 3D power Doppler images were obtained using a Voluson730 US system (GE, Zipf, Austria) equipped with a RSP 6-12 transducer and tissue harmonic imaging modalities. Imaging analysis was performed using the Virtual Organ Computer-aided Analysis (VOCAL)-imaging program. Histogram indices, the vascularization index (VI), flow index (FI) and vascularization-flow index (VFI), were calculated for the intra-tumor and for shells with an outside thickness of 3 mm surrounding the breast tumors. The receiver operating characteristic (ROC) curves were calculated to estimate the diagnostic performances. Results: The results revealed that the choice of decision model comprised the parameters of patient age, intra-tumor VI, and tumor volume to classify benign and malignant breast tumors. The area under the ROC curve (Az) was 0.910, accuracy was 81.4%, and sensitivity and specificity were 81.4% and 81.4%, respectively. The parameter intra-tumor VI was the choice for all of the histogram indices in differentiating between malignant and benign lesions. Conclusion: The decision model, which was composed of patient age, tumor volume and intra-tumor VI, and a cut-off value for intra-tumor VI at the upper end of patient age and tumor volume, was recommended in clinical application.
Energy Technology Data Exchange (ETDEWEB)
Chinthavali, Madhu Sudhan [ORNL; Onar, Omer C [ORNL; Miller, John M [ORNL; Tang, Lixin [ORNL
2013-01-01
Wireless Power Transfer (WPT) technology is a novel research area in the charging technology that bridges utility and the automotive industries. There are various solutions that are currently being evaluated by several research teams to find the most efficient way to manage the power flow from the grid to the vehicle energy storage system. There are different control parameters that can be utilized to compensate for the change in the impedance. To understand the power flow through the system this paper presents a novel approach to the system model and the impact of different control parameters on the load power. The implementation of an active front-end rectifier on the grid side for power factor control and voltage boost capability for load power regulation is also discussed.
Directory of Open Access Journals (Sweden)
Ruiqing Shao
2012-12-01
Full Text Available According to optimal contracting theory, compensation contracts are effective in solving the agency problem between stockholders and managers. Executive compensation is naturally related to firm performance. However, contracts are not always perfect. Managers may exert influence on the formulation and implementation of compensation contracts by means of their managerial power. As fair value has been introduced into the new accounting standards in China, new concerns have arisen over the relationship between profits and losses from changes in fair value (CFV and levels of executive compensation. In this study, we find that executive compensation is significantly related to CFV. However, this sensitivity is asymmetric in that increases to compensation due to profits from changes in fair value (PCFV are higher than reductions to compensation due to losses from changes in fair value (LCFV. Furthermore, we find that managerial power determines the strength of this asymmetry.
Modeling and Simulation of DC Power Electronics Systems Using Harmonic State Space (HSS) Method
DEFF Research Database (Denmark)
Kwon, Jun Bum; Wang, Xiongfei; Bak, Claus Leth
2015-01-01
based on the state-space averaging and generalized averaging, these also have limitations to show the same results as with the non-linear time domain simulations. This paper presents a modeling and simulation method for a large dc power electronic system by using Harmonic State Space (HSS) modeling......For the efficiency and simplicity of electric systems, the dc based power electronics systems are widely used in variety applications such as electric vehicles, ships, aircrafts and also in homes. In these systems, there could be a number of dynamic interactions between loads and other dc-dc....... Through this method, the required computation time and CPU memory for large dc power electronics systems can be reduced. Besides, the achieved results show the same results as with the non-linear time domain simulation, but with the faster simulation time which is beneficial in a large network....
Yin, Qiwei; Lu, Huadong; Su, Jing; Peng, Kunchi
2016-05-01
The thermal lens effect of terbium gallium garnet (TGG) crystal in a high power single-frequency laser severely limits the output power and the beam quality of the laser. By inserting a potassium dideuterium phosphate (DKDP) slice with negative thermo-optical coefficient into the laser resonator, the harmful influence of the thermal lens effect of the TGG crystal can be effectively mitigated. Using this method, the stable range of the laser is broadened, the bistability phenomenon of the laser during the process of changing the pump power is completely eliminated, the highest output power of an all-solid-state continuous-wave intracavity-frequency-doubling single-frequency laser at 532 nm is enhanced to 30.2 W, and the beam quality of the laser is significantly improved.
DEFF Research Database (Denmark)
Mousazadeh, Seyyed Yousef; Jalilian, Alireza; Savaghebi, Mehdi
2018-01-01
In this paper, a coordinated harmonic compensation and voltage support scheme is presented for distributed generations’ (DGs’) interface inverters in a resistive grid-connected microgrid. Voltage support is performed by reactive power compensation which can mitigate the over/under voltage problem...
Wife Beating in South Africa: An Imbalance Theory of Resources and Power
Choi, Susanne Y. P.; Ting, Kwok-Fai
2008-01-01
This article develops an imbalance theory to explain physical violence against women in intimate relationships in South Africa. The theory proposes four typologies: dependence, compensation, submission, and transgression, through which imbalances in resource contribution and power distribution between spouses are hypothesized to contribute to…
Distributed power quality improvement in residential microgrids
DEFF Research Database (Denmark)
Naderi Zarnaghi, Yahya; Hosseini, Seyed Hossein; Ghassem Zadeh, Saeid
2017-01-01
The importance of power quality issue on micro grids and also the changing nature of power system distortions will lead the future power systems to use distributed power quality improvement (DPQI) devices. One possible choice of these DPQIs are multifunctional DGs that could compensate some...... harmonics in the location of generation and prevent the harmonics to enter main power grid. In this paper a control method based on virtual harmonic impedance is presented for these multifunctional DGs and the effect of the location of these DGs on compensation procedure is studied with simulating...
Power Swing Detection in UPFC-Compensated Line by Phase Angle of Current
DEFF Research Database (Denmark)
Khodaparast, Jalal; Khederzadeh, M.; Silva, Filipe Miguel Faria da
2017-01-01
Power swing blocker (PSB) is a complementary part of distance relay protection, that detects power swing, in order to prevent unintended operation of a distance relay. Unified power flow controller (UPFC) is used in power system to control both active and reactive powers and its operation during...... condition. The results show that these indices may no longer work in systems with UPFC. In addition, this paper proposes a new method for detecting power swing based on the phase angle of current at relay point and compares it with two other methods. The new method distinguishes power swing from a fault...
DEFF Research Database (Denmark)
Khazraj, Hesam; Silva, Filipe Miguel Faria da; Bak, Claus Leth
2016-01-01
Dynamic State Estimation (DSE) is a critical tool for analysis, monitoring and planning of a power system. The concept of DSE involves designing state estimation with Extended Kalman Filter (EKF) or Unscented Kalman Filter (UKF) methods, which can be used by wide area monitoring to improve......-linear state estimator is developed in MatLab to solve states by applying the unscented Kalman filter (UKF) and Extended Kalman Filter (EKF) algorithm. Finally, a DSE model is built for a 14 bus power system network to evaluate the proposed algorithm for the networks.This article will focus on comparing...
Methods for in-place testing of HEPA and iodine filters used in nuclear power plants
International Nuclear Information System (INIS)
Holmberg, R.; Laine, J.
1978-04-01
The purpose of this work was a general investigation of existing in-place test methods and to build an equipment for in-place testing of HEPA and iodine sorption filters. In this work the discussion is limited to methods used in in-place testing of HEPA and iodine sorption filters used in light-water-cooled reactor plants. Dealy systems, built for the separation of noble gases, and testing of them is not discussed in the work. Contaminants present in the air of a reactor containment can roughly be diveded into three groups: aerosols, reactive gases, and noble gases. The aerosols are filtered with HEPA (High Efficiency Particulate Air) filters. The most important reactive gases are molecular iodine and its two compounds: hydrogen iodide and methyl iodide. Of gases to be removed by the filters methyl iodide is the gas most difficult to remove especially at high relative humidities. Impregnated activated charcoal is generally used as sorption material in the iodine filters. Experience gained from the use of nuclear power plants proves that the function of high efficiency air filter systems can not be considered safe until this is proved by in-place tests. In-place tests in use are basically equal. A known test agent is injected upstream of the filter to be tested. The efficiency is calculated from air samples taken from both sides of the filter. (author)
Command Filtered Adaptive Fuzzy Neural Network Backstepping Control for Marine Power System
Directory of Open Access Journals (Sweden)
Xin Zhang
2014-01-01
Full Text Available In order to retrain chaotic oscillation of marine power system which is excited by periodic electromagnetism perturbation, a novel command-filtered adaptive fuzzy neural network backstepping control method is designed. First, the mathematical model of marine power system is established based on the two parallel nonlinear model. Then, main results of command-filtered adaptive fuzzy neural network backstepping control law are given. And the Lyapunov stability theory is applied to prove that the system can remain closed-loop asymptotically stable with this controller. Finally, simulation results indicate that the designed controller can suppress chaotic oscillation with fast convergence speed that makes the system return to the equilibrium point quickly; meanwhile, the parameter which induces chaotic oscillation can also be discriminated.
A High Power Density Single-Phase PWM Rectifier With Active Ripple Energy Storage
Energy Technology Data Exchange (ETDEWEB)
Wang, Ruxi [Virginia Polytechnic Institute and State University (Virginia Tech); Wang, Fei [ORNL; Boroyevich, Dushan [Virginia Polytechnic Institute and State University (Virginia Tech); Burgos, Rolando [ABB; Lai, Rixin [General Electric; Ning, Puqi [ORNL; Rajashekara, Kaushik [Rolls Royce
2011-01-01
It is well known that single-phase pulse width modulation rectifiers have second-order harmonic currents and corresponding ripple voltages on the dc bus. The low-frequency harmonic current is normally filtered using a bulk capacitor in the bus, which results in low power density. However, pursuing high power density in converter design is a very important goal in the aerospace applications. This paper studies methods for reducing the energy storage capacitor for single-phase rectifiers. The minimum ripple energy storage requirement is derived independently of a specific topology. Based on theminimum ripple energy requirement, the feasibility of the active capacitor s reduction schemes is verified. Then, we propose a bidirectional buck boost converter as the ripple energy storage circuit, which can effectively reduce the energy storage capacitance. The analysis and design are validated by simulation and experimental results.
Dispersion compensated mid-infrared quantum cascade laser frequency comb with high power output
Directory of Open Access Journals (Sweden)
Q. Y. Lu
2017-04-01
Full Text Available Chromatic dispersion control plays an underlying role in optoelectronics and spectroscopy owing to its enhancement to nonlinear interactions by reducing the phase mismatching. This is particularly important to optical frequency combs based on quantum cascade lasers which require negligible dispersions for efficient mode locking of the dispersed modes into equally spaced comb modes. Here, we demonstrated a dispersion compensated mid-IR quantum cascade laser frequency comb with high power output at room temperature. A low-loss dispersive mirror has been engineered to compensate the device’s dispersion residue for frequency comb generation. Narrow intermode beating linewidths of 40 Hz in the comb-working currents were identified with a high power output of 460 mW and a broad spectral coverage of 80 cm-1. This dispersion compensation technique will enable fast spectroscopy and high-resolution metrology based on QCL combs with controlled dispersion and suppressed noise.
Agent-based Distributed Unbalance Compensation for Optimal Power Quality in Islanded Microgrids
DEFF Research Database (Denmark)
Meng, Lexuan; Dragicevic, Tomislav; Guerrero, Josep M.
2014-01-01
-based distributed hierarchical control method. Communication links are required between neighboring units. Consensus algorithm and optimization algorithm are implemented in tertiary control for global information discovery and local optimal decision-making respectively. The tertiary control gives lower level......In microgrids, the distributed generators (DG) can be used as distributed compensators so as to compensate the voltage unbalances in the critical bus. However, the power quality disturbance in generator sides and local buses may be affected and exceeds the limit. It can be more convenient...... to implement tertiary control so as to adjust the compensation efforts among DGs and ensure the acceptable power quality in local buses. Moreover, as centralized control methods have certain disadvantages, such as low flexibility, expandability and heavy computation burden, this paper proposes an agent...
Power filtering of n-th order in the fractional Fourier domain
Alieva, T.; Calvo, M.L.; Bastiaans, M.J.
2002-01-01
The main properties of the power filtering operation in the fractional Fourier domain and its relationship to the differentiation operation are considered. The application of linear power filtering for solving the phase retrieval problem from only intensity distributions is proposed. The optical
LOW-POWER AC LOADS AND ELECTRICAL POWER QUALITY
Directory of Open Access Journals (Sweden)
EPURE S.
2016-12-01
Full Text Available This paper deals with experimental study and numerical simulation of single phase AC low power loads: artificial light sources, personal computers, refrigeration units, air conditioning units and TV receivers. These loads are in such large numbers that represents the main source of disturbances (harmonic current, reactive power and unbalanced three-phase network. The obtained simulation models, verified by comparison with experimental results may be used in larger simulation models for testing and sizing the optimum parameters of active power filters. Models can also be used to study the interactions between grid elements and various loads or situations.
Low Power and Low Leakage Implementation of RNS FIR Filters
DEFF Research Database (Denmark)
Cardarilli, Gian Carlo; Re, Andrea Del; Nannarelli, Alberto
2005-01-01
The CMOS technology scaling is leading to the integration of ever more complex systems on silicon. On the other hand, the shrinking of the devices and the reduction of the supply voltage have significantly increased the static power dissipation, that in power budgets of nanometer technologies, ca...
Low-power implementation of polyphase filters in Quadratic Residue Number System
DEFF Research Database (Denmark)
Cardarilli, Gian Carlo; Re, Andrea Del; Nannarelli, Alberto
2004-01-01
The aim of this work is the reduction of the power dissipated in digital filters, while maintaining the timing unchanged. A polyphase filter bank in the Quadratic Residue Number System (QRNS) has been implemented and then compared, in terms of performance, area, and power dissipation...... to the implementation of a polyphase filter bank in the traditional two's complement system (TCS). The resulting implementations, designed to have the same clock rates, show that the QRNS filter is smaller and consumes less power than the TCS one....
Broussard, John R.
1987-01-01
Relationships between observers, Kalman Filters and dynamic compensators using feedforward control theory are investigated. In particular, the relationship, if any, between the dynamic compensator state and linear functions of a discrete plane state are investigated. It is shown that, in steady state, a dynamic compensator driven by the plant output can be expressed as the sum of two terms. The first term is a linear combination of the plant state. The second term depends on plant and measurement noise, and the plant control. Thus, the state of the dynamic compensator can be expressed as an estimator of the first term with additive error given by the second term. Conditions under which a dynamic compensator is a Kalman filter are presented, and reduced-order optimal estimaters are investigated.
Wireless power pad with local power activation for portable devices
Waffenschmidt, E.; Zheglov, V.
2007-01-01
Wireless power transfer by magnetic induction offers a simple to use way to recharge mobile devices like e.g. mobile phone, music players or medical sensors. As shown by a previous report and an existing Power Pad demonstrator, wireless inductive power transfer is possible with a good power
A dynamic voltage restorer (DVR) with selective harmonic compensation at medium voltage level
DEFF Research Database (Denmark)
Newman, M.J.; Holmes, D.G.; Nielsen, J.G.
2005-01-01
Dynamic voltage restorers (DVRs) are now becoming more established in industry to reduce the impact of voltage sags to sensitive loads. However, DVRs spend most of their time in standby mode, since voltage sags occur very infrequently, and hence their utilization is low. In principle, it would...... be advantageous if the series-connected inverter of a DVR could also be used to compensate for any steady-state load voltage harmonics, since this would increase the power quality "value-added" benefits to the grid system. However, before this can be done, consideration must be given to the control of steady......-state power through the DVR, the increased losses, and the low modulation depths at which the scheme must operate to achieve acceptable harmonic compensation performance. This paper presents a selective harmonic feedback control strategy that can be easily added to medium-voltage DVR systems to provide...
The Theory of Separation of Powers in Nigeria: An Assessment ...
African Journals Online (AJOL)
The Theory of Separation of Powers means that, a different body of persons is to administer each of the three departments of government. That no one of them is to have a controlling power over either of the others. For the purpose of preserving the liberty of the individual and for avoiding tyranny separation of powers is ...
An LLCL Power Filter for Single-Phase Grid-Tied Inverter
DEFF Research Database (Denmark)
Wu, Weimin; He, Yuanbin; Blaabjerg, Frede
2012-01-01
This paper presents a new topology of higher order power filter for grid-tied voltage-source inverters, named the LLCL filter, which inserts a small inductor in the branch loop of the capacitor in the traditional LCL filter to compose a series resonant circuit at the switching frequency. Particul......This paper presents a new topology of higher order power filter for grid-tied voltage-source inverters, named the LLCL filter, which inserts a small inductor in the branch loop of the capacitor in the traditional LCL filter to compose a series resonant circuit at the switching frequency...... to the inverter system control. The parameter design criteria of the proposed LLCL filter is also introduced. The comparative analysis and discussions regarding the traditional LCL filter and the proposed LLCL filter have been presented and evaluated through experiment on a 1.8-kW-single-phase grid-tied inverter...
Microchip power compensated calorimetry applied to metal hydride characterization
Energy Technology Data Exchange (ETDEWEB)
Sepulveda, A.; Lopeandia, A.F.; Domenech-Ferrer, R.; Garcia, G.; Pi, F.; Rodriguez-Viejo, J. [Nanomaterials and Microsystems Group, Physics Department, Universitat Autonoma de Barcelona, 08193 Bellaterra (Spain); Munoz, F.J. [Instituto de Microelectronica de Barcelona, Centro Nacional de Microelectronica, Campus UAB, 08193 Bellaterra (Spain)
2008-06-15
In this work, we show the suitability of the thin film membrane-based calorimetric technique to measure kinetically limited phase transitions such as the dehydrogenation of metallic hydrides. Different compounds such as Mg, Mg/Al and Mg{sub 80}Ti{sub 20} have been deposited over the active area of the microchip by electron beam evaporation. After several hydrogenation treatments at different temperatures to induce the hydride formation, calorimetric measurements on the dehydrogenation process of those thin films, either in vacuum or in air, are performed at a heating rate of 10 C/min. We observe a significant reduction in the onset of dehydrogenation for Mg{sub 80}Ti{sub 20} compared with pure Mg or Mg/Al layers, which confirms the beneficial effect of Ti on dehydrogenation. We also show the suitability of the membrane-based nanocalorimeters to be used in parallel with optical methods. Quantification of the energy released during hydrogen desorption remains elusive due to the semi-insulating to metallic transition of the film which affects the calorimetric trace. (author)
Power to Production: Activity Guide.
Massachusetts Univ., Lowell. Tsongas Industrial History Center.
This field trip program consists of a 90-minute interpretive tour and a 90-minute hands-on workshop. The tour and workshop explore the role of water power in the Industrial Revolution. On the tour, students discover firsthand the unique resources of Lowell, Massachusetts, and the Park, while the workshop brings these historic resources to life as…
Directory of Open Access Journals (Sweden)
Palanisamy Ramasamy
2017-11-01
Full Text Available A Unified Power Quality Conditioner (UPQC is designed using a Neutral Point Clamped (NPC multilevel inverter to improve the power quality. When designed for high/medium voltage and power applications, the voltage stress across the switches and harmonic content in the output voltage are increased. A 3-phase 4-wire NPC inverter system is developed as Power Quality Conditioner using an effectual three dimensional Space Vector Modulation (3D-SVM technique. The proposed system behaves like a UPQC with shunt and series active filter under balanced and unbalanced loading conditions. In addition to the improvement of the power quality issues, it also balances the neutral point voltage and voltage balancing across the capacitors under unbalanced condition. The hardware and simulation results of proposed system are compared with 2D-SVM and 3D-SVM. The proposed system is stimulated using MATLAB and the hardware is designed using FPGA. From the results it is evident that effectual 3D-SVM technique gives better performance compared to other control methods.
Enhancement of Non-Stationary Speech using Harmonic Chirp Filters
DEFF Research Database (Denmark)
Nørholm, Sidsel Marie; Jensen, Jesper Rindom; Christensen, Mads Græsbøll
2015-01-01
In this paper, the issue of single channel speech enhancement of non-stationary voiced speech is addressed. The non-stationarity of speech is well known, but state of the art speech enhancement methods assume stationarity within frames of 20–30 ms. We derive optimal distortionless filters that take...... the non-stationarity nature of voiced speech into account via linear constraints. This is facilitated by imposing a harmonic chirp model on the speech signal. As an implicit part of the filter design, the noise statistics are also estimated based on the observed signal and parameters of the harmonic chirp...... model. Simulations on real speech show that the chirp based filters perform better than their harmonic counterparts. Further, it is seen that the gain of using the chirp model increases when the estimated chirp parameter is big corresponding to periods in the signal where the instantaneous fundamental...
DEFF Research Database (Denmark)
Wang, Yanbo; Wang, Xiongfei; Blaabjerg, Frede
2017-01-01
parameters on the harmonic instability of the power system. Moreover, the harmonic-frequency oscillation modes are identified, where participation analysis is presented to evaluate the contributions of different states to these modes and to further reveal how the system gives rise to harmonic instability......This paper presents a harmonic instability analysis method using state-space modeling and participation analysis in the inverter-fed ac power systems. A full-order state-space model for the droop-controlled Distributed Generation (DG) inverter is built first, including the time delay of the digital...... control system, inner current and voltage control loops, and outer droop-based power control loop. Based on the DG inverter model, an overall state-space model of a two-inverter-fed system is established. The eigenvalue-based stability analysis is then presented to assess the influence of controller...
Rethinking Rectification: AC-DC Power Supply in Package
DEFF Research Database (Denmark)
Pejtersen, Jens; Knott, Arnold; Jørgensen, Ivan Harald Holger
efficiency, while drawing high input peak current with a high harmonic content. Mitigating these non-idealities requires higher order EMI filters and a subsequent power factor correction stage. Advanced active rectifier topologies can mitigate all three non-idealities simultaneously while balancing power...
Song, S. Y.; Liu, Q. H.; Zhao, Y. N.; Liu, S. Y.
2016-08-01
With the rapid development of wind power generation, the related research of wind power control and integration issues has attracted much attention, and the focus of the research are shifting away from the ideal power grid environment to the actual power grid environment. As the main stream wind turbine generator, a doubly-fed induction generator (DFIG) is connected to the power grid directly by its stator, so it is particularly sensitive to the power grid. This paper studies the improvement of DFIG control technology in the power grid harmonic environment. Based on the DFIG dynamic model considering the power grid harmonic environment, this paper introduces the shortcomings of the common control strategy of DFIG, and puts forward the enhanced method. The decoupling control of the system is realized by compensating the coupling between the rotor harmonic voltage and harmonic current, improving the control performance. In addition, the simulation experiments on PSCAD/EMTDC are carried out to verify the correctness and effectiveness of the improved scheme.
Power laws from linear neuronal cable theory
DEFF Research Database (Denmark)
Pettersen, Klas H; Lindén, Henrik Anders; Tetzlaff, Tom
2014-01-01
suggested to be at the root of this phenomenon, we here demonstrate a possible origin of such power laws in the biophysical properties of single neurons described by the standard cable equation. Taking advantage of the analytical tractability of the so called ball and stick neuron model, we derive general...... are homogeneously distributed across the neural membranes and themselves exhibit pink ([Formula: see text]) noise distributions. While the PSD noise spectra at low frequencies may be dominated by synaptic noise, our findings suggest that the high-frequency power laws may originate in noise from intrinsic ion...
Economic analysis of reactive power compensation in a wind farm: Influence of Spanish energy policy
Energy Technology Data Exchange (ETDEWEB)
Martinez, E.; Daroca, F. [Grupo Eolicas Riojanas, Carretera de Laguardia, 91-93, 26006 Logrono, La Rioja (Spain); Sanz, F.; Blanco, J. [Department of Mechanical Engineering, University of La Rioja, Logrono, La Rioja (Spain); Jimenez, E. [Department of Electrical Engineering, University of La Rioja, Logrono, La Rioja (Spain)
2008-08-15
Presently, renewable energies and especially wind energy are gaining a special relevance in the electrical market worldwide. This current rate of growth brings with it the need for the various wind farms to not limit themselves to producing energy but also provide stability to the network within its capabilities. So, the actual objective is to adapt the installations that produce wind energy in such a way that they give a maximum amount of support in any given moment to the electrical network. For this purpose, there are governing techno-economic parameters that influence the economic behavior of commercial wind farms. A complete cost-benefit analysis model is developed, focused on incorporating automatic capacitor banks into wind farms for the compensation of reactive power. This economic analysis is about doubly fed induction generator (DFIG) wind turbines. Although this kind of wind turbines have a certain capability in terms of modulating reactive power, this capacity is not enough to achieve the new requirements of reactive power regulation in Spain and it is necessary to invest in systems of external compensation. In this paper, we have studied the case of DFIG wind turbine and capacitor banks, although the used methodology can be applied to other technologies as well by simply amplifying the algorithms according to the specific characteristics of the option elected. Following this premise, a detailed analysis of the specific needs of a wind farm has been carried out, as well as a search for the optimum performance for the compensation of reactive power. (author)
Economic analysis of reactive power compensation in a wind farm: Influence of Spanish energy policy
International Nuclear Information System (INIS)
Martinez, E.; Daroca, F.; Sanz, F.; Blanco, J.; Jimenez, E.
2008-01-01
Presently, renewable energies and especially wind energy are gaining a special relevance in the electrical market worldwide. This current rate of growth brings with it the need for the various wind farms to not limit themselves to producing energy but also provide stability to the network within its capabilities. So, the actual objective is to adapt the installations that produce wind energy in such a way that they give a maximum amount of support in any given moment to the electrical network. For this purpose, there are governing techno-economic parameters that influence the economic behavior of commercial wind farms. A complete cost-benefit analysis model is developed, focused on incorporating automatic capacitor banks into wind farms for the compensation of reactive power. This economic analysis is about doubly fed induction generator (DFIG) wind turbines. Although this kind of wind turbines have a certain capability in terms of modulating reactive power, this capacity is not enough to achieve the new requirements of reactive power regulation in Spain and it is necessary to invest in systems of external compensation. In this paper, we have studied the case of DFIG wind turbine and capacitor banks, although the used methodology can be applied to other technologies as well by simply amplifying the algorithms according to the specific characteristics of the option elected. Following this premise, a detailed analysis of the specific needs of a wind farm has been carried out, as well as a search for the optimum performance for the compensation of reactive power. (author)
Directory of Open Access Journals (Sweden)
Aslan İNAN
2005-01-01
Full Text Available The losses in the power systems should be low as possible as. Saving energy instead of loses (kWh in power utilities can supply much more energy to the consumers. The lower losses the more energy is saved and thus the power system becomes more economical. In recent years, the increasing number of applications and power ratings of the devices which have nonlinear voltage-current characteristics cause voltage waveform distortion and additional losses. While evaluating losses considering harmonics will provide more contribution to obtain more accurate results. In this study, Artificial Neural Networks (ANN method has been presented to predict the harmonic losses in unbalanced power systems by using the data from balanced power system with nonlinear loads.
Mitigation of Voltage and Current Harmonics in Grid-Connected Microgrids
DEFF Research Database (Denmark)
Savaghebi, Mehdi; Guerrero, Josep M.; Jalilian, Alireza
2012-01-01
In this paper, a control approach is proposed for selective compensation of main voltage and current harmonics in grid-connected microgrids. Two modes of compensation are considered, i.e. voltage and current compensation modes. In the case that sensitive loads are connected to the point of common...... coupling (PCC), voltage compensation mode is activated in order to provide a high voltage quality at PCC. Otherwise, grid current harmonics are mitigated (current compensation mode) in order to avoid excessive harmonic supply by the grid. In both modes, harmonic compensation is achieved through proper...... control of distributed generators (DGs) interface converters. The compensation effort of each harmonic is shared considering the corresponding current harmonic supplied by the DGs. The control system of each DG comprises harmonic compensator, power controllers, voltage and current controllers and virtual...
International Nuclear Information System (INIS)
Seegmiller, D.S.
1984-01-01
The usefulness of a nuclear power plant training simulator for developing and testing modern estimation and control applications for nuclear power plants is demonstrated. A Kalman filter based instrument failure detection technique for a pressurized water reactor pressurizer is implemented on the Department of Energy N Reactor Training Simulator. This real-time failure detection method computes the first two moments (mean and variance) of each element of a normalized filter innovations vector. Failed pressurizer instrumentation can be detected by comparing these moments to the known statistical properties of the steady state, linear Kalman fitler innovations sequence. The capabilities of the detection system are evaluated using simulated plant transients and instrument failures
DEFF Research Database (Denmark)
Savaghebi, Mehdi; Guerrero, Josep M.; Jalilian, Alireza
2011-01-01
In this paper, a microgrid hierarchical control scheme is proposed which includes primary and secondary control levels. The primary level comprises distributed generators (DGs) local controllers. The local controller mainly consists of active and reactive power controllers, voltage and current...... controllers, and virtual impedance loop. A novel virtual impedance structure is proposed to achieve proper sharing of non-fundamental power among the microgrid DGs. The secondary level is designed to manage compensation of voltage harmonics at the microgrid load bus (LB) to which the sensitive loads may...... be connected. Also, restoration of LB voltage amplitude and microgrid frequency to the rated values is directed by the secondary level. These functions are achieved by sending proper control signals to the local controllers. The simulation results show the effectiveness of the proposed control scheme....
Siemaszko, Daniel
2015-06-15
The handling of weak networks with asymmetric loads and disturbances im- plies the accurate handling of the second-harmonic component that appears in an unbalanced network. This paper proposes a classic vector control approach using a PI-based controller with superior decoupling capabilities for operation in weak networks with unbalanced phase voltages. A synchronization method for weak unbalanced networks is detailed, with dedicated dimensioning rules. The use of a double-frame controller allows a current symmetry or controlled imbalance to be forced for compensation of power oscillations by controlling the negative current sequence. This paper also serves as a useful reminder of the proper way to cancel the inherent coupling effect due to the transformation to the synchronous rotating reference frame, and of basic considerations of the relationship between switching frequency and control bandwidth.
Challenges facing the European power transmission tariffs: The case of inter-TSO compensation
International Nuclear Information System (INIS)
Stoilov, Dimo; Dimitrov, Yulian; Francois, Bruno
2011-01-01
This article draws attention to problems important for all EU power consumers-the unfairness in individual payments for power transmission and in the cross-border subsidy element in the mechanism of Inter-Transmission System Operators (TSO) Compensation (ITC). A brief review of power transmission tariffs brings out the structure of the problems. A short retrospection explains their growth. The essence of the ITC mechanism is explained and existing shortcomings are illustrated. The deficiencies of existing regulations for transmission pricing are analyzed. In the light of this analysis, the ITC problem is reconsidered and defined more precisely. The basic prerequisites to an ITC reformulation process are presented. The main principles of a new simple, transparent and equitable approach are suggested, in accordance with the contemporary legal positions and functions of the TSOs. - Highlights: → Investigations in the mechanism known as Inter-TSO Compensation (ITC). → Deficiencies in European regulations for cross-border power transmission payments. → Main principles of a new approach avoiding the existing cross-subsidies. → Appeal for reconsideration and a more precise definition of the ITC problem. → Public welfare enhancement by fairness in payment for power transmission.
A combined compensation method for the output voltage of an insulated core transformer power supply
Energy Technology Data Exchange (ETDEWEB)
Yang, L.; Yang, J., E-mail: jyang@mail.hust.edu.cn; Liu, K. F.; Qin, B.; Chen, D. Z. [State Key Laboratory of Advanced Electromagnetic Engineering and Technology, Huazhong University of Science and Technology, Wuhan 430074 (China)
2014-06-15
An insulated core transformer (ICT) power supply is an ideal high-voltage generator for irradiation accelerators with energy lower than 3 MeV. However, there is a significant problem that the structure of the segmented cores leads to an increase in the leakage flux and voltage differences between rectifier disks. A high level of consistency in the output of the disks helps to achieve a compact structure by improving the utilization of both the rectifier components and the insulation distances, and consequently increase the output voltage of the power supply. The output voltages of the disks which are far away from the primary coils need to be improved to reduce their inhomogeneity. In this study, by investigating and comparing the existing compensation methods, a new combined compensation method is proposed, which increases the turns on the secondary coils and employs parallel capacitors to improve the consistency of the disks, while covering the entire operating range of the power supply. This method turns out to be both feasible and effective during the development of an ICT power supply. The non-uniformity of the output voltages of the disks is less than 3.5% from no-load to full-load, and the power supply reaches an output specification of 350 kV/60 mA.
Directory of Open Access Journals (Sweden)
Pedro Roncero-Sànchez
2014-04-01
Full Text Available Electric power systems are among the greatest achievements of the last century. Today, important issues, such as an ever-increasing demand, the flexible and reliable integration of distributed generation or a growth in disturbing loads, must be borne in mind. In this context, smart grids play a key role, allowing better efficiency of power systems. Power electronics provides solutions to the aforementioned matters, since it allows various energy sources to be integrated into smart grids. Nevertheless, the design of the various control schemes that are necessary for the correct operation of the power-electronic interface is a very important issue that must always be taken into consideration. This paper deals with the design of the control system of a distribution static synchronous compensator (DSTATCOM based on flying-capacitor multilevel converters. The control system is tailored to compensate for both voltage sags by means of reactive-power injection and voltage imbalances caused by unbalanced loads. The design of the overall control is carried out by using the root-locus and frequency-response techniques, improving both the transient response and the steady-state error of the closed-loop system. Simulation results obtained using PSCADTM/EMTDCTM (Manitoba Hydro International Ltd., Commerce Drive, Winnipeg, MB, Canada show the resultant voltage regulation.
Power, privilege and disadvantage: Intersectionality theory and political representation
Directory of Open Access Journals (Sweden)
Eline Severs
2017-06-01
Full Text Available This article critically reviews the extant literature on social group representation and clarifies the advantages of intersectionality theory for studying political representation. It argues that the merit of intersectionality theory can be found in its ontology of power. Intersectionality theory is founded on a relational conception of political power that locates the constitution of power relations within social interactions, such as political representation. As such, intersectionality theory pushes scholarship beyond studying representation inequalities —that are linked to presumably stable societal positions— to also consider the ways in which political representation (recreates positions of privilege and disadvantage.
Power grid, mains filtering and power line communications ... a root cause for incompatibilities
Coenen, Mart
2013-01-01
The power grid is intentionally meant to distribute electrical energy at the mains frequency, as produced by the electricity generating plants, towards the end-users. The three-phase low-voltage distribution network can be utilized more efficiently when a power factor of 1 is achieved and no
A Spatial Model for the Instantaneous Estimation of Wind Power at a Large Number of Unobserved Sites
DEFF Research Database (Denmark)
Lenzi, Amanda; Guillot, Gilles; Pinson, Pierre
2015-01-01
We propose a hierarchical Bayesian spatial model to obtain predictive densities of wind power at a set of un-monitored locations. The model consists of a mixture of Gamma density for the non-zero values and degenerated distributions at zero. The spatial dependence is described through a common...... Gaussian random field with a Matérn covariance. For inference and prediction, we use the GMRF-SPDE approximation implemented in the R-INLA package. We showcase the method outlined here on data for 336 wind farms located in Denmark. We test the predictions derived from our method with model-diagnostic tools...
Mobile Hybrid Power System Theory of Operation
Pierce, Timothy M. Jr.
2016-01-01
Efficiency is a driving constraint for electrical power systems as global energy demands are ever increasing. Followed by the introduction of diesel generators, electricity has become available in more locations than ever. However, operating a diesel generator on its own is not the most energy efficient. This is because the high crest factor loads, of many applications, decrease the fuel efficiency of a hydrocarbon generator. To understand this, we need to understand how an electrical load af...
Fulmer, Ingrid Smithey; Shaw, Jason D
2018-06-07
Compensation research has focused traditionally on how pay design characteristics (e.g., pay level, individual or group incentives) relate to average employee outcomes and, in toto, on how these outcomes affect organizational performance. Recently, scholars have begun to pay more attention to how individuals vary in the strength of their reactions to pay. Empirical research in several disciplines examines how the interplay of pay systems and person-based characteristics (psychological individual differences, demographics, and relative performance or position in a group) relate to important work-related outcomes. We develop a compensation-activation theory that frames compensation design characteristics as workplace "situations" providing cues that activate individuals' corresponding fundamental social motives made salient due to chronic or transient person-based characteristics. Where activation occurs, stronger-than-average responses to the compensation "situation" are expected. Using the theory as a lens, we synthesize and reinterpret existing research on person-based reactions to pay characteristics, including sorting, incentive/motivational effects, and effects on collective pay system reactions and unit/organizational outcomes. We conclude with a research agenda aimed at refining compensation-activation theory and advancing the study of compensation as it affects individual and organizational outcomes. (PsycINFO Database Record (c) 2018 APA, all rights reserved).
Kumar, Sanjiv; Kumar, Narendra
2017-06-01
In this work, supplementary sub-synchronous damping controllers (SSDC) are proposed for damping sub-synchronous oscillations in power systems with series compensated transmission lines. Series compensation have extensively been used as effective means of increasing the power transfer capability of a transmission lines and improving transient stability limits of power systems. Series compensation with transmission lines may cause sub-synchronous resonance (SSR). The eigenvalue investigation tool is used to ascertain the existence of SSR. It is shown that the addition of supplementary controller is able to stabilize all unstable modes for T-network model. Eigenvalue investigation and time domain transient simulation of detailed nonlinear system are considered to investigate the performance of the controllers. The efficacies of the suggested supplementary controllers are compared on the IEEE first benchmark model for computer simulations of SSR by means of time domain simulation in Matlab/Simulink environment. Supplementary SSDC are considered in order to compare effectiveness of SSDC during higher loading in alleviating the small signal stability problem.
Transistor-based filter for inhibiting load noise from entering a power supply
Taubman, Matthew S
2013-07-02
A transistor-based filter for inhibiting load noise from entering a power supply is disclosed. The filter includes a first transistor having an emitter coupled to a power supply, a collector coupled to a load, and a base. The filter also includes a first capacitor coupled between the base of the first transistor and a ground terminal. The filter further includes an impedance coupled between the base and a node between the collector and the load, or a second transistor and second capacitor. The impedance can be a resistor or an inductor.
A fast switch, combiner and narrow-band filter for high-power millimetre wave beams
Kasparek, W.; Petelin, M. I.; Shchegolkov, D. Yu; Erckmann, V.; Plaum, B.; Bruschi, A.; ECRH Groups at IPP Greifswald; Karlsruhe, FZK; Stuttgart, IPF
2008-05-01
A fast directional switch (FADIS) is described, which allows controlled switching of high-power microwaves between two outputs. A possible application could be synchronous stabilization of neoclassical tearing modes (NTMs). Generally, the device can be used to share the installed EC power between different types of launchers or different applications (e.g. in ITER, midplane/upper launcher). The switching is performed electronically without moving parts by a small frequency-shift keying of the gyrotron (some tens of megahertz), and a narrow-band diplexer. The device can be operated as a beam combiner also, which offers attractive transmission perspectives in multi-megawatt ECRH systems. In addition, these diplexers are useful for plasma diagnostic systems employing high-power sources due to their filter characteristics. The principle and the design of a four-port quasi-optical resonator diplexer is presented. Low-power measurements of switching contrast, mode purity and efficiency show good agreement with theory. Preliminary frequency modulation characteristics of gyrotrons are shown, and first results from high-power switching experiments using the ECRH system for W7-X are presented.
A fast switch, combiner and narrow-band filter for high-power millimetre wave beams
International Nuclear Information System (INIS)
Kasparek, W.; Plaum, B.; Petelin, M.I.; Shchegolkov, D.Yu; Erckmann, V.; Bruschi, A.
2008-01-01
A fast directional switch (FADIS) is described, which allows controlled switching of high-power microwaves between two outputs. A possible application could be synchronous stabilization of neoclassical tearing modes (NTMs). Generally, the device can be used to share the installed EC power between different types of launchers or different applications (e.g. in ITER, midplane/upper launcher). The switching is performed electronically without moving parts by a small frequency-shift keying of the gyrotron (some tens of megahertz), and a narrow-band diplexer. The device can be operated as a beam combiner also, which offers attractive transmission perspectives in multi-megawatt ECRH systems. In addition, these diplexers are useful for plasma diagnostic systems employing high-power sources due to their filter characteristics. The principle and the design of a four-port quasi-optical resonator diplexer is presented. Low-power measurements of switching contrast, mode purity and efficiency show good agreement with theory. Preliminary frequency modulation characteristics of gyrotrons are shown, and first results from high-power switching experiments using the ECRH system for W7-X are presented
Time delay control of power converters: Mixed frame and stationary-frame variants
DEFF Research Database (Denmark)
Blaabjerg, Frede; Loh, P.C.; Tang, Y.
2008-01-01
In this paper, a mixed-frame and a stationary-frame time delay current controller are proposed for high precision reference tracking and disturbance rejection of power converters. In particular, the controllers use a proportional-resonant regulator in the stationary frame for regulating...... the positive and negative-sequence fundamental currents, which are known to directly influence the flow of active and reactive power in most energy conversion systems. Moreover, for the tracking or compensation of harmonics, the controllers include a time delay control path in either the synchronous...... or stationary frame, whose inherent feedback and feedforward structure can be proven to resemble a bank of resonant filters in either reference frames. Unlike other existing controllers, the proposed time delay controllers function by introducing multiple resonant peaks at only those harmonic frequencies...
DEFF Research Database (Denmark)
Bai, Haofeng; Wang, Xiongfei; Blaabjerg, Frede
2018-01-01
The output currents of high-power Voltage Source Inverters (VSIs) are distorted by the switching harmonics and the background harmonics in the grid voltage. This paper presents an active harmonic filtering scheme for high-power, low-frequency switching VSIs with an additional auxiliary VSI. In th...
Z-Source Inverter Based Power Quality Compensator with Enhanced Ride-Through Capability
DEFF Research Database (Denmark)
Gajanayake, C.J.; Vilathgamuwa, D.M.; Loh, P.C.
2007-01-01
Distributed generation has been gaining acceptance over the years and it has the potential to provide reliable power to sensitive loads. However, distributed networks are prone to unbalanced faults conditions. This makes single inverter DG systems unsuitable as UPS systems. This paper proposes...... a Zsource inverter based power quality compensator and a control structure that supplies high quality voltage to the connected sensitive load in the presence of other non linear loads. The proposed topology consists of combination of shunt and series inverters connected to a common Z-source impedance...... network. The shunt inverter is controlled to maintain a quality voltage waveform at the load bus. Whereas the series inverter enhances the ride-through capability during grid faults, protects the shunt inverter by limiting the current and also controls the power delivered to the grid. The performance...
Multimedia transmission in MC-CDMA using adaptive subcarrier power allocation and CFO compensation
Chitra, S.; Kumaratharan, N.
2018-02-01
Multicarrier code division multiple access (MC-CDMA) system is one of the most effective techniques in fourth-generation (4G) wireless technology, due to its high data rate, high spectral efficiency and resistance to multipath fading. However, MC-CDMA systems are greatly deteriorated by carrier frequency offset (CFO) which is due to Doppler shift and oscillator instabilities. It leads to loss of orthogonality among the subcarriers and causes intercarrier interference (ICI). Water filling algorithm (WFA) is an efficient resource allocation algorithm to solve the power utilisation problems among the subcarriers in time-dispersive channels. The conventional WFA fails to consider the effect of CFO. To perform subcarrier power allocation with reduced CFO and to improve the capacity of MC-CDMA system, residual CFO compensated adaptive subcarrier power allocation algorithm is proposed in this paper. The proposed technique allocates power only to subcarriers with high channel to noise power ratio. The performance of the proposed method is evaluated using random binary data and image as source inputs. Simulation results depict that the bit error rate performance and ICI reduction capability of the proposed modified WFA offered superior performance in both power allocation and image compression for high-quality multimedia transmission in the presence of CFO and imperfect channel state information conditions.
International Nuclear Information System (INIS)
Park, Seong Ho; Kim, Tae Kyoung; Lee, Kyoung Ho; Kim, Ah Young; Han, Joon Koo; Choi, Byung Ihn
1999-01-01
For the quantitative comparison of the degree of enhancement in nodular hepatocellular carcinoma (HCC) at conventional and harmonic Power Doppler (PD) ultrasound (US). The average of %PDA of ten nodules gradually increased until 60 seconds after contrast injection and then gradually decreased. The average %PDA on conventional and harmonic PD US at 60 seconds were 34.9% and 19.5%, respectively. The average %PDA were significantly higher on conventional PD US than those on harmonic PD US at all times except at 20 seconds. The ratio of average %pda on conventional PD US to those on harmonic PD US became gradually larger after 120 seconds. Although contrast-enhanced harmonic PD US can be an effective method in evaluating the tumor vascularity of HCC because of less PD artifacts, the duration of effective enhancement was shorter and degree of enhancement is less than that of conventional PD US.
Extremum seeking x-ray position feedback using power line harmonic leakage as the perturbation
Directory of Open Access Journals (Sweden)
S. Zohar
2016-09-01
Full Text Available Small x-ray beam sizes necessary for probing nanoscale phenomena require exquisite stability to prevent data corruption by noise. One source of instability at synchrotron radiation x-ray beamlines is the slow detuning of x-ray optics to marginal alignment where the onset of clipping increases the beam’s susceptibility to higher frequency position oscillations. In this article, we show that a 1 μm amplitude horizontal x-ray beam oscillation driven by power line harmonic leakage into the electron storage ring can be used as perturbation for horizontal position extremum seeking feedback. Feedback performance is characterized by convergence to 1.5% away from maximum intensity at optimal alignment.
Directory of Open Access Journals (Sweden)
N. J. Milardovich
2014-10-01
Full Text Available A numerical investigation on the harmonic disturbances in low-voltage cables feeding large LED loads is reported. A frequency domain analysis on several commercially-available LEDs was performed to investigate the signature of the harmonic current injected into the power system. Four-core cables and four single-core cable arrangements (three phases and neutral of small, medium, and large conductor cross sections, with the neutral conductor cross section approximately equal to the half of the phase conductors, were examined. The cables were modelled by using electromagnetic finite-element analysis software. High harmonic power losses (up to 2.5 times the value corresponding to an undistorted current of the same rms value of the first harmonic of the LED current were found. A generalized ampacity model was employed for re-rating the cables. It was found that the cross section of the neutral conductor plays an important role in the derating of the cable ampacity due to the presence of a high-level of triplen harmonics in the distorted current. The ampacity of the cables should be derated by about 40 %, almost independent of the conductor cross sections. The calculation have shown that an incoming widespread use of LED lamps in lighting could create significant additional harmonic losses in the supplying low-voltage lines, and thus more severely harmonic emission limits should be defined for LED lamps.
DEFF Research Database (Denmark)
Mortezaei, Ali; Simoes, Marcelo; Savaghebi, Mehdi
2018-01-01
Cooperative control of power converters in a microgrid offers power quality enhancement at sensitive load buses. Such cooperation is particularly important in the presence of reactive, nonlinear and unbalanced loads. In this paper, a multi-master-slave-based control of Distributed Generators (DGs...... in a selective control strategy able to share each current component with desired percentage among the microgrid inverters. Simulation results are presented to demonstrate the effectiveness of the proposed method.......) interface converters in a three-phase four-wire islanded microgrid using the Conservative Power Theory (CPT) is proposed. Inverters located in close proximity operate as a group in master-salve mode. Slaves inject the available energy and compensate selectively unwanted current components of local loads...
Directory of Open Access Journals (Sweden)
Santosh Kumar Singh
2017-06-01
Full Text Available This paper presents a new hybrid method based on Gravity Search Algorithm (GSA and Recursive Least Square (RLS, known as GSA-RLS, to solve the harmonic estimation problems in the case of time varying power signals in presence of different noises. GSA is based on the Newton’s law of gravity and mass interactions. In the proposed method, the searcher agents are a collection of masses that interact with each other using Newton’s laws of gravity and motion. The basic GSA algorithm strategy is combined with RLS algorithm sequentially in an adaptive way to update the unknown parameters (weights of the harmonic signal. Simulation and practical validation are made with the experimentation of the proposed algorithm with real time data obtained from a heavy paper industry. A comparative performance of the proposed algorithm is evaluated with other recently reported algorithms like, Differential Evolution (DE, Particle Swarm Optimization (PSO, Bacteria Foraging Optimization (BFO, Fuzzy-BFO (F-BFO hybridized with Least Square (LS and BFO hybridized with RLS algorithm, which reveals that the proposed GSA-RLS algorithm is the best in terms of accuracy, convergence and computational time.
Directory of Open Access Journals (Sweden)
Nian-Cheng Zhou
2015-02-01
Full Text Available Unbalanced voltage will inevitably cause power and DC voltage fluctuations in a three-phase PV system. The deterioration of power quality will do great harm to the PV panels and the loads, so it is necessary to suppress the power fluctuations. This paper further explores the coefficients control strategy of PV converters under unbalanced voltage conditions, aiming to suppress power fluctuations by controlling the injection of some specific orders of current harmonics into the grid. In order to achieve this, the current reference of the PV inverter has been changed by bringing in two control coefficients, and the expression of each order of the current harmonics has been deduced. Based on the standards of PV systems, the regions from which the coefficients can be selected are determined. Then, by tuning these coefficients in the feasible regions, the output parameters (power fluctuation, current THD and odd harmonics can be controlled precisely. The model of this method is built and simulated in PSCAD/EMTDC, and as a result, it is shown that the power fluctuations can be restricted according to different power quality requirements.
Intrinsic dendritic filtering gives low-pass power spectra of local field potentials
DEFF Research Database (Denmark)
Lindén, Henrik; Pettersen, Klas H; Einevoll, Gaute T
2010-01-01
of contributions to the LFP from a single layer-5 pyramidal neuron and a single layer-4 stellate neuron receiving synaptic input. An intrinsic dendritic low-pass filtering effect of the LFP signal, previously demonstrated for extracellular signatures of action potentials, is seen to strongly affect the LFP power...... spectra, even for frequencies as low as 10 Hz for the example pyramidal neuron. Further, the LFP signal is found to depend sensitively on both the recording position and the position of the synaptic input: the LFP power spectra recorded close to the active synapse are typically found to be less low......The local field potential (LFP) is among the most important experimental measures when probing neural population activity, but a proper understanding of the link between the underlying neural activity and the LFP signal is still missing. Here we investigate this link by mathematical modeling...
Directory of Open Access Journals (Sweden)
Menxi Xie
2017-06-01
Full Text Available High performance synchronization methord is citical for grid connected power converter. For single-phase system, power based phase-locked loop(pPLL uses a multiplier as phase detector(PD. As single-phase grid voltage is distorted, the phase error information contains ac disturbances oscillating at integer multiples of fundamental frequency which lead to detection error. This paper presents a new scheme based on moving average filter(MAF applied in-loop of pPLL. The signal characteristic of phase error is dissussed in detail. A predictive rule is adopted to compensate the delay induced by MAF, thus achieving fast dynamic response. In the case of frequency deviate from nomimal, estimated frequency is fed back to adjust the filter window length of MAF and buffer size of predictive rule. Simulation and experimental results show that proposed PLL achieves good performance under adverse grid conditions.
Cyber Power Theory First, Then Information Operations
National Research Council Canada - National Science Library
Smart, Antoinette G
2001-01-01
...) seems disconcerting, at least on the surface. Think tanks, government research organizations, and learned individuals have all pointed to the need for a viable theory of IO, yet no such theory has emerged...
Utilization of graph theory in security analysis of power grid
Directory of Open Access Journals (Sweden)
Dalibor Válek
2014-12-01
Full Text Available This paper describes way how to use graph theory in security analysis. As an environment is used network of power lines and devices which are included here. Power grid is considered as a system of nodes which make together graph (network. On the simple example is applied Fiedler´s theory which is able to select the most important power lines of whole network. Components related to these lines are logicly ordered and considered by author´s modified analysis. This method has been improved and optimalized for risks related with illegal acts. Each power grid component has been connected with possible kind of attack and every of this device was gradually evaluated by five coefficients which takes values from 1 to 10. On the coefficient basis was assessed the level of risk. In the last phase the most risky power grid components have been selected. On the selected devices have been proposed security measures.