Load calculations of radiant cooling systems for sizing the plant
DEFF Research Database (Denmark)
Bourdakis, Eleftherios; Kazanci, Ongun Berk; Olesen, Bjarne W.
2015-01-01
The aim of this study was, by using a building simulation software, to prove that a radiant cooling system should not be sized based on the maximum cooling load but at a lower value. For that reason six radiant cooling models were simulated with two control principles using 100%, 70% and 50......% of the maximum cooling load. It was concluded that all tested systems were able to provide an acceptable thermal environment even when the 50% of the maximum cooling load was used. From all the simulated systems the one that performed the best under both control principles was the ESCS ceiling system. Finally...... it was proved that ventilation systems should be sized based on the maximum cooling load....
DEFF Research Database (Denmark)
Causone, Francesco; Corgnati, Stefano P.; Filippi, Marco
2010-01-01
The study of the influence of solar radiation on the built environment is a basic issue in building physics and currently it is extremely important because glazed envelopes are widely used in contemporary architecture. In the present study, the removal of solar heat gains by radiant cooling systems...... is investigated. Particular attention is given to the portion of solar radiation converted to cooling load, without taking part in thermal absorption phenomena due to the thermal mass of the room. This specific component of the cooling load is defined as the Direct Solar Load. A simplified procedure to correctly...... calculate the magnitude of the Direct Solar Load in cooling load calculations is proposed and it is implemented with the Heat Balance method and the Radiant Time Series method. The F ratio of the solar heat gains directly converted to cooling load, in the case of a low thermal mass radiant ceiling...
Cooling load calculation by the radiant time series method - effect of solar radiation models
Energy Technology Data Exchange (ETDEWEB)
Costa, Alexandre M.S. [Universidade Estadual de Maringa (UEM), PR (Brazil)], E-mail: amscosta@uem.br
2010-07-01
In this work was analyzed numerically the effect of three different models for solar radiation on the cooling load calculated by the radiant time series' method. The solar radiation models implemented were clear sky, isotropic sky and anisotropic sky. The radiant time series' method (RTS) was proposed by ASHRAE (2001) for replacing the classical methods of cooling load calculation, such as TETD/TA. The method is based on computing the effect of space thermal energy storage on the instantaneous cooling load. The computing is carried out by splitting the heat gain components in convective and radiant parts. Following the radiant part is transformed using time series, which coefficients are a function of the construction type and heat gain (solar or non-solar). The transformed result is added to the convective part, giving the instantaneous cooling load. The method was applied for investigate the influence for an example room. The location used was - 23 degree S and 51 degree W and the day was 21 of January, a typical summer day in the southern hemisphere. The room was composed of two vertical walls with windows exposed to outdoors with azimuth angles equals to west and east directions. The output of the different models of solar radiation for the two walls in terms of direct and diffuse components as well heat gains were investigated. It was verified that the clear sky exhibited the less conservative (higher values) for the direct component of solar radiation, with the opposite trend for the diffuse component. For the heat gain, the clear sky gives the higher values, three times higher for the peek hours than the other models. Both isotropic and anisotropic models predicted similar magnitude for the heat gain. The same behavior was also verified for the cooling load. The effect of room thermal inertia was decreasing the cooling load during the peak hours. On the other hand the higher thermal inertia values are the greater for the non peak hours. The effect
A RTS-based method for direct and consistent calculating intermittent peak cooling loads
International Nuclear Information System (INIS)
Chen Tingyao; Cui, Mingxian
2010-01-01
The RTS method currently recommended by ASHRAE Handbook is based on continuous operation. However, most of air-conditioning systems, if not all, in commercial buildings, are intermittently operated in practice. The application of the current RTS method to intermittent air-conditioning in nonresidential buildings could result in largely underestimated design cooling loads, and inconsistently sized air-conditioning systems. Improperly sized systems could seriously deteriorate the performance of system operation and management. Therefore, a new method based on both the current RTS method and the principles of heat transfer has been developed. The first part of the new method is the same as the current RTS method in principle, but its calculation procedure is simplified by the derived equations in a close form. The technical data available in the current RTS method can be utilized to compute zone responses to a change in space air temperature so that no efforts are needed for regenerating new technical data. Both the overall RTS coefficients and the hourly cooling loads computed in the first part are used to estimate the additional peak cooling load due to a change from continuous operation to intermittent operation. It only needs one more step after the current RTS method to determine the intermittent peak cooling load. The new RTS-based method has been validated by EnergyPlus simulations. The root mean square deviation (RMSD) between the relative additional peak cooling loads (RAPCLs) computed by the two methods is 1.8%. The deviation of the RAPCL varies from -3.0% to 5.0%, and the mean deviation is 1.35%.
International Nuclear Information System (INIS)
Simonkova, J.
1988-01-01
The problems are summed up of the dynamic calculation of cooling towers with forced and natural air draft. The quantities and relations are given characterizing the simultaneous exchange of momentum, heat and mass in evaporative water cooling by atmospheric air in the packings of cooling towers. The method of solution is clarified in the calculation of evaporation criteria and thermal characteristics of countercurrent and cross current cooling systems. The procedure is demonstrated of the calculation of cooling towers, and correction curves and the effect assessed of the operating mode at constant air number or constant outlet air volume flow on their course in ventilator cooling towers. In cooling towers with the natural air draft the flow unevenness is assessed of water and air relative to its effect on the resulting cooling efficiency of the towers. The calculation is demonstrated of thermal and resistance response curves and cooling curves of hydraulically unevenly loaded towers owing to the water flow rate parameter graded radially by 20% along the cross-section of the packing. Flow rate unevenness of air due to wind impact on the outlet air flow from the tower significantly affects the temperatures of cooled water in natural air draft cooling towers of a design with lower demands on aerodynamics, as early as at wind velocity of 2 m.s -1 as was demonstrated on a concrete example. (author). 11 figs., 10 refs
Dijk, H.A.L. van; Spiekman, M.E.; Hoes-van Oeffelen, E.C.M.
2016-01-01
EN ISO 52016-1 presents a coherent set of calculation methods at different levels of detail, for the (sensible) energy needs for the space heating and cooling and (latent) energy needs (de)humidification of a building and/or internal temperatures and heating and/or cooling loads, including the
Cooling load calculations of radiant and all-air systems for commercial buildings
DEFF Research Database (Denmark)
Bourdakis, Eleftherios; Bauman, Fred; Schiavon, Stefano
The authors simulated in TRNSYS three radiant systems coupled with a 50% sized variable air volume (VAV) system and a 50% sized all-air VAV system with night ventilation. The objective of this study was to identify the differences in the cooling load profiles of the examined systems when they are......The authors simulated in TRNSYS three radiant systems coupled with a 50% sized variable air volume (VAV) system and a 50% sized all-air VAV system with night ventilation. The objective of this study was to identify the differences in the cooling load profiles of the examined systems when...
Energy Technology Data Exchange (ETDEWEB)
Nadler, Norbert [CSE Nadler, Oranienburg (Germany)
2010-07-01
Due to the publication of the regulation DIN EN 15 251, the design criteria for the thermal indoor climate during the cooling load calculation and heating load calculation also are specified on European level. The regulation determines that the design values for the operational ambient temperature can be determined from the percentage of the dissatisfied values (PPD value according to DIN EN ISO 773). On national level, the exact definition is to take place for typical activities and thermal insulation values of the clothing. Alternatively, the direct use of the PPD value during the layout also is possible. It is shown that this method is to be preferred and that the most cooling load programs available at the market do not correspond to the generally accepted rules of the technology any longer.
24 CFR 3280.508 - Heat loss, heat gain and cooling load calculations.
2010-04-01
....506). The effect of framing on the U-value must be included in the Uo calculation. Other low-R-value... chapters are not applicable: 23.1Steel Frame Construction 23.2Masonry Construction 23.3Foundations and...
International Nuclear Information System (INIS)
Coic, P.
1984-01-01
The principle of a cooling tower is first presented. The equations of the problem are given; the modeling of load losses and heat transfer is described. Then, the numerical method based on a finite difference discrete method is described. Finally, the different results of the calculations carried out in the case of an industrial operation are presented [fr
International Nuclear Information System (INIS)
EL Fawal, M.M.; Gadalla, A.A.; Taher, B.M.
2010-01-01
In terms of nuclear safety, the most important function of ventilation air conditioning (VAC) systems is to maintain safe ambient conditions for components and structures important to safety inside the nuclear facility and to maintain appropriate working conditions for the plant's operating and maintenance staff. As a part of a study aimed to evaluate the performance of VAC system of the nuclear fuel cycle facility (NFCF) a computer model was developed and verified to evaluate the thermal loads and cooling requirements for different zones of fuel processing facility. The program is based on transfer function method (TFM) and it is used to calculate the dynamic heat gain by various multilayer walls constructions and windows hour by hour at any orientation of the building. The developed model was verified by comparing the obtained calculated results of the solar heat gain by a given building with the corresponding calculated values using finite difference method (FDM) and total equivalent temperature different method (TETD). As an example the developed program is used to calculate the cooling loads of the different zones of a typical nuclear fuel facility the results showed that the cooling capacities of the different cooling units of each zone of the facility meet the design requirements according to safety regulations in nuclear facilities.
Procedures for Calculating Residential Dehumidification Loads
Energy Technology Data Exchange (ETDEWEB)
Winkler, Jon [National Renewable Energy Lab. (NREL), Golden, CO (United States); Booten, Chuck [National Renewable Energy Lab. (NREL), Golden, CO (United States)
2016-06-01
Residential building codes and voluntary labeling programs are continually increasing the energy efficiency requirements of residential buildings. Improving a building's thermal enclosure and installing energy-efficient appliances and lighting can result in significant reductions in sensible cooling loads leading to smaller air conditioners and shorter cooling seasons. However due to fresh air ventilation requirements and internal gains, latent cooling loads are not reduced by the same proportion. Thus, it's becoming more challenging for conventional cooling equipment to control indoor humidity at part-load cooling conditions and using conventional cooling equipment in a non-conventional building poses the potential risk of high indoor humidity. The objective of this project was to investigate the impact the chosen design condition has on the calculated part-load cooling moisture load, and compare calculated moisture loads and the required dehumidification capacity to whole-building simulations. Procedures for sizing whole-house supplemental dehumidification equipment have yet to be formalized; however minor modifications to current Air-Conditioner Contractors of America (ACCA) Manual J load calculation procedures are appropriate for calculating residential part-load cooling moisture loads. Though ASHRAE 1% DP design conditions are commonly used to determine the dehumidification requirements for commercial buildings, an appropriate DP design condition for residential buildings has not been investigated. Two methods for sizing supplemental dehumidification equipment were developed and tested. The first method closely followed Manual J cooling load calculations; whereas the second method made more conservative assumptions impacting both sensible and latent loads.
Technical manual for calculating cooling pond performance
International Nuclear Information System (INIS)
Krstulovich, S.F.
1988-01-01
This manual is produced in response to a growing number of requests for a technical aid to explain methods for simulating cooling pond performance. As such, it is a compilation of reports, charts and graphs developed through the years for use in analyzing situations. Section II contains a report summarizing the factors affecting cooling pond performance and lists statistical parameters used in developing performance simulations. Section III contains the graphs of simulated cooling pond performance on an hourly basis for various combinations of criteria (wind, solar, depth, air temperature and humidity) developed from the report in Section II. Section IV contains correspondence describing how to develop further data from the graphs in Section III, as well as mathematical models for the system of performance calculation. Section V contains the formulas used to simulate cooling pond performances in a cascade arrangement, such as the Fermilab Main Ring ponds. Section VI contains the calculations currently in use to evaluate the Main Ring pond performance based on current flows and Watts loadings. Section VII contains the overall site drawing of the Main Ring cooling ponds with thermal analysis and physical data
Alaska Village Electric Load Calculator
Energy Technology Data Exchange (ETDEWEB)
Devine, M.; Baring-Gould, E. I.
2004-10-01
As part of designing a village electric power system, the present and future electric loads must be defined, including both seasonal and daily usage patterns. However, in many cases, detailed electric load information is not readily available. NREL developed the Alaska Village Electric Load Calculator to help estimate the electricity requirements in a village given basic information about the types of facilities located within the community. The purpose of this report is to explain how the load calculator was developed and to provide instructions on its use so that organizations can then use this model to calculate expected electrical energy usage.
Thermal calculations for water cooled research reactors
International Nuclear Information System (INIS)
Fabrega, S.
1979-01-01
The formulae and the more important numerical data necessary for thermic calculations on the core of a research reactor, cooled with low pressure water, are presented. Most of the problems met by the designer and the operator are dealt with (calculations margins, cooling after shut-down). Particular cases are considered (gas release, rough walls, asymmetric cooling slabs etc.), which are not generally envisaged in works on general thermics
Energy Technology Data Exchange (ETDEWEB)
Rojas Garcia, E.; Fonseca Gonzalez, N. A.
2005-07-01
The present report tries to develop the calculation of thermical loads and to define the capacity of the equipments of cooling and ventilation that should have the engines test bench that is being ensemble in the installation of the CIEMAT named {sup D}iesel engine emissions study bench (E65-P0). The test bench is formed essentially by a dynamometrical brake and an engine connected at previous one, both of them inside a cabin of isolation acoustic. The thermical loads to be dissipated will be calculated for all the elements that compose the bench and considering his maximum values, to determine the suitable system of cooling air - water of the devices and ventilation in the cabin. (Author) 2 refs.
Directory of Open Access Journals (Sweden)
Norbert Moritz
2013-03-01
Full Text Available Great efforts are still put into the design process of advanced film-cooling configurations. In particular, the vanes and blades of turbine front stages have to be cooled extensively for a safe operation. The conjugate calculation technique is used for the three-dimensional thermal load prediction of a film-cooled test blade of a modern gas turbine. Thus, it becomes possible to take into account the interaction of internal flows, external flow, and heat transfer without the prescription of heat transfer coefficients. The focus of the investigation is laid on the leading edge part of the blade. The numerical model consists of all internal flow passages and cooling hole rows at the leading edge. Furthermore, the radial gap flow is also part of the model. The comparison with thermal pyrometer measurements shows that with respect to regions with high thermal load a qualitatively and quantitatively good agreement of the conjugate results and the measurements can be found. In particular, the region in the vicinity of the mid-span section is exposed to a higher thermal load, which requires further improvement of the cooling arrangement. Altogether the achieved results demonstrate that the conjugate calculation technique is applicable for reasonable prediction of three-dimensional thermal load of complex cooling configurations for blades.
A simplified model of dynamic interior cooling load evaluation for office buildings
International Nuclear Information System (INIS)
Ding, Yan; Zhang, Qiang; Wang, Zhaoxia; Liu, Min; He, Qing
2016-01-01
Highlights: • The core interior disturbance was determined by principle component analysis. • Influences of occupants on cooling load should be described using time series. • A simplified model was built to evaluate dynamic interior building cooling load. - Abstract: Predicted cooling load is a valuable tool for assessing the operation of air-conditioning systems. Compared with exterior cooling load, interior cooling load is more unpredictable. According to principle components analysis, occupancy was proved to be a typical factor influencing interior cooling loads in buildings. By exploring the regularity of interior disturbances in an office building, a simplified evaluation model for interior cooling load was established in this paper. The stochastic occupancy rate was represented by a Markov transition model. Equipment power, lighting power and fresh air were all related to occupancy rate based on time sequence. The superposition of different types of interior cooling loads was also considered in the evaluation model. The error between the evaluation results and measurement results was found to be lower than 10%. In reference to the cooling loads calculated by the traditional design method and area-based method in case study office rooms, the evaluated cooling loads were suitable for operation regulation.
Influence of buildings geometrical and physical parameters on thermal cooling load
International Nuclear Information System (INIS)
Melo, C.
1980-09-01
A more accurate method to evaluate the thermal cooling load in buildings and to analyze the influence of geometrical and physical parameters on air conditioning calculations is presented. The sensitivity of the cooling load, considering the thermal capacity of the materials, was simulated in a computer for several different situations. (Author) [pt
Pile Load Capacity – Calculation Methods
Directory of Open Access Journals (Sweden)
Wrana Bogumił
2015-12-01
Full Text Available The article is a review of the current problems of the foundation pile capacity calculations. The article considers the main principles of pile capacity calculations presented in Eurocode 7 and other methods with adequate explanations. Two main methods are presented: α – method used to calculate the short-term load capacity of piles in cohesive soils and β – method used to calculate the long-term load capacity of piles in both cohesive and cohesionless soils. Moreover, methods based on cone CPTu result are presented as well as the pile capacity problem based on static tests.
Energy Technology Data Exchange (ETDEWEB)
Silva, Hilton Penha [Parana Univ., Curitiba, PR (Brazil). Dept. de Engenharia Mecanica. Dept. de Engenharia do Produto; Passos, Alex Sandro Barbosa [Parana Univ., Curitiba, PR (Brazil). Dept. de Engenharia Mecanica. Dept. de Pesquisa e Desenvolvimento do Produto
2001-07-01
This article describes a method for calculation of the loss of load curve for the ventilation axial circuits. The method assumes the ventilation circuit representation in a way similar to the electrical circuits. The great difficulty of circuit solution resides in the non linearity of the loss of load resistances and the equations relating the pressures and flows. The method is based on the association of the resistance curves of loss of load in a such way that, when the resistance curve of the total circuit loss of load is obtained, the blower operation point can be easily obtained and, consequently, the individual flows for each section of the circuit.
Calculations of slurry pump jet impingement loads
International Nuclear Information System (INIS)
Wu, T.T.
1996-01-01
This paper presents a methodology to calculate the impingement load in the region of a submerged turbulent jet where a potential core exits and the jet is not fully developed. The profile of the jet flow velocities is represented by a piece-wise linear function which satisfies the conservation of momentum flux of the jet flow. The adequacy of the of the predicted jet expansion is further verified by considering the continuity of the jet flow from the region of potential core to the fully developed region. The jet impingement load can be calculated either as a direct impingement force or a drag force using the jet velocity field determined by the methodology presented
Load calculation and system evaluation for electric vehicle climate control
International Nuclear Information System (INIS)
Aceves-Saborio, S.; Comfort, W.J.
1994-01-01
Providing air conditioning for electric vehicles (EV's) represents an important challenge, because vapor-compression air conditioners, which are common in gasoline-powered vehicles, may consume a substantial part of the total energy stored in the EV battery. The authors' work has two major parts: a cooling and heating load calculation for EV's, and an evaluation of several systems that can be used to provide the desired cooling and heating in EV's. Four cases are studied: short-range and full-range EV's are each analyzed twice, first with the regular vehicle equipment, and then with a fan and heat-reflecting windows, to reduce hot soak. Results indicate that for the batteries currently available for EV propulsion, an ice storage system has the minimum weight of all the systems considered. Vapor-compression air conditioners have the minimum for battery storage capacities above 270 kJ/kg
Calculation of thermal deformations in water-cooled monochromator crystals
International Nuclear Information System (INIS)
Nakamura, Ario; Hashimoto, Shinya; Motohashi, Haruhiko
1994-11-01
Through calculation of temperature distribution and thermal deformation of monochromators, optical degradation by the heat loads in SPring-8 have been discussed. Cooling experiments were made on three models of copper structures with the JAERI Electron Beam Irradiation Stand (JEBIS) and the results were used to estimate heat transfer coefficients in the models. The heat transfer coefficients have been adopted to simulate heating processes on silicon models of the same structures as the copper models, for which radiations from the SPring-8 bending magnet and the JAERI prototype undulator (WPH-33J) were considered. It has been concluded that, in the case of bending magnet (with power density of 0.27[MW/m 2 ] on monochromator surface), the temperature at the surface center reaches about 30[degC] from the initial temperature of 27[degC] in all the models. In the case of WPH-33J (with power density of 8.2[MW/m 2 ]), the temperature reaches about 200 to 280[degC] depending on the models. The radiation from WPH-33J yields slope errors bigger than the Darwin's width(23[μrad]). (author)
Calculation of cooling tower plumes for high pressure wintry situations
International Nuclear Information System (INIS)
Gassmann, F.; Tinguely, M.; Haschke, D.
1982-12-01
The diffusion of the plumes of the projected nuclear power plants at Kaiseraugst and Schwoerstadt, during high pressure wintry conditions, has been examined using a mathematical model to simulate the plumes. For these calculations, microaerological measurements were made in the proximity of Kaiseraugst and Schwoerstadt. These give a typical image of the weather during high pressure wintry conditions, which is normally associated with an inversion, sometimes strong, at a low height. Dry cooling towers with natural draught, which offer an alternative solution to the wet cooling towers proposed for Kasieraugst, are examined equally. (Auth./G.T.H.)
Amelioration of the cooling load based chiller sequencing control
International Nuclear Information System (INIS)
Huang, Sen; Zuo, Wangda; Sohn, Michael D.
2016-01-01
Highlights: • We developed a new approach for the optimal load distribution for chillers. • We proposed a new approach to optimize the number of operating chillers. • We provided a holistic solution to address chiller sequencing control problems. - Abstract: Cooling Load based Control (CLC) for the chiller sequencing is a commonly used control strategy for multiple-chiller plants. To improve the energy efficiency of these chiller plants, researchers proposed various CLC optimization approaches, which can be divided into two groups: studies to optimize the load distribution and studies to identify the optimal number of operating chillers. However, both groups have their own deficiencies and do not consider the impact of each other. This paper aims to improve the CLC by proposing three new approaches. The first optimizes the load distribution by adjusting the critical points for the chiller staging, which is easier to be implemented than existing approaches. In addition, by considering the impact of the load distribution on the cooling tower energy consumption and the pump energy consumption, this approach can achieve a better energy saving. The second optimizes the number of operating chillers by modulating the critical points and the condenser water set point in order to achieve the minimal energy consumption of the entire chiller plant that may not be guaranteed by existing approaches. The third combines the first two approaches to provide a holistic solution. The proposed three approaches were evaluated via a case study. The results show that the total energy consumption saving for the studied chiller plant is 0.5%, 5.3% and 5.6% by the three approaches, respectively. An energy saving of 4.9–11.8% can be achieved for the chillers at the cost of more energy consumption by the cooling towers (increases of 5.8–43.8%). The pumps’ energy saving varies from −8.6% to 2.0%, depending on the approach.
Calculating the evaporated water flow in a wet cooling tower
International Nuclear Information System (INIS)
Grange, J.L.
1994-04-01
On a cooling tower, it is necessary to determine the evaporated water flow in order to estimate the water consumption with a good accuracy according to the atmospheric conditions, and in order to know the characteristics of the plume. The evaporated flow is small compared to the circulating flow. A direct measurement is very inaccurate and cannot be used. Only calculation can give a satisfactory valuation. The two usable theories are the Merkel's one in which there are some simplifying assumptions, and the Poppe's one which is more exact. Both theories are used in the numerical code TEFERI which has been developed and is run by Electricite de France. The results obtained by each method are compared and validated by measurements made in the hot air of a cooling tower. The consequences of each hypothesis of Merkel's theory are discussed. This theory does not give the liquid water content in the plume and it under-estimates the evaporated flow all the lower the ambient temperature is. On the other hand, the Poppe's method agrees very closely with the measurements as well for the evaporated flow than for the liquid water concentration. This method is used to establish the specific consumption curves of the great nuclear plants cooling towers as well as to calculate the emission of liquid water drops in the plumes. (author). 11 refs., 9 figs
Heat transfer calculations on the KNK II emergency cooling system
International Nuclear Information System (INIS)
Vossebrecker, H.; Groenefeld, G.
1976-12-01
The Licensing Authority had demanded that in case of the change of the KNK thermal core into a fast core the decay heat removal system must be improved by a diverse and spatially separated emergency cooling system. In order to meet this requirement an existing nitrogen system of the facility is extended in such a manner that the decay heat will be removed by a nitrogen flow passing through the gap between reactor vessel and guard vessel. The heat transport from the core to the vessel is accomplished by natural convection flow rates which are generated by density differences between the hot core subassemblies, the reflector subassemblies and other passages between the upper and the lower plenum. The calculations show that the maximum temperatures in the core do not reach the sodium boiling-point. The maximum vessel temperature is 673 deg. C. In this report the function of the emergency cooling system and the methods of calculation are described, the input data and the results are stated and it is shown that the calculated temperatures are conservative [de
Mathematical model and calculation of water-cooling efficiency in a film-filled cooling tower
Laptev, A. G.; Lapteva, E. A.
2016-10-01
Different approaches to simulation of momentum, mass, and energy transfer in packed beds are considered. The mathematical model of heat and mass transfer in a wetted packed bed for turbulent gas flow and laminar wave counter flow of the fluid film in sprinkler units of a water-cooling tower is presented. The packed bed is represented as the set of equivalent channels with correction to twisting. The idea put forward by P. Kapitsa on representation of waves on the interphase film surface as elements of the surface roughness in interaction with the gas flow is used. The temperature and moisture content profiles are found from the solution of differential equations of heat and mass transfer written for the equivalent channel with the volume heat and mass source. The equations for calculation of the average coefficients of heat emission and mass exchange in regular and irregular beds with different contact elements, as well as the expression for calculation of the average turbulent exchange coefficient are presented. The given formulas determine these coefficients for the known hydraulic resistance of the packed bed element. The results of solution of the system of equations are presented, and the water temperature profiles are shown for different sprinkler units in industrial water-cooling towers. The comparison with experimental data on thermal efficiency of the cooling tower is made; this allows one to determine the temperature of the cooled water at the output. The technical solutions on increasing the cooling tower performance by equalization of the air velocity profile at the input and creation of an additional phase contact region using irregular elements "Inzhekhim" are considered.
A risk analysis for natural-draught cooling towers under wind load
International Nuclear Information System (INIS)
Niemann, H.J.
1977-01-01
A satisfactory safety level of natural-draught cooling towers is usually reached by assuming an extreme wind load, for which the probability of being exceeded is very low. Taking into account the dispersion of strength, the relevant extreme wind velocity for the limiting carrying capacity is calculated for a desired probability of failure. Compared with the method of partial safety coefficients, the reliability can be calculated more exactly in this way, even though the probability distribution of the extreme wind velocity must be extrapolated from limited observations. (orig.) [de
Load Balancing of Parallel Monte Carlo Transport Calculations
International Nuclear Information System (INIS)
Procassini, R J; O'Brien, M J; Taylor, J M
2005-01-01
The performance of parallel Monte Carlo transport calculations which use both spatial and particle parallelism is increased by dynamically assigning processors to the most worked domains. Since he particle work load varies over the course of the simulation, this algorithm determines each cycle if dynamic load balancing would speed up the calculation. If load balancing is required, a small number of particle communications are initiated in order to achieve load balance. This method has decreased the parallel run time by more than a factor of three for certain criticality calculations
Dynamic Load Balancing of Parallel Monte Carlo Transport Calculations
International Nuclear Information System (INIS)
O'Brien, M; Taylor, J; Procassini, R
2004-01-01
The performance of parallel Monte Carlo transport calculations which use both spatial and particle parallelism is increased by dynamically assigning processors to the most worked domains. Since the particle work load varies over the course of the simulation, this algorithm determines each cycle if dynamic load balancing would speed up the calculation. If load balancing is required, a small number of particle communications are initiated in order to achieve load balance. This method has decreased the parallel run time by more than a factor of three for certain criticality calculations
Strength Calculation of Locally Loaded Orthotropic Shells
Directory of Open Access Journals (Sweden)
Yu. I. Vinogradov
2015-01-01
Full Text Available The article studies laminated orthotropic cylindrical, conic, spherical, and toroidal shells, which are often locally loaded in the aircraft designs over small areas of their surfaces.The aim of this work is to determine stress concentration in shells versus structure of orthotropic composite material, shell form and parameters, forms of loading areas, which borders do not coincide with lines of main curvatures of shells. For this purpose, an analytical computing algorithm to estimate strength of shells in terms of stress is developed. It enables us to have solution results of the boundary value problem with a controlled error. To solve differential equations an analytical method is used. An algorithm of the boundary value problem solution is multiplicative.The main results of researches are graphs of stress concentration in the orthotropic shells versus their parameters and areas of loading lineated by circles and ellipses.Among the other works aimed at determination of stress concentration in shells, the place of this one is defined by the analytical solution of applied problems for strength estimation in terms of shell stresses of classical forms.The developed effective analytical algorithm to solve the boundary value problem and received results are useful in research and development.
Part load efficiency of packaged air-cooled water chillers with inverter driven scroll compressors
International Nuclear Information System (INIS)
Cecchinato, Luca
2010-01-01
In this paper different packaged air-cooled systems, operating on scroll compressors, are experimentally analysed from the point of view of the relation between energy efficiency and actual capacity. Single compressor, double compressors and double compressors with uneven volumetric capacity units are tested. Experimental tests demonstrated that cooling capacity control by means of variation of rotational speed is an suitable solution for improving the part load efficiency of these systems. Step capacity units obtained by splitting the system volumetric capacity between two compressors are also effective solutions. Nevertheless they appear to be more efficient than single inverter driven chillers only for part load conditions lower than 60%. In the analysed cooling capacity range (25-50 kW), tandem compressors chillers with one inverter driven compressor appear the most efficient solution combining rotational speed with step capacity control. Seasonal energy efficiency ratios were obtained with prEN 14825 calculation method confirming reduced energy consumption associated to continuous and step cooling capacity control.
Thermal loading studies using cooling enhancement and ventilation
International Nuclear Information System (INIS)
Danko, G.
1993-01-01
Thermal loading studies are presented for short vertical emplacement, application of cooling enhancement, and drift ventilation. Two 25-m-long heat pipes upward oriented at 45 deg are installed at each emplacement borehole to promote heat transport into the pillar area. In addition, ventilation of the emplacement drifts is assumed for a 2- to 20-yr period. It is concluded that the maximum borehole temperature can be reduced from 230 to 136 C using only the heat pipes, and to 110 C applying the heat pipes together with moderate air cooling. The ventilation along without heat pipes can reduce the temperature to only ∼200 C. It is also demonstrated that the heat transferred from the container area to farther distances into the pillar raises rock temperatures significantly, by 10 to 20 C, and the increase in temperature remains noticeable for at least 1,000 yr. In addition, because of the more efficient heat distribution caused by the heat pipes, lower temperatures will be achieved in the container area together with improved drying and permanent as well as temporary water removal in the pillar area
Helium release rates and ODH calculations from RHIC magnet cooling line failure
Energy Technology Data Exchange (ETDEWEB)
Liaw, C.J.; Than, Y.; Tuozzolo, J.
2011-03-28
A catastrophic failure of the magnet cooling lines, similar to the LHC superconducting bus failure incident, could discharge cold helium into the RHIC tunnel and cause an Oxygen Deficiency Hazard (ODH) problem. A SINDA/FLUINT{reg_sign} model, which simulated the 4.5K/4 atm helium flowing through the magnet cooling system distribution lines, then through a line break into the insulating vacuum volumes and discharging via the reliefs into the RHIC tunnel, had been developed. Arc flash energy deposition and heat load from the ambient temperature cryostat surfaces are included in the simulations. Three typical areas: the sextant arc, the Triplet/DX/D0 magnets, and the injection area, had been analyzed. Results, including helium discharge rates, helium inventory loss, and the resulting oxygen concentration in the RHIC tunnel area, are reported. Good agreement had been achieved when comparing the simulation results, a RHIC sector depressurization test measurement, and some simple analytical calculations.
The cryogenic cooling program in high-heat-load optics at the Advanced Photon Source
International Nuclear Information System (INIS)
Rogers, C.S.
1993-07-01
This paper describes some of the aspects of the cryogenic optics program at the Advanced Photon Source (APS). A liquid-nitrogen-cooled, high-vacuum, double crystal monochromator is being fabricated at Argonne National Laboratory (ANL). A pumping system capable of delivering a variable flow rate of up to 10 gallons per minute of pressurized liquid nitrogen and removing 5 kilowatts of x-ray power is also being constructed. This specialized pumping system and monochromator will be used to test the viability of cryogenically cooled, high-heat-load synchrotron optics. It has been determined that heat transfer enhancement will be required for optics used with APS insertion devices. An analysis of a porous-matrix-enhanced monochromator crystal is presented. For the particular case investigated, a heat transfer enhancement factor of 5 to 6 was calculated
International Nuclear Information System (INIS)
Aktacir, Mehmet Azmi; Bueyuekalaca, Orhan; Bulut, Huesamettin; Yilmaz, Tuncay
2008-01-01
Outdoor design conditions are important parameters for energy efficiency of buildings. The result of incorrect selection of outdoor design conditions can be dramatic in view of comfort and energy consumption. In this study, the influence of different outdoor design conditions on air conditioning systems is investigated. For this purpose, cooling loads and capacities of air conditioning equipments for a sample building located in Adana, Turkey are calculated using different outdoor design conditions recommended by ASHRAE, the current design data used in Turkey and the daily maximum dry and wet bulb temperatures of July 21st, which is generally accepted as the design day. The cooling coil capacities obtained from the different outdoor design conditions considered in this study are compared with each other. The cost analysis of air conditioning systems is also performed. It is seen that the selection of outdoor design conditions is a very critical step in calculation of the building cooling loads and design capacities of air conditioning equipments
Heat Load and Cooling Configurations of the PEFP DTL
International Nuclear Information System (INIS)
Kim, Han Sung; Kwon, Hyeok Jung; Cho, Yong Sub
2012-01-01
A 100 MeV proton linac is under development for Proton Engineering Frontier Project (PEFP). It consists of a 50 keV injector, 3 MeV RFQ and 100 MeV DTL. The accelerated proton beam can be extracted at 20 MeV and 100 MeV by using bending magnets. Therefore, the DTL for PEFP can be divided into two sections; one for 20 MeV DTL and the other is 100 MeV DTL. The 20 MeV DTL is composed of 4 tanks and driven by a single klystron. Duty factor of the 20 MeV section is 24%. To accelerate the beam from 20 MeV to 100 MeV, we use 7 tanks, which are driven by 7 independent RF sources. Duty factor of the 100 MeV section is reduced to 8%. From the viewpoint of the heat load, there are several differences between the 20 MeV section and 100 MeV section. First, as mentioned before, the duty factors are different. Second, the accelerating gradient is changed from 1.3 MV/m for 20 MeV section to 2.58 MV/m for 100 MeV section. Third, the types of the electroquadrupole magnets inside each drift tube are different. For the 20 MeV section, we used the pool type quadrupole magnets made of enamel wires due to the limited space. The hollow conductor type quadrupole magnets are used for 100 MeV section. The heat generations of each quadrupole magnet are 1.5 kW and 0.4 kW for 20 MeV section and 100 MeV section, respectively. Detailed heat load of DTL and the configuration of cooling loop are presented in this paper
Heat Load and Cooling Configurations of the PEFP DTL
Energy Technology Data Exchange (ETDEWEB)
Kim, Han Sung; Kwon, Hyeok Jung; Cho, Yong Sub [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2012-05-15
A 100 MeV proton linac is under development for Proton Engineering Frontier Project (PEFP). It consists of a 50 keV injector, 3 MeV RFQ and 100 MeV DTL. The accelerated proton beam can be extracted at 20 MeV and 100 MeV by using bending magnets. Therefore, the DTL for PEFP can be divided into two sections; one for 20 MeV DTL and the other is 100 MeV DTL. The 20 MeV DTL is composed of 4 tanks and driven by a single klystron. Duty factor of the 20 MeV section is 24%. To accelerate the beam from 20 MeV to 100 MeV, we use 7 tanks, which are driven by 7 independent RF sources. Duty factor of the 100 MeV section is reduced to 8%. From the viewpoint of the heat load, there are several differences between the 20 MeV section and 100 MeV section. First, as mentioned before, the duty factors are different. Second, the accelerating gradient is changed from 1.3 MV/m for 20 MeV section to 2.58 MV/m for 100 MeV section. Third, the types of the electroquadrupole magnets inside each drift tube are different. For the 20 MeV section, we used the pool type quadrupole magnets made of enamel wires due to the limited space. The hollow conductor type quadrupole magnets are used for 100 MeV section. The heat generations of each quadrupole magnet are 1.5 kW and 0.4 kW for 20 MeV section and 100 MeV section, respectively. Detailed heat load of DTL and the configuration of cooling loop are presented in this paper
Cooling load reduction by means of night sky radiation
International Nuclear Information System (INIS)
Kamaruddin Abdullah; Armansyah, H.T.; Dyah, W.; Gunadnya, I.B.P.
2006-01-01
Nocturnal cooling can work under clear sky condition of the humid tropical climate. Such effect had been observed in a cool storage facilities for potatoes and for temporary storage of fresh vegetables installed in highland area of Candi kuning village of Bali. Test results have shown that the rate of heat dissipation to the sky could reduce storage temperature to 15 o C had been achieved when the nocturnal cooling unit was combined with modified cooling tower and 1 kW cooling effect of an auxiliary cooling unit. Under such condition the facility could maintain better quality of stored vegetables, such as broccoli, shallot, and celery as compared to those stored in room without cooling facility. The estimated average cooling rate due to night sky radiation was 47.6 W/m 2 , on September 28, 1999 and 47.2 W/m 2 with the lowest water temperature of 14 o C under ambient temperature of 16 o C
International Nuclear Information System (INIS)
Solmaz, Ozgur; Ozgoren, Muammer; Aksoy, Muharrem Hilmi
2014-01-01
Highlights: • An ANN model was developed to predict hourly cooling load of a vehicle. • Hourly meteorological data of 5 different provinces was used. • The agreement of the cooling load values between the calculations and predictions was fairly promising. • The ANN model could be successfully used to design automotive air conditioning systems. - Abstract: In this study, Artificial Neural Networks (ANNs) method for prediction hourly cooling load of a vehicle was implemented. The cooling load of the vehicle was calculated along the cooling season (1 May–30 September) for Antalya, Konya, Mersin, Mugla and Sanliurfa provinces in Turkey. For ANN model, seven neurons determinated as input signals of latitude, longitude, altitude, day of the year, hour of the day, hourly mean ambient air temperature and hourly solar radiation were used for the input layer of the network. One neuron producing an output signal of the hourly cooling load was utilized in the output layer. All data were divided into two categories for training and testing of the ANN. The 80% of the data was reserved to training and the remaining was used for testing of the model. Neuron numbers in the hidden layer from 7 to 40 were tested step by step to find the best matching ANN structure. The obtained results for different numbers of neurons were compared in terms of root mean squared error (RMSE), coefficient of determination (R 2 ) and mean absolute error (MAE). The best matching results for the training and testing were obtained as 8 neurons for the minimum testing RMSE value for the prediction of cooling load by the ANN model on the 23rd day of each month along the cooling season. For the model with 8 neurons RMSE, R 2 and MAE (Training/Testing) were found to be 0.0128/0.0259, 0.9959/0.9818 and 78.81/174.71 W/m 2 , respectively. It is shown that the cooling load of a vehicle can be successfully predicted by means of the ANNs from geographical characteristics and meteorological data
International Nuclear Information System (INIS)
Lei, Jiawei; Kumarasamy, Karthikeyan; Zingre, Kishor T.; Yang, Jinglei; Wan, Man Pun; Yang, En-Hua
2017-01-01
Highlights: • Cool colored coating and PCM are two complementary passive cooling strategies. • A PCM cool colored coating system is developed. • The coating reduces cooling energy by 8.5% and is effective yearly in tropical Singapore. - Abstract: Cool colored coating and phase change materials (PCM) are two passive cooling strategies often used separately in many studies and applications. This paper investigated the integration of cool colored coating and PCM for building cooling through experimental and numerical studies. Results showed that cool colored coating and PCM are two complementary passive cooling strategies that could be used concurrently in tropical climate where cool colored coating in the form of paint serves as the “first protection” to reflect solar radiation and a thin layer of PCM forms the “second protection” to absorb the conductive heat that cannot be handled by cool paint. Unlike other climate zones where PCM is only seasonally effective and cool paint is only beneficial during summer, the application of the proposed PCM cool colored coating in building envelope could be effective throughout the entire year with a monthly cooling energy saving ranging from 5 to 12% due to the uniform climatic condition all year round in tropical Singapore.
Energy Technology Data Exchange (ETDEWEB)
Ziver, A.K. E-mail: a.k.ziver@imperial.ac.uk; Pain, C.C; Carter, J.N.; Oliveira, C.R.E. de; Goddard, A.J.H.; Overton, R.S
2004-03-01
A non-generational genetic algorithm (GA) has been developed for fuel management optimisation of Advanced Gas-Cooled Reactors, which are operated by British Energy and produce around 20% of the UK's electricity requirements. An evolutionary search is coded using the genetic operators; namely selection by tournament, two-point crossover, mutation and random assessment of population for multi-cycle loading pattern (LP) optimisation. A detailed description of the chromosomes in the genetic algorithm coded is presented. Artificial Neural Networks (ANNs) have been constructed and trained to accelerate the GA-based search during the optimisation process. The whole package, called GAOPT, is linked to the reactor analysis code PANTHER, which performs fresh fuel loading, burn-up and power shaping calculations for each reactor cycle by imposing station-specific safety and operational constraints. GAOPT has been verified by performing a number of tests, which are applied to the Hinkley Point B and Hartlepool reactors. The test results giving loading pattern (LP) scenarios obtained from single and multi-cycle optimisation calculations applied to realistic reactor states of the Hartlepool and Hinkley Point B reactors are discussed. The results have shown that the GA/ANN algorithms developed can help the fuel engineer to optimise loading patterns in an efficient and more profitable way than currently available for multi-cycle refuelling of AGRs. Research leading to parallel GAs applied to LP optimisation are outlined, which can be adapted to present day LWR fuel management problems.
Integrity of reinforced concrete cooling towers under extreme loads: Wind and earthquake
International Nuclear Information System (INIS)
Louhi, Amine
2015-01-01
The authorities have planned to increase the lifetime of currently operating nuclear power plants. The ageing of reinforced concrete structures such as cooling towers should be evaluated and its impact on the bearing capacity calculated. In the case of significant damage, the strengthening must be considered to ensure the sustainability of these towers facing the risk of storms and earthquakes becoming more and more frequent. This work aims to quantify the adverse effects that can generate concrete cracks and rebar section loss induced by corrosion, especially on the bearing capacity of nuclear power plant cooling towers under monotonic or cyclic extreme load conditions (wind and earthquake). These loads are certainly the most severe, since they take the structure into the nonlinear domain and can induce or amplify cracking damage. Numerical simulations are proposed to determine the quasi-static or dynamic response of the structure, taking into account appearance of concrete cracks and their evolution via an appropriate material concrete law and rebar's yielding. In the case of a seismic load, the responses are evaluated by three different methods; the nonlinear response history analysis (NLRHA), the response spectrum analysis and the modal response history analysis (MRHA) in order to compare the earthquake modeling approaches and to evaluate the robustness of the results. Parametric studies on damping, load combinations and structural configurations, are also performed. In the case of a wind load, the strengthening technique using composite materials, such as carbon fiber reinforced plastic (CFRP) is modeled. The behavior of the damaged structure with an advanced corrosion rate is estimated in the pre- and post-cracking regime, compared to the undamaged structure. The drop of bearing capacity is quantified, a reinforcement designed is proposed to restore the integrity and thus increase the lifetime of the structure. (author)
Energy Technology Data Exchange (ETDEWEB)
Kim, Myoung Jun; Lee, Hee Joon [Kookmin University, Seoul (Korea, Republic of); Moon, Joo Hyung; Bae, Youngmin; Kim, Young-In [KAERI, Daejeon (Korea, Republic of)
2015-05-15
In the event of a 'loss of coolant accident'(LOCA) and a non-LOCA, the secondary passive cooling system would be activated to cool the steam in a condensing heat exchanger that is immersed in an emergency cooldown tank (ECT). Currently, the capacities of these ECTs are designed to be sufficient to remove the sensible and residual heat from the reactor coolant system for 72 hours after the occurrence of an accident. After the operation of a conventional passive cooling system for an extended period, however, the water level falls as a result of the evaporation from the ECT, as steam is emitted from the open top of the tank. Therefore, the tank should be refilled regularly from an auxiliary water supply system when the system is used for more than 72 hours. Otherwise, the system would fail to dissipate heat from the condensing heat exchanger due to the loss of the cooling water. Ultimately, the functionality of the passive cooling system would be seriously compromised. As a passive means of overcoming the water depletion in the tank, Kim et al. applied for a Korean patent covering the concept of a long-term passive cooling system for an ECT even after 72 hours. This study presents transient performance of ECT with installing air-cooled condensing heat exchanger under decay heat load. The cooling capacity of an air-cooled condensing heat exchanger was evaluated to determine its practicality.
Preliminary calculations on the cooling rate of the Renca batholit, Sierra de San Luis, Argentina
International Nuclear Information System (INIS)
Lopez de Luchi, M.G.; Ostera, H.A.; Linares, E; Rosello, E.A
2001-01-01
Cooling rates can be used to constrain the unroofing history of plutonic-metamorphic system. Geocronological cooling rates (Spear and Parrish, 1996) can be unravelled using age calculations on minerals that were open systems and subsequently passed through their closure temperatures (Dodson, 1973) during cooling. Several age determinations on different minerals are needed in order to accurately constrain the cooling path of a pluton (Hodges 1991, Spear and Parrish, 1996 and references therein). Isotopic open-system behaviour in minerals can be modelled as volume diffusion process (Hodges, 1991 and references therein), which depends on the cooling rate of the whole system. We present the first results on the calculation of the cooling rate of the Renca batholith on the basis of the combination of both thermometric calculations and available crystallization and cooling ages (au)
International Nuclear Information System (INIS)
Kwok, Simon S.K.; Lee, Eric W.M.
2011-01-01
Research highlights: → The building occupancy affecting the cooling load prediction is studied. → PENN model is adopted in this study for predicting the building cooling load. → Statistical approach is adopted to result a less prejudice prediction performance. → Results show that occupancy data can significantly improve the prediction. -- Abstract: Building cooling load prediction is one of the key factors in the success of energy-saving measures. Many computational models available in the industry today have been developed from either forward or inverse modeling approaches. However, most of these models require extensive computer resources and involve lengthy computation. This paper discusses the use of data-driven intelligent approaches, a probabilistic entropy-based neural (PENN) model to predict the cooling load of a building. Although it is common knowledge that the presence and activity of building occupants have a significant impact on the required cooling load of buildings, practices currently adopted in modeling the presence and activity of people in buildings do not reflect the complexity of the impact occupants have on building cooling load. In contrast to previous artificial neural network (ANN) models, most of which employ a fixed schedule or historic load data to represent building occupancy in simulating building cooling load, this paper introduces two input parameters, dynamic occupancy area and rate and uses it to mimic building cooling load. The training samples used include weather data obtained from the Hong Kong Observatory and building-related data acquired from an existing grade A mega office buildings in Hong Kong with tenants including many multi-national financial companies that require 24-h air conditioning seven days a week. The dynamic changes that occur in the occupancy of these buildings therefore make it very difficult to forecast building cooling load by means of a fixed time schedule. The performance of simulation results
Energy Technology Data Exchange (ETDEWEB)
Kwok, Simon S.K. [Department of Building and Construction, City University of Hong Kong, Tat Chee Avenue, Kowloon Tong (Hong Kong); Lee, Eric W.M., E-mail: ericlee@cityu.edu.h [Department of Building and Construction, City University of Hong Kong, Tat Chee Avenue, Kowloon Tong (Hong Kong)
2011-07-15
Research highlights: {yields} The building occupancy affecting the cooling load prediction is studied. {yields} PENN model is adopted in this study for predicting the building cooling load. {yields} Statistical approach is adopted to result a less prejudice prediction performance. {yields} Results show that occupancy data can significantly improve the prediction. -- Abstract: Building cooling load prediction is one of the key factors in the success of energy-saving measures. Many computational models available in the industry today have been developed from either forward or inverse modeling approaches. However, most of these models require extensive computer resources and involve lengthy computation. This paper discusses the use of data-driven intelligent approaches, a probabilistic entropy-based neural (PENN) model to predict the cooling load of a building. Although it is common knowledge that the presence and activity of building occupants have a significant impact on the required cooling load of buildings, practices currently adopted in modeling the presence and activity of people in buildings do not reflect the complexity of the impact occupants have on building cooling load. In contrast to previous artificial neural network (ANN) models, most of which employ a fixed schedule or historic load data to represent building occupancy in simulating building cooling load, this paper introduces two input parameters, dynamic occupancy area and rate and uses it to mimic building cooling load. The training samples used include weather data obtained from the Hong Kong Observatory and building-related data acquired from an existing grade A mega office buildings in Hong Kong with tenants including many multi-national financial companies that require 24-h air conditioning seven days a week. The dynamic changes that occur in the occupancy of these buildings therefore make it very difficult to forecast building cooling load by means of a fixed time schedule. The performance of
Energy Technology Data Exchange (ETDEWEB)
Kaellblad, K
1998-05-01
The need to estimate indoor temperatures, heating or cooling load and energy requirements for buildings arises in many stages of a buildings life cycle, e.g. at the early layout stage, during the design of a building and for energy retrofitting planning. Other purposes are to meet the authorities requirements given in building codes. All these situations require good calculation methods. The main purpose of this report is to present the authors work with problems related to thermal models and calculation methods for determination of temperatures and heating or cooling loads in buildings. Thus the major part of the report deals with treatment of solar radiation in glazing systems, shading of solar and sky radiation and the computer program JULOTTA used to simulate the thermal behavior of rooms and buildings. Other parts of thermal models of buildings are more briefly discussed and included in order to give an overview of existing problems and available solutions. A brief presentation of how thermal models can be built up is also given and it is a hope that the report can be useful as an introduction to this part of building physics as well as during development of calculation methods and computer programs. The report may also serve as a help for the users of energy related programs. Independent of which method or program a user choose to work with it is his or her own responsibility to understand the limits of the tool, else wrong conclusions may be drawn from the results 52 refs, 22 figs, 4 tabs
Load calculation methods for offshore wind turbine foundations
DEFF Research Database (Denmark)
Passon, Patrik; Branner, Kim
2014-01-01
Calculation of design loads for offshore wind turbine (OWT) foundations is typically performed in a joint effort between wind turbine manufactures and foundation designers (FDs). Ideally, both parties would apply the same fully integrated design tool and model for that purpose. However, such solu...
Calculation of equivalent static loads and its application
International Nuclear Information System (INIS)
Choi, Woo-Seok; Park, K.B.; Park, G.J.
2005-01-01
All the forces in the real world act dynamically on structures. Since dynamic loads are extremely difficult to handle in analysis and design, static loads are usually utilized with dynamic factors. Generally, the dynamic factors are determined from design codes or experience. Therefore, static loads may not give accurate solutions in analysis and design and structural engineers often come up with unreliable solutions. Two different methods are proposed for the transformation of dynamic loads into equivalent static loads (ESLs). One is an analytical method for exact ESLs and the other is an approximation method. The exact ESLs are calculated to generate identical response fields such as displacement and stress with those from dynamic loads at a certain time. Some approximation methods are proposed in engineering applications, which generate similar response fields from dynamic loads. They are divided into the displacement-based approach and the stress-based approach. The process is derived and evaluated mathematically. Standard examples are selected and solved by the proposed method and error analyses are conducted. Applications of the method to structural optimization are discussed
International Nuclear Information System (INIS)
Man, Yi; Yang, Hongxing; Spitler, Jeffrey D.; Fang, Zhaohong
2011-01-01
Highlights: → Propose a novel HGCHP system with NCR works as supplemental heat rejecter. → Establish the analytical model and computer program of NCR and novel HGCHP system to simulate their operation performance. → Design the novel HGCHP system for a sample building located in Hong Kong. → It is found to be feasible to use NCR serves as supplemental heat rejecter of the novel HGCHP system. → The novel HGCHP system provides a new valuable choice for air conditioning in cooling load dominated buildings. -- Abstract: When the ground coupled heat pump (GCHP) system is utilized for air conditioning in cooling load dominated buildings, the heat rejected into ground will accumulate around the ground heat exchangers (GHE) and results in system performance degradation. A novel hybrid ground coupled heat pump (HGCHP) system with nocturnal cooling radiator (NCR) works as supplemental heat rejecter is proposed in this paper to resolve this problem. The practical analytical model of NCR and novel HGCHP system are established. The computer program based on established model is developed to simulate the system operation performance. The novel HGCHP system is designed and simulated for a sample building located in Hong Kong, and a simple life cycle cost comparisons are carried out between this system and conventional GCHP system. The results indicate that it is feasible to use NCR serves as supplemental heat rejecter of the novel HGCHP system for cooling load dominated buildings even those located in humid subtropical climate areas. This novel HGCHP system provides a new valuable choice for air conditioning in cooling load dominated buildings, and it is especially suitable for buildings with limited surface land areas.
Numerical research of a super-large cooling tower subjected to accidental loads
Energy Technology Data Exchange (ETDEWEB)
Li, Yi; Lin, Feng [Department of Building Engineering, Tongji University, Shanghai 200092 (China); Gu, Xianglin, E-mail: gxl@tongji.edu.cn [Department of Building Engineering, Tongji University, Shanghai 200092 (China); Lu, Xiaoqin [Guangdong Electric Power Design Institute, Guangzhou 510660 (China)
2014-04-01
With the continued development of nuclear power plants, more and more super-large cooling towers are to be built in China and around the world. For the safe operation of nuclear power plants, research work has been done on the causes of collapse of cooling towers, collapse modes and the secondary disasters caused by the collapse of cooling towers. However, the collapse modes and the ground vibration induced by the collapse of cooling towers subjected to the accidental loads have not been fully understood. This paper has been focused on the modes and mechanisms behavior of the collapse of cooling towers subjected to accidental loads. Meanwhile, prediction of the ground vibration due to the collapse of the cooling towers has also been completed in a parallel project. Using dynamic finite element program LS-DYNA, a 3D finite element model for a super-large cooling tower was developed and the nonlinear material models were incorporated. In this paper, four types of accidental loads were considered to trigger the collapse or local failure of the tower, including vehicle collision, airplane impact, local explosion and missile attack. It was found that vehicle collision, missile attack and small TNT equivalent explosives (2 kg, 20 kg, 200 kg) might result in local failure of the cooling tower, however, the tower can still keep stable. On the other hand, large TNT equivalent explosives (2000 kg, 4500 kg) could cause severe damages in the inclined columns of the cooling tower, and lead to progressive collapse of the entire cooling tower. The two kinds of TNT equivalent explosives caused the same collapse mode while the collapsing duration was different. The airplane impacted at the throat of the cooling tower caused the local failure of shell structure of the tower, and then the progressive collapse of the cooling tower happened due to the gravitational action. The resulting collapse mode was different from that triggered by the local explosion.
Numerical research of a super-large cooling tower subjected to accidental loads
International Nuclear Information System (INIS)
Li, Yi; Lin, Feng; Gu, Xianglin; Lu, Xiaoqin
2014-01-01
With the continued development of nuclear power plants, more and more super-large cooling towers are to be built in China and around the world. For the safe operation of nuclear power plants, research work has been done on the causes of collapse of cooling towers, collapse modes and the secondary disasters caused by the collapse of cooling towers. However, the collapse modes and the ground vibration induced by the collapse of cooling towers subjected to the accidental loads have not been fully understood. This paper has been focused on the modes and mechanisms behavior of the collapse of cooling towers subjected to accidental loads. Meanwhile, prediction of the ground vibration due to the collapse of the cooling towers has also been completed in a parallel project. Using dynamic finite element program LS-DYNA, a 3D finite element model for a super-large cooling tower was developed and the nonlinear material models were incorporated. In this paper, four types of accidental loads were considered to trigger the collapse or local failure of the tower, including vehicle collision, airplane impact, local explosion and missile attack. It was found that vehicle collision, missile attack and small TNT equivalent explosives (2 kg, 20 kg, 200 kg) might result in local failure of the cooling tower, however, the tower can still keep stable. On the other hand, large TNT equivalent explosives (2000 kg, 4500 kg) could cause severe damages in the inclined columns of the cooling tower, and lead to progressive collapse of the entire cooling tower. The two kinds of TNT equivalent explosives caused the same collapse mode while the collapsing duration was different. The airplane impacted at the throat of the cooling tower caused the local failure of shell structure of the tower, and then the progressive collapse of the cooling tower happened due to the gravitational action. The resulting collapse mode was different from that triggered by the local explosion
Calculation of loading on pipes during filling processes
International Nuclear Information System (INIS)
Thiele, Thomas; Swidersky, Harald
2013-01-01
Filling processes in pipe systems do normally not belong to load design cases for which the integrity of pipelines and their mountings are verified with fluid- and structure-dynamic analysis. However, their frequency of occurrence is several times higher than those of the postulated incident-induced transients. That is why they have to be taken into consideration within fatigue analysis. The loading on pipes or rather on their mountings during filling processes originates from differences in the density of the transported fluids, e.g. at transport of gas slugs within water flow. The exposure time of the flow momentum force is fixed by the height of the flow velocity and by the length of discontinuities in the pipeline sections. Filling procedures frequently end with a pressure surge which was caused by the impingement and decelaration of the water plug at orifices in pipe systems. The calculation of such processes with 1D fluid-dynamic or rather thermal-hydraulic programs requires an idealization of the real form of the two phase flow or respectively of the two phase interface. In the past, several two phase flow regime maps were developed and implemented in codes for this. In this paper, the applicability of the thermo-hydraulic program RELAP5/MOD3.3 which is established in nuclear engineering is examined in order to calculate realistic loads from plug flows during the filling processes. For this, post-test calculations of experiments have been performed and the results have been compared with the experimental results as well as with the classical analytical approach according to Joukowsky. The comparison shows that, dependent on the discretization, the calculated loads are indeed partly underestimated, though the calculation results according to the Joukowsky-approach lie above the measurements. (orig.)
An Overview of the Thermal Calculation and the Cooling Technology for Active Magnetic Bearing
Zhang, Li; Yu, Meiyun; Luo, Yanyan; Liu, Jun; Ren, Yafeng
2017-10-01
The cooling process of AMB is that the energy loss is sent out to the outside world when the system is operating. The energy loss transfers to the surrounding medium in the form of heat, which leads to raise the temperature of system components and influences the performance of the system. So it is necessary to study the internal loss of the magnetic bearing system and thermal calculation method. Three kinds of thermal calculation methods are compared, which is important for the design and calculation of cooling. At the same time, the cooling way, the cooling method, and the cooling system is summarized on the basis of cooling technology of active magnetic bearing, and the design method of the cooling system is studied. But for the active magnetic bearing system, when designing the cooling system, heat dissipation of the motor can not be ignored. It is important not only for the performance of the active magnetic bearing system and stable operation, and but also for the improvement of the cooling technology.
The Impact of Roof Pitch and Ceiling Insulation on Cooling Load of Naturally-Ventilated Attics
Directory of Open Access Journals (Sweden)
Linxia Gu
2012-07-01
Full Text Available A 2D unsteady computational fluid dynamics (CFD model is employed to simulate buoyancy-driven turbulent ventilation in attics with different pitch values and ceiling insulation levels under summer conditions. The impacts of roof pitch and ceiling insulation on the cooling load of gable-roof residential buildings are investigated based on the simulation of turbulent air flow and natural convection heat transfer in attic spaces with roof pitches from 3/12 to 18/12 combined with ceiling insulation levels from R-1.2 to R-40. The modeling results show that the air flows in the attics are steady and exhibit a general streamline pattern that is qualitatively insensitive to the investigated variations of roof pitch and ceiling insulation. Furthermore, it is predicted that the ceiling insulation plays a control role on the attic cooling load and that an increase of roof pitch from 3/12 to 8/12 results in a decrease in the cooling load by around 9% in the investigated cases. The results suggest that the increase of roof pitch alone, without changing other design parameters, has limited impact on attics cooling load and airflow pattern. The research results also suggest both the predicted ventilating mass flow rate and attic cooling load can be satisfactorily correlated by simple relationships in terms of appropriately defined Rayleigh and Nusselt numbers.
Transient Three-Dimensional Analysis of Nozzle Side Load in Regeneratively Cooled Engines
Wang, Ten-See
2005-01-01
Three-dimensional numerical investigations on the start-up side load physics for a regeneratively cooled, high-aspect-ratio nozzle were performed. The objectives of this study are to identify the three-dimensional side load physics and to compute the associated aerodynamic side load using an anchored computational methodology. The computational methodology is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, and a transient inlet condition based on an engine system simulation. Computations were performed for both the adiabatic and cooled walls in order to understand the effect of boundary conditions. Finite-rate chemistry was used throughout the study so that combustion effect is always included. The results show that three types of shock evolution are responsible for side loads: generation of combustion wave; transitions among free-shock separation, restricted-shock separation, and simultaneous free-shock and restricted shock separations; along with oscillation of shocks across the lip. Wall boundary conditions drastically affect the computed side load physics: the adiabatic nozzle prefers free-shock separation while the cooled nozzle favors restricted-shock separation, resulting in higher peak side load for the cooled nozzle than that of the adiabatic nozzle. By comparing the computed physics with those of test observations, it is concluded that cooled wall is a more realistic boundary condition, and the oscillation of the restricted-shock separation flow pattern across the lip along with its associated tangential shock motion are the dominant side load physics for a regeneratively cooled, high aspect-ratio rocket engine.
Bulk Electric Load Cost Calculation Methods: Iraqi Network Comparative Study
Directory of Open Access Journals (Sweden)
Qais M. Alias
2016-09-01
Full Text Available It is vital in any industry to regain the spent capitals plus running costs and a margin of profits for the industry to flourish. The electricity industry is an everyday life touching industry which follows the same finance-economic strategy. Cost allocation is a major issue in all sectors of the electric industry, viz, generation, transmission and distribution. Generation and distribution service costing’s well documented in the literature, while the transmission share is still of need for research. In this work, the cost of supplying a bulk electric load connected to the EHV system is calculated. A sample basic lump-average method is used to provide a rough costing guide. Also, two transmission pricing methods are employed, namely, the postage-stamp and the load-flow based MW-distance methods to calculate transmission share in the total cost of each individual bulk load. The three costing methods results are then analyzed and compared for the 400kV Iraqi power grid considered for a case study.
Calculation of projected waste loads for transuranic waste management alternatives
International Nuclear Information System (INIS)
Hong, K.; Kotek, T.; Koebnick, B.; Wang, Y.; Kaicher, C.
1995-01-01
The level of treatment and the treatment and interim storage site configurations (decentralized, regional, or centralized) impact transuranic (TRU) waste loads at and en route to sites in the US Department of Energy (DOE) complex. Other elements that impact waste loads are the volume and characteristics of the waste and the unit operation parameters of the technologies used to treat it. Projected annual complexwide TRU waste loads under various TRU waste management alternatives were calculated using the WASTEunderscoreMGMT computational model. WASTEunderscoreMGMT accepts as input three types of data: (1) the waste stream inventory volume, mass, and contaminant characteristics by generating site and waste stream category; (2) unit operation parameters of treatment technologies; and (3) waste management alternative definitions. Results indicate that the designed capacity of the Waste Isolation Pilot Plant, identified under all waste management alternatives as the permanent disposal facility for DOE-generated TRU waste, is sufficient for the projected complexwide TRU waste load under any of the alternatives
Calculation of piping loads due to filling procedures
International Nuclear Information System (INIS)
Swidersky, Harald; Thiele, Thomas
2012-01-01
Filling procedures in piping systems are usually not load cases that are studied by fluid dynamic and structure dynamic analyses with respect to the integrity of pipes and supports. Although, their frequency is higher than that of postulated accidental transients, therefore they have to be considered for fatigue analyses. The piping and support loads due to filling procedures are caused by the density differences if the transported fluids, for instance in flows with the transport of gas bubbles. The impact duration of the momentum forces is defined by the flow velocity and the length of discontinuities in the piping segments. Filling procedures end very often with a shock pressure, caused by the impact and decelerating of the fluid front at smaller cross sections. The suitability of the thermally hydraulics program RELAP/MOD3.3 for the calculation of realistic loads from filling procedures was studied, the results compared with experimental data. It is shown that dependent on the discretization level the loads are partial significantly underestimated.
Comfort air temperature influence on heating and cooling loads of a residential building
Stanciu, C.; Șoriga, I.; Gheorghian, A. T.; Stanciu, D.
2016-08-01
The paper presents the thermal behavior and energy loads of a two-level residential building designed for a family of four, two adults and two students, for different inside comfort levels reflected by the interior air temperature. Results are intended to emphasize the different thermal behavior of building elements and their contribution to the building's external load. The most important contributors to the building thermal loss are determined. Daily heating and cooling loads are computed for 12 months simulation in Bucharest (44.25°N latitude) in clear sky conditions. The most important aspects regarding sizing of thermal energy systems are emphasized, such as the reference months for maximum cooling and heating loads and these loads’ values. Annual maximum loads are encountered in February and August, respectively, so these months should be taken as reference for sizing thermal building systems, in Bucharest, under clear sky conditions.
FEATURES OF TECHNO-ECONOMIC CALCULATION OF COMMERCIAL COOLING CHAMBERS
Directory of Open Access Journals (Sweden)
M. Khmelniuk
2017-10-01
Full Text Available The article touches upon the design and calculation of trade objects refrigerating chambers. The influence of the cost of various groups of components and equipment on the final cost of the camera is analyzed. The influence of such factors as noise, fire safety and location of equipment during operation and installation is described. Recommendations are given on the choice of components in the design.
Improving prediction accuracy of cooling load using EMD, PSR and RBFNN
Shen, Limin; Wen, Yuanmei; Li, Xiaohong
2017-08-01
To increase the accuracy for the prediction of cooling load demand, this work presents an EMD (empirical mode decomposition)-PSR (phase space reconstruction) based RBFNN (radial basis function neural networks) method. Firstly, analyzed the chaotic nature of the real cooling load demand, transformed the non-stationary cooling load historical data into several stationary intrinsic mode functions (IMFs) by using EMD. Secondly, compared the RBFNN prediction accuracies of each IMFs and proposed an IMF combining scheme that is combine the lower-frequency components (called IMF4-IMF6 combined) while keep the higher frequency component (IMF1, IMF2, IMF3) and the residual unchanged. Thirdly, reconstruct phase space for each combined components separately, process the highest frequency component (IMF1) by differential method and predict with RBFNN in the reconstructed phase spaces. Real cooling load data of a centralized ice storage cooling systems in Guangzhou are used for simulation. The results show that the proposed hybrid method outperforms the traditional methods.
Calculations on heavy-water moderated and cooled natural uranium fuelled power reactors
International Nuclear Information System (INIS)
Pinedo V, J.L.
1979-01-01
One of the codes that the Instituto Nacional de Investigaciones Nucleares (Mexico) has for the nuclear reactors design calculations is the LEOPARD code. This work studies the reliability of this code in reactors design calculations which component materials are the same of the heavy water moderated and cooled, natural uranium fuelled power reactors. (author)
SALLY - a computer programme for the calculation of the dynamical behaviour of a cooling channel
International Nuclear Information System (INIS)
Reiche, C.; Ziegenbein, D.
1978-12-01
This report describes the mathematical-physical fundamentals and provides a user's manual as well as some test examples for the programme SALLY. SALLY is suitable for the calculation of the dynamical behaviour of a cooling channel under following conditions: point-kinetics, heat transfer in the fuel in radial direction only, reactivity feedback, simple model of the first cooling cycle. Reactivity, coolant inlet temperature or coolant velocity can be disturbed. (author)
International Nuclear Information System (INIS)
Coman, Aurelia Camelia; Tenescu, Mircea
2010-01-01
The paper purpose is to analyze the chiller units capacity to determine whether they can cope with high air and cooling water temperatures during summer time to remove heat loads imposed from Heating, Ventilation and Air Conditioning (HVAC) units in a CANDU 6 Nuclear Power Plant. The starting point is calculation of the overall heat transfer coefficient at the evaporator and condenser. They are used in heat balance equations of heat exchangers. A mathematical model was developed that simulates the refrigeration cycle to assess the response of chilled water system and its performance at different heat loads. In this analysis there were calculated values for inlet/outlet chilled water temperature and the refrigerant cycle thermodynamic parameters (condenser and evaporator pressure/temperature, refrigerant mass flowrate, refrigerant quality at the evaporator, refrigerant vapour superheated temperature at the compressor outlet, refrigerant subcooled temperature at the condenser outlet). To find the adequate functioning parameters of the installation, the MathCAD 13 software was used in all cases analyzed. The behaviour of the chiller units was investigated by examining the variation of three basic parameters, namely: - cooling water (river water) temperature; - air temperature; - heat load. The simultaneous variation of these three independent parameters allows to identify the actual chillers unit operating point (including chiller trip). (authors)
Part load performance of air-cooled centrifugal chillers with variable speed condenser fan control
Energy Technology Data Exchange (ETDEWEB)
Yu, F.W.; Chan, K.T. [Department of Building Services Engineering, The Hong Kong Polytechnic University, Hung Hom, Kowloon, Hong Kong (China)
2007-11-15
Air-cooled centrifugal chillers are commonly used in commercial buildings but their performance analysis is lacking. This paper investigates the part load performance of the chillers via a thermodynamic model. The model was validated using a wide range of operating data from an existing chiller with specific settings of outdoor temperature and condensing pressure in controlling the condensing temperature. The validated model was developed specifically to ascertain the maximum coefficient of performance of chiller (COP) together with the strategy for optimizing the condensing temperature under various operating conditions. It is found that the highest COP occurs at a part load ratio (PLR) of 0.71-0.84, depending on the outdoor temperature and the control of condensing temperature, rather than at full load. Yet the chillers operating at such part load conditions will cause extra energy used for the early staging of chilled water pumps. To minimize the overall chiller plant energy consumption, it is still preferable to implement chiller sequencing based on the full load condition than on the aforementioned PLRs. The results of this paper present criteria for implementing low-energy strategies for operating air-cooled chillers satisfying a given building cooling load profile. (author)
Transient Three-Dimensional Side Load Analysis of a Film Cooled Nozzle
Wang, Ten-See; Guidos, Mike
2008-01-01
Transient three-dimensional numerical investigations on the side load physics for an engine encompassing a film cooled nozzle extension and a regeneratively cooled thrust chamber, were performed. The objectives of this study are to identify the three-dimensional side load physics and to compute the associated aerodynamic side load using an anchored computational methodology. The computational methodology is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, and a transient inlet history based on an engine system simulation. Ultimately, the computational results will be provided to the nozzle designers for estimating of effect of the peak side load on the nozzle structure. Computations simulating engine startup at ambient pressures corresponding to sea level and three high altitudes were performed. In addition, computations for both engine startup and shutdown transients were also performed for a stub nozzle, operating at sea level. For engine with the full nozzle extension, computational result shows starting up at sea level, the peak side load occurs when the lambda shock steps into the turbine exhaust flow, while the side load caused by the transition from free-shock separation to restricted-shock separation comes at second; and the side loads decreasing rapidly and progressively as the ambient pressure decreases. For the stub nozzle operating at sea level, the computed side loads during both startup and shutdown becomes very small due to the much reduced flow area.
Body drop into a fluid tank and dynamic loads calculation
Directory of Open Access Journals (Sweden)
Komarov Aleksandr Andreevich
2014-05-01
Full Text Available The theory of a body striking a fluid began intensively developing due to the tasks of hydroplanes landing. For the recent years the study of a stroke and submersion of bodies into fluid became even more current. We face them in the process of strength calculation of ship hulls and other structures in modern technology. These tasks solution represents great mathematical difficulty even in case of the mentioned simplifications. These difficulties emerge due to the unsteady character of fluid motion in case of body submersion, and also jet and spray phenomena, which lead to discontinuous motions. On the basis of G.V. Logvinovich’s concept the problem of loads determination with consideration for air gap is solved for both a body and reservoir enclosing structures when a body falls into a fluid. Numerical method is based on the decay of an arbitrary discontinuity.
The evaluation of stress and piping support loads on RSG-GAS secondary cooling system
International Nuclear Information System (INIS)
Pustandyo, W.; Sitandung, Y. B.; Sujalmo, S.
1998-01-01
The evaluation of stress and piping support loads was evaluated on piping segment of secondary cooling water piping. In this paper, the analysis methods are presented with the use of computer code PS + CAEPIPE Version 3. 4. 05. W. From the selected pipe segment, the data of pipe characteristic, material properties, operation and design condition, equipment and support were used as inputs. The result of analysis show that stress and support loads if using location, kind and number of support equal with the system that have been installed for sustain load 3638 psi (node 160), thermal 13517 psi (node 90) and combination of sustain and thermal (node 90) 16747 psi. Meanwhile,if the optimization support, stress and support load for sustain load are respectively 4238 psi (node 10), thermal 13517 psi (node 90) and combination of sustain + thermal (node 90) 17350 psi. The limit values of permitted support based on Code PS+CAEPIPE of sustain load are 15000 psi, thermal 22500 psi and combination of sustain + thermal 37500 psi. The conclusion of evaluation result, that stress support load of pipe secondary cooling system are sufficiently low and using support show excessive and not economic
International Nuclear Information System (INIS)
Jia, Jie; Lee, W.L.; Chen, Hua
2013-01-01
Highlights: • This is an experimental study of the use of DCDV system for achieving the decoupling and energy saving objectives. • The study focuses on side-by-side comparison of the DCDV and conventional systems. • DCDV system can better achieve the desired space air conditions and is more energy efficient. • A prediction model has been developed to relate the possible condensation period with different operating parameters. • The results are useful for wider application of DCDV system. - Abstract: The use of DCDV system for decoupling dehumidification from cooling to achieve energy saving objective for air-conditioning of office environments in Hong Kong was confirmed effective based on simulation studies by the authors. However, given that simulation typically assumes a perfect control and feedback system, whether or not the benefits of DCDV system can be realized in practice, in particular under various space part load ratio (PLR) and sensible heat ratio (SHR) conditions, is subject to experimental verifications. In this study, a prototype which could be switched between the proposed DCDV system mode and the conventional system mode was constructed in a test facility for laboratory experiments. Through two sets of identical experiments under various space cooling load conditions, it was found that if compared to the conventional system, DCDV system could perform slightly better in achieving the desired indoor condition and in reducing the moisture-related air quality problems, but would result in 1–3% higher in cooling output. As for the overall coefficient of performance (COP o ), the DCDV system was found performed better by 5.6–7.2%. Additional experimental analysis was conducted for the development of a prediction model to relate the possible condensation period (ψ) on the DC coil with different operating parameters
Directory of Open Access Journals (Sweden)
SIBGHA SIDDIQUE SIDDIQUE
2016-10-01
Full Text Available Thermal insulation is the most effective energy saving measure for cooling in buildings. Therefore, the main subject of many engineering investigations is the selection and determination of the optimum insulation thickness. In the present study, the optimum insulation thickness on external walls and roofs is determined based on the peak cooling loads for an existing residential building in Lahore, Pakistan. Autodesk® Revit 2013 is used for the analysis of the building and determination of the peak cooling loads. The analysis shows that the optimum insulation thickness to reduce peak cooling loads up to 40.1% is 1 inch for external walls and roof respectively.
International Nuclear Information System (INIS)
Siddique, S.; Arif, S.; Khan, A.; Alam, A.T.
2016-01-01
Thermal insulation is the most effective energy saving measure for cooling in buildings. Therefore, the main subject of many engineering investigations is the selection and determination of the optimum insulation thickness. In the present study, the optimum insulation thickness on external walls and roofs is determined based on the peak cooling loads for an existing residential building in Lahore, Pakistan. Autodesk at the rate Revit 2013 is used for the analysis of the building and determination of the peak cooling loads. The analysis shows that the optimum insulation thickness to reduce peak cooling loads up to 40.1 percent is 1 inch for external walls and roof respectively. (author)
Prediction calculation of HTR-10 fuel loading for the first criticality
International Nuclear Information System (INIS)
Jing Xingqing; Yang Yongwei; Gu Yuxiang; Shan Wenzhi
2001-01-01
The 10 MW high temperature gas cooled reactor (HTR-10) was built at Institute of Nuclear Energy Technology, Tsinghua University, and the first criticality was attained in Dec. 2000. The high temperature gas cooled reactor physics simulation code VSOP was used for the prediction of the fuel loading for HTR-10 first criticality. The number of fuel element and graphite element was predicted to provide reference for the first criticality experiment. The prediction calculations toke into account the factors including the double heterogeneity of the fuel element, buckling feedback for the spectrum calculation, the effect of the mixture of the graphite and the fuel element, and the correction of the diffusion coefficients near the upper cavity based on the transport theory. The effects of impurities in the fuel and the graphite element in the core and those in the reflector graphite on the reactivity of the reactor were considered in detail. The first criticality experiment showed that the predicted values and the experiment results were in good agreement with little relative error less than 1%, which means the prediction was successful
International Nuclear Information System (INIS)
Sun, K.H.; Gonzalez-Santalo, J.M.; Tien, C.L.
1976-01-01
A model has been developed to calculate the heat transfer coefficients from the fuel rods to the steam-droplet mixture typical of Boiling Water Reactors under Emergency Core Cooling System (ECCS) operation conditions during a postulated loss-of-coolant accident. The model includes the heat transfer by convection to the vapor, the radiation from the surfaces to both the water droplets and the vapor, and the effects of droplet evaporation. The combined convection and radiation heat transfer coefficient can be evaluated with respect to the characteristic droplet size. Calculations of the heat transfer coefficient based on the droplet sizes obtained from the existing literature are consistent with those determined empirically from the Full-Length-Emergency-Cooling-Heat-Transfer (FLECHT) program. The present model can also be used to assess the effects of geometrical distortions (or deviations from nominal dimensions) on the heat transfer to the cooling medium in a rod bundle
Energy Technology Data Exchange (ETDEWEB)
Dho, Ho Seog; Kim, Tae Man; Cho, Chun Hyung [Korea Radioactive Waste Agency, Daejeon (Korea, Republic of)
2016-12-15
Recently, because the wet pool storage facilities of NPPs in Korea has become saturated, there has been much active R and D on an interim dry storage system using a transportation and storage cask. Generally, the shielding evaluation for the design of a spent fuel transportation and storage cask is performed by the design basis fuel, which selects the most conservative fuel among the fuels to be loaded into the cask. However, the loading of actual spent fuel into the transportation metal cask is not limited to the design basis fuel used in the shielding evaluation; the loading feasibility of actual spent fuel is determined by the shielding evaluation that considers the characteristics of the initial enrichment, the maximum burnup and the minimum cooling period. This study describes a shielding analysis method for determining the minimum cooling period of spent fuel that meets the domestic transportation standard of the dual purpose metal cask. In particular, the spent fuel of 3.0-4.5wt% initial enrichment, which has a large amount of release, was evaluated by segmented shielding calculations for efficient improvement of the results. The shielding evaluation revealed that about 81% of generated spent fuel from the domestic nuclear power plants until 2008 could be transported by the dual purpose metal cask. The results of this study will be helpful in establishing a technical basis for developing operating procedures for transportation of the dual purpose metal cask.
International Nuclear Information System (INIS)
Dho, Ho Seog; Kim, Tae Man; Cho, Chun Hyung
2016-01-01
Recently, because the wet pool storage facilities of NPPs in Korea has become saturated, there has been much active R and D on an interim dry storage system using a transportation and storage cask. Generally, the shielding evaluation for the design of a spent fuel transportation and storage cask is performed by the design basis fuel, which selects the most conservative fuel among the fuels to be loaded into the cask. However, the loading of actual spent fuel into the transportation metal cask is not limited to the design basis fuel used in the shielding evaluation; the loading feasibility of actual spent fuel is determined by the shielding evaluation that considers the characteristics of the initial enrichment, the maximum burnup and the minimum cooling period. This study describes a shielding analysis method for determining the minimum cooling period of spent fuel that meets the domestic transportation standard of the dual purpose metal cask. In particular, the spent fuel of 3.0-4.5wt% initial enrichment, which has a large amount of release, was evaluated by segmented shielding calculations for efficient improvement of the results. The shielding evaluation revealed that about 81% of generated spent fuel from the domestic nuclear power plants until 2008 could be transported by the dual purpose metal cask. The results of this study will be helpful in establishing a technical basis for developing operating procedures for transportation of the dual purpose metal cask
Directory of Open Access Journals (Sweden)
Xiaoqing Wei
2017-02-01
Full Text Available As one of the most widely used units in water cooling systems, the closed wet cooling towers (CWCTs have two typical counter-flow constructions, in which the spray water flows from the top to the bottom, and the moist air and cooling water flow in the opposite direction vertically (parallel or horizontally (cross, respectively. This study aims to present a simplified calculation method for conveniently and accurately analyzing the thermal performance of the two types of counter-flow CWCTs, viz. the parallel counter-flow CWCT (PCFCWCT and the cross counter-flow CWCT (CCFCWCT. A simplified cooling capacity model that just includes two characteristic parameters is developed. The Levenberg–Marquardt method is employed to determine the model parameters by curve fitting of experimental data. Based on the proposed model, the predicted outlet temperatures of the process water are compared with the measurements of a PCFCWCT and a CCFCWCT, respectively, reported in the literature. The results indicate that the predicted values agree well with the experimental data in previous studies. The maximum absolute errors in predicting the process water outlet temperatures are 0.20 and 0.24 °C for the PCFCWCT and CCFCWCT, respectively. These results indicate that the simplified method is reliable for performance prediction of counter-flow CWCTs. Although the flow patterns of the two towers are different, the variation trends of thermal performance are similar to each other under various operating conditions. The inlet air wet-bulb temperature, inlet cooling water temperature, air flow rate, and cooling water flow rate are crucial for determining the cooling capacity of a counter-flow CWCT, while the cooling tower effectiveness is mainly determined by the flow rates of air and cooling water. Compared with the CCFCWCT, the PCFCWCT is much more applicable in a large-scale cooling water system, and the superiority would be amplified when the scale of water
Heat load studies of a water-cooled minichannel monochromator for synchrotron x-ray beams
Freund, Andreas K.; Arthur, John R.; Zhang, Lin
1997-12-01
We fabricated a water-cooled silicon monochromator crystal with small channels for the special case of a double-crystal fixed-exit monochromator design where the beam walks across the crystal when the x-ray energy is changed. The two parts of the cooled device were assembled using a new technique based on low melting point solder. The bending of the system produced by this technique could be perfectly compensated by mechanical counter-bending. Heat load tests of the monochromator in a synchrotron beam of 75 W total power, 3 mm high and 15 mm wide, generated by a multipole wiggler at SSRL, showed that the thermal slope error of the crystal is 1 arcsec/40 W power, in full agreement with finite element analysis. The cooling scheme is adequate for bending magnet beamlines at the ESRF and present wiggler beamlines at the SSRL.
Passive Method to Reduce Solar Energy Effect on the Cooling Load in Buildings
Directory of Open Access Journals (Sweden)
Orfi J.
2012-10-01
Full Text Available Energy needed for cooling residential and industrial buildings in hot weather countries is the major issue. The period needed for cooling or comfort conditions in those countries exceeds five months and outdoor temperature reaches more than 40 °C. Also, the solar intensity usually high and can reach about one kW per m2. Hence, any attempt to reduce the effect of solar energy on the cooling load is worthy to investigate. The present work analyzes using artificial, naturally ventilated, shading covers to reduce the effect of solar energy. Analytical and numerical analyzes were performed on the effect of adding a ventilated cover to walls and roof exposed to the solar energy.
Directory of Open Access Journals (Sweden)
Trzaska J.
2016-09-01
Full Text Available In this paper, the equations applied for the purpose of the calculations of the hardness of continuously cooled structural steels upon the basis of the temperature of austenitizing. The independent variables of the hardness model were: the mass concentrations of elements, the austenitizing temperature and the cooling rate. The equations were developed with the application of the following methods: multiple regression and logistic regression. In this paper, attention was paid to preparing data for the purpose of calculations, to the methodology of the calculations, and also to the assessment of the quality of developed formulas. The collection of empirical data was prepared upon the basis of more than 500 CCT diagrams.
CSIR Research Space (South Africa)
Kumirai, T
2012-10-01
Full Text Available reduces its heating and cooling loads the most. 3. Applying both roof and ceiling insulation should always be avoided. 4. Building insulation is an effective intervention in all climatic regions. 5. Slightly increasing the thermal mass of a wall... were designed to evaluate the following: ? Case A ? base case ? Case B ? insulated walls ? Case C ? insulated walls and insulated ceiling ? Case D ? insulated walls, insulated ceiling and roof ? Case E ? increased thermal mass wall and insulated...
Study on simulation methods of atrium building cooling load in hot and humid regions
Energy Technology Data Exchange (ETDEWEB)
Pan, Yiqun; Li, Yuming; Huang, Zhizhong [Institute of Building Performance and Technology, Sino-German College of Applied Sciences, Tongji University, 1239 Siping Road, Shanghai 200092 (China); Wu, Gang [Weldtech Technology (Shanghai) Co. Ltd. (China)
2010-10-15
In recent years, highly glazed atria are popular because of their architectural aesthetics and advantage of introducing daylight into inside. However, cooling load estimation of such atrium buildings is difficult due to complex thermal phenomena that occur in the atrium space. The study aims to find out a simplified method of estimating cooling loads through simulations for various types of atria in hot and humid regions. Atrium buildings are divided into different types. For every type of atrium buildings, both CFD and energy models are developed. A standard method versus the simplified one is proposed to simulate cooling load of atria in EnergyPlus based on different room air temperature patterns as a result from CFD simulation. It incorporates CFD results as input into non-dimensional height room air models in EnergyPlus, and the simulation results are defined as a baseline model in order to compare with the results from the simplified method for every category of atrium buildings. In order to further validate the simplified method an actual atrium office building is tested on site in a typical summer day and measured results are compared with simulation results using the simplified methods. Finally, appropriate methods of simulating different types of atrium buildings are proposed. (author)
International Nuclear Information System (INIS)
Yu, F.W.; Chan, K.T.
2005-01-01
In cities located in a subtropical climate, air-cooled chillers are commonly used to provide cooling to the indoor environment. This accounts for the increasing electricity demand of buildings over the decades. This paper investigates how the condensing temperature serves to accurately determine the energy efficiency, or coefficient of performance (COP), of air-cooled chillers under part load conditions. An experiment on an air-cooled reciprocating chiller showed that for any given operating condition, the COP of the chiller varies, depending on how the condensing temperature is controlled. A sensitivity analysis is implemented to investigate to what extent COP is responding to changes in operating variables and confirms that the condensing temperature is an adequate variable to gauge COP under various operating conditions. The specifications of the upper limit for the condensing temperature in order to improve the energy efficiency of air-cooled chillers are discussed. The results of this work will give designers and researchers a good idea about how to model chiller energy performance curves in the thermal and energy computation exercises
Forest fuel reduces the nitrogen load - calculations of nitrogen flows
International Nuclear Information System (INIS)
Burstroem, F.; Johansson, Jan.
1995-12-01
Nitrogen deposition in Sweden has increased strongly during recent decades, particularly in southern Sweden. Nitrogen appears to be largely accumulated in biomass and in the soil. It is therefore desirable to check the accumulation of nitrogen in the forest. The most suitable way of doing this is to remove more nitrogen-rich biomass from the forest, i.e., increase the removal of felling residues from final fellings and cleanings. An ecological condition for intensive removal of fuel is that the ashes are returned. The critical load for nitrogen, CL(N), indicates the level of nitrogen deposition that the forest can withstand without leading to ecological changes. Today, nitrogen deposition is higher than the CL(N) in almost all of Sweden. CL(N) is calculated in such a manner that nitrogen deposition should largely be balanced by nitrogen losses through harvesting during a forest rotation. The value of CL(N) thus largely depends on how much nitrogen is removed with the harvested biomass. When both stems and felling residues are harvested, the CL(N) is about three times higher than in conventional forestry. The increase is directly related to the amount of nitrogen in the removed biofuel. Use of biofuel also causes a certain amount of nitrogen emissions. From the environmental viewpoint there is no difference between the sources of the nitrogen compounds. An analysis of the entire fuel chain shows that, compared with the amount of nitrogen removed from the forest with the fuel, about 5 % will be emitted as nitrogen oxides or ammonia during combustion, and a further ca 5 % during handling and transports. A net amount of about 90 % of biomass nitrogen is removed from the system and becomes inert nitrogen (N 2 ). 60 refs, 3 figs, 4 tabs, 11 appendices
Energy Technology Data Exchange (ETDEWEB)
Pahn, T. [Pahn Ingenieure, Am Seegraben 17b 03051 Cottbus Germany; Rolfes, R. [Institut f?r Statik und Dynamik, Leibniz Universit?t Hannover, Appelstra?e 9A 30167 Hannover Germany; Jonkman, J. [National Renewable Energy Laboratory, 15013 Denver West Parkway Golden Colorado 80401 USA
2017-02-20
A significant number of wind turbines installed today have reached their designed service life of 20 years, and the number will rise continuously. Most of these turbines promise a more economical performance if they operate for more than 20 years. To assess a continued operation, we have to analyze the load-bearing capacity of the support structure with respect to site-specific conditions. Such an analysis requires the comparison of the loads used for the design of the support structure with the actual loads experienced. This publication presents the application of a so-called inverse load calculation to a 5-MW wind turbine support structure. The inverse load calculation determines external loads derived from a mechanical description of the support structure and from measured structural responses. Using numerical simulations with the software fast, we investigated the influence of wind-turbine-specific effects such as the wind turbine control or the dynamic interaction between the loads and the support structure to the presented inverse load calculation procedure. fast is used to study the inverse calculation of simultaneously acting wind and wave loads, which has not been carried out until now. Furthermore, the application of the inverse load calculation procedure to a real 5-MW wind turbine support structure is demonstrated. In terms of this practical application, setting up the mechanical system for the support structure using measurement data is discussed. The paper presents results for defined load cases and assesses the accuracy of the inversely derived dynamic loads for both the simulations and the practical application.
Performance of an optimally contact-cooled high-heat-load mirror at the APS
International Nuclear Information System (INIS)
Cai, Z.; Khounsary, A.; Lai, B.; McNulty, I.; Yun, W.
1998-01-01
X-ray undulator beamlines at third-generation synchrotrons facilities use either a monochromator or a mirror as the first optical element. In this paper, the thermal and optical performance of an optimally designed contact-cooled high-heat-load x-ray mirror used as the first optical element on the 2ID undulator beamline at the Advanced Photon Source (APS) is reported. It is shown that this simple and economical mirror design can comfortably handle the high heat load of undulator beamlines and provide good performance with long-term reliability and ease of operation. Availability and advantages of such mirrors can make the mirror-first approach to high-heat-load beamline design an attractive alternative to monochromator-first beamlines in many circumstances
Transient Side Load Analysis of Out-of-Round Film-Cooled Nozzle Extensions
Wang, Ten-See; Lin, Jeff; Ruf, Joe; Guidos, Mike
2012-01-01
There was interest in understanding the impact of out-of-round nozzle extension on the nozzle side load during transient startup operations. The out-of-round nozzle extension could be the result of asymmetric internal stresses, deformation induced by previous tests, and asymmetric loads induced by hardware attached to the nozzle. The objective of this study was therefore to computationally investigate the effect of out-of-round nozzle extension on the nozzle side loads during an engine startup transient. The rocket engine studied encompasses a regeneratively cooled chamber and nozzle, along with a film cooled nozzle extension. The computational methodology is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, and transient inlet boundary flow properties derived from an engine system simulation. Six three-dimensional cases were performed with the out-of-roundness achieved by three different degrees of ovalization, elongated on lateral y and z axes: one slightly out-of-round, one more out-of-round, and one significantly out-of-round. The results show that the separation line jump was the primary source of the peak side loads. Comparing to the peak side load of the perfectly round nozzle, the peak side loads increased for the slightly and more ovalized nozzle extensions, and either increased or decreased for the two significantly ovalized nozzle extensions. A theory based on the counteraction of the flow destabilizing effect of an exacerbated asymmetrical flow caused by a lower degree of ovalization, and the flow stabilizing effect of a more symmetrical flow, created also by ovalization, is presented to explain the observations obtained in this effort.
Transient Three-Dimensional Side Load Analysis of Out-of-Round Film Cooled Nozzles
Wang, Ten-See; Lin, Jeff; Ruf, Joe; Guidos, Mike
2010-01-01
The objective of this study is to investigate the effect of nozzle out-of-roundness on the transient startup side loads at a high altitude, with an anchored computational methodology. The out-of-roundness could be the result of asymmetric loads induced by hardware attached to the nozzle, asymmetric internal stresses induced by previous tests, and deformation, such as creep, from previous tests. The rocket engine studied encompasses a regeneratively cooled thrust chamber and a film cooled nozzle extension with film coolant distributed from a turbine exhaust manifold. The computational methodology is based on an unstructured-grid, pressure-based computational fluid dynamics formulation, and a transient inlet history based on an engine system simulation. Transient startup computations were performed with the out-of-roundness achieved by four different degrees of ovalization: one perfectly round, one slightly out-of-round, one more out-of-round, and one significantly out-of-round. The results show that the separation-line-jump is the peak side load physics for the round, slightly our-of-round, and more out-of-round cases, and the peak side load increases as the degree of out-of-roundness increases. For the significantly out-of-round nozzle, however, the peak side load reduces to comparable to that of the round nozzle and the separation line jump is not the peak side load physics. The counter-intuitive result of the significantly out-of-round case is found to be related to a side force reduction mechanism that splits the effect of the separation-line-jump into two parts, not only in the circumferential direction and most importantly in time.
Miller, R. D.; Anderson, L. R.
1979-01-01
The LOADS program L218, a digital computer program that calculates dynamic load coefficient matrices utilizing the force summation method, is described. The load equations are derived for a flight vehicle in straight and level flight and excited by gusts and/or control motions. In addition, sensor equations are calculated for use with an active control system. The load coefficient matrices are calculated for the following types of loads: translational and rotational accelerations, velocities, and displacements; panel aerodynamic forces; net panel forces; shears and moments. Program usage and a brief description of the analysis used are presented. A description of the design and structure of the program to aid those who will maintain and/or modify the program in the future is included.
Effect of LED lighting on the cooling and heating loads in office buildings
International Nuclear Information System (INIS)
Ahn, Byung-Lip; Jang, Cheol-Yong; Leigh, Seung-Bok; Yoo, Seunghwan; Jeong, Hakgeun
2014-01-01
Highlights: • Application of heat control strategy reduces total energy consumption of LED lighting. • Convective heat from LED lighting should be emitted outdoors during cooling period. • Seasonal optimization of convective heat lowers total energy consumption. - Abstract: LED lighting has the potential to provide energy savings, and in many countries, there are policies to encourage its use owing to its higher efficiency and longer life in comparison to other lighting fixtures. However, since 75–85% of the light electric power in LED lights is still generated as heat, the sole use of LED lighting in a building could have a negative effect on the cooling load. In this paper, we study the heating properties of LED lighting and establish a management strategy to exploit these properties to reduce the energy used for heating and cooling of buildings. Using a simulation program, the energy consumption of the Green Building in Daejeon, Korea, and the virtual building provided by the U.S. Department of Energy (DOE) was computed according for different light fixtures. A control strategy is more applicable to LED lighting than to general fluorescent lighting, especially for the cooling of a building, because the use of a return-air duct and the heat sinks on the LED fixtures allow the heat to be better directed. Deployment of LED lights in combination with such a control strategy can help to increase the energy efficiency of a building
Directory of Open Access Journals (Sweden)
Ji Li
2018-05-01
Full Text Available Evaporative cooling is a green, energy-efficient cooling technology adopted in hot and dry regions, which has wider application in the field of air-conditioning systems. Outdoor meteorological parameters have a great influence on the operation mode and control strategy of evaporative cooling air-conditioning systems, and the system load distribution and system configuration will be affected. This paper aims at investigating the load distribution of semi-central evaporative cooling air-conditioning systems under the condition of hourly outdoor meteorological parameters. Firstly, this paper introduced the design partition, operation mode, controlling strategy and load distribution method on semi-central evaporative cooling air-conditioning system. Then, taking an office building in Lanzhou (China as an example, the evaporative cooling air-conditioning system was divided into five regions and the load distribution was simulated by TRNSYS (The Transient Energy System Simulation Tool under the condition of hourly outdoor meteorological parameters. Finally, the results have shown that the evaporative cooling air-conditioning system can provide 25.46% of the building loads, which was of great significance to reduce the energy consumption of air-conditioning system.
Measurement and calculation of radiation sources in the primary cooling system of JOYO
International Nuclear Information System (INIS)
Suzuki, S.; Iizawa, K.; Ohtani, N.; Kobayashi, T.; Horie, J.; Handa, H.
1987-01-01
Production and transfer of radiation sources in the primary cooling system are important consideration in the LMFBR plant from the viewpoint of radiation protection and shielding design. These items were evaluated with calculations and/or measurements in the Japanese experimental fast reactor JOYO. In this study, calculations were made with the DOT3.5 0 two-dimensional discrete ordinate transport code to determine the neutron flux and production rate distributions of radiation sources in the reactor vessel. Using the DOT results, the behavior in primary coolant sodium of the CP (radioactive corrosion products) which were released from the reactor structural material was also calculationally analyzed with the PSYCHE code developed by PNC. These analytical results were compared with the measured results to get the verification of analysis methods and to estimate the accuracy of calculations
Post-examination of helium-cooled tungsten components exposed to DEMO specific cyclic thermal loads
International Nuclear Information System (INIS)
Ritz, G.; Hirai, T.; Linke, J.; Norajitra, P.; Giniyatulin, R.; Singheiser, L.
2009-01-01
A concept of helium-cooled tungsten finger module was developed for the European DEMO divertor. The concept was realized and tested under DEMO specific cyclic thermal loads up to 10 MW/m 2 . The modules were examined carefully before and after loading by metallography and microstructural analyses. While before loading mainly discrete and shallow cracks were found on the tungsten surface due to the manufacturing process, dense crack networks were observed at the loaded surfaces due to the thermal stress. In addition, cracks occurred in the structural, heat sink part and propagated along the grains orientation of the deformed tungsten material. Facilitated by cracking, the molten brazing metal between the tungsten plasma facing material and the W-La 2 O 3 heat sink, that could not withstand the operational temperatures, infiltrated the tungsten components and, due to capillary forces, even reached the plasma facing surface through the cracks. The formed cavity in the brazed layer reduced the heat conduction and the modules were further damaged due to overheating during the applied heat loads. Based on this detailed characterization and possible improvements of the design and of the manufacturing routes are discussed.
Maximizing allowable cask payloads using zone-loading and cooling table specifications
International Nuclear Information System (INIS)
Hopf, J.E.; Lloyd, T.
2004-01-01
The newer dual-purpose canister designs generally have a higher fuel assembly capacity than earlier designs. Due to the resulting increases in thermal and radiological source terms from the assembly payload, this will generally result in higher cask system temperatures and cask external dose rates, making it more difficult to meet 10CFR71 and 10CFR72 thermal and radiological requirements. One approach to addressing this issue would be to employ advanced, and potentially expensive, engineering features to enhance cask shielding and heat removal capabilities. Another approach involves the strategic loading of fuel assemblies in specific locations within the dual-purpose canister, along with a more rigorous analysis of the specific assembly payload configuration inside the canister. This second approach, which does not involve difficult engineering design and fabrication, and which does not add to the cost of the canister or cask, is the subject of this paper. Traditional cask licensing analyses simply model a uniform assembly payload over the entire canister interior. One, or perhaps a few ''design-basis'' combinations of burnup, enrichment, and cooling time are analyzed and qualified. All loaded assemblies must be completely bounded by one or more of the analyzed sets of design basis assembly parameters. Effectively, the ''hottest'' possible assembly is modeled in all loading slots. This paper discusses two techniques that could greatly increase the number of spent fuel pool assemblies that qualify for storage or transportation, especially when taken together. The first technique, referred to as ''zone loading'' involves loading relatively ''cold'' assemblies in the locations around the edge of the canister. The outer assemblies will almost entirely shield the neutron and gamma fluxes from the interior assemblies, reducing their contribution to cask external dose rate to very low levels. This allows much ''hotter'' possible assembly is modeled in all loading slots
International Nuclear Information System (INIS)
Cherkashov, Yu.M.; Vasilevskij, V.P.; Labazov, V.H.; Loninov, A.Ya.; Molochnikov, Yu.S.; Novosel'skij, O.Yu.; Podlazov, L.N.; Pavlov, V.B.; Pushkarev, V.I.
1981-01-01
The analysis of thermohydraulic and neutron-physical processes occurring in the RBMK-1500 reactor during the reactor emergency cooling system triggering (RECS) after the maximum designed accident (MDA) is conducted. The MDA means hypothetical instant hilliotine break of the main circulating pump head collector. During the whole cooling down period the RECS should provide the temperature level of the fuel elements not exceeding 1200 deg C and the channel pipe temperature - 600 deg C. The principal flowsheet of the balloon type RECS is described. Calculations of the valve fast response effect on the RECS productivity are carried out. It is concluded that the chosen balloon RECS provides reliable temperature modes of fuel elements naand channel pipes under the MDA conditions. At the same time a momentary splash of neutron power by the value not more than 10% can take place [ru
ATHENA calculation model for the ITER-FEAT divertor cooling system. Final report with updates
International Nuclear Information System (INIS)
Eriksson, John; Sjoeberg, A.; Sponton, L.L.
2001-05-01
An ATHENA model of the ITER-FEAT divertor cooling system has been developed for the purpose of calculating and evaluating consequences of different thermal-hydraulic accidents as specified in the Accident Analysis Specifications for the ITER-FEAT Generic Site Safety Report. The model is able to assess situations for a variety of conceivable operational transients from small flow disturbances to more critical conditions such as total blackout caused by a loss of offsite and emergency power. The main objective for analyzing this type of scenarios is to determine margins against jeopardizing the integrity of the divertor cooling system components and pipings. The model of the divertor primary heat transport system encompasses the divertor cassettes, the port limiter systems, the pressurizer, the heat exchanger and all feed and return pipes of these components. The development was pursued according to practices and procedures outlined in the ATHENA code manuals using available modelling components such as volumes, junctions, heat structures and process controls
Calculations of the Acceleration of Centrifugal Loading on Adherent Cells
Chen, Kang; Song, Yang; Liu, Qing; Zhang, Chunqiu
2017-07-01
Studies have shown that the morphology and function of living cells are greatly affected by the state of different high acceleration. Based on the centrifuge, we designed a centrifugal cell loading machine for the mechanical biology of cells under high acceleration loading. For the machine, the feasibility of the experiment was studied by means of constant acceleration or variable acceleration loading in the Petri dish fixture and/or culture flask. Here we analyzed the distribution of the acceleration of the cells with the change of position and size of the culturing device quantitatively. It is obtained that Petri dish fixture and/or culture flask can be used for constant acceleration loading by experiments; the centripetal acceleration of the adherent cells increases with the increase of the distance between the rotor center of the centrifuge and the fixture of the Petri dish and the size of the fixture. It achieves the idea that the general biology laboratory can conduct the study of mechanical biology at high acceleration. It also provides a basis for more accurate study of the law of high acceleration on mechanobiology of cells.
Accurate green water loads calculation using naval hydro pack
Jasak, H.; Gatin, I.; Vukčević, V.
2017-12-01
An extensive verification and validation of Finite Volume based CFD software Naval Hydro based on foam-extend is presented in this paper for green water loads. Two-phase numerical model with advanced methods for treating the free surface is employed. Pressure loads on horizontal deck of Floating Production Storage and Offloading vessel (FPSO) model are compared to experimental results from [1] for three incident regular waves. Pressure peaks and integrals of pressure in time are measured on ten different locations on deck for each case. Pressure peaks and integrals are evaluated as average values among the measured incident wave periods, where periodic uncertainty is assessed for both numerical and experimental results. Spatial and temporal discretization refinement study is performed providing numerical discretization uncertainties.
Calculations of concrete plates and shells under impact load
International Nuclear Information System (INIS)
Kappler, H.; Krings, W.
1982-01-01
The dynamic behaviour of concrete slabs and shells is determined for a given load time function using axisymmetric computational models with an exact formulation for the midpoint. On the basis of a finite difference method, rotational inertia, shear deformation, elasticity and cracking are taken into account. For shells the coupling of bending moment and normal force is considered. Comparisons with two-dimensional models show good agreement connected with a considerable reduction of computational time. (orig.) [de
Osuský, F.; Bahdanovich, R.; Farkas, G.; Haščík, J.; Tikhomirov, G. V.
2017-01-01
The paper is focused on development of the coupled neutronics-thermal hydraulics model for the Gas-cooled Fast Reactor. It is necessary to carefully investigate coupled calculations of new concepts to avoid recriticality scenarios, as it is not possible to ensure sub-critical state for a fast reactor core under core disruptive accident conditions. Above mentioned calculations are also very suitable for development of new passive or inherent safety systems that can mitigate the occurrence of the recriticality scenarios. In the paper, the most promising fuel material compositions together with a geometry model are described for the Gas-cooled fast reactor. Seven fuel pin and fuel assembly geometry is proposed as a test case for coupled calculation with three different enrichments of fissile material in the form of Pu-UC. The reflective boundary condition is used in radial directions of the test case and vacuum boundary condition is used in axial directions. During these condition, the nuclear system is in super-critical state and to achieve a stable state (which is numerical representation of operational conditions) it is necessary to decrease the reactivity of the system. The iteration scheme is proposed, where SCALE code system is used for collapsing of a macroscopic cross-section into few group representation as input for coupled code NESTLE.
Multicycle Optimization of Advanced Gas-Cooled Reactor Loading Patterns Using Genetic Algorithms
International Nuclear Information System (INIS)
Ziver, A. Kemal; Carter, Jonathan N.; Pain, Christopher C.; Oliveira, Cassiano R.E. de; Goddard, Antony J. H.; Overton, Richard S.
2003-01-01
A genetic algorithm (GA)-based optimizer (GAOPT) has been developed for in-core fuel management of advanced gas-cooled reactors (AGRs) at HINKLEY B and HARTLEPOOL, which employ on-load and off-load refueling, respectively. The optimizer has been linked to the reactor analysis code PANTHER for the automated evaluation of loading patterns in a two-dimensional geometry, which is collapsed from the three-dimensional reactor model. GAOPT uses a directed stochastic (Monte Carlo) algorithm to generate initial population members, within predetermined constraints, for use in GAs, which apply the standard genetic operators: selection by tournament, crossover, and mutation. The GAOPT is able to generate and optimize loading patterns for successive reactor cycles (multicycle) within acceptable CPU times even on single-processor systems. The algorithm allows radial shuffling of fuel assemblies in a multicycle refueling optimization, which is constructed to aid long-term core management planning decisions. This paper presents the application of the GA-based optimization to two AGR stations, which apply different in-core management operational rules. Results obtained from the testing of GAOPT are discussed
ASSESSMENT OF CLIMATE CHANGE IMPACT ON THE REQUIRED COOLING LOAD OF THE HOSPITAL BUILDINGS
Directory of Open Access Journals (Sweden)
M. AHMADZADEHTALATAPEH
2017-08-01
Full Text Available The impact of climate change on the energy performance of the Heating, Ventilation and Air Conditioning (HVAC systems was studied in this research. The present research employs the Transient System Simulation Software (TRNSYS to study the hour-by-hour influence of the climate change scenario on a HVAC system performance by modeling the system in the TRNSYS software as the base line model. To this end, a HVAC system operating in a hospital as a high energy demanding building was selected for data collection, analysis and simulation. Three sets of predicted Typical Meteorological Year (TMY data for the region are used for simulation in the TRNSYS to analyze the established indoor air conditions and yearly required cooling loads by the building. Based on the predictions and comparison of the findings with the year 2000, it can be estimated that the yearly required cooling load for 2020 and 2050 would be increased by 4.66% and 7.3%, respectively.
A Technique for Temperature and Ultimate Load Calculations of Thin Targets in a Pulsed Electron Beam
DEFF Research Database (Denmark)
Hansen, Jørgen-Walther; Lundsager, Per
1979-01-01
A technique is presented for the calculation of transient temperature distributions and ultimate load of rotationally symmetric thin membranes with uniform lateral load and exposed to a pulsed electron beam from a linear accelerator. Heat transfer by conduction is considered the only transfer...... mechanism. The ultimate load is calculated on the basis of large plastic strain analysis. Analysis of one aluminum and one titanium membrane is shown....
International Nuclear Information System (INIS)
Tanaka, Mitsugu
1978-01-01
LWR plants have a containment spray system to reduce the escape of radioactive material to the environment in a loss-of-coolant accident (LOCA) by washing out fission products, especially radioiodine, and condensing the steam to lower the pressure. For carrying out the containment spray tests, pressure and temperature behaviour of the JAERI Model Containment Vessel in spray cooling has been calculated with computer program CONTEMPT-LT. The following could be studied quantitatively: (1) pressure and temperature raise rates for steam addition rate and (2) pressure fall rate for spray flow rate and spray heat transfer efficiency. (auth.)
CFD results for temperature dependence water cooling pump NPSH calculations - 15425
International Nuclear Information System (INIS)
Strongin, M.P.
2015-01-01
In this work the possibility to model the pump for water cooling reactors behavior in the critical situation was considered for cases when water temperature suddenly increases. In cases like this, cavitation effects may cause pump shutoff and consequently stop the reactor cooling. Centrifugal pump was modeled. The calculations demonstrate strong dependence of NPSH (net-positive-suction-head) on the water temperature on the pump inlet. The water temperature on the inlet lies between 25 and 180 C. degrees. The pump head performance curve has a step-like slope below NPSH point. Therefore, if the pressure on the pump inlet is below than NPSH, it leads to the pump shutoff. For high water temperature on the pump inlet, NPSH follows the vapor saturated pressure for given temperature with some offset. The results clearly show that in case of accidental increase of temperature in the cooling loop, special measures are needed to support the pressure on the pump inlet to prevent pump shutoff. (author)
Time domain calculation of connector loads of a very large floating structure
Gu, Jiayang; Wu, Jie; Qi, Enrong; Guan, Yifeng; Yuan, Yubo
2015-06-01
Loads generated after an air crash, ship collision, and other accidents may destroy very large floating structures (VLFSs) and create additional connector loads. In this study, the combined effects of ship collision and wave loads are considered to establish motion differential equations for a multi-body VLFS. A time domain calculation method is proposed to calculate the connector load of the VLFS in waves. The Longuet-Higgins model is employed to simulate the stochastic wave load. Fluid force and hydrodynamic coefficient are obtained with DNV Sesam software. The motion differential equation is calculated by applying the time domain method when the frequency domain hydrodynamic coefficient is converted into the memory function of the motion differential equation of the time domain. As a result of the combined action of wave and impact loads, high-frequency oscillation is observed in the time history curve of the connector load. At wave directions of 0° and 75°, the regularities of the time history curves of the connector loads in different directions are similar and the connector loads of C1 and C2 in the X direction are the largest. The oscillation load is observed in the connector in the Y direction at a wave direction of 75° and not at 0°. This paper presents a time domain calculation method of connector load to provide a certain reference function for the future development of Chinese VLFS
Application of CFD based wave loads in aeroelastic calculations
DEFF Research Database (Denmark)
Schløer, Signe; Paulsen, Bo Terp; Bredmose, Henrik
2014-01-01
Two fully nonlinear irregular wave realizations with different significant wave heights are considered. The wave realizations are both calculated in the potential flow solver Ocean-Wave3D and in a coupled domain decomposed potential-flow CFD solver. The surface elevations of the calculated wave...... domain decomposed potentialflow CFD solver result in different dynamic forces in the tower and monopile, despite that the static forces on a fixed monopile are similar. The changes are due to differences in the force profiles and wave steepness in the two solvers. The results indicate that an accurate...
Cyclic complex loading of 316 stainless steel: Experiments and calculations
International Nuclear Information System (INIS)
Jacquelin, B.; Hourlier, F.; Dang Van, K.; Stolz, C.
1981-01-01
To test the ability of cyclic constitutive law established by mean of uniaxial test a benchmark is proposed. The calculated results using the model of Chaboche-Cordier-Dang Van are compared with experimental data obtained on cylindrical specimens undergoing simultaneously constant torque and cyclic tension. (orig.)
Bakker, A; Siegel, J A; Mendell, M J; Peccia, J
2018-05-30
We investigated bacterial and fungal concentrations on cooling coils of commercial AC units and quantified associations between microbial loads and AC unit or building operational parameters. A field campaign was conducted to sample 25 AC units in the humid, subtropical climate of Southern CT, USA and 15 AC units in the hot-summer Mediterranean climate of Sacramento, CA, USA. Median concentrations (with interquartile range) of bacteria and fungi on the cooling coils were 1.2 × 10 7 (5.1 × 10 6 -3.9 × 10 7 ) cells/m 2 and 7.6 × 10 5 (5.6 × 10 4 -4.4 × 10 6 ) spore equivalents (SE)/m 2 , respectively. Concentrations varied among units with median unit concentrations ranging three orders of magnitude for bacteria and seven orders of magnitude for fungi. Controlled comparisons and multivariable regressions indicate that dominant factors associated with AC coil loading include the nominal efficiency of upstream filters (P = .008 for bacteria and P < .001 for fungi) and coil moisture, which was reflected in fungal loading differences between top and bottom halves of the AC coils in Southern CT (P = .05) and the dew points of the two climates considered (P = .04). Environmental and building characteristics explained 42% (P < .001) of bacterial concentration variability and 66% (P < .001) of fungal concentration variability among samples. © 2018 John Wiley & Sons A/S. Published by John Wiley & Sons Ltd.
International Nuclear Information System (INIS)
Chevet, G; Schlosser, J; Courtois, X; Escourbiac, F; Missirlian, M; Herb, V; Martin, E; Camus, G; Braccini, M
2009-01-01
In order to predict the lifetime of carbon fibre composite (CFC) armoured plasma-facing components in magnetic fusion devices, it is necessary to analyse the damage mechanisms and to model the damage propagation under cycling heat loads. At Tore Supra studies have been launched to better understand the damage process of the armoured flat tile elements of the actively cooled toroidal pump limiter, leading to the characterization of the damageable mechanical behaviour of the used N11 CFC material and of the CFC/Cu bond. Up until now the calculations have shown damage developing in the CFC (within the zone submitted to high shear stress) and in the bond (from the free edge of the CFC/Cu interface). Damage is due to manufacturing shear stresses and does not evolve under heat due to stress relaxation. For the ITER divertor, NB31 material has been characterized and the characterization of NB41 is in progress. Finite element calculations show again the development of CFC damage in the high shear stress zones after manufacturing. Stresses also decrease under heat flux so the damage does not evolve. The characterization of the CFC/Cu bond is more complex due to the monoblock geometry, which leads to more scattered stresses. These calculations allow the fabrication difficulties to be better understood and will help to analyse future high heat flux tests on various mock-ups.
Impact of nuclear data on sodium-cooled fast reactor calculations
International Nuclear Information System (INIS)
Aures, A.; Bostelmann, F.; Zwermann, W.; Velkov, K.
2016-01-01
Neutron transport and depletion calculations are performed in combination with various nuclear data libraries in order to assess the impact of nuclear data on safety-relevant parameters of sodium-cooled fast reactors. These calculations are supplemented by systematic uncertainty analyses with respect to nuclear data. Analysed quantities are the multiplication factor and nuclide densities as a function of burn-up and the Doppler and Na-void reactivity coefficients at begin of cycle. While ENDF/B-VII.0 / -VII.1 yield rather consistent results, larger discrepancies are observed between the JEFF libraries. While the newest evaluation, JEFF-3.2, agrees with the ENDF/B-VII libraries, the JEFF-3.1.2 library yields significant larger multiplication factors. (authors)
Directory of Open Access Journals (Sweden)
Tran Hoang Hai Nam
2015-01-01
Full Text Available This study aims to evaluate the influence of urban heat island (UHI under the Hanoi Master Plan 2030 on the energy consumption for space cooling in residential buildings. The weather conditions under the current and future status (master plan condition simulated in the previous study (Trihamdani et al., 2014 were used and cooling loads in all the residential buildings in Hanoi over the hottest month were estimated under the simulated current and future conditions by using the building simulation program, TRNSYS (v17. Three most typical housing types in the city were selected for the simulation. The cooling loads of respective housing types were obtained in each of the districts in Hanoi. The results show that the total cooling loads over June 2010 is approximately 683 Terajoule (TJ under the current status, but it is predicted to increase to 903 TJ under the master plan condition. The increment is largely due to the increase in number of households (203 TJ or 92%, but partially due to the increase in urban temperature, i.e. UHI effect (17 TJ or 8%. The increments in new built-up areas were found to be larger than those in existing built-up areas. The cooling load in apartment is approximately half of that in detached house, which is approximately half of that in row house. Moreover, it was seen that although sensible cooling loads increased with the increase in outdoor temperature, the latent cooling loads decreased due to the decrease in absolute humidity and the increase in air temperature.
International Nuclear Information System (INIS)
Han Song; Yang Yongwei
2007-01-01
Through the analysis of the effect of heavy metal actinides on the effective multiplication constant (k eff ) of the core in accelerator-driven system (ADS) sodium-cooled fast reactor loaded with metallic fuel, we gave the method for determining fuel components. the characteristics of minor actinides (MAs) transmutation was analyzed in detail. 3D burn-up code COUPLE, which couples MCNP4c3 and ORIGEN2, was applied to the neutron simulation and burn up calculation. The results of optimized scheme shows that adjusting the proportion of 239 Pu and maintaining the value during the burn-up cycle is an efficient method of designing k eff and keeping stable during the burn-up cycle. Spallation neutrons lead to the neutron spectrum harder at inner core than that at outer core. It is in favor of improving MA's fission cross sections and the capture-to-fission ratio. The total MAs transmutation support ratio 8.3 achieves excellent transmutation effect. For higher flux at inner core leads to obvious differences on transmutation efficiency,only disposing MAs at inner core is in favor of decreasing the loading mass and improving MAs transmutation effect. (authors)
Wang, Yaping; Lin, Shunjiang; Yang, Zhibin
2017-05-01
In the traditional three-phase power flow calculation of the low voltage distribution network, the load model is described as constant power. Since this model cannot reflect the characteristics of actual loads, the result of the traditional calculation is always different from the actual situation. In this paper, the load model in which dynamic load represented by air conditioners parallel with static load represented by lighting loads is used to describe characteristics of residents load, and the three-phase power flow calculation model is proposed. The power flow calculation model includes the power balance equations of three-phase (A,B,C), the current balance equations of phase 0, and the torque balancing equations of induction motors in air conditioners. And then an alternating iterative algorithm of induction motor torque balance equations with each node balance equations is proposed to solve the three-phase power flow model. This method is applied to an actual low voltage distribution network of residents load, and by the calculation of three different operating states of air conditioners, the result demonstrates the effectiveness of the proposed model and the algorithm.
Cooling load and coefficient of performance optimizations for real air-refrigerators
International Nuclear Information System (INIS)
Tu Youming; Chen Lingen; Sun Fengrui; Wu Chih
2006-01-01
Based on a simple irreversible variable-temperature heat reservoir air (Brayton) refrigeration cycle model, a performance analysis and optimization of a real air refrigerator is carried out using finite-time thermodynamics. To maximize the cooling load and the coefficient of performance (COP) of the cycle, the allocation of a fixed total heat-exchanger inventory and thermal-capacity rate matching between the working fluid and heat reservoirs are optimized, respectively. The influences of pressure ratio, the total heat-exchanger inventory, the efficiencies of the compressor and expander, the thermal capacity rate of the working fluid and the ratio of the thermal-capacity rates of the heat reservoirs on the performance of the cycle are shown by numerical examples. The results obtained provide guidances for the design of practical air-refrigeration plants
Measurements and simulations for peak electrical load reduction in cooling dominated climate
International Nuclear Information System (INIS)
Sadineni, Suresh B.; Boehm, Robert F.
2012-01-01
Peak electric demand due to cooling load in the Desert Southwest region of the US has been an issue for the electrical energy suppliers. To address this issue, a consortium has been formed between the University of Nevada Las Vegas, Pulte Homes (home builder) and NV Energy (local utility) in order to reduce the peak load by more than 65%. The implemented strategies that were used to accomplish that goal consist of energy efficiency in homes, onsite electricity generation through roof integrated PV, direct load control, and battery storage at the substation level. The simulation models developed using building energy analysis software were validated against measured data. The electrical energy demand for the upgraded home during peak period (1:00–7:00 PM) decreased by approximately 37% and 9% compared to a code standard home of the same size, due to energy efficiency and PV generation, respectively. The total decrease in electrical demand due to energy efficiency and PV generation during the peak period is 46%. Additionally, a 2.2 °C increase in thermostat temperature from 23.9 °C to 26.1 °C between 4:00 PM and 7:00 PM has further decreased the average demand during the peak period by 69% of demand from a standard home. -- Highlights: ► A study to demonstrate peak load reductions of 65% at the substation. ► A new residential energy efficient community named Villa Trieste is being developed. ► The peak demand from the homes has decreased by 37% through energy efficiency. ► A 1.8 kWp system along with energy efficiency measures decreased peak by 46%.
MIF-SCD computer code for thermal hydraulic calculation of supercritical water cooled reactor core
International Nuclear Information System (INIS)
Galina P Bogoslovskaia; Alexander A Karpenko; Pavel L Kirillov; Alexander P Sorokin
2005-01-01
Full text of publication follows: Supercritical pressure power plants constitute the basis of heat power engineering in many countries to day. Starting from a long-standing experience of their operation, it is proposed to develop a new type of fast breeder reactor cooled by supercritical water, which enables the economical indices of NPP to be substantially improved. In the Thermophysical Department of SSC RF-IPPE, an attempt is made to provide thermal-hydraulic validation of the reactor under discussion. The paper presents the results of analysis of the thermal-hydraulic characteristics of fuel subassemblies cooled by supercritical water based on subchannel analysis. Modification of subchannel code MIF - MIF-SCD Code - developed in the SSC RF IPPE is designed as block code and permits one to calculate the coolant temperature and velocity distributions in fuel subassembly channels, the temperature of fuel pin claddings and fuel subassembly wrapper under conditions of irregular geometry and non-uniform axial and radial power generation. The thermal hydraulics under supercritical pressure of water exhibits such peculiarities as abrupt variation of the thermal physical properties in the range of pseudo-critical temperature, the absence of such phenomenon as the critical heat flux which can lead to fuel element burnout in WWERs. As compared with subchannel code for light water, in order to take account of the variation of the coolant properties versus temperature in more detail, a block for evaluating the thermal physical properties of supercritical water versus the local coolant temperature in the fuel subassembly channels was added. The peculiarities of the geometry and power generation in the fuel subassembly of the supercritical reactor are considered as well in special blocks. The results of calculations have shown that considerable preheating of supercritical coolant (several hundreds degrees) can occur in the fuel subassembly. The test calculations according to
International Nuclear Information System (INIS)
Guo, Yin; Nazarian, Ehsan; Ko, Jeonghan; Rajurkar, Kamlakar
2014-01-01
Highlights: • Developed hourly-indexed ARX models for robust cooling-load forecasting. • Proposed a two-stage weighted least-squares regression approach. • Considered the effect of outliers as well as trend of cooling load and weather patterns. • Included higher order terms and day type patterns in the forecasting models. • Demonstrated better accuracy compared with some ARX and ANN models. - Abstract: This paper presents a robust hourly cooling-load forecasting method based on time-indexed autoregressive with exogenous inputs (ARX) models, in which the coefficients are estimated through a two-stage weighted least squares regression. The prediction method includes a combination of two separate time-indexed ARX models to improve prediction accuracy of the cooling load over different forecasting periods. The two-stage weighted least-squares regression approach in this study is robust to outliers and suitable for fast and adaptive coefficient estimation. The proposed method is tested on a large-scale central cooling system in an academic institution. The numerical case studies show the proposed prediction method performs better than some ANN and ARX forecasting models for the given test data set
The study on the evaporation cooling efficiency and effectiveness of cooling tower of film type
International Nuclear Information System (INIS)
Li Yingjian; You Xinkui; Qiu Qi; Li Jiezhi
2011-01-01
Based on heat and mass transport mechanism of film type cooling, which was combined with an on-site test on counter flow film type cooling tower, a mathematical model on the evaporation and cooling efficiency and effectiveness has been developed. Under typical climatic conditions, air conditioning load and the operating condition, the mass and heat balances have been calculated for the air and the cooling water including the volume of evaporative cooling water. Changing rule has been measured and calculated between coefficient of performance (COP) and chiller load. The influences of air and cooling water parameters on the evaporative cooling efficiency were analyzed in cooling tower restrained by latent heat evaporative cooling, and detailed derivation and computation revealed that both the evaporative cooling efficiency and effectiveness of cooling tower are the same characteristics parameters of the thermal performance of a cooling tower under identical assumptions.
Sodium pool fire analysis of sodium-cooled fast reactor by calculation
International Nuclear Information System (INIS)
Yu Hong; Xu Mi; Jin Degui
2002-01-01
Theoretical models were established according to the characteristic of sodium pool fire, and the SPOOL code was created independently. Some transient processes in sodium pool fire were modeled, including chemical reaction of sodium and oxygen; sodium combustion heat transfer modes in several kids of media; production, deposition and discharge of sodium aerosol; mass and energy exchange between different media in different ventilating conditions. The important characteristic parameters were calculated, such as pressure and temperature of gas, temperature of building materials, mass concentration of sodium aerosol, and so on. The SPOOL code, which provided available safety analysis tool for sodium pool fire accidents in sodium-cooled fast reactor, was well demonstrated with experimental data
International Nuclear Information System (INIS)
Garrison, B.J.
1975-08-01
In order to test a collisional pumping model as a mechanism for cooling the 6 cm and 2 cm doublets of interstellar formaldehyde, a quantum mechanical scattering calculation is performed. To obtain the intermolecular interaction between H 2 CO( 1 A 1 ) and He( 1 S) two calculations are performed, a Hartree-Fock (HF) potential surface and a configuration interaction (CI) surface. A basis set of better than ''triple zeta plus polarization'' quality is used to compute the HF portion of the potential energy surface. This portion is highly anisotropic and has a slight attraction arising from induction effects at intermolecular separations around 9 a.u. The HF surface is modified through a series of CI calculations. Correlation is found to have little effect in the strongly anisotropic repulsive region of the interaction potential but dominates the well and long-range regions. The maximum well depth is attained for in-plane approaches of He and lies in the range 35-40 0 K for arbitrary theta at center of mass separation of 7.5 a.u. The entire surface is fit to a spherical harmonic expansion to facilitate scattering applications. (auth)
Calculation and mapping of critical loads in Europe: Status report 1993
International Nuclear Information System (INIS)
Downing, R.J.; Hettelingh, J.P.; De Smet, P.A.M.
1993-01-01
The work of the RIVM Coordination Center for Effects (CCE) and National Focal Centers (NFCs) for Mapping over the past two years is summarized. The primary task of the critical loads mapping program during this period was to compute and map critical loads of sulphur in Europe. Efforts were undertaken to enhance the scientific foundations and policy relevance of the critical load program, and to foster consensus among producers and users of this information by means of three workshops. The applied calculation methods are described, as well as the resulting critical loads maps, based upon the outcomes of the workshops. Chapter 2 contains the most recent maps (May 1993) of the critical load of acidity as well as the critical load of sulphur and critical sulphur deposition, which are derived from the critical load of acidity. The chapter also contains maps of the sulphur deposition in Europe in 1980 and 1990, and the resulting exceedances. In chapter 3 the methods and equations used to derive the maps of critical loads and exceedances of acidity and sulphur are described with emphasis on the advances in the calculation methods used since the first European critical loads maps were produced in 1991. In chapter 4 the methods to be used to compute and map critical loads in the future are presented. In chapter 5 an overview of the data inputs is given, and the methods of data handling performed by the CCE to produce the current European maps of critical loads. In chapter 6 the results of an uncertainty analysis is described, which was performed on the critical loads computation methodology to assess the reliability of the computation results and the importance of the various input variables. Chapter 7 provides some conclusions and recommendations resulting from the critical load mapping activities. In Appendix 1 the reports of the can be found, with additional maps of critical loads and background variables in Appendix 2. 15 figs., 11 tabs., 156 refs
International Nuclear Information System (INIS)
Liu Yuanzhong
1993-01-01
The calculations of the release of radionuclides to environment are the basis of environmental impact assessment during the normal operation of a module high temperature gas-cooled reactor of the Institute of Nuclear Energy Technology, Tsinghua University, China. According to the features of the reactor it is pointed out that only five sources of the airborne radioactive materials released to environment are important. They are: (1) the activation of the air in the reactor cavity; (2) the escape from the primary coolant systems; (3) the release of radioactively contaminated helium from storage tanks; (4) the release of radioactively contaminated helium from the gas evacuation system of fuel load and unload system; (5) the leakage of the vapour from water-steam loop. In accordance with five release sources the calculating methods of radionuclides released to environment are worked out respectively and the respective calculating formulas are derived for the normal operation of the reactor
Elwan, Ahmed; Singh, Ranvir; Patterson, Maree; Roygard, Jon; Horne, Dave; Clothier, Brent; Jones, Geoffrey
2018-01-11
Better management of water quality in streams, rivers and lakes requires precise and accurate estimates of different contaminant loads. We assessed four sampling frequencies (2 days, weekly, fortnightly and monthly) and five load calculation methods (global mean (GM), rating curve (RC), ratio estimator (RE), flow-stratified (FS) and flow-weighted (FW)) to quantify loads of nitrate-nitrogen (NO 3 - -N), soluble inorganic nitrogen (SIN), total nitrogen (TN), dissolved reactive phosphorus (DRP), total phosphorus (TP) and total suspended solids (TSS), in the Manawatu River, New Zealand. The estimated annual river loads were compared to the reference 'true' loads, calculated using daily measurements of flow and water quality from May 2010 to April 2011, to quantify bias (i.e. accuracy) and root mean square error 'RMSE' (i.e. accuracy and precision). The GM method resulted into relatively higher RMSE values and a consistent negative bias (i.e. underestimation) in estimates of annual river loads across all sampling frequencies. The RC method resulted in the lowest RMSE for TN, TP and TSS at monthly sampling frequency. Yet, RC highly overestimated the loads for parameters that showed dilution effect such as NO 3 - -N and SIN. The FW and RE methods gave similar results, and there was no essential improvement in using RE over FW. In general, FW and RE performed better than FS in terms of bias, but FS performed slightly better than FW and RE in terms of RMSE for most of the water quality parameters (DRP, TP, TN and TSS) using a monthly sampling frequency. We found no significant decrease in RMSE values for estimates of NO 3 - N, SIN, TN and DRP loads when the sampling frequency was increased from monthly to fortnightly. The bias and RMSE values in estimates of TP and TSS loads (estimated by FW, RE and FS), however, showed a significant decrease in the case of weekly or 2-day sampling. This suggests potential for a higher sampling frequency during flow peaks for more precise
International Nuclear Information System (INIS)
Schoenfelder, C.; Kellner, A.
1985-01-01
An approximated representative part of a PWR-feed-water-line was modelled and used to calculate the displacements of the piping system and the loads on it, caused by pressure pulse due to pump failure and subsequent check valve closure. The computation was performed with the code SAPHYR which contains the fluid code ROLAST and the structure code SAPIENS, calculating simultaneously and interactively. The results were compared with an uncoupled calculation without fluid/structure interaction. It was shown that neglecting the fluid/structure interaction can lead to considerable overestimations - in some cases up to a factor of 3 - of the loads on the structures. (orig.)
Stormwater Management: Calculation of Traffic Area Runoff Loads and Traffic Related Emissions
Directory of Open Access Journals (Sweden)
Maximilian Huber
2016-07-01
Full Text Available Metals such as antimony, cadmium, chromium, copper, lead, nickel, and zinc can be highly relevant pollutants in stormwater runoff from traffic areas because of their occurrence, toxicity, and non-degradability. Long-term measurements of their concentrations, the corresponding water volumes, the catchment areas, and the traffic volumes can be used to calculate specific emission loads and annual runoff loads that are necessary for mass balances. In the literature, the annual runoff loads are often specified by a distinct catchment area (e.g., g/ha. These loads were summarized and discussed in this paper for all seven metals and three types of traffic areas (highways, parking lots, and roads; 45 sites. For example, the calculated median annual runoff loads of all sites are 355 g/ha for copper, 110 g/ha for lead (only data of the 21st century, and 1960 g/ha for zinc. In addition, historical trends, annual variations, and site-specific factors were evaluated for the runoff loads. For Germany, mass balances of traffic related emissions and annual heavy metal runoff loads from highways and total traffic areas were calculated. The influences on the mass fluxes of the heavy metal emissions and the runoff pollution were discussed. However, a statistical analysis of the annual traffic related metal fluxes, in particular for different traffic area categories and land uses, is currently not possible because of a lack of monitoring data.
A study on nuclear heat load tolerable for NET/TF coils cooled by internal flow of helium II
International Nuclear Information System (INIS)
Hofmann, A.
1988-02-01
NbTi cables cooled by internal flow of superfluid helium are considered an option for the design of NET/TF coils with about 11 T peak fields. Starting from an available winding cross section of 0.61x0.61 m 2 for a 8 MA turns coil made of a 16 kA conductor it is shown that sufficient hydraulic cross section can be provided within such cables to remove the expected thermal load resulting from nuclear heating with exponential decay from inboard to outboard side of the winding. The concept is a pancake type coil with 1.8 K helium fed-in the high field region of each pancake. The temperature distribution within such coils is calculated, and the local safety margin is determined from temperature and field. The calculation takes account of nuclear and a.c. heating, and of thermal conductance between the individual layers and the coil casing. It is shown that operation with 1.8 K inlet and about 3 K outlet temperature is possible. The electrical insulation with about 0.5 mm thickness proves to provide sufficient thermal insulation. No additional thermal shield is required between the coil casing and the winding package. Two different types of conductors are being considered: a) POLO type cable with quadratic cross section and a central circular coolant duct, and b) an LCT type cable with two conductors wound in hand. Both concepts with about 500 m length of the cooland channels are shown to meet the requirements resulting from a peak nuclear heat load of 0.3 mW/cm 3 in the inboard turns. The hydraulic diameters are sufficient to operate each coils with self-sustained fountain effect pumps. Even appreciably higher heat loads with up to 3 mW/cm 3 of nuclear heating can be tolerated for the POLO type cable when the hydraulic diameter is enlarged to its maximum of 17 mm. (orig.) [de
VALIDATION OF NUMERICAL METHODS TO CALCULATE BYPASS FLOW IN A PRISMATIC GAS-COOLED REACTOR CORE
Directory of Open Access Journals (Sweden)
NAM-IL TAK
2013-11-01
Full Text Available For thermo-fluid and safety analyses of a High Temperature Gas-cooled Reactor (HTGR, intensive efforts are in progress in the developments of the GAMMA+ code of Korea Atomic Energy Research Institute (KAERI and the AGREE code of the University of Michigan (U of M. One of the important requirements for GAMMA+ and AGREE is an accurate modeling capability of a bypass flow in a prismatic core. Recently, a series of air experiments were performed at Seoul National University (SNU in order to understand bypass flow behavior and generate an experimental database for the validation of computer codes. The main objective of the present work is to validate the GAMMA+ and AGREE codes using the experimental data published by SNU. The numerical results of the two codes were compared with the measured data. A good agreement was found between the calculations and the measurement. It was concluded that GAMMA+ and AGREE can reliably simulate the bypass flow behavior in a prismatic core.
Development of the model for the stress calculation of fuel assembly under accident load
International Nuclear Information System (INIS)
Kim, Il Kon
1993-01-01
The finite element model for the stress calculation in guide thimbles of a fuel assembly (FA) under seismic and loss-of-coolant-accident (LOCA) load is developed. For the stress calculation of FA under accident load, at first the program MAIN is developed to select the worst bending mode shaped FA from core model. And then the model for the stress calculation of FA is developed by means of the finite element code. The calculated results of program MAIN are used as the kinematic constraints of the finite element model of a FA. Compared the calculated results of the stiffness of the finite element model of FA with the test results they have good agreements. (Author)
Comparison of three methods of calculating strain in the mouse ulna in exogenous loading studies.
Norman, Stephanie C; Wagner, David W; Beaupre, Gary S; Castillo, Alesha B
2015-01-02
Axial compression of mouse limbs is commonly used to induce bone formation in a controlled, non-invasive manner. Determination of peak strains caused by loading is central to interpreting results. Load-strain calibration is typically performed using uniaxial strain gauges attached to the diaphyseal, periosteal surface of a small number of sacrificed animals. Strain is measured as the limb is loaded to a range of physiological loads known to be anabolic to bone. The load-strain relationship determined by this subgroup is then extrapolated to a larger group of experimental mice. This method of strain calculation requires the challenging process of strain gauging very small bones which is subject to variability in placement of the strain gauge. We previously developed a method to estimate animal-specific periosteal strain during axial ulnar loading using an image-based computational approach that does not require strain gauges. The purpose of this study was to compare the relationship between load-induced bone formation rates and periosteal strain at ulnar midshaft using three different methods to estimate strain: (A) Nominal strain values based solely on load-strain calibration; (B) Strains calculated from load-strain calibration, but scaled for differences in mid-shaft cross-sectional geometry among animals; and (C) An alternative image-based computational method for calculating strains based on beam theory and animal-specific bone geometry. Our results show that the alternative method (C) provides comparable correlation between strain and bone formation rates in the mouse ulna relative to the strain gauge-dependent methods (A and B), while avoiding the need to use strain gauges. Published by Elsevier Ltd.
Determining the optimal load for jump squats: a review of methods and calculations.
Dugan, Eric L; Doyle, Tim L A; Humphries, Brendan; Hasson, Christopher J; Newton, Robert U
2004-08-01
There has been an increasing volume of research focused on the load that elicits maximum power output during jump squats. Because of a lack of standardization for data collection and analysis protocols, results of much of this research are contradictory. The purpose of this paper is to examine why differing methods of data collection and analysis can lead to conflicting results for maximum power and associated optimal load. Six topics relevant to measurement and reporting of maximum power and optimal load are addressed: (a) data collection equipment, (b) inclusion or exclusion of body weight force in calculations of power, (c) free weight versus Smith machine jump squats, (d) reporting of average versus peak power, (e) reporting of load intensity, and (f) instructions given to athletes/ participants. Based on this information, a standardized protocol for data collection and reporting of jump squat power and optimal load is presented.
Risk, probability and uncertainty in the calculations of gas cooled reactor of PBMR type. Part 2
International Nuclear Information System (INIS)
Serbanescu, Dan
2004-01-01
The paper presents the main conclusions of the insights to a cooled gas reactor from the perspective of the following notions: probability, uncertainty, entropy and risk. Some results of the on-going comparison between the insights obtained from three models and approaches are presented. The approaches consider the Pebble Bed Module Reactor (PBMR) NPP as a thermodynamic installation and as hierarchical system with or without considering the information exchange between its various levels. The existing model was a basis for a PRA going on in phases for PBMR. In the first part of this paper results from phase II of this PRA were presented. Further activities going on in the preparation for phase II PRA and for the development of a specific application of using PRA during the design phases for PBMR are undergoing with some preliminary results and conclusions. However, for the purposes of this paper and the comparative review of various models in the part two one presents the risk model (model B) based on the assumption and ideas laid down at the basis of the future inter-comparison of this model with other plant models. The assumptions concern: the uncertainties for the quantification of frequencies; list of initiated events; interfaces with the deterministic calculation; integrated evaluation of all the plant states; risk of the release of radionuclide; the balance between the number and function of the active systems and the passive systems; systems interdependencies in PBMR PRA; use of PRA for the evaluation of the impact of various design changes on plant risk. The model B allows basically evaluating the level of risk of the plant by calculating it as a result of acceptance challenge to the plant. By using this model the departure from a reference state is given by the variation in the risk metrics adopted for the study. The paper present also the synergetic model (model C). The evaluation of risk in the model C is considering also the information process. The
STRUCTURAL CALCULATION OF AN EMPLACEMENT PALLET STATICALLY LOADED BY A WASTE PACKAGE
International Nuclear Information System (INIS)
S. Mastilovic
2000-01-01
The purpose of this calculation is to determine the structural response of the emplacement pallet (EP) subjected to static load from the mounted waste package (WP). The scope of this document is limited to reporting the calculation results in terms of stress intensity magnitudes. This calculation is associated with the waste emplacement systems design; calculations are performed by the Waste Package Design group. AP-3.12Q, Revision 0, ICN 0, Calculations, is used to perform the calculation and develop the document. The finite element solutions are performed by using the commercially available ANSYS Version (V) 5.4 finite element code. The results of these calculations are provided in terms of maximum stress intensity magnitudes
International Nuclear Information System (INIS)
Arakcheev, A.S.; Skovorodin, D.I.; Burdakov, A.V.; Shoshin, A.A.; Polosatkin, S.V.; Vasilyev, A.A.; Postupaev, V.V.; Vyacheslavov, L.N.; Kasatov, A.A.; Huber, A.; Mertens, Ph; Wirtz, M.; Linsmeier, Ch; Kreter, A.; Löwenhoff, Th; Begrambekov, L.; Grunin, A.; Sadovskiy, Ya
2015-01-01
A mathematical model of surface cracking under pulsed heat load was developed. The model correctly describes a smooth brittle–ductile transition. The elastic deformation is described in a thin-heated-layer approximation. The plastic deformation is described with the Hollomon equation. The time dependence of the deformation and stresses is described for one heating–cooling cycle for a material without initial plastic deformation. The model can be applied to tungsten manufactured according to ITER specifications. The model shows that the stability of stress-relieved tungsten deteriorates when the base temperature increases. This proved to be a result of the close ultimate tensile and yield strengths. For a heat load of arbitrary magnitude a stability criterion was obtained in the form of condition on the relation of the ultimate tensile and yield strengths.
International Nuclear Information System (INIS)
Li, Zeyu; Liu, Jinping
2015-01-01
Highlights: • Effect of heat load ratio of generator on the performance was analyzed. • The performance is sensitive to heat load ratio of generator. • The appropriate heat load ratio of generator for four systems was obtained. • The change of appropriate heat load ratio of generator for four systems was studied. - Abstract: The lower coefficient of performance and higher risk of crystallization in the higher surrounding temperature is the primary disadvantage of air cooled lithium bromide–water double effect absorption chiller. Since the coefficient of performance and risk of crystallization strongly depend on the heat load ratio of generator, the appropriate heat load ratio of generator can improve the performance as the surrounding temperature is higher. The paper mainly deals with the appropriate heat load ratio of generator of air cooled lithium bromide–water double effect absorption chiller. Four type systems named series, pre-parallel, rear parallel and reverse parallel flow configuration were considered. The corresponding parametric model was developed to analyze the comprehensive effect of heat load ratio of generator on the coefficient of performance and risk of crystallization. It was found that the coefficient of performance goes up linearly with the decrease of heat load ratio of generator. Simultaneously, the risk of crystallization also rises slowly at first but increases fast finally. Consequently, the appropriate heat load ratio of generator for the series and pre-parallel flow type systems is suggested to be 0.02 greater than the minimum heat load ratio of generator and that for the rear parallel and reverse parallel flow chillers should be 0.01 higher than the minimum heat load ratio of generator. Besides, the changes of minimum heat load ratio of generator for different type systems with the working condition were analyzed and compared. It was found that the minimum heat load ratio of generator goes up with the increase of
International Nuclear Information System (INIS)
Li Qiong; Meng Qinglin; Cai Jiejin; Yoshino, Hiroshi; Mochida, Akashi
2009-01-01
This study presents four modeling techniques for the prediction of hourly cooling load in the building. In addition to the traditional back propagation neural network (BPNN), the radial basis function neural network (RBFNN), general regression neural network (GRNN) and support vector machine (SVM) are considered. All the prediction models have been applied to an office building in Guangzhou, China. Evaluation of the prediction accuracy of the four models is based on the root mean square error (RMSE) and mean relative error (MRE). The simulation results demonstrate that the four discussed models can be effective for building cooling load prediction. The SVM and GRNN methods can achieve better accuracy and generalization than the BPNN and RBFNN methods
Calculation and characteristics analysis of blade pitch loads for large scale wind turbines
Institute of Scientific and Technical Information of China (English)
无
2010-01-01
Based on the electric pitch system of large scale horizontal-axis wind turbines,the blade pitch loads coming mainly from centrifugal force,aerodynamic force and gravity are analyzed,and the calculation models for them are established in this paper.For illustration,a 1.2 MW wind turbine is introduced as a practical sample,and its blade pitch loads from centrifugal force,aerodynamic force and gravity are calculated and analyzed separately and synthetically.The research results showed that in the process of rotor rotating 360o,the fluctuation of blade pitch loads is similar to cosine curve when the rotor rotational speed,in-flow wind speed and pitch angle are constant.Furthermore,the amplitude of blade pitch load presents quite a difference at a different pitch angle.The ways of calculation for blade pitch loads are of the universality,and are helpful for further research of the individual pitch control system.
International Nuclear Information System (INIS)
Eid, M.; Nimal, J.C.; Gerat, L.M.
1994-01-01
This is a revision of the past seven years experience in activation calculations for dismantling. It aims at evaluating the experience and at making better understanding to help in decision making during the following phases. Five gas cooled reactors are shutdown and are waiting for the EDF (Electricite De France) dismantling decision. The sixth (BUGEY1) will be shutdown by 1994 and will be waiting a dismantling decision as well. (authors). 3 figs., 3 tabs
International Nuclear Information System (INIS)
Illing, Bjoern
2014-01-01
Dominated by the energy policy the decentralized German energy market is changing. One mature target of the government is to increase the contribution of renewable generation to the gross electricity consumption. In order to achieve this target disadvantages like an increased need for capacity management occurs. Load reduction and variable grid fees offer the grid operator solutions to realize capacity management by influencing the load profile. The evolution of the current grid fees towards more causality is required to adapt these approaches. Two calculation approaches are developed in this assignment. On the one hand multivariable grid fees keeping the current components demand and energy charge. Additional to the grid costs grid load dependent parameters like the amount of decentralized feed-ins, time and local circumstances as well as grid capacities are considered. On the other hand the grid fee flat-rate which represents a demand based model on a monthly level. Both approaches are designed to meet the criteria for future grid fees. By means of a case study the effects of the grid fees on the load profile at the low voltage grid is simulated. Thereby the consumption is represented by different behaviour models and the results are scaled at the benchmark grid area. The resulting load curve is analyzed concerning the effects of peak load reduction as well as the integration of renewable energy sources. Additionally the combined effect of grid fees and electricity tariffs is evaluated. Finally the work discusses the launching of grid fees in the tense atmosphere of politics, legislation and grid operation. Results of this work are two calculation approaches designed for grid operators to define the grid fees. Multivariable grid fees are based on the current calculation scheme. Hereby demand and energy charges are weighted by time, locational and load related dependencies. The grid fee flat-rate defines a limitation in demand extraction. Different demand levels
Development of load calculation techniques on screw and screw press energy consumption
Татарьянц, Максим Сергеевич; Завинский, Сергей Иванович; Трошин, Алексей Георгиевич
2015-01-01
The process of pressing of wood chips in screw machines is researched. It is defined processes taking place in different parts of the screw, formulas allowing to calculate the loads acting on the screw flights, as well as to determine the power required for compression. The unit costs of energy consumption and raw materials in the degree of heat pressing are determined
DEFF Research Database (Denmark)
Krabbenhøft, Sven; Damkilde, Lars; Krabbenhøft, Kristian
2012-01-01
Lower-bound calculations based on the finite element method are used to determine the bearing capacity of a strip foundation subjected to a vertical, eccentric load on cohesionless soil with varying surcharges. The soil is assumed perfectly plastic following the Mohr-Coulomb failure criterion. Th...
Calculation of neutron shielding for a real loaded C-30 cask by code DORT
International Nuclear Information System (INIS)
Lacina, J.
1999-01-01
Measured neutron dose rates of real loaded C-30 casks for WWER spent fuel assemblies are compared with calculated values in the frame of benchmark calculation task. The part of this benchmark task concerning neutron shielding was calculated. Neutron sources values were taken from data presented by V. Chrapciak during the eighth symposium Atomic Energy Research, Bystrice pod Perstejnem in 1998 and the data about cask from the article of the same author from the Atomic Energy Research working group E meeting at Stolpen in 1998. (Author)
New heating load calculation in practice; Neue Heizlastberechnung in der Praxis
Energy Technology Data Exchange (ETDEWEB)
Kroeber, C [REHAU AG und Co., REHAU-Akademie, Erlangen (Germany)
2004-07-01
First the heating demand/standard heat load of the building is calculated related to DIN 4701 and than by DIN EN 12831. The topic is to considerate not new formulas and calculation steps but looking on the results of the calculation and discussing it. (GL) [German] Am Beispiel eines Mehrfamilienhauses soll dieser Frage auf den Grund gegangen werden. Dazu wird der Norm-Waermebedarf/die Norm-Heizlast des Gebaeudes zuerst nach DIN 4701 und dann nach DIN EN 12831 berechnet. Dabei liegt der Schwerpunkt der Betrachtung nicht auf den neuen Berechnungsansaetzen und Formeln, sondern vielmehr auf der Betrachtung der Berechnungsergebnisse. (orig.)
International Nuclear Information System (INIS)
Zhang, Youpeng; Wallenius, Janne
2014-01-01
Highlights: • The americium transmutation capability of Integral Fast Reactor was investigated. • The impact from americium introduction was parameterized by applying SERPENT Monte Carlo calculations. • Higher americium content in metallic fuel leads to a power penalty, preserving consistent safety margins. - Abstract: Transient analysis of a large sized sodium-cooled reactor loaded with metallic fuel modified by different fractions of americium have been performed. Unprotected loss-of-offsite power, unprotected loss-of-flow and unprotected transient-over-power accidents were simulated with the SAS4A/SASSYS code based on the geometrical model of an IFR with power rating of 2500 MW th , using safety parameters obtained with the SERPENT Monte Carlo code. The Ti-modified austenitic D9 steel, having higher creep rupture strength, was considered as the cladding and structural material apart from the ferritic/martensitic HT9 steel. For the reference case of U–12Pu–1Am–10Zr fuel at EOEC, the margin to fuel melt during a design basis condition UTOP is about 50 K for a maximum linear rating of 30 kW/m. In order to maintain a margin of 50 K to fuel failure, the linear power rating has to be reduced by ∼3% and 6% for 2 wt.% and 3 wt.% Am introduction into the fuel respectively. Hence, an Am concentration of 2–3 wt.% in the fuel would lead to a power penalty of 3–6%, permitting a consumption rate of 3.0–5.1 kg Am/TW h th . This consumption rate is significantly higher than the one previously obtained for oxide fuelled SFRs
Numerical Calculation of the Peaking Factor of a Water-Cooled W/Cu Monoblock for a Divertor
Han, Le; Chang, Haiping; Zhang, Jingyang; Xu, Tiejun
2015-09-01
In order to accurately predict the incident critical heat flux (ICHF, the heat flux at the heated surface when CHF occurs) of a water-cooled W/Cu monoblock for a divertor, the exact knowledge of its peaking factors (fp) under one-sided heating conditions with different design parameters is a key issue. In this paper, the heat conduction in the solid domain of a water-cooled W/Cu monoblock is calculated numerically by assuming the local heat transfer coefficients (HTC) of the cooling wall to be functions of the local wall temperature, so as to obtain fp. The reliability of the calculation method is validated by an experimental example result, with the maximum error of 2.1% only. The effects of geometric and flow parameters on the fp of a water-cooled W/Cu monoblock are investigated. Within the scope of this study, it is shown that the fp increases with increasing dimensionless W/Cu monoblock width and armour thickness (the shortest distance between the heated surface and Cu layer), and the maximum increases are 43.8% and 22.4% respectively. The dimensionless W/Cu monoblock height and Cu thickness have little effect on fp. The increase of Reynolds number and Jakob number causes the increase of fp, and the maximum increases are 6.8% and 9.6% respectively. Based on the calculated results, an empirical correlation on peaking factor is obtained via regression. These results provide a valuable reference for the thermal-hydraulic design of water-cooled divertors. supported by National Magnetic Confinement Fusion Science Program of China (No. 2010GB104005) and Funding of Jiangsu Innovation Program for Graduate Education, China (CXLX12_0170), the Fundamental Research Funds for the Central Universities of China
Numerical Calculation of the Peaking Factor of a Water-Cooled W/Cu Monoblock for a Divertor
International Nuclear Information System (INIS)
Han Le; Chang Haiping; Zhang Jingyang; Xu Tiejun
2015-01-01
In order to accurately predict the incident critical heat flux (ICHF, the heat flux at the heated surface when CHF occurs) of a water-cooled W/Cu monoblock for a divertor, the exact knowledge of its peaking factors (f p ) under one-sided heating conditions with different design parameters is a key issue. In this paper, the heat conduction in the solid domain of a water-cooled W/Cu monoblock is calculated numerically by assuming the local heat transfer coefficients (HTC) of the cooling wall to be functions of the local wall temperature, so as to obtain f p . The reliability of the calculation method is validated by an experimental example result, with the maximum error of 2.1% only. The effects of geometric and flow parameters on the f p of a water-cooled W/Cu monoblock are investigated. Within the scope of this study, it is shown that the f p increases with increasing dimensionless W/Cu monoblock width and armour thickness (the shortest distance between the heated surface and Cu layer), and the maximum increases are 43.8% and 22.4% respectively. The dimensionless W/Cu monoblock height and Cu thickness have little effect on f p . The increase of Reynolds number and Jakob number causes the increase of f p , and the maximum increases are 6.8% and 9.6% respectively. Based on the calculated results, an empirical correlation on peaking factor is obtained via regression. These results provide a valuable reference for the thermal-hydraulic design of water-cooled divertors. (paper)
Energy Technology Data Exchange (ETDEWEB)
Nakaya, Hiroyuki, E-mail: nakaya@nucl.kyushu-u.ac.jp [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 8190395 (Japan); Matsuura, Hideaki [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 8190395 (Japan); Katayama, Kazunari [Department of Advanced Energy Engineering Science, Kyushu University, 6-1 Kasuga-koen, Kasuga 8168580 (Japan); Goto, Minoru; Nakagawa, Shigeaki [Japan Atomic Energy Agency, 4002 Oarai, Ibaraki (Japan)
2015-10-15
Highlights: • Tritium production by a high-temperature gas-cooled reactor was studied. • The loading method considering tritium outflow suppression was estimated. • A reactor with 600 MWt produced 400–600 g of tritium for 180 days. • A possibility that tritium outflow can be sufficiently suppressed was shown. - Abstract: Tritium production using high-temperature gas-cooled reactors and its outflow from the region loading Li compound into the helium coolant are estimated when considering the suppression of tritium outflow. A Li rod containing a cylindrical Li compound placed in an Al{sub 2}O{sub 3} cladding tube is assumed as a method for loading Li compound. A gas turbine high-temperature reactor of 300 MW electrical nominal capacity (GTHTR300) with 600 MW thermal output power is considered and modeled using the continuous-energy Monte Carlo transport code MVP-BURN, where burn-up simulations are carried out. Tritium outflow is estimated from equilibrium solution for the tritium diffusion equation in the cladding tube. A GTHTR300 can produce 400–600 g of tritium over a 180-day operation using the chosen method of loading the Li compound while minimizing tritium outflow from the cladding tube. Optimizing tritium production while suppressing tritium outflow is discussed.
Energy Technology Data Exchange (ETDEWEB)
Graf, Peter; Damiani, Rick R.; Dykes, Katherine; Jonkman, Jason M.
2017-01-09
A new adaptive stratified importance sampling (ASIS) method is proposed as an alternative approach for the calculation of the 50 year extreme load under operational conditions, as in design load case 1.1 of the the International Electrotechnical Commission design standard. ASIS combines elements of the binning and extrapolation technique, currently described by the standard, and of the importance sampling (IS) method to estimate load probability of exceedances (POEs). Whereas a Monte Carlo (MC) approach would lead to the sought level of POE with a daunting number of simulations, IS-based techniques are promising as they target the sampling of the input parameters on the parts of the distributions that are most responsible for the extreme loads, thus reducing the number of runs required. We compared the various methods on select load channels as output from FAST, an aero-hydro-servo-elastic tool for the design and analysis of wind turbines developed by the National Renewable Energy Laboratory (NREL). Our newly devised method, although still in its infancy in terms of tuning of the subparameters, is comparable to the others in terms of load estimation and its variance versus computational cost, and offers great promise going forward due to the incorporation of adaptivity into the already powerful importance sampling concept.
Real-time POD-CFD Wind-Load Calculator for PV Systems
Energy Technology Data Exchange (ETDEWEB)
Huayamave, Victor [Centecorp; Divo, Eduardo [Centecorp; Ceballos, Andres [Centecorp; Barriento, Carolina [Centecorp; Stephen, Barkaszi [FSEC; Hubert, Seigneur [FSEC
2014-03-21
The primary objective of this project is to create an accurate web-based real-time wind-load calculator. This is of paramount importance for (1) the rapid and accurate assessments of the uplift and downforce loads on a PV mounting system, (2) identifying viable solutions from available mounting systems, and therefore helping reduce the cost of mounting hardware and installation. Wind loading calculations for structures are currently performed according to the American Society of Civil Engineers/ Structural Engineering Institute Standard ASCE/SEI 7; the values in this standard were calculated from simplified models that do not necessarily take into account relevant characteristics such as those from full 3D effects, end effects, turbulence generation and dissipation, as well as minor effects derived from shear forces on installation brackets and other accessories. This standard does not include provisions that address the special requirements of rooftop PV systems, and attempts to apply this standard may lead to significant design errors as wind loads are incorrectly estimated. Therefore, an accurate calculator would be of paramount importance for the preliminary assessments of the uplift and downforce loads on a PV mounting system, identifying viable solutions from available mounting systems, and therefore helping reduce the cost of the mounting system and installation. The challenge is that although a full-fledged three-dimensional computational fluid dynamics (CFD) analysis would properly and accurately capture the complete physical effects of air flow over PV systems, it would be impractical for this tool, which is intended to be a real-time web-based calculator. CFD routinely requires enormous computation times to arrive at solutions that can be deemed accurate and grid-independent even in powerful and massively parallel computer platforms. This work is expected not only to accelerate solar deployment nationwide, but also help reach the SunShot Initiative goals
The United States of America as represented by the United States Department of Energy
2009-12-15
An apparatus and method for transferring thermal energy from a heat load is disclosed. In particular, use of a phase change material and specific flow designs enables cooling with temperature regulation well above the fusion temperature of the phase change material for medium and high heat loads from devices operated intermittently (in burst mode). Exemplary heat loads include burst mode lasers and laser diodes, flight avionics, and high power space instruments. Thermal energy is transferred from the heat load to liquid phase change material from a phase change material reservoir. The liquid phase change material is split into two flows. Thermal energy is transferred from the first flow via a phase change material heat sink. The second flow bypasses the phase change material heat sink and joins with liquid phase change material exiting from the phase change material heat sink. The combined liquid phase change material is returned to the liquid phase change material reservoir. The ratio of bypass flow to flow into the phase change material heat sink can be varied to adjust the temperature of the liquid phase change material returned to the liquid phase change material reservoir. Varying the flowrate and temperature of the liquid phase change material presented to the heat load determines the magnitude of thermal energy transferred from the heat load.
Assessment of Calculation Procedures for Piles in Clay Based on Static Loading Tests
DEFF Research Database (Denmark)
Augustesen, Anders; Andersen, Lars
2008-01-01
College in London. The calculation procedures are assessed based on an established database of static loading tests. To make a consistent evaluation of the design methods, corrections related to undrained shear strength and time between pile driving and testing have been employed. The study indicates...... that the interpretation of the field tests is of paramount importance, both with regard to the soil profile and the loading conditions. Based on analyses of 253 static pile loading tests distributed on 111 sites, API-RP2A provides the better description of the data. However, it should be emphasised that some input......Numerous methods are available for the prediction of the axial capacity of piles in clay. In this paper, two well-known models are considered, namely the current API-RP2A (1987 to present) and the recently developed ICP method. The latter is developed by Jardine and his co-workers at Imperial...
Gas-Induced Water-hammer Loads Calculation for Safety Related Systems
Energy Technology Data Exchange (ETDEWEB)
Lee, Seungchan; Yoon, Dukjoo [Korea Hydro and Nuclear Power Co., LTd, Daejeon (Korea, Republic of); Lee, Dooyong [Seoul National Univ., Seoul (Korea, Republic of)
2013-05-15
Of particular interest, gas accumulation can result in system pressure transient in pump discharge piping following a pump start. Consequently, this evolves into a gas-water, a water-hammer event and the accompanying force imbalances on the piping segments can be sufficient to challenge the piping supports and restraint. This paper describes an method performing to the water-hammer loads to determine the maximum loading that would occur in the piping system following the safety injection signal and to evaluate its integrity. For a given gas void volumes in the discharge piping, the result of the calculation shows the maximum loads of 18,894.2psi, which is smaller than the allowable criteria. Also, the maximum peak axial force imbalances acting on the support is 1,720lbf as above.
Gas-Induced Water-hammer Loads Calculation for Safety Related Systems
International Nuclear Information System (INIS)
Lee, Seungchan; Yoon, Dukjoo; Lee, Dooyong
2013-01-01
Of particular interest, gas accumulation can result in system pressure transient in pump discharge piping following a pump start. Consequently, this evolves into a gas-water, a water-hammer event and the accompanying force imbalances on the piping segments can be sufficient to challenge the piping supports and restraint. This paper describes an method performing to the water-hammer loads to determine the maximum loading that would occur in the piping system following the safety injection signal and to evaluate its integrity. For a given gas void volumes in the discharge piping, the result of the calculation shows the maximum loads of 18,894.2psi, which is smaller than the allowable criteria. Also, the maximum peak axial force imbalances acting on the support is 1,720lbf as above
Calculation of steam content in a draught section of a tank-type boiling water cooled reactor
International Nuclear Information System (INIS)
Panajotov, D.P.; Gorburov, V.I.
1989-01-01
Structural and hydrodynamic features of a two-phase flow in a draught section of a tank-type boiling water cooled reactor are considered. A calculated model of the steady flow and methods for determining steam content and phase rate profiles under the maximum steam content at the section axis and at some distance from it are proposed. Steam content distribution by height quantitatively agrees with experimental data for the VK-50 reactor. Calculation technique allows one to obtain steam content and phase rate profiles at the section outlet
Tests and calculations of reinforced concrete beams subject to dynamic reversed loads
International Nuclear Information System (INIS)
Livolant, M.; Hoffmann, A.; Gauvain, J.
1978-01-01
This study presents the tests of a reinforced concrete beam conducted by the Department of Mechanical and Thermal Studies at the Centre d'Etudes Nucleaires, Saclay, France. The actual behavior of nuclear power plant buildings submitted to seismic loads is generally non linear even for moderate seismic levels. The non linearity is specially important for reinforced concrete beams type buildings. To estimate the safety factors when the building is designed by standard methods, accurate non linear calculations are necessary. For such calculations one of the most difficult point is to define a correct model for the behavior of a reinforced beam subject to reversed loads. For that purpose, static and dynamic experimental tests on a shaking table have been carried out and a model reasonably accurate has been established and checked on the tests results
International Nuclear Information System (INIS)
Huang, Jie; Ding, Ming
2017-01-01
Highlights: • Four-level of spatial separation is described in a block-type thorium-loaded HTR. • A traditional two-step calculation scheme is used to get the neutronic performance. • Fuel cycle cost is calculated by the levelised lifetime cost method. • Fuel cycle cost decreases with the increase of separation level or thorium content. • Effective enrichment basically determines the fuel cycle cost. - Abstract: With nuclear energy’s rapid development in recent years, supply of nuclear fuel has become increasingly important. Thorium has re-gained attention because of its abundant reserves and excellent physical properties. Compared to the homogeneous Th/U MOX fuel, separation of thorium and uranium in space is a better use of thorium. Therefore, this paper describes four-level spatial separation – no separation, tristructural-isotropic (TRISO) level, channel level and block level – in a block-type thorium-loaded helium-cooled high-temperature reactor (HTR). A traditional two-step calculation scheme, lattice calculation followed by core calculation, is used to get the neutronic performance of the equilibrium cycle, including uranium enrichment, mass of fuel, effective multiplication factor, and average conversion ratio. Based on these data, the fuel cycle cost of different-scale spatial separation can be calculated by the levelised lifetime cost method as a function of thorium content. As the separation level increases from no separation to channel level, the effective enrichment decreases 15% due to the increase of resonance escape probability. So there is a 13% drop for the fuel cycle cost. For TRISO-level separation, as the thorium content increases from 9 to 57%, the effective enrichment decreases 14% because of the superior breeding capacity of U-233. As a result, the fuel cycle cost also has about a 12% decrease. From the perspective of fuel cycle economics, channel-level separation with 60% thorium content is suggested.
Correction of the calculation of beam loading based in the RF power diffusion equation
International Nuclear Information System (INIS)
Silva, R. da.
1980-01-01
It is described an empirical correction based upon experimental datas of others authors in ORELA, GELINA and SLAC accelerators, to the calculation of the energy loss due to the beam loading effect as stated by the RF power diffusion equation theory an accelerating structure. It is obtained a dependence of this correction with the electron pulse full width half maximum, but independent of the electron energy. (author) [pt
Fluid and structural dynamics calculations to determine core barrel loads during blowdown (EV 3,000)
International Nuclear Information System (INIS)
Krieg, R.; Schlechtendahl, E.G.
1977-01-01
To begin with, the main physical phenomena in connection with blowdown loads on the care barrel and the computer models used are briefly described. These models have also been used in the design of the HTR test care barrel. The fluid dynamics part of the calculations was carried out using the WHAMMOD and DAPSY codes; for the structural dynamics part, the STRUDL/Dynal code was employed. (orig./RW) [de
Directory of Open Access Journals (Sweden)
Plotnikov Aleksandr Aleksandrovich
Full Text Available Glass unit consists of glasses hermetically-united together. The cavity of an insulating glass unit contains a fixed volume of air (gas. In the process of production regular air with atmospheric pressure and temperature is sealed inside a glass unit. During operation the atmospheric pressure is constantly changing, but the pressure inside remains constant (at a constant temperature. A change of temperature or of the external air pressure results in a pressure difference and therefore in a load on the glass panes. The action may exceed the usual load considerably. This pressure effects the glasses of the unit, deforms them, lowers the thermotechnical properties of glass units and can lead to their destruction. The action of the inside pressure can be seen all around as convex and concaved glasses, which destroys the architectural look of buildings. It is obvious that it is incorrect to calculate thin glass plates on such a load only by classical methods of strength of materials theory. In this case we need a special calculation method. The effects of a change in temperature, altitude or meteorological pressure are easily covered by the definition of an isochore pressure. This is necessary, to determine the change of pressure due to the temperature induced gas expansion in the cavity of the insulating glass according to the ideal gas law. After the integration of the analytical plate solution and the ideal gas law, the final pressure states can easily be calculated by coupling the change of volume and the change of pressure.
International Nuclear Information System (INIS)
Zylbersztejn, F.; Tran, H.N.; Pazsit, I.; Filliatre, P.; Jammes, C.
2014-01-01
The subject of this paper is the calculation of the neutron noise induced by small-amplitude stationary radial variations of the core size (core expansion/compaction, also called core flowering) of a large sodium-cooled fast reactor. The calculations were performed on a realistic model of the European Sodium Fast Reactor (ESFR) core with a thermal output of 3600 MW(thermal), using a multigroup neutron noise simulator. The multigroup cross sections and their fluctuations that represent the core geometry changes for the neutron noise calculations were generated by the code ERANOS. The space and energy dependences of the noise source represented by the core expansion/compaction and the induced neutron noise are calculated and discussed. (authors)
Radiation cooling and gain calculation for C VI 182 A line in C/Se plasma
International Nuclear Information System (INIS)
Nam, C.H.; Valeo, E.; Suckewer, S.; Feldman, U.
1986-04-01
A model is developed which is capable of describing the evolution of gain resulting from both rapid radiative and expansion cooling of a recombining, freely expanding plasma. It is demonstrated for the particular case of a carbon/selenium plasma that the cooling rate which leads to optimal gain can be achieved by adjusting the admixture of an efficiently radiating material (selenium) in the gain medium (carbon). Comparison is made to a recent observation of gain in a recent NRL/Rochester experiment with carbon/selenium plasma for the n = 3 → 2 transition in C VI occurring at 182 A. The predicted maximum gain is approx.10 cm -1 , as compared to observation of 2 to 3 cm -1
Shield design and streaming calculations for the sodium cooled PEC reactor
International Nuclear Information System (INIS)
Prosperi, M.; Tavoni, R.; Travaglini, N.
1977-01-01
This paper summarises the shielding calculations carried out for the PEC reactor. A brief description of calculation methods and of the work carried out to set them up is given; the most representative calculations with the relative isoflux curves are also referred. A general outline is then given for the main shielding problems of the PEC reactor
International Nuclear Information System (INIS)
Trobitz, M.; Mattheis, A.; Kerkhof, K.; Hippelein, K.; Hofstoetter, P.
1998-01-01
Within the framework of periodic safety inspection of the Gundremmingen power station (RWE-Bayernwerk - KRB II), the load collectives used for the design of safety-relevant systems and components were checked for their consistency with latest updates of the design basis. It was found that there was no analytical information or study available describing a particular process and its effects, namely switch-off of the high-pressure feedwater pump of the emergency core cooling system. The paper reports the work performed for closing the gap, including preparatory analyses, accompanying measures such as vibration measurements during plant shut-down, as well as the preparation and performance of the in-situ test. The experimental results and the comparative evaluation of calculated and experimental data are presented. (orig./CB) [de
Modeling of the corium cooling and loading factor analysis for containment during severe accidents
International Nuclear Information System (INIS)
Konoval, A.V.; Kalvand, Ali.; Kazachkov, I.V.
2013-01-01
The paper is devoted to the development and study of the mathematical model for corium melt interaction with low-temperature melting blocks in the passive protection systems (PPS) against severe accidents at the NPP, and learning the peculiarities of construction and operation of the PPS. The configurations of cooling blocks' distributions considered and the results of their work in the corium cooling pool are compared to the data of other PPS's conceptions. The conclusion is made that the models developed and the results obtained may be useful for constructing the PPS against severe accidents
Modeling of the corium cooling and loading factor analysis for containment during severe accidents
Directory of Open Access Journals (Sweden)
O. V. Konoval
2013-09-01
Full Text Available The paper is devoted to the development and study of the mathematical model for corium melt interaction with low-temperature melting blocks in the passive protection systems (PPS against severe accidents at the NPP, and learning the peculiarities of construction and operation of the PPS. The configurations of cooling blocks’ distributions considered and the results of their work in the corium cooling pool are compared to the data of oth-er PPS’s conceptions. The conclusion is made that the models developed and the results obtained may be useful for constructing the PPS against severe accidents.
Calculating the sensitivity of wind turbine loads to wind inputs using response surfaces
International Nuclear Information System (INIS)
Rinker, Jennifer M.
2016-01-01
This paper presents a methodology to calculate wind turbine load sensitivities to turbulence parameters through the use of response surfaces. A response surface is a highdimensional polynomial surface that can be calibrated to any set of input/output data and then used to generate synthetic data at a low computational cost. Sobol sensitivity indices (SIs) can then be calculated with relative ease using the calibrated response surface. The proposed methodology is demonstrated by calculating the total sensitivity of the maximum blade root bending moment of the WindPACT 5 MW reference model to four turbulence input parameters: a reference mean wind speed, a reference turbulence intensity, the Kaimal length scale, and a novel parameter reflecting the nonstationarity present in the inflow turbulence. The input/output data used to calibrate the response surface were generated for a previous project. The fit of the calibrated response surface is evaluated in terms of error between the model and the training data and in terms of the convergence. The Sobol SIs are calculated using the calibrated response surface, and the convergence is examined. The Sobol SIs reveal that, of the four turbulence parameters examined in this paper, the variance caused by the Kaimal length scale and nonstationarity parameter are negligible. Thus, the findings in this paper represent the first systematic evidence that stochastic wind turbine load response statistics can be modeled purely by mean wind wind speed and turbulence intensity. (paper)
International Nuclear Information System (INIS)
Sienicki, J.J.; Horak, W.C.
1989-01-01
Analyses have been carried out of the pressurization of the accident release mitigation structures of Soviet-designed VVER (Water-Cooled, Water-Moderated Energy Reactor) pressurized water reactors following large-break loss-of-coolant accidents. Specific VVER systems for which calculations were performed are the VVER-440 model V230, VVER-440 model V213, and VVER-1000 model V320. Descriptions of the designs of these and other VVER models are contained in the report DOE/NE-0084. The principal objective of the current analyses is to calculate the time dependent pressure loadings inside the accident localization or containment structures immediately following the double-ended guillotine rupture of a primary coolant pipe. In addition, the pressures are compared with the results of calculations of the response of the structures to overpressure. Primary coolant system thermal hydraulic conditions and the fluid conditions at the break location were calculated with the RETRAN-02 Mod2 computer code (Agee, 1984). Pressures and temperatures inside the building accident release mitigation structures were obtained from the PACER (Pressurization Accompanying Coolant Escape from Ruptures) multicompartment containment analysis code developed at Argonne National Laboratory. The analyses were carried out using best estimate models and conditions rather than conservative, bounding-type assumptions. In particular, condensation upon structure and equipment was calculated using correlations based upon analyses of the HDR, Marviken, and Battelle Frankfurt containment loading experiments. The intercompartment flow rates incorporate an effective discharge coefficient and liquid droplet carryover fraction given by expressions of Schwan determined from analyses of the Battelle Frankfurt and Marviken tests. 5 refs., 4 figs
Automatic mesh generation for finite element calculations in the case of thermal loads
International Nuclear Information System (INIS)
Cords, H.; Zimmermann, R.
1975-01-01
The presentation describes a method to generate finite element nodal point networks on the basis of isothermals and flux lines. Such a mesh provides a relatively fine partitioning at regions where pronounced temperature variations exist. In case of entirely thermal loads a net of this kind is advantageous since the refinement is provided at exactly those locations where high stress levels are expected. In the present contribution the method was employed to analyze the structural behavior of a nuclear fuel element under operating conditions. The graphite block fuel elements for high temperature reactors are of prismatic shape with a large number of parallel bores in the axial direction. Some of these bores are open at both ends and cooling is effected by helium flowing through. Blind holes contain the fuel as compacts or cartridges. The basic temperature distribution in a horizontal section of the block was obtained by the boundary point least squares method which yields analytical expressions for both temperature and thermal flux. The corresponding computer code was presented at an earlier SMiRT conference. The method is particularly useful for regular arrays of heat sources and sinks as encountered in heat exchanger problems. The generated mesh matches the requirements of a subsequent structural analysis with finite elements provided there are no other than thermal loads
International Nuclear Information System (INIS)
Nabi, Jameel-Un
2010-01-01
An accurate estimate of the neutrino cooling rates is required in order to study the various stages of stellar evolution of massive stars. Neutrino losses from proto-neutron stars play a crucial role in deciding whether these stars would be crushed into black holes or explode as supernovae. Both pure leptonic and weak-interaction processes contribute to the neutrino energy losses in stellar matter. At low temperatures and densities, the characteristics of the early phase of presupernova evolution, cooling through neutrinos produced via the weak interaction, are important. Proton-neutron quasi-particle random phase approximation (pn-QRPA) theory has recently been used with success for the calculation of stellar weak-interaction rates of fp-shell nuclide. The lepton-to-baryon ratio (Y e ) during early phases of stellar evolution of massive stars changes substantially, mainly due to electron captures on 56 Ni. The stellar matter is transparent to the neutrinos produced during the presupernova evolution of massive stars. These neutrinos escape the site and assist the stellar core in maintaining a lower entropy. Here, an expanded calculation of weak-interaction-mediated neutrino and antineutrino cooling rates due to 56 Ni in stellar matter using the pn-QRPA theory is presented. This detailed scale is appropriate for interpolation purposes and is of greater utility for simulation codes. The calculated rates are compared with earlier calculations. During the relevant temperature and density regions of stellar matter the reported rates show few differences compared with the shell model rates and might contribute in fine-tuning of the lepton-to-baryon ratio during the presupernova phases of stellar evolution of massive stars.
Calculating the sensitivity of wind turbine loads to wind inputs using response surfaces
DEFF Research Database (Denmark)
Rinker, Jennifer M.
2016-01-01
at a low computational cost. Sobol sensitivity indices (SIs) can then be calculated with relative ease using the calibrated response surface. The proposed methodology is demonstrated by calculating the total sensitivity of the maximum blade root bending moment of the WindPACT 5 MW reference model to four......This paper presents a methodology to calculate wind turbine load sensitivities to turbulence parameters through the use of response surfaces. A response surface is a high-dimensional polynomial surface that can be calibrated to any set of input/output data and then used to generate synthetic data...... turbulence input parameters: a reference mean wind speed, a reference turbulence intensity, the Kaimal length scale, and a novel parameter reflecting the nonstationarity present in the inflow turbulence. The input/output data used to calibrate the response surface were generated for a previous project...
Calculation Method for Load Capacity of Urban Rail Transit Station considering Cascading Failure
Directory of Open Access Journals (Sweden)
Jiajun Huang
2018-01-01
Full Text Available The load capacity of urban rail transit station is of great significance to provide reference in station design and operation management. However, it is difficult to carry out quantitative calculation quickly and accurately due to the complex interaction among passenger behaviors, facility layout, and the limit capacity of single facility. In this paper, the association network of facilities is set up based on the analysis of passenger service chain in station. Then the concept of cascading failure is introduced to the dynamic calculation model of load capacity, which is established on the user-equilibrium allocation model. The solution algorithm is optimized with node attack strategy of complex network to effectively reduce the computational complexity. Finally, a case study of Lujiabang Road Station in Shanghai is carried out and compared with the simulation results of StaPass, verifying the feasibility of this approach. The proposed method can not only search for the bottleneck of capacity, but also help to trace the loading variation of facilities network in different scenarios, providing theoretical supports on passenger flow organization.
International Nuclear Information System (INIS)
Stubbe, E.J.; VanHoenacker, L.; Otero, R.
1994-02-01
This report presents an assessment study for the use of the code RELAP 5/MOD3/5M5 in the calculation of transient hydrodynamic loads on safety and relief discharge pipes. Its predecessor, RELAP 5/MOD1, was found adequate for this kind of calculations by EPRI. The hydrodynamic loads are very important for the discharge piping design because of the fast opening of the valves and the presence of liquid in the upstream loop seals. The code results are compared to experimental load measurements performed at the Combustion Engineering Laboratory in Windsor (US). Those measurements were part of the PWR Valve Test Program undertaken by EPRI after the TMI-2 accident. This particular kind of transients challenges the applicability of the following code models: two-phase choked discharge; interphase drag in conditions with large density gradients; heat transfer to metallic structures in fast changing conditions; two-phase flow at abrupt expansions. The code applicability to this kind of transients is investigated. Some sensitivity analyses to different code and model options are performed. Finally, the suitability of the code and some modeling guidelines are discussed
Impact Load of Welds After Micro-Jet Cooling / Dynamiczne Obciążenie Spoin Chłodzonych Mikrojetowo
Directory of Open Access Journals (Sweden)
Hadryś D.
2015-12-01
Full Text Available Micro-jet cooling is an innovative method of forced cooling. It could be used to cooling after welding immediately. It allows to obtain welds with better properties in comparison to ordinary welding method. Favourable structure of weld metal deposit (WMD with higher content of acicular ferrite (AF could be obtained. These properties can be controlled by several variables (e. g. type of cooling gas, number of jets. Plastic properties are particularly important in case of impact load. This type of strength is very dangerous for the structure and for safety of users (ex. car body during car crash. This article presents the influence of the cooling gas and the number of jets on plastic properties of the weld joint for impact load. It is described by restitution coefficient and plastic strain.
Energy Technology Data Exchange (ETDEWEB)
Swidersky, Harald; Thiele, Thomas [TUeV Sued Industrie Service GmbH, Muenchen (Germany)
2012-11-01
Filling procedures in piping systems are usually not load cases that are studied by fluid dynamic and structure dynamic analyses with respect to the integrity of pipes and supports. Although, their frequency is higher than that of postulated accidental transients, therefore they have to be considered for fatigue analyses. The piping and support loads due to filling procedures are caused by the density differences if the transported fluids, for instance in flows with the transport of gas bubbles. The impact duration of the momentum forces is defined by the flow velocity and the length of discontinuities in the piping segments. Filling procedures end very often with a shock pressure, caused by the impact and decelerating of the fluid front at smaller cross sections. The suitability of the thermally hydraulics program RELAP/MOD3.3 for the calculation of realistic loads from filling procedures was studied, the results compared with experimental data. It is shown that dependent on the discretization level the loads are partial significantly underestimated.
International Nuclear Information System (INIS)
Hermanns, H.J.
1977-04-01
By the example of light-water cooled nuclear reactors, the state of the calculation methods at disposal for calculating mass flow and steam quality distribution (sub-channel analysis) is indicated. Particular regard was paid to the transport phenomena occurring in reactor fuel elements in the range of two phase flow. Experimentally determined values were compared with recalculations of these experiments with the sub-channel code COBRA; from the results of these comparing calculations, conclusions could be drawn on the suitability of this code for defined applications. Limits of reliability could be determined to some extent. Based on the experience gained and the study of individual physical model concepts, recognized as being important, a sub-channel model was drawn up and the corresponding numerical computer code (SIEWAS) worked out. Experiments made at GE could be reproduced with the code SIEWAS with sufficient accuracy. (orig.) [de
Comparison of Steady-State SVC Models in Load Flow Calculations
DEFF Research Database (Denmark)
Chen, Peiyuan; Chen, Zhe; Bak-Jensen, Birgitte
2008-01-01
This paper compares in a load flow calculation three existing steady-state models of static var compensator (SVC), i.e. the generator-fixed susceptance model, the total susceptance model and the firing angle model. The comparison is made in terms of the voltage at the SVC regulated bus, equivalent...... SVC susceptance at the fundamental frequency and the load flow convergence rate both when SVC is operating within and on the limits. The latter two models give inaccurate results of the equivalent SVC susceptance as compared to the generator model due to the assumption of constant voltage when the SVC...... is operating within the limits. This may underestimate or overestimate the SVC regulating capability. Two modified models are proposed to improve the SVC regulated voltage according to its steady-state characteristic. The simulation results of the two modified models show the improved accuracy...
LOFC fission product release and circulating activity calculations for gas-cooled reactors
International Nuclear Information System (INIS)
Apperson, C.E. Jr.; Carruthers, L.M.; Lee, C.E.
1977-01-01
The inventories of fission products in a gas-cooled reactor under accident and normal steady state conditions are time and temperature dependent. To obtain a reasonable estimate of these inventories it is necessary to consider fuel failure, a temperature dependent variable, and radioactive decay, a time dependent variable. Using arbitrary radioactive decay chains and published fuel failure models for the High Temperature Gas-Cooled Reactor (HTGR), methods have been developed to evaluate the release of fission products during the Loss of Forced Circulation (LOFC) accident and the circulating and plateout fission product inventories during steady state non-accident operation. The LARC-2 model presented here neglects the time delays in the release from the HTGR due to diffusion of fission products from particles in the fuel rod through the graphite matrix. It also neglects the adsorption and evaporation process of metallics at the fuel rod-graphite and graphite-coolant hole interfaces. Any time delay due to the finite time of transport of fission products by convection through the coolant to the outside of the prestressed concrete reactor vessel (PCRV) is also neglected. This model assumes that all fission products released from fuel particles are immediately deposited outside the PCRV with no time delay
International Nuclear Information System (INIS)
Agostinetti, P.; Palma, M. Dalla; Fantini, F.; Fellin, F.; Pasqualotto, R.
2011-01-01
The analytical interpretative models for calorimetric measurements currently available in the literature can consider close systems in steady-state and transient conditions, or open systems but only in steady-state conditions. The PCCE code (Predictive Code for Calorimetric Estimations), here presented, introduces some novelties. In fact, it can simulate with an analytical approach both the heated component and the cooling circuit, evaluating the heat fluxes due to conductive and convective processes both in steady-state and transient conditions. The main goal of this code is to model heating and cooling processes in actively cooled components of fusion experiments affected by high pulsed power loads, that are not easily analyzed with purely numerical approaches (like Finite Element Method or Computational Fluid Dynamics). A dedicated mathematical formulation, based on concentrated parameters, has been developed and is here described in detail. After a comparison and benchmark with the ANSYS commercial code, the PCCE code is applied to predict the calorimetric parameters in simple scenarios of the SPIDER experiment.
International Nuclear Information System (INIS)
Takeda, Tsuneo
1977-11-01
This report is prepared as a user's input manual for a computer code CODAC-No.5 and provides a general description of the code and instructions for its use. The code represents a modified version of the CODAC-No.4 code. The code developed is capable of calculating radioactive nuclide yields in an any given complex decay and activation chain independent of irradiation history. In this code, eighteen kinds of valuable tables and graphs can be prepared for output. They are available for selection of optimum irradiation and cooling conditions and for other intentions in accordance with irradiation and cooling. For a example, the ratio of a nuclide yield to total nuclide yield depending on irradiation and cooling times is obtained. In these outputs, several kinds of complex and intricate equations and others are included. This code has almost the same input forms as that of CODAC-No.4 code excepting input of irradiation history data. Input method and formats used for this code are very simple for any kinds of nuclear data. List of FORTRAN statements, examples of input data and output results and list of input parameters and its definitions are given in this report. (auth.)
Temperature calculations of heat loads in rotating target wheels exposed to high beam currents
International Nuclear Information System (INIS)
Greene, John P.; Gabor, Rachel; Neubauer, Janelle
2001-01-01
In heavy-ion physics, high beam currents can eventually melt or destroy the target. Tightly focused beams on stationary targets of modest melting point will exhibit short lifetimes. Defocused or 'wobbled' beams are employed to enhance target survival. Rotating targets using large diameter wheels can help overcome target melting and allow for higher beam currents to be used in experiments. The purpose of the calculations in this work is to try and predict the safe maximum beam currents which produce heat loads below the melting point of the target material
Temperature calculations of heat loads in rotating target wheels exposed to high beam currents
International Nuclear Information System (INIS)
Greene, J. P.; Gabor, R.; Neubauer, J.
2000-01-01
In heavy-ion physics, high beam currents can eventually melt or destroy the target. Tightly focused beams on stationary targets of modest melting point will exhibit short lifetimes. Defocused or wobbled beams are employed to enhance target survival. Rotating targets using large diameter wheels can help overcome target melting and allow for higher beam currents to be used in experiments. The purpose of the calculations in this work is to try and predict the safe maximum beam currents which produce heat loads below the melting point of the target material
Life time calculations for LCF loading combined with tensional hold periods
International Nuclear Information System (INIS)
Bocek, M.; Armas, A.; Piel, D.
1983-01-01
The life time in high amplitude strain cycling with tensional hold periods is analysed presuming that creep failure damage is life determining. The life fraction rule (LFR) is used to calculate the life time consumpted during the dwell period in strain controlled tests as well as during tensional hold time stress cycles. It follows from the present investigation that stress relaxation occurring during the strain hold periods plays the dominant influence upon the relationship between life and dwell time. For strong stress relaxation (e.g. high temperature) less damage is accumulated as compared to suppressed relaxation (low temperature). The damage in stress relaxation is calculated by means of the LFR and the results are compared to experiments conducted on Zircaloy-4 and the austenitic stainless stell Type AISI 304. From the very good agreement between both it is concluded that under the loading conditions considered, creep failure damage is the main life determining damage contribution. (orig.)
Deetjen, Thomas A.; Reimers, Andrew S.; Webber, Michael E.
2018-02-01
This study estimates changes in grid-wide, energy consumption caused by load shifting via cooling thermal energy storage (CTES) in the building sector. It develops a general equation for relating generator fleet fuel consumption to building cooling demand as a function of ambient temperature, relative humidity, transmission and distribution current, and baseline power plant efficiency. The results present a graphical sensitivity analysis that can be used to estimate how shifting load from cooling demand to cooling storage could affect overall, grid-wide, energy consumption. In particular, because power plants, air conditioners and transmission systems all have higher efficiencies at cooler ambient temperatures, it is possible to identify operating conditions such that CTES increases system efficiency rather than decreasing it as is typical for conventional storage approaches. A case study of the Dallas-Fort Worth metro area in Texas, USA shows that using CTES to shift daytime cooling load to nighttime cooling storage can reduce annual, system-wide, primary fuel consumption by 17.6 MWh for each MWh of installed CTES capacity. The study concludes that, under the right circumstances, cooling thermal energy storage can reduce grid-wide energy consumption, challenging the perception of energy storage as a net energy consumer.
International Nuclear Information System (INIS)
Rudolf, B.
1983-01-01
Based on a large amount of aerological data, the simulation model for cooling tower cloud propagation Smoka has been used to allow for a statistical evaluation of the influence of cooling towers. In addition to local differences, the annual and daily variations in the formation of clouds can be obtained together with the dependence on the cloud coverage conditions and the cooling tower characteristics. With these model calculations of the cooling tower clouds, the respective decrease in sunshine duration can be evaluated. (orig.) [de
Burnable poison calculations for Mk.III gas-cooled reactor systems
Energy Technology Data Exchange (ETDEWEB)
Gubbins, M E
1971-02-15
A method of calculating the reactivity and burn-up hisotry of a Mk.III GCR system containing burnable poisons has been described. The method allows for poison-fuel interaction. Using the method it has been shown that burn-up of the poison under a constant incident flux can give errors of the order of 1-2 niles. A calculation using the method described will take about 50% longer than a straightforward fuel burn-up calculation in the same number of groups. The multi-cell approach has a potential for handling greater geometrical complexity. It is intended to compare the method against experiment as soon as suitable experimental results become available.
Load calculation on the nozzle in a flue gas desulphurization system
Róbert, Olšiak; Zoltán, Fuszko; Zoltán, Csuka
2017-09-01
The desulphurization system is used to remove sulfur oxides from exhaust, so-called flue gases through absorbing them via the sprayed suspension. The suspension delivered from the pump system to the atmospheric bi-directional double hollow cone nozzle has the prescribed working pressure. The unknown mechanical load on the solid body of the nozzle is present through the change of moment due to the flow of the suspension through the bi-directional outflow areas [1], [4]. The calculation of the acting forces and torques in the 3 directions was carried out with the methods of computational fluid dynamics (CFD) in the software ANSYS Fluent. The geometric model of the flow areas of the nozzle were created with the methods of reverse engineering. The computational mesh required by the CFD solver was created, and its quality verified with the standard criteria. The used boundary conditions were defined by the hydraulic parameters of the pump system, the properties of the suspension present in the hydraulic system were specified by sample analysis. The post-processed and analyzed results of the CFD calculation, the pressure-field and the velocity magnitudes in particular directions were further used as input parameters at the mechanical analysis of the load on the bi-directional nozzle.
International Nuclear Information System (INIS)
Schott, G.
1989-01-01
It is well-known that collective form, stress intensity and loading sequence of individual stresses as well as size of repeated stress blocks can influence fatigue life, significantly. The basic variant of the consecutive Woehler curve concept will permit these effects to be involved into fatigue life computation. The paper presented will demonstrate that fatigue life computations using fatigue functions reflect the loading sequence effect with multilevel loading precisely and provide reliable fatigue life data. Effects of size of repeated stress block and loading sequence on fatigue life as observed with block program tests can be reproduced using the new computation method. (orig.) [de
International Nuclear Information System (INIS)
Butland, A.T.D.; Reddell, G.
1979-01-01
After a survey of the requirements, an assessment of UK methods and data is made on the basis of the following work. First, the analysis of the SEFOR Doppler experiments, carried out using the UK FGL5 fine group nuclear data library, the MURAL cell code and whole reactor diffusion theory calculations of the neutron flux. Second, the analysis of some Japanese FCA central sample perturbation measurements of structural material Doppler effects. Third, an assessment of the accuracy of Doppler predictions in a sodium voided core using results from Zebra 5 and BIZET, and theoretical studies of additional effects relevant to power reactors and not covered by the above analyses, including the following, the calculation of Doppler effects at high temperature, fuel cycle and burn-up effects, and the heterogeneity effects of large fuelled subassemblies in pin geometry. The importance of crystalline binding effects in the fuel are discussed as is the importance of reactor material boundaries in the calculation of resonance shielding effects. Some suggestions for further Doppler studies are made. (U.K.)
Hasegawa, M; Tajima, O; Chinone, Y; Hazumi, M; Ishidoshiro, K; Nagai, M
2011-05-01
We present a novel system to calibrate millimeter-wave polarimeters for cosmic microwave background (CMB) polarization measurements. This technique is an extension of the conventional metal mirror rotation approach, however, it employs cryogenically-cooled blackbody absorbers. The primary advantage of this system is that it can generate a slightly polarized signal (∼100 mK) in the laboratory; this is at a similar level to that measured by ground-based CMB polarization experiments observing a ∼10 K sky. It is important to reproduce the observing condition in the laboratory for reliable characterization of polarimeters before deployment. In this paper, we present the design and principle of the system and demonstrate its use with a coherent-type polarimeter used for an actual CMB polarization experiment. This technique can also be applied to incoherent-type polarimeters and it is very promising for the next-generation CMB polarization experiments.
Energy Technology Data Exchange (ETDEWEB)
Belov, Nikolay, E-mail: n.n.belov@mail.ru; Kopanitsa, Dmitry, E-mail: kopanitsa@mail.ru; Yugov, Alexey, E-mail: yugalex@mail.ru; Kaparulin, Sergey, E-mail: kaparulin@mail.ru; Plyaskin, Andrey, E-mail: plyaskinandrei@mail.ru; Kalichkina, Anna, E-mail: aniotka@mail.ru; Ustinov, Artyom, E-mail: artemustinov@bk.ru [Tomsk State University of Architecture and Building, 2, Solyanaya Sq. Tomsk, 634003 (Russian Federation); Yugov, Nikolay, E-mail: n.t.yugov@mail.ru [Tomsk State University for Radio Electronics and Control Systems, 40, Lenin Av. Tomsk, 634050 (Russian Federation); Kopanitsa, Georgy, E-mail: kopanitsa@mail.ru [National Research Tomsk Polytechnic University, 30, Lenin Av. Tomsk, 634050 (Russian Federation)
2016-01-15
When designing buildings with reinforced concrete that are planned to resist dynamic loads it is necessary to calculate this structural behavior under operational static and emergency impact and blast loads. Calculations of the structures under shock-wave loads can be performed by solving dynamic equations that do not consider static loads. Due to this fact the calculation of reinforced concrete frame under a simultaneous static and dynamic load in full 3d settings becomes a very non trivial and resource consuming problem. This problem can be split into two tasks. The first one is a shock-wave problem that can be solved using software package RANET-3, which allows solving the problem using finite elements method adapted for dynamic task. This method calculates strain-stress state of the material and its dynamic destruction, which is considered as growth and consolidation of micro defects under loading. On the second step the results of the first step are taken as input parameters for quasi static calculation of simultaneous static and dynamic load using finite elements method in AMP Civil Engineering-11.
International Nuclear Information System (INIS)
Belov, Nikolay; Kopanitsa, Dmitry; Yugov, Alexey; Kaparulin, Sergey; Plyaskin, Andrey; Kalichkina, Anna; Ustinov, Artyom; Yugov, Nikolay; Kopanitsa, Georgy
2016-01-01
When designing buildings with reinforced concrete that are planned to resist dynamic loads it is necessary to calculate this structural behavior under operational static and emergency impact and blast loads. Calculations of the structures under shock-wave loads can be performed by solving dynamic equations that do not consider static loads. Due to this fact the calculation of reinforced concrete frame under a simultaneous static and dynamic load in full 3d settings becomes a very non trivial and resource consuming problem. This problem can be split into two tasks. The first one is a shock-wave problem that can be solved using software package RANET-3, which allows solving the problem using finite elements method adapted for dynamic task. This method calculates strain-stress state of the material and its dynamic destruction, which is considered as growth and consolidation of micro defects under loading. On the second step the results of the first step are taken as input parameters for quasi static calculation of simultaneous static and dynamic load using finite elements method in AMP Civil Engineering-11
Compressive Loads on the Lumbar Spine During Lifting: 4D WATBAK versus Inverse Dynamics Calculations
Directory of Open Access Journals (Sweden)
M. H. Cole
2005-01-01
Full Text Available Numerous two- and three-dimensional biomechanical models exist for the purpose of assessing the stresses placed on the lumbar spine during the performance of a manual material handling task. More recently, researchers have utilised their knowledge to develop specific computer-based models that can be applied in an occupational setting; an example of which is 4D WATBAK. The model used by 4D WATBAK bases its predications on static calculations and it is assumed that these static loads reasonably depict the actual dynamic loads acting on the lumbar spine. Consequently, it was the purpose of this research to assess the agreement between the static predictions made by 4D WATBAK and those from a comparable dynamic model. Six individuals were asked to perform a series of five lifting tasks, which ranged from lifting 2.5 kg to 22.5 kg and were designed to replicate the lifting component of the Work Capacity Assessment Test used within Australia. A single perpendicularly placed video camera was used to film each performance in the sagittal plane. The resultant two-dimensional kinematic data were input into the 4D WATBAK software and a dynamic biomechanical model to quantify the compression forces acting at the L4/L5 intervertebral joint. Results of this study indicated that as the mass of the load increased from 2.5 kg to 22.5 kg, the static compression forces calculated by 4D WATBAK became increasingly less than those calculated using the dynamic model (mean difference ranged from 22.0% for 2.5 kg to 42.9% for 22.5 kg. This study suggested that, for research purposes, a validated three-dimensional dynamic model should be employed when a task becomes complex and when a more accurate indication of spinal compression or shear force is required. Additionally, although it is clear that 4D WATBAK is particularly suited to industrial applications, it is suggested that the limitations of such modelling tools be carefully considered when task-risk and employee
Loading, absorption, and Fokker-Planck calculations for upcoming ICRF experiments on ATF
International Nuclear Information System (INIS)
Shepard, T.D.; Carter, M.D.; Goulding, R.H.; Kwon, M.
1989-01-01
ICRF experiments on ATF at the 100-kW level are planned for the current 1989 operating period. These plans include the 2ω/sub cH/ regime at f/sub RF/ = 28.88 MHz, D(H) at 14.44 MHz, and 4 He( 3 He) and D( 3 He) at 9.63 MHz. ECH target plasmas have n/sub eO/ /approxreverse arrowlt/ 0.15 /times/ 10 20 m/sup /minus/3/ and B = 0.95 T. The density and temperature profiles obtained are broader than those from 1988, owing to recent field error corrections. The values used for target-plasma parameters in the calculations were taken from initial 1989 ATF data. Loading and absorption calculations have been performed using the 3D RF heating code ORION with a helically symmetric equilibrium, and Fokker-Planck calculations were performed using the steady-state code RFTRANS with two velocity dimensions and one spatial dimension. 6 refs., 3 figs
Chen, Yunxia; Cui, Yuxuan; Gong, Wenjun
2017-01-01
Static fatigue behavior is the main failure mode of optical fibers applied in sensors. In this paper, a computational framework based on continuum damage mechanics (CDM) is presented to calculate the crack propagation process and failure time of optical fibers subjected to static bending and tensile loads. For this purpose, the static fatigue crack propagation in the glass core of the optical fiber is studied. Combining a finite element method (FEM), we use the continuum damage mechanics for the glass core to calculate the crack propagation path and corresponding failure time. In addition, three factors including bending radius, tensile force and optical fiber diameter are investigated to find their impacts on the crack propagation process and failure time of the optical fiber under concerned situations. Finally, experiments are conducted and the results verify the correctness of the simulation calculation. It is believed that the proposed method could give a straightforward description of the crack propagation path in the inner glass core. Additionally, the predicted crack propagation time of the optical fiber with different factors can provide effective suggestions for improving the long-term usage of optical fibers. PMID:29140284
Efficient Finite Element Models for Calculation of the No-load losses of the Transformer
Directory of Open Access Journals (Sweden)
Kamran Dawood
2017-10-01
Full Text Available Different transformer models are examined for the calculation of the no-load losses using finite element analysis. Two-dimensional and three-dimensional finite element analyses are used for the simulation of the transformer. Results of the finite element method are also compared with the experimental results. The Result shows that 3-dimensional provide high accuracy as compared to the 2 dimensional full and half model. However, the 2-dimensional half model is the less time-consuming method as compared to the 3 and 2-dimensional full model. Simulation time duration taken by the different models of the transformer is also compared. The difference between the 3-dimensional finite element method and experimental results are less than 3%. These numerical methods can help transformer designers to minimize the development of the prototype transformers.
Suspended sediment measurements and calculation of the particle load at HPP Fieschertal
Felix, D.; Albayrak, I.; Abgottspon, A.; Boes, R. M.
2016-11-01
In the scope of a research project on hydro-abrasive erosion of Pelton turbines, a field study was conducted at the high-head HPP Fieschertal in Valais, Switzerland. The suspended sediment mass concentration (SSC) and particle size distribution (PSD) in the penstock have been continuously measured since 2012 using a combination of six measuring techniques. The SSC was on average 0.52 g/l and rose to 50 g/l in a major flood event in July 2012. The median particle size d 50 was usually 15 pm, rising up to 100 μm when particles previously having settled in the headwater storage tunnel were re-suspended at low water levels. The annual suspended sediment loads (SSL) varied considerably depending on flood events. Moreover, so-called particle loads (PLs) according to the relevant guideline of the International Electrotechnical Commission (IEC 62364) were calculated using four relations between particle size and the relative abrasion potential. For the investigated HPP, the time series of the SSL and the PLs had generally similar shapes over the three years. The largest differences among the PLs were observed during re-suspension events when the particles were considerably coarser than usual. Further investigations on the effects of particle sizes on hydroabrasive erosion of splitters and cut-outs of coated Pelton turbines are recommended.
Cost-Effective Integration of Efficient Low-Lift Base Load Cooling Equipment
Energy Technology Data Exchange (ETDEWEB)
Jiang, Wei; Winiarski, David W.; Katipamula, Srinivas; Armstrong, Peter R.
2008-01-14
The long-term goal of DOE’s Commercial Buildings Integration subprogram is to develop cost-effective technologies and building practices that will enable the design and construction of net Zero Energy Buildings — commercial buildings that produce as much energy as they use on an annual basis — by 2025. To support this long-term goal, DOE further called for — as part of its FY07 Statement of Needs — the development by 2010 of “five cost-effective design technology option sets using highly efficient component technologies, integrated controls, improved construction practices, streamlined commissioning, maintenance and operating procedures that will make new and existing commercial buildings durable, healthy and safe for occupants.” In response, PNNL proposed and DOE funded a scoping study investigation of one such technology option set, low-lift cooling, that offers potentially exemplary HVAC energy performance relative to ASHRAE Standard 90.1-2004. The primary purpose of the scoping study was to estimate the national technical energy savings potential of this TOS.
International Nuclear Information System (INIS)
Grabezhnaya, V.A.
2008-01-01
Paper reviews the numerical investigation into the heat transfer in the supercritical water cooled fuel assemblies on the basis of the various commercial codes. The turbulence available models specified in the codes describe adequately the experimental data in tubes within the range of flow temperatures away from the pseudocritical point, as well as under high mass velocities. There are k-ε type turbulence models that show qualitatively the local acceleration (slowdown) of the heat transfer in tubes, but they fail to describe the mentioned phenomena quantitatively. To determine the effect of grid spacers on the suppression of the heat transfer local slowdown and on the heat transfer acceleration in fuel assemblies and to ensure more accurate calculation of the fuel element cladding maximum temperature one should perform a number of the experiments making use of the fuel assembly models [ru
Schwarte, Kirk A; Russell, James R; Kovar, John L; Morrical, Daniel G; Ensley, Steven M; Yoon, Kyoung-Jin; Cornick, Nancy A; Cho, Yong Il
2011-01-01
Erosion and runoff from pastures may lead to degradation of surface water. A 2-yr grazing study was conducted to quantify the effects of grazing management on sediment, phosphorus (P), and pathogen loading of streams in cool-season grass pastures. Six adjoining 12.1-ha pastures bisected by a stream in central Iowa were divided into three treatments: continuous stocking with unrestricted stream access (CSU), continuous stocking with restricted stream access (CSR), and rotational stocking (RS). Rainfall simulations on stream banks resulted in greater ( CSR pastures. Bovine enterovirus was shed by an average of 24.3% of cows during the study period and was collected in the runoff of 8.3 and 16.7% of runoff simulations on bare sites in CSU pastures in June and October of 2008, respectively, and from 8.3% of runoff simulations on vegetated sites in CSU pastures in April 2009. Fecal pathogens (bovine coronavirus [BCV], bovine rotavirus group A, and O157:H7) shed or detected in runoff were almost nonexistent; only BCV was detected in feces of one cow in August of 2008. Erosion of cut-banks was the greatest contributor of sediment and P loading to the stream; contributions from surface runoff and grazing animals were considerably less and were minimized by grazing management practices that reduced congregation of cattle by pasture streams. Copyright © by the American Society of Agronomy, Crop Science Society of America, and Soil Science Society of America, Inc.
REFLOS, Fuel Loading and Cost from Burnup and Heavy Atomic Mass Flow Calculation in HWR
International Nuclear Information System (INIS)
Boettcher, W.; Schmidt, E.
1969-01-01
1 - Nature of physical problem solved: REFLOS is a programme for the evaluation of fuel-loading schemes in heavy water moderated reactors. The problems involved in this study are: a) Burn-up calculation for the reactor cell. b) Determination of reactivity behaviour, power distribution, attainable burn-up for both the running-in period and the equilibrium of a 3-dimensional heterogeneous reactor model; investigation of radial fuel movement schemes. c) Evaluation of mass flows of heavy atoms through the reactor and fuel cycle costs for the running-in, the equilibrium, and the shut down of a power reactor. If the subroutine for treating the reactor cell were replaced by a suitable routine, other reactors with weakly absorbing moderators could be analyzed. 2 - Method of solution: Nuclear constants and isotopic compositions of the different fuels in the reactor are calculated by the cell-burn-up programme and tabulated as functions of the burn-up rate (MWD/T). Starting from a known state of the reactor, the 3-dimensional heterogeneous reactor programme (applying an extension of the technique of Feinberg and Galanin) calculates reactivity and neutron flux distribution using one thermal and one or two fast neutron groups. After a given irradiation time, the new state of the reactor is determined, and new nuclear constants are assigned to the various defined locations in the reactor. Reloading of fuel may occur if the prescribed life of the reactor is reached or if the effective multiplication factor or the power form factor falls below a specified level. The scheme of reloading to be carried out is specified by a load vector, giving the number of channels to be discharged, the kind of movement from one to another channel and the type of fresh fuel to be charged for each single reloading event. After having determined the core states characterizing the equilibrium period, and having decided the fuel reloading scheme for the running-in period of the reactor life, the fuel
Vries, de W.; Bakker, D.J.
1996-01-01
Methodologies are described for calculating critical loads of lead, cadmium, copper, zinc, nickel, chromium and mercury for soils and surface waters. The aspects which are discussed are: selection of a computation model, determination of environmental-quality criteria for the metals, collection of
International Nuclear Information System (INIS)
Spandagos, Constantinos; Ng, Tze Ling
2017-01-01
Highlights: • EFLH for estimating cooling/heating energy demand in Asian buildings are provided. • Net increases in building energy consumption over the next 30 years are predicted. • Switching to more efficient AC devices can offset much of the increases. - Abstract: Estimating cooling and heating energy requirements is an integral part of designing and managing buildings. Further, as buildings are among the largest energy consumers in cities, the estimates are important for formulating effective energy conservation strategies. Where complex hourly simulation models are not favored, such estimates may be derived by simplified methods that are less computationally intensive but still provide results that are reasonably close to those obtained from the more complicated approach. The equivalent full load hours (EFLH) method is a simplified energy estimation method that has recently gained popularity. It offers a straightforward means of evaluating energy efficiency programs. However, to date, easily accessible EFLH data exist only for a very limited number of countries in North America and Europe, but not Asia. This current work provides previously unavailable monthly EFLH data for building cooling and heating in three large Asian cities, viz. Hong Kong, Seoul and Tokyo. To assess the effects of changing temperature over the course of decades on building cooling and heating energy consumption, EFLH data are calculated for three time periods: past (1983–2005), present (2006–2014) and future (2015–2044). The projections for the future time period are based on the climate scenarios Representative Concentration Pathways (RCPs) 4.5 and 8.5 of the Intergovernmental Panel on Climate Change (IPCC) Fifth Assessment Report. RCP-4.5 assumes a stabilization of future greenhouse gas (GHG) emissions followed by a reduction, while RCP-8.5 assumes their further increase. From the EFLH data, considering just the effects of ambient temperature changes, it is projected the
International Nuclear Information System (INIS)
Byun, Choong Sup; Song, Dong Soo; Jun, Hwang Yong
2006-01-01
In a design point of view, component cooling water (CCW) system is not full-interactively designed with its heat loads. Heat loads are calculated from the CCW design flow and temperature condition which is determined with conservatism. Then the CCW heat exchanger is sized by using total maximized heat loads from above calculation. This approach does not give the optimized performance results and the exact trends of CCW system and the loads during transient. Therefore a combined model for performance analysis of containment and the component cooling water(CCW) system is developed by using GOTHIC software code. The model is verified by using the design parameters of component cooling water heat exchanger and the heat loads during the recirculation mode of loss of coolant accident scenario. This model may be used for calculating the realistic containment response and CCW performance, and increasing the ultimate heat sink temperature limits
International Nuclear Information System (INIS)
Fahmy, M.F.M.; Nabih, H.I.
2016-01-01
Highlights: • An analytical method regulated the air flow rate in an air-cooled heat exchanger. • Performance of an ACHE in a propane cycle in an LNG plant was evaluated. • Summer inlet air temperature had higher impact on ACHE air flow rate requirement. - Abstract: An analytical method is presented to evaluate the air flow rate required in an air-cooled heat exchanger used in a propane pre-cooling cycle operating in an LNG (liquefied natural gas) plant. With variable ambient air inlet temperature, the air flow rate is to be increased or decreased so as to assure and maintain good performance of the operating air-cooled heat exchanger at the designed parameters and specifications. This analytical approach accounts for the variations in both heat load and ambient air inlet temperature. The ambient air inlet temperature is modeled analytically by simplified periodic relations. Thus, a complete analytical method is described so as to manage the problem of determining and accordingly regulate, either manually or automatically, the flow rate of air across the finned tubes of the air-cooled heat exchanger and thus, controls the process fluid outlet temperature required for the air-cooled heat exchangers for both cases of constant and varying heat loads and ambient air inlet temperatures. Numerical results are obtained showing the performance of the air-cooled heat exchanger of a propane cycle which cools both NG (natural gas) and MR (mixed refrigerant) streams in the LNG plant located at Damietta, Egypt. The inlet air temperature variation in the summer time has a considerable effect on the required air mass flow rate, while its influence becomes relatively less pronounced in winter.
International Nuclear Information System (INIS)
Harnach, R.
1977-01-01
The natural wind is the decisive risk factor in natural-draught cooling towers; therefore, the establishment of an assumed velocity is indispensable for the safety and reliability of the construction. In the framework of a statistical wind concept, static substitution loads for the assumed dynamic wind pressure have been determined, also including dynamic wind effects and the resonance response of the structure. On this basis, it has been studied how wind loads with different periodicity affect the material requirements of reinforced-concrete natural-draught cooling towers. It is found that the additional steel requirements, related to the total building cost, remain within acceptable limits even for extreme wind loads. (orig.) [de
Agapov, Vladimir; Golovanov, Roman; Aidemirov, Kurban
2017-10-01
The technique of calculation of prestressed reinforced concrete trusses with taking into account geometrical and physical nonlinearity is considered. As a tool for solving the problem, the finite element method has been chosen. Basic design equations and methods for their solution are given. It is assumed that there are both a prestressed and nonprestressed reinforcement in the bars of the trusses. The prestress is modeled by setting the temperature effect on the reinforcement. The ways of taking into account the physical and geometrical nonlinearity for bars of reinforced concrete trusses are considered. An example of the analysis of a flat truss is given and the behavior of the truss on various stages of its loading up to destruction is analyzed. A program for the analysis of flat and spatial concrete trusses taking into account the nonlinear deformation is developed. The program is adapted to the computational complex PRINS. As a part of this complex it is available to a wide range of engineering, scientific and technical workers
Energy Technology Data Exchange (ETDEWEB)
Dai, J.C. [College of Mechanical and Electrical Engineering, Central South University, Changsha (China); School of Electromechanical Engineering, Hunan University of Science and Technology, Xiangtan (China); Hu, Y.P.; Liu, D.S. [School of Electromechanical Engineering, Hunan University of Science and Technology, Xiangtan (China); Long, X. [Hara XEMC Windpower Co., Ltd., Xiangtan (China)
2011-03-15
The aerodynamic loads for MW scale horizontal-axis wind turbines are calculated and analyzed in the established coordinate systems which are used to describe the wind turbine. In this paper, the blade element momentum (BEM) theory is employed and some corrections, such as Prandtl and Buhl models, are carried out. Based on the B-L semi-empirical dynamic stall (DS) model, a new modified DS model for NACA63-4xx airfoil is adopted. Then, by combing BEM modified theory with DS model, a set of calculation method of aerodynamic loads for large scale wind turbines is proposed, in which some influence factors such as wind shear, tower, tower and blade vibration are considered. The research results show that the presented dynamic stall model is good enough for engineering purpose; the aerodynamic loads are influenced by many factors such as tower shadow, wind shear, dynamic stall, tower and blade vibration, etc, with different degree; the single blade endures periodical changing loads but the variations of the rotor shaft power caused by the total aerodynamic torque in edgewise direction are very small. The presented study approach of aerodynamic loads calculation and analysis is of the university, and helpful for thorough research of loads reduction on large scale wind turbines. (author)
International Nuclear Information System (INIS)
Yazdani-Asrami, Mohammad; Mirzaie, Mohammad; Shayegani Akmal, Amir Abbas
2013-01-01
Transformers are basically designed to operate under nominal voltage, rated frequency and also, pure sinusoidal load current. In recent decade, change in the type of loads and increasing use of power electronic devices with their nonsinusoidal current waveform has distorted the system voltage waveform as well. The losses of transformers include load and no-load losses. No-load loss continuously led to loss of energy in transformers that are connected to the network in all 24 h. With respect to high significance of energy and undesirable impacts of losses on the aging of transformers, the no-load loss is considered as a critical factor. Nowadays, it is necessary to apply a suitable method for calculation of no-load loss in presence of the voltage harmonics and over-excite conditions, especially for distribution transformers, as a result of harmonic increase in the voltage and current in the network and particular applications. In this paper, Finite Element Method (FEM) has been used to simulate nonsinusoidal voltage effects on no-load loss of transformers. Such simulation enables the software to simulate and analyze different electromagnetic parameters such as flux lines, flux density, losses, and etc under different input sources and with high accuracy. In addition, effect of nonsinusoidal voltages on no-load loss has been investigated by a typical experimental transformer using several practical tests. - Highlights: ► FEM has been employed to loss calculation of distribution transformer under distorted voltages. ► This method gives accurate results in comparison with standard or circuit based methods. ► A new version of 3D FEM has been used, this approach is electromagnetic based. ► In literature, FEM always used for study of transformer load loss and most of them based on magneto-static FEM. ► FEM results are validated by experiment for small test transformer
Calculation of design load for the MOD-5A 7.3 mW wind turbine system
Mirandy, L.; Strain, J. C.
1995-01-01
Design loads are presented for the General Electric MOD-SA wind turbine. The MOD-SA system consists of a 400 ft. diameter, upwind, two-bladed, teetered rotor connected to a 7.3 mW variable-speed generator. Fatigue loads are specified in the form of histograms for the 30 year life of the machine, while limit (or maximum) loads have been derived from transient dynamic analysis at critical operating conditions. Loads prediction was accomplished using state of the art aeroelastic analyses developed at General Electric. Features of the primary predictive tool - the Transient Rotor Analysis Code (TRAC) are described in the paper. Key to the load predictions are the following wind models: (1) yearly mean wind distribution; (2) mean wind variations during operation; (3) number of start/shutdown cycles; (4) spatially large gusts; and (5) spatially small gusts (local turbulence). The methods used to develop statistical distributions from load calculations represent an extension of procedures used in past wind programs and are believed to be a significant contribution to Wind Turbine Generator analysis. Test/theory correlations are presented to demonstrate code load predictive capability and to support the wind models used in the analysis. In addition MOD-5A loads are compared with those of existing machines. The MOD-5A design was performed by the General Electric Company, Advanced Energy Program Department, under Contract DEN3-153 with NASA Lewis Research Center and sponsored by the Department of Energy.
Energy Technology Data Exchange (ETDEWEB)
Campolina, Daniel; Costa, Antonio Carlos L. da; Andrade, Edison P., E-mail: campolina@cdtn.br, E-mail: aclp@cdtn.br, E-mail: epa@cdtn.br [Centro de Desenvolvimento da Tecnologia Nuclear (SETRE/CDTN/CNEN-MG), Belo Horizonte, MG (Brazil). Servico de Tecnologia de Reatores
2017-07-01
The structuring project of the Brazilian Multipurpose Reactor (RMB) is responsible for meeting the capacity to develop and test materials and nuclear fuel for the Brazilian Nuclear Program. An irradiation test device (Loop) capable of performing fuel test for power reactor rods is being conceived for RMB reflector. In this work preliminary neutronic calculations have been carried out in order to determine parameters to the cooling system of the Loop basic design. The heat released as a result of radioactive decay of fuel samples was calculated using ORIGEN-ARP and it resulted less than 200 W after 1 hour of irradiation interruption. (author)
International Nuclear Information System (INIS)
Pham Nhu Viet Ha; Min Jae Lee; Sunghwan Yun; Sang Ji Kim
2015-01-01
Power regulation systems of fast reactors are based on the signals of excore detectors. The excore detector weighting functions, which establish correspondence between the core power distribution and detector signal, are very useful for detector response analyses, e.g., in rod drop experiments. This paper presents the calculation of the weighting functions for a TRU burner mockup of the Korean Prototype Generation-IV Sodium-cooled Fast Reactor (named BFS-76-1A) using the MCNP5 multi-group adjoint capability. For generation of the weighting functions, all fuel assemblies were considered and each of them was divided into ten horizontal layers. Then the weighting functions for individual fuel assembly horizontal layers, the assembly weighting functions, and the shape annealing functions at RCP (Reactor Critical Point) and at conditions under which a control rod group was fully inserted into the core while other control rods at RCP were determined and evaluated. The results indicate that the weighting functions can be considered relatively insensitive to the control rods position during the rod drop experiments and therefore those weighting values at RCP can be applied to the dynamic rod worth simulation for the BFS-76-1A. (author)
AC-DC integrated load flow calculation for variable speed offshore wind farms
DEFF Research Database (Denmark)
Zhao, Menghua; Chen, Zhe; Blaabjerg, Frede
2005-01-01
This paper proposes a sequential AC-DC integrated load flow algorithm for variable speed offshore wind farms. In this algorithm, the variable frequency and the control strategy of variable speed wind turbine systems are considered. In addition, the losses of wind turbine systems and the losses...... of converters are also integrated into the load flow algorithm. As a general algorithm, it can be applied to different types of wind farm configurations, and the load flow is related to the wind speed....
Jutte, Christine V.; Ko, William L.; Stephens, Craig A.; Bakalyar, John A.; Richards, W. Lance
2011-01-01
A ground loads test of a full-scale wing (175-ft span) was conducted using a fiber optic strain-sensing system to obtain distributed surface strain data. These data were input into previously developed deformed shape equations to calculate the wing s bending and twist deformation. A photogrammetry system measured actual shape deformation. The wing deflections reached 100 percent of the positive design limit load (equivalent to 3 g) and 97 percent of the negative design limit load (equivalent to -1 g). The calculated wing bending results were in excellent agreement with the actual bending; tip deflections were within +/- 2.7 in. (out of 155-in. max deflection) for 91 percent of the load steps. Experimental testing revealed valuable opportunities for improving the deformed shape equations robustness to real world (not perfect) strain data, which previous analytical testing did not detect. These improvements, which include filtering methods developed in this work, minimize errors due to numerical anomalies discovered in the remaining 9 percent of the load steps. As a result, all load steps attained +/- 2.7 in. accuracy. Wing twist results were very sensitive to errors in bending and require further development. A sensitivity analysis and recommendations for fiber implementation practices, along with, effective filtering methods are included
Energy Technology Data Exchange (ETDEWEB)
Grozdek, Marino
2009-10-15
Ice based Cool Thermal Energy Storage (CTES) systems have attracted much attention during last few decades. The reasons are mainly of economical and environmental nature. Compared to conventional refrigeration and air-conditioning systems without cool thermal energy storage, implementation of CTES will increase environmental standards and overall efficiency of the energy systems as it contributes to the phase-out of synthetic refrigerants and reduces peak loads in electricity grids. For the application of a cool thermal energy storages in refrigeration installations and HVAC systems in industry and building sector, it is necessary to have appropriate design tools in order to sufficiently accurate predict their performance. In this thesis theoretical and experimental investigations of two ice based cool thermal energy storage systems, namely static, indirect, external melt, ice-on-coil, i.e. ice bank system and dynamic, ice slurry cool thermal energy storage system are carried out. An ice bank storage technology for cooling purposes is known for a long time. The main drawbacks which are hindering its wider use are the system complexity, high first costs, system efficiency which is highly dependant on design, control and monitoring of the system, etc. On the other hand, ice slurry technology was not well studied until recently, while in the current scientific literature there are still differences between results and conclusions reported by different investigators. The aim of the present thesis is to extend the knowledge in the field of ice based CTES systems, thereby contributing in the development and wider utilization of those systems. In the first part of the thesis a computer application, named 'BankaLeda' is presented. It enables simulation of an ice bank system performance. In order to verify developed simulation model an experimental evaluation has been performed. Field measurements have been conducted on a two module silo which was installed as a
Kim, Myoung Soo; Park, Jung Ha; Park, Kyung Yeon
2012-10-01
This study was done to develop and evaluate a drug dosage calculation training program using cognitive loading theory based on a smartphone application. Calculation ability, dosage calculation related self-efficacy and anxiety were measured. A nonequivalent control group design was used. Smartphone application and a handout for self-study were developed and administered to the experimental group and only a handout was provided for control group. Intervention period was 4 weeks. Data were analyzed using descriptive analysis, χ²-test, t-test, and ANCOVA with the SPSS 18.0. The experimental group showed more 'self-efficacy for drug dosage calculation' than the control group (t=3.82, psmartphone application is effective in improving dosage calculation related self-efficacy and calculation ability. Further study should be done to develop additional interventions for reducing anxiety.
A method for calculation of finite fatigue life under multiaxial loading in high-cycle domain
Directory of Open Access Journals (Sweden)
M. Malnati
2014-04-01
Full Text Available A method for fatigue life assessment in high-cycle domain under multiaxial loading is presented in this paper. This approach allows fatigue assessment under any kind of load history, without limitations. The methodology lies on the construction - at a macroscopic level - of an “indicator” in the form of a set of cycles, representing plasticity that can arise at mesoscopic level throughout fatigue process. During the advancement of the loading history new cycles are created and a continuous evaluation of the damage is made.
Energy Technology Data Exchange (ETDEWEB)
Kamykowski, E.A. (Grumman Corporate Research Center, Bethpage, NY (United States))
1992-07-15
Boron-loaded scintillators offer the potential for neutron spectrometers with a simplified, peak-shaped response. The Monte Carlo code, MCNP, has been used to calculate the detector characteristics of a scintillator made of a boron-loaded plastic, BC454, for neutrons between 1 and 7 MeV. Comparisons with measurements are made of spectral response for neutron energies between 4 and 6 MeV and of intrinsic efficiencies for neutrons up to 7 MeV. In order to compare the calculated spectra with measured data, enhancements to MCNP were introduced to generate tallies of light output spectra for recoil events terminating in a final capture by {sup 10}B. The comparison of measured and calculated spectra shows agreement in response shape, full width at half maximum, and recoil energy deposition. Intrinsic efficiencies measured to 7 MeV are also in agreement with the MCNP calculations. These results validate the code predictions and affirm the value of MCNP as a useful tool for development of sensor concepts based on boron-loaded plastics. (orig.).
International Nuclear Information System (INIS)
Li, Zeyu; Liu, Liming; Liu, Jinping
2016-01-01
Highlights: • Design criterion of heat load ratio of generator is vital to system performance. • Heat load ratio of generator changes with working condition. • Change of heat load ratio of generator for four systems was obtained and compared. • Design criterion of heat load ratio of generator was presented. - Abstract: The heat load ratio of generator (HLRG) is a special system parameter because it is not fixed at the design value but changes with the working condition. For the air cooled chiller, the deviation from the design working condition occurs easily due to the variation of the surrounding temperature. The system is likely to suffer from crystallization when the working condition is different from the designed one if the HLRG is designed improperly. Consequently, the design criterion of HLRG based on a broad range of working condition is essential and urgent to the development of air cooled lithium bromide–water double effect absorption chiller. This paper mainly deals with the variation of HLRG with the working condition as well as corresponding design criterion. Four types of double effect chillers named series, pre-parallel, rear parallel and reverse parallel flow system were considered. The parametric model was developed by the introduction of a new thermodynamic relationship of generator. The change of HLRG for different types of chillers with the working condition was analyzed and compared. The corresponding design criterion of HLRG was presented. This paper is helpful for further improvement of the performance and reliability of air cooled lithium bromide–water double effect absorption chiller.
System incremental cost calculations using the participation factor load-flow formulation
International Nuclear Information System (INIS)
Meisel, J.
1993-01-01
The load-flow problem is reformulated such that the use of a slack-bus generator is included only as a special case. This reformulation, known as the participation factor load-flow, includes a total mismatch variable and a defined participation vector, which, in general, distributes this mismatch to all system buses. The slack-bus constraint can still be obtained by defining a particular participation vector. In using the participation factor load-flow in the transpose Jacobian approach to the economic optimal dispatch problem, the paper shows that the value of the system-λ can be controlled such that this value represents the minimal incremental change in generation costs per unit change in system total demand with this demand distributed according to the specified participation vector. Methods using the conventional B-coefficient loss formulas or slack-bus load-flows give system-λ values whereby the unit change in demand must be placed on a fictitious single load-bus or on the slack-bus, respectively. Having a system-λ value which more accurately represents a proposed energy interchange between interconnected systems is very important in developing valid costs for each system. An extensive 28-bus, 8-generator system is included to illustrate these results
Influence of Shading on Cooling Energy Demand
Rabczak, Sławomir; Bukowska, Maria; Proszak-Miąsik, Danuta; Nowak, Krzysztof
2017-10-01
The article presents an analysis of the building cooling load taking into account the variability of the factors affecting the size of the heat gains. In order to minimize the demand for cooling, the effect of shading elements installed on the outside on the windows and its effect on size of the cooling capacity of air conditioning system for the building has been estimated. Multivariate building cooling load calculations to determine the size of the reduction in cooling demand has derived. Determination of heat gain from the sun is laborious, but gives a result which reflects the influence of the surface transparent partitions, devices used as sunscreen and its location on the building envelope in relation to the world, as well as to the internal heat gains has great attention in obtained calculation. In this study, included in the balance sheet of solar heat gains are defined in three different shading of windows. Calculating the total demand cooling is made for variants assuming 0% shading baffles transparent, 50% shading baffles transparent external shutters at an angle of 45 °, 100% shading baffles transparent hours 12 from the N and E and from 12 from the S and W of the outer slat blinds. The calculation of the average hourly cooling load was taken into account the option assuming the hypothetical possibility of default by up to 10% of the time assumed the cooling season temperatures in the rooms. To reduce the consumption of electricity energy in the cooling system of the smallest variant identified the need for the power supply for the operation of the cooling system. Also assessed the financial benefits of the temporary default of comfort.
International Nuclear Information System (INIS)
Williams, D.C.; Bergeron, K.D.; Carroll, D.E.; Gasser, R.D.; Tills, J.L.; Washington, K.E.
1987-05-01
One of the most important unresolved issues governing risk in many nuclear power plants involves the phenomenon called direct containment heating (DCH), in which it is postulated that molten corium ejected under high pressure from the reactor vessel is dispersed into the containment atmosphere, thereby causing sufficient heating and pressurization to threaten containment integrity. Models for the calculation of potential DCH loads have been developed and incorporated into the CONTAIN code for severe accident analysis. Using CONTAIN, DCH scenarios in PWR plants having three different representative containment types have been analyzed: Surry (subatmospheric large dry containment), Sequoyah (ice condenser containment), and Bellefonte (atmospheric large dry containment). A large number of parameter variation and phenomenological uncertainty studies were performed. Response of DCH loads to these variations was found to be quite complex; often the results differ substantially from what has been previously assumed concerning DCH. Containment compartmentalization offers the potential of greatly mitigating DCH loads relative to what might be calculated using single-cell representations of containments, but the actual degree of mitigation to be expected is sensitive to many uncertainties. Dominant uncertainties include hydrogen combustion phenomena in the extreme environments produced by DCH scenarios, and factors which affect the rate of transport of DCH energy to the upper containment. In addition, DCH loads can be aggravated by rapid blowdown of the primary system, co-dispersal of moderate quantities of water with the debris, and quenching of de-entrained debris in water; these factors act by increasing steam flows which, in turn, accelerates energy transport. It may be noted that containment-threatening loads were calculated for a substantial portion of the scenarios treated for some of the plants considered
Calculation and measurement of space charge in MV-size xxtruded cables systems under load conditions
Morshuis, P.H.F.; Bodega, R.; Fabiani, D.; Montanari, G.C.; Dissado, L.A.; Smit, J.J.
2007-01-01
A load current in dc high voltage cables results in a temperature drop across the insulation and hence a radial distribution of the insulation conductivity is found. Direct consequence is an accumulation of space charge in the bulk of the nsulation, that may significantly affect its reliability.
DEFF Research Database (Denmark)
Bayat, Mehdi; Andersen, Lars Vabbersgaard; Andersen, Søren
2013-01-01
in ABAQUS by coding input files, utilizing Python and MATLAB. A parametric study is performed to illustrate the effects of model size, soil properties such as permeability, void ratio, Young’s modulus, bulk modulus, and load parameters such as amplitude and frequency. It is found that by increasing the bulk...
Model for calculation of concentration and load on behalf of accidents with radioactive materials
International Nuclear Information System (INIS)
Janssen, L.A.M.; Heugten, W.H.H. van
1987-04-01
In the project 'Information- and calculation-system for disaster combatment', by order of the Dutch government, a demonstration model has been developed for a diagnosis system for accidents. In this demonstration a model is used to calculate the concentration- and dose-distributions caused by incidental emissions of limited time. This model is described in this report. 4 refs.; 2 figs.; 3 tabs
Calculation of fluid (steam) hammer loading to piping systems by the response spectrum method
International Nuclear Information System (INIS)
Krause, G.; Schrader, W.; Leimbach, K.R.
1983-01-01
Today computations of fluid and steam hammer loading to piping systems are usually performed as a time-history analysis in which the transient pressure forces act as external excitations. For practical purposes it is desirable to be able to treat fluid hammer loading using the response spectrum method similarily as loads from external events. Two advantages arise from the use of spectra in the analysis of piping systems subjected to dynamic force excitations. Firstly, the response spectrum method is much less sensitive to model idealization than the time-history method. Secondly, computational efforts are reduced. In this paper the algorithm for the treatment of force excitations through the modal response spectrum method is briefly presented. The effect of the residuum accounting for higher modes which are not part of the modal decomposition is considered. In particular various methods of superposition of the responses of the dynamic forces and of the modes are investigated. Results and comparisons are presented of several response spectrum analyses and time-history analyses. (orig.)
Energy Technology Data Exchange (ETDEWEB)
Hendron, R.; Eastment, M.
2006-08-01
In order to meet whole-house energy savings targets beyond 50% in residential buildings, it will be essential that new technologies and systems approaches be developed to address miscellaneous electric loads (MELs). These MELs are comprised of the small and diverse collection of energy-consuming devices found in homes, including what are commonly known as plug loads (televisions, stereos, microwaves), along with all hard-wired loads that do not fit into other major end-use categories (doorbells, security systems, garage door openers). MELs present special challenges because their purchase and operation are largely under the control of the occupants. If no steps are taken to address MELs, they can constitute 40-50% of the remaining source energy use in homes that achieve 60-70% whole-house energy savings, and this percentage is likely to increase in the future as home electronics become even more sophisticated and their use becomes more widespread. Building America (BA), a U.S. Department of Energy research program that targets 50% energy savings by 2015 and 90% savings by 2025, has begun to identify and develop advanced solutions that can reduce MELs.
International Nuclear Information System (INIS)
Aydogdu, K.
1998-01-01
Nine components determine the moderator-system heat load during full-power operation and during a reactor power transient in a CANDU reactor. The components that contribute to the total moderator-system heat load at any time consist of the heat generated in the calandria tubes, guide tubes and reactivity mechanisms, moderator and reflector; the heat transferred from calandria shell, the inner tubesheets and the fuel channels; and the heat gained from moderator pumps and heat lost from piping. The contributions from each of these components will vary with time during a reactor transient. The sources of heat that arise from the deposition of nuclear energy can be divided into two categories, viz., a) the neutronic component (which is directly proportional to neutronic power), which includes neutron energy absorption, prompt-fission gamma absorption and capture gamma absorption; and b) the fission-product decay-gamma component, which also varies with time after initiation of the transient. An equation was derived to calculate transient heat loads to the moderator. The equation includes two independent variables that are the neutronic power and fission-product decay-gamma power fractions during the transient and a constant term that represents the heat gained from moderator pumps and heat lost from piping. The calculated heat load in the moderator during steady-state full-power operation for a CANDU 6 reactor was compared with available measurements from the Point Lepreau, Wolsong 1 and Gentilly-2 nuclear generating stations. The calculated and measured values were in reasonably good agreement. (author)
International Nuclear Information System (INIS)
Mikhaylov, A.V.; Moryakov, A.V.; Nikitin, A.V.
2012-09-01
The RAPK-7 code was developed to simulate formation of non-irradiated and activated corrosion products, their transport and deposition on inner surfaces of primary components and in primary coolant of water-cooled reactors during their operation on power and after shutdown. The key feature of this code is its particular emphasis on the contamination of circulation loops by radioactive corrosion products of reactor which operates on variable modes. Such reactors typically are: research reactors and their experimental loops, naval nuclear power systems, etc. It's typical for such reactors to have repeated (over the campaign) and frequent variations in power (activating neutron fluxes), thermal-physical, hydrodynamic and other parameters of coolant, intensive water mass exchange between the circulation loop and the pressuriser, etc. The processes of mass-transfer are described by the RAPK-7 code with the use of models similar to those employed by the COTRAN and PACTOLE codes. The circulation circuit is broken down into computation areas. The user will then set the concentrations of water chemistry adjusting additives (alkali, boric acid, ammonia, hydrogen), as well as parameters in each area, such as wall temperature, coolant flow core temperature, pressure, flow rate, velocity, the radial component of coolant flowrate and activating neutron flux density. All the above parameters can be set as time-dependent step functions (bar charts), with independent time steps for each of them. The number of computation areas, the number of time dependencies and the level of detail in their description are limited by computer capabilities only. A 'brake' mode with a single-step change of the required set of parameters is provided to allow for jump-type events, such as replacement of contaminated components with clean ones during core refueling or repairs, emergency injection of boric acid, water mass exchange between the circulation circuit and the pressuriser, etc
Model for calculating shock loading and release paths for multicomponent geologic media
International Nuclear Information System (INIS)
Butkovich, T.R.; Moran, B.; Burton, D.E.
1981-07-01
A model has been devised to calculate shock Hugoniots and release paths off the Hugoniots for multicomponent rocks containing silicate, carbonate, and water. Hugoniot equations of state are constructed from relatively simple measurements of rock properties including bulk density, grain density of the silicate component, and weight fractions of water and carbonate. Release paths off the composite Hugoniot are calculated by mixing release paths off the component Hugoniots according to their weight fractions. If the shock imparts sufficient energy to the component to cause vaporization, a gas equation of state is used to calculate the release paths. For less energetic shocks, the rock component will unload like a solid or liquid, taking into account the irreversible removal of air-filled porosity
International Nuclear Information System (INIS)
Hou Zhijian; Lian Zhiwei; Yao Ye; Yuan Xinjian
2006-01-01
A novel method integrating rough sets (RS) theory and an artificial neural network (ANN) based on data-fusion technique is presented to forecast an air-conditioning load. Data-fusion technique is the process of combining multiple sensors data or related information to estimate or predict entity states. In this paper, RS theory is applied to find relevant factors to the load, which are used as inputs of an artificial neural-network to predict the cooling load. To improve the accuracy and enhance the robustness of load forecasting results, a general load-prediction model, by synthesizing multi-RSAN (MRAN), is presented so as to make full use of redundant information. The optimum principle is employed to deduce the weights of each RSAN model. Actual prediction results from a real air-conditioning system show that, the MRAN forecasting model is better than the individual RSAN and moving average (AMIMA) ones, whose relative error is within 4%. In addition, individual RSAN forecasting results are better than that of ARIMA
Calculation of the Thermal Loading of the Cylinder-Piston Group of the Automobile Engine
Barchenko, F. B.; Bakulin, V. N.
2017-05-01
We propose a mathematical model for calculating thermal loods of parts of the cylinder-piston group of the automobile engine operating under unstable conditions in its complete life cycle. Methods have been described for calculating the boundary conditions to determine the thermal state of the parts of the cylinder-piston group of such an engine with the use of theoretical formulas, empirical and semiempirical relations, and tabulated data. In modeling, we calculated the work of all systems of the engine (pumps, pipelines, heat exchangers) influencing directly or indirectly the thermal state of its cylinder-piston group. The nonstationary thermal state was calculated once in the operating cycle of the engine with the use of the cycle-averaged values of the local heat transfer coefficients and the resulting temperature of the medium. The personal computer counting time for one time step of a transport diesel engine of typical design with a number of units of the order of 500 was 5 s.
Improvement of the skeleton tables for calculation of the critical heat load
International Nuclear Information System (INIS)
Gotovskij, M.A.; Kvetnyj, M.A.
2002-01-01
Paper presents analysis of drawbacks of the skeleton tables of the critical heat flows applied in calculated heat and hydraulic codes. Paper demonstrates the necessity to take account of specific nature of mechanisms of dryout crisis, of boiling crisis at slow mass rates and the range of small underheatings up to temperature of saturation. Attention is drawn to necessity of detailed account of the natural limitations of the application field of the skeleton tables [ru
International Nuclear Information System (INIS)
Ritz, G; Pintsuk, G; Linke, J; Hirai, T; Norajitra, P; Reiser, J; Giniyatulin, R; Makhankov, A; Mazul, I
2009-01-01
Tungsten was selected as armor material for the helium-cooled divertor in future DEMO-type fusion reactors and fusion power plants. After realizing the design and testing of them under cyclic thermal loads of up to ∼14 MW m -2 , the tungsten divertor plasma-facing units were examined by metallography; they revealed failures such as cracks at the thermal loaded and as-machined surfaces, as well as degradation of the brazing layers. Furthermore, in order to optimize the machining processes, the quality of tungsten surfaces prepared by turning, milling and using a diamond cutting wheel were examined. This paper presents a metallographic examination of the tungsten plasma-facing units as well as technical studies and the characterization on machining of tungsten and alternative brazing joints.
Ritz, G.; Hirai, T.; Norajitra, P.; Reiser, J.; Giniyatulin, R.; Makhankov, A.; Mazul, I.; Pintsuk, G.; Linke, J.
2009-12-01
Tungsten was selected as armor material for the helium-cooled divertor in future DEMO-type fusion reactors and fusion power plants. After realizing the design and testing of them under cyclic thermal loads of up to ~14 MW m-2, the tungsten divertor plasma-facing units were examined by metallography; they revealed failures such as cracks at the thermal loaded and as-machined surfaces, as well as degradation of the brazing layers. Furthermore, in order to optimize the machining processes, the quality of tungsten surfaces prepared by turning, milling and using a diamond cutting wheel were examined. This paper presents a metallographic examination of the tungsten plasma-facing units as well as technical studies and the characterization on machining of tungsten and alternative brazing joints.
Nemec, Patrik; Malcho, Milan
2018-06-01
This work deal with experimental measurement and calculation cooling efficiency of the cooling device working with a heat pipe technology. The referred device in the article is cooling device capable transfer high heat fluxes from electric elements to the surrounding. The work contain description, working principle and construction of cooling device. The main factor affected the dissipation of high heat flux from electronic elements through the cooling device to the surrounding is condenser construction, its capacity and option of heat removal. Experimental part describe the measuring method cooling efficiency of the cooling device depending on ambient temperature in range -20 to 40°C and at heat load of electronic components 750 W. Measured results are compared with results calculation based on physical phenomena of boiling, condensation and natural convection heat transfer.
Kosovic, B.; Bryan, G. H.; Haupt, S. E.
2012-12-01
Schwartz et al. (2010) recently reported that the total gross energy-generating offshore wind resource in the United States in waters less than 30m deep is approximately 1000 GW. Estimated offshore generating capacity is thus equivalent to the current generating capacity in the United States. Offshore wind power can therefore play important role in electricity production in the United States. However, most of this resource is located along the East Coast of the United States and in the Gulf of Mexico, areas frequently affected by tropical cyclones including hurricanes. Hurricane strength winds, associated shear and turbulence can affect performance and structural integrity of wind turbines. In a recent study Rose et al. (2012) attempted to estimate the risk to offshore wind turbines from hurricane strength winds over a lifetime of a wind farm (i.e. 20 years). According to Rose et al. turbine tower buckling has been observed in typhoons. They concluded that there is "substantial risk that Category 3 and higher hurricanes can destroy half or more of the turbines at some locations." More robust designs including appropriate controls can mitigate the risk of wind turbine damage. To develop such designs good estimates of turbine loads under hurricane strength winds are essential. We use output from a large-eddy simulation of a hurricane to estimate shear and turbulence intensity over first couple of hundred meters above sea surface. We compute power spectra of three velocity components at several distances from the eye of the hurricane. Based on these spectra analytical spectral forms are developed and included in TurbSim, a stochastic inflow turbulence code developed by the National Renewable Energy Laboratory (NREL, http://wind.nrel.gov/designcodes/preprocessors/turbsim/). TurbSim provides a numerical simulation including bursts of coherent turbulence associated with organized turbulent structures. It can generate realistic flow conditions that an operating turbine
Energy Technology Data Exchange (ETDEWEB)
Moore, Keith; McLaughlin, Brendan M.; Lane, Ian C., E-mail: i.lane@qub.ac.uk [School of Chemistry and Chemical Engineering, Queen’s University Belfast, Stranmillis Road, Belfast BT9 5AG (United Kingdom)
2016-04-14
BaH (and its isotopomers) is an attractive molecular candidate for laser cooling to ultracold temperatures and a potential precursor for the production of ultracold gases of hydrogen and deuterium. The theoretical challenge is to simulate the laser cooling cycle as reliably as possible and this paper addresses the generation of a highly accurate ab initio {sup 2}Σ{sup +} potential for such studies. The performance of various basis sets within the multi-reference configuration-interaction (MRCI) approximation with the Davidson correction is tested and taken to the Complete Basis Set (CBS) limit. It is shown that the calculated molecular constants using a 46 electron effective core-potential and even-tempered augmented polarized core-valence basis sets (aug-pCVnZ-PP, n = 4 and 5) but only including three active electrons in the MRCI calculation are in excellent agreement with the available experimental values. The predicted dissociation energy D{sub e} for the X{sup 2}Σ{sup +} state (extrapolated to the CBS limit) is 16 895.12 cm{sup −1} (2.094 eV), which agrees within 0.1% of a revised experimental value of <16 910.6 cm{sup −1}, while the calculated r{sub e} is within 0.03 pm of the experimental result.
Shyam, Sangeetha; Wai, Tony Ng Kock; Arshad, Fatimah
2012-01-01
This paper outlines the methodology to add glycaemic index (GI) and glycaemic load (GL) functionality to food DietPLUS, a Microsoft Excel-based Malaysian food composition database and diet intake calculator. Locally determined GI values and published international GI databases were used as the source of GI values. Previously published methodology for GI value assignment was modified to add GI and GL calculators to the database. Two popular local low GI foods were added to the DietPLUS database, bringing up the total number of foods in the database to 838 foods. Overall, in relation to the 539 major carbohydrate foods in the Malaysian Food Composition Database, 243 (45%) food items had local Malaysian values or were directly matched to International GI database and another 180 (33%) of the foods were linked to closely-related foods in the GI databases used. The mean ± SD dietary GI and GL of the dietary intake of 63 women with previous gestational diabetes mellitus, calculated using DietPLUS version3 were, 62 ± 6 and 142 ± 45, respectively. These values were comparable to those reported from other local studies. DietPLUS version3, a simple Microsoft Excel-based programme aids calculation of diet GI and GL for Malaysian diets based on food records.
Cretcher, C. K.; Rountredd, R. C.
1980-11-01
Customer Load Management Systems, using off-peak storage and control at the residences, are analyzed to determine their potential for capacity and energy savings by the electric utility. Areas broadly representative of utilities in the regions around Washington, DC and Albuquerque, NM were of interest. Near optimum tank volumes were determined for both service areas, and charging duration/off-time were identified as having the greatest influence on tank performance. The impacts on utility operations and corresponding utility/customer economics were determined in terms of delta demands used to estimate the utilities' generating capacity differences between the conventional load management, (CLM) direct solar with load management (DSLM), and electric resistive systems. Energy differences are also determined. These capacity and energy deltas are translated into changes in utility costs due to penetration of the CLM or DSLM systems into electric resistive markets in the snapshot years of 1990 and 2000.
International Nuclear Information System (INIS)
Fanning, D.N.
1978-04-01
A computer program is described for calculating the equivalent nodal loads resulting from distributed loads on a three-dimensional finite-element model. Included is a listing of the computer program, a description of the input data, and an example of the output
Energy Technology Data Exchange (ETDEWEB)
Heselhaus, A.
1997-05-01
In this work a hybrid program system consisting of a 3D finite-volume Navier-Stokes flow solver and a 3D finite-element heat conduction solver has been developed. It enables the coupled calculation of structure temperatures in diabatic solid/fluid configurations. The grids of both the finite element and the finite volume computational domain may be completely independent. The coupled program fully resolves the thermal interaction between heat transfer and the resulting material temperatures. The developed coupling algorithm is numerically stable, conservative and works without the need to define ambient temperatures in the flowfield. This allows for the simulation of any solid/fluid configuration. When simulating combined blade/endwall cooling or filmcooling, only a coupled procedure is capable to completely account for the interaction between all relevant thermal parameters. It is found that the coupled calculation of convective cooling in a realistic guide vane leads locally to 45 K higher and 107 K lower blade temperatures than the uncoupled calculation. This shows that accounting for the thermal interaction between the flow and the structure offers both potential to save cooling air and a lower margin of safety when designing cooling systems close to the thermal limits of the blade material. (orig.) [Deutsch] Im Rahmen der vorliegenden Arbeit wurde ein Verfahren zur Berechnung der Temperaturverteilung in diabat umstroemten Koerpern entwickelt, bei dem ein 3D-Finite Volumen Navier-Stokes Stroemungsloeser und ein 3D-Finite Elemente Waermeleitungsloeser zu einem hybriden Programmsystem gekoppelt werden. Dabei besteht die Moeglichkeit, voellig unabhaengige Rechennetze fuer Stroemung und Struktur zu verwenden. Mit dem gekoppelten Verfahren kann die Wechselwirkung zwischen resultierenden Materialtemperaturen und dem davon rueck-beeinflussten Waermeuebergang beruecksichtigt werden. Weiterhin ist der hier entwickelte, stabile und konservative Kopplungsalgorithmus nicht
Energy Technology Data Exchange (ETDEWEB)
Weissglas, P [The Swedish State Power Board, Stockholm (Sweden)
1960-11-15
The purpose of the present study was to evaluate theoretically the effect of coolant boiling and subsequent void formation in a pressurized D{sub 2}O moderated and cooled reactor. The fuel rods were arranged in a cluster geometry and clad in Zr-2. The coolant was separated from the moderator by a Zr-2 shroud. In this geometry the following problems have been given special attention: l) calculation of the effective resonance integral, 2) thermal disadvantage factors, 3) fast fission effects, 4) leakage effects, 5) changes in epithermal absorption. No account has up to now been taken of the variation of these effects with position in the reactor and burnup. Some comparisons of the theoretical methods and measurements have been attempted. It is concluded that at the present time it is not possible to calculate the void coefficient with any accuracy but it may be possible to give an upper limit from theoretical consideration.
International Nuclear Information System (INIS)
Marcinkiewicz, Jerzy; Adamowski, Adam; Lewandowski, Mariusz
2008-01-01
Mechanical loadings on pipe systems caused by water hammer (hydraulic transients) belong to the most important and most difficult to calculate design loadings in nuclear power plants. The most common procedure in Sweden is to calculate the water hammer loadings on pipe segments, according to the classical one-dimensional (1D) theory of liquid transient flow in a pipeline, and then transfer the results to strength analyses of pipeline structure. This procedure assumes that there is quasi-steady respond of the pipeline structure to pressure surges-no dynamic interaction between the fluid and the pipeline construction. The hydraulic loadings are calculated with 1D so-called 'network' programs. Commonly used in Sweden are Relap5, Drako and Flowmaster2-all using quasi-steady wall friction model. As a third party accredited inspection body Inspecta Nuclear AB reviews calculations of water hammer loadings. The presented work shall be seen as an attempt to illustrate ability of Relap5, Flowmaster2 and Drako programs to calculate the water hammer loadings. A special attention was paid to using of Relap5 for calculation of water hammer pressure surges and forces (including some aspects of influence of Courant number on the calculation results) and also the importance of considering the dynamic (or unsteady) friction models. The calculations are compared with experimental results. The experiments have been conducted at a test rig designed and constructed at the Szewalski Institute of Fluid Flow Machinery of the Polish Academy of Sciences (IMP PAN) in Gdansk, Poland. The analyses show quite small differences between pressures and forces calculated with Relap5, Flowmaster2 and Drako (the differences regard mainly damping of pressure waves). The comparison of calculated and measured pressures and also a force acting on a pre-defined pipe segment shows significant differences. It is shown that the differences can be reduced by using unsteady friction models in calculations
Calculation of deuteron interactions within micro-cracks of a D2 loaded lattice at room temperature
International Nuclear Information System (INIS)
Fulvio, F.
2007-01-01
We have analyzed the possibility that the coefficient of lattice deformation, linked to the formation of micro-cracks at room temperature and low energies, could influence the process of fusion. The calculated probability of fusion within a micro-crack, in the presence of D 2 loading at room temperature and for impure metals, shows moderately elevated values compared with the probability of fusion on the surface. For all the temperatures in the 150-350 K range and for all the energies between 150 and 250 eV, the formation of micro-cracks increases the probability of fusion compared to non-deformed lattices, and also reduces the thickness of the Coulomb barrier. Using the trend of the curve of potential to evaluate the influence of the concentration of impurities, a very high barrier is found within the pure lattice (J ∼ 0.25%). However, under the same thermodynamic conditions, the probability of fusion in the impure metal (J ∼ 0.75%) could be higher, with a total energy less than the potential so that the tunneling effect is amplified. Finally, we have analysed the influence of forced D 2 loading on the process. (author)
International Nuclear Information System (INIS)
Vladimir Ya Kumaev; Andrei A Lebezov; Victor V Alexeev
2005-01-01
Full text of publication follows: The report is devoted to the development and application of the two-dimensional MASKA-LM computer code intended for numerical calculations of lead coolant flows, temperatures and transport of impurities in BREST-type reactors of the integral design. The description of heat and mass transfer in liquid metal systems, proceeding in the coolant and at the interface 'coolant - structural materials', is a complex problem involving the joint simulation of thermal-hydraulic, physical and chemical processes in view of the real configuration of the reactor circuit. The report presents the state-of-the-art in the development of the two-dimensional code MASKA-LM and the results of trial calculations of heat and mass transfer in the primary circuit of the lead cooled reactor. The set of governing equations to be solved is based on the porous body model and describes the thermal-hydraulic processes in the reactor as a whole. The numerical method for solution of the governing equations is discussed. To check the code workability and study the technique by the way of solution of a particular task, calculations were performed in reference to the chosen version of the lead cooled BREST reactor under design. The examined domain of the reactor was simulated by a porous body with the parameters corresponding to those of the real reactor medium in terms of heat generation, resistance and the geometry of the hydraulic path of coolant. Analysis of the calculated two-dimensional fields of velocities, pressure and temperatures shows the existence of a complex coolant flow with stagnant and vortex zones. A nonuniform distribution of the coolant flow rate along the core radius was obtained. The results of calculations of the impurity transport of iron, oxygen and magnetite in the primary reactor circuit are discussed as well. The developed code MASKA-LM allows one to evaluate the issue of components of structural materials into coolant as impurities, their
Comparison of MCNPX-C90 and TRIPOLI-4-D for fuel depletion calculations of a Gas-cooled Fast Reactor
International Nuclear Information System (INIS)
Reyes-Ramirez, Ricardo; Martin-del-Campo, Cecilia; Francois, Juan-Luis; Brun, Emeric; Dumonteil, Eric; Malvagi, Fausto
2010-01-01
The Gas-cooled Fast Reactor is one of the reactor concepts selected by the Generation IV International Forum for the next generation of innovative nuclear energy systems. Several fuel design concepts are being investigated. Burnup depletion of mixed fuel of uranium and plutonium, cooled with gas in a fast neutron energy spectrum must be simulated. Various codes are being developed and/or adapted to improve the quality of the results, and also to reduce the computing time required for the simulations. The main objective of this work is to compare the fuel depletion results obtained with MCNPX-CINDER90 code and the new TRIPOLI-4-Depletion code (developed by the Commissariat a l'Energie Atomique) of a fuel design concept for the Gas-cooled Fast Reactor. Calculations were made for an equivalent homogeneous model of fuel rods in a hexagonal mesh assembly. Total reflection conditions were applied on the six lateral faces and the two axial faces of the assembly. The materials used in the fuel assembly are: carbide of uranium and plutonium as fuel, silicon carbide as cladding, and helium gas as coolant. JEFF libraries of effective cross sections were used in both codes. Two methods of burnup step calculations were performed with TRIPOLI-4-D, the Euler and the CSADA, and their results were compared with the MCNPX-CINDER90 CSADA method. A period of 300 days of irradiation time was considered, which was divided into 12 steps. Results of the infinite multiplication factor as function of the irradiation time, and the evolution of the isotope concentrations for a selected group of nuclides were compared. The main conclusion is that very similar results were obtained for the three types of depletion calculations which were compared: (1) MCNPX-C90 CSADA; (2) TRIPOLI-4-D CSADA, and (3) TRIPOLI-4-D EULER. The best calculation time was obtained with the TRIPOLI-4-D EULER method, which needed approximately half the time than the other two. In summary, it is sufficiently good to use
International Nuclear Information System (INIS)
Ganzmann, I.; Schulte, C.
2010-01-01
Emergency cooling pumps are essential and indispensable components of the NPP safety philosophy. In case of a loss-of coolant accident solid matter (debris: fibrous insulation material, concrete dust, pigment particles) might be released into the coolant, LHSI (low head safety injection) pumps have to ensure their performance capacity for a certain amount of debris without damage or loss of power. The authors describe the development of a test facility. The LHSI was tested in continuous operation over a time period of 14 days with a debris content of 1500 ppm (90% mineral wool fibers, 3% concrete dust, 3% pigment particles, 4% microporous insulation material). The pump did not show any damage or loss of hydraulic power. Further tests including thermoshock conditions (temperature changes of 160 C) are planned.
Aksenov, Andrey; Malysheva, Anna
2018-03-01
An exact calculation of the heat exchange of evaporative surfaces is possible only if the physical processes of hydrodynamics of two-phase flows are considered in detail. Especially this task is relevant for the design of refrigeration supply systems for high-rise buildings, where powerful refrigeration equipment and branched networks of refrigerants are used. On the basis of experimental studies and developed mathematical model of asymmetric dispersed-annular flow of steam-water flow in horizontal steam-generating pipes, a calculation formula has been obtained for determining the boundaries of the zone of improved heat transfer and the critical value of the heat flux density. A new theoretical approach to the solution of the problem of the flow structure of a two-phase flow is proposed. The applied method of dissipative characteristics of a two-phase flow in pipes and the principle of a minimum rate of entropy increase in stabilized flows made it possible to obtain formulas that directly reflect the influence of the viscous characteristics of the gas and liquid media on their distribution in the flow. The study showed a significant effect of gravitational forces on the nature of the phase distribution in the cross section of the evaporative tubes. At a mass velocity of a two-phase flow less than 700 kg / m2s, the volume content of the liquid phase near the upper outer generating lines of the tube is almost an order of magnitude lower than the lower one. The calculation of the heat transfer crisis in horizontal evaporative tubes is obtained. The calculated dependence is in good agreement with the experimental data of the author and a number of foreign researchers. The formula generalizes the experimental data for pipes with the diameter of 6-40 mm in the pressure of 2-7 MPa.
International Nuclear Information System (INIS)
Watakabe, Tomoyoshi; Wakai, Takashi; Jin, Chuanrong; Usui, Yoshiya; Sakai, Shinkichi; Ooshika, Junji; Tsukimori, Kazuyuki
2015-01-01
For the purpose of confirming failure modes and safety margin, some studies on the ultimate strength of thin-walled piping components for Sodium-cooled Fast Reactors (SFRs) under extreme loading conditions such as large earthquakes have been reported these several years. Nonlinear finite element analysis has been applied in these studies to simulate buckling and yielding with large deformation, whose accuracy is dependent on the element type, the mesh size, the elasto-plastic model and so on. It is important to check the validation of a finite element model for nonlinear analysis especially under extreme loading conditions. This paper presents static and dynamic analyses of a thin-walled elbow with large deformation under large seismic loading, and discusses the validation of the FEA models comparing with experimental results. The finite element analysis models in this study are generated by shell elements for a stainless steel pipe elbow of diameter-to-thickness ratio 59:1 similar to the main pipe of SFRs, which is used for shaking table tests. At first, a static analysis is carried out for an in-plane monotonic bending test, in order to confirm that the shell element is appropriate to the large deformation analysis and the material parameters are proper for the strain level in the experiments. And then, a dynamic in-plane bending test with the maximum acceleration of 11.7G is simulated by the nonlinear FEA with stiffness-proportional damping. The influence of mesh sizes on results is investigated, to determine proper mesh sizes and reduce the computational cost. Finally, comparing the results of the FEM analyses with those of experiments, it is concluded that the appropriately generated FEA models are effective and give accurate results for nonlinear analyses of the thin-walled elbow under large seismic loading. (author)
International Nuclear Information System (INIS)
Forsberg, C.; McDaniel, P.; Zohuri, B.
2015-01-01
Advances in utility natural-gas-fired air-Brayton combed cycle technology is creating the option of coupling salt-, helium-, and sodium-cooled nuclear reactors to Nuclear air-Brayton Combined Cycle (NACC) power systems. NACC may enable a zero-carbon electricity grid and improve nuclear power economics by enabling variable electricity output with base-load nuclear reactor operations. Variable electricity output enables selling more electricity at times of high prices that increases plant revenue. Peak power is achieved using stored heat or auxiliary fuel (natural gas, bio-fuels, hydrogen). A typical NACC cycle includes air compression, heating compressed air using nuclear heat and a heat exchanger, sending air through a turbine to produce electricity, reheating compressed air, sending air through a second turbine, and exhausting to a heat recovery steam generator (HRSG). In the HRSG, warm air produces steam that is used to produce added electricity. For peak power production, auxiliary heat (natural gas, stored heat) is added before the air enters the second turbine to raise air temperatures and power output. Like all combined cycle plants, water cooling requirements are dramatically reduced relative to other power cycles because much of the heat rejection is in the form of hot air. (authors)
International Nuclear Information System (INIS)
Kolahdooz, M.; Abotalebi, A.; Sheikh Aleslam, F.
2011-01-01
The goal of this article is calculation of the electric field at the end of loaded path in solid-state track detectors. For the calculation, Laplace-Equation has been solved numerically. By solving the equation, upon considering a specific potential at the boundary of the region, in addition to calculating the electric field at the end of path, the parameters which are affecting the electric field have also been investigated.
Efficiency of an on-line isotope separator system employing cooled and NaCl-loaded He-jet methods
International Nuclear Information System (INIS)
Aeystoe, J.; Rantala, V.; Valli, K.; Hillebrand, S.; Kortelahti, M.; Eskola, K.; Raunemaa, T.
1976-01-01
A pure helium-jet at liquid nitrogen temperature coupled to a Nielsen type ion source, and a NaCl-loaded helium-jet coupled to a hollow-cathode ion source have been investigated as means to connect a cyclotron target chamber on-line to a mass separator. Technical details and performances of some critical parts of the system are described. Total separation efficiencies measured under various experimental conditions for several nuclides vary between 0.01 and 1.0%. (Auth.)
International Nuclear Information System (INIS)
Guo Chunqiu; Xie Jiachun; Liu Xingmin
2013-01-01
In-pile irradiation and in-situ tritium extraction experiment is one of associated domestic research projects in ITER special program. According to the technical requirements of in-pile irradiation experiment of helium cooled ceramic breeder (ceramic) pebble bed assembly in a research reactor, the feasibility of the design for the in-pile irradiation and in-situ tritium extraction experiment of ceramic pebble bed assembly was evaluated. By conducting thermal-hydraulic design calculation with different in-pile irradiation channels, locations and structure parameters for ceramic pebble bed assembly, a reasonable design scheme of ceramic pebble bed assembly satisfying the design requirements for in-pile irradiation was obtained. (authors)
International Nuclear Information System (INIS)
Wang Jinhua; Huang Yifan; Wu Bin
2013-01-01
The spent fuel of 10 MW High Temperature Gas Cooled Reactor (HTR-10) could be stored in the shielded tank, and the tank is stored in the concrete shielded canister in spent fuel storage room, the residual heat of the spent fuel could be removed by the air. The ability of residual heat removal is analyzed in the paper, and the temperature field is numerically calculated through FEA program ANSYS, the analysis and the calculation are used to validate the safety of the spent fuel and the tank, the ultimate temperature of the spent fuel and the tank should below the safety limit. The calculation shows that the maximum temperature locates in the middle of the fuel pebble bed in the spent fuel tank, and the temperature decreases gradually with radial distance, the temperature in the tank body is evenly distributed, and the temperature in the concrete shielded canister decreases gradually with radial distance. It is feasible to remove the residual heat of the spent fuel storage tank by natural ventilation, in natural ventilation condition, the temperature of the spent fuel and the tank is lower than the temperature limit, which provides theoretical evidence for the choice of the residual heat removal method. (authors)
International Nuclear Information System (INIS)
Poquillon, D.
1997-10-01
Usually, for the integrity assessment of defective components, well established rules are used: global approach to fracture. A more fundamental way to deal with these problems is based on the local approach to fracture. In this study, we choose this way and we perform numerical simulations of intergranular crack initiation and intergranular crack propagation. This type of damage can be find in components of fast breeder reactors in 316 L austenitic stainless steel which operate at high temperatures. This study deals with methods coupling partly the behaviour and the damage for crack growth in specimens submitted to various thermomechanical loadings. A new numerical method based on finite element computations and a damage model relying on quantitative observations of grain boundary damage is proposed. Numerical results of crack initiation and growth are compared with a number of experimental data obtained in previous studies. Creep and creep-fatigue crack growth are studied. Various specimen geometries are considered: compact Tension Specimens and axisymmetric notched bars tested under isothermal (600 deg C) conditions and tubular structures containing a circumferential notch tested under thermal shock. Adaptative re-meshing technique and/or node release technique are used and compared. In order to broaden our knowledge on stress triaxiality effects on creep intergranular damage, new experiments are defined and conducted on sharply notched tubular specimens in torsion. These isothermal (600 deg C) Mode II creep tests reveal severe intergranular damage and creep crack initiation. Calculated damage fields at the crack tip are compared with the experimental observations. The good agreement between calculations and experimental data shows the damage criterion used can improve the accuracy of life prediction of components submitted to intergranular creep damage. (author)
International Nuclear Information System (INIS)
Korik, L.; Burger, R.
1992-01-01
What is the effect of 0.6C (1F) temperature rise across turbines, compressors, or evaporators? Enthalpy charts indicate for every 0.6C (1F) hotter water off the cooling tower will require an additional 2 1/2% more energy cost. Therefore, running 2.2C (4F) warmer due to substandard cooling towers could result in a 10% penalty for overcoming high heads and temperatures. If it costs $1,250,000.00 a year to operate the system, $125,000.00 is the energy penalty for hotter water. This paper investigates extra fuel costs involved in maintaining design electric production with cooling water 0.6C (1F) to 3C (5.5F) hotter than design. If design KWH cannot be maintained, paper will calculate dollar loss of saleable electricity. The presentation will conclude with examining the main causes of deficient cold water production. State-of-the-art upgrading and methodology available to retrofit existing cooling towers to optimize lower cooling water temperatures will be discussed
International Nuclear Information System (INIS)
Macrander, A.T.; Lee, W.K.; Smither, R.K.; Mills, D.M.
1992-01-01
Recent results for the performance of a novel double crystal monochromator subjected to high heat loads on an APS prototype undulator at the Cornell High Energy Synchrotron Source (CHESS) are presented. The monochromator was designed to achieve symmetric diffraction from asymmetric planes to spread out the beam footprint thereby lowering the incident power density. Both crystals had (111) oriented surfaces and were arranged such that the beam was diffracted from the (11 bar 1) planes at 5 KeV. Rocking curves with minimal distortion were obtained at a ring electron current of 100 mA. This corresponded to 380 Watts total power and an average power density of 40 Watts/mm 2 normal to the incident beam. These results are compared to data obtained from the same crystals in the standard geometry (diffracting planes parallel to surface). The footprint area in the inclined case was three times that of the standard case. We also obtained rocking curve data for the (333) reflection at 15 KeV for both standard and inclined cases, and these data also showed a minimal distortion only for the inclined case. In addition, thermal data were obtained via infrared pyrometry. Liquid gallium flow rates of up to 2 gallons per minute were investigated. The diffraction data revealed a dramatically improved performance for the inclined crystal case
Energy Technology Data Exchange (ETDEWEB)
Jordan, K. A.; Schubring, D. [Univ. of Florida, Florida (United States); Girardin, G.; Pautz, A. [Swiss Federal Institute of Technology, Zuerich (Switzerland)
2013-07-01
domains will be expanded and the validation base of commonlyused calculation methods will be expanded to cover a new range of research reactor types. From a practical perspective, CROCUS and the UFTR will have fully validated reactor dynamic and transient models for dynamic and accident analysis. With these validated models, both facilities will have improved capabilities and flexibility for extended operations in the future. CROCUS and the UFTR will be able to make future reactor modifications with reduced regulatory resistance. A feasibility analysis of future power uprates at these facilities will also result.
International Nuclear Information System (INIS)
Jordan, K. A.; Schubring, D.; Girardin, G.; Pautz, A.
2013-01-01
domains will be expanded and the validation base of commonlyused calculation methods will be expanded to cover a new range of research reactor types. From a practical perspective, CROCUS and the UFTR will have fully validated reactor dynamic and transient models for dynamic and accident analysis. With these validated models, both facilities will have improved capabilities and flexibility for extended operations in the future. CROCUS and the UFTR will be able to make future reactor modifications with reduced regulatory resistance. A feasibility analysis of future power uprates at these facilities will also result
Dyachenko, Leonid K.; Benin, Andrey V.
2017-06-01
When the high-speed railway traffic is being organized, it becomes necessary to elaborate bridge design standards for high-speed railways (HSR). Methodology of studying the issues of HSR bridge design is based on the comprehensive analysis of domestic research as well as international experience in design, construction and operation of high-speed railways. Serious requirements are imposed on the HSR artificial structures, which raise a number of scientific tasks associated mainly with the issues of the dynamic interaction of the rolling stock and the bridge elements. To ensure safety of traffic and reliability of bridges during the whole period of operation one needs to resolve the dynamic problems of various types of high-speed trains moving along the structures. The article analyses dependences of the magnitude of inertial response on the external stress parameters and proposes a simplified method of determination of the dynamic live load factor caused by the passage of high-speed trains. The usefulness of the given research arises from the reduction of complexity of the complicated dynamic calculations needed to describe a high-speed train travelling along the artificial structures.
Directory of Open Access Journals (Sweden)
N. J. Milardovich
2014-10-01
Full Text Available A numerical investigation on the harmonic disturbances in low-voltage cables feeding large LED loads is reported. A frequency domain analysis on several commercially-available LEDs was performed to investigate the signature of the harmonic current injected into the power system. Four-core cables and four single-core cable arrangements (three phases and neutral of small, medium, and large conductor cross sections, with the neutral conductor cross section approximately equal to the half of the phase conductors, were examined. The cables were modelled by using electromagnetic finite-element analysis software. High harmonic power losses (up to 2.5 times the value corresponding to an undistorted current of the same rms value of the first harmonic of the LED current were found. A generalized ampacity model was employed for re-rating the cables. It was found that the cross section of the neutral conductor plays an important role in the derating of the cable ampacity due to the presence of a high-level of triplen harmonics in the distorted current. The ampacity of the cables should be derated by about 40 %, almost independent of the conductor cross sections. The calculation have shown that an incoming widespread use of LED lamps in lighting could create significant additional harmonic losses in the supplying low-voltage lines, and thus more severely harmonic emission limits should be defined for LED lamps.
Directory of Open Access Journals (Sweden)
Dyachenko Leonid K.
2017-06-01
Full Text Available When the high-speed railway traffic is being organized, it becomes necessary to elaborate bridge design standards for high-speed railways (HSR. Methodology of studying the issues of HSR bridge design is based on the comprehensive analysis of domestic research as well as international experience in design, construction and operation of high-speed railways. Serious requirements are imposed on the HSR artificial structures, which raise a number of scientific tasks associated mainly with the issues of the dynamic interaction of the rolling stock and the bridge elements. To ensure safety of traffic and reliability of bridges during the whole period of operation one needs to resolve the dynamic problems of various types of high-speed trains moving along the structures. The article analyses dependences of the magnitude of inertial response on the external stress parameters and proposes a simplified method of determination of the dynamic live load factor caused by the passage of high-speed trains. The usefulness of the given research arises from the reduction of complexity of the complicated dynamic calculations needed to describe a high-speed train travelling along the artificial structures.
Dai, Aiquan; Li, Keqiang; Ding, Dongsheng; Li, Yan; Liang, Shengkang; Li, Yanbin; Su, Ying; Wang, Xiulin
2015-12-01
The equal percent removal (EPR) method, in which pollutant reduction ratio was set as the same in all administrative regions, failed to satisfy the requirement for water quality improvement in the Bohai Sea. Such requirement was imposed by the developed Coastal Pollution Total Load Control Management. The total maximum allocated load (TMAL) of nitrogen pollutants in the sea-sink source regions (SSRs) around the Bohai Rim, which is the maximum pollutant load of every outlet under the limitation of water quality criteria, was estimated by optimization-simulation method (OSM) combined with loop approximation calculation. In OSM, water quality is simulated using a water quality model and pollutant load is calculated with a programming model. The effect of changes in pollutant loads on TMAL was discussed. Results showed that the TMAL of nitrogen pollutants in 34 SSRs was 1.49×105 ton/year. The highest TMAL was observed in summer, whereas the lowest in winter. TMAL was also higher in the Bohai Strait and central Bohai Sea and lower in the inner area of the Liaodong Bay, Bohai Bay and Laizhou Bay. In loop approximation calculation, the TMAL obtained was considered satisfactory for water quality criteria as fluctuation of concentration response matrix with pollutant loads was eliminated. Results of numerical experiment further showed that water quality improved faster and were more evident under TMAL input than that when using the EPR method
Optimization of cooling strategy and seeding by FBRM analysis of batch crystallization
Zhang, Dejiang; Liu, Lande; Xu, Shijie; Du, Shichao; Dong, Weibing; Gong, Junbo
2018-03-01
A method is presented for optimizing the cooling strategy and seed loading simultaneously. Focused beam reflectance measurement (FBRM) was used to determine the approximating optimal cooling profile. Using these results in conjunction with constant growth rate assumption, modified Mullin-Nyvlt trajectory could be calculated. This trajectory could suppress secondary nucleation and has the potential to control product's polymorph distribution. Comparing with linear and two step cooling, modified Mullin-Nyvlt trajectory have a larger size distribution and a better morphology. Based on the calculating results, the optimized seed loading policy was also developed. This policy could be useful for guiding the batch crystallization process.
Energy Technology Data Exchange (ETDEWEB)
Kouwenhoven, H.J.L. [Frigidarium, Driebergen-Rijsenburg (Netherlands); Huizinga, H.T. [Heat Transfer Holland HTH, Zuidwolde (Netherlands); Bootsveld, N.R. [YNO, Delft (Netherlands); Janssen, M. [Re-gent, Helmond (Netherlands); Uges, P.G.H. [StatiqCooling, Deventer (Netherlands)
2007-04-15
The use of direct and indirect adiabatic cooling, and recently in particular indirect diabatic cooling (dew point cooling) require knowledge of the Mollier diagram. [Dutch] Het gebruik van direct en indirect werkende adiabatische koeling en recentlijk vooral de indirect werkende systemen zoals diabatische koeling (dauwpuntkoeling, al of niet uitgevoerd als statische koeling) vragen om kennis van het Mollierdiagram.
Energy Technology Data Exchange (ETDEWEB)
Gartiser, S; Urich, E
2002-02-01
In Germany about 32 billion m{sup 3}/a cooling water are discharged from industrial plants and power industry. These are conditioned partly with biocides, scaling and corrosion inhibitors. Within the research project the significance of cooling water chemicals was evaluated, identifying the chemicals from product information, calculating their loads from consumption data of more than 180 cooling plants and investigating the basic data needed for an environmental hazard assessment. Additionally the effects of cooling water samples and products were determined in biological test systems. Batch tests were performed under defined conditions in order to measure the inactivation of cooling water biocides. (orig.)
International Nuclear Information System (INIS)
Jamema, S.V.; Deshpande, D.D.; Kirisits, C.; Trnkova, P.; Poetter, R.; Mahantshetty, U.; Shrivastava, S.K.; Dinshaw, K.A.
2008-01-01
In the recent past, inverse planning algorithms were introduced for intracavitary brachytherapy planning (ICBT) for cervical cancer. The loading pattern of these algorithms in comparison with traditional systems may not be similar. The purpose of this study was to objectively compare the loading patterns of traditional systems with the inverse optimization. Based on the outcome of the comparison, an attempt was made to obtain a loading pattern that takes into account the experience made with the inverse optimization
Energy Technology Data Exchange (ETDEWEB)
Petrovic, Bojan [Georgia Inst. of Technology, Atlanta, GA (United States); Maldonado, Ivan [Univ. of Tennessee, Knoxville, TN (United States)
2016-04-14
The research performed in this project addressed the issue of low heavy metal loading and the resulting reduced cycle length with increased refueling frequency, inherent to all FHR designs with solid, non-movable fuel based on TRISO particles. Studies performed here focused on AHTR type of reactor design with plate (“plank”) fuel. Proposal to FY12 NEUP entitled “Fuel and Core Design Options to Overcome the Heavy Metal Loading Limit and Improve Performance and Safety of Liquid Salt Cooled Reactors” was selected for award, and the 3-year project started in August 2012. A 4-month NCE was granted and the project completed on December 31, 2015. The project was performed by Georgia Tech (Prof. Bojan Petrovic, PI) and University of Tennessee (Prof. Ivan Maldonado, Co-PI), with a total funding of $758,000 over 3 years. In addition to two Co-PIs, the project directly engaged 6 graduate students (at doctoral or MS level) and 2 postdoctoral researchers. Additionally, through senior design projects and graduate advanced design projects, another 23 undergraduate and 12 graduate students were exposed to and trained in the salt reactor technology. We see this as one of the important indicators of the project’s success and effectiveness. In the process, 1 journal article was published (with 3 journal articles in preparation), together with 8 peer-reviewed full conference papers, 8 peer-reviewed extended abstracts, as well as 1 doctoral dissertation and 2 master theses. The work included both development of models and methodologies needed to adequately analyze this type of reactor, fuel, and its fuel cycle, as well as extensive analyses and optimization of the fuel and core design.
International Nuclear Information System (INIS)
Petrovic, Bojan; Maldonado, Ivan
2016-01-01
The research performed in this project addressed the issue of low heavy metal loading and the resulting reduced cycle length with increased refueling frequency, inherent to all FHR designs with solid, non-movable fuel based on TRISO particles. Studies performed here focused on AHTR type of reactor design with plate ('plank') fuel. Proposal to FY12 NEUP entitled 'Fuel and Core Design Options to Overcome the Heavy Metal Loading Limit and Improve Performance and Safety of Liquid Salt Cooled Reactors' was selected for award, and the 3-year project started in August 2012. A 4-month NCE was granted and the project completed on December 31, 2015. The project was performed by Georgia Tech (Prof. Bojan Petrovic, PI) and University of Tennessee (Prof. Ivan Maldonado, Co-PI), with a total funding of $758,000 over 3 years. In addition to two Co-PIs, the project directly engaged 6 graduate students (at doctoral or MS level) and 2 postdoctoral researchers. Additionally, through senior design projects and graduate advanced design projects, another 23 undergraduate and 12 graduate students were exposed to and trained in the salt reactor technology. We see this as one of the important indicators of the project's success and effectiveness. In the process, 1 journal article was published (with 3 journal articles in preparation), together with 8 peer-reviewed full conference papers, 8 peer-reviewed extended abstracts, as well as 1 doctoral dissertation and 2 master theses. The work included both development of models and methodologies needed to adequately analyze this type of reactor, fuel, and its fuel cycle, as well as extensive analyses and optimization of the fuel and core design.
International Nuclear Information System (INIS)
Ramadan, W.; Sleva, S.; Dufner, K.; Snow, S.; Kersteter, S.L.
1993-04-01
The report discusses part of EPA's program to identify and characterize emissions sources not currently accounted for by either the existing Aerometric Information Retrieval System (AIRS) or State Implementation Plan (SIP) area source methodologies and to develop appropriate emissions estimation methodologies and emission factors for a group of these source categories. Based on the results of the identification and characterization portions of this research, three source categories were selected for methodology and emission factor development: oil spills, petroleum vessel loading and unloading, and cooling towers. The report describes the category selection process and presents emissions estimation methodologies and emission factor data for the selected source categories. The discussions for each category include general background information, emissions generation activities, pollutants emitted, sources of activity and pollutant data, emissions estimation methodologies and data issues. The information used in these discussions was derived from various sources including available literature, industrial and trade association publications and contracts, experts on the category and activity, and knowledgeable federal and state personnel
International Nuclear Information System (INIS)
Park, Young Sung; Jeong, Ji Hwan; Ahn, Byoung Ha
2014-01-01
Highlights: • New heat pump control method was developed. • Experimental investigation on performance of heat pump with various control method. • New control method appeared to improve the stability of indoor air temperature. • New control method appeared to have a potential to reduce power consumption. - Abstract: The control systems of conventional heat pumps have an input of refrigerant temperature at the evaporator outlet to maintain superheat at proper level. In order to develop a control method that can be used to achieve better indoor thermal comfort and energy efficiency at a low cooling load condition than the current control method, a new method of the evaporation pressure control based on the evaporator outlet pressure reading (EPCP) was developed. The changes in the stability of indoor air temperature and power consumption were measured while changing the compressor frequency in accordance with the new control method. Compared with the evaporation pressure control based on the evaporator outlet temperature reading, the EPCP control method appeared to improve the stability of room air temperature or occupant thermal comfort significantly
Cooling Characteristic Analysis of Transformer's Radiator
International Nuclear Information System (INIS)
Kim, Hyun Jae; Yang, Si Won; Kim, Won Seok; Kweon, Ki Yeoung; Lee, Min Jea
2007-01-01
A transformer is a device that changes the current and voltage by electricity induced between coil and core steel, and it is composed of metals and insulating materials. In the core of the transformer, the thermal load is generated by electric loss and the high temperature can make the break of insulating. So we must cool down the temperature of transformer by external radiators. According to cooling fan's usage, there are two cooling types, OA(Oil Natural Air Natural) and FA(Oil Natural Air Forced). For this study , we used Fluent 6.2 and analyzed the cooling characteristic of radiator. we calculated 1-fin of detail modeling that is similar to honeycomb structure and multi-fin(18-fin) calculation for OA and FA types. For the sensitivity study, we have different positions(side, under) of cooling fans for forced convection of FA type. The calculation results were compared with the measurement data which obtained from 135.45/69kV ultra transformer flowrate and temperature test. The aim of the study is to assess the Fluent code prediction on the radiator calculation and to use the data for optimizing transformer radiator design
Energy Technology Data Exchange (ETDEWEB)
Illing, Bjoern
2014-09-08
Dominated by the energy policy the decentralized German energy market is changing. One mature target of the government is to increase the contribution of renewable generation to the gross electricity consumption. In order to achieve this target disadvantages like an increased need for capacity management occurs. Load reduction and variable grid fees offer the grid operator solutions to realize capacity management by influencing the load profile. The evolution of the current grid fees towards more causality is required to adapt these approaches. Two calculation approaches are developed in this assignment. On the one hand multivariable grid fees keeping the current components demand and energy charge. Additional to the grid costs grid load dependent parameters like the amount of decentralized feed-ins, time and local circumstances as well as grid capacities are considered. On the other hand the grid fee flat-rate which represents a demand based model on a monthly level. Both approaches are designed to meet the criteria for future grid fees. By means of a case study the effects of the grid fees on the load profile at the low voltage grid is simulated. Thereby the consumption is represented by different behaviour models and the results are scaled at the benchmark grid area. The resulting load curve is analyzed concerning the effects of peak load reduction as well as the integration of renewable energy sources. Additionally the combined effect of grid fees and electricity tariffs is evaluated. Finally the work discusses the launching of grid fees in the tense atmosphere of politics, legislation and grid operation. Results of this work are two calculation approaches designed for grid operators to define the grid fees. Multivariable grid fees are based on the current calculation scheme. Hereby demand and energy charges are weighted by time, locational and load related dependencies. The grid fee flat-rate defines a limitation in demand extraction. Different demand levels
Directory of Open Access Journals (Sweden)
Kukhar Volodymir
2018-01-01
Full Text Available This paper presents the results of experimental studies of load characteristic changes during the upsetting of high billets with the upsetting ratio (height to diameter ratio from 3.0 to 6.0, which is followed by buckling. Such pass is an effective way of preforming the workpiece for production of forgings with a bended axis or dual forming, and belongs to impression-free (dieless operation of bulk forming. Based on the experimental data analysis, an engineering method for calculation of workpiece pre-forming load as a maximum buckling force has been developed. The analysis of the obtained data confirmed the possibility of performing of this pre-forming operation on the main forging equipment, since the load of shaping by buckling does not exceed the load of the dieforging.
Kukhar, Volodymir; Artiukh, Victor; Prysiazhnyi, Andrii; Pustovgar, Andrey
2018-03-01
This paper presents the results of experimental studies of load characteristic changes during the upsetting of high billets with the upsetting ratio (height to diameter ratio) from 3.0 to 6.0, which is followed by buckling. Such pass is an effective way of preforming the workpiece for production of forgings with a bended axis or dual forming, and belongs to impression-free (dieless) operation of bulk forming. Based on the experimental data analysis, an engineering method for calculation of workpiece pre-forming load as a maximum buckling force has been developed. The analysis of the obtained data confirmed the possibility of performing of this pre-forming operation on the main forging equipment, since the load of shaping by buckling does not exceed the load of the dieforging.
International Nuclear Information System (INIS)
Moeller, S.P.
1994-01-01
After an introduction to the general concepts of cooling of charged particle beams, some specific cooling methods are discussed, namely stochastic, electron and laser cooling. The treatment concentrates on the physical ideas of the cooling methods and only very crude derivations of cooling times are given. At the end three other proposed cooling schemes are briefly discussed. (orig.)
International Nuclear Information System (INIS)
Bond, J.R.; Wilson, J.R.
1984-01-01
In theories of galaxy formation with a damping cut-off in the density fluctuation spectrum, the first non-linear structures to form are Zeldovich pancakes in which dissipation separates gas from any collisionless dark matter then present. One-dimensional numerical simulations of the collapse, shock heating, and subsequent thermal evolution of pancakes are described. Neutrinos (or any other cool collisionless particles) are followed by direct N-body methods and the gas by Eulerian hydrodynamics with conduction as well as cooling included. It is found that the pressure is relatively uniform within the shocked region and approximately equals the instantaneous ram pressure acting at the shock front. An analytic theory based upon this result accurately describes the numerical calculations. (author)
Specific cooling capacity of liquid nitrogen
Kilgore, R. A.; Adcock, J. B.
1977-01-01
The assumed cooling process and the method used to calculate the specific cooling capacity of liquid nitrogen are described, and the simple equation fitted to the calculated specific cooling capacity data, together with the graphical form calculated values of the specific cooling capacity of nitrogen for stagnation temperatures from saturation to 350 K and stagnation pressures from 1 to 10 atmospheres, are given.
Cooling concepts for HTS components
International Nuclear Information System (INIS)
Binneberg, A.; Buschmann, H.; Neubert, J.
1993-01-01
HTS components require that low-cost, reliable cooling systems be used. There are no general solutions to such systems. Any cooling concept has to be tailored to the specific requirements of a system. The following has to he taken into consideration when designing cooling concepts: - cooling temperature - constancy and controllability of the cooling temperature - cooling load and refrigerating capacity - continuous or discontinuous mode - degree of automation - full serviceability or availability before evacuation -malfunctions caused by microphonic, thermal or electromagnetic effects -stationary or mobile application - investment and operating costs (orig.)
International Nuclear Information System (INIS)
Jang, Hwan Hak; Jeong, Seong Beom; Park, Gyung Jin
2012-01-01
A shape optimization is proposed to obtain the desired final shape of forming and forging products in the manufacturing process. The final shape of a forming product depends on the shape parameters of the initial blank shape. The final shape of a forging product depends on the shape parameters of the billet shape. Shape optimization can be used to determine the shape of the blank and billet to obtain the appropriate final forming and forging products. The equivalent static loads method for non linear static response structural optimization (ESLSO) is used to perform metal forming and forging optimization since nonlinear dynamic analysis is required. Stress equivalent static loads (stress ESLs) are newly defined using a virtual model by redefining the value of the material properties. The examples in this paper show that optimization using the stress ESLs is quite useful and the final shapes of a forming and forging products are identical to the desired shapes
Energy Technology Data Exchange (ETDEWEB)
Trzcinski, A.; Zwieglinski, B. [Soltan Inst. for Nuclear Studies, Warsaw (Poland); Lynen, U. [Gesellschaft fuer Schwerionenforschung mbH, Darmstadt (Germany); Pochodzalla, J. [Max-Planck-Institut fuer Kernphysik, Heidelberg (Germany)
1998-10-01
This paper reports on a Monte-Carlo program, MSX, developed to evaluate the performance of large-volume, Gd-loaded liquid scintillation detectors used in neutron multiplicity measurements. The results of simulations are presented for the detector intended to count neutrons emitted by the excited target residue in coincidence with the charged products of the projectile fragmentation following relativistic heavy-ion collisions. The latter products could be detected with the ALADIN magnetic spectrometer at GSI-Darmstadt. (orig.) 61 refs.
On the calculation of dynamic and heat loads on a three-dimensional body in a hypersonic flow
Bocharov, A. N.; Bityurin, V. A.; Evstigneev, N. M.; Fortov, V. E.; Golovin, N. N.; Petrovskiy, V. P.; Ryabkov, O. I.; Teplyakov, I. O.; Shustov, A. A.; Solomonov, Yu S.
2018-01-01
We consider a three-dimensional body in a hypersonic flow at zero angle of attack. Our aim is to estimate heat and aerodynamic loads on specific body elements. We are considering a previously developed code to solve coupled heat- and mass-transfer problem. The change of the surface shape is taken into account by formation of the iterative process for the wall material ablation. The solution is conducted on the multi-graphics-processing-unit (multi-GPU) cluster. Five Mach number points are considered, namely for M = 20-28. For each point we estimate body shape after surface ablation, heat loads on the surface and aerodynamic loads on the whole body and its elements. The latter is done using Gauss-type quadrature on the surface of the body. The comparison of the results for different Mach numbers is performed. We also estimate the efficiency of the Navier-Stokes code on multi-GPU and central processing unit architecture for the coupled heat and mass transfer problem.
International Nuclear Information System (INIS)
Cunningham, R.; Bernardin, J.D.; Simon-Gillo, J.
1997-11-01
This report presents a summary of an experimental investigation of a closed loop air cooling system designed to control the temperature and humidity in the main enclosure of the multiplicity and vertex detector (MVD). Measurements of the cooling air flow rate, the humidity levels inside and outside of the MVD, and the cooling air temperatures were used to assess the performance of the system and to characterize the system limitations and potential assembly problems. The results of the study indicate that several design changes are needed in the final design to meet the temperature and humidity operating requirements. A thorough set of design change recommendations that satisfy these operating criteria completes this report
A temperature rise equation for predicting environmental impact and performance of cooling ponds
Energy Technology Data Exchange (ETDEWEB)
Serag-Eldin, M.A. [American Univ. in Cairo, Cairo (Egypt). Dept. of Mechanical Engineering
2009-07-01
Cooling ponds are used to cool the condenser water used in large central air-conditioning systems. However, larger cooling loads can often increase pond surface evaporation rates. A temperature-rise energy equation was developed to predict temperature rises in cooling ponds subjected to heating loads. The equation was designed to reduce the need for detailed meteorological data as well as to determine the required surface area and depth of the pond for any given design criteria. Energy equations in the presence and absence of cooling loads were subtracted from each other to determine increases in pond temperature resulting from the cooling load. The energy equations include solar radiation, radiation exchange with sky and surroundings, heat convection from the surface, evaporative cooling, heat conducted to the walls, and rate of change of water temperature. Results of the study suggested that the environmental impact and performance of the cooling pond is a function of temperature only. It was concluded that with the aid of the calculated flow field and temperature distribution, the method can be used to position sprays in order to produce near-uniform pond temperatures. 10 refs., 12 figs.
Energy Technology Data Exchange (ETDEWEB)
Magan Romero, M.; Sordo Balbin, F.; Domingo, S.; Bermejo, J.; Perlado, J. M.
2010-07-01
In this document is simulated the tantalum water cooling, that is going to be used in the ESS-Bilbao, using fluent. The target mesh, the models used and the options choices are displayed. At the end, the results and design recommendations are analyzed.
International Nuclear Information System (INIS)
Jordanova, J.; Poitevin, Y.; Li Puma, A.; Kirov, N.
2003-01-01
The paper summarizes the main results of the initial three-dimensional radiation transport analysis of the EU water-cooled lithium-lead test blanket module performed using the Monte Carlo code MCNP. Estimates of tritium production rate, nuclear energy deposition and cumulative fluence effects such as radiation damage through atomic displacement and production of He and H are presented. (author)
International Nuclear Information System (INIS)
Apostolov, T.; Ivanov, K.; Prodanova, R.; Manolova, M.; Petrova, T.; Alekova, G.
1993-01-01
Two directions for investigations are suggested: 1) Analysis and evaluation of the real loading patterns and operational regimes for Kozloduy NPP WWER-440 and WWER-1000 in the frame of the recent safety criteria and nuclear power plant operating limits. 2) Development of modern code system for WWER type reactor core analysis with advanced features: new design and materials for fuel and control rods, increasing the fuel enrichment, using the integral and discrete burnable absorbers etc. The fuel technology design evolution maximizes the fuel utilization efficiency, improves operation performance and enhances safety margins. By the joint efforts of specialists from INRNE, Sofia (BG) and KAB, Berlin (GE), the codes NESSEL-IV-EC, PYTHIA and DERAB have been developed and verified. In the frame of the PHARE programme the joint project ASPERCA has been proposed intended for reactor physics calculations with PHYBER-WWER code for safety enhancement and operation reliability improvement. In-core fuel management benchmarks for 4 cycles of unit 2 (WWER-440) and 2 cycles of unit 5 (WWER-1000) have been performed. The coordination of burnable absorber design implementation, low leakage loadings usage, reloading enrichment increase and steel content reduction in the core have made the reactor core analysis more demanding and the definition of loading patterns - more difficult. This complexity requires routine use of three-dimensional fast accurate core model with extended and updated cross section libraries. To meet the needs of WWER advanced loading patterns and in-core fuel management improvements the HEXANES code systems is being developed and qualified. Some test calculations have been carried out by the HEXANES code system investigating the influence of Gd in the fuel on the main reactor physics parameters. For reevaluation of the core safety-related design limits forming the basis of licensing procedure, the code DYN3D/M2 is used. 16 refs., 3 figs. (author)
Beam-envelope calculations of space-charge loaded beams in MeV dc ion-implantation facilities
International Nuclear Information System (INIS)
Urbanus, W.H.; Bannenberg, J.G.; Doorn, S.; Saris, F.W.; Koudijs, R.; Dubbelman, P.; Koelewijn, W.
1989-01-01
MeV dc ion accelerators are being developed that can deliver a beam current up to several hundred micro-amperes. At the low-energy part of the accelerator, the beam transport is space-charge dominated rather than emittance dominated. A system of differential equations has been derived, based on the Kapchinski-Vladimirski equations, which describe the envelope of a space-charge loaded ion beam, taking a longitudinal electrical field in an accelerating tube into account. The equations have been used to design the accelerator of a high-current 1 MV heavy-ion implantation facility. Furthermore, the design of a 2 MV accelerator is presented, which is used for analyzing techniques such as RBS and PIXE. Both facilities are based on single-ended Van de Graaff accelerators. (orig.)
International Nuclear Information System (INIS)
Kuznetsov, D.V.; Kormilitsyn, V.M.; Proskuryakov, K.N.
2010-01-01
Calculation results of acoustic parameters fluctuations in low-pressure regenerative heating system of NPP with WWER-1000 type reactor were presented. The spectral structure of acoustic fluctuations was shown to depend on configuration of secondary circuit equipment, its geometrical sizes and operation mode. Estimations of natural oscillations frequencies of working medium pressure in the secondary circuit equipment were resulted. The developed calculation methods and algorithms are intended for revealing and prevention of initiation conditions of vibrations resonances in elements of the secondary circuit equipment with acoustic oscillations in working medium, both under operating conditions and in the design stage of the second circuit of NPP with WWER-1000 type reactor. Analysis of pass-band dependence on operation mode was carried out to solve the given problem [ru
Directory of Open Access Journals (Sweden)
Muharrem Imal
2015-09-01
Full Text Available Increasing attention has been given to energy utilization in Turkey. In this report, we present an energy efficiency evaluation and economic feasibility analysis of a geothermal heating and cooling system (GSHP and a mechanical compression water chiller system (ACHP to improve the energy utilization efﬁciency and reduce the primary energy demand for industrial use. Analyses of a mechanical water chiller unit, GSW 180, and geothermal heating and cooling system, EAR 431 SK, were conducted in experimental working areas of the office buildings in a cigarette factory in Mersin, Turkey. The heating and cooling loads of the cigarette factory building were calculated, and actual thermal data were collected and analyzed. To calculate these loads, the cooling load temperature difference method was used. It was concluded that the geothermal heating and cooling system was more useful and productive and provides substantial economic beneﬁts.
Energy Technology Data Exchange (ETDEWEB)
Dunn, W.N. [Sandia National Labs., Albuquerque, NM (United States). Mechanical and Thermal Environments Dept.
1998-03-01
LUG and Sway brace ANalysis (LUGSAN) II is an analysis and database computer program that is designed to calculate store lug and sway brace loads for aircraft captive carriage. LUGSAN II combines the rigid body dynamics code, SWAY85, with a Macintosh Hypercard database to function both as an analysis and archival system. This report describes the LUGSAN II application program, which operates on the Macintosh System (Hypercard 2.2 or later) and includes function descriptions, layout examples, and sample sessions. Although this report is primarily a user`s manual, a brief overview of the LUGSAN II computer code is included with suggested resources for programmers.
International Nuclear Information System (INIS)
Vrban, B.; Lueley, J.; Farkas, G.; Hascik, J.; Hinca, R.; Petriska, M.; Slugen, V.
2012-01-01
The purpose of the analysis was the determination of critical H_3BO_3 concentrations for the first fuel loading into the reactor core of MO34 units using 2"n"d generation fuel during the first start-up of new unit using calculation code MCNP 1.60. H_3BO_3 concentrations were computed for the given temperature of the primary circuit and position of the 6"t"h safety control rod group. Because of the very first start-up of these units, detailed analyses of active-core parameters are required by National Regulatory Authority and needed for safe operation of nuclear facility. (authors)
Energy Technology Data Exchange (ETDEWEB)
Cousineau, Justine E [National Renewable Energy Laboratory (NREL), Golden, CO (United States); Bennion, Kevin S [National Renewable Energy Laboratory (NREL), Golden, CO (United States); Chieduko, Victor [UQM Technologies, Inc.; Lall, Rajiv [UQM Technologies, Inc.; Gilbert, Alan [UQM Technologies, Inc.
2018-05-08
Cooling of electric machines is a key to increasing power density and improving reliability. This paper focuses on the design of a machine using a cooling jacket wrapped around the stator. The thermal contact resistance (TCR) between the electric machine stator and cooling jacket is a significant factor in overall performance and is not well characterized. This interface is typically an interference fit subject to compressive pressure exceeding 5 MPa. An experimental investigation of this interface was carried out using a thermal transmittance setup using pressures between 5 and 10 MPa. The results were compared to currently available models for contact resistance, and one model was adapted for prediction of TCR in future motor designs.
Energy Technology Data Exchange (ETDEWEB)
Boyarinov, V.F.; Davidenko, V.D.; Polismakov, A.A.; Tsybulsky, V.F. [RRC Kurchatov Institute, Moscow (Russian Federation)
2005-07-01
At the present time, the new code system SUHAM-U for calculation of the neutron-physical processes in nuclear reactor core with triangular and square lattices based both on the modern micro-group (about 7000 groups) cross-sections library of code system UNK and on solving the multigroup (up to 89 groups) neutron transport equation by Surface Harmonics Method is elaborated. In this paper the procedure for generation of multigroup cross-sections from micro-group ones for calculation of VVER-1000 reactor core with MOX loading is described. The validation has consisted in computing VVER-1000 fuel assemblies with uranium and MOX fuel and has shown enough high accuracy under corresponding selection of the number and boundaries of the energy groups. This work has been fulfilled in the frame of ISTC project 'System Analyses of Nuclear Safety for VVER Reactors with MOX Fuels'.
International Nuclear Information System (INIS)
Smith, R.E.; Waisman, R.; Hu, M.H.; Frick, T.M.
1995-01-01
A non-linear analysis has been performed to determine relative motions between tubes and tube support plates (TSP) during a steam line break (SLB) event for steam generators. The SLB event results in blowdown of steam and water out of the steam generator. The fluid blowdown generates pressure drops across the TSPS, resulting in out-of-plane motion. The SLB induced pressure loads are calculated with a computer program that uses a drift-flux modeling of the two-phase flow. In order to determine the relative tube/TSP motions, a nonlinear dynamic time-history analysis is performed using a structural model that considers all of the significant component members relative to the tube support system. The dynamic response of the structure to the pressure loads is calculated using a special purpose computer program. This program links the various substructures at common degrees of freedom into a combined mass and stiffness matrix. The program accounts for structural non-linearities, including potential tube and TSP interaction at any given tube position. The program also accounts for structural damping as part of the dynamic response. Incorporating all of the above effects, the equations of motion are solved to give TSP displacements at the reduced set of DOF. Using the displacement results from the dynamic analysis, plate stresses are then calculated using the detailed component models. Displacements form the dynamic analysis are imposed as boundary conditions at the DOF locations, and the finite element program then solves for the overall distorted geometry. Calculations are also performed to assure that assumptions regarding elastic response of the various structural members and support points are valid
International Nuclear Information System (INIS)
Mansfeld, G.
1974-12-01
ZOCO VI is a computer code to investigate the time and space dependent pressure distribution in full pressure containment of water cooled nuclear power reactors following a loss-of-coolant accident, which is caused by the rupture of a main coolant or steam line. ZOCO VI is an improved version of the computer code ZOCO V with enlarged description of condensing events. (orig.) [de
Directory of Open Access Journals (Sweden)
Alessandro Ruggiero
2018-04-01
Full Text Available The hip joint replacement is one of the most successful orthopedic surgical procedures although it involves challenges to overcome. The patient group undergoing total hip arthroplasty now includes younger and more active patients who require a broad range of motion and a longer service lifetime for the replacement joint. It is well known that wear tests have a long duration and they are very expensive, thus studying the effects of geometry, loading, or alignment perturbations may be performed by Finite Element Analysis. The aim of the study was to evaluate total deformation and stress intensity on ultra-high molecular weight polyethylene liner coupled with hard material head during one step. Moving toward in-silico wear assessment of implants, in the presented simulations we used a musculoskeletal multibody model of a human body giving the loading and relative kinematic of the investigated tribo-system during the gait. The analysis compared two frictional conditions -dry and wet and two geometrical cases- with and without radial clearance. The loads and rotations followed the variability of the gait cycle as well as stress/strain acting in the UHWMPE cup. The obtained results allowed collection of the complete stress/strain description of the polyethylene cup during the gait and calculation of the maximum contact pressure on the lateral edge of the insert. The tensional state resulted in being more influenced by the geometrical conditions in terms of radial clearance than by the variation of the friction coefficients due to lubrication phenomena.
Ruggiero, Alessandro; Merola, Massimiliano; Affatato, Saverio
2018-04-09
The hip joint replacement is one of the most successful orthopedic surgical procedures although it involves challenges to overcome. The patient group undergoing total hip arthroplasty now includes younger and more active patients who require a broad range of motion and a longer service lifetime for the replacement joint. It is well known that wear tests have a long duration and they are very expensive, thus studying the effects of geometry, loading, or alignment perturbations may be performed by Finite Element Analysis. The aim of the study was to evaluate total deformation and stress intensity on ultra-high molecular weight polyethylene liner coupled with hard material head during one step. Moving toward in-silico wear assessment of implants, in the presented simulations we used a musculoskeletal multibody model of a human body giving the loading and relative kinematic of the investigated tribo-system during the gait. The analysis compared two frictional conditions -dry and wet and two geometrical cases- with and without radial clearance. The loads and rotations followed the variability of the gait cycle as well as stress/strain acting in the UHWMPE cup. The obtained results allowed collection of the complete stress/strain description of the polyethylene cup during the gait and calculation of the maximum contact pressure on the lateral edge of the insert. The tensional state resulted in being more influenced by the geometrical conditions in terms of radial clearance than by the variation of the friction coefficients due to lubrication phenomena.
CALIOP: a multichannel design code for gas-cooled fast reactors. Code description and user's guide
International Nuclear Information System (INIS)
Thompson, W.I.
1980-10-01
CALIOP is a design code for fluid-cooled reactors composed of parallel fuel tubes in hexagonal or cylindrical ducts. It may be used with gaseous or liquid coolants. It has been used chiefly for design of a helium-cooled fast breeder reactor and has built-in cross section information to permit calculations of fuel loading, breeding ratio, and doubling time. Optional cross-section input allows the code to be used with moderated cores and with other fuels
DEFF Research Database (Denmark)
Mustakallio, Panu; Kosonen, Risto; Melikov, Arsen Krikor
2016-01-01
arrangement and air distribution generated in a room by linear slot diffuser, radial multi-nozzle diffuser and radial swirl induction unit on the cooling power of radiant panels was compared. The impact on the thermal environment was also studied. Measurements were carried out without and with supply air...
Experimental evaluation of cooling efficiency of the high performance cooling device
Nemec, Patrik; Malcho, Milan
2016-06-01
This work deal with experimental evaluation of cooling efficiency of cooling device capable transfer high heat fluxes from electric elements to the surrounding. The work contain description of cooling device, working principle of cooling device, construction of cooling device. Experimental part describe the measuring method of device cooling efficiency evaluation. The work results are presented in graphic visualization of temperature dependence of the contact area surface between cooling device evaporator and electronic components on the loaded heat of electronic components in range from 250 to 740 W and temperature dependence of the loop thermosiphon condenser surface on the loaded heat of electronic components in range from 250 to 740 W.
Experimental evaluation of cooling efficiency of the high performance cooling device
Energy Technology Data Exchange (ETDEWEB)
Nemec, Patrik, E-mail: patrik.nemec@fstroj.uniza.sk; Malcho, Milan, E-mail: milan.malcho@fstroj.uniza.sk [University of Žilina, Faculty of Mechanical Engineering, Department of Power Engineering, Univerzitna 1, 010 26 Žilina (Slovakia)
2016-06-30
This work deal with experimental evaluation of cooling efficiency of cooling device capable transfer high heat fluxes from electric elements to the surrounding. The work contain description of cooling device, working principle of cooling device, construction of cooling device. Experimental part describe the measuring method of device cooling efficiency evaluation. The work results are presented in graphic visualization of temperature dependence of the contact area surface between cooling device evaporator and electronic components on the loaded heat of electronic components in range from 250 to 740 W and temperature dependence of the loop thermosiphon condenser surface on the loaded heat of electronic components in range from 250 to 740 W.
Semioptimal practicable algorithmic cooling
International Nuclear Information System (INIS)
Elias, Yuval; Mor, Tal; Weinstein, Yossi
2011-01-01
Algorithmic cooling (AC) of spins applies entropy manipulation algorithms in open spin systems in order to cool spins far beyond Shannon's entropy bound. Algorithmic cooling of nuclear spins was demonstrated experimentally and may contribute to nuclear magnetic resonance spectroscopy. Several cooling algorithms were suggested in recent years, including practicable algorithmic cooling (PAC) and exhaustive AC. Practicable algorithms have simple implementations, yet their level of cooling is far from optimal; exhaustive algorithms, on the other hand, cool much better, and some even reach (asymptotically) an optimal level of cooling, but they are not practicable. We introduce here semioptimal practicable AC (SOPAC), wherein a few cycles (typically two to six) are performed at each recursive level. Two classes of SOPAC algorithms are proposed and analyzed. Both attain cooling levels significantly better than PAC and are much more efficient than the exhaustive algorithms. These algorithms are shown to bridge the gap between PAC and exhaustive AC. In addition, we calculated the number of spins required by SOPAC in order to purify qubits for quantum computation. As few as 12 and 7 spins are required (in an ideal scenario) to yield a mildly pure spin (60% polarized) from initial polarizations of 1% and 10%, respectively. In the latter case, about five more spins are sufficient to produce a highly pure spin (99.99% polarized), which could be relevant for fault-tolerant quantum computing.
Adsorption Cooling System Using Metal-Impregnated Zeolite-4A
Directory of Open Access Journals (Sweden)
Somsuk Trisupakitti
2016-01-01
Full Text Available The adsorption cooling systems have been developed to replace vapor compression due to their benefits of being environmentally friendly and energy saving. We prepared zeolite-4A and experimental cooling performance test of zeolite-water adsorption system. The adsorption cooling test-rig includes adsorber, evaporator, and condenser which perform in vacuum atmosphere. The maximum and minimum water adsorption capacity of different zeolites and COP were used to assess the performance of the adsorption cooling system. We found that loading zeolite-4A with higher levels of silver and copper increased COP. The Cu6%/zeolite-4A had the highest COP at 0.56 while COP of zeolite-4A alone was 0.38. Calculating the acceleration rate of zeolite-4A when adding 6% of copper would accelerate the COP at 46%.
International Nuclear Information System (INIS)
Boernke, F.
1975-01-01
The need for the use of cooling systems in power plant engineering is dealt with from the point of view of a non-polluting form of energy production. The various cooling system concepts up to the modern natural-draught cooling towers are illustrated by examples. (TK/AK) [de
Project W-320, 241-C-106 sluicing HVAC calculations, Volume 4
Energy Technology Data Exchange (ETDEWEB)
Bailey, J.W.
1998-07-30
This supporting document has been prepared to make the FDNW calculations for Project W-320, readily retrievable. The report contains the following design calculations: Cooling load in pump pit 241-AY-102; Pressure relief seal loop design; Process building piping stress analysis; Exhaust skid maximum allowable leakage criteria; and Recirculation heat, N509 duct requirements.
Simulations of floor cooling system capacity
International Nuclear Information System (INIS)
Odyjas, Andrzej; Górka, Andrzej
2013-01-01
Floor cooling system capacity depends on its physical and operative parameters. Using numerical simulations, it appears that cooling capacity of the system largely depends on the type of cooling loads occurring in the room. In the case of convective cooling loads capacity of the system is small. However, when radiation flux falls directly on the floor the system significantly increases productivity. The article describes the results of numerical simulations which allow to determine system capacity in steady thermal conditions, depending on the type of physical parameters of the system and the type of cooling load occurring in the room. Moreover, the paper sets out the limits of system capacity while maintaining a minimum temperature of the floor surface equal to 20 °C. The results are helpful for designing system capacity in different type of cooling loads and show maximum system capacity in acceptable thermal comfort condition. -- Highlights: ► We have developed numerical model for simulation of floor cooling system. ► We have described floor system capacity depending on its physical parameters. ► We have described floor system capacity depending on type of cooling loads. ► The most important in the obtained cooling capacities is the type of cooling loads. ► The paper sets out the possible maximum cooling floor system capacity
Araque, Oscar; Arzola, Nelson; Hernández, Edgar
2018-04-12
This research deals with the fatigue behavior of butt-welded joints, by considering the geometry and post-welding cooling cycles, as a result of cooling in quiet air and immersed in water. ASTM A-36 HR structural steel was used as the base metal for the shielded metal arc welding (SMAW) process with welding electrode E6013. The welding reinforcement was 1 mm and 3 mm, respectively; axial fatigue tests were carried out to determine the life and behavior in cracks propagation of the tested welded joints, mechanical characterization tests of properties in welded joints such as microhardness, Charpy impact test and metallographic analysis were carried out. The latter were used as input for the analysis by finite elements which influence the initiation and propagation of cracks and the evaluation of stress intensity factors (SIF). The latter led to obtaining the crack propagation rate and the geometric factor. The tested specimens were analyzed, by taking photographs of the cracks at its beginning in order to make a count of the marks at the origin of the crack. From the results obtained and the marks count, the fatigue crack growth rate and the influence of the cooling media on the life of the welded joint are validated, according to the experimental results. It can be concluded that the welded joints with a higher weld reinforcement have a shorter fatigue life. This is due to the stress concentration that occurs in the vicinity of the weld toe.
International Nuclear Information System (INIS)
Chaudhary, V; Wang, Z; Ray, A; Ramanujan, R V; Sridhar, I
2017-01-01
Efficient thermal management and heat recovery devices are of high technological significance for innovative energy conservation solutions. We describe a study of a self-pumping magnetic cooling device, which does not require external energy input, employing Mn–Zn ferrite nanoparticles suspended in water. The device performance depends strongly on magnetic field strength, nanoparticle content in the fluid and heat load temperature. Cooling (Δ T ) by ∼20 °C and ∼28 °C was achieved by the application of 0.3 T magnetic field when the initial temperature of the heat load was 64 °C and 87 °C, respectively. These experiments results were in good agreement with simulations performed with COMSOL Multiphysics. Our system is a self-regulating device; as the heat load increases, the magnetization of the ferrofluid decreases; leading to an increase in the fluid velocity and consequently, faster heat transfer from the heat source to the heat sink. (letter)
International Nuclear Information System (INIS)
Amamoto, Ippei; Kobayashi, Hidekazu; Yokozawa, Takuma; Yamashita, Teruo; Nagai, Takayuki; Kitamura, Naoto; Takebe, Hiromichi; Mitamura, Naoki; Tsuzuki, Tatsuya
2013-01-01
As the part of investigation for immobilization of the sludge as one of the radioactive wastes arising from the treatment of contaminated water at Fukushima Dai-ichi nuclear power plant, applicability of vitrification method has been evaluated as a candidate technique. The aim of this study is to evaluate the influence of NaCl as one of the main constituents of sludge, on glass formation and glass properties. Two kinds of iron phosphate glass (IPG) media in the xFe 2 O 3 -(100-x)P 2 O 5 , with x=30 and 35 (mol%) were chosen and the glass formation, structure and properties including density, coefficient of thermal expansion, glass transition temperature, onset crystallization temperature and chemical durability of NaCl-loaded IPG were studied. The results are summarized as follows. Sodium chloride, NaCl could be loaded into IPG medium as Na 2 O and Cl contents and their loading ratio could be up to 19 and 15 mol%, respectively. Majority of Cl content of raw material NaCl was thought to be volatilized during glass melting. Loading NaCl into IPG induces to de-polymerize glass network of phosphate chains, leads to decrease both glass transition and onset crystallization temperatures, and to increase coefficient of thermal expansion. NaCl-loaded IPG indicated good chemical durability in case of using 35Fe 2 O 3 - 65P 2 O 5 medium. (authors)
International Nuclear Information System (INIS)
Kussmaul, K.; Kobes, E.; Diem, H.; Schrammel, D.; Brosi, S.
1994-01-01
Within the scope of the German HDR safety programme, several tests were carried out to investigate transient pipe loading initiated by a simulated double-ended guillotine break event, and subsequent closure of a feedwater check valve (water hammer, blow-down). Numerical analyses by means of finite element programmes were performed in parallel to the experiments. Using water hammer tests of a DN 425 piping system with predamaged components, the procedure of such analyses will be demonstrated. The results are presented, beginning with structural dynamic calculations of the undamaged piping; followed by coupling of structural dynamics and fracture mechanics computations with simple flaw elements (line spring); and finishing with costly three-dimensional fracture mechanics analyses. A good description of the real piping behaviour can be made by the numerical methods, even in the case of high plastification processes. ((orig.))
1992-12-01
ESDU 92035 provides details of a FORTRAN program that implements the calculation method of ESDU 83004. It allows performance analysis of an existing design, or the design of a bearing dimensions, subject to any space constraint, are recommended. The predicted performance includes the lubricant film thickness under load, its temperature and flow rate, the power loss, and the bearing temperature. Recommendations are also made on surface finish. Warning messages are output in the following cases, for each of which possible remedial actions are suggested: drain or pad temperature too high, churning losses too great, film thickness too small, pad number too high, ratio or inner to outer pad radius too large, flow rate too great, lubricant or pad temperature outside usable range. A lubricant database is provided that may be extended or edited. The program applies to Newtonian lubricants in laminar flow. Worked examples illustrate the use of the program.
National Research Council Canada - National Science Library
Kotlar, Anthony
1999-01-01
.... These calculations give limiting values for projectile muzzle kinetic energy (KE), assuming complete mixing of the liquid additive and the solid propellant This is a worst-case scenario for the new concept to reduce gun barrel heating...
Hybrid Geothermal Heat Pumps for Cooling Telecommunications Data Centers
Energy Technology Data Exchange (ETDEWEB)
Beckers, Koenraad J [National Renewable Energy Laboratory (NREL), Golden, CO (United States); Zurmuhl, David P. [Cornell University; Lukawski, Maciej Z. [Cornell University; Aguirre, Gloria A. [Cornell University; Schnaars, George P. [Cornell University; Anderson, C. Lindsay [Cornell University; Tester, Jefferson W. [Cornell University
2018-02-14
The technical and economic performance of geothermal heat pump (GHP) systems supplying year-round cooling to representative small data centers with cooling loads less than 500 kWth were analyzed and compared to air-source heat pumps (ASHPs). A numerical model was developed in TRNSYS software to simulate the operation of air-source and geothermal heat pumps with and without supplementary air cooled heat exchangers - dry coolers (DCs). The model was validated using data measured at an experimental geothermal system installed in Ithaca, NY, USA. The coefficient of performance (COP) and cooling capacity of the GHPs were calculated over a 20-year lifetime and compared to the performance of ASHPs. The total cost of ownership (TCO) of each of the cooling systems was calculated to assess its economic performance. Both the length of the geothermal borehole heat exchangers (BHEs) and the dry cooler temperature set point were optimized to minimize the TCO of the geothermal systems. Lastly, a preliminary analysis of the performance of geothermal heat pumps for cooling dominated systems was performed for other locations including Dallas, TX, Sacramento, CA, and Minneapolis, MN.
Przybycin, Anna M.; Scheck-Wenderoth, Magdalena; Schneider, Michael
2014-05-01
The North Alpine Foreland Basin is situated in the northern front of the European Alps and extends over parts of France, Switzerland, Germany and Austria. It formed as a wedge shaped depression since the Tertiary in consequence of the Euro - Adriatic continental collision and the Alpine orogeny. The basin is filled with clastic sediments, the Molasse, originating from erosional processes of the Alps and underlain by Mesozoic sedimentary successions and a Paleozoic crystalline crust. For our study we have focused on the German part of the basin. To investigate the deep structure, the isostatic state and the load distribution of this region we have constructed a 3D structural model of the basin and the Alpine area using available depth and thickness maps, regional scale 3D structural models as well as seismic and well data for the sedimentary part. The crust (from the top Paleozoic down to the Moho (Grad et al. 2008)) has been considered as two-parted with a lighter upper crust and a denser lower crust; the partition has been calculated following the approach of isostatic equilibrium of Pratt (1855). By implementing a seismic Lithosphere-Asthenosphere-Boundary (LAB) (Tesauro 2009) the crustal scale model has been extended to the lithospheric-scale. The layer geometry and the assigned bulk densities of this starting model have been constrained by means of 3D gravity modelling (BGI, 2012). Afterwards the 3D load distribution has been calculated using a 3D finite element method. Our results show that the North Alpine Foreland Basin is not isostatically balanced and that the configuration of the crystalline crust strongly controls the gravity field in this area. Furthermore, our results show that the basin area is influenced by varying lateral load differences down to a depth of more than 150 km what allows a first order statement of the required compensating horizontal stress needed to prevent gravitational collapse of the system. BGI (2012). The International
International Nuclear Information System (INIS)
Rollin, Philippe.
1975-01-01
Spray cooling - using water spraying in air - is surveyed as a possible system for make-up (peak clipping in open circuit) or major cooling (in closed circuit) of the cooling water of the condensers in thermal power plants. Indications are given on the experiments made in France and the systems recently developed in USA, questions relating to performance, cost and environmental effects of spray devices are then dealt with [fr
Energy Technology Data Exchange (ETDEWEB)
Ritz, G., E-mail: Guillaume.ritz@gmail.com [CEA, Institut de la Recherche sur la Fusion Magnétique (IRFM), 13108 Saint Paul-lez-Durance (France); Corre, Y., E-mail: Yann.corre@cea.fr [CEA, Institut de la Recherche sur la Fusion Magnétique (IRFM), 13108 Saint Paul-lez-Durance (France); Rault, M.; Missirlian, M. [CEA, Institut de la Recherche sur la Fusion Magnétique (IRFM), 13108 Saint Paul-lez-Durance (France); Portafaix, C. [ITER Organization, Route de Vinon-sur-Verdon, 13115 Saint Paul-lez-Durance (France); Martinez, A.; Ekedahl, A.; Colas, L.; Guilhem, D.; Salami, M.; Loarer, T. [CEA, Institut de la Recherche sur la Fusion Magnétique (IRFM), 13108 Saint Paul-lez-Durance (France)
2013-10-15
Highlights: ► The heat flux generated by radiofrequency (RF) heating was calculated using Tore Supra's heating antennas. ► The highest heat flux value, generated by ions accelerated in RF-rectified sheath potentials, was 5 MW/m{sup 2}. ► The heat flux on the limiters of antennas was in the same order of magnitude as that on the toroidal pumping limiter. -- Abstract: Lower hybrid current drive (LHCD) and ion cyclotron resonance heating (ICRH) are recognized as important auxiliary heating and current drive methods for present and next step fusion devices. However, these radio frequency (RF) systems generate a heat flux up to several MW/m{sup 2} on the RF antennas during plasma operation. This paper focuses on the determination of the heat flux deposited on the lateral protections of the RF antennas in Tore Supra. The heat flux was calculated by finite element method (FEM) using a model of the lateral protection. The FEM calculation was based on surface temperature measurements using infrared cameras monitoring the RF antennas. The heat flux related to the acceleration of electrons in front of the LHCD grills (LHCD active) and to the acceleration of ions in RF-rectified sheath potentials (ICRH active) were calculated. Complementary results on the heat flux related to fast ions (ICRH active with a relatively low magnetic field) are also reported in this paper.
Bovino, S; Bodo, E; Yurtsever, E; Gianturco, F A
2008-06-14
The interaction between the triplet state of the lithium dimer, (7)Li(2), with (4)He is obtained from accurate ab initio calculations where the vibrational dependence of the potential is newly computed. Vibrational quenching dynamics within a coupled-channel quantum treatment is carried out at ultralow energies, and large differences in efficiency as a function of the initial vibrational state of the targets are found as one compares the triplet results with those of the singlet state of the same target.
Winkler, T.; Koettig, T.; van Weelderen, R.; Bremer, J.; ter Brake, H. J. M.
Management of transient heat deposition in superconducting magnets and its extraction from the aforementioned is becoming increasingly important to bring high energy particle accelerator performance to higher beam energies and intensities. Precise knowledge of transient heat deposition phenomena in the magnet cables will permit to push the operation of these magnets as close as possible to their current sharing limit, without unduly provoking magnet quenches. With the prospect of operating the Large Hadron Collider at CERN at higher beam energies and intensities an investigation into the response to transient heat loads of LHC magnets, operating in pressurized superfluid helium, is being performed. The more frequently used approach mimics the cable geometry by resistive wires and uses Joule-heating to deposit energy. Instead, to approximate as closely as possible the real magnet conditions, a novel method for depositing heat in cable stacks made out of superconducting magnet-cables has been developed. The goal is to measure the temperature difference as a function of time between the cable stack and the superfluid helium bath depending on heat load and heat pulse length. The heat generation in the superconducting cable and precise measurement of small temperature differences are major challenges. The functional principle and experimental set-up are presented together with proof of principle measurements.
Response Analysis of an RC Cooling Tower Under Seismic and Windstorm Effects
Directory of Open Access Journals (Sweden)
D. Makovička
2006-01-01
Full Text Available The paper compares the RC structure of a cooling tower unit under seismic loads and under strong wind loads. The calculated values of the envelopes of the displacements and the internal forces due to seismic loading states are compared with the envelopes of the loading states due to the dead, operational and live loads, wind and temperature actions. The seismic effect takes into account the seismic area of ground motion 0.3 g and the ductility properties of a relatively rigid structure. The ductility is assessed as the reduction in seismic load. In this case the actions of wind pressure are higher than the seismicity effect under ductility correction. The seismic effects, taking into account the ductility properties of the structure, are lower than the actions of the wind pressure. The other static loads, especially temperature action due to the environment and surface insulation are very important for the design of the structure.
International Nuclear Information System (INIS)
Fuse, Toshiaki; Tachikawa, Nobuo.
1996-01-01
A cooling tube made of a pure copper is connected to the inner portion of an armour (heat resistant member) made of an anisotropic carbon/carbon composite (CFC) material. The CFC material has a high heat conductivity in longitudinal direction of fibers and has low conductivity in perpendicular thereto. Fibers extending in the armour from a heat receiving surface just above the cooling tube are directly connected to the cooling tube. A portion of the fibers extending from a heat receiving surface other than portions not just above the cooling tube is directly bonded to the cooling tube. Remaining fibers are disposed so as to surround the cooling tube. The armour and the cooling tube are soldered using an active metal flux. With such procedures, high thermal load components for use in a thermonuclear reactor are formed, which are excellent in a heat removing characteristic and hardly causes defects such as crackings and peeling. (I.N.)
Energy Technology Data Exchange (ETDEWEB)
Tollestrup, A.V.; Dugan, G
1983-12-01
Major headings in this review include: proton sources; antiproton production; antiproton sources and Liouville, the role of the Debuncher; transverse stochastic cooling, time domain; the accumulator; frequency domain; pickups and kickers; Fokker-Planck equation; calculation of constants in the Fokker-Planck equation; and beam feedback. (GHT)
Energy Technology Data Exchange (ETDEWEB)
Escarela-Perez, R. [Departamento de Energia, Universidad Autonoma Metropolitana, Av. San Pablo 180, Col. Reynosa, C.P. 02200, Mexico D.F. (Mexico); Kulkarni, S.V. [Electrical Engineering Department, Indian Institute of Technology, Bombay (India); Melgoza, E. [Instituto Tecnologico de Morelia, Av. Tecnologico 1500, Morelia, Mich., C.P. 58120 (Mexico)
2008-11-15
A six-port impedance network for a three-phase transformer is obtained from a 3D time-harmonic finite-element (FE) model. The network model properly captures the eddy current effects of the transformer tank and frame. All theorems and tools of passive linear networks can be used with the multi-port model to simulate several important operating conditions without resorting anymore to computationally expensive 3D FE simulations. The results of the network model are of the same quality as those produced by the FE program. Although the passive network may seem limited by the assumption of linearity, many important transformer operating conditions imply unsaturated states. Single-phase load-loss measurements are employed to demonstrate the effectiveness of the network model and to understand phenomena that could not be explained with conventional equivalent circuits. In addition, formal deduction of novel closed-form formulae is presented for the calculation of the leakage impedance measured at the high and low voltage sides of the transformer. (author)
APS high heat load monochromator
International Nuclear Information System (INIS)
Lee, W.K.; Mills, D.
1993-02-01
This document contains the design specifications of the APS high heat load (HHL) monochromator and associated accessories as of February 1993. It should be noted that work is continuing on many parts of the monochromator including the mechanical design, crystal cooling designs, etc. Where appropriate, we have tried to add supporting documentation, references to published papers, and calculations from which we based our decisions. The underlying philosophy behind performance specifications of this monochromator was to fabricate a device that would be useful to as many APS users as possible, that is, the design should be as generic as possible. In other words, we believe that this design will be capable of operating on both bending magnet and ID beamlines (with the appropriate changes to the cooling and crystals) with both flat and inclined crystal geometries and with a variety of coolants. It was strongly felt that this monochromator should have good energy scanning capabilities over the classical energy range of about 4 to 20 keywith Si (111) crystals. For this reason, a design incorporating one rotation stage to drive both the first and second crystals was considered most promising. Separate rotary stages for the first and second crystals can sometimes provide more flexibility in their capacities to carry heavy loads (for heavily cooled first crystals or sagittal benders of second crystals), but their tuning capabilities were considered inferior to the single axis approach
Energy Technology Data Exchange (ETDEWEB)
Schlicht, Gerhard; Roloff-Bock, Iris; Schenk, Ulrike [AREVA GmbH, Erlangen (Germany)
2013-07-01
Until now the thermal loads for the pressurizer and the spray line were constructed in a very conservative way using abrupt temperature changes. This leads to overestimated thermal loads. To have a better rating of these thermal loads of the pressurizer, it is necessary to describe the phenomena of phase change (boiling and condensation) with sufficient accuracy. For this purpose we have added the phase change phenomena to the fluid code STADRU. This code can analyze time dependent thermal loads in components or systems. Furthermore the temperature course over the wall thickness is determined leading to a realistic description of thermal loads. (orig.)
Aksenov, Andrey; Malysheva, Anna
2018-03-01
The analytical solution of one of the urgent problems of modern hydromechanics and heat engineering about the distribution of gas and liquid phases along the channel cross-section, the thickness of the annular layer and their connection with the mass content of the gas phase in the gas-liquid flow is given in the paper.The analytical method is based on the fundamental laws of theoretical mechanics and thermophysics on the minimum of energy dissipation and the minimum rate of increase in the system entropy, which determine the stability of stationary states and processes. Obtained dependencies disclose the physical laws of the motion of two-phase media and can be used in hydraulic calculations during the design and operation of refrigeration and air conditioning systems.
Directory of Open Access Journals (Sweden)
Maciej STANECKI
2014-12-01
Full Text Available The article will present the role of the humanitarian aid in the process of creating the US foreign policy. The study will examine two interesting case studies: the Polish Medical Aid Project and the creation of the American Research Hospital for Children in Poland. The work will show the most important aspects of the planning and implementation of those initiatives. This approach will be aimed at answering the title question and will try to define the extent to which the humanitarian aid offered to Poland within a certain period was a political calculation. The final analysis of the congressional hearings conducted in 1962 presents and confirms the complexity of the process of helping the “Captive Nations” in Central Eastern Europe.
International Nuclear Information System (INIS)
1999-01-01
The results of testing of equipment at Bohunice NPP and pipeline systems at Unit 3 of Kozloduy NPP (WWER-440 type reactors) are presented in this Final Report. These results side by side with experimental values of natural frequencies and decrements also include experimental data about vibration modes of tested equipment and pipelines. For the first time the results of new calculational-experimental examination of equipment seismic resistance at Unit 2 of Armenian NPP are presented. At Kozloduy NPP direction's request the planed additional tests of some selected items were put off on 1997. Instead of postponed tests we carried out detailed analysis of our past inspections of numerous equipment seismic resistance at the Unit 5 of Kozloduy NPP. Experimental data with results of additional analysis are presented
Directory of Open Access Journals (Sweden)
Aksenov Andrey
2018-01-01
Full Text Available The analytical solution of one of the urgent problems of modern hydromechanics and heat engineering about the distribution of gas and liquid phases along the channel cross-section, the thickness of the annular layer and their connection with the mass content of the gas phase in the gas-liquid flow is given in the paper.The analytical method is based on the fundamental laws of theoretical mechanics and thermophysics on the minimum of energy dissipation and the minimum rate of increase in the system entropy, which determine the stability of stationary states and processes. Obtained dependencies disclose the physical laws of the motion of two-phase media and can be used in hydraulic calculations during the design and operation of refrigeration and air conditioning systems.
DEFF Research Database (Denmark)
Heiselberg, Per Kvols; Kolokotroni, Maria
This report, by venticool, summarises the outcome of the work of the initial working phase of IEA ECB Annex 62 Ventilative Cooling and is based on the findings in the participating countries. It presents a summary of the first official Annex 62 report that describes the state-of-the-art of ventil......This report, by venticool, summarises the outcome of the work of the initial working phase of IEA ECB Annex 62 Ventilative Cooling and is based on the findings in the participating countries. It presents a summary of the first official Annex 62 report that describes the state......-of-the-art of ventilative cooling potentials and limitations, its consideration in current energy performance regulations, available building components and control strategies and analysis methods and tools. In addition, the report provides twenty six examples of operational buildings using ventilative cooling ranging from...
Solar thermal heating and cooling. A bibliography with abstracts
Arenson, M.
1979-01-01
This bibliographic series cites and abstracts the literature and technical papers on the heating and cooling of buildings with solar thermal energy. Over 650 citations are arranged in the following categories: space heating and cooling systems; space heating and cooling models; building energy conservation; architectural considerations, thermal load computations; thermal load measurements, domestic hot water, solar and atmospheric radiation, swimming pools; and economics.
International Nuclear Information System (INIS)
Pelloni, S.
1992-02-01
We have obtained results for a large sodium-cooled fast breeder reactor benchmark using data from the ENDF/B-VI and from Revision 1 of the JEF-1 (JEF-1.1) evaluation. The required cross sections were processed with the NJOY code system (Version 89.62) and homogenized with the spectrum cell code MICROX-2. Multigroup transport-theory calculations in 33 neutron groups (forward and adjoint) were performed using the two-dimensional code TWODANT and kinetic parameters were determined using the first-order perturbation-theory code PERT-V. We calculated eigenvalues, neutron balance data, global and regional breeding and conversion ratios, central rate ratios and reactivity worths with and without sodium, effective delayed neutron fraction and inhour reactivity, regional sodium void reactivity, and isothermal core fuel Doppler-reactivities. In particular, it is shown that good agreement (generally within one standard deviation) is achieved between these results and the average values over sixteen benchmark solutions obtained in the past. The eigenvalues predicted with ENDF/B-VI are up to 0.7% larger than those calculated with JEF-1.1 cross sections. This discrepancy is mainly due to different inelastic scattering cross sections for 23 Na and 238 U, and to different fast fission and nubar data for 239 Pu. (author) 5 figs., 30 tabs., 24 refs
DETERMINATION OF RADIATOR COOLING SURFACE
Directory of Open Access Journals (Sweden)
A. I. Yakubovich
2009-01-01
Full Text Available The paper proposes a methodology for calculation of a radiator cooling surface with due account of heat transfer non-uniformity on depth of its core. Calculation of radiator cooling surfaces of «Belarus-1221» and «Belarus-3022» tractors has been carried out in the paper. The paper also advances standard size series of radiators for powerful «Belarus» tractor type.
Energy Technology Data Exchange (ETDEWEB)
Sogn, T A; Stuanes, A O; Abrahamsen, G
1996-01-01
The conference paper deals with the accumulation of nitrogen in forests in Norway. The level of accumulation is a critical factor for the calculation of load limits. The paper compares the average rapidity values of accumulation since the last glacial age with the calculated values from the more short-lasting period based on data from surveying programs of the State Pollution Control Authority, manuring experiments, and other relevant research programs in this field. 8 refs., 1 fig., 1 tab.
Energy Technology Data Exchange (ETDEWEB)
Vasquez, V.R., E-mail: vrvasquez@ucla.edu [Environmental Science and Engineering Program, University of California, Los Angeles, Los Angeles, CA 90095-1496 (United States); Curren, J., E-mail: janecurren@yahoo.com [Environmental Science and Engineering Program, University of California, Los Angeles, Los Angeles, CA 90095-1496 (United States); Lau, S.-L., E-mail: simlin@ucla.edu [Department of Civil and Environmental Engineering, University of California, Los Angeles, Los Angeles, CA 90095-1496 (United States); Stenstrom, M.K., E-mail: stenstro@seas.ucla.edu [Department of Civil and Environmental Engineering, University of California, Los Angeles, Los Angeles, CA 90095-1496 (United States); Suffet, I.H., E-mail: msuffet@ucla.edu [Environmental Science and Engineering Program, University of California, Los Angeles, Los Angeles, CA 90095-1496 (United States)
2011-09-01
Echo Park Lake is a small lake in Los Angeles, CA listed on the USA Clean Water Act Section 303(d) list of impaired water bodies for elevated levels of organochlorine pesticides (OCPs) and polychlorinated biphenyls (PCBs) in fish tissue. A lake water and sediment sampling program was completed to support the development of total maximum daily loads (TMDL) to address the lake impairment. The field data indicated quantifiable levels of OCPs and PCBs in the sediments, but lake water data were all below detection levels. The field sediment data obtained may explain the contaminant levels in fish tissue using appropriate sediment-water partitioning coefficients and bioaccumulation factors. A partition-equilibrium fugacity model of the whole lake system was used to interpret the field data and indicated that half of the total mass of the pollutants in the system are in the sediments and the other half is in soil; therefore, soil erosion could be a significant pollutant transport mode into the lake. Modeling also indicated that developing and quantifying the TMDL depends significantly on the analytical detection level for the pollutants in field samples and on the choice of octanol-water partitioning coefficient and bioaccumulation factors for the model. - Research highlights: {yields} Fugacity model using new OCP and PCB field data supports lake TMDL calculations. {yields} OCP and PCB levels in lake sediment were found above levels for impairment. {yields} Relationship between sediment data and available fish tissue data evaluated. {yields} Model provides approximation of contaminant sources and sinks for a lake system. {yields} Model results were sensitive to analytical detection and quantification levels.
Workshop on high heat load x-ray optics
International Nuclear Information System (INIS)
1990-01-01
A workshop on ''High Heat Load X-Ray Optics'' was held at Argonne National Laboratory on August 3--5, 1989. The object of this workshop was to discuss recent advances in the art of cooling x-ray optics subject to high heat loads from synchrotron beams. The cooling of the first optical element in the intense photon beams that will be produced in the next generation of synchrotron sources is recognized as one of the major challenges that must be faced before one will be able to use these very intense beams in future synchrotron experiments. Considerable advances have been made in this art during the last few years, but much work remains to be done before the heating problem can be said to be completely solved. Special emphasis was placed on recent cooling experiments and detailed ''finite element'' and ''finite difference'' calculations comparing experiment with theory and extending theory to optimize performance
Kostinskiy, Sergey S.; Troitskiy, Anatoly I.
2016-01-01
This article deals with the problem of calculating the additional real-power losses in double-wound supply transformers with voltage class 6 (10)/0,4 kV, caused by unbalanced active inductive load connected in a star connection with an insulated neutral. When solving the problem, authors used the theory of electric circuits, method of balanced…
Energy Technology Data Exchange (ETDEWEB)
Norbaeck, P; Heneby, H
1976-01-22
Cooling towers to be transported on road vehicles as a unit are not allowed to exceed certain dimensions. In order to improve the efficiency of such a cooling tower (of cross-flow design and box-type body) with given dimensions, it is proposed to arrange at least one of the scrubbing bodies displaceable within a module or box. Then it can be moved out of the casing into working position, thereby increasing the front surface available for the inlet of air (and with it the efficiency) by nearly a factor of two.
Energy Technology Data Exchange (ETDEWEB)
Trobitz, M.; Mattheis, A. [Kernkraftwerke Gundremmingen Betriebsgesellschaft m.b.H. (Germany); Kerkhof, K.; Hippelein, K. [Stuttgart Univ. (Germany). Staatliche Materialpruefungsanstalt; Gurr-Beyer, C. [Buero fuer Baudynamik, Stuttgart (Germany); Hofstoetter, P. [Technischer Ueberwachungs-Verein Rheinland e.V., Koeln (Germany)
1998-11-01
Within the framework of periodic safety inspection of the Gundremmingen power station (RWE-Bayernwerk - KRB II), the load collectives used for the design of safety-relevant systems and components were checked for their consistency with latest updates of the design basis. It was found that there was no analytical information or study available describing a particular process and its effects, namely switch-off of the high-pressure feedwater pump of the emergency core cooling system. The paper reports the work performed for closing the gap, including preparatory analyses, accompanying measures such as vibration measurements during plant shut-down, as well as the preparation and performance of the in-situ test. The experimental results and the comparative evaluation of calculated and experimental data are presented. (orig./CB) [Deutsch] Im Rahmen der periodischen Sicherheitsueberpruefung des Kernkraftwerkes Gundremmingen (Kernkraftwerke RWE-Bayernwerk - KRB II) wurden u.a. die Lastkollektive, die zur Auslegung sicherheitstechnisch relevanter Systeme und Komponenten herangezogen wurden, auf Aktualitaet ueberprueft. Dabei zeigte sich, dass bislang fuer eine Betriebsweise - naemlich das Abschalten der Hochdruckeinspeisepumpe des nuklearen Not- und Nachkuehlsystems (TH-HD-Pumpe) - keine analytischen Untersuchungen vorliegen. Vorbetrachtungen fuer analytische Untersuchungen, begleitende Massnahmen wie Schwingungsmessungen waehrend des Anlagenstillstandes, sowie der Versuchsaufbau und die Versuchsdurchfuehrung des Anlagenversuches werden hier dargestellt. Die Ergebnisse und der Vergleich Rechnung-Messung zum Grossversuch werden in diesem Beitrag vorgestellt. (orig.)
Shot loading platform analysis
International Nuclear Information System (INIS)
Norman, B.F.
1994-01-01
This document provides the wind/seismic analysis and evaluation for the shot loading platform. Hand calculations were used for the analysis. AISC and UBC load factors were used in this evaluation. The results show that the actual loads are under the allowable loads and all requirements are met
Shope, Christopher L.; Angeroth, Cory E.
2015-01-01
Effective management of surface waters requires a robust understanding of spatiotemporal constituent loadings from upstream sources and the uncertainty associated with these estimates. We compared the total dissolved solids loading into the Great Salt Lake (GSL) for water year 2013 with estimates of previously sampled periods in the early 1960s.We also provide updated results on GSL loading, quantitatively bounded by sampling uncertainties, which are useful for current and future management efforts. Our statistical loading results were more accurate than those from simple regression models. Our results indicate that TDS loading to the GSL in water year 2013 was 14.6 million metric tons with uncertainty ranging from 2.8 to 46.3 million metric tons, which varies greatly from previous regression estimates for water year 1964 of 2.7 million metric tons. Results also indicate that locations with increased sampling frequency are correlated with decreasing confidence intervals. Because time is incorporated into the LOADEST models, discrepancies are largely expected to be a function of temporally lagged salt storage delivery to the GSL associated with terrestrial and in-stream processes. By incorporating temporally variable estimates and statistically derived uncertainty of these estimates,we have provided quantifiable variability in the annual estimates of dissolved solids loading into the GSL. Further, our results support the need for increased monitoring of dissolved solids loading into saline lakes like the GSL by demonstrating the uncertainty associated with different levels of sampling frequency.
International Nuclear Information System (INIS)
Bisognano, J.; Leemann, C.
1982-03-01
Stochastic cooling is the damping of betatron oscillations and momentum spread of a particle beam by a feedback system. In its simplest form, a pickup electrode detects the transverse positions or momenta of particles in a storage ring, and the signal produced is amplified and applied downstream to a kicker. The time delay of the cable and electronics is designed to match the transit time of particles along the arc of the storage ring between the pickup and kicker so that an individual particle receives the amplified version of the signal it produced at the pick-up. If there were only a single particle in the ring, it is obvious that betatron oscillations and momentum offset could be damped. However, in addition to its own signal, a particle receives signals from other beam particles. In the limit of an infinite number of particles, no damping could be achieved; we have Liouville's theorem with constant density of the phase space fluid. For a finite, albeit large number of particles, there remains a residue of the single particle damping which is of practical use in accumulating low phase space density beams of particles such as antiprotons. It was the realization of this fact that led to the invention of stochastic cooling by S. van der Meer in 1968. Since its conception, stochastic cooling has been the subject of much theoretical and experimental work. The earliest experiments were performed at the ISR in 1974, with the subsequent ICE studies firmly establishing the stochastic cooling technique. This work directly led to the design and construction of the Antiproton Accumulator at CERN and the beginnings of p anti p colliding beam physics at the SPS. Experiments in stochastic cooling have been performed at Fermilab in collaboration with LBL, and a design is currently under development for a anti p accumulator for the Tevatron
Analysis of passive moderator cooling system of Candu-6A reactor at emergency condition
International Nuclear Information System (INIS)
Umar, Efrizon; Subki, M. Hadid; Vecchiarelli, Jack
2001-01-01
Analysis of passive moderator cooling system subject to in-core LOCA with no emergency core cooling injection has been done. In this study, the new model of passive moderator system has been tested for emergency conditions and CATHENA code Mod-3.5b/Rev1 is used to calculate some parameters of this passive moderator cooling system. This result of simulation show that the proposed moderator cooling system have given satisfactory result, especially for the case with 0.7 m riser diameter and the number of heat exchanger tubes 8100. For PEWS tank containing 3000 m3 of light water initially at 30 0C and a 3641 m2 moderator heat exchanger, the average long-term heat removed rate balances the moderator heat load and the flow through the passive moderator loop remains stable for over 72 hours with no saturated boiling in the calandria and flow instabilities do not develop during long-term period
A parametric study of solar operated cooling system
International Nuclear Information System (INIS)
Zagalei, Abdullatif Salin
2006-01-01
Because of energy for air conditioning has been the fastest-growing segment of energy of consumption market in Libya and generally in north Africa, and with the realization depleting nature of fossil fuel, solar cooling of buildings which leads to the improvement of human comfort represents a potentially significant application of solar energy where the availability of solar radiation meets with the cooling load demand. This application has been shown to be technically feasible but the equipment needs further investigative research to improve its performance and feasibility. A solar operated absorption cooling system with energy storage is selected. A latent heat storage would be a space saver for such application for solar energy. A system modeling is an essential activity in order to go for system simulation. A complete solar cooling system to be modeled through the thermodynamic analysis of each system components. Resulting a package of equations used directly to the system simulation in order to predict the system performance to obtain the optimum working conditions for the selected cooling system. A computer code which is used to simulate a series of calculations was written in Fortran language according to the constructed information flow diagram and simulation program flow char. For a typical input data a set of results are reported and discussed and shows that the selected system promises to be a good choice for air conditioning application in Libya specially for large building as storehouses, shopping centers, public administrative.(Author)
Antonella Del Rosso
2015-01-01
The NA62 Gigatracker is a jewel of technology: its sensor, which delivers the time of the crossing particles with a precision of less than 200 picoseconds (better than similar LHC detectors), has a cooling system that might become the precursor to a completely new detector technique. The 115 metre long vacuum tank of the NA62 experiment. The NA62 Gigatracker (GTK) is composed of a set of three innovative silicon pixel detectors, whose job is to measure the arrival time and the position of the incoming beam particles. Installed in the heart of the NA62 detector, the silicon sensors are cooled down (to about -20 degrees Celsius) by a microfluidic silicon device. “The cooling system is needed to remove the heat produced by the readout chips the silicon sensor is bonded to,” explains Alessandro Mapelli, microsystems engineer working in the Physics department. “For the NA62 Gigatracker we have designed a cooling plate on top of which both the silicon sensor and the...
International Nuclear Information System (INIS)
Chung, T.; Solack, T.; Hortel, J.
1991-01-01
As part of the plant upgrade program, structural analyses and field inspections were performed on four redwood cooling towers at the DOE Portsmouth gaseous diffusion plant located in Piketon, Ohio. The cooling towers are categorized as important hazard facilities. The loadings are derived from UCRL-15910 according to the pertinent hazard category. In addition to the seismic and wind loadings, the wood cooling towers are constantly subject to adverse environmental effects such as elevated temperature, chemical attack, icing and snow load, and motor vibrations. A thorough structural evaluation for all load combinations was performed for each of the cooling towers based on the structural code requirements of the Cooling Tower Institute and National Forest Products Association. Most stress criteria are unique for the redwood material. This evaluation was performed using finite element techniques on the global structural integrity and supplemented by hand calculations on the individual connection joints. Overloaded wood structural members and joints are identified by the analysis. The rectangular tower structure sits on a concrete basin that span across 60 ft by 200 ft. A major part of the cooling towers upgrading program involved field inspections of the individual cells of each tower. The primary purpose of these inspections was to identify any existing structural damage or deficiencies such as failed members, degraded wood, and deficiencies resulting from poor construction practice. Inspection of 40 cells identified some generic deficiencies that mostly are consistent with the analytical finding. Based on the analysis, some effective but inexpensive upgrading techniques were developed and recommended to bring the cooling towers into compliance with current DOE requirements
Fracture of thermally loaded disks of materials in elastic-brittle state
International Nuclear Information System (INIS)
Egorov, V.S.; Lanin, A.G.; Fedik, I.I.
1981-01-01
Fracture kinetics and limiting supporting power were studied in a solid thin disk axisymmetrically cooled from the periphery depending on the deqree of the stressed state nonuniformity and crack interaction. Basing on a strength approach of fracture linear mechanism it has become possible to obtain limit equilibrium curves and to evaluate thermoelastic stress redistribution on the boundary of the disk with one, two and four symmetrical radial cracks. Calculated data are confirmed by the results of the experiments performed with zirconium carbide water-cooled disks. It is shown that while determining the limit supporting power of a thermally loaded body, the loading history and fracture kinetics should be taken into account
1982-01-01
New athletic wear design based on the circulating liquid cooling system used in the astronaut's space suits, allows athletes to perform more strenuous activity without becoming overheated. Techni-Clothes gear incorporates packets containing a heat-absorbing gel that slips into an insulated pocket of the athletic garment and is positioned near parts of the body where heat transfer is most efficient. A gel packet is good for about one hour. Easily replaced from a supply of spares in an insulated container worn on the belt. The products, targeted primarily for runners and joggers and any other athlete whose performance may be affected by hot weather, include cooling headbands, wrist bands and running shorts with gel-pack pockets.
International Nuclear Information System (INIS)
Coutant, C.C.
1978-01-01
Progress on the thermal effects project is reported with regard to physiology and distribution of Corbicula; power plant effects studies on burrowing mayfly populations; comparative thermal responses of largemouth bass from northern and southern populations; temperature selection by striped bass in Cherokee Reservoir; fish population studies; and predictive thermoregulation by fishes. Progress is also reported on the following; cause and ecological ramifications of threadfin shad impingement; entrainment project; aquaculture project; pathogenic amoeba project; and cooling tower drift project
Thermoelectric air-cooling module for electronic devices
International Nuclear Information System (INIS)
Chang, Yu-Wei; Chang, Chih-Chung; Ke, Ming-Tsun; Chen, Sih-Li
2009-01-01
This article investigates the thermoelectric air-cooling module for electronic devices. The effects of heat load of heater and input current to thermoelectric cooler are experimentally determined. A theoretical model of thermal analogy network is developed to predict the thermal performance of the thermoelectric air-cooling module. The result shows that the prediction by the model agrees with the experimental data. At a specific heat load, the thermoelectric air-cooling module reaches the best cooling performance at an optimum input current. In this study, the optimum input currents are from 6 A to 7 A at the heat loads from 20 W to 100 W. The result also demonstrates that the thermoelectric air-cooling module performs better performance at a lower heat load. The lowest total temperature difference-heat load ratio is experimentally estimated as -0.54 W K -1 at the low heat load of 20 W, while it is 0.664 W K -1 at the high heat load of 100 W. In some conditions, the thermoelectric air-cooling module performs worse than the air-cooling heat sink only. This article shows the effective operating range in which the cooling performance of the thermoelectric air-cooling module excels that of the air-cooling heat sink only.
Energy Technology Data Exchange (ETDEWEB)
Huehnerbein, Benjamin Rudolf
2011-07-01
The load flow situation has significantly changed in electric power systems throughout the deregulation of European electricity market and the development of renewable energy sources. In the past load profiles of transmission lines and transformers were only dependent on the customers power demand. Today it is a mixture of load curves, power feed in by renewables and power transits which affect the usage of the transmission system. This leads to a fluctuating utilisation with a certain probability for each state with respect to the stochastic character of the above influences. Knowledge of the utilisation is the precondition for an efficient dimensioning of the power system. For these specific requirements the probabilistic power flow calculation is introduced and further developed. The state variables of the power system are defined as random variables and the probability of each grid state is determined. Different types of network equations and calculation techniques, resulting from various assumptions and simplifications of the well-known power flow equations are compared. The solution is found by either convolution techniques or Monte-Carlo-Simulation. The mathematic models is completed by implementation of a balanced power generation as well as by the integration of a correlation approach. This allows more or less realistic behavior for the interaction of load and generation on the one hand and the concurrence of similar nodal powers on the other hand. The result is proven by a boundary load flow on the base of the exact load flow equations. This allows a comparison of the minimum and the maximum values between the linearised and the exact solution. As long as this deviation is known, the results of the probabilistic power flow can be used in power system evaluation. At least an approach for the combination of probabilistic power flow and reliability evaluation is outlined to determine the probability for overloading components for the reason of network
Cooling system for superconducting magnet
Gamble, Bruce B.; Sidi-Yekhlef, Ahmed
1998-01-01
A cooling system is configured to control the flow of a refrigerant by controlling the rate at which the refrigerant is heated, thereby providing an efficient and reliable approach to cooling a load (e.g., magnets, rotors). The cooling system includes a conduit circuit connected to the load and within which a refrigerant circulates; a heat exchanger, connected within the conduit circuit and disposed remotely from the load; a first and a second reservoir, each connected within the conduit, each holding at least a portion of the refrigerant; a heater configured to independently heat the first and second reservoirs. In a first mode, the heater heats the first reservoir, thereby causing the refrigerant to flow from the first reservoir through the load and heat exchanger, via the conduit circuit and into the second reservoir. In a second mode, the heater heats the second reservoir to cause the refrigerant to flow from the second reservoir through the load and heat exchanger via the conduit circuit and into the first reservoir.
Directory of Open Access Journals (Sweden)
Walt Wells
2008-01-01
Full Text Available Our objective in this paper is to solve a second order differential equation for a long, simply supported column member subjected to a lateral axial load using Heun's numerical method. We will use the solution to find the critical load at which the column member will fail due to buckling. We will calculate this load using Euler's derived analytical approach for an exact solution, as well as Euler's Numerical Method. We will then compare the three calculated values to see how much they deviate from one another. During the critical load calculation, it will be necessary to calculate the moment of inertia for the column member.
Devriendt, L.; Burghouwt, G.; Derudder, B.; de Wit, J.; Witlox, F.
2009-01-01
This paper takes a critical view of the verification of load factors for the direct transatlantic airline market by combining supply and demand-data. The supply-related data originate from the Official Airline Guide, a well-known data source that contains information on scheduled flights. The
Effect of highly reflective roofing sheet on building thermal loads for a school in Osaka
Directory of Open Access Journals (Sweden)
Yuan Jihui
2017-01-01
Full Text Available Currently, urban heat island (UHI phenomenon and building energy consumptions are becoming serious. Strategies to mitigate UHI and reduce building energy consumptions are implemented worldwide. In Japan, as an effective means of mitigating UHI and saving energy of buildings, highly reflective (HR and green roofs are increasingly used. In order to evaluate the effect of roofs with high reflection and thermal insulation on the energy conservation of buildings, we investigated the roof solar reflectivity of the subject school in Osaka, in which the HR roofing sheet was installed on the roof from 2010. Thermal loads, including cooling and heating loads of the top floor of school, were calculated using the thermal load calculation software, New HASP/ACLD-β. Comparing the thermal loads after HR roofing sheet installation to previous, the annual thermal load decreased about 25 MJ/m2-year and the cooling load decreased about 112 MJ/m2-year. However, the heating load increased about 87 MJ/m2-year in winter. To minimize the annual thermal load, thermal insulation of the roof was also considered be used together with HR roofing sheet in this study. The results showed that the combination of HR roofing sheet and high thermal insulation is more effective to reduce the annual thermal load.
Chiral symmetry breaking and cooling in lattice QCD
International Nuclear Information System (INIS)
Woloshyn, R.M.; Lee, F.X.
1995-08-01
Chiral symmetry breaking is calculated as a function of cooling in quenched lattice QCD. A non-zero signal is found for the chiral condensate beyond one hundred cooling steps, suggesting that there is chiral symmetry breaking associated with instantons. Quantitatively, the chiral condensate in cooled gauge field configurations is small compared to the value without cooling. (author) 7 refs., 1 tab., 3 figs
40 CFR 92.106 - Equipment for loading the engine.
2010-07-01
...: electrical resistance load bank; fans or other means for cooling of the load bank; wattmeter, including phase... electrical shunt and voltmeter is allowed for current measurement); meter(s) to measure the voltage across... locomotives are equipped with an internal electrical resistance load bank and fans for cooling of the load...
Helical muon beam cooling channel engineering design
International Nuclear Information System (INIS)
Johnson, Rolland
2015-01-01
The Helical Cooling Channel (HCC) achieves effective ionization cooling of the six-dimensional (6d) phase space of a muon beam by means of a series of 21st century inventions. In the HCC, hydrogen-pressurized RF cavities enable high RF gradients in strong external magnetic fields. The theory of the HCC, which requires a magnetic field with solenoid, helical dipole, and helical quadrupole components, demonstrates that dispersion in the gaseous hydrogen energy absorber provides effective emittance exchange to enable longitudinal ionization cooling. The 10-year development of a practical implementation of a muon-beam cooling device has involved a series of technical innovations and experiments that imply that an HCC of less than 300 m length can cool the 6d emittance of a muon beam by six orders of magnitude. We describe the design and construction plans for a prototype HCC module based on oxygen-doped hydrogen-pressurized RF cavities that are loaded with dielectric, fed by magnetrons, and operate in a superconducting helical solenoid magnet. The first phase of this project saw the development of a conceptual design for the integration of 805 MHz RF cavities into a 10 T Nb 3 Sn-based HS test section. Two very novel ideas are required to realize the design. The first idea is the use of dielectric inserts in the RF cavities to make them smaller for a given frequency so that the cavities and associated plumbing easily fit inside the magnet cryostat. Calculations indicate that heat loads will be tolerable, while RF breakdown of the dielectric inserts will be suppressed by the pressurized hydrogen gas. The second new idea is the use of a multi-layer Nb 3 Sn helical solenoid. The technology demonstrations for the two aforementioned key components of a 10T, 805 MHz HCC were begun in this project. The work load in the Fermilab Technical Division made it difficult to test a multi-layer Nb 3 Sn solenoid as originally planned. Instead, a complementary project was approved by the
Helical muon beam cooling channel engineering design
Energy Technology Data Exchange (ETDEWEB)
Johnson, Rolland [Muons, Inc., Batavia, IL (United States)
2015-08-07
The Helical Cooling Channel (HCC) achieves effective ionization cooling of the six-dimensional (6d) phase space of a muon beam by means of a series of 21st century inventions. In the HCC, hydrogen-pressurized RF cavities enable high RF gradients in strong external magnetic fields. The theory of the HCC, which requires a magnetic field with solenoid, helical dipole, and helical quadrupole components, demonstrates that dispersion in the gaseous hydrogen energy absorber provides effective emittance exchange to enable longitudinal ionization cooling. The 10-year development of a practical implementation of a muon-beam cooling device has involved a series of technical innovations and experiments that imply that an HCC of less than 300 m length can cool the 6d emittance of a muon beam by six orders of magnitude. We describe the design and construction plans for a prototype HCC module based on oxygen-doped hydrogen-pressurized RF cavities that are loaded with dielectric, fed by magnetrons, and operate in a superconducting helical solenoid magnet. The first phase of this project saw the development of a conceptual design for the integration of 805 MHz RF cavities into a 10 T Nb_{3}Sn-based HS test section. Two very novel ideas are required to realize the design. The first idea is the use of dielectric inserts in the RF cavities to make them smaller for a given frequency so that the cavities and associated plumbing easily fit inside the magnet cryostat. Calculations indicate that heat loads will be tolerable, while RF breakdown of the dielectric inserts will be suppressed by the pressurized hydrogen gas. The second new idea is the use of a multi-layer Nb_{3}Sn helical solenoid. The technology demonstrations for the two aforementioned key components of a 10T, 805 MHz HCC were begun in this project. The work load in the Fermilab Technical Division made it difficult to test a multi-layer Nb_{3}Sn solenoid as originally planned. Instead, a complementary
High thermal load receiving heat plate
International Nuclear Information System (INIS)
Shibutani, Jun-ichi; Shibayama, Kazuhito; Yamamoto, Keiichi; Uchida, Takaho.
1993-01-01
The present invention concerns a high thermal load heat receiving plate such as a divertor plate of a thermonuclear device. The high thermal load heat receiving plate of the present invention has a cooling performance capable of suppressing the temperature of an armour tile to less than a threshold value of the material against high thermal loads applied from plasmas. Spiral polygonal pipes are inserted in cooling pipes at a portion receiving high thermal loads in the high temperature load heat receiving plate of the present invention. Both ends of the polygonal pipes are sealed by lids. An area of the flow channel in the cooling pipes is thus reduced. Heat conductivity on the cooling surface of the cooling pipes is increased in the high thermal load heat receiving plate having such a structure. Accordingly, temperature elevation of the armour tile can be suppressed. (I.S.)
Climate Control Load Reduction Strategies for Electric Drive Vehicles in Warm Weather
Energy Technology Data Exchange (ETDEWEB)
Jeffers, M. A.; Chaney, L.; Rugh, J. P.
2015-04-30
Passenger compartment climate control is one of the largest auxiliary loads on a vehicle. Like conventional vehicles, electric vehicles (EVs) require climate control to maintain occupant comfort and safety, but cabin heating and air conditioning have a negative impact on driving range for all electric vehicles. Range reduction caused by climate control and other factors is a barrier to widespread adoption of EVs. Reducing the thermal loads on the climate control system will extend driving range, thereby reducing consumer range anxiety and increasing the market penetration of EVs. Researchers at the National Renewable Energy Laboratory have investigated strategies for vehicle climate control load reduction, with special attention toward EVs. Outdoor vehicle thermal testing was conducted on two 2012 Ford Focus Electric vehicles to evaluate thermal management strategies for warm weather, including solar load reduction and cabin pre-ventilation. An advanced thermal test manikin was used to assess a zonal approach to climate control. In addition, vehicle thermal analysis was used to support testing by exploring thermal load reduction strategies, evaluating occupant thermal comfort, and calculating EV range impacts. Through stationary cooling tests and vehicle simulations, a zonal cooling configuration demonstrated range improvement of 6%-15%, depending on the drive cycle. A combined cooling configuration that incorporated thermal load reduction and zonal cooling strategies showed up to 33% improvement in EV range.
Study of a two-pipe chilled beam system for both cooling and heating of office buildings
Energy Technology Data Exchange (ETDEWEB)
Norouzi, R. [Univ. of Boraes, Boraes (Sweden); Hultmark, G. [Lindab Comfort A/S, Farum (Denmark); Afshari, A. (ed.); Bergsoee, N.C. [Aalborg Univ.. Statens Byggeforskningsinstitut (SBi), Copenhagen (Denmark)
2013-05-15
The main aim of this master thesis was to investigate possibilities and limitations of a new system in active chilled beam application for office buildings. Lindab Comfort A/S pioneered the presented system. The new system use two-pipe system, instead of the conventional active chilled beam four-pipe system for heating and cooling purposes. The Two-Pipe System which is studied in this project use high temperature cooling and low temperature heating with water temperatures of 20 deg. C to 23 deg. C, available for free most of the year. The system can thus take advantage of renewable energy. It was anticipated that a Two-Pipe System application enables transfer of energy from warm spaces to cold spaces while return flows, from cooling and heating beams, are mixed. BSim software was chosen as a simulation tool to model a fictional office building and calculate heating and cooling loads of the building. Moreover, the effect of using outdoor air as a cooling energy source (free cooling) is investigated through five possible scenarios in both the four pipe system and the Two-Pipe System. The calculations served two purposes. Firstly, the effect of energy transfer in the Two-Pipe System were calculated and compared with the four pipe system. Secondly, free cooling effect was calculated in the Two-Pipe System and compared with the four pipe system. The simulation results showed that the energy transfer, as an inherent characteristic in the Two-Pipe System, is able to reduce up to 3 % of annual energy use compared to the four pipe system. Furthermore, different free cooling applications in the Two-Pipe System and the four pipe system respectively showed that the Two-Pipe System requires 7-15 % less total energy than the four pipe system in one year. In addition, the Two-Pipe System can save 18-57 % of annual cooling energy when compared to the four pipe system. (Author)
DEFF Research Database (Denmark)
Grunert, Klaus G; Brock, Steen; Brunsø, Karen
2016-01-01
Young people snack and their snacking habits are not always healthy. We address the questions whether it is possible to develop a new snack product that adolescents will find attractive, even though it is based on ingredients as healthy as fruits and vegetables, and we argue that developing...... such a product requires an interdisciplinary effort where researchers with backgrounds in psychology, anthropology, media science, philosophy, sensory science and food science join forces. We present the COOL SNACKS project, where such a blend of competences was used first to obtain thorough insight into young...... people's snacking behaviour and then to develop and test new, healthier snacking solutions. These new snacking solutions were tested and found to be favourably accepted by young people. The paper therefore provides a proof of principle that the development of snacks that are both healthy and attractive...
2006-01-01
Pictured, from left to right: Tim Izo (saxophone, flute, guitar), Bobby Grant (tour manager), George Pajon (guitar). What do the LHC and a world-famous hip-hop group have in common? They are cool! On Saturday, 1st July, before their appearance at the Montreux Jazz Festival, three members of the 'Black Eyed Peas' came on a surprise visit to CERN, inspired by Dan Brown's Angels and Demons. At short notice, Connie Potter (Head of the ATLAS secretariat) organized a guided tour of ATLAS and the AD 'antimatter factory'. Still curious, lead vocalist Will.I.Am met CERN physicist Rolf Landua after the concert to ask many more questions on particles, CERN, and the origin of the Universe.
The cryogenic cooling program at the Advanced Photon Source
International Nuclear Information System (INIS)
Rogers, C.S.; Mills, D.M.; Assoufid, L.
1994-06-01
This paper describes the experimental and analytical program in cryogenic cooling of high-heat-load optics at the Advanced-Photon Source. A prototype liquid nitrogen pumping system has been procured. This pump provides a variable flow rate of 1 to 10 gpm of pressurized liquid nitrogen and is sized to handle up to 5 kW of optic heat load. Also, a high-vacuum, double-crystal monochromator testing tank has been fabricated. This system will be used to test cryogenic crystals at existing synchrotron sources. A finite element analysis has been performed for a cryogenically cooled Si crystal in the inclined geometry for Undulator A at 100 mA. The inclination angle was 80 degrees. It was set to diffract from the (111) planes at the first harmonic energy of 4.2 keV. The maximum slope error in the diffraction plane was calculated to be about 1 μrad with a peak temperature of 94 K. An analysis has also been performed for a cryogenically-cooled ''thin'' crystal oriented in the Bragg geometry which accepts 87% of the lst harmonic photons at 3.866 keV. The total absorbed power was 131 W at 100 mA current and the peak temperature was 124 K
Results of strategic calculations for optimizing the first wall life in a tokamak fusion reactor
International Nuclear Information System (INIS)
Daenner, W.
1981-01-01
The development of the FWLTB computer program has reached a stage where prediction of the first wall lifetime is possible. Because of the large number of free parameters strategic calculations were found to be the most appropriate way to arrive at load design conditions which allow optimum life expectancy. In this paper a revised set of life criteria is presented this being followed by the results of parameter studies in which single parameters were varied while the remaining ones were kept fixed at a reference value. These results are used as a guide during the subsequent strategic calculations. In a first strategy we aimed at finding the maximum lifetime for the case that the reactor is operated at a neutron wall loading of 10 MW/m 2 . We found that operation over a period of more than one year is possible if the first wall is designed in a very tiny geometry and cooled by a low-pressure coolant. In a second strategy the aim was to find the design conditions for the case that the first wall is cooled by a high-pressure coolant. It is shown that liquid-lithium cooling is manageable up to high wall loadings, but the lifetime is restricted to about 6 MWa/m 2 . Helium cooling allows a higher lifetime, but the design conditions are such that only modest wall loadings can be permitted. (orig.)
Thermo-economic Optimization of Solar Assisted Heating and Cooling (SAHC System
Directory of Open Access Journals (Sweden)
A. Ghafoor
2014-12-01
Full Text Available The energy demand for cooling is continuously increasing due to growing thermal loads, changing architectural modes of building, and especially due to occupants indoor comfort requirements resulting higher electricity demand notably during peak load hours. This increasing electricity demand is resulting higher primary energy consumption and emission of green house gases (GHG due to electricity generation from fossil fuels. An exciting alternative to reduce the peak electricity consumption is the possible utilization of solar heat to run thermally driven cooling machines instead of vapor compression machines utilizing high amount of electricity. In order to widen the use of solar collectors, they should also be used to contribute for sanitary hot water production and space heating. Pakistan lying on solar belt has a huge potential to utilize solar thermal heat for heating and cooling requirement because cooling is dominant throughout the year and the enormous amount of radiation availability provides an opportunity to use it for solar thermal driven cooling systems. The sensitivity analysis of solar assisted heating and cooling system has been carried out under climatic conditions of Faisalabad (Pakistan and its economic feasibility has been calculated using maximization of NPV. Both storage size and collector area has been optimized using different economic boundary conditions. Results show that optimum area of collector lies between 0.26m2 to 0.36m2 of collector area per m2 of conditioned area for ieff values of 4.5% to 0.5%. The optimum area of collector increases by decreasing effective interest rate resulting higher solar fraction. The NPV was found to be negative for all ieff values which shows that some incentives/subsidies are needed to be provided to make the system cost beneficial. Results also show that solar fraction space heating varies between 87 and 100% during heating season and solar fraction cooling between 55 and 100% during
Demineralised water cooling in the LHC accelerator
Peón-Hernández, G
2002-01-01
In spite of the LHC accelerator being a cryogenic machine, it remains nevertheless a not negligible heat load to be removed by conventional water-cooling. About 24MW will be taken away by demineralised water cooled directly by primary water from the LHC cooling towers placed at the even points. This paper describes the demineralised water network in the LHC tunnel including pipe diameters, lengths, water speed, estimated friction factor, head losses and available supply and return pressures for each point. It lists all water cooled equipment, highlights the water cooled cables as the most demanding equipment followed by the radio frequency racks and cavities, and by the power converters. Their main cooling requirements and their positions in the tunnel are also presented.
International Nuclear Information System (INIS)
Nakayama, Tadakazu; Hayashi, Katsumi; Handa, Hiroyuki
1993-01-01
Cooling water for a divertor cooling system cools the divertor, thereafter, passes through pipelines connecting the exit pipelines of the divertor cooling system and the inlet pipelines of a blanket cooling system and is introduced to the blanket cooling system in a vacuum vessel. It undergoes emission of neutrons, and cooling water in the divertor cooling system containing a great amount of N-16 which is generated by radioactivation of O-16 is introduced to the blanket cooling system in the vacuum vessel by way of pipelines, and after cooling, passes through exit pipelines of the blanket cooling system and is introduced to the outside of the vacuum vessel. Radiation of N-16 in the cooling water is decayed sufficiently with passage of time during cooling of the blanket, thereby enabling to decrease the amount of shielding materials such as facilities and pipelines, and ensure spaces. (N.H.)
Ben-Zvi, Ilan; Barton, Donald; Beavis, Dana; Blaskiewicz, Michael; Bluem, Hans; Brennan, Joseph M; Bruhwiler, David L; Burger, Al; Burov, Alexey; Burrill, Andrew; Calaga, Rama; Cameron, Peter; Chang, Xiangyun; Cole, Michael; Connolly, Roger; Delayen, Jean R; Derbenev, Yaroslav S; Eidelman, Yury I; Favale, Anthony; Fedotov, Alexei V; Fischer, Wolfram; Funk, L W; Gassner, David M; Hahn, Harald; Harrison, Michael; Hershcovitch, Ady; Holmes, Douglas; Hseuh Hsiao Chaun; Johnson, Peter; Kayran, Dmitry; Kewisch, Jorg; Kneisel, Peter; Koop, Ivan; Lambiase, Robert; Litvinenko, Vladimir N; MacKay, William W; Mahler, George; Malitsky, Nikolay; McIntyre, Gary; Meng, Wuzheng; Merminga, Lia; Meshkov, Igor; Mirabella, Kerry; Montag, Christoph; Nagaitsev, Sergei; Nehring, Thomas; Nicoletti, Tony; Oerter, Brian; Parkhomchuk, Vasily; Parzen, George; Pate, David; Phillips, Larry; Preble, Joseph P; Rank, Jim; Rao, Triveni; Rathke, John; Roser, Thomas; Russo, Thomas; Scaduto, Joseph; Schultheiss, Tom; Sekutowicz, Jacek; Shatunov, Yuri; Sidorin, Anatoly O; Skrinsky, Aleksander Nikolayevich; Smirnov, Alexander V; Smith, Kevin T; Todd, Alan M M; Trbojevic, Dejan; Troubnikov, Grigory; Wang, Gang; Wei, Jie; Williams, Neville; Wu, Kuo-Chen; Yakimenko, Vitaly; Zaltsman, Alex; Zhao, Yongxiang; ain, Animesh K
2005-01-01
We report progress on the R&D program for electron-cooling of the Relativistic Heavy Ion Collider (RHIC). This electron cooler is designed to cool 100 GeV/nucleon at storage energy using 54 MeV electrons. The electron source will be a superconducting RF photocathode gun. The accelerator will be a superconducting energy recovery linac. The frequency of the accelerator is set at 703.75 MHz. The maximum electron bunch frequency is 9.38 MHz, with bunch charge of 20 nC. The R&D program has the following components: The photoinjector and its photocathode, the superconducting linac cavity, start-to-end beam dynamics with magnetized electrons, electron cooling calculations including benchmarking experiments and development of a large superconducting solenoid. The photoinjector and linac cavity are being incorporated into an energy recovery linac aimed at demonstrating ampere class current at about 20 MeV. A Zeroth Order Design Report is in an advanced draft state, and can be found on the web at http://www.ags...
International Nuclear Information System (INIS)
Anon.
1994-01-01
Cooling - the control of unruly particles to provide well-behaved beams - has become a major new tool in accelerator physics. The main approaches of electron cooling pioneered by Gersh Budker at Novosibirsk and stochastic cooling by Simon van der Meer at CERN, are now complemented by additional ideas, such as laser cooling of ions and ionization cooling of muons
Darlow, M. S.; Smalley, A. J.
1977-01-01
A test rig designed to measure stiffness and damping of elastomer cartridges under a rotating load excitation is described. The test rig employs rotating unbalance in a rotor which runs to 60,000 RPM as the excitation mechanism. A variable resonant mass is supported on elastomer elements and the dynamic characteristics are determined from measurements of input and output acceleration. Five different cartridges are considered: three of these are buttons cartridges having buttons located in pairs, with 120 between each pair. Two of the cartridges consist of 360 elastomer rings with rectangular cross-sections. Dynamic stiffness and damping are measured for each cartridge and compared with predictions at different frequencies and different strains.
Energy Technology Data Exchange (ETDEWEB)
Manning, Karessa L. [Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States); Dolislager, Fredrick G. [Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States); Bellamy, Michael B. [Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States)
2016-11-01
The Preliminary Remediation Goal (PRG) and Dose Compliance Concentration (DCC) calculators are screening level tools that set forth Environmental Protection Agency's (EPA) recommended approaches, based upon currently available information with respect to risk assessment, for response actions at Comprehensive Environmental Response, Compensation, and Liability Act (CERCLA) sites, commonly known as Superfund. The screening levels derived by the PRG and DCC calculators are used to identify isotopes contributing the highest risk and dose as well as establish preliminary remediation goals. Each calculator has a residential gardening scenario and subsistence farmer exposure scenarios that require modeling of the transfer of contaminants from soil and water into various types of biota (crops and animal products). New publications of human intake rates of biota; farm animal intakes of water, soil, and fodder; and soil to plant interactions require updates be implemented into the PRG and DCC exposure scenarios. Recent improvements have been made in the biota modeling for these calculators, including newly derived biota intake rates, more comprehensive soil mass loading factors (MLFs), and more comprehensive soil to tissue transfer factors (TFs) for animals and soil to plant transfer factors (BV's). New biota have been added in both the produce and animal products categories that greatly improve the accuracy and utility of the PRG and DCC calculators and encompass greater geographic diversity on a national and international scale.
International Nuclear Information System (INIS)
Manning, Karessa L.; Dolislager, Fredrick G.; Bellamy, Michael B.
2016-01-01
The Preliminary Remediation Goal (PRG) and Dose Compliance Concentration (DCC) calculators are screening level tools that set forth Environmental Protection Agency's (EPA) recommended approaches, based upon currently available information with respect to risk assessment, for response actions at Comprehensive Environmental Response, Compensation, and Liability Act (CERCLA) sites, commonly known as Superfund. The screening levels derived by the PRG and DCC calculators are used to identify isotopes contributing the highest risk and dose as well as establish preliminary remediation goals. Each calculator has a residential gardening scenario and subsistence farmer exposure scenarios that require modeling of the transfer of contaminants from soil and water into various types of biota (crops and animal products). New publications of human intake rates of biota; farm animal intakes of water, soil, and fodder; and soil to plant interactions require updates be implemented into the PRG and DCC exposure scenarios. Recent improvements have been made in the biota modeling for these calculators, including newly derived biota intake rates, more comprehensive soil mass loading factors (MLFs), and more comprehensive soil to tissue transfer factors (TFs) for animals and soil to plant transfer factors (BV's). New biota have been added in both the produce and animal products categories that greatly improve the accuracy and utility of the PRG and DCC calculators and encompass greater geographic diversity on a national and international scale.
Gas hydrate cool storage system
Ternes, M.P.; Kedl, R.J.
1984-09-12
The invention presented relates to the development of a process utilizing a gas hydrate as a cool storage medium for alleviating electric load demands during peak usage periods. Several objectives of the invention are mentioned concerning the formation of the gas hydrate as storage material in a thermal energy storage system within a heat pump cycle system. The gas hydrate was formed using a refrigerant in water and an example with R-12 refrigerant is included. (BCS)
Airfoil, platform, and cooling passage measurements on a rotating transonic high-pressure turbine
Nickol, Jeremy B.
An experiment was performed at The Ohio State University Gas Turbine Laboratory for a film-cooled high-pressure turbine stage operating at design-corrected conditions, with variable rotor and aft purge cooling flow rates. Several distinct experimental programs are combined into one experiment and their results are presented. Pressure and temperature measurements in the internal cooling passages that feed the airfoil film cooling are used as boundary conditions in a model that calculates cooling flow rates and blowing ratio out of each individual film cooling hole. The cooling holes on the suction side choke at even the lowest levels of film cooling, ejecting more than twice the coolant as the holes on the pressure side. However, the blowing ratios are very close due to the freestream massflux on the suction side also being almost twice as great. The highest local blowing ratios actually occur close to the airfoil stagnation point as a result of the low freestream massflux conditions. The choking of suction side cooling holes also results in the majority of any additional coolant added to the blade flowing out through the leading edge and pressure side rows. A second focus of this dissertation is the heat transfer on the rotor airfoil, which features uncooled blades and blades with three different shapes of film cooling hole: cylindrical, diffusing fan shape, and a new advanced shape. Shaped cooling holes have previously shown immense promise on simpler geometries, but experimental results for a rotating turbine have not previously been published in the open literature. Significant improvement from the uncooled case is observed for all shapes of cooling holes, but the improvement from the round to more advanced shapes is seen to be relatively minor. The reduction in relative effectiveness is likely due to the engine-representative secondary flow field interfering with the cooling flow mechanics in the freestream, and may also be caused by shocks and other
Renewable heating and cooling is a set of alternative resources and technologies that can be used in place of conventional heating and cooling technologies for common applications such as water heating, space heating, space cooling and process heat.
International Nuclear Information System (INIS)
Brandt, K.; Krutzik, N.; Kaiser, A.
1982-01-01
For different dynamic soil properties and soil dampings - ranging from very soft to very rigid soil parameters - time histoires of displacements and accelerations as well as response spectra are calculated for several floors for the reactor building of a nuclear power plant using a finite element shell model. As regards the loadcase safety earthquake the computations are carried out for four different soil properties, and the response spectra of different floors are compared. In the loadcase exterior explosion, results for three different soils are obtained. All results are discussed and explained extensively. (Author) [pt
Design and Test of Wendelstein 7-X Water-Cooled Divertor Scraper
Energy Technology Data Exchange (ETDEWEB)
Boscary, J. [Max-Planck-Institut fur Plasmaphysik, EURATOM Association, Garching, Germany; Greuner, Henri [Max Planck Institute for Plasma Physics, Garching, Germany; Ehrke, Gunnar [Max Planck Institute of Plasma Physics, Greifswald, Germany; Boeswirth, Bernd [Max Planck Institute for Plasma Physics, Garching, Germany; Wang, Zhongwei [Max Planck Institute for Plasma Physics, Garching, Germany; Clark, Emily [The University of Tennessee, Knoxville; Lumsdaine, Arnold [ORNL; Tretter, Jorg [Max Planck Institute for Plasma Physics, Garching, Germany; Junghanns, Patrick [Max Planck Institute for Plasma Physics, Garching, Germany; Stadler, Reinhold [Max Planck Institute for Plasma Physics, Garching, Germany; McGinnis, William Dean [ORNL; Lore, Jeremy D. [ORNL; Team, W7-X [Max-Planck-Institut fur Plasmaphysik, Griefswald, Germany
2018-04-01
Heat load calculations have indicated the possible overloading of the ends of the water-cooled divertor facing the pumping gap beyond their technological limit. The intention of the scraper is the interception of some of the plasma fluxes both upstream and downstream before they reach the divertor surface. The scraper is divided into six modules of four plasma facing components (PFCs); each module has four PFCs hydraulically connected in series by two water boxes (inlet and outlet). A full-scale prototype of one module has been manufactured. Development activities have been carried out to connect the water boxes to the cooling pipes of the PFCs by tungsten inert gas internal orbital welding. This prototype was successfully tested in the GLADIS facility with 17 MW/m2 for 500 cycles. The results of these activities have confirmed the possible technological basis for a fabrication of the water-cooled scraper.
Building concept of cooling towers for WWER-1000 nuclear power plants
International Nuclear Information System (INIS)
Bucha, V.; David, M.
1984-01-01
A project is described of cooling towers with natural draught for the Temelin nuclear power plant. The concept proceeds from the classical design of the so-called Itterson type, i.e., the outer cladding of the draught stack is made of a monolithic reinforced concrete unit in the shape of a hyperboloid of revolution supported by a system of oblique supports mounted along the edge of the cooled water tank. The procedure is explained of the thermal calculation for the given operating conditions. The basic alternatives are considered of the choice of material and design of the cooling system. Questions are discussed relating to the design of the eliminator, the windwart wall and the shape of the shell of the draught stack and its loading by wind and seismic effects. (E.S.)
Cooling for SC devices of test cryomodule for ADS Injector II at IMP
Energy Technology Data Exchange (ETDEWEB)
Wang, L.; Wang, S. Y.; Sun, S.; Wang, S. H.; Liu, Y. Y. [Shanghai Institute of Applied Physics, CAS, Shanghai 201204 (China); Guo, X. L. [JiangSu University, Zhenjiang 212013 (China)
2014-01-29
The superconducting half-wave resonance cavities connected in series with superconducting solenoids will be applied to the Injector II of the Accelerator Driven Sub-critical System (ADS) to be built at the Modern Physics Institute, China. A test system has been developed for the purpose of performance test of the HWR cavities as well as validating the relevant technique for cooling the cavity and the solenoids together. It mainly comprises a cryogenic valve box (TVB), a test cryomodule (TCM1) and transfer lines. The TCM1 includes one HWR cavity, two superconducting solenoids, one cold BPM and their cooling system. The design of the TCM1 cryostat was carried out by the Shanghai Institute of Applied Physics (SINAP), CAS. Both the cavity and the solenoids will work at 4.4 K by bath cooling. The fast cooling down for the cavity from around 100 K to 120 K is required to avoid degrading of the cavity performance. After cool down and before energization, the solenoids should be warmed up to above 10 K and re-cooled down for the purpose of degaussing. The TCM1 can not only be cooled by using the dewar-filling system, but also operated by the refrigerator system. For the purpose of reducing the heat loads to the cold mass at 4 K from room temperature, thermal radiation shields cooled by liquid nitrogen flowing in tubing were employed. This paper presents the design details of cooling circuits and thermal shields of the TCM1 as well as related calculations and analyses.
Restaurant food cooling practices.
Brown, Laura Green; Ripley, Danny; Blade, Henry; Reimann, Dave; Everstine, Karen; Nicholas, Dave; Egan, Jessica; Koktavy, Nicole; Quilliam, Daniela N
2012-12-01
Improper food cooling practices are a significant cause of foodborne illness, yet little is known about restaurant food cooling practices. This study was conducted to examine food cooling practices in restaurants. Specifically, the study assesses the frequency with which restaurants meet U.S. Food and Drug Administration (FDA) recommendations aimed at reducing pathogen proliferation during food cooling. Members of the Centers for Disease Control and Prevention's Environmental Health Specialists Network collected data on food cooling practices in 420 restaurants. The data collected indicate that many restaurants are not meeting FDA recommendations concerning cooling. Although most restaurant kitchen managers report that they have formal cooling processes (86%) and provide training to food workers on proper cooling (91%), many managers said that they do not have tested and verified cooling processes (39%), do not monitor time or temperature during cooling processes (41%), or do not calibrate thermometers used for monitoring temperatures (15%). Indeed, 86% of managers reported cooling processes that did not incorporate all FDA-recommended components. Additionally, restaurants do not always follow recommendations concerning specific cooling methods, such as refrigerating cooling food at shallow depths, ventilating cooling food, providing open-air space around the tops and sides of cooling food containers, and refraining from stacking cooling food containers on top of each other. Data from this study could be used by food safety programs and the restaurant industry to target training and intervention efforts concerning cooling practices. These efforts should focus on the most frequent poor cooling practices, as identified by this study.
Core configuration of a gas-cooled reactor as a tritium production device for fusion reactor
Energy Technology Data Exchange (ETDEWEB)
Nakaya, H., E-mail: nakaya@nucl.kyushu-u.ac.jp [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 8190395 (Japan); Matsuura, H.; Nakao, Y. [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 8190395 (Japan); Shimakawa, S.; Goto, M.; Nakagawa, S. [Japan Atomic Energy Agency, 4002 Oarai, Ibaraki (Japan); Nishikawa, M. [Malaysia-Japan International Institute of Technology, UTM, Kuala Lumpur 54100 (Malaysia)
2014-05-01
The performance of a high-temperature gas-cooled reactor as a tritium production device is examined, assuming the compound LiAlO{sub 2} as the tritium-producing material. A gas turbine high-temperature reactor of 300 MWe nominal capacity (GTHTR300) is assumed as the calculation target, and using the continuous-energy Monte Carlo transport code MVP-BURN, burn-up simulations are carried out. To load sufficient Li into the core, LiAlO{sub 2} is loaded into the removable reflectors that surround the ring-shaped fuel blocks in addition to the burnable poison insertion holes. It is shown that module high-temperature gas-cooled reactors with a total thermal output power of 3 GW can produce almost 8 kg of tritium in a year.
Demand Response Load Following of Source and Load Systems
DEFF Research Database (Denmark)
Hu, Jianqiang; Cao, Jinde; Yong, Taiyou
2017-01-01
This paper presents a demand response load following strategy for an interconnected source and load system, in which we utilize traditional units and population of cooling thermostatically controlled loads (TCLs) to follow the mismatched power caused by the load activities and the renewable power...... injection in real time. In the demand side of power systems, these TCLs are often affiliated to a bus load agent and can be aggregated to multiple TCL aggregators. Firstly, aggregate evaluation of the TCL aggregator is carried out based on a bilinear aggregate model so as to derive the available regulation...
Sensitivity Analysis of Depletion Parameters for Heat Load Evaluation of PWR Spent Fuel Storage Pool
International Nuclear Information System (INIS)
Kim, In Young; Lee, Un Chul
2011-01-01
As necessity of safety re-evaluation for spent fuel storage facility has emphasized after the Fukushima accident, accuracy improvement of heat load evaluation has become more important to acquire reliable thermal-hydraulic evaluation results. As groundwork, parametric and sensitivity analyses of various storage conditions for Kori Unit 4 spent fuel storage pool and spent fuel depletion parameters such as axial burnup effect, operation history, and specific heat are conducted using ORIGEN2 code. According to heat load evaluation and parametric sensitivity analyses, decay heat of last discharged fuel comprises maximum 80.42% of total heat load of storage facility and there is a negative correlation between effect of depletion parameters and cooling period. It is determined that specific heat is most influential parameter and operation history is secondly influential parameter. And decay heat of just discharged fuel is varied from 0.34 to 1.66 times of average value and decay heat of 1 year cooled fuel is varied from 0.55 to 1.37 times of average value in accordance with change of specific power. Namely depletion parameters can cause large variation in decay heat calculation of short-term cooled fuel. Therefore application of real operation data instead of user selection value is needed to improve evaluation accuracy. It is expected that these results could be used to improve accuracy of heat load assessment and evaluate uncertainty of calculated heat load.
Rymszewicz, A; O'Sullivan, J J; Bruen, M; Turner, J N; Lawler, D M; Conroy, E; Kelly-Quinn, M
2017-09-01
The use of turbidity for indicating environmentally detrimental levels of suspended and colloidal matter in freshwater systems, and for defining acceptable water quality standards in national and European drinking water regulations, is well established. Turbidity is therefore frequently adopted as a surrogate for suspended sediment concentrations (SSC), or as a relative and objective measure of water clarity in monitoring programmes. Through systematic, controlled experimentation, we tested the response of 12 commercially available turbidity sensors, of various designs, to gauge their measurement consistency when benchmarked against pre-prepared sediment suspensions of known SSC. Results showed that despite calibration to a Formazin standard, sensor responses to identical SSC solutions (in the range of 20-1000 mg L -1 ) varied considerably. For a given SSC, up to five-fold differences in recorded turbidity were recorded across the tested instruments. Furthermore, inconsistent measurements were identified across instruments, regardless of whether they operated using backscatter or side-scatter optical principles. While the findings may have implications for compliance with turbidity-based water quality standards, they are less likely to be an issue when turbidity is being used as a surrogate for SSC, provided that instrument use remains constant and that instrument drift is not an issue. In this study, a field comparison of a subset of four study sensors showed that despite very different absolute turbidity readings for a given SSC, well correlated and reliable turbidity - SSC ratings were established (as evidenced by r 2 coefficients from 0.92 to 0.98). This led to reasonably consistent suspended sediment load estimates of between 64.7 and 70.8 tonnes for a rainfall event analysed. This study highlights the potential for issues to arise when interpreting water turbidity datasets that are often assumed to be comparable, in that measurement inconsistency of the
The Damaging Effects of Earthquake Excitation on Concrete Cooling Towers
International Nuclear Information System (INIS)
Abedi-Nik, Farhad; Sabouri-Ghomi, Saeid
2008-01-01
Reinforced concrete cooling towers of hyperbolic shell configuration find widespread application in utilities engaged in the production of electric power. In design of critical civil infrastructure of this type, it is imperative to consider all the possible loading conditions that the cooling tower may experience, an important loading condition in many countries is that of the earthquake excitation, whose influence on the integrity and stability of cooling towers is profound. Previous researches have shown that the columns supporting a cooling tower are sensitive to earthquake forces, as they are heavily loaded elements that do not possess high ductility, and understanding the behavior of columns under earthquake excitation is vital in structural design because they provide the load path for the self weight of the tower shell. This paper presents the results of a finite element investigation of a representative 'dry' cooling tower, using realistic horizontal and vertical acceleration data obtained from the recent and widely-reported Tabas, Naghan and Bam earthquakes in Iran. The results of both linear and nonlinear analyses are reported in the paper, the locations of plastic hinges within the supporting columns are identified and the ramifications of the plastic hinges on the stability of the cooling tower are assessed. It is concluded that for the (typical) cooling tower configuration analyzed, the columns that are instrumental in providing a load path are influenced greatly by earthquake loading, and for the earthquake data used in this study the representative cooling tower would be rendered unstable and would collapse under the earthquake forces considered
Cooled Water Production System,
The invention refers to the field of air conditioning and regards an apparatus for obtaining cooled water . The purpose of the invention is to develop...such a system for obtaining cooled water which would permit the maximum use of the cooling effect of the water -cooling tower.
International Nuclear Information System (INIS)
Farquhar, N.G.; Schwab, J.A.
1977-01-01
A system of heat exchangers is disclosed for cooling process fluids. The system is particularly applicable to cooling steam generator blowdown fluid in a nuclear plant prior to chemical purification of the fluid in which it minimizes the potential of boiling of the plant cooling water which cools the blowdown fluid
Hybrid radiator cooling system
France, David M.; Smith, David S.; Yu, Wenhua; Routbort, Jules L.
2016-03-15
A method and hybrid radiator-cooling apparatus for implementing enhanced radiator-cooling are provided. The hybrid radiator-cooling apparatus includes an air-side finned surface for air cooling; an elongated vertically extending surface extending outwardly from the air-side finned surface on a downstream air-side of the hybrid radiator; and a water supply for selectively providing evaporative cooling with water flow by gravity on the elongated vertically extending surface.
The future cooling tower; Fremtidens koeletaarn
Energy Technology Data Exchange (ETDEWEB)
Ibsen, C.H. (Vestas Aircoil A/S, Lem St. (Denmark)); Schneider, P. (Teknologisk Institut, AArhus (Denmark)); Haaning, N. (Ramboell A/S, Copenhagen (Denmark)); Lund, K. (Nyrup Plast A/S, Nyrup (Denmark)); Soerensen, Ole (MultiWing A/S, Vedbaek (Denmark)); Dalsgaard, T. (Silhorko A/S, Skanderborg (Denmark)); Pedersen, Michael (Skive Kommune, Skive (Denmark))
2011-03-15
This project has designed and built a pilot-scale cooling tower with an output of up to 100 kW for which good correlation has been ascertained between measured and calculated values for output and pressure loss. The new cooling tower will save approximately 15% of electricity consumption compared with the widespread dry coolers. The pilot tower uses rainwater so that both water consumption and electricity consumption are saved in softening plants. On the basis of this cooling tower, models have been made and these have been implemented in PackCalc II in order to calculate electricity and other operating savings. (Energy 11)
Directory of Open Access Journals (Sweden)
Chen X.
2006-11-01
Full Text Available Le problème considéré ici est celui de l'évaluation des efforts excitateurs de deuxième ordre (en mode somme, c'est-à-dire prenant place aux sommes deux à deux des fréquences de houle sur des plates-formes à lignes tendues. Ces efforts sont tenus pour responsables de comportements résonnants (en roulis, tangage et pilonnement observés lors d'essais en bassin et pourraient réduire sensiblement la durée de vie en fatigue des tendons. Des résultats sont tout d'abord présentés pour une structure simplifiée, consistant en 4 cylindres verticaux reposant sur le fond marin. L'intérêt de cette géométrie est que tous les calculs peuvent être menés à terme de façon quasi analytique. Les résultats obtenus permettent d'illustrer le haut degré d'interaction entre les colonnes, et la faible décroissance du potentiel de diffraction de deuxième ordre avec la profondeur. On présente ensuite des résultats pour une plate-forme réelle, celle de Snorre. Tension Leg Platforms (TLP's are now regarded as a promising technology for the development of deep offshore fields. As the water depth increases however, their natural periods of heave, roll and pitch tend to increase as well (roughly to the one-half power, and it is not clear yet what the maximum permissible values for these natural periods can be. For the Snorre TLP for instance, they are only about 2. 5 seconds, which seems to be sufficiently low since there is very limited free wave energy at such periods. Model tests, however, have shown some resonant response in sea states with peak periods of about 5 seconds. Often referred to as springing , this resonant motion can severely affect the fatigue life of tethers and increase their design loads. In order to calculate this springing motion at the design stage, it is necessary to identify and evaluate both the exciting loads and the mechanisms of energy dissipation. With the help of the French Norwegian Foundation a joint effort was
Cooling Performance of ALIP according to the Air or Sodium Cooling Type
Energy Technology Data Exchange (ETDEWEB)
Ye, Huee-Youl; Yoon, Jung; Lee, Tae-Ho [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2015-05-15
ALIP pumps the liquid sodium by Lorentz force produced by the interaction of induced current in the liquid metal and their associated magnetic field. Even though the efficiency of the ALIP is very low compared to conventional mechanical pumps, it is very useful due to the absence of moving parts, low noise and vibration level, simplicity of flow rate regulation and maintenance, and high temperature operation capability. Problems in utilization of ALIP concern a countermeasure for elevation of internal temperature of the coil due to joule heating and how to increase magnetic flux density of Na channel gap. The conventional ALIP usually used cooling methods by circulating the air or water. On the other hand, GE-Toshiba developed a double stator pump adopting the sodium-immersed self-cooled type, and it recovered the heat loss in sodium. Therefore, the station load factor of the plant could be reduced. In this study, the cooling performance with cooling types of ALIP is analyzed. We developed thermal analysis models to evaluate the cooling performance of air or sodium cooling type of ALIP. The cooling performance is analyzed for operating parameters and evaluated with cooling type. 1-D and 3-D thermal analysis model for IHTS ALIP was developed, and the cooling performance was analyzed for air or sodium cooling type. The cooling performance for air cooling type was better than sodium cooling type at higher air velocity than 0.2 m/s. Also, the air temperature of below 270 .deg. demonstrated the better cooling performance as compared to sodium.
Liquid gallium cooling of silicon crystals in high intensity photon beams
International Nuclear Information System (INIS)
Smither, R.K.; Forster, G.A.; Bilderback, D.H.; Bedzyk, M.; Finkelstein, K.; Henderson, C.; White, J.; Berman, L.E.; Stefan, P.; Oversluizen, T.
1989-01-01
The high-brilliance, insertion-device-based photon beams of the next generation of synchrotron sources (Argonne's APS and Grenoble's ESRF) will deliver large thermal loads (1--10 kW) to the first optical elements. Considering the problems that present synchrotron users are experiencing with beams from recently installed insertion devices, new and improved methods of cooling these first optical elements, particularly when they are diffraction crystals, are clearly needed. A series of finite element calculations were performed to test the efficiency of new cooling geometries and various cooling fluids. The best results were obtained with liquid Ga metal flowing in channels just below the surface of the crystal. Ga was selected because of its good thermal conductivity and thermal capacity, low melting point, high boiling point, low kinetic viscosity, and very low vapor pressure. Its very low vapor pressure, even at elevated temperatures, makes it especially attractive in UHV conditions. A series of experiments were conducted at CHESS in February of 1988 that compared liquid gallium-cooled silicon diffraction crystals with water-cooled crystals. A six-pole wiggler beam was used to perform these tests on three different Si crystals, two with new cooling geometries and the one presently in use. A special high-pressure electromagnetic induction pump, recently developed at Argonne, was used to circulate the liquid gallium through the silicon crystals. In all experiments, the specially cooled crystal was used as the first crystal in a two crystal monochromator. An infrared camera was used to monitor the thermal profiles and correlated them with rocking curve measurements. A second set of cooling experiments were conducted in June of 1988 that used the intense, highly collimated beam from the newly installed ANL/CHESS undulator
Energy Technology Data Exchange (ETDEWEB)
Kim, Myoung Jun; Lee, Hee Joon [Kookmin Univ., Seoul (Korea, Republic of); Moon, Joo Hyung; Bae, Youngmin; Kim, Youngin [Korea Atomic Energy Research Institute, Daejeon (Korea, Republic of)
2014-05-15
For the long operation of secondary passive cooling system, however, water level goes down by evaporation in succession at emergency cooling tank. At the end there would be no place to dissipate heat from condensation heat exchanger. Therefore, steam cooling heat exchanger is put on the top of emergency cooling tank to maintain appropriate water level by collecting evaporating steam. Steam cooling heat exchanger is installed inside an air chimney and evaporated steam is cooled down by air natural convection. In this study, thermal sizing of steam cooling heat exchanger under air natural convection was conducted by TSCON program for the design of experimental setup as shown in Fig. 2. Thermal sizing of steam cooling heat exchanger tube under air natural convection was conducted by TSCON program for the design of experimental setup. 25 - 1' tubes which has a length 1687 mm was determined as steam cooling heat exchanger at 2 kW heat load and 100 liter water pool in emergency cooling tank (experimental limit condition). The corresponding width of two tubes is 50 mm and has 5 by 5 tube array for heat exchanger.
International Nuclear Information System (INIS)
Kim, Myoung Jun; Lee, Hee Joon; Moon, Joo Hyung; Bae, Youngmin; Kim, Youngin
2014-01-01
For the long operation of secondary passive cooling system, however, water level goes down by evaporation in succession at emergency cooling tank. At the end there would be no place to dissipate heat from condensation heat exchanger. Therefore, steam cooling heat exchanger is put on the top of emergency cooling tank to maintain appropriate water level by collecting evaporating steam. Steam cooling heat exchanger is installed inside an air chimney and evaporated steam is cooled down by air natural convection. In this study, thermal sizing of steam cooling heat exchanger under air natural convection was conducted by TSCON program for the design of experimental setup as shown in Fig. 2. Thermal sizing of steam cooling heat exchanger tube under air natural convection was conducted by TSCON program for the design of experimental setup. 25 - 1' tubes which has a length 1687 mm was determined as steam cooling heat exchanger at 2 kW heat load and 100 liter water pool in emergency cooling tank (experimental limit condition). The corresponding width of two tubes is 50 mm and has 5 by 5 tube array for heat exchanger
Holtz, Ronald; Matic, Peter; Mott, David
2013-03-01
Warfighter performance can be adversely affected by heat load and weight of equipment. Current tactical vest designs are good insulators and lack ventilation, thus do not provide effective management of metabolic heat generated. NRL has undertaken a systematic study of tactical vest thermal management, leading to physics-based strategies that provide improved cooling without undesirable consequences such as added weight, added electrical power requirements, or compromised protection. The approach is based on evaporative cooling of sweat produced by the wearer of the vest, in an air flow provided by ambient wind or ambulatory motion of the wearer. Using an approach including thermodynamic analysis, computational fluid dynamics modeling, air flow measurements of model ventilated vest architectures, and studies of the influence of fabric aerodynamic drag characteristics, materials and geometry were identified that optimize passive cooling of tactical vests. Specific architectural features of the vest design allow for optimal ventilation patterns, and selection of fabrics for vest construction optimize evaporation rates while reducing air flow resistance. Cooling rates consistent with the theoretical and modeling predictions were verified experimentally for 3D mockups.
Liu, W; Collins, C M; Smith, M B
2005-03-01
A numerical model of a female body is developed to study the effects of different body types with different coil drive methods on radio-frequency magnetic ( B 1 ) field distribution, specific energy absorption rate (SAR), and intrinsic signal-to-noise ratio (ISNR) for a body-size birdcage coil at 64 and 128 MHz. The coil is loaded with either a larger, more muscular male body model (subject 1) or a newly developed female body model (subject 2), and driven with two-port (quadrature), four-port, or many (ideal) sources. Loading the coil with subject 1 results in significantly less homogeneous B 1 field, higher SAR, and lower ISNR than those for subject 2 at both frequencies. This dependence of MR performance and safety measures on body type indicates a need for a variety of numerical models representative of a diverse population for future calculations. The different drive methods result in similar B 1 field patterns, SAR, and ISNR in all cases.
Cool metal roofing tested for energy efficiency and sustainability
Energy Technology Data Exchange (ETDEWEB)
Miller, W.A.; Desjarlais, A. [Oak Ridge National Laboratory, Oakridge, TN (United States); Parker, D.S. [Florida Solar Energy Center, Cocoa, FL (United States); Kriner, S. [Metal Construction Association, Glenview, IL (United States)
2004-07-01
A 3 year field study was conducted in which temperature, heat flow, reflectance and emittance field data were calculated for 12 different painted and unpainted metal roofs exposed to weathering at an outdoor test facility at Oak Ridge National Laboratory in Oakridge, Tennessee. In addition, the Florida Solar Energy Center tested several Habitat for Humanity homes during one summer in Fort Myers, Florida. The objective was to determine how cooling and heating energy loads in a building are affected by the solar reflectance and infrared emittance of metal roofs. The Habitat for Humanities houses had different roofing systems which reduced the attic heat gain. White reflective roofs were shown to reduce cooling energy needs by 18 to 26 per cent and peak demand by 28 to 35 per cent. High solar reflectance and high infrared emittance roofs incur surface temperatures that are about 3 degrees C warmer than the ambient air temperature. A dark absorptive roof exceeds the ambient air temperature by more than 40 degrees C. It hot climates, a high solar reflectance and high infrared emittance roof can reduce the air conditioning load and reduce peak energy demands on the utility. It was concluded that an informed decision of the roof surface properties of reflectance and emittance can significantly reduce energy costs for homeowners and builders in hot climates. 7 refs., 2 tabs., 7 figs.
Restaurant Food Cooling Practices†
BROWN, LAURA GREEN; RIPLEY, DANNY; BLADE, HENRY; REIMANN, DAVE; EVERSTINE, KAREN; NICHOLAS, DAVE; EGAN, JESSICA; KOKTAVY, NICOLE; QUILLIAM, DANIELA N.
2017-01-01
Improper food cooling practices are a significant cause of foodborne illness, yet little is known about restaurant food cooling practices. This study was conducted to examine food cooling practices in restaurants. Specifically, the study assesses the frequency with which restaurants meet U.S. Food and Drug Administration (FDA) recommendations aimed at reducing pathogen proliferation during food cooling. Members of the Centers for Disease Control and Prevention’s Environmental Health Specialists Network collected data on food cooling practices in 420 restaurants. The data collected indicate that many restaurants are not meeting FDA recommendations concerning cooling. Although most restaurant kitchen managers report that they have formal cooling processes (86%) and provide training to food workers on proper cooling (91%), many managers said that they do not have tested and verified cooling processes (39%), do not monitor time or temperature during cooling processes (41%), or do not calibrate thermometers used for monitoring temperatures (15%). Indeed, 86% of managers reported cooling processes that did not incorporate all FDA-recommended components. Additionally, restaurants do not always follow recommendations concerning specific cooling methods, such as refrigerating cooling food at shallow depths, ventilating cooling food, providing open-air space around the tops and sides of cooling food containers, and refraining from stacking cooling food containers on top of each other. Data from this study could be used by food safety programs and the restaurant industry to target training and intervention efforts concerning cooling practices. These efforts should focus on the most frequent poor cooling practices, as identified by this study. PMID:23212014
Component Cooling Heat Exchanger Heat Transfer Capability Operability Monitoring
International Nuclear Information System (INIS)
Mihalina, M.; Djetelic, N.
2010-01-01
.g. using CC Heat Exchanger bypass valves for CC temperature control, variation of plant heat loads, pumps performance, and day-night temperature difference, with lagging effects on heat transfer dynamics). Krsko NPP is continuously monitoring the Component Cooling (CC) Heat Exchanger performance using the on-line process information system (PIS). By defining the mathematical algorithm, it is possible to continuously evaluate the CC Heat Exchanger operability by verifying if the heat transfer rate calculation is in accordance with the heat exchanger design specification sheet requirements. These calculations are limited to summer periods only when the bypass valves are neither throttled nor open.(author).
Liquid gallium cooling of silicon crystals in high intensity photon beam
International Nuclear Information System (INIS)
Smither, R.K.; Forster, G.A.; Bilderback, D.H.
1988-11-01
The high-brilliance, insertion-device-based, photon beams of the next generation of synchrotron sources will deliver large thermal loads (1 kW to 10 kW) to the first optical elements. Considering the problems that present synchrotron users are experiencing with beams from recently installed insertion devices, new and improved methods of cooling these first optical elements, particularly when they are diffraction crystals, are clearly needed. A series of finite element calculations were performed to test the efficiency of new cooling geometries and new cooling fluids. The best results were obtained with liquid Ga metal flowing in channels just below the surface of the crystal. Ga was selected because of its good thermal conductivity and thermal capacity, low melting point, high boiling point, low kinetic viscosity, and very low vapor pressure. Its very low vapor pressure, even at elevated temperatures, makes it especially attractive in uhv conditions. A series of experiments were conducted at CHESS in February of 1988 that compared liquid gallium cooled silicon diffraction crystals with water cooled crystals. 2 refs., 16 figs., 1 tab
International Nuclear Information System (INIS)
Weaver, K.D.; Herring, J.S.; Macdonald, P.E.
2001-01-01
Various methods have been proposed to ''incinerate'' or ''transmute'' the current inventory of transuranic waste (TRU) that exits in spent light-water-reactor (LWR) fuel, and weapons plutonium. These methods include both critical (e.g., fast reactors) and non-critical (e.g., accelerator transmutation) systems. The work discussed here is part of a larger effort at the Idaho National Engineering and Environmental Laboratory (INEEL) and at the Massachusetts Institute of Technology (MIT) to investigate the suitability of lead and lead-alloy cooled fast reactors for producing low-cost electricity as well as for actinide burning. The neutronics of non fertile fuel loaded with 20 or 30-wt% light water reactor (LWR) plutonium plus minor actinides for use in a lead-bismuth cooled fast reactor are discussed in this paper, with an emphasis on the fuel cycle life and isotopic content. Calculations show that the average actinide burn rate is similar for both the sodium and lead-bismuth cooled cases ranging from -1.02 to -1.16 g/MWd, compared to a typical LWR actinide generation rate of 0.303 g/MWd. However, when using the same parameters, the sodium-cooled case went subcritical after 0.2 to 0.8 effective full power years, and the lead-bismuth cooled case ranged from 1.5 to 4.5 effective full power years. (author)
Cryogenic analysis of forced-cooled, superconducting TF magnets for compact tokamak reactors
International Nuclear Information System (INIS)
Kerns, J.A.; Slack, D.S.; Miller, J.R.
1988-01-01
Current designs for compact tokamak reactors require the toroidal- field (TF) superconducting magnets to produce fields from 10 to 15 T at the winding pack, using high-current densities to high nuclear heat loads (greater than 1 kW/coil in some instances), which are significantly greater than the conduction and radiation heat loads for which cryogenic systems are usually designed. A cryogenic system for the TF winding pack for two such tokamak designs has been verified by performing a detailed, steady-state heat-removal analysis. Helium properties along the forced-cooled conductor flow path for a range of nuclear heat loads have been calculated. The results and implications of this analysis are presented. 12 refs., 6 figs
Model-based energy monitoring and diagnosis of telecommunication cooling systems
International Nuclear Information System (INIS)
Sorrentino, Marco; Acconcia, Matteo; Panagrosso, Davide; Trifirò, Alena
2016-01-01
A methodology is proposed for on-line monitoring of cooling load supplied by Telecommunication (TLC) cooling systems. Sensible cooling load is estimated via a proportional integral controller-based input estimator, whereas a lumped parameters model was developed aiming at estimating air handling units (AHUs) latent heat load removal. The joint deployment of above estimators enables accurate prediction of total cooling load, as well as of related AHUs and free-coolers energy performance. The procedure was then proven effective when extended to cooling systems having a centralized chiller, through model-based estimation of a key performance metric, such as the energy efficiency ratio. The results and experimental validation presented throughout the paper confirm the suitability of the proposed procedure as a reliable and effective energy monitoring and diagnostic tool for TLC applications. Moreover, the proposed modeling approach, beyond its direct contribution towards smart use and conservation of energy, can be fruitfully deployed as a virtual sensor of removed heat load into a variety of residential and industrial applications. - Highlights: • Accurate cooling load prediction in telecommunication rooms. • Development of an input-estimator for sensible cooling load simulation. • Model-based estimation of latent cooling load. • Model-based prediction of centralized chiller energy performance in central offices. • Diagnosis-oriented application of proposed cooling load estimator.
Performance of cooling installation for cyclotron Decy-13
International Nuclear Information System (INIS)
Edi Trijono Budisantoso; Suprapto; Sutadi
2015-01-01
Has been calculated the cooling installation performance of Decy-13 cyclotron. The cooling installation is analysed based on the technical specifications of each cooling component to proof the results of the design and implementation of installations meet the cooling requirement. Analysis of loss of pressure and flow rate in the piping installation is done empirically using Hazen-Williams equation while the analysis of heat transfer processes in the cooling tower is done using the help of psychometric charts that available. Cooling component consists of a condenser and associated piping systems with cooling towers and equipped with a pump to push the circulation of cooling. The calculations show that the installation of the condenser cooler uses the cooling tower LiangChi LBC-30 with a booster pump Grundfos 4 kW NF30-36T powered 47kW able to transfer heat with the coolant flow rate 136 lpm, input to output coolant pressure difference 2.1atm and the cooling temperature difference 5 °C. Conclusion of the calculation is the technical specifications of cooling components and installation already meets the needs of the cooling expected. (author)
Burial container subsidence load stress calculations
International Nuclear Information System (INIS)
Veith, E.M.
1995-11-01
This document captures the supporting analyses conducted to determine if the LLCE (Long-Length Contaminated Equipment) burial containers are structurally adequate under different trench closure scenarios. The LLCE is equipment that was inside tank farm tanks
Hierarchy of Loading Calculations | ECHO | US EPA
ECHO, Enforcement and Compliance History Online, provides compliance and enforcement information for approximately 800,000 EPA-regulated facilities nationwide. ECHO includes permit, inspection, violation, enforcement action, and penalty information about facilities regulated under the Clean Air Act (CAA) Stationary Source Program, Clean Water Act (CWA) National Pollutant Elimination Discharge System (NPDES), and/or Resource Conservation and Recovery Act (RCRA). Information also is provided on surrounding demographics when available.
Final Report for 'ParSEC-Parallel Simulation of Electron Cooling''
International Nuclear Information System (INIS)
David L Bruhwiler
2005-01-01
The Department of Energy has plans, during the next two or three years, to design an electron cooling section for the collider ring at RHIC (Relativistic Heavy Ion Collider) [1]. Located at Brookhaven National Laboratory (BNL), RHIC is the premier nuclear physics facility. The new cooling section would be part of a proposed luminosity upgrade [2] for RHIC. This electron cooling section will be different from previous electron cooling facilities in three fundamental ways. First, the electron energy will be 50 MeV, as opposed to 100's of keV (or 4 MeV for the electron cooling system now operating at Fermilab [3]). Second, both the electron beam and the ion beam will be bunched, rather than being essentially continuous. Third, the cooling will take place in a collider rather than in a storage ring. Analytical work, in combination with the use and further development of the semi-analytical codes BETACOOL [4,5] and SimCool [6,7] are being pursued at BNL [8] and at other laboratories around the world. However, there is a growing consensus in the field that high-fidelity 3-D particle simulations are required to fully understand the critical cooling physics issues in this new regime. Simulations of the friction coefficient, using the VORPAL code [9], for single gold ions passing once through the interaction region, have been compared with theoretical calculations [10,11], and the results have been presented in conference proceedings papers [8,12,13,14] and presentations [15,16,17]. Charged particles are advanced using a fourth-order Hermite predictor corrector algorithm [18]. The fields in the beam frame are obtained from direct calculation of Coulomb's law, which is more efficient than multipole-type algorithms for less than ∼ 10 6 particles. Because the interaction time is so short, it is necessary to suppress the diffusive aspect of the ion dynamics through the careful use of positrons in the simulations, and to run 100's of simulations with the same physical
Energy Technology Data Exchange (ETDEWEB)
Suzuki, S; Ito, Y; Kazawa, Y
1975-02-05
Object: To provide a water cooling coil in a toroidal nuclear fusion device, in which coil is formed into a small-size in section so as not to increase dimensions, weight or the like of machineries including the coil. Structure: A conductor arranged as an outermost layer of a multiple-wind water cooling coil comprises a hollow conductor, which is directly cooled by fluid, and as a consequence, a solid conductor disposed interiorly thereof is cooled indirectly.
Internally cooled V-shape inclined monochromator
Czech Academy of Sciences Publication Activity Database
Oberta, Peter; Áč, V.; Hrdý, Jaromír
2008-01-01
Roč. 15, - (2008), 8-11 ISSN 0909-0495 R&D Projects: GA AV ČR IAA100100716 Grant - others:VEGA(SK) 1/4134/07 Institutional research plan: CEZ:AV0Z10100522 Keywords : inclined monochromator * heat load * internal cooling Subject RIV: BH - Optics, Masers, Lasers Impact factor: 2.333, year: 2008
Radiant Heating and Cooling Systems. Part two
DEFF Research Database (Denmark)
Kim, Kwan Woo; Olesen, Bjarne W.
2015-01-01
Control of the heating and cooling system needs to be able to maintain the indoor temperatures within the comfort range under the varying internal loads and external climates. To maintain a stable thermal environment, the control system needs to maintain the balance between the heat gain...
Transient Three-Dimensional Analysis of Side Load in Liquid Rocket Engine Nozzles
Wang, Ten-See
2004-01-01
Three-dimensional numerical investigations on the nozzle start-up side load physics were performed. The objective of this study is to identify the three-dimensional side load physics and to compute the associated aerodynamic side load using an anchored computational methodology. The computational methodology is based on an unstructured-grid, and pressure-based computational fluid dynamics formulation, and a simulated inlet condition based on a system calculation. Finite-rate chemistry was used throughout the study so that combustion effect is always included, and the effect of wall cooling on side load physics is studied. The side load physics captured include the afterburning wave, transition from free- shock to restricted-shock separation, and lip Lambda shock oscillation. With the adiabatic nozzle, free-shock separation reappears after the transition from free-shock separation to restricted-shock separation, and the subsequent flow pattern of the simultaneous free-shock and restricted-shock separations creates a very asymmetric Mach disk flow. With the cooled nozzle, the more symmetric restricted-shock separation persisted throughout the start-up transient after the transition, leading to an overall lower side load than that of the adiabatic nozzle. The tepee structures corresponding to the maximum side load were addressed.
International Nuclear Information System (INIS)
Kaznovsky, S.
1995-01-01
This final report involves the calculation and experimental examination and ensuring the seismic resistance of the reactor equipment and pipelines at start up and operation of WWER type nuclear power plants. Shake table experiments performed at the Paks NPP are included. Namely the following devices of the emergency cooling system were tested: pump of low pressure; valve of low pressure; intermediate heat exchanger. The following values were determined: natural frequencies and vibration decrements and the main modes of normal vibrations for the heat exchanger
Desiccant-assisted cooling fundamentals and applications
Brum, Nisio
2014-01-01
The increasing concern with indoor air quality has led to air-quality standards with increased ventilation rates. Although increasing the volume flow rate of outside air is advisable from the perspective of air-quality, it is detrimental to energy consumption, since the outside air has to be brought to the comfort condition before it is insufflated to the conditioned ambient. Moreover, the humidity load carried within outside air has challenging HVAC engineers to design cooling units which are able to satisfactorily handle both sensible and latent contributions to the thermal load. This constitutes a favorable scenario for the use of solid desiccants to assist the cooling units. In fact, desiccant wheels have been increasingly applied by HVAC designers, allowing distinct processes for the air cooling and dehumidification. In fact, the ability of solid desiccants in moisture removal is effective enough to allow the use of evaporative coolers, in opposition to the traditional vapor-compression cycle, resultin...
DEFF Research Database (Denmark)
Raun Gottfredsen, F.
In this thesis results from experiments on mortar joints and masonry as well as methods of calculation of strength and deformation of laterally loaded masonry are presented. The strength and deformation capacity of mortar joints have been determined from experiments involving a constant compressive...... stress and increasing shear. The results show a transition to pure friction as the cohesion is gradually destroyed. An interface model of a mortar joint that can take into account this aspect has been developed. Laterally loaded masonry panels have also been tested and it is found to be characteristic...... that laterally loaded masonry exhibits a non-linear load-displacement behaviour with some ductility....
Energy Technology Data Exchange (ETDEWEB)
Valgas, Helio Moreira; Pinto, Roberto del Giudice R.; Franca, Carlos [Companhia Energetica de Minas Gerais (CEMIG), Belo Horizonte, MG (Brazil); Lambert-Torres, Germano; Silva, Alexandre P. Alves da; Pires, Robson Celso; Costa, Junior, Roberto Affonso [Escola Federal de Engenharia de Itajuba, MG (Brazil)
1994-12-31
Accurate dynamic load models allow more precise calculations of power system controls and stability limits, which are critical mainly in the operation planning of power systems. This paper describes the development of a computer program (software) for static and dynamic load model studies using the measurement approach for the CEMIG system. Two dynamic load model structures are developed and tested. A procedure for applying a set of measured data from an on-line transient recording system to develop load models is described. (author) 6 refs., 17 figs.
Energy Technology Data Exchange (ETDEWEB)
Delfani, Shahram; Esmaeelian, Jafar; Karami, Maryam [Department of Installation, Building and Housing Research Center (BHRC), PO Box 13145-1696, Tehran (Iran, Islamic Republic of); Pasdarshahri, Hadi [Department of Mechanical Engineering, Tarbiat Modares University, PO Box 14115-143, Tehran (Iran, Islamic Republic of)
2010-11-15
The performance of indirect evaporative cooling system (IEC) to pre-cool air for a conventional mechanical cooling system has been investigated for four cities of Iran. For this purpose, a combined experimental setup consisting of an IEC unit followed by a packaged unit air conditioner (PUA) was designed, constructed and tested. Two air simulators were designed and used to simulate indoor heating load and outdoor design conditions. Using of experimental data and an appropriate analytical method, the performance and energy reduction capability of combined system has been evaluated through the cooling season. The results indicate IEC can reduce cooling load up to 75% during cooling seasons. Also, 55% reduction in electrical energy consumption of PUA can be obtained. (author)
Gov. Arnold Schwarzenegger, second from left, a sample from the Cool Colors Project, a roof product ) (Jeff Chiu - AP) more Cool Colors make the front page of The Sacramento Bee (3rd highest circulation newspaper in California) on 14 August 2006! Read the article online or as a PDF. The Cool Colors Project
Energy Technology Data Exchange (ETDEWEB)
Glienicke, J.; Lindloff, K.; Medhioub, M.
1997-12-31
The reliable pre-calculation of the important axial bearing parameters is of decisive importance for the safe running of high speed rotors with high axial thrust. However, the computer programs available now contain simplified assumptions which can lead to considerable discrepancies between measured and calculated values at high speeds of sliding and high specific loads. By expanding the existing sliding bearing computer program, in which the exact segment geometry, the local lubricating film turbulence, the centrifugal forces and entry losses of the oil, the flow resistance, both incoming and outgoing, the thermal conduction in the tracking ring and the bearing, the thermal pocket mixing, the elastic and thermal segment deformation and the coupling of the lubrication films in double-acting axial bearings are now included, good agreement between measured and calculated results is obtained for all bearing shapes examined. (orig./AKF) [Deutsch] Fuer den betriebssicheren Lauf hochtouriger Rotoren mit hohem Axialschub ist die zuverlaessige Vorausberechnung der massgebenden Axiallager-Kennwerte von entscheidender Bedeutung. Die heute verfuegbaren Rechenprogramme enthalten jedoch vereinfachende Annahmen, die bei hohen Gleitgeschwindigkeiten und hohen spezifischen Belastungen zu wesentlichen Abweichungen zwischen Mess- und Rechenwerten fuehren koennen. Durch Erweiterung eines vorhandenen Gleitlager-Rechenprogramms, in dem nun die genaue Segmentgeometrie, die lokale Schmierfilmturbulenz, die Fliehkraefte und Eintrittsverluste des Oels, die Durchflusswiderstaende im Zu- und Abfluss, die Waermeleitung in Spurscheibe und Lager, die thermische Taschenmischung, die elastischen und thermischen Segmentverformungen und die Kopplung der Schmierfilme bei doppeltwirkenden Axiallagern erfasst werden, wird fuer alle untersuchten Lagerbauformen eine gute Uebereinstimmung von Mess- und Rechenwerten erreicht. (orig./AKF)
Cooling devices and methods for use with electric submersible pumps
Jankowski, Todd A; Hill, Dallas D
2014-12-02
Cooling devices for use with electric submersible pump motors include a refrigerator attached to the end of the electric submersible pump motor with the evaporator heat exchanger accepting all or a portion of the heat load from the motor. The cooling device can be a self-contained bolt-on unit, so that minimal design changes to existing motors are required.
Simulated Measurements of Cooling in Muon Ionization Cooling Experiment
Energy Technology Data Exchange (ETDEWEB)
Mohayai, Tanaz [IIT, Chicago; Rogers, Chris [Rutherford; Snopok, Pavel [Fermilab
2016-06-01
Cooled muon beams set the basis for the exploration of physics of flavour at a Neutrino Factory and for multi-TeV collisions at a Muon Collider. The international Muon Ionization Cooling Experiment (MICE) measures beam emittance before and after an ionization cooling cell and aims to demonstrate emittance reduction in muon beams. In the current MICE Step IV configuration, the MICE muon beam passes through low-Z absorber material for reducing its transverse emittance through ionization energy loss. Two scintillating fiber tracking detectors, housed in spectrometer solenoid modules upstream and downstream of the absorber are used for reconstructing position and momentum of individual muons for calculating transverse emittance reduction. However, due to existence of non-linear effects in beam optics, transverse emittance growth can be observed. Therefore, it is crucial to develop algorithms that are insensitive to this apparent emittance growth. We describe a different figure of merit for measuring muon cooling which is the direct measurement of the phase space density.
Dustproof cooling of the electrical box
Directory of Open Access Journals (Sweden)
Nemec Patrik
2018-01-01
Full Text Available In present are electrical boxes cooled by air through the intake hole on the bottom electrical box to the box space with electrotechnical elements and exhaust through the hole at the top to the surrounding by natural convection. This cooling method is effective but operate with the risk of contamination electrotechnical elements by dust sucking from surrounding air. The goal of this work is solution of the dustproof cooling of the electrical box by natural convection. The work deal with design of the device with the heat transfer by the phase change of the working fluid and experimental measuring its thermal performance at the cooling electrotechnical elements loaded by heat 1 200 W in the dustproof electrical box.
Cooling Performance Analysis of ThePrimary Cooling System ReactorTRIGA-2000Bandung
Irianto, I. D.; Dibyo, S.; Bakhri, S.; Sunaryo, G. R.
2018-02-01
The conversion of reactor fuel type will affect the heat transfer process resulting from the reactor core to the cooling system. This conversion resulted in changes to the cooling system performance and parameters of operation and design of key components of the reactor coolant system, especially the primary cooling system. The calculation of the operating parameters of the primary cooling system of the reactor TRIGA 2000 Bandung is done using ChemCad Package 6.1.4. The calculation of the operating parameters of the cooling system is based on mass and energy balance in each coolant flow path and unit components. Output calculation is the temperature, pressure and flow rate of the coolant used in the cooling process. The results of a simulation of the performance of the primary cooling system indicate that if the primary cooling system operates with a single pump or coolant mass flow rate of 60 kg/s, it will obtain the reactor inlet and outlet temperature respectively 32.2 °C and 40.2 °C. But if it operates with two pumps with a capacity of 75% or coolant mass flow rate of 90 kg/s, the obtained reactor inlet, and outlet temperature respectively 32.9 °C and 38.2 °C. Both models are qualified as a primary coolant for the primary coolant temperature is still below the permitted limit is 49.0 °C.
KUEBEL. A Fortran program for computation of cooling-agent-distribution within reactor fuel-elements
International Nuclear Information System (INIS)
Inhoven, H.
1984-12-01
KUEBEL is a Fortran-program for computation of cooling-agent-distribution within reactor fuel-elements or -zones of theirs. They may be assembled of max. 40 cooling-channels with laminar up to turbulent type of flow (respecting Reynolds' coefficients up to 2.0E+06) at equal pressure loss. Flow-velocity, dynamic flow-, contraction- and friction-losses will be calculated for each channel and for the total zone. Other computations will present mean heat-up of cooling-agent, mean outlet-temperature of the core, boiling-temperature and absolute pressure at flow-outlet. All characteristic coolant-values, including the factor of safety for flow-instability of the most-loaded cooling gap are computed by 'KUEBEL' too. Absolute pressure at flow-outlet or is-factor may be defined as dependent or independent variables of the program alternatively. In latter case 3 variations of solution will be available: Adapted flow of cooling-agent, inlet-temperature of the core and thermal power. All calculations can be done alternatively with variation of parameters: flow of cooling-agent, inlet-temperature of the core and thermal power, which are managed by the program itself. 'KUEBEL' is able to distinguish light- and heavy-water coolant, flow-direction of coolant and fuel elements with parallel, rectangular, respectively concentric, cylindrical shape of their gaps. Required material specifics are generated by the program. Segments of fuel elements or constructively unconnected gaps can also be computed by means of interposition of S.C. 'phantom channels'. (orig.) [de
Cooling water distribution system
Orr, Richard
1994-01-01
A passive containment cooling system for a nuclear reactor containment vessel. Disclosed is a cooling water distribution system for introducing cooling water by gravity uniformly over the outer surface of a steel containment vessel using an interconnected series of radial guide elements, a plurality of circumferential collector elements and collector boxes to collect and feed the cooling water into distribution channels extending along the curved surface of the steel containment vessel. The cooling water is uniformly distributed over the curved surface by a plurality of weirs in the distribution channels.
EVAPORATIVE COOLING - CONCEPTUAL DESIGN FOR ATLAS SCT
Niinikoski, T O
1998-01-01
The conceptual design of an evaporative two-phase flow cooling system for the ATLAS SCT detector is described, using perfluorinated propane (C3F8) as a coolant. Comparison with perfluorinated butane (C4F10) is made, although the detailed design is presented only for C3F8. The two-phase pressure drop and heat transfer coefficient are calculated in order to determine the dimensions of the cooling pipes and module contacts for the Barrel SCT. The region in which the flow is homogeneous is determined. The cooling cycle, pipework, compressor, heat exchangers and other main elements of the system are calculated in order to be able to discuss the system control, safety and reliability. Evaporative cooling appears to be substantially better than the binary ice system from the point of view of safety, reliability, detector thickness, heat transfer coefficient, cost and simplicity.
Burn-up calculation of fusion-fission hybrid reactor using thorium cycle
International Nuclear Information System (INIS)
Shido, S.; Matsunaka, M.; Kondo, K.; Murata, I.; Yamamoto, Y.
2006-01-01
A burn-up calculation system has been developed to estimate performance of blanket in a fusion-fission hybrid reactor which is a fusion reactor with a blanket region containing nuclear fuel. In this system, neutron flux is calculated by MCNP4B and then burn-up calculation is performed by ORIGEN2. The cross-section library for ORIGEN2 is made from the calculated neutron flux and evaluated nuclear data. The 3-dimensional ITER model was used as a base fusion reactor. The nuclear fuel (reprocessed plutonium as the fission materials mixed with thorium as the fertile materials), transmutation materials (minor actinides and long-lived fission products) and tritium breeder were loaded into the blanket. Performances of gas-cooled and water-cooled blankets were compared with each other. As a result, the proposed reactor can meet the requirement for TBP and power density. As far as nuclear waste incineration is concerned, the gas-cooled blanket has advantages. On the other hand, the water cooled-blanket is suited to energy production. (author)
Heating up the gas cooling market
International Nuclear Information System (INIS)
Watt, G.
2001-01-01
Gas cooling is an exciting technology with a potentially bright future. It comprises the production of cooling (and heating) in buildings and industry, by substituting environmentally-friendlier natural gas or LPG over predominantly coal-fired electricity in air conditioning equipment. There are currently four established technologies using gas to provide cooling energy or conditioned air. These are: absorption, both direct gas-fired and utilising hot water or steam; gas engine driven vapour compression (GED); cogeneration, with absorption cooling driven by recovered heat; and desiccant systems. The emergence of gas cooling technologies has been, and remains, one of evolution rather than revolution. However, further development of the technology has had a revolutionary effect on the performance, reliability and consumer acceptability of gas cooling products. Developments from world-renowned manufacturers such as York, Hitachi, Robur and Thermax have produced a range of absorption equipment variously offering: the use of 100 percent environmentally-friendly refrigerants, with zero global warming potential; the ideal utilisation of waste heat from cogeneration systems; a reduction in electrical distribution and stand-by generation capacity; long product life expectancy; far less noise and vibration; performance efficiency maintained down to about 20 percent of load capacity; and highly automated and low-cost maintenance. It is expected that hybrid systems, that is a mixture of gas and electric cooling technologies, will dominate the future market, reflecting the uncertainty in the electricity market and the prospects of stable future gas prices
Directory of Open Access Journals (Sweden)
Dalin Tang
Full Text Available Accurate calculation of ventricular stress and strain is critical for cardiovascular investigations. Sarcomere shortening in active contraction leads to change of ventricular zero-stress configurations during the cardiac cycle. A new model using different zero-load diastole and systole geometries was introduced to provide more accurate cardiac stress/strain calculations with potential to predict post pulmonary valve replacement (PVR surgical outcome.Cardiac magnetic resonance (CMR data were obtained from 16 patients with repaired tetralogy of Fallot prior to and 6 months after pulmonary valve replacement (8 male, 8 female, mean age 34.5 years. Patients were divided into Group 1 (n = 8 with better post PVR outcome and Group 2 (n = 8 with worse post PVR outcome based on their change in RV ejection fraction (EF. CMR-based patient-specific computational RV/LV models using one zero-load geometry (1G model and two zero-load geometries (diastole and systole, 2G model were constructed and RV wall thickness, volume, circumferential and longitudinal curvatures, mechanical stress and strain were obtained for analysis. Pairwise T-test and Linear Mixed Effect (LME model were used to determine if the differences from the 1G and 2G models were statistically significant, with the dependence of the pair-wise observations and the patient-slice clustering effects being taken into consideration. For group comparisons, continuous variables (RV volumes, WT, C- and L- curvatures, and stress and strain values were summarized as mean ± SD and compared between the outcome groups by using an unpaired Student t-test. Logistic regression analysis was used to identify potential morphological and mechanical predictors for post PVR surgical outcome.Based on results from the 16 patients, mean begin-ejection stress and strain from the 2G model were 28% and 40% higher than that from the 1G model, respectively. Using the 2G model results, RV EF changes correlated negatively with
International Nuclear Information System (INIS)
Wang, Zengli; Wang, Zhenbo; Wang, Jun; Jiang, Wenchun; Feng, Quanke
2017-01-01
Highlights: • Theoretical models of SSRC under part-load condition have been established. • The experiment of SSRC performance under part-load condition was conducted. • Thermal dynamic characteristic of SSRC under part-load condition was gained. • Economy and reliability of SSRC under part-load condition was analyzed. - Abstract: In the single screw refrigeration compressor (SSRC), the capacity control mechanism is normally employed to meet the actual required cooling capacity under different load conditions. In this paper, theoretical calculation models describing the working process of the SSRC with the single slide valve capacity control mechanism (SVCCM) and SSRC with the frequency conversion regulating mechanism (FCRM) are established to research the thermal dynamic characteristics for variable load SSRC under part-load conditions. Experimental investigation on a SSRC under part-load conditions is also carried out to verify the theoretical calculation models. By using these validated models, the thermodynamic performances and dynamic characteristics of the SSRC with different capacity control mechanism under part-load conditions have been analyzed and compared. Through the comparison, the economical efficiency and reliability of the SSRC with different capacity control mechanism were obtained. All of these works can provide the basis for the later optimization design for the variable load single screw refrigeration compressor.
Peltier cooling in molecular junctions
Cui, Longji; Miao, Ruijiao; Wang, Kun; Thompson, Dakotah; Zotti, Linda Angela; Cuevas, Juan Carlos; Meyhofer, Edgar; Reddy, Pramod
2018-02-01
The study of thermoelectricity in molecular junctions is of fundamental interest for the development of various technologies including cooling (refrigeration) and heat-to-electricity conversion1-4. Recent experimental progress in probing the thermopower (Seebeck effect) of molecular junctions5-9 has enabled studies of the relationship between thermoelectricity and molecular structure10,11. However, observations of Peltier cooling in molecular junctions—a critical step for establishing molecular-based refrigeration—have remained inaccessible. Here, we report direct experimental observations of Peltier cooling in molecular junctions. By integrating conducting-probe atomic force microscopy12,13 with custom-fabricated picowatt-resolution calorimetric microdevices, we created an experimental platform that enables the unified characterization of electrical, thermoelectric and energy dissipation characteristics of molecular junctions. Using this platform, we studied gold junctions with prototypical molecules (Au-biphenyl-4,4'-dithiol-Au, Au-terphenyl-4,4''-dithiol-Au and Au-4,4'-bipyridine-Au) and revealed the relationship between heating or cooling and charge transmission characteristics. Our experimental conclusions are supported by self-energy-corrected density functional theory calculations. We expect these advances to stimulate studies of both thermal and thermoelectric transport in molecular junctions where the possibility of extraordinarily efficient energy conversion has been theoretically predicted2-4,14.
The Schmehausen cable net cooling tower
International Nuclear Information System (INIS)
Schlaich, J.; Mayr, G.; Weber, P.; Jasch, E.
1976-01-01
The prototype of a large cable net shell as a natural-draught cooling tower for the THTR-300 is presented. Results of wind tunnel tests and calculations are given, and the capacity is discussed. Design features of the main components are presented in illustrations and are described with regard to the construction process of the cooling tower. Finally, it is shown that the cable net cooling tower is a suitable construction for large dimensions and caving-in or seismic areas. (orig./HP) [de
International Nuclear Information System (INIS)
Fong, K.F.; Chow, T.T.; Lee, C.K.; Lin, Z.; Chan, L.S.
2011-01-01
Highlights: → A solar hybrid cooling system is proposed for high-tech offices in subtropical climate. → An integration of radiant cooling, absorption refrigeration and desiccant dehumidification. → Year-round cooling and energy performances were evaluated through dynamic simulation. → Its annual primary energy consumption was lower than conventional system up to 36.5%. → The passive chilled beams were more energy-efficient than the active chilled beams. - Abstract: A solar hybrid cooling design is proposed for high cooling load demand in hot and humid climate. For the typical building cooling load, the system can handle the zone cooling load (mainly sensible) by radiant cooling with the chilled water from absorption refrigeration, while the ventilation load (largely latent) by desiccant dehumidification. This hybrid system utilizes solar energy for driving the absorption chiller and regenerating the desiccant wheel. Since a high chilled water temperature generated from the absorption chiller is not effective to handle the required latent load, desiccant dehumidification is therefore involved. It is an integration of radiant cooling, absorption refrigeration and desiccant dehumidification, which are powered up by solar energy. In this study, the application potential of the solar hybrid cooling system was evaluated for the high-tech offices in the subtropical climate through dynamic simulation. The high-tech offices are featured with relatively high internal sensible heat gains due to the intensive office electric equipment. The key performance indicators included the solar fraction and the primary energy consumption. Comparative study was also carried out for the solar hybrid cooling system using two common types of chilled ceilings, the passive chilled beams and active chilled beams. It was found that the solar hybrid cooling system was technically feasible for the applications of relatively higher cooling load demand. The annual primary energy
Cooling Rates of Lunar Volcanic Glass Beads
Hui, Hejiu; Hess, Kai-Uwe; Zhang, Youxue; Peslier, Anne; Lange, Rebecca; Dingwell, Donald; Neal, Clive
2016-01-01
It is widely accepted that the Apollo 15 green and Apollo 17 orange glass beads are of volcanic origin. The diffusion profiles of volatiles in these glass beads are believed to be due to degassing during eruption (Saal et al., 2008). The degree of degassing depends on the initial temperature and cooling rate. Therefore, the estimations of volatiles in parental magmas of lunar pyroclastic deposits depend on melt cooling rates. Furthermore, lunar glass beads may have cooled in volcanic environments on the moon. Therefore, the cooling rates may be used to assess the atmospheric condition in an early moon, when volcanic activities were common. The cooling rates of glasses can be inferred from direct heat capacity measurements on the glasses themselves (Wilding et al., 1995, 1996a,b). This method does not require knowledge of glass cooling environments and has been applied to calculate the cooling rates of natural silicate glasses formed in different terrestrial environments. We have carried out heat capacity measurements on hand-picked lunar glass beads using a Netzsch DSC 404C Pegasus differential scanning calorimeter at University of Munich. Our preliminary results suggest that the cooling rate of Apollo 17 orange glass beads may be 12 K/min, based on the correlation between temperature of the heat capacity curve peak in the glass transition range and glass cooling rate. The results imply that the parental magmas of lunar pyroclastic deposits may have contained more water initially than the early estimations (Saal et al., 2008), which used higher cooling rates, 60-180 K/min in the modeling. Furthermore, lunar volcanic glass beads could have been cooled in a hot gaseous medium released from volcanic eruptions, not during free flight. Therefore, our results may shed light on atmospheric condition in an early moon.
International Nuclear Information System (INIS)
Kaznovski, S.
1999-01-01
In conformity with request from Paks NPP in July 1997 the additional dynamic tests of the following units of equipment were carried out: Heat exchanger (Diesel Generator Station); Jalousie (Diesel Generator Station); Axial ventilator (Main Building, gallery of electric equipment). The natural frequencies of equipment were obtained as results of these testing. For all tested units the calculations of seismic resistance were carried out. The method of finite elements and special computer programmes of KBGU (ISPA, and others) were used. Calculations were carried out in accordance with modem standards. The calculations of tested equipment seismic resistance are carried out based on the obtained experimental data and NPP floor response spectra. The necessary recommendations for unsatisfactory equipment are worked out
International Nuclear Information System (INIS)
Kaznovski, S.
1996-01-01
The method for examination and ensuring of equipment seismic resistance is based on the resonance character of the seismic influence on structures and equipment. Values of natural dynamic characteristics are obtained by using external source for exciting the vibrations of the testing unit. These characteristics with the floor response spectra enabled calculations of the seismic resistance. For tests of Kozloduy NPP equipment a simple shock method was used. The presentation includes the list of inspected equipment. The calculations of the equipment seismic resistance were carried out on the basis of Russian and International standards and demands
International Nuclear Information System (INIS)
LeSage, L.G.; McKnight, R.D.; Wade, D.C.; Freese, K.E.; Collins, P.J.
1980-08-01
The results of an international comparison calculation of a large (1250 MWe) LMFBR benchmark model are presented and discussed. Eight reactor configurations were calculated. Parameters included with the comparison were: eigenvalue, k/sub infinity/, neutron balance data, breeding reaction rate ratios, reactivity worths, central control rod worth, regional sodium void reactivity, core Doppler and effective delayed neutron fraction. Ten countries participated in the comparison, and sixteen solutions were contributed. The discussion focuses on the variation in parameter values, the degree of consistency among the various parameters and solutions, and the identification of unexpected results. The results are displayed and discussed both by individual participants and by groupings of participants
Directory of Open Access Journals (Sweden)
Ozgoren M.
2013-04-01
Full Text Available In this study, an absorption system using ammonia-water (NH3-H2O solution has been theoretically examined in order to meet the cooling need of a detached building having 150 m2 floor area for Antalya, Mersin and Mugla provinces in Turkey. Hourly dynamic cooling load capacities of the building were determined by using Radiant Time Series (RTS method in the chosen cities. For the analysis, hourly average meteorological data such as atmospheric air temperature and solar radiation belonging to the years 1998-2008 are used for performance prediction of the proposed system. Thermodynamic relations for each component of absorption cooling system is explained and coefficients of performance of the system are calculated. The maximum daily total radiation data were calculated as 7173 W/m2day on July 15, 7277 W/m2 day on July 19 and 7231 W/m2day on July 19 for Mersin, Antalya and Mugla, respectively on the 23° toward to south oriented panels from horizontal surface. The generator operating temperatures are considered between 90-130°C and the best result for 110°C is found the optimum degree for maximum coefficient of performance (COP values at the highest solar radiation occurred time during the considered days for each province. The COP values varies between 0.521 and 0.530 for the provinces. In addition, absorber and condenser capacities and thermal efficiency for the absorption cooling system were calculated. The necessary evacuated tube collector area for the different provinces were found in the range of 45 m2 to 47 m2. It is shown that although the initial investment cost is higher for the proposed absorption cooling system, it is economically feasible because of its lower annual operation costs and can successfully be operated for the considered provinces.
Energy Technology Data Exchange (ETDEWEB)
Poquillon, D
1997-10-01
Usually, for the integrity assessment of defective components, well established rules are used: global approach to fracture. A more fundamental way to deal with these problems is based on the local approach to fracture. In this study, we choose this way and we perform numerical simulations of intergranular crack initiation and intergranular crack propagation. This type of damage can be find in components of fast breeder reactors in 316 L austenitic stainless steel which operate at high temperatures. This study deals with methods coupling partly the behaviour and the damage for crack growth in specimens submitted to various thermomechanical loadings. A new numerical method based on finite element computations and a damage model relying on quantitative observations of grain boundary damage is proposed. Numerical results of crack initiation and growth are compared with a number of experimental data obtained in previous studies. Creep and creep-fatigue crack growth are studied. Various specimen geometries are considered: compact Tension Specimens and axisymmetric notched bars tested under isothermal (600 deg C) conditions and tubular structures containing a circumferential notch tested under thermal shock. Adaptative re-meshing technique and/or node release technique are used and compared. In order to broaden our knowledge on stress triaxiality effects on creep intergranular damage, new experiments are defined and conducted on sharply notched tubular specimens in torsion. These isothermal (600 deg C) Mode II creep tests reveal severe intergranular damage and creep crack initiation. Calculated damage fields at the crack tip are compared with the experimental observations. The good agreement between calculations and experimental data shows the damage criterion used can improve the accuracy of life prediction of components submitted to intergranular creep damage. (author) 200 refs.
Loading Conditions and Longitudinal Strength
DEFF Research Database (Denmark)
Sørensen, Herman
1995-01-01
Methods for the calculation of the lightweight of the ship.Loading conditions satisfying draught, trim and intact stability requirements and analysis of the corresponding stillwater longitudinal strength.......Methods for the calculation of the lightweight of the ship.Loading conditions satisfying draught, trim and intact stability requirements and analysis of the corresponding stillwater longitudinal strength....
Petrushkin, S V
2009-01-01
Laser cooling is an important emerging technology in such areas as the cooling of semiconductors. The book examines and suggests solutions for a range of problems in the development of miniature solid-state laser refrigerators, self-cooling solid-state lasers and optical echo-processors. It begins by looking at the basic theory of laser cooling before considering such topics as self-cooling of active elements of solid-state lasers, laser cooling of solid-state information media of optical echo-processors, and problems of cooling solid-state quantum processors. Laser Cooling of Solids is an important contribution to the development of compact laser-powered cryogenic refrigerators, both for the academic community and those in the microelectronics and other industries. Provides a timely review of this promising field of research and discusses the fundamentals and theory of laser cooling Particular attention is given to the physics of cooling processes and the mathematical description of these processes Reviews p...
Emergency reactor cooling device
International Nuclear Information System (INIS)
Arakawa, Ken.
1993-01-01
An emergency nuclear reactor cooling device comprises a water reservoir, emergency core cooling water pipelines having one end connected to a water feeding sparger, fire extinguishing facility pipelines, cooling water pressurizing pumps, a diesel driving machine for driving the pumps and a battery. In a water reservoir, cooling water is stored by an amount required for cooling the reactor upon emergency and for fire extinguishing, and fire extinguishing facility pipelines connecting the water reservoir and the fire extinguishing facility are in communication with the emergency core cooling water pipelines connected to the water feeding sparger by system connection pipelines. Pumps are operated by a diesel power generator to introduce cooling water from the reservoir to the emergency core cooling water pipelines. Then, even in a case where AC electric power source is entirely lost and the emergency core cooling system can not be used, the diesel driving machine is operated using an exclusive battery, thereby enabling to inject cooling water from the water reservoir to a reactor pressure vessel and a reactor container by the diesel drive pump. (N.H.)
Workshop on high heat load x-ray optics
Energy Technology Data Exchange (ETDEWEB)
1990-01-01
A workshop on High Heat Load X-Ray Optics'' was held at Argonne National Laboratory on August 3--5, 1989. The object of this workshop was to discuss recent advances in the art of cooling x-ray optics subject to high heat loads from synchrotron beams. The cooling of the first optical element in the intense photon beams that will be produced in the next generation of synchrotron sources is recognized as one of the major challenges that must be faced before one will be able to use these very intense beams in future synchrotron experiments. Considerable advances have been made in this art during the last few years, but much work remains to be done before the heating problem can be said to be completely solved. Special emphasis was placed on recent cooling experiments and detailed finite element'' and finite difference'' calculations comparing experiment with theory and extending theory to optimize performance.
Neutron spectrum effects on TRU recycling in Pb-Bi cooled fast reactor core
International Nuclear Information System (INIS)
Kim, Yong Nam; Kim, Jong Kyung; Park, Won Seok
2003-01-01
This study is intended to evaluate the dependency of TRU recycling characteristics on the neutron spectrum shift in a Pb-Bi cooled core. Considering two Pb-Bi cooled cores with the soft and the hard spectrum, respectively, various characteristics of the recycled core are carefully examined and compared with each other. Assuming very simplified fuel cycle management with the homogeneous and single region fuel loading, the burnup calculations are performed until the recycled core reached to the (quasi-) equilibrium state. The mechanism of TRU recycling toward the equilibrium is analyzed in terms of burnup reactivity and the isotopic compositions of TRU fuel. In the comparative analyses, the difference in the recycling behavior between the two cores is clarified. In addition, the basic safety characteristics of the recycled core are also discussed in terms of the Doppler coefficient, the coolant loss reactivity coefficient, and the effective delayed neutron fraction
Study on blast furnace cooling stave for various refractory linings based on numerical modeling
International Nuclear Information System (INIS)
Mohanty, T R; Sahoo, S K; Moharana, M K
2016-01-01
Cooling technology for refractory lining of blast furnace is very important for the metallurgical industry, because it can substantially increase output and operation life of furnaces. A three dimensional mathematical model for the temperature field of the blast furnace stave cooler with refractory lining has been developed and analyzed. The temperature and heat dissipated by stave cooler is examined by using the finite element method. The cast steel stave is studied and computational analysis is made to know the effect of the cooling water velocity, temperature, and the lining material on the maximum temperature of the stave hot surface. The refractory lining materials, which are used in this experiment, are high alumina bricks with different stave materials (copper, aluminum and cast iron). The obtained numerical calculations are compared with that obtained from experiments performed at Rourkela Steel Plant, Odisha taking a stave in belly zone having maximum heat load shows very good agreement. (paper)
Energy Technology Data Exchange (ETDEWEB)
Weissfloch, R
1973-07-15
The fuel elements of high-temperature reactors, coated with pyrolitic carbon and covered with graphite, release fission products like all other fuel elements. Because of safety reasons, the rate of this release has to be kept low and has also to be predictable. Measured values from irradiation tests and from post-irradiation tests about the actual release of different fission products are presented. The physical and chemical mechanism, which determines the release, is extraordinarily complex and in particular not clearly defined. Because of the mentioned reasons, a simplified calculation model was developed, which only considers the release-mechanisms phenomenologically. This calculation model coincides very well in its results with values received in experiments until now. It can be held as an interim state on the way to a complete theory.
International Nuclear Information System (INIS)
Weissfloch, R.
The fuel elements of High-Temperature Reactors, coated with pyrolitic carbon and covered with graphite, release fission products like all other fuel elements. Because of safety reasons the rate of this release has to be kept low and has also to be predictable. Measured values from irradiation tests and from post-irradiation tests about the actual release of different fission products are present. The physical and chemical mechanism, which determines the release, is extraordinarily complex and in particular not clearly defined. Because of the mentioned reasons a simplified calculation model was developed, which only considers the release-mechanisms phenomenologically. This calculation model coincides very well in its results with values received in experiments until now. It can serve as an interim state on the way to a complete theory. (U.S.)
Integrated cooling system for the Mirror Fusion Test Facility
International Nuclear Information System (INIS)
Johnson, B.; Chang, Y.
1979-01-01
The MFTF components that require water cooling include the neutral beam dumps, ion dumps, plasma dumps, baffle plates, magnet liners, gas boxes, streaming guns, and the neutral beam injectors. A total heat load of nearly 500 MW for 0.5 s dissipates over 4-min intervals. A steady-flow, closed-loop system is utilized. The design of the cooling system assumes that all components require cooling simultaneously. The cooling system contains process instrumentation for loop control. Alarms and safety interlocks are incorporated for the safe operation of the system
International Nuclear Information System (INIS)
Tsujimura, Seiichi; Toyota, Masahiko.
1995-01-01
A highly thermal load structure applied to a plasma-opposed equipment of a thermonuclear device comprises heat resistant protection tiles and a cooling tube disposed in the protection tiles. As the protection tiles, a carbon/carbon composite material is used. The carbon/carbon composite material on the heat receiving surface comprises carbon fibers disposed in one direction (one dimensionally) arranged from the heat receiving surface toward the cooling tube. The carbon/carbon composite material on the side opposite to the heat receiving surface comprises carbon fibers arranged two-dimensionally in the direction perpendicular to the longitudinal direction of the cooling tube. Then, the cooling tube is interposed between the one-dimensional carbon/carbon composite material and the two-dimensional carbon/carbon composite material, and they are joined with each other by vacuum brazing. This can improve heat removing performance. In addition, thermal stresses at the joined portion is reduced. Further, electromagnetic force generated in the thermonuclear device is reduced. (I.N.)
Energy Technology Data Exchange (ETDEWEB)
Tsujimura, Seiichi; Toyota, Masahiko
1995-06-16
A highly thermal load structure applied to a plasma-opposed equipment of a thermonuclear device comprises heat resistant protection tiles and a cooling tube disposed in the protection tiles. As the protection tiles, a carbon/carbon composite material is used. The carbon/carbon composite material on the heat receiving surface comprises carbon fibers disposed in one direction (one dimensionally) arranged from the heat receiving surface toward the cooling tube. The carbon/carbon composite material on the side opposite to the heat receiving surface comprises carbon fibers arranged two-dimensionally in the direction perpendicular to the longitudinal direction of the cooling tube. Then, the cooling tube is interposed between the one-dimensional carbon/carbon composite material and the two-dimensional carbon/carbon composite material, and they are joined with each other by vacuum brazing. This can improve heat removing performance. In addition, thermal stresses at the joined portion is reduced. Further, electromagnetic force generated in the thermonuclear device is reduced. (I.N.).
DEFF Research Database (Denmark)
Olesen, Bjarne W.
2008-01-01
In many countries, hydronic radiant floor systems are widely used for heating all types of buildings such as residential, churches, gymnasiums, hospitals, hangars, storage buildings, industrial buildings, and smaller offices. However, few systems are used for cooling.This article describes a floor...... cooling system that includes such considerations as thermal comfort of the occupants, which design parameters will influence the cooling capacity and how the system should be controlled. Examples of applications are presented....
International Nuclear Information System (INIS)
Sessler, A.M.
1994-10-01
A review is given of the various methods which can be employed for cooling particle beams. These methods include radiation damping, stimulated radiation damping, ionization cooling, stochastic cooling, electron cooling, laser cooling, and laser cooling with beam coupling. Laser Cooling has provided beams of the lowest temperatures, namely 1 mK, but only for ions and only for the longitudinal temperature. Recent theoretical work has suggested how laser cooling, with the coupling of beam motion, can be used to reduce the ion beam temperature in all three directions. The majority of this paper is devoted to describing laser cooling and laser cooling with beam coupling
Current interruption transients calculation
Peelo, David F
2014-01-01
Provides an original, detailed and practical description of current interruption transients, origins, and the circuits involved, and how they can be calculated Current Interruption Transients Calculationis a comprehensive resource for the understanding, calculation and analysis of the transient recovery voltages (TRVs) and related re-ignition or re-striking transients associated with fault current interruption and the switching of inductive and capacitive load currents in circuits. This book provides an original, detailed and practical description of current interruption transients, origins,
Turbine airfoil cooling system with cooling systems using high and low pressure cooling fluids
Marsh, Jan H.; Messmann, Stephen John; Scribner, Carmen Andrew
2017-10-25
A turbine airfoil cooling system including a low pressure cooling system and a high pressure cooling system for a turbine airfoil of a gas turbine engine is disclosed. In at least one embodiment, the low pressure cooling system may be an ambient air cooling system, and the high pressure cooling system may be a compressor bleed air cooling system. In at least one embodiment, the compressor bleed air cooling system in communication with a high pressure subsystem that may be a snubber cooling system positioned within a snubber. A delivery system including a movable air supply tube may be used to separate the low and high pressure cooling subsystems. The delivery system may enable high pressure cooling air to be passed to the snubber cooling system separate from low pressure cooling fluid supplied by the low pressure cooling system to other portions of the turbine airfoil cooling system.
Power electronics cooling apparatus
Sanger, Philip Albert; Lindberg, Frank A.; Garcen, Walter
2000-01-01
A semiconductor cooling arrangement wherein a semiconductor is affixed to a thermally and electrically conducting carrier such as by brazing. The coefficient of thermal expansion of the semiconductor and carrier are closely matched to one another so that during operation they will not be overstressed mechanically due to thermal cycling. Electrical connection is made to the semiconductor and carrier, and a porous metal heat exchanger is thermally connected to the carrier. The heat exchanger is positioned within an electrically insulating cooling assembly having cooling oil flowing therethrough. The arrangement is particularly well adapted for the cooling of high power switching elements in a power bridge.
Performance characteristic of hybrid cooling system based on cooling pad and evaporator
Yoon, J. I.; Son, C. H.; Choi, K. H.; Kim, Y. B.; Sung, Y. H.; Roh, S. J.; Kim, Y. M.; Seol, S. H.
2018-01-01
In South Korea, most of domestic animals such as pigs and chickens might die due to thermal diseases if they are exposed to the high temperature consistently. In order to save them from the heat wave, numerous efforts have been carried out: installing a shade net, adjusting time of feeding, spraying mist and setting up a circulation fan. However, these methods have not shown significant improvements. Thus, this study proposes a hybrid cooling system combining evaporative cooler and air-conditioner in order to resolve the conventional problems caused by the high temperature in the livestock industry. The problem of cooling systems using evaporative cooling pads is that they are not effective for eliminating huge heat load due to their limited capacity. And, temperature of the supplied air cannot be low enough compared to conventional air-conditioning systems. On the other hand, conventional air-conditioning systems require relatively expensive installation cost, and high operating cost compared to evaporative cooling system. The hybrid cooling system makes up for the lack of cooling capacity of the evaporative cooler by employing the conventional air-conditioner. Additionally, temperature of supplied air can be lowered enough. In the hybrid cooling system, induced air by a fan is cooled by the evaporation of water in the cooling pad, and it is cooled again by an evaporator in the air-conditioner. Therefore, the more economical operation is possible due to additionally obtained cooling capacity from the cooling pads. Major results of experimental analysis of hybrid cooling system are as follows. The compressor power consumption of the hybrid cooling system is about 23% lower, and its COP is 17% higher than that of the conventional air-conditioners. Regarding the condition of changing ambient temperature, the total power consumption decreased by about 5% as the ambient temperature changed from 28.7°C to 31.7°C. Cooling capacity and COP also presented about 3% and 1
Applying water cooled air conditioners in residential buildings in Hong Kong
International Nuclear Information System (INIS)
Chen Hua; Lee, W.L.; Yik, F.W.H.
2008-01-01
The objective of this study is to conduct a realistic prediction of the potential energy saving for using water cooled air conditioners in residential buildings in Hong Kong. A split type air conditioner with air cooled (AAC) and water cooled (WAC) options was set up for experimental study at different indoor and outdoor conditions. The cooling output, power consumption and coefficient of performance (COP) of the two options were measured and calculated for comparison. The experimental results showed that the COP of the WAC is, on average, 17.4% higher than that of the AAC. The results were used to validate the mathematical models formulated for predicting the performance of WACs and AACs at different operating conditions and load characteristics. While the development of the mathematical models for WACs was reported in an earlier paper, this paper focuses on the experimental works for the AAC. The mathematical models were further used to predict the potential energy saving for application of WACs in residential buildings in Hong Kong. The predictions were based on actual building developments and realistic operating characteristics. The overall energy savings were estimated to be around 8.7% of the total electricity consumption for residential buildings in Hong Kong. Wider use of WACs in subtropical cities is, therefore, recommended
Cooling of electronic equipment
DEFF Research Database (Denmark)
A. Kristensen, Anders Schmidt
2003-01-01
Cooling of electronic equipment is studied. The design size of electronic equipment decrease causing the thermal density to increase. This affect the cooling which can cause for example failures of critical components due to overheating or thermal induced stresses. Initially a pin fin heat sink...
Kim, D.S.
2007-01-01
As the world concerns more and more on global climate changes and depleting energy resources, solar cooling technology receives increasing interests from the public as an environment-friendly and sustainable alternative. However, making a competitive solar cooling machine for the market still
International Nuclear Information System (INIS)
Vakilian, M.
1977-05-01
The present study is the second part of a general survey of Gas Cooled Reactors (GCRs). In this part, the course of development, overall performance and present development status of High Temperature Gas Cooled Reactors (HTCRs) and advances of HTGR systems are reviewed. (author)
Energy Technology Data Exchange (ETDEWEB)
Litvinenko,V.
2009-05-04
Cooling intense high-energy hadron beams remains a major challenge in modern accelerator physics. Synchrotron radiation is still too feeble, while the efficiency of two other cooling methods, stochastic and electron, falls rapidly either at high bunch intensities (i.e. stochastic of protons) or at high energies (e-cooling). In this talk a specific scheme of a unique cooling technique, Coherent Electron Cooling, will be discussed. The idea of coherent electron cooling using electron beam instabilities was suggested by Derbenev in the early 1980s, but the scheme presented in this talk, with cooling times under an hour for 7 TeV protons in the LHC, would be possible only with present-day accelerator technology. This talk will discuss the principles and the main limitations of the Coherent Electron Cooling process. The talk will describe the main system components, based on a high-gain free electron laser driven by an energy recovery linac, and will present some numerical examples for ions and protons in RHIC and the LHC and for electron-hadron options for these colliders. BNL plans a demonstration of the idea in the near future.
Thursday 29th May, the cool-down of the final sector (sector 4-5) of LHC has begun, one week after the start of the cool-down of sector 1-2. It will take five weeks for the sectors to be cooled from room temperature to 5 K and a further two weeks to complete the cool down to 1.9 K and the commissioning of cryogenic instrumentation, as well as to fine tune the cryogenic plants and the cooling loops of cryostats.Nearly a year and half has passed since sector 7-8 was cooled for the first time in January 2007. For Laurent Tavian, AT/CRG Group Leader, reaching the final phase of the cool down is an important milestone, confirming the basic design of the cryogenic system and the ability to operate complete sectors. “All the sectors have to operate at the same time otherwise we cannot inject the beam into the machine. The stability and reliability of the cryogenic system and its utilities are now very important. That will be the new challenge for the coming months,” he explains. The status of the cool down of ...
Kley, Philipp; Frentzen, Matthias; Küpper, Katharina; Braun, Andreas; Kecsmar, Susann; Jäger, Andreas; Wolf, Michael
2016-05-01
Recent studies have indicated possible thermal damage to pulpal tissue during orthodontic debonding. This study aimed to analyze the thermal loads acting upon dental structures and their transfer to the pulp during orthodontic debonding. Specific goals were to analyze temperature changes in local dental tissues, thermotransduction to the pulp cavity, and the effectiveness of common cooling strategies and of simulated intrapulpal circulation. Metal brackets were bonded to five extracted human molars and subsequently removed. While a carbide bur was applied to debond the residual composite from the tooth surface, various cooling strategies (no/air/water cooling) were employed with or without simulated intrapulpal circulation, accompanied by temperature measurements with a thermographic infrared camera on the enamel surface and with measuring probes in the pulp cavity. Appropriate evaluation software was used to calculate the enamel-to-pulp temperature gradients and for statistical analysis. Significant differences in temperature rise and heat development over time, both on the enamel surfaces and in the pulp cavities were found. The mean temperature rises associated with no/air/water cooling were 90.7/46.6/9.2 °C on the enamel surface versus 9/8/4.6 °C inside the pulp. However, thermotransduction from enamel to pulp remained below 10 % of the surface measurements in all groups. Simulated intrapulpal microcirculation was found to significantly reduce intrapulpal temperature levels. During debonding of residual bracket adhesives, provided that a carbide bur is properly used, our data indicate a low risk of reaching critical intrapulpal temperatures even in the absence of dedicated cooling and no risk if the instrumentation is accompanied by air or water cooling.
DEFF Research Database (Denmark)
Bellemo, Lorenzo; Elmegaard, Brian; Reinholdt, Lars O.
2013-01-01
This paper focuses on the numerical modeling and analysis of a Desiccant Cooling (DEC) system with regenerative indirect evaporative cooling, termed Desiccant Dewpoint Cooling (DDC) system. The DDC system includes a Desiccant Wheel (DW), Dew Point Coolers (DPCs), a heat recovery unit and a heat...... in different climates: temperate in Copenhagen and Mediterranean in Venice. Cheap and clean heat sources (e.g. solar energy) strongly increase the attractiveness of the DDC system. For the Mediterranean climate the DDC system represents a convenient alternative to chiller-based systems in terms of energy costs...... and CO2 emissions. The electricity consumption for auxiliaries in the DDC system is higher than in the chiller-based systems. The number of commercial-size DPC units required to cover the cooling load during the whole period is high: 8 in Copenhagen and 12 in Venice....
Residential building envelope heat gain and cooling energy requirements
International Nuclear Information System (INIS)
Lam, Joseph C.; Tsang, C.L.; Li, Danny H.W.; Cheung, S.O.
2005-01-01
We present the energy use situation in Hong Kong from 1979 to 2001. The primary energy requirement (PER) nearly tripled during the 23-year period, rising from 195,405 TJ to 572,684 TJ. Most of the PER was used for electricity generation, and the electricity use in residential buildings rose from 7556 TJ (2099 GWh) to 32,799 TJ (9111 GWh), an increase of 334%. Air-conditioning accounted for about 40% of the total residential sector electricity consumption. A total of 144 buildings completed in the month of June during 1992-2001 were surveyed. Energy performance of the building envelopes was investigated in terms of the overall thermal transfer value (OTTV). To develop the appropriated parameters used in OTTV calculation, long-term measured weather data such as ambient temperature (1960-2001), horizontal global solar radiation (1992-2001) and global solar radiation on vertical surfaces (1996-2001) were examined. The OTTV found varied from 27 to 44 W/m 2 with a mean value of 37.7 W/m 2 . Building energy simulation technique using DOE-2.1E was employed to determine the cooling requirements and hence electricity use for building envelope designs with different OTTVs. It was found that cooling loads and electricity use could be expressed in terms of a simple two-parameter linear regression equation involving OTTV
Experiments with a laser cooled cloud of atoms
International Nuclear Information System (INIS)
Natarajan, Vasant; Banerjee, Ayan; Rapol, Umakant
1999-01-01
We discuss two experiments that can be performed using a cloud of laser-cooled and trapped atoms, namely Bose-Einstein condensation (BEC) and search for a permanent Electric Dipole Moment (EDM). BEC can be observed in Rb atoms in a magnetic trap by using forced evaporative cooling to continuously lower the temperature below the condensation limit. The cloud is cooled by preferentially ejecting the hottest atoms from a magnetic trap. The magnetic trap is loaded with laser-cooled atoms from a magneto-optic trap. The EDM experiment can be performed with a laser-cooled cloud of Yb atoms. The atoms are spin polarized and the precession of the spin is measured in the presence of a strong electric field applied perpendicular to the spin direction. The use of laser-cooled atoms should greatly enhance the sensitivity of the experiment. (author)
Theoretical insight of adsorption cooling
Chakraborty, Anutosh
2011-06-03
This letter proposes and presents a thermodynamic formulation to calculate the energetic performances of an adsorption cooler as a function of pore widths and volumes of solid adsorbents. The simulated results in terms of the coefficient of performance are validated with experimental data. It is found from the present analysis that the performance of an adsorption cooling device is influenced mainly by the physical characteristics of solid adsorbents, and the characteristics energy between the adsorbent-adsorbate systems. The present study confirms that there exists a special type of silicagel having optimal physical characteristics that allows us to obtain the best performance.
Theoretical insight of adsorption cooling
Chakraborty, Anutosh; Leong, Kai Choong; Thu, Kyaw; Saha, Bidyut Baran; Ng, Kim Choon
2011-01-01
This letter proposes and presents a thermodynamic formulation to calculate the energetic performances of an adsorption cooler as a function of pore widths and volumes of solid adsorbents. The simulated results in terms of the coefficient of performance are validated with experimental data. It is found from the present analysis that the performance of an adsorption cooling device is influenced mainly by the physical characteristics of solid adsorbents, and the characteristics energy between the adsorbent-adsorbate systems. The present study confirms that there exists a special type of silicagel having optimal physical characteristics that allows us to obtain the best performance.
International Nuclear Information System (INIS)
Kobayashi, Masahiro.
1986-01-01
Purpose: To safely and effectively cool down the reactor core after it has been shut down but is still hot due to after-heat. Constitution: Since the coolant extraction nozzle is situated at a location higher than the coolant injection nozzle, the coolant sprayed from the nozzle, is free from sucking immediately from the extraction nozzle and is therefore used effectively to cool the reactor core. As all the portions from the top to the bottom of the reactor are cooled simultaneously, the efficiency of the reactor cooling process is increased. Since the coolant extraction nozzle can be installed at a point considerably higher than the coolant injection nozzle, the distance from the coolant surface to the point of the coolant extraction nozzle can be made large, preventing cavitation near the coolant extraction nozzle. Therefore, without increasing the capacity of the heat exchanger, the reactor can be cooled down after a shutdown safely and efficiently. (Kawakami, Y.)
Stochastic cooling at Fermilab
International Nuclear Information System (INIS)
Marriner, J.
1986-08-01
The topics discussed are the stochastic cooling systems in use at Fermilab and some of the techniques that have been employed to meet the particular requirements of the anti-proton source. Stochastic cooling at Fermilab became of paramount importance about 5 years ago when the anti-proton source group at Fermilab abandoned the electron cooling ring in favor of a high flux anti-proton source which relied solely on stochastic cooling to achieve the phase space densities necessary for colliding proton and anti-proton beams. The Fermilab systems have constituted a substantial advance in the techniques of cooling including: large pickup arrays operating at microwave frequencies, extensive use of cryogenic techniques to reduce thermal noise, super-conducting notch filters, and the development of tools for controlling and for accurately phasing the system
International Nuclear Information System (INIS)
Nicolai, A.; Fuchs, G.
1978-01-01
The plasma parameters in the scrape-off layer (SoL) of a tokamak are calculated by introducing appropriate particles and energy loss terms into the six-regime version of Duechs code. These terms take secondary electron smission from the limiter surface and a potential sheath in front of it into account. In the SoL Bohn diffusion is assumed. Limiter materials with large secondary emission coefficients (SEC)(e.g. Mo) give lower potential steps (U = 90 V) than low SEC materials (e.g. Be) which cause (U = 250 V). The flux of the sputtered liner material and the resulting radiation losses can be decreased by neutral gas influx. When the same neutral gas influx and the same additional heating are used, it is found that radiation losses due to molybdenum are lower than those due to iron, although Mo is more toxic. (Auth.)
Cooled-Spool Piston Compressor
Morris, Brian G.
1994-01-01
Proposed cooled-spool piston compressor driven by hydraulic power and features internal cooling of piston by flowing hydraulic fluid to limit temperature of compressed gas. Provides sufficient cooling for higher compression ratios or reactive gases. Unlike conventional piston compressors, all parts of compressed gas lie at all times within relatively short distance of cooled surface so that gas cooled more effectively.
International Nuclear Information System (INIS)
Jan, Yih-Kuen; Liao, Fuyuan; Lee, Bernard; Foreman, Robert D
2012-01-01
The objectives of this study were to investigate the effects of local cooling on skin blood flow response to prolonged surface pressure and to identify associated physiological controls mediating these responses using the wavelet analysis of blood flow oscillations in rats. Twelve Sprague–Dawley rats were randomly assigned to three protocols, including pressure with local cooling (Δt = −10 °C), pressure with local heating (Δt = 10 °C) and pressure without temperature changes. Pressure of 700 mmHg was applied to the right trochanter area of rats for 3 h. Skin blood flow was measured using laser Doppler flowmetry. The 3 h loading period was divided into non-overlapping 30 min epochs for the analysis of the changes of skin blood flow oscillations using wavelet spectral analysis. The wavelet amplitudes and powers of three frequencies (metabolic, neurogenic and myogenic) of skin blood flow oscillations were calculated. The results showed that after an initial loading period of 30 min, skin blood flow continually decreased under the conditions of pressure with heating and of pressure without temperature changes, but maintained stable under the condition of pressure with cooling. Wavelet analysis revealed that stable skin blood flow under pressure with cooling was attributed to changes in the metabolic and myogenic frequencies. This study demonstrates that local cooling may be useful for reducing ischemia of weight-bearing soft tissues that prevents pressure ulcers. (paper)
Molecules cooled below the Doppler limit
Truppe, S.; Williams, H. J.; Hambach, M.; Caldwell, L.; Fitch, N. J.; Hinds, E. A.; Sauer, B. E.; Tarbutt, M. R.
2017-12-01
Magneto-optical trapping and sub-Doppler cooling have been essential to most experiments with quantum degenerate gases, optical lattices, atomic fountains and many other applications. A broad set of new applications await ultracold molecules, and the extension of laser cooling to molecules has begun. A magneto-optical trap (MOT) has been demonstrated for a single molecular species, SrF, but the sub-Doppler temperatures required for many applications have not yet been reached. Here we demonstrate a MOT of a second species, CaF, and we show how to cool these molecules to 50 μK, well below the Doppler limit, using a three-dimensional optical molasses. These ultracold molecules could be loaded into optical tweezers to trap arbitrary arrays for quantum simulation, launched into a molecular fountain for testing fundamental physics, and used to study collisions and chemistry between atoms and molecules at ultracold temperatures.
Energy Technology Data Exchange (ETDEWEB)
Werner, Rolf [Wieland-Werke AG, Ulm (Germany). Technisches Marketing Haustechnik
2010-07-01
The active cooling of offices generally is accepted ever more. Among other things this is due to the fact that the climatic change results in a hotter summer on a long-term basis also in Germany. Also the use of computers, printing and copying machines increases the thermal load of the rooms considerably. The architecturally affected facade design with large glass areas also has an impact. The thermal comfort maintains the efficiency in offices. Thus, the efficient space cooling has become standard.
Murphy, Mark Allen
2010-01-01
The largest potential for decreasing green house gas emissions, and therewith mitigating the effects of global climate change, comes from improving energy efficiency. Through the integration of heating and cooling systems into building elements, such as the thermo-active ceiling, improvements in energy efficiency can be achieved. Utilizing thermal mass to buffer temperature variations and to level out peak loads reduces the instantaneous power demands and enables traditional cooling e...
Murphy, Mark Allen
2010-01-01
- The largest potential for decreasing green house gas emissions, and therewith mitigating the effects of global climate change, comes from improving energy efficiency. Through the integration of heating and cooling systems into building elements, such as the thermo-active ceiling, improvements in energy efficiency can be achieved. Utilizing thermal mass to buffer temperature variations and to level out peak loads reduces the instantaneous power demands and enables traditional cool...
Energy Technology Data Exchange (ETDEWEB)
Hernandez R, Alejandro; Garcia I, Rafael; Mazur C, Zdislaw [Instituto de Investigaciones Electricas, Cuernavaca, Morelos (Mexico)
2004-07-01
The analysis begins with the generation of a computational geometric model of the gas turbine nozzle using reverse engineering techniques. For the obtaining of the original geometry of the blade, a measurement machine by coordinates and computerized numerical control was used. Next, the computational model is converted into a three-dimensional mesh. In advance, a study of boundary conditions was made of the nozzle material as well as of the turbine operating conditions during non-operating cycles, start-ups and shut-downs. On the other hand, with the boundary conditions imposed to the model, the distributions of the temperature and pressures on the aerofoil profile of the nozzle blade were calculated. These results had to be manipulated to be exported to a finite element software (ANSYS); at this point, another nozzle model was elaborated to be able to import the temperature distribution. With the temperatures correctly imported, the simulations for the calculation of the thermal stresses were made in the nozzle. [Spanish] El analisis inicia con la generacion de un modelo geometrico computacional de la tobera de la turbina de gas utilizando tecnicas de ingenieria inversa. Para la obtencion de la geometria original del alabe, se utilizo una maquina de medicion por coordenadas y control numerico computarizado. A continuacion, el modelo computacional es convertido en una malla tridimensional. Con antelacion, se realizo un estudio de las condiciones de frontera, tanto del material de la tobera como de las condiciones de operacion de la turbina, durante ciclos de paro, arranque y disparo. Por otra parte, con las condiciones de frontera impuestas al modelo, se calcularon las distribuciones de las temperaturas y presiones sobre el perfil aerodinamico de la paleta de la tobera. Estos resultados tuvieron que ser manipulados para ser exportados a un software de elemento finito (ANSYS); en este punto, se elaboro otro modelo de la tobera para poder importar la distribucion de
Neutronics investigation of advanced self-cooled liquid blanket systems in helical reactor
International Nuclear Information System (INIS)
Tanaka, T.; Sagara, A.; Muroga, T.; Youssef, M.Z.
2006-10-01
Neutronics performances of advanced self-cooled liquid blanket systems have been investigated in design activity of the helical-type reactor FFHR2. In the present study, a new three-dimensional (3-D) neutronics calculation system has been developed for the helical-type reactor to enhance quick feedback between neutronics evaluation and design modification. Using this new calculation system, advanced Flibe-cooled and Li-cooled liquid blanket systems proposed for FFHR2 have been evaluated to make clear design issues to enhance neutronics performance. Based on calculated results, modification of the blanket dimensions and configuration have been attempted to achieve the adequate tritium breeding ability and neutron shielding performance in the helical reactor. The total tritium breeding ratios (TBRs) obtained after modifying the blanket dimensions indicated that all the advanced blanket systems proposed for FFHR2 would achieve adequate tritium self-sufficiency by dimension adjustment and optimization of structures in the breeder layers. Issues in neutron shielding performance have been investigated quantitatively using 3-D geometry of the helical blanket system, support structures, poloidal coils etc. Shielding performance of the helical coils against direct neutrons from core plasma would achieve design target by further optimization of shielding materials. However, suppression of the neutron streaming and reflection through the divertor pumping areas in the original design is important issue to protect the poloidal coils and helical coils, respectively. Investigation of the neutron wall loading indicated that the peaking factor of the neutron wall load distribution would be moderated by the toroidal and helical effect of the plasma distribution in the helical reactor. (author)
Energy Technology Data Exchange (ETDEWEB)
Matsuura, Hideaki, E-mail: mat@nucl.kyushu-u.ac.jp [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 819-0395 (Japan); Nakaya, Hiroyuki; Nakao, Yasuyuki [Department of Applied Quantum Physics and Nuclear Engineering, Kyushu University, 744 Motooka, Fukuoka 819-0395 (Japan); Shimakawa, Satoshi; Goto, Minoru; Nakagawa, Shigeaki [Japan Atomic Energy Agency, 4002 Oarai, Ibaraki 311-1393 (Japan); Nishikawa, Masabumi [Graduate School of Engineering Science, Kyushu University, 6-10-1 Hakozaki, Fukuoka 812-8581 (Japan)
2013-10-15
Highlights: • The performance of a gas-cooled reactor as a tritium production system was studied. • A continuous tritium recovery using helium gas was considered. • Gas-cooled reactors with 3 GW output in all can produce ∼6 kg of tritium in a year • Performance of the system was examined for Li{sub 4}SiO{sub 4}, Li{sub 2}TiO{sub 3} and LiAlO{sub 2} compounds. -- Abstract: The performance of a high-temperature gas-cooled reactor as a tritium production with continuous tritium recovery system is examined. A gas turbine high-temperature reactor of 300-MWe (600 MW) nominal capacity (GTHTR300) is assumed as the calculation target, and using the continuous-energy Monte Carlo transport code MVP-BURN, burn-up simulations for the three-dimensional entire-core region of the GTHTR300 were performed. A Li loading pattern for the continuous tritium recovery system in the gas-cooled reactor is presented. It is shown that module gas-cooled reactors with a total thermal output power of 3 GW in all can produce ∼6 kg of tritium maximum in a year.
International Nuclear Information System (INIS)
Lee, W.L.; Chen Hua; Leung, Y.C.; Zhang, Y.
2012-01-01
Highlights: ► The combined use of dedicated ventilation and dry cooling (DCDV) system was investigated. ► Investigations were based actual equipment performance data and realistic building and system characteristics. ► DCDV system could save 54% of the annual energy use for air-conditioning. ► DCDV system could better achieve the desired space air conditions. ► DCDV system could decouple dehumidification and cooling. - Abstract: The combined use of dedicated outdoor air ventilation (DV) and dry cooling (DC) air-conditioning system to decouple sensible and latent cooling for desirable space air conditions, better indoor air quality, and energy efficiency is proposed for hot and humid climates like Hong Kong. In this study, the performance and energy saving potential of DCDV system in comparison to conventional systems (constant air volume (CAV) system with and without reheat) for air conditioning of a typical office building in Hong Kong are evaluated. Through hour-by-hour simulations, using actual equipment performance data and realistic building and system characteristics, the cooling load profile, resultant indoor air conditions, condensation at the DC coil, and energy consumptions are calculated and analyzed. The results indicate that with the use of DCDV system, the desirable indoor conditions could be achieved and the annual energy use could be reduced by 54% over CAV system with reheat. The condensate-free characteristic at the DC coil to reduce risk of catching disease could also be realized.
When Newton's cooling law doesn't hold
International Nuclear Information System (INIS)
Tarnow, E.
1994-01-01
What is the fastest way to cool something? If the object is macroscopic it is to lower the surrounding temperature as much as possible and let Newton's cooling law take effect. If we enter the microscopic world where quantum mechanics rules, this procedure may no longer be the best. This is shown in a simple example where we calculate the optimum cooling rate for an asymmetric two-state system
Savings in Cooling Energy with a Thermal Management System for LED Lighting in Office Buildings
Directory of Open Access Journals (Sweden)
Byung-Lip Ahn
2015-06-01
Full Text Available Light-emitting diode (LED lighting should be considered for lighting efficiency enhancement, however, waste heat from light-emitting diode (LED lighting increases the internal cooling load during the summer season. In order to solve this problem we propose a thermal management system for light-emitting diode (LED lighting with a heat exchanger module integrated with the building’s heating, ventilation, and air conditioning (HVAC system to move the lighting’s waste heat outdoors. An experiment was carried out to investigate the thermal effects in a test chamber and the heat exchange rate between the heat sink and the duct air. The heat generated by the light-emitting diode (LED lighting was calculated as 78.1% of light-emitting diode (LED input power and the heat exchange rate of the lighting heat exchange module was estimated to be between 86.5% and 98.1% according to the light-emitting diode (LED input power and the flow rate of air passing the heat sink. As a result, the average light-emitting diode (LED lighting heat contribution rate for internal heat gain was determined as 0.05; this value was used to calculate the heating and cooling energy demand of the office building through an energy simulation program. In the simulation results, the cooling energy demand was reduced by 19.2% compared with the case of conventionally installed light-emitting diode (LED lighting.
RF, Thermal and Structural Analysis of the 201.25 MHz Muon Ionization Cooling Cavity
International Nuclear Information System (INIS)
Virostek, S.; Li, D.
2005-01-01
A finite element analysis has been carried out to characterize the RF, thermal and structural behavior of the prototype 201.25 MHz cavity for a muon ionization cooling channel. A single ANSYS model has been developed to perform all of the calculations in a multi-step process. The high-gradient closed-cell cavity is currently being fabricated for the MICE (international Muon Ionization Cooling Experiment) and MUCOOL experiments. The 1200 mm diameter cavity is constructed of 6 mm thick copper sheet and incorporates a rounded pillbox-like profile with an open beam iris terminated by 420 mm diameter, 0.38 mm thick curved beryllium foils. Tuning is accomplished through elastic deformation of the cavity, and cooling is provided by external water passages. Details of the analysis methodology will be presented including a description of the ANSYS macro that computes the heat loads from the RF solution and applies them directly to the thermal model. The process and results of a calculation to determine the resulting frequency shift due to thermal and structural distortion of the cavity will also be presented
International Nuclear Information System (INIS)
Winter, R.J.
1989-01-01
Plastic film packings were first used in CEGB natural draught cooling towers in 1985. Since then, cooling towers at seven power stations have been repacked using various commercial designs of plastic packing, with generally satisfactory results in economic terms. However, fouling of all the packings has occurred to some extent, ranging from very thin films on the surface of the sheets, which actually enhances performance, to heavy and voluminous formations which severely constrict the inter-sheet passages, causing performance loss and threatening the structural integrity of the whole fill. At CERL, methods have been developed to relate the degree of fouling to the thermal performance loss. This information is enabling accurate calculations to be made of the economics of repacking. Samples of fouled packing from operation towers are tested using the Experimental Cooling Tower at the Central Electricity Research Laboratories at Leatherhead. A systematic investigation is also underway of the changes in pressure drop and mass transfer coefficients which take place as fouling develops, using progressively-fouled packing samples from a purpose-built Packing Fouling Facility located at one of the power stations. The performance data obtained is fed-back into models by which the effect of high fouling loadings on various packings is calculated, enabling packing economic life to be predicted
National Oceanic and Atmospheric Administration, Department of Commerce — Declination is calculated using the current International Geomagnetic Reference Field (IGRF) model. Declination is calculated using the current World Magnetic Model...
Liquid metal cooling of synchrotron optics
International Nuclear Information System (INIS)
Smither, R.K.
1993-01-01
The installation of insertion devices at existing synchrotron facilities around the world has stimulated the development of new ways to cool the optical elements in the associated x-ray beamlines. Argonne has been a leader in the development of liquid metal cooling for high heat load x-ray optics for the next generation of synchrotron facilities. The high thermal conductivity, high volume specific heat, low kinematic viscosity, and large working temperature range make liquid metals a very efficient heat transfer fluid. A wide range of liquid metals were considered in the initial phase of this work. The most promising liquid metal cooling fluid identified to date is liquid gallium, which appears to have all the desired properties and the fewest number of undesired features of the liquid metals examined. Besides the special features of liquid metals that make them good heat transfer fluids, the very low vapor pressure over a large working temperature range make liquid gallium an ideal cooling fluid for use in a high vacuum environment. A leak of the liquid gallium into the high vacuum and even into very high vacuum areas will not result in any detectable vapor pressure and may even improve the vacuum environment as the liquid gallium combines with any water vapor or oxygen present in the system. The practical use of a liquid metal for cooling silicon crystals and other high heat load applications depends on having a convenient and efficient delivery system. The requirements for a typical cooling system for a silicon crystal used in a monochromator are pumping speeds of 2 to 5 gpm (120 cc per sec to 600 cc per sec) at pressures up to 100 psi. No liquid metal pump with these capabilities was available commercially when this project was started, so it was necessary to develop a suitable pump in house
International Nuclear Information System (INIS)
Bethge, K.
1989-05-01
Theoretical and experimental investigations of crack growth under thermal and thermomechanical fatigue loading are presented. The experiments were performed with a ferritic reactor pressure vessel steel 20 MnMoNi 5 5 and an austenitic stainless steel X6 CrNi 18 11. A plate containing a semi-elliptical surface crack is heated up to a homogeneous temperature and cyclically cooled down by a jet of cold water. On the basis of linear elastic fracture mechanics stress-intensity factors are calculated with the weight function method. The prediction of crack growth under thermal fatigue loading using data from mechanical fatigue tests is compared with the experimental result. (orig.) [de
2007-01-01
At the beginning of July, cool-down is starting in the second LHC sector, sector 4-5. The cool down of sector 4-5 may occasionally generate mist at Point 4, like that produced last January (photo) during the cool-down of sector 7-8.Things are getting colder in the LHC. Sector 7-8 has been kept at 1.9 K for three weeks with excellent stability (see Bulletin No. 16-17 of 16 April 2007). The electrical tests in this sector have got opt to a successful start. At the beginning of July the cryogenic teams started to cool a second sector, sector 4-5. At Point 4 in Echenevex, where one of the LHC’s cryogenic plants is located, preparations for the first phase of the cool-down are underway. During this phase, the sector will first be cooled to 80 K (-193°C), the temperature of liquid nitrogen. As for the first sector, 1200 tonnes of liquid nitrogen will be used for the cool-down. In fact, the nitrogen circulates only at the surface in the ...
International Nuclear Information System (INIS)
Suzuki, Hiroyuki.
1997-01-01
A plurality of blowing ports with introduction units are disposed to a plurality of ducts in a dry well, and a cooling unit comprising a cooler, a blower and an isolating valve is disposed outside of the dry well. Cooling air and the atmosphere in the dry well are mixed to form a cooling gas and blown into the dry well to control the temperature. Since the cooling unit is disposed outside of the dry well, the maintenance of the cooling unit can be performed even during the plant operation. In addition, since dampers opened/closed depending on the temperature of the atmosphere are disposed to the introduction units for controlling the temperature of the cooling gas, the temperature of the atmosphere in the dry well can be set to a predetermined level rapidly. Since an axial flow blower is used as the blower of the cooling unit, it can be contained in a ventilation cylinder. Then, the atmosphere in the dry well flowing in the ventilation cylinder can be prevented from leaking to the outside. (N.H.)
Biofouling control of industrial seawater cooling towers
Albloushi, Mohammed
2017-11-01
The use of seawater in cooling towers for industrial applications has much merit in the Gulf Cooperation Council countries due to the scarcity and availability of fresh water. Seawater make-up in cooling towers is deemed the most feasible because of its unlimited supply in coastal areas. Such latent-heat removal with seawater in cooling towers is several folds more efficient than sensible heat extraction via heat exchangers. Operational challenges such as scaling, corrosion, and biofouling are a major challenge in conventional cooling towers, where the latter is also a major issue in seawater cooling towers. Biofouling can significantly hamper the efficiency of cooling towers. The most popular methods used in cooling treatment to control biofouling are disinfection by chlorination. However, the disadvantages of chlorination are formation of harmful disinfection byproducts in the presence of high organic loading and safety concerns in the storage of chlorine gas. In this study, the research focuses on biofouling control in seawater cooling towers by investigating two different approaches. The first strategy addresses the use of alternative oxidants (i.e. ozone micro-bubbles and chlorine dioxide) in treatment of cooling towers. The second strategy investigates removing nutrients in seawater using granular activated carbon filter column and ultrafiltration to prevent the growth of microorganisms. Laboratory bench-scale tests in terms of temperature, cycle of concentration, dosage, etc. indicated that, at lower oxidant dosages (total residual oxidant (TRO) equivalent = 0.1 mg/l Cl2), chlorine dioxide had a better disinfection effect than chlorine and ozone. The performance of oxidizing biocides at pilot scale, operating at assorted conditions, showed that for the disinfectants tested, ozone could remove 95 % bioactivity of total number of bacteria and algae followed by chlorine dioxide at 85%, while conventional chlorine dosing only gave 60% reduction in bioactivities
Optimal design of district heating and cooling pipe network of seawater-source heat pump
Energy Technology Data Exchange (ETDEWEB)
Li, Xiang-li; Duanmu, Lin; Shu, Hai-wen [School of Civil and Hydraulic Engineering, Dalian University of Technology, Dalian, Liaoning Province 116024 (China)
2010-01-15
The district heating and cooling (DHC) system of a seawater-source heat pump is large system engineering. The investments and the operational cost of DHC pipe network are higher than a tradition system. Traditional design methods only satisfy the needs of the technology but dissatisfy the needs of the economy, which not only waste a mass of money but also bring problems to the operation, the maintenance and the management. So we build a least-annualized-cost global optimal mathematic model that comprises all constrict conditions. Furthermore, this model considers the variety of heating load and cooling load, the operational adjustment in different periods of the year. Genetic algorithm (GA) is used to obtain the optimal combinations of discrete diameters. Some operators of GA are selected to reduce the calculation time and obtain good calculation accuracy. This optimal method is used to the design of the DHC network of Xinghai Bay commercial district which is a real engineering. The design optimization can avoid the matter of the hydraulic unbalance of the system, enhance the running efficiency and greatly reduce the annualized-cost comparing with the traditional design method. (author)
International Nuclear Information System (INIS)
Mak, H.
1995-01-01
Slides used in a presentation at The Power of Change Conference in Vancouver, BC in April 1995 about the changing needs for load forecasting were presented. Technological innovations and population increase were said to be the prime driving forces behind the changing needs in load forecasting. Structural changes, market place changes, electricity supply planning changes, and changes in planning objectives were other factors discussed. It was concluded that load forecasting was a form of information gathering, that provided important market intelligence
Preliminary design concept of HYPER cooling system using Pb-Bi coolant
Energy Technology Data Exchange (ETDEWEB)
Tak, Nam Il; Song, Tae Y.; Park, Won S.; Kim, Chang H
2001-09-01
The present study focuses on providing the basic concept of HYPER's cooling system based on simple and fundamental calculations. The system operating temperature was preliminarily determined as 340/510 .deg. C. The total system flow rate of HYPER is {approx} 40,000kg/sec and the flow velocity in the core is preliminarily designed to be {approx}1.5 m/sec. For hot conditions of HYPER core, the simple analytic calculation predicted that the maximum temperature of the cladding outer surface is 634 .deg. C, which is below the design limit, 650 .deg. C. However, the SLTHEN code modified for HYPER's subchannel analysis predicted that the maximum temperature of the cladding outer surface in the same conditions is higher than the design limit by 4.7 .deg. C. The comparison with the results of the analytic model and additional sensitivity calculations showed that the modified SLTHEN code can reasonably simulate the heat transfer between subchannels of the HYPER core and be used effectively for thermal hydraulic design of the HYPER core in conceptual design stage. A forced circulation is inevitable during a full power condition since natural circulation is not sufficient to cool the core with reasonable system pressure drop and reasonable system height. However, a natural circulation can be an excellent method for decay heat removal when the height difference between the core and the heat exchanger is above 10 m. In order to avoid high pressure loads on the vessel, loop configuration was chosen. The simplification of cooling system and high system efficiency were attained by removing independent target cooling system and intermediate heat transport system. A superheated rankle cycle was chosen since it is technically matured and its thermal efficiency is reasonably high.
ELECTRONIC CIRCUIT BOARDS NON-UNIFORM COOLING SYSTEM MODEL
Directory of Open Access Journals (Sweden)
D. V. Yevdulov
2016-01-01
Full Text Available Abstract. The paper considers a mathematical model of non-uniform cooling of electronic circuit boards. The block diagram of the system implementing this approach, the method of calculation of the electronic board temperature field, as well as the principle of its thermal performance optimizing are presented. In the considered scheme the main heat elimination from electronic board is produced by the radiator system, and additional cooling of the most temperature-sensitive components is produced by thermoelectric batteries. Are given the two-dimensional temperature fields of the electronic board during its uniform and non-uniform cooling, is carried out their comparison. As follows from the calculations results, when using a uniform overall cooling of electronic unit there is a waste of energy for the cooling 0f electronic board parts which temperature is within acceptable temperature range without the cooling system. This approach leads to the increase in the cooling capacity of used thermoelectric batteries in comparison with the desired values. This largely reduces the efficiency of heat elimination system. The use for electronic boards cooling of non-uniform local heat elimination removes this disadvantage. The obtained dependences show that in this case, the energy required to create a given temperature is smaller than when using a common uniform cooling. In this approach the temperature field of the electronic board is more uniform and the cooling is more efficient.
Cooling towers: a bibliography
International Nuclear Information System (INIS)
Whitson, M.O.
1981-02-01
This bibliography cites 300 selected references containing information on various aspects of large cooling tower technology, including design, construction, operation, performance, economics, and environmental effects. The towers considered include natural-draft and mechanical-draft types employing wet, dry, or combination wet-dry cooling. A few references deal with alternative cooling methods, principally ponds or spray canals. The citations were compiled for the DOE Energy Information Data Base (EDB) covering the period January to December 1980. The references are to reports from the Department of Energy and its contractors, reports from other government or private organizations, and journal articles, books, conference papers, and monographs from US originators